13339 Hagers Ferry Road

Huntersville, NC 28078-7929

McGuire Nuclear Complex - MG03A2

Phone: 980-875-5245 Fax: 980-875-4349

Order Summary Report

Analytical Laboratory

Order Number: J12080483

Project Name: Somerville Waste Water

Lab Contact: Jason C Perkins

Date: 9/26/2012

Customer Address: 253 Plant Allen Road

Customer Name(s): BillK-RonL--RobnJ-DonS

Belmont, NC 28012

Phone: 980-875-5348

Report Authorized By:

(Signature)

Program Comments:

Please contact the Program Manager (Jason C Perkins) with any questions regarding this report.

Data Flags & Calculations:

Any analytical tests or individual analytes within a test flagged with a Qualifier indicate a deviation from the method quality 

system or quality control requirement. The qualifier description is found at the end of the Certificate of Analysis (sample results) 

under the qualifiers heading. All results are reported on a dry weight basis unless otherwise noted. Subcontracted data 

included on the Duke Certificate of Analysis is to be used as information only. Certified vendor results can be found in the 

subcontracted lab final report. Duke Energy Analytical Laboratory subcontracts analyses to other vendor laboratories that have 

been qualified by Duke Energy to perform these analyses except where noted.

Data Package:

This data package includes analytical results that are applicable only to the samples described in this narrative. An estimation of 

the uncertainty of measurement for the results in the report is available upon request. This report shall not be reproduced, except 

in full, without the written consent of the Analytical Laboratory. Please contact the Analytical laboratory with any questions. The 

order of individual sections within this report is as follows:

Job Summary Report, Sample Identification, Technical Validation of Data Package, Analytical Laboratory Certificate of Analysis, 

Analytical Laboratory QC Reports, Sub-contracted Laboratory Results, Customer Specific Data Sheets, Reports & 

Documentation, Customer Database Entries, Test Case Narratives, Chain of Custody (COC)

Certification:

The Analytical Laboratory holds the following State Certifications : North Carolina (DENR) Certificate #248, South Carolina 

(DHEC) Laboratory ID # 99005. Contact the Analytical Laboratory for definitive information about the certification status of 

specific methods. 

Page 1 of 39
Sample ID's & Descriptions:

Sample ID Plant/Station

Collection 

Date and Time Collected By Sample Description

2012018800 ALLEN 29-Aug-12 7:50 AM BILL HASKINS FGD Purge Eff 

2012018801 ALLEN 29-Aug-12 8:00 AM Jeremy D. EQ Tank Eff 

2012018802 ALLEN 29-Aug-12 8:05 AM Jeremy D. BioReactor 1 Inf 

2012018803 ALLEN 29-Aug-12 2:30 PM Jeremy D. BioReactor 1 Inf BLANK 

2012018804 ALLEN 29-Aug-12 8:03 AM BILL HASKINS BioReactor 2 Inf 

2012018805 ALLEN 29-Aug-12 2:34 PM Jeremy D. BioReactor 2 Inf BLANK 

2012018806 ALLEN 29-Aug-12 8:12 AM Jeremy D. BioReactor 2 Eff 

2012018807 ALLEN 29-Aug-12 2:32 PM Jeremy D. BioReactor 2 Eff BLANK 

2012018808 ALLEN 29-Aug-12 8:19 AM BILL HASKINS Filter Blk 

9 Total Samples

Page 2 of 39
COC and .pdf report are in agreement with sample totals 

and analyses (compliance programs and procedures).

All Results are less than the laboratory reporting limits.

All laboratory QA/QC requirements are acceptable.

Yes No

Technical Validation Review

Checklist:

Yes No

Yes No

Report Sections Included:

Job Summary Report Sub-contracted Laboratory Results

Sample Identification Customer Specific Data Sheets, Reports, & Documentation

Technical Validation of Data Package Customer Database Entries

Analytical Laboratory Certificate of Analysis

Analytical Laboratory QC Report

Chain of Custody

Reviewed By: DataBase Administrator Date: 9/26/2012

Electronic Data Deliverable (EDD) Sent Separately

Page 3 of 39
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J12080483

2012018800

Collection Date: 29-Aug-12 7:50 AM

Site: FGD Purge Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

ALKALINITY - (Analysis Performed by Prism Labs)

Vendor Parameter Complete Vendor Method V_PRISM

INORGANIC IONS BY IC

Bromide 530 mg/L 50 500 EPA 300.0 9/5/2012 12:28:00 AM JAHERMA

Chloride 2300 mg/L 50 500 EPA 300.0 9/5/2012 12:28:00 AM JAHERMA

Sulfate 1400 mg/L 50 500 EPA 300.0 9/5/2012 12:28:00 AM JAHERMA

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) 34.2 ug/L 2.5 50 EPA 245.1 9/13/2012 1:11:08 PM AGIBBS

DISSOLVED METALS BY ICP

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/12/2012 9:21:00 AM MHH7131

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 125 mg/L 0.5 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

Calcium (Ca) 1890 mg/L 0.1 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

Iron (Fe) 79.9 mg/L 0.1 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

Lithium (Li) 0.146 mg/L 0.05 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

Magnesium (Mg) 625 mg/L 0.05 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

Manganese (Mn) 3.07 mg/L 0.05 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

Potassium (K) 35.3 mg/L 1 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

Sodium (Na) 29.3 mg/L 0.5 10 EPA 200.7 9/21/2012 11:44:00 AM DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 3960 ug/L 10 10 EPA 200.8 9/12/2012 3:29:00 PM KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) 161 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

