Name: Jason Wilkerson

Title: Senior Environmental Engineer

Company: E.ON US

Sign Date: 8/31/2010

Name: Mike Taylor

Title: President

Company: Catalyst Air Management

Sign Date: 8/31/2010

Permitted Facility Representative / Date Testing Company Representative / Date

KY 1357 Green River Boiler 5

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Saturday, February 12, 2011 Page 1 of 24
KY 1357 Green River Boiler 5

8/31/2010

Facility Information:

KY1357 Green River Boiler 5

811 Power Plant Drive

Central City KY 42330

Contact: Jason Wilkerson

Phone: 502-627-4043

Fax:

Email: Jason.Wilkerson@eon-us.com

Testing Company:

Catalyst Air Management

2505 Byington-Solway Rd

Knoxville TN 37931

Contact:Mike Taylor

Phone: 865-531-0075

Fax:

Email: mike.taylor@catalystair.com

Air Permit Number:

1357

Permitted Source ID/Name:

5 Kentucky Utilities Green River Generating Station

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Green River Boiler 5 is a wall-fired, utility boiler that combusts bituminous coal. The unit is equipped with an 

electrostatic precipitator (ESP) for particulate matter (PM) control.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 2117700001 FRS #: 110008360969

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

GR Boiler 5 146 0 0 146 817.2 208.8 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

GR Boiler 5 2,3,7,8-TCDD Method 23 3 480 0

GR Boiler 5 1,2,3,7,8-PeCDD Method 23 3 480 0

GR Boiler 5 1,2,3,4,7,8-HxCDD Method 23 3 480 0

GR Boiler 5 1,2,3,6,7,8-HxCDD Method 23 3 480 0

GR Boiler 5 1,2,3,7,8,9-HxCDD Method 23 3 480 0

GR Boiler 5 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

NA 0

Saturday, February 12, 2011 Page 2 of 24
KY 1357 Green River Boiler 5

8/31/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

GR Boiler 5 OCDD Method 23 3 480 0

GR Boiler 5 2,3,7,8-TCDF Method 23 3 480 0

GR Boiler 5 1,2,3,7,8-PeCDF Method 23 3 480 0

GR Boiler 5 2,3,4,7,8-PeCDF Method 23 3 480 0

GR Boiler 5 1,2,3,4,7,8-HxCDF Method 23 3 480 0

GR Boiler 5 1,2,3,6,7,8-HxCDF Method 23 3 480 0

GR Boiler 5 2,3,4,6,7,8-HxCDF Method 23 3 480 0

GR Boiler 5 1,2,3,7,8,9-HxCDF Method 23 3 480 0

GR Boiler 5 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

GR Boiler 5 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

GR Boiler 5 OCDF Method 23 3 480 0

GR Boiler 5 Total Dioxins Method 23 3 480 0

GR Boiler 5 Total Furans Method 23 3 480 0

GR Boiler 5 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

GR Boiler 5 3,4,4',5-TCB (PCB81) Method 23 3 480 0

GR Boiler 5 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

GR Boiler 5 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

GR Boiler 5 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

GR Boiler 5 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

GR Boiler 5 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

GR Boiler 5 Method 23 3 480 0

GR Boiler 5 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

GR Boiler 5 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

GR Boiler 5 Method 23 3 480 0

GR Boiler 5 O2 Method 3A O2 12 120 0

GR Boiler 5 Co2 Method 3A CO2 12 120 0

Saturday, February 12, 2011 Page 3 of 24
KY 1357 Green River Boiler 5

8/31/2010

Sampling / Stack Data Results Summary

Location GR Boiler 5 - Method 23

Average

Run Number M23-1 M23-2 M23-3

Test Date 4/20/2010 4/21/2010 4/22/2010

Run Start Time 9:27:00 AM 9:11:00 

AM

8:49:00 AM

Run Finish Time 5:59:00 PM 5:24:00 PM 5:04:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 317.660 300.069 301.713 306.481

Moisture Content of Stack Gas, % 7.44 7.28 6.95 7.223

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.15 10.49 10.39 10.343

Oxygen, % 8.52 8.02 8.19 8.243

Average Stack Gas Temperature, °F 355.23 352.98 348.38 352.197

Dry Volumetric Flow Rate, dry scfm 325,072.0 319,254.1 320,635.9 321,654.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 553,727.9 541,381.0 538,730.2 544,613.033

