### Federal Register / Vol. 50, No. 198 / Friday, October 11, 1985 / Notices

they will do the same for fiscal year 1986 funds. If this happens, the fund raising deadline will most likely be July 15, 1987. However, if these funds are only available for one year, then the fund raising deadline will most likely be July 15, 1986. After the Congress enacts the fiscal year 1986 appropriation for the Endowment Grant program, the Secretary will announce in the Federal Register the deadline by which an institution selected to receive'an endowment grant in the fiscal year 1986 competition must raise matching funds and certify the amount of such funds raised by the institution. (34 CFR 628.41(b)) 

### Available funds: Fiscal year 1986 funds have not yet been appropriated for the Endowment Grant Program. However, applications for new grants under the Endowment Grant Program are being requested at this time so they can be evaluated and the grants process completed as early as possible in order that selected institutions can have as long a fund-raising period as possible. The Administration's fiscal year 1986 budget request included $141,208,000 for the Institutional Air Programs. Of that amount $23,208,000 was requested for FY 1986 grants under the Endowment Grant Program.
Grants awarded under the Endowment Grant Program in FY 1986 will range from $50,000 to $500,000. Applicants are urged to request grants in an amount that they will realistically beable to match by the end of the fundraising period. The Secretary anticipates awarding approximately 60 grants in FY 1986. 

### These estimates do not bind the U.S. Department of Education to a specific number of grants, or to the amount of any grant, unless that amount is otherwise specified by statute or regulations.
With funds transferred from the Special Needs Program to the Endowment Grant Program, the Secretary awards endowment grants so that the amounts required under 34 CFR 626.31(a) and (b) of the Special Needs Program regulations to be awarded to junior or community colleges and to institutions with special needs that have historically served substantial numbers of black students will be so awarded. (20 U.S.C. 1085a, 1069c). The Administration's fiscal year 1986 budget request recommended that $45,741,000 of the monies appropriated for the Institutional Aid Programs be available for awards to historically black colleges and universities. This reservation may
limit funds available to institutions that 

### are not historically black institutions under this competition. Application Forms: Application forms and program information packages are expected to be ready for mailing by October 18, 1985. Interested parties may obtain a copy of the application form by writing to the Institutional Aid Programs, U.S. Department of Education, L'Enfant Plaza Station, Post Office Box 23868 , Washington, DC 20024. The program information packages will include the Endowment Grant Program regulations. An application must be prepared and
submitted in accordance with the regulations, instructions, and forms included in the program information. package. However, the program information package is only intended to aid applicants in applying for assistance under this program. Nothing in the program information package is intended to impose any paperwork, application content, reporting , or grantee performance requirements beyond those specifically imposed under the statute and regulations governing this program. The Secretary strongly urges that applicants not submit information that is not required. (Approved by the Office of Management and Budget under Control Number 1840-0531). 

### Applicable regulations: Regulations applicable to the Endowment Grant Program include: (1) The regulations in 34 CFR 824.1 through 824.3, 624.6, 624.10, 624.20, 624.22 and 624.40. (2) The regulations in 34 CFR 625.2,
626.2 and 627.2. (3) The regulations in 34 CFR Part 628 published in the Federal Register on July 12, 1984 (49 FR 28520-28536) and amended on September 21, 1984 (49 FR 37325). - (3) The regulations in 34 CFR Part 628 published in the Federal Register on July 12,1984 (49 FR 28520-28536) and amended on September 21, 1984 (49 FR 37325). (4) The Education Department General Administrative Regulations (EDGAR) in 34 CFR 74.62(h); 34 CFR 74.80 through 74.85; 34 CFR 75.100 through 75.102 and 75.217; and 34 CFR
Part 78. Further Information: For furtherinformation, contact Ms. Anne PriceCollins, Chief, Challenge Grant and Endowment Branch, Division of Institutional Development, Department of Education, Room 3045, Regional Office Building 3, 400 Maryland Avenue, SW., Washington, DC 20202. Telephone: (202) 245-9091.

(20 U.S.C.1064-1089c) 

### 41553

(Catalog of Federal Domestic Assistance No. 84.0316-Endowment) Dated: October 8, 1985. C. Ronald Kimberling, . Acting Assistant Secretary for Postsecondary Education.