Cadmium (Cd) < 10 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

Chromium (Cr) 173 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

Copper (Cu) 126 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

Nickel (Ni) 211 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

Selenium (Se) 4330 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

Silver (Ag) < 10 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

Zinc (Zn) 260 ug/L 10 10 EPA 200.8 9/12/2012 1:53:00 PM KRICHAR

SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC)

Vendor Parameter Complete Vendor Method V_AS&C

TOTAL DISSOLVED SOLIDS

TDS 13000 mg/L 200 1 SM2540C 9/6/2012 2:40:00 PM TJA7067

TOTAL SUSPENDED SOLIDS

TSS 2300 mg/L 250 1 SM2540D 9/7/2012 11:05:00 AM TJA7067

Page 4 of 39
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J12080483

2012018800

Collection Date: 29-Aug-12 7:50 AM

Site: FGD Purge Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

2012018801

Collection Date: 29-Aug-12 8:00 AM

Site: EQ Tank Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) 27.6 ug/L 2.5 50 EPA 245.1 9/13/2012 1:18:15 PM AGIBBS

DISSOLVED METALS BY ICP

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/12/2012 9:24:00 AM MHH7131

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 137 mg/L 0.5 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

Calcium (Ca) 1720 mg/L 0.1 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

Iron (Fe) 51.5 mg/L 0.1 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

Lithium (Li) 0.112 mg/L 0.05 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

Magnesium (Mg) 589 mg/L 0.05 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

Manganese (Mn) 1.94 mg/L 0.05 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

Potassium (K) 30.1 mg/L 1 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

Sodium (Na) 45.4 mg/L 0.5 10 EPA 200.7 9/21/2012 11:48:00 AM DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 2860 ug/L 10 10 EPA 200.8 9/12/2012 3:32:00 PM KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) 93.4 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

Cadmium (Cd) < 10 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

Chromium (Cr) 118 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

Copper (Cu) 84.6 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

Nickel (Ni) 140 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

Selenium (Se) 2950 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

Silver (Ag) < 10 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

Zinc (Zn) 169 ug/L 10 10 EPA 200.8 9/12/2012 1:56:00 PM KRICHAR

2012018802

Collection Date: 29-Aug-12 8:05 AM

Site: BioReactor 1 Inf 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

ALKALINITY - (Analysis Performed by Prism Labs)

Vendor Parameter Complete Vendor Method V_PRISM

Page 5 of 39
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J12080483

2012018802

Collection Date: 29-Aug-12 8:05 AM

Site: BioReactor 1 Inf 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

DISSOLVED METALS BY ICP

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/12/2012 9:27:00 AM MHH7131

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 150 mg/L 0.5 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

Calcium (Ca) 1490 mg/L 0.1 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

Iron (Fe) < 0.1 mg/L 0.1 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

Lithium (Li) 0.062 mg/L 0.05 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

Magnesium (Mg) 517 mg/L 0.05 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

Potassium (K) 16.1 mg/L 1 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

Sodium (Na) 73.4 mg/L 0.5 10 EPA 200.7 9/21/2012 11:52:00 AM DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 2040 ug/L 10 10 EPA 200.8 9/12/2012 3:35:00 PM KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

Cadmium (Cd) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

Chromium (Cr) 28.8 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

Copper (Cu) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

Nickel (Ni) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

Selenium (Se) 2160 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

Silver (Ag) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

Zinc (Zn) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:00:00 PM KRICHAR

SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC)

Vendor Parameter Complete Vendor Method V_AS&C

2012018803

Collection Date: 29-Aug-12 2:30 PM

Site: BioReactor 1 Inf BLANK 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

Page 6 of 39
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J12080483

2012018803

Collection Date: 29-Aug-12 2:30 PM

Site: BioReactor 1 Inf BLANK 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

2012018804

Collection Date: 29-Aug-12 8:03 AM

Site: BioReactor 2 Inf 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

ALKALINITY - (Analysis Performed by Prism Labs)

Vendor Parameter Complete Vendor Method V_PRISM

MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

DISSOLVED METALS BY ICP

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/12/2012 9:30:00 AM MHH7131

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 157 mg/L 0.5 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

Calcium (Ca) 1460 mg/L 0.1 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

Iron (Fe) 0.392 mg/L 0.1 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

Lithium (Li) 0.057 mg/L 0.05 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

Magnesium (Mg) 540 mg/L 0.05 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

Potassium (K) 23.8 mg/L 1 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

Sodium (Na) 73.0 mg/L 0.5 10 EPA 200.7 9/21/2012 11:56:00 AM DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 263 ug/L 10 10 EPA 200.8 9/12/2012 3:39:00 PM KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Cadmium (Cd) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Chromium (Cr) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Copper (Cu) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Nickel (Ni) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Selenium (Se) 350 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Silver (Ag) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Zinc (Zn) < 10 ug/L 10 10 EPA 200.8 9/12/2012 2:03:00 PM KRICHAR

Page 7 of 39
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J12080483

2012018804

Collection Date: 29-Aug-12 8:03 AM

Site: BioReactor 2 Inf 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC)

Vendor Parameter Complete Vendor Method V_AS&C

2012018805

Collection Date: 29-Aug-12 2:34 PM

Site: BioReactor 2 Inf BLANK 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

2012018806

Collection Date: 29-Aug-12 8:12 AM

Site: BioReactor 2 Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

ALKALINITY - (Analysis Performed by Prism Labs)