Percent Isokinetic of Sampling Rate, % 98.4 94.6 94.8 95.933

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location GR Boiler 5 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 12, 2011 Page 4 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location GR Boiler 5 - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 12, 2011 Page 5 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A CO2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location GR Boiler 5 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 12, 2011 Page 6 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location GR Boiler 5 - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 12, 2011 Page 7 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A O2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 12, 2011 Page 8 of 24
KY 1357 Green River Boiler 5

8/31/2010

Emissions Summary

Location: GR Boiler 5 - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000052 0.0000000047 0.0000000046 0.000

lb/mmBtuO2 5.96E-13 5.48E-13 5.41E-13 0.000

ng/dscm 5.78E-04 5.53E-04 5.38E-04 0.001

ng/dscm@7%O2 6.49E-04 5.97E-04 5.88E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000073 0.0000000041 0.0000000044 0.000

lb/mmBtuO2 8.36E-13 4.78E-13 5.17E-13 0.000

ng/dscm 8.12E-04 4.83E-04 5.15E-04 0.001

ng/dscm@7%O2 9.12E-04 5.21E-04 5.63E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000019 0.0000000019 0.0000000018 0.000

lb/mmBtuO2 2.18E-13 2.22E-13 2.12E-13 0.000

ng/dscm 2.11E-04 2.24E-04 2.11E-04 0.000

ng/dscm@7%O2 2.37E-04 2.42E-04 2.31E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000018 0.0000000017 0.0000000017 0.000

lb/mmBtuO2 2.06E-13 1.98E-13 2.00E-13 0.000

ng/dscm 2.00E-04 2.00E-04 1.99E-04 0.000

ng/dscm@7%O2 2.25E-04 2.16E-04 2.18E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000052 0.0000000035 0.0000000037 0.000

lb/mmBtuO2 5.96E-13 4.08E-13 4.35E-13 0.000

ng/dscm 5.78E-04 4.12E-04 4.33E-04 0.000

ng/dscm@7%O2 6.49E-04 4.45E-04 4.74E-04 0.001

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000017 0.0000000017 0.0000000016 0.000

lb/mmBtuO2 1.95E-13 1.98E-13 1.88E-13 0.000

ng/dscm 1.89E-04 2.00E-04 1.87E-04 0.000

ng/dscm@7%O2 2.12E-04 2.16E-04 2.05E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Saturday, February 12, 2011 Page 9 of 24
KY 1357 Green River Boiler 5

8/31/2010

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000036 0.0000000029 0.000000003 0.000

lb/mmBtuO2 4.13E-13 3.38E-13 3.53E-13 0.000

ng/dscm 4.00E-04 3.41E-04 3.51E-04 0.000

ng/dscm@7%O2 4.49E-04 3.68E-04 3.84E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000016 0.0000000016 0.0000000016 0.000

lb/mmBtuO2 1.83E-13 1.87E-13 1.88E-13 0.000

ng/dscm 1.78E-04 1.88E-04 1.87E-04 0.000

ng/dscm@7%O2 2.00E-04 2.03E-04 2.05E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000019 0.0000000019 0.0000000018 0.000

lb/mmBtuO2 2.18E-13 2.22E-13 2.12E-13 0.000

ng/dscm 2.11E-04 2.24E-04 2.11E-04 0.000

ng/dscm@7%O2 2.37E-04 2.42E-04 2.31E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000016 0.0000000018 0.0000000016 0.000

lb/mmBtuO2 1.83E-13 2.10E-13 1.88E-13 0.000

ng/dscm 1.78E-04 2.12E-04 1.87E-04 0.000

ng/dscm@7%O2 2.00E-04 2.29E-04 2.05E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.000000004 0.0000000056 0.0000000044 0.000

lb/mmBtuO2 4.58E-13 6.53E-13 5.17E-13 0.000

ng/dscm 4.45E-04 6.59E-04 5.15E-04 0.001

ng/dscm@7%O2 5.00E-04 7.11E-04 5.63E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000051 0.0000000037 0.0000000079 0.000