[FR Doc. 24175 Filed 10-10-85; 8:45 am]

BILLING CODE 4000

- 01-M



### DEPARTMENT OF ENERGY

Nevada Operations Office, Dose Assessment Advisory Group; Open Meeting

Correction
In FR Doc. 85-24002, appearing on page 40992 in the issue of Tuesday, October 8,1985, make the following correction: In the first column, the third and fourth lines of meeting description should have read:
Date and Time: Thursday, October 24, 1985, 8:30 a.m.-5:00 p.m.; Friday, October 25, 1985, 8:30 a.m.-4:00 p.m.

BILLING CODE 1505-01-M



### Office of Conservation and Renewable Energy

[Case No. F-0141

Energy Conservation Program for Consumer Products; Decision and Order Granting Waiver From Furnaces Test Procedures to Magic Chef CO., Inc.

AGENCY : Department of Energy.

ACTION : Decision and Order.

SUMMARY: Notice is given of the Decision and Order [Case No. F-014] granting Magic Chef Company, Inc. a
waiver for its Ultra series warm air furnaces from the existing DOE furnace test procedures.

FOR FURTHER INFORMATION CONTACT: Michael J. McCabe, U.S. Department of Energy, Office of Conservation andRenewable Energy, Mail Station CE112, Forrestal Building, 1000 Independence Avenue SW., Washington, DC 20585, (202) 252-9127; Eugene Margolis, Esq., U.S. Department of Energy, Office of General Counsel, Mail Station GC-12, Forrestal Building, 1000 Independence Avenue SW., Washington, DC 20585, (202) 252-9513.

SUPPLEMENTAL INFORMATION: In accordance with 10 CFR 430.27(g), notice is hereby given of the issuance of the
Decision and order set out below. In the Decision and Order, Magic Chef

HeinOnline -- 50 Fed. Reg. 41553 1985

### 41554 Federal Register / Vol. 50, No. 198 / Friday, October 11, 1985 / Notices



### Copmpany, Inc. has been granted a waiver for its Ultra series warm air furnaces, permitting the company to use an alternate test method.

Issued in Washington, DC, September 27,
1985
Derma R. Fitzpatrick,
Acting Assistant Secretary, Conservation and Renewable Energy.

Decision and Order of the Department of Energy, Office of Conservation and Renewable Energy

(Case No. F

### -014)

In the Matter of: Magic Chef Company, Inc.
The Energy Conservation Program for Consumer Products was established pursuant to the Energy Policy and Conservation Act, Pub. L. 94-163.89 Stat. 917, as amended by the National Energy Conservation Policy Act, Pub. L. 95-619, 92 Stat. 32G3, which requires the Department of Energy (DOE) to prescribe standardized test procedures to measure the energy consumption of certain consumer products, including furnaces. The intent of the test procedures is to provide a comparable measure of energy consumption that will assist consumers in making purchase decisions. These test procedures appear at 10 CFR Part 430, Subpart B. The Department of Energy amended the prescribed test procedure regulations, by adding § 430.27, to allow the Department to waive temporarily test procedures for a particular basic model when a petitioner
shows that the basic model contains one or more design characteristics which prevent testing of the basic model according to the prescribed test procedures or when the prescribed test procedures may evaluate the basic model in a manner so unrepresentative of its true energy consumption characteristics

as to provide materially inadequate comparative data. 45 FR 64108 (September 28, 1980). Pursuant to § 430

. 27(g), the Department shall publish in the Federal Register notice of each waiver granted, and any limiting
conditions of each waiver. Magic Chef Company. Inc. (Magic Chef),
filed a "Petition for Waiver" in accordance with § 430.27 of 10 CFR Part 430. DOE published in the Federal Register the Magic Chef petition and solicited comments, data. and information respecting the petition. 50 FR
24288 (June 10

, 1985 ). No comments were
received. DOE consulted with the Federal Trade Commission on July 29,1985, concerning the Magic Chef petition.