Vendor Parameter Complete Vendor Method V_PRISM

INORGANIC IONS BY IC

Bromide 15 mg/L 5 50 EPA 300.0 9/5/2012 2:34:00 AM JAHERMA

Chloride 2000 mg/L 50 500 EPA 300.0 9/5/2012 2:34:00 AM JAHERMA

Sulfate 1900 mg/L 50 500 EPA 300.0 9/5/2012 2:34:00 AM JAHERMA

MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

DISSOLVED METALS BY ICP

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/12/2012 9:33:00 AM MHH7131

Page 8 of 39
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J12080483

2012018806

Collection Date: 29-Aug-12 8:12 AM

Site: BioReactor 2 Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 147 mg/L 0.5 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

Calcium (Ca) 1270 mg/L 0.1 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

Iron (Fe) 0.717 mg/L 0.1 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

Lithium (Li) 0.059 mg/L 0.05 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

Magnesium (Mg) 494 mg/L 0.05 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

Manganese (Mn) < 0.05 mg/L 0.05 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

Potassium (K) 26.1 mg/L 1 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

Sodium (Na) 68.0 mg/L 0.5 10 EPA 200.7 9/21/2012 12:00:00 PM DJSULL1

DISSOLVED METALS BY ICP-MS

Selenium (Se) 5.61 ug/L 5 5 EPA 200.8 9/12/2012 3:42:00 PM KRICHAR

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) < 5 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

Cadmium (Cd) < 5 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

Chromium (Cr) < 5 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

Copper (Cu) < 5 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

Nickel (Ni) 11.8 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

Selenium (Se) 11.5 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

Silver (Ag) < 5 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

Zinc (Zn) < 5 ug/L 5 5 EPA 200.8 9/12/2012 2:06:00 PM KRICHAR

SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC)

Vendor Parameter Complete Vendor Method V_AS&C

2012018807

Collection Date: 29-Aug-12 2:32 PM

Site: BioReactor 2 Eff BLANK 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC)

Vendor Parameter Complete Vendor Method V_BRAND

Page 9 of 39
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J12080483

2012018808

Collection Date: 29-Aug-12 8:19 AM

Site: Filter Blk 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

DF Analyst

DISSOLVED METALS BY ICP

Manganese (Mn) < 0.005 mg/L 0.005 1 EPA 200.7 9/12/2012 9:36:00 AM MHH7131

DISSOLVED METALS BY ICP-MS

Selenium (Se) < 1 ug/L 1 1 EPA 200.8 9/12/2012 2:56:00 PM KRICHAR

Page 10 of 39
 

September 10, 2012 

Jay Perkins 

Duke Energy Analytical Laboratory 

Mail Code MGO3A2 (Building 7405) 

13339 Hagers Ferry Rd. 

Huntersville, NC 28078 

(704) 875-5245 

Project: Allen Shay/MillerCreek (LIMS#J12080483) 

Dear Mr. Perkins, 

Attached is the report associated with four (4) aqueous samples submitted for selenium 

speciation analysis on August 30, 2012. The samples were received in a sealed cooler at -0.3°C 

on August 31, 2012. Selenium speciation analysis was performed via ion chromatography 

inductively coupled plasma collision reaction cell mass spectrometry (IC-ICP-CRC-MS). Any 

issues associated with the analysis are addressed in the following report. 

If you have any questions, please feel free to contact me at your convenience. 

 Sincerely, 

 

 Russell Gerads 

 Vice President 

 Applied Speciation and Consulting, LLC 

 

Page 11 of 39
Applied Speciation and Consulting, LLC 

Report prepared for: 

Jay Perkins 

Duke Energy Analytical Laboratory 

Mail Code MGO3A2 (Building 7405) 

13339 Hagers Ferry Rd. 

Huntersville, NC 28078 

Project: Allen Shay/MillerCreek (LIMS#J12080483) 

September 10, 2012 

1. Sample Reception 

Four (4) aqueous samples in 125mL HDPE bottles (provided by Applied Speciation and 

Consulting) were submitted for selenium speciation analysis on August 30, 2012. The 

samples were received on August 31, 2012 in a sealed container at -0.3°C. 

The samples were received in a laminar flow clean hood, void of trace metals contamination 

and ultra-violet radiation, and were designated discrete sample identifiers. An aliquot of 

each sample was filtered (0.45μm) and each filtrate was stored in a secure, monitored 

cryofreezer (maintained at a temperature of -80oC) until selenium speciation analysis could 

be performed via ion chromatography inductively coupled plasma collision reaction cell 

mass spectrometry (IC-ICP-CRC-MS). 

2. Sample Preparation 

All sample preparation is performed in laminar flow clean hoods known to be free from trace 

metals contamination. All applied water for dilutions and sample preservatives are 

monitored for contamination to account for any biases associated with the sample results. 

Selenium Speciation Analysis by IC-ICP-CRC-MS Prior to analysis, an aliquot of each 

sample was filtered with a syringe filter (0.45μm) and injected directly into a sealed 

autosampler vial. No further sample preparation was performed as any chemical alteration of 

a sample may shift the equilibrium of the system, resulting in changes in speciation ratios. 

3. Sample Analysis 

All sample analysis is preceded by a minimum of a five-point calibration curve spanning the 

entire concentration range of interest. Calibration curves are performed at the beginning of 

each analytical day. All calibration curves, associated with each species of interest, are 

Page 12 of 39
standardized by linear regression resulting in a response factor. All sample results are 

instrument blank corrected to account for any operational biases associated with the 

analytical platform. 

Prior to sample analysis, all calibration curves are verified using second source standards 

which are identified as initial calibration verification standards (ICV). 

Ongoing instrument performance is identified by the analysis of continuing calibration 

verification standards (CCV) and continuing calibration blanks (CCB) at a minimal interval 

of every ten analytical runs. 