lb/mmBtuO2 5.84E-13 4.31E-13 9.28E-13 0.000

ng/dscm 5.67E-04 4.36E-04 9.25E-04 0.001

ng/dscm@7%O2 6.37E-04 4.71E-04 1.01E-03 0.001

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.000000055 0.000000058 0.000000062 0.000

lb/mmBtuO2 6.30E-12 6.76E-12 7.29E-12 0.000

ng/dscm 6.12E-03 6.83E-03 7.26E-03 0.007

ng/dscm@7%O2 6.87E-03 7.37E-03 7.94E-03 0.007

Saturday, February 12, 2011 Page 10 of 24
KY 1357 Green River Boiler 5

8/31/2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.00000034 0.00000046 0.0000004 0.000

lb/mmBtuO2 3.90E-11 5.36E-11 4.70E-11 0.000

ng/dscm 3.78E-02 5.41E-02 4.68E-02 0.046

ng/dscm@7%O2 4.24E-02 5.84E-02 5.12E-02 0.051

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.00000002 0.000000021 0.000000025 0.000

lb/mmBtuO2 2.29E-12 2.45E-12 2.94E-12 0.000

ng/dscm 2.22E-03 2.47E-03 2.93E-03 0.003

ng/dscm@7%O2 2.49E-03 2.67E-03 3.20E-03 0.003

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.000000023 0.000000031 0.000000033 0.000

lb/mmBtuO2 2.64E-12 3.61E-12 3.88E-12 0.000

ng/dscm 2.56E-03 3.65E-03 3.86E-03 0.003

ng/dscm@7%O2 2.87E-03 3.94E-03 4.22E-03 0.004

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.00000083 0.0000011 0.00000086 0.000

lb/mmBtuO2 9.51E-11 1.28E-10 1.01E-10 0.000

ng/dscm 9.23E-02 1.29E-01 1.01E-01 0.107

ng/dscm@7%O2 1.04E-01 1.39E-01 1.10E-01 0.118

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000087 0.0000000053 0.000000013 0.000

lb/mmBtuO2 9.97E-13 6.18E-13 1.53E-12 0.000

ng/dscm 9.67E-04 6.24E-04 1.52E-03 0.001

ng/dscm@7%O2 1.09E-03 6.73E-04 1.66E-03 0.001

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000041 0.0000000033 0.0000000036 0.000

lb/mmBtuO2 4.70E-13 3.85E-13 4.23E-13 0.000

ng/dscm 4.56E-04 3.88E-04 4.21E-04 0.000

ng/dscm@7%O2 5.12E-04 4.19E-04 4.60E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000055 0.0000000088 0.0000000075 0.000

lb/mmBtuO2 6.30E-13 1.03E-12 8.81E-13 0.000

Saturday, February 12, 2011 Page 11 of 24
KY 1357 Green River Boiler 5

8/31/2010

ng/dscm 6.12E-04 1.04E-03 8.78E-04 0.001

ng/dscm@7%O2 6.87E-04 1.12E-03 9.60E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000023 0.0000000027 0.0000000018 0.000

lb/mmBtuO2 2.64E-13 3.15E-13 2.12E-13 0.000

ng/dscm 2.56E-04 3.18E-04 2.11E-04 0.000

ng/dscm@7%O2 2.87E-04 3.43E-04 2.31E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000134 0.000000034 0.000000025 0.000

lb/mmBtuO2 1.54E-12 3.96E-12 2.94E-12 0.000

ng/dscm 1.49E-03 4.00E-03 2.93E-03 0.003

ng/dscm@7%O2 1.67E-03 4.32E-03 3.20E-03 0.003

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000034 0.0000000051 0.0000000077 0.000

lb/mmBtuO2 3.90E-13 5.95E-13 9.05E-13 0.000

ng/dscm 3.78E-04 6.00E-04 9.01E-04 0.001

ng/dscm@7%O2 4.24E-04 6.48E-04 9.85E-04 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000059 0.0000000032 0.000000012 0.000

lb/mmBtuO2 6.76E-13 3.73E-13 1.41E-12 0.000

ng/dscm 6.56E-04 3.77E-04 1.40E-03 0.001

ng/dscm@7%O2 7.37E-04 4.07E-04 1.53E-03 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.00000013 0.00000061 0.0000004 0.000

