56FR51713

Federal Register / Vol. 56, No. 199 / Tuesday, October 15, 1991 / Notices

!Case No. F-0301

Energy Conservation Program for

Consumer Products; Decision and

Order Granting a Waiver From the

Furnace Test Procedures to Goodman

Manufacturing Corp.

AGENCY. Office of Conservation and

Renewable Energy, Department of

Energy.

ACTION: Decision and Order.

SUMMARY: Notice is given of the

Decision and Order (Case No. F-030)

granting a Waiver to Goodman

Manufacturing Corporation (Goodman)

from the existing Department of Energy

(DOE) test procedures for furnaces. The

Department is granting the company its

Petition for Waiver regarding blower

time delay in calculation of Annual Fuel

Utilization Efficiency (AFUE) for its PG

and PGX series rooftop furnaces.

FOR FURTHER INFORMATION CONTACT:

Cyrus H. Nasseri. U.S. Department of

Energy, Office of Conservation and

Renewable Energy, Mail Station CE43, Forrestal Building, 1000

Independence Avenue, SW.

Washington, DC 20585, (202) 586-9127.

Eugene Margolis, Esq., U.S. Department

of Energy, Office of General Counsel,

Mail Station GC-41, Forrestal

Building, 1000 Independence Avenue,

SW. Washington, DC 20585, (202) 586-

9507.

SUPPLEMENTARY INFORMATION: In

accordance with 10 CFR 430.27(g). notice

is hereby given of the issuance of the

Decision and Order as set out below. In

the Decision and Order, Goodman has

been granted a waiver for its PG and

PGX series rooftop furnaces, permitting

the company to use an alternate test

method in determining the Annual Fuel

Utilization Efficiency (AFUE).

Issued in Washington. DC. October 3,1991.

1. Michael Davis,

Assistant Secretary, Conservation and

Renewable Energy.

Decision and Order

In the matter of Goodman

Manufacturing Corporation (Case No. F030)

Background

The Energy Conservation Program for

Consumer Products (other than

automobiles) established pursuant to the

Energy Policy and Conservation Act

(EPCA), Public Law 94-163, 89 Stat. 917.

as amended by the National Energy

Conservation Policy Act (NECPA).

Public Law 95-619.92 Stat. 3266, the

National Appliance Energy

Conservation Act of 1987 (NAECA).

61713

Public Law 100-12, and the National

Appliance Energy Conservation

Amendments of 1988 (NAECA 1988).

Public Law 100-357, requires DOE to

prescribe standardized test procedures

to meaure the energy consumption of

certain consumer products, including

furnaces. The intent of the test

procedures is to provide a comparable

measure of energy consumption that will

assist consumers in making purchasing

decisions. These test procedures appear

at 10 CFR part 430, subpart B.

DOE amended the prescribed test

procedures by adding 10 CFR 430.27 to

create a waiver process. 45 FR 64108,

September 26, 1980. Thereafter, DOE

further amended its appliance test

procedure waiver process to allow the

Assistant Secretary for Conservation

and Renewable Energy (Assistant

Secretary) to grant an Interim Waiver

from test procedure requirements to

manufacturers that have petitioned DOE

for a waiver of such prescribed test

procedures. 51 FR 42823, November 26,

1986.

The waiver process allows the

Assistant Secretary to waive

temporarily test procedures for a

particular basic model when a petitioner

shows that the basic model contains one

or more design characteristics which

prevent testing according to the

prescribed test procedures or when the

prescribed test procedures may evaluate

the basic model in a manner so

unrepresentative of its true energy

consumption as to provide materially

inaccurate comparative data. Waivers

generally remain in effect until final test

procedure amendments become

effective, resolving the problem that is

the subject of the waiver.

The Interim Waiver provisions, added

by the 1986 amendment, allow the

Assistant Secretary to grant an Interim

Waiver when it is determined that the

applicant will experience economic

hardship if the Application for Interim

Waiver is denied, if it appears likely

that Petition for Waiver will be granted,

and/or the Assistant Secretary

determines that it would be desirable for

public policy reasons to grant immediate

relief pending a determination on the

Petition for Waiver. An Interim Waiver

remains in effect for a period of 180 days

or until DOE issues its determinaton on

the Petition for Waiver, whichever is

sooner, and may be extended for an

additional 180 days, if necessary.

Goodman filed a "Petition for Wavier"

dated January 16, 1991 , in accordance

with 1430.27 of 10 CFR part 430. DOE

published in the Federal Register on

May 3,1991 , Goodman's petition and

solicited comments, data and

CAS-RM-79-104 COMMENT 65
51714

56FR51713

Federal Register / Vol. 56, No. 199 / Tuesday, October 15, 1991 / Notices

information respecting the petition. 56

FR 20421. Goodman also filed an

"Application for Interim Waiver" under

§ 430.27(g) which DOE granted on April

26, 1991. 56. 20421, May 3, 1991.

No comments were received

concerning either the "Petition for

Waiver" or the "Interim Waiver." DOE

consulted with Federal Trade

Commission (FTC), concerning the

Goodman Petition. The FTC did not

have any objections to the issuance of

the Waiver to Goodman.

Assertions and Determinations

Goodman's Petition seeks a Waiver

from the DOE test provisions that

require a 1.5-minute time delay between

the ignition of the burner and the

starting of the circulating air blower.

Goodman requests the allowance to test

using a 30-second blower time delay

when testing its PG and PGX series

rooftop furnaces. Goodman states that

since the 30-second delay is indicative

of how these models actually operate

and since such a delay results in an

improvement in efficiency of

approximately 1.0 percent, the Waiver

should be granted.

Under specific circumstances, the

DOE test procedures contain exceptions

which allow testing with blower delay

times of less than the prescribed 1.5-

minute delay. Goodman indicates that it

is unable to take advantage of any of

these exceptions for its PG and PGX

series rooftop furnaces.

Since the blower controls

incorporated on the Goodman furnaces

are designed to impose a 30-second

blower delay in every instance of start

up. and since the current provisions do

not specifically address this type of

control, DOE agrees that a Waiver

should be granted to allow the 30-

second blower time delay when testing

the Goodman PG, PSX series rooftop

furnaces. Accordingly, with regard to

testing the PG and PGX series rooftop

furnaces, today's Decision and Order

exempts Goodman from the existing

provisions regarding blower controls

and allows testing with the 30-second

delay.

It is therefore, ordered that:

(1) The "Petition for Waiver" filed by

the Goodman Manufacturing

Corporation (Case No. F-030) is hereby

granted as set forth in paragraph (2)

below, subject to the provisions of

paragraphs (3), (4), and (5