Selenium Speciation Analysis by IC-ICP-CRC-MS Each sample for selenium speciation 

analysis was analyzed by ion chromatography inductively coupled plasma collision reaction 

cell mass spectrometry (IC-ICP-CRC-MS) on September 7, 2012. An aliquot of each sample 

is injected onto an anion exchange column and mobilized by a basic (pH > 7) gradient. The 

eluting selenium species are then introduced into a radio frequency (RF) plasma where 

energy-transfer processes cause desolvation, atomization, and ionization. The ions are 

extracted from the plasma through a differentially-pumped vacuum interface and travel 

through a pressurized chamber (CRC) containing a reaction gas which preferentially reacts 

with interfering ions of the same target mass to charge ratios (m/z). A solid-state detector 

detects ions transmitted through the mass analyzer and the resulting current is processed by a 

data handling system. 

Retention times for each eluting species are compared to known standards for species 

identification. 

4. Analytical Issues 

The overall analyses went well and no significant analytical issues were encountered. All 

other quality control parameters associated with the samples were within acceptance limits.

The estimated method detection limits (eMDLs) for selenite, selenate, and selenocyanate are 

generated from replicate analyses of the lowest standard in the calibration curve. Not all 

selenium species are present in preparation blanks; therefore, eMDL calculations based on 

preparation blanks are artificially biased low. 

The eMDL for methylseleninic acid and selenomethionine is calculated from the average 

eMDL of selenite, selenate, and selenocyanate. The calibration does not contain 

methylseleninic acid or selenomethionine due to impurities in these standards which would 

bias the results for other selenium species. 

Page 13 of 39
If you have any questions or concerns regarding this report, please feel free to contact me. 

Sincerely, 

Russell Gerads 

Vice President 

Applied Speciation and Consulting, LLC 

Page 14 of 39
Sample Results

Sample ID Se(IV) Se(VI) SeCN MeSe(IV) SeMe

Unknown Se 

Species (n)

FGD Purge Eff ND (<1.9) 4180 ND (<0.79) ND (<1.7) ND (<1.7) 0.0 (0)

BioReactor 1 Inf 0.90 2070 ND (<0.20) 0.74 ND (<0.42) 0.0 (0)

BioReactor 2 Inf 51.0 210 0.94 0.84 ND (<0.42) 0.52 (1)

BioReactor 2 Eff 1.23 ND (<0.58) ND (<0.20) ND (<0.42) ND (<0.42) 0.0 (0)

All results reflect the applied dilution and are reported in μg/L

ND = Not detected at the applied dilution

SeCN = Selenocyanate

MeSe(IV) = Methylseleninic acid

SeMe = Selenomethionine

Unknown Se Species = Total concentration of all unknown Se species observed by IC-ICP-MS

n = number of unknown Se species observed

Report Generated by: Russell Gerads

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Allen Shay/MillerCreek

Contact: Jay Perkins

Date: September 10, 2012

LIMS #J12080483

Page 15 of 39
Quality Control Summary - Preparation Blank Summary

Analyte (μg/L) PBW1 PBW2 PBW3 PBW4 Mean StdDev eMDL* eMDL 250x eMDL 1000x

Se(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.0019 0.47 1.9

Se(VI) 0.000 0.000 0.000 0.000 0.000 0.000 0.0023 0.58 2.3

SeCN 0.000 0.000 0.000 0.000 0.000 0.000 0.0008 0.20 0.79

MeSe(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.0017 0.42 1.7

SeMe 0.000 0.000 0.000 0.000 0.000 0.000 0.0017 0.42 1.7

eMDL = Estimated Method Detection Limit

*Please see narrative regarding eMDL calculations

Quality Control Summary - Certified Reference Materials

Analyte (μg/L) CRM True Value Result Recovery

Se(IV) LCS 9.57 9.59 100.2

Se(VI) LCS 9.48 9.19 96.9

SeCN LCS 8.92 8.70 97.6

MeSe(IV) LCS 6.47 6.18 95.5

SeMe LCS 9.32 8.82 94.6

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Allen Shay/MillerCreek

Contact: Jay Perkins

LIMS #J12080483

Date: September 10, 2012

Report Generated by: Russell Gerads

Page 16 of 39
Quality Control Summary - Matrix Duplicates

Analyte (μg/L) Sample ID Rep 1 Rep 2 Mean RPD

Se(IV) Batch QC ND (<0.47) ND (<0.47) NC NC

Se(VI) Batch QC 3.58 3.59 3.59 0.3

SeCN Batch QC 0.52 0.47 0.49 11.4

MeSe(IV) Batch QC ND (<0.42) ND (<0.42) NC NC

SeMe Batch QC ND (<0.42) ND (<0.42) NC NC

ND = Not detected at the applied dilution

NC = Value was not calculated due to one or more concentrations below the eMDL

Quality Control Summary - Matrix Spike/ Matrix Spike Duplicate

Analyte (μg/L) Sample ID Spike Conc MS Result Recovery Spike Conc MSD Result Recovery RPD

Se(IV) Batch QC 1390 1444 103.9 1390 1436 103.3 0.5

Se(VI) Batch QC 1261 1279 101.1 1261 1273 100.7 0.4

SeCN Batch QC 1144 1118 97.7 1144 1129 98.7 1.0

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Allen Shay/MillerCreek

Contact: Jay Perkins

LIMS #J12080483

Date: September 10, 2012

Report Generated by: Russell Gerads

Page 17 of 39
Page 18 of 39
September 14, 2012

Duke Energy

ATTN: Jay Perkins

Scientific Support-Laboratory

13339 Hagers Ferry Road

Huntersville NC 28078

jcperkins@duke-energy.com

labcustomer@duke-energy.com

RE: Project DUK-HV1201 Client Project: J12080483

Dear Mr. Perkins,

On August 31, 2012, Brooks Rand Labs (BRL) received three (3) wastewater samples and three

(3) corresponding field blanks. An aliquot was removed from each sample bottle and filtered into 

a separate container designed for dissolved mercury (Hg) analysis. The sample volume from 

the original container was logged-in for total Hg analysis. All samples were received, prepared, 

analyzed, and stored according to BRL SOPs and EPA methodology.