lb/mmBtuO2 1.49E-11 7.11E-11 4.70E-11 0.000

ng/dscm 1.45E-02 7.18E-02 4.68E-02 0.044

ng/dscm@7%O2 1.63E-02 7.75E-02 5.12E-02 0.048

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000076 0.000000012 0.0000000046 0.000

lb/mmBtuO2 8.71E-13 1.40E-12 5.41E-13 0.000

ng/dscm 8.45E-04 1.41E-03 5.38E-04 0.001

ng/dscm@7%O2 9.49E-04 1.52E-03 5.88E-04 0.001

Compound: OCDD

Average

RunNumber M23-1 M23-2 M23-3

Saturday, February 12, 2011 Page 12 of 24
KY 1357 Green River Boiler 5

8/31/2010

Process Run Data

Mass_mg 0.0000000141 0.0000000157 0.0000000141 0.000

lb/mmBtuO2 1.62E-12 1.83E-12 1.66E-12 0.000

ng/dscm 1.57E-03 1.85E-03 1.65E-03 0.002

ng/dscm@7%O2 1.76E-03 2.00E-03 1.80E-03 0.002

Compound: OCDF

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000055 0.0000000035 0.000000005 0.000

lb/mmBtuO2 6.30E-13 4.08E-13 5.88E-13 0.000

ng/dscm 6.12E-04 4.12E-04 5.85E-04 0.001

ng/dscm@7%O2 6.87E-04 4.45E-04 6.40E-04 0.001

Compound: Total Dioxins

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000263 0.0000000299 0.000000026 0.000

lb/mmBtuO2 3.01E-12 3.49E-12 3.06E-12 0.000

ng/dscm 2.92E-03 3.52E-03 3.04E-03 0.003

ng/dscm@7%O2 3.28E-03 3.80E-03 3.32E-03 0.003

Compound: Total Furans

Average

RunNumber M23-1 M23-2 M23-3

Mass_mg 0.0000000524 0.0000000695 0.0000000602 0.000

lb/mmBtuO2 6.00E-12 8.10E-12 7.07E-12 0.000

ng/dscm 5.83E-03 8.18E-03 7.05E-03 0.007

ng/dscm@7%O2 6.55E-03 8.83E-03 7.71E-03 0.008

Saturday, February 12, 2011 Page 13 of 24
KY 1357 Green River Boiler 5

8/31/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 1051.3 Green River Boiler 