Assertions and Determinations Magic Chefs petition seeks a waiver from the DOE test provisions that require a 1.5 minute time delay between the ignition of the burner and the starting of the circulating air blower. Instead, Magic Chef requests the allowance to test using a 20 second blower time delay when testing its Ultra series gas furnaces. Magic Chef states that the 20 second delay is indicative of how the Ultra series models actually operate and because such a delay results in an improvement in efficiency of approximatley 0.5%, the waiver should be granted. The blower controls incorpc need on the Magic Chef furnace are designed to impose a 20 second blower delay in every instance of start-up, Since the current provisions do not specifically address this type of control and since no comments objecting to the petition were reccivad, DOE zbices that a waiver sha:):i be granted to nl ow the 20 second blower time delay when testing the Magic Chef Ultra series furnancea. Accordingly, with regard to testing the Ultra series furnaces only, today's decision and order exempts Magic Chef from the existing provisions regarding blower controls and allows testing with the 20 second delay.
It is therefore ordered that: (1) The "Petition for Waiver" filed by Magic Chef Company, Inc. (F-014), is hereby granted as set forth in paragraph (2) below, subject to the provisions of paragraphs (3) and (4). (2) Notwithstanding any contrary provisions of Appendix N of 10 CFR, Part 430, Subpart B. Magic Chef Company, Inc. shall be permitted to test its Ultra series gas furnaces on the basis of the test procedure specified in 10 CFR, Part 430, with the modification set forth below: (i) Section 9.3.1 of ANSI/ASHRAE Standard 103-1982 is deleted and replaced with the following paragraph:
Gas- and Oil-Fueled Central Furnaces. After equilibrium conditions are achieved following the cool-down test and the required measurements performed, turn on the furnace and measure the flue gas temperature, using the thermecopule grid described above, at 0.5 and 2.5 minutes after the main burner(s)

comes on. After the burner start -up, delay the blower start-up by 1.5 minutes (t-), unless: (1) The furnace employs a single motor to drive the power burner and the indoor air circulation blower, in which case the burner and blower shall be started together, (2) the furnace is designed to operate using an unvarying delay time that is other than 1.5 minutes, in which case the fan control shall be permitted to start the blower; or (31 the delay time result in the activation of a temperature safety device which shuts off the burner, in which case the fan control shall be permitted to start the blower. In the latter

case, if the fan control is adjustable

, set it to start the blower at the highest temperature. If the fan control is permitted to start the blower, measure time delay, (t-), using a stop watch. Record the measured temperatures. During the heat-up test for oil-fueled furnaces, maintain the draft in the flue pipe with ±- 0.01 in. of water gauge of the manufacturer's recommended on-period draft. (ii) With the exception of the modification set forth in subparagraph (i) above, Magic Chef Company, Inc. shall comply in all respects with the test procedures specified in Appendix N of 10 CFR Part 430 , Subpart D. (3) The waiver shall remain in effect from
the date of issuance of this order until the Department of Energy prescribes final test procedures appropriate to the Ultra series warm air furnace controls manufactured by Magic Chef Company, Inc. (4) This waiver is based upon the presumed validity of statements, allegations, and documentary materials submitted by applicant. This waiver may be revoked or modified at any time upon a determination that the factual basis underlying the application is incorrect.
Issued in Washington, DC, September 27,

was. Deana R. Fitzpatrick, Acting Assistant Secretary Conservation and Renewable Energy.

[FR Doc. 85-24437 Filed 10-10-85; 8:45 am]

BILLING CODE 6450-e1-M

Economic Regulatory Administration

[ Docket No. r-RA-FC-85-016 ; OFP Case No. 67043--5280.20-221


### Order Granting the City of Santa Clara, CA, Proposed Peaking Facility, Exemption From the Prohibitions of the Powerplant and Industrial Fuel Use.

AGENCY: Economic Regulatory Administration, DOE.

ACTION : Order granting the city of Santa Clara, California proposed peaking facility, exemption from the prohibitions of the Powerplant and Industrial Fuel
Use Act of 1978.

SUMMARY: On May 28,1985, the city of ' Santa Clara, California (Santa Clara), filed a petition with the Economic Regulatory Administration (ERA) of the Department of Energy (DOE) for an order permanently exempting a proposed new powerplant from the provisions of the Powerplant and Industrial Fuel Use Act of 1978 ("FUA" or "the Act") (42 U.S.C. 8301 et seq.), which (1) prohibit the use of petroleum and natural gas as a primary energy source in new electric powerplants and (2) prohibit the construction of a new powerplant without the capability to use an alternate fuel as a primary energy source, The final rule containing the criteria and procedures for petitioning for exemption from the prohibitions of FUA was published in the Federal Register at 46 FR 59872 (December 7, 1931).

Santa Clara requested a permanent peakload exemption ender 10 CFR
503.41 for a simple-cycle combustion turbine installation consisting of one General Electric 29.4 MW gas turbine, generator auxiliaries and associated facilities. The proposed unit is to be installed in the northwest portion of the city of Santa Clara, California. The powerplant will be capable of burning natural gas and petroleum. Pursuant to section 212(g) of the Act and 10 CFR 503.41, ERA hereby issues this order granting to Santa Clara a

HeinOnline -- 50 Fed. Reg. 41554 1985