Data used for regulatory purposes has a 24 hour filtration holding time requirement. Nonregulatory purposed data has a 48 hour filtration holding time. The samples were received

within of the non-regulatory requirement holding time and were qualified. 

The results were blank-corrected as described in the calculations section of the applicable 

SOP(s) and may be evaluated using adjusted reporting limits to account for sample aliquot size. 

Please refer to the Sample Results page for sample-specific detection limits and other details. 

The initial analysis of method blank, -BLK2, produced an abnormal peak shape. This blank was 

reanalyzed as –BLK5 and produced a normal peak. Therefore, -BLK5 was reported in place of –

BLK2.

BRL, an accredited laboratory, certifies the reported results of all analyses for which BRL is 

NELAP accredited meet all NELAP requirements. For more details, see the Report Information

page of the report. Please feel free to contact us if you have any questions regarding this report.

Sincerely,

 

Lydia Greaves Mi Sun Um 

Project Manager Data Manager

lydia@brooksrand.com misun@brooksrand.com

Page 19 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Definition of Data Qualifiers

(Effective 9/23/09)

Laboratory Accreditation

BRL is accredited by the National Environmental Laboratory Accreditation Program (NELAP) through the State of Florida 

Department of Health, Bureau of Laboratories (E87982) and is certified to perform many environmental analyses. BRL is 

also certified by many other states to perform environmental analyses. For a current list of our accreditations /certifications, 

please visit our website at <http://www.brooksrand.com/default.asp?contentID=586>. Results reported relate only to the 

samples listed in the report.

Report Information

BLK

BRL

BS

CAL

CCV

CRM

D

DUP

ICV

MSD

ND

NR

PS

REC

RPD

RSD

SCV

SOP

method blank 

Brooks Rand Labs

laboratory fortified blank

calibration standard

continuing calibration verification

certified reference material

dissolved fraction

duplicate

initial calibration verification

matrix spike duplicate

non-detect

non-reportable

post preparation spike

percent recovery

relative percent difference

relative standard deviation

secondary calibration verification

standard operating procedure

MDL

MRL

MS

method detection limit

method reporting limit

matrix spike

SRM

T

COC

standard reference material

total recoverable fraction

chain of custody record 

Common Abbreviations

These qualifiers are based on those previously utilized by Brooks Rand Labs, those found in the EPA SOW ILM03.0, 

Exhibit B, Section III, pg. B-18, and the USEPA Contract Laboratory Program National Functional Guidelines for Inorganic 

Superfund Data Review; USEPA; January 2010. These supersede all previous qualifiers ever employed by BRL.

B Detected by the instrument, the result is > the MDL but ≤ the MRL. Result is reported and considered an estimate.

E An estimated value due to the presence of interferences. A full explanation is presented in the narrative.

H Holding time and/or preservation requirements not met. Result is estimated.

J Estimated value. A full explanation is presented in the narrative.

J-M Duplicate precision (RPD) for associated QC sample was not within acceptance criteria. Result is estimated.

J-N Spike recovery for associated QC sample was not within acceptance criteria. Result is estimated.

M Duplicate precision (RPD) was not within acceptance criteria. Result is estimated.

N Spike recovery was not within acceptance criteria. Result is estimated.

R Rejected, unusable value. A full explanation is presented in the narrative.

U Result is ≤ the MDL or client requested reporting limit (CRRL). Result reported as the MDL or CRRL.

X Result is not BLK-corrected and is within 10x the absolute value of the highest detectable BLK in the batch. 

Result is estimated.

Field Quality Control Samples

Please be notified that certain EPA methods require the collection of field quality control samples of an appropriate type 

and frequency; failure to do so is considered a deviation from some methods and for compliance purposes should only be 

done with the approval of regulatory authorities. Please see the specific EPA methods for details regarding required field 

quality control samples.

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 20 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Sample Information

Sample Lab ID Report Matrix Type Sampled Received

BioReactor 1 Inf 1235054-01 Influent Sample 08/29/2012 08/31/2012

BioReactor 1 Inf 1235054-02 Influent Sample 08/29/2012 08/31/2012

BioReactor 1 Inf Hg Blk 1235054-03 DIW Field Blank 08/29/2012 08/31/2012

BioReactor 1 Inf Hg Blk 1235054-04 DIW Field Blank 08/29/2012 08/31/2012

BioReactor 2 Inf 1235054-05 Influent Sample 08/29/2012 08/31/2012

BioReactor 2 Inf 1235054-06 Influent Sample 08/29/2012 08/31/2012

BioReactor 2 Inf Hg Blk 1235054-07 DIW Field Blank 08/29/2012 08/31/2012

BioReactor 2 Inf Hg Blk 1235054-08 DIW Field Blank 08/29/2012 08/31/2012

BioReactor 2 Eff 1235054-09 Effluent Sample 08/29/2012 08/31/2012

BioReactor 2 Eff 1235054-10 Effluent Sample 08/29/2012 08/31/2012

BioReactor 2 Eff Hg Blk 1235054-11 DIW Field Blank 08/29/2012 08/31/2012

BioReactor 2 Eff Hg Blk 1235054-12 DIW Field Blank 08/29/2012 08/31/2012

Batch Summary

Analyte Lab Matrix Method Prepared Analyzed Batch Sequence

Hg Water EPA 1631 09/10/2012 09/11/2012 B121645 1200699

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 21 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Sample Results

