From: Stevens, William
To: Kordzi, Joe Subject: RE: Updated Sargent & Lundy retrofit countrols - Cost Models
Date: Thursday, December 19, 2013 1:20:53 PM

Joe – In the SDA paper at http://www.epa.gov/airmarkets/progsregs/epaipm/docs/v513/attachment5_3.pdf

BM = BMR+BMF+BMW+BMB Good catch! BMW does not have a formula in the SDA paper and should not be included in the sum. It looks like a typo carryover from the Wet FGD sheet, where BMW does have a formula. None of the other papers have this typo. It makes sense that SDA does not have a base materials cost for a waste handling system like Wet FGD does.

Also in the SDA paper, in the VMOP=M*R*10 formula ... Converting R $/kWh to $/MWh requires multiplying by 1000, but we’re only applying M%/100 of that to each MWh, so the net multiplier is 10. So that formula is correct.

Please let me know of any more errata you find. I’ll plan on publishing an online errata sheet in a
month or so.
Thanks –
Bill

From: Kordzi, Joe Sent: Wednesday, December 18, 2013 6:34 PM To: Stevens, William Subject: FW: Updated Sargent & Lundy retrofit countrols - Cost Models

One more: The formla for BM is BMR + BMF + BMW = BMB. However, there is no formula provided
for BMW.

From: Kordzi, Joe Sent: Wednesday, December 18, 2013 4:16 PM To: Stevens, William Subject: RE: Updated Sargent & Lundy retrofit countrols - Cost Models

Hi Bill,

Another question: The VOMP variable is listed as having units of $/MWh. It’s formula is listed as
M*R*10. M is a percentage and R is $/kWh. So if I multiply $/KWh by 10, I don’t see how I end up with $/MWh. Can you explain? Thanks.

From: Stevens, William Sent: Tuesday, December 17, 2013 1:00 PM To: Kordzi, Joe Subject: RE: Updated Sargent & Lundy retrofit countrols - Cost Models

Joe –Yes, but the addition of a check-box to include the cost of Aux Power in the VOM cost was just a convenience for those who might be doing manual desktop calcs. IPM actually uses the %Aux Power value as a derate on the unit output, with the loss being optimally made up by other units according to their relative long term economics.
Bill S

From: Kordzi, Joe Sent: Tuesday, December 17, 2013 10:28 AM To: Stevens, William Subject: RE: Updated Sargent & Lundy retrofit countrols - Cost Models

Hi Bill,

For the new SDA cost model, page 7, it looks like there is now a check box that enables the user to include or not include auxiliary power (M) in the VOM calculation. Is this correct – if you check the box, then M gets included as VOMP?

It looks like the previous version (enclosed) just included an advisory that M should be used for model input.

From: Stevens, William Sent: Monday, December 16, 2013 6:46 AM To: Kordzi, Joe Subject: Updated Sargent & Lundy retrofit countrols - Cost Models

Joe – I was out of the office Friday. Sorry to have missed your call.

Here’s the link to our new IPMv5.13 documentation. http://www.epa.gov/airmarkets/progsregs/epa-ipm/BaseCasev513.html

Retrofit controls are covered in Chapter 5. Updated versions of the Sargent & Lundy cost models are listed as Attachments 5-1 thru 5-7. Note that IPM does not always include all of the features that S&L includes. One example: ACI as modeled in IPM uses only brominated carbon, whereas S&L allows user to select from three types of
sorbent.

Call anytime with questions/comments.
Bill

William Stevens Senior Advisor - Power Technologies Office of Atmospheric Programs
Clean Air Markets Division U.S. Environmental Protection Agency stevens.william@epa.gov
202-343-9642