5, Method 23, Run 

1, 4/20/2010, 

9:27AM-5:59PM

2 Heat Input Million Btus/million BTU using O2 1032.7 Green River Boiler 

5, Method 23, Run 

2, 4/21/2010, 

9:11AM-5:24PM

3 Heat Input Million Btus/million BTU using O2 1000.4 Green River Boiler 

5, Method 23, Run 

3, 4/22/2010, 

8:49AM-5:04PM

1 Steam Rate 738.1 1000 lb/hr Green River Boiler 

5, Method 23, Run 

1, 4/20/2010, 

9:27AM-5:59PM

2 Steam Rate 738.5 1000 lb/hr Green River Boiler 

5, Method 23, Run 

2, 4/21/2010, 

9:11AM-5:24PM

3 Steam Rate 731 1000 lb/hr Green River Boiler 

5, Method 23, Run 

3, 4/22/2010, 

8:49AM-5:04PM

1 Fuel Input Rate 79831 lbs/hr Green River Boiler 

5, Method 23, Run 

1, 4/20/2010, 

9:27AM-5:59PM

2 Fuel Input Rate 87363 lbs/hr Green River Boiler 

5, Method 23, Run 

2, 4/21/2010, 

9:11AM-5:24PM

3 Fuel Input Rate 83841 lbs/hr Green River Boiler 

5, Method 23, Run 

3, 4/22/2010, 

8:49AM-5:04PM

1 Unit Load 102.7 MW Green River Boiler 

5, Method 23, Run 

1, 4/20/2010, 

9:27AM-5:59PM

2 Unit Load 102.5 MW Green River Boiler 

5, Method 23, Run 

2, 4/21/2010, 

9:11AM-5:24PM

Saturday, February 12, 2011 Page 14 of 24
KY 1357 Green River Boiler 5

8/31/2010

APCD Run Data

Process Lab Run Data

3 Unit Load 102 MW Green River Boiler 

5, Method 23, Run 

3, 4/22/2010, 

8:49AM-5:04PM

Run Name Value UOM Comments

Target

Value

1 ELECTROSTATIC PRECIPITATOR 232 KV

2 ELECTROSTATIC PRECIPITATOR 207 KV

3 ELECTROSTATIC PRECIPITATOR 228.9 KV

Run Name Value UOM Comments

1 Fuel Higher Heating Value (Dry Basis) 13220 Btu/lb

2 Fuel Higher Heating Value (Dry Basis) 13264 Btu/lb

3 Fuel Higher Heating Value (Dry Basis) 13277 Btu/lb

1 Fuel Moisture 3.03 %

2 Fuel Moisture 3.08 %

3 Fuel Moisture 3.12 %

1 Fuel Ash (Dry Basis) 9.42 %

2 Fuel Ash (Dry Basis) 9.27 %

3 Fuel Ash (Dry Basis) 9.09 %

1 Fuel Sulfur (Dry Basis) 2.83 %

2 Fuel Sulfur (Dry Basis) 2.83 %

3 Fuel Sulfur (Dry Basis) 2.91 %

1 Fuel Chlorine (Dry Basis) 3158 ppm

2 Fuel Chlorine (Dry Basis) 3242 ppm

3 Fuel Chlorine (Dry Basis) 3124 ppm

Saturday, February 12, 2011 Page 15 of 24
KY 1357 Green River Boiler 5

8/31/2010

Sampling / Stack Data Results Detail

Location GR Boiler 5 - Method 23

Average

Run Number M23-1 M23-2 M23-3

Test Date 4/20/2010 4/21/2010 4/22/2010

Run Start Time 9:27:00 AM 9:11:00 AM 8:49:00 AM

Run Finish Time 5:59:00 PM 5:24:00 PM 5:04:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.21 0.21 0.21 0.210

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.01 1.01 1.01 1.010

Barometric Pressure, inches of Mercury 29.2 29.2 29.2 29.200

Average Orifice Meter Differential, inches H2O 1.38 1.33 1.30 1.337

Dry Gas Meter Volume Sampled, cubic feet 334.195 315.274 314.009 321.159

Average Dry Gas Meter Temperature, °F 89.44 88.65 83.43 87.173

Dry Gas Meter Volume Sampled, dscf 317.660 300.069 301.713 306.481

Total Moisture Liquid collected, g 542.8 500.3 478.7 507.267

Volume of Water Vapor, standard cubic feet 25.55 23.55 22.53 23.877

Moisture Content of Stack Gas, % 7.44 7.28 6.95 7.223

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9256 0.9272 0.9305 0.928

Carbon Dioxide, % 10.15 10.49 10.39 10.343

Oxygen, % 8.52 8.02 8.19 8.243

Carbon Monoxide & Nitrogen, % 81.33 81.49 81.42 81.413

Fuel Factor 1.22 1.23 1.22

Dry Molecular Weight, lb/lb-Mole 29.96 30.00 29.99 29.983

Wet Molecular weight, lb/lb-Mole 29.07 29.13 29.16 29.120

Flue Gas Static Pressure, inches of H2O 1.4 1.4 1.4 1.400

Absolute Flue Gas Pressure, inches of Mercury 29.30 29.30 29.30 29.300

Average Stack Gas Temperature, °F 355.23 352.98 348.38 352.197

Average Velocity Head, inches of H2O 1.2767027265

3575

1.226144390

85621

1.222396070

05909

1.242

Average Stack Gas Velocity, feet/second 79.38 77.61 77.23 78.073

Stack Cross-Sectional Area, square feet 116.261 116.261 116.261 116.261

Dry Volumetric Flow Rate, dry scfm 325,072.0 319,254.1 320,635.9 321,654.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 553,727.9 541,381.0 538,730.2 544,613.033

Percent Isokinetic of Sampling Rate, % 98.4 94.6 94.8 95.933

Percent Excess Air, % 65.8 59.4 61.6 62.267

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 146 146 146

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, February 12, 2011 Page 16 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 17 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 18 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 19 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A CO2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 20 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 21 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 22 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 23 of 24
KY 1357 Green River Boiler 5

8/31/2010

Location GR Boiler 5 - Method 3A O2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 12, 2011 Page 24 of 24