Sample Analyte Report Matrix Basis Result Qualifier MDL MRL Unit Batch Sequence

BioReactor 1 Inf

1235054-01 Hg Influent T 17800 50.5 135 ng/L B121645 1200699

1235054-02 Hg Influent D 17600 30.3 80.8 ng/L B121645 1200699

BioReactor 1 Inf Hg Blk

1235054-03 Hg DIW T 0.15 U 0.15 0.40 ng/L B121645 1200699

1235054-04 Hg DIW D 0.15 U 0.15 0.40 ng/L B121645 1200699

BioReactor 2 Eff

1235054-09 Hg Effluent T 24.6 0.76 2.02 ng/L B121645 1200699

1235054-10 Hg Effluent D 21.0 0.30 0.81 ng/L B121645 1200699

BioReactor 2 Eff Hg Blk

1235054-11 Hg DIW T 0.15 U 0.15 0.41 ng/L B121645 1200699

1235054-12 Hg DIW D 0.15 U 0.15 0.40 ng/L B121645 1200699

BioReactor 2 Inf

1235054-05 Hg Influent T 426 15.2 40.4 ng/L B121645 1200699

1235054-06 Hg Influent D 17.7 0.30 0.79 ng/L B121645 1200699

BioReactor 2 Inf Hg Blk

1235054-07 Hg DIW T 0.15 U 0.15 0.41 ng/L B121645 1200699

1235054-08 Hg DIW D 0.15 U 0.15 0.40 ng/L B121645 1200699

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 22 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Accuracy & Precision Summary

Batch: B121645

Analyte Native Spike Result Units REC & Limits RPD & Limits

Method: EPA 1631

Lab Matrix: Water

Sample

B121645-SRM1 Certified Reference Material (1237042, NIST 1641d 1000x dilution)

Hg 15.68 14.69 ng/L 94% 85-115

B121645-MS1 Matrix Spike (1235054-05)

Hg 426.5 2121 2715 ng/L 108% 71-125

B121645-MSD1 Matrix Spike Duplicate (1235054-05)

Hg 426.5 2121 2556 ng/L 100% 71-125 246%

B121645-MS2 Matrix Spike (1235054-09)

Hg 24.63 126.5 173.3 ng/L 118% 71-125

B121645-MSD2 Matrix Spike Duplicate (1235054-09)

Hg 24.63 118.1 140.6 ng/L 98% 71-125 2421%

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 23 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Method Blanks & Reporting Limits

Batch: B121645

Method: EPA 1631

Matrix: Water

Analyte: Hg

Sample Result Units

B121645-BLK1 0.06 ng/L

B121645-BLK3 0.11 ng/L

B121645-BLK4 0.20 ng/L

B121645-BLK5 0.05 ng/L

Average: 0.11 Standard Deviation: 0.07 MDL: 0.15

Limit: 0.50 Limit: 0.10 MRL: 0.41

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 24 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Instrument Calibration

Sequence: 1200699

Instrument: THG-05 Method: EPA 1631

Date: 09/11/2012

Total Mercury and Mercury Speciation by CVAFS

Analyte: Hg

Lab ID True Value Result Units REC & Limits

1200699-IBL1 4.03 pg of Hg

1200699-IBL2 6.20 pg of Hg

1200699-IBL3 5.33 pg of Hg

1200699-IBL4 5.25 pg of Hg

1200699-CAL1 25.00 29.65 pg of Hg 119%

1200699-CAL2 100.0 92.53 pg of Hg 93%

1200699-CAL3 500.0 475.4 pg of Hg 95%

1200699-CAL4 2500 2393 pg of Hg 96%

1200699-CAL5 10000 10210 pg of Hg 102%

1200699-ICV1 1568 1469 pg of Hg 94% 85-115

1200699-CCV1 500.0 600.2 pg of Hg 120% 77-123

1200699-CCB1 9.56 pg of Hg

1200699-CCV2 500.0 457.9 pg of Hg 92% 77-123

1200699-CCV3 500.0 559.7 pg of Hg 112% 77-123

1200699-CCV4 500.0 384.6 pg of Hg 77% 77-123

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 25 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Sample Containers

Lab ID: 1235054-01 Report Matrix: Influent

Sample: BioReactor 1 Inf Sample Type: Sample Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71666330

10

Bottle FLPE Hg-T 500 mL none n/a Cooler

Lab ID: 1235054-02 Report Matrix: Influent

Sample: BioReactor 1 Inf Sample Type: Sample Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71659890

20

Bottle FLPE Hg-T 250 mL none n/a Cooler

Comments: Split from THg Container

Lab ID: 1235054-03 Report Matrix: DIW

Sample: BioReactor 1 Inf Hg Blk Sample Type: Field Blank Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71666330

10

Bottle FLPE Hg-T 500 mL none n/a Cooler

Lab ID: 1235054-04 Report Matrix: DIW

Sample: BioReactor 1 Inf Hg Blk Sample Type: Field Blank Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71659890

20

Bottle FLPE Hg-T 250 mL none n/a Cooler

Comments: Split from THg Container

Lab ID: 1235054-05 Report Matrix: Influent

Sample: BioReactor 2 Inf Sample Type: Sample Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71666330

10

Bottle FLPE Hg-T 500 mL none n/a Cooler

Lab ID: 1235054-06 Report Matrix: Influent

Sample: BioReactor 2 Inf Sample Type: Sample Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71659890

20

Bottle FLPE Hg-T 250 mL none n/a Cooler

Comments: Split from THg Container

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 26 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Sample Containers

Lab ID: 1235054-07 Report Matrix: DIW

Sample: BioReactor 2 Inf Hg Blk Sample Type: Field Blank Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71666330

10

Bottle FLPE Hg-T 500 mL none n/a Cooler

Lab ID: 1235054-08 Report Matrix: DIW

Sample: BioReactor 2 Inf Hg Blk Sample Type: Field Blank Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71659890

20

Bottle FLPE Hg-T 250 mL none n/a Cooler

Comments: Split from THg Container

Lab ID: 1235054-09 Report Matrix: Effluent

Sample: BioReactor 2 Eff Sample Type: Sample Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71666330

10

Bottle FLPE Hg-T 500 mL none n/a Cooler

Lab ID: 1235054-10 Report Matrix: Effluent

Sample: BioReactor 2 Eff Sample Type: Sample Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71659890

20

Bottle FLPE Hg-T 250 mL none n/a Cooler

Comments: Split from THg Container

Lab ID: 1235054-11 Report Matrix: DIW

Sample: BioReactor 2 Eff Hg Blk Sample Type: Field Blank Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71666330

10

Bottle FLPE Hg-T 500 mL none n/a Cooler

Lab ID: 1235054-12 Report Matrix: DIW

Sample: BioReactor 2 Eff Hg Blk Sample Type: Field Blank Received: 08/31/2012

Collected: 08/29/2012

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71659890

20

Bottle FLPE Hg-T 250 mL none n/a Cooler

Comments: Split from THg Container

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 27 of 39
Project ID: DUK-HV1201

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Shipping Containers

Cooler

Tracking No: 5353 0519 3682 via FedEx

Temperature: -0.3 °C

Coolant Type: Ice

Description: Cooler

Damaged in transit? No

Returned to client? No

Custody seals present? No

Custody seals intact? No

COC present? Yes

Received: August 31, 2012 9:45

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Page 28 of 39
Page 29 of 39
This data package contains the analytical results for the project identified above and includes a Case Narrative, Sample 

Results and Chain of Custody. Unless otherwise noted, all samples were received in acceptable condition and processed 

according to the referenced methods. 

Data qualifiers are flagged individually on each sample. A key reference for the data qualifiers appears at the end of this case 

narrative.

NC Certification No. 402

SC Certification No. 99012

NC Drinking Water Cert No. 37735

Case Narrative

09/07/2012

Duke Energy Corporation (04)

Jay Perkins

13339 Hagers Ferry Road

Huntersville, NC 28078

Project: Allen Shay/Miller Creek

Project No.: J12080483

Lab Submittal Date: 08/30/2012

Prism Work Order: 2080758

VA Certification No. 1287

Please call if you have any questions relating to this analytical report.

Respectfully,

PRISM LABORATORIES, INC.

VP Laboratory Services Reviewed By

Data Qualifiers Key Reference:

HT Sample received and analyzed outside of the hold time.

MDL Method Detection Limit

BRL Below Reporting Limit

RPD Relative Percent Difference

*

Results reported to the reporting limit. All other results are reported to the MDL with values between MDL and 

reporting limit indicated with a J.

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 1 of 9

Page 30 of 39
Sample Receipt Summary

09/07/2012

Prism Work Order: 2080758

Client Sample ID Lab Sample ID Matrix Date Sampled Date Received

2012018800/FGD Purge Eff 2080758-01 Water 08/29/12 08/30/12

2012018802/BioReactor 1 Inf 2080758-02 Water 08/29/12 08/30/12

2012018804/BioReactor 2 Inf 2080758-03 Water 08/29/12 08/30/12

2012018806/BioReactor 2 Eff 2080758-04 Water 08/29/12 08/30/12

Samples received in good condition at 4.4 degrees C unless otherwise noted.

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 2 of 9

Page 31 of 39
Laboratory Report

09/07/2012

Parameter Result Batch

ID

Report

Limit

Analysis

Date/Time

Dilution Method

Factor

Units MDL Analyst

13339 Hagers Ferry Road Project No.: 

Duke Energy Corporation (04) Project: Allen Shay/Miller Creek

Huntersville, NC 28078

Attn: Jay Perkins

Sample Matrix: Water

Client Sample ID: 

Prism Sample ID: 2080758-01

Prism Work Order: 2080758

Time Collected: 08/29/12 07:50

Time Submitted: 08/30/12 12:05

2012018800/FGD Purge Eff

J12080483

General Chemistry Parameters

pH 7.0 HT pH Units 1 *SM4500-H B 8/30/12 13:30 JAB P2H0669

Total Alkalinity 49 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0693

Carbonate Alkalinity BRL mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0694

Bicarbonate Alkalinity 49 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0695

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 3 of 9

Page 32 of 39
Laboratory Report

09/07/2012

Parameter Result Batch

ID

Report

Limit

Analysis

Date/Time

Dilution Method

Factor

Units MDL Analyst

13339 Hagers Ferry Road Project No.: 

Duke Energy Corporation (04) Project: Allen Shay/Miller Creek

Huntersville, NC 28078

Attn: Jay Perkins

Sample Matrix: Water

Client Sample ID: 

Prism Sample ID: 2080758-02

Prism Work Order: 2080758

Time Collected: 08/29/12 08:05

Time Submitted: 08/30/12 12:05

2012018802/BioReactor 1 Inf

J12080483

General Chemistry Parameters

pH 7.1 HT pH Units 1 *SM4500-H B 8/30/12 13:30 JAB P2H0669

Total Alkalinity 42 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0693

Carbonate Alkalinity BRL mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0694

Bicarbonate Alkalinity 42 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0695

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 4 of 9

Page 33 of 39
Laboratory Report

09/07/2012

Parameter Result Batch

ID

Report

Limit

Analysis

Date/Time

Dilution Method

Factor

Units MDL Analyst

13339 Hagers Ferry Road Project No.: 

Duke Energy Corporation (04) Project: Allen Shay/Miller Creek

Huntersville, NC 28078

Attn: Jay Perkins

Sample Matrix: Water

Client Sample ID: 

Prism Sample ID: 2080758-03

Prism Work Order: 2080758

Time Collected: 08/29/12 08:03

Time Submitted: 08/30/12 12:05

2012018804/BioReactor 2 Inf

J12080483

General Chemistry Parameters

pH 6.8 HT pH Units 1 *SM4500-H B 8/30/12 13:30 JAB P2H0669

Total Alkalinity 160 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0693

Carbonate Alkalinity BRL mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0694

Bicarbonate Alkalinity 160 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0695

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 5 of 9

Page 34 of 39
Laboratory Report

09/07/2012

Parameter Result Batch

ID

Report

Limit

Analysis

Date/Time

Dilution Method

Factor

Units MDL Analyst

13339 Hagers Ferry Road Project No.: 

Duke Energy Corporation (04) Project: Allen Shay/Miller Creek

Huntersville, NC 28078

Attn: Jay Perkins

Sample Matrix: Water

Client Sample ID: 

Prism Sample ID: 2080758-04

Prism Work Order: 2080758

Time Collected: 08/29/12 08:12

Time Submitted: 08/30/12 12:05

2012018806/BioReactor 2 Eff

J12080483

General Chemistry Parameters

pH 7.2 HT pH Units 1 *SM4500-H B 8/30/12 13:30 JAB P2H0669

Total Alkalinity 220 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0693

Carbonate Alkalinity BRL mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0694

Bicarbonate Alkalinity 220 mg/L 5.0 0.66 1 *SM2320 B 8/31/12 11:00 JAB P2H0695

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 6 of 9

Page 35 of 39
9/7/12

Level II QC Report

13339 Hagers Ferry Road Project No: J12080483

Duke Energy Corporation (04) Project: Allen Shay/Miller Creek

Huntersville, NC 28078

Attn: Jay Perkins

Prism Work Order: 2080758

Time Submitted: 8/30/2012 12:05:00PM

Result Limit

Reporting

Units Level

Spike

Result

Source

%REC

%REC

Limits RPD

RPD

 Analyte Limit Notes 

General Chemistry Parameters - Quality Control

Batch P2H0669 - NO PREP

LCS (P2H0669-BS1) Prepared & Analyzed: 08/30/12 

pH 6.82 pH Units 6.860 99 99-101

Batch P2H0693 - NO PREP

Blank (P2H0693-BLK1) Prepared & Analyzed: 08/31/12 

Total Alkalinity BRL 5.0 mg/L

LCS (P2H0693-BS1) Prepared & Analyzed: 08/31/12 

Total Alkalinity 249 5.0 mg/L 250.0 100 90-110

LCS Dup (P2H0693-BSD1) Prepared & Analyzed: 08/31/12 

Total Alkalinity 247 5.0 mg/L 250.0 99 90-110 0.8 200

Duplicate (P2H0693-DUP2) Source: 2080758-04 Prepared & Analyzed: 08/31/12 

Total Alkalinity 212 5.0 mg/L 219 3 20

Batch P2H0694 - NO PREP

Blank (P2H0694-BLK1) Prepared & Analyzed: 08/31/12 

Carbonate Alkalinity BRL 5.0 mg/L

LCS (P2H0694-BS1) Prepared & Analyzed: 08/31/12 

Carbonate Alkalinity 249 5.0 mg/L 90-110

LCS Dup (P2H0694-BSD1) Prepared & Analyzed: 08/31/12 

Carbonate Alkalinity 247 5.0 mg/L 90-110 0.8 200

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 7 of 9

Page 36 of 39
9/7/12

Level II QC Report

13339 Hagers Ferry Road Project No: J12080483

Duke Energy Corporation (04) Project: Allen Shay/Miller Creek

Huntersville, NC 28078

Attn: Jay Perkins

Prism Work Order: 2080758

Time Submitted: 8/30/2012 12:05:00PM

Result Limit

Reporting

Units Level

Spike

Result

Source

%REC

%REC

Limits RPD

RPD

 Analyte Limit Notes 

General Chemistry Parameters - Quality Control

Batch P2H0694 - NO PREP

Duplicate (P2H0694-DUP2) Source: 2080758-04 Prepared & Analyzed: 08/31/12 

Carbonate Alkalinity BRL 5.0 mg/L BRL 20

Batch P2H0695 - NO PREP

Blank (P2H0695-BLK1) Prepared & Analyzed: 08/31/12 

Bicarbonate Alkalinity BRL 5.0 mg/L

LCS (P2H0695-BS1) Prepared & Analyzed: 08/31/12 

Bicarbonate Alkalinity 249 5.0 mg/L 250.0 100 90-110

LCS Dup (P2H0695-BSD1) Prepared & Analyzed: 08/31/12 

Bicarbonate Alkalinity 247 5.0 mg/L 250.0 99 90-110 0.8 200

Duplicate (P2H0695-DUP2) Source: 2080758-04 Prepared & Analyzed: 08/31/12 

Bicarbonate Alkalinity 212 5.0 mg/L 219 3 20

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543

Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 Page 8 of 9

Page 37 of 39
Page 9 of 9

Page 38 of 39
Page 39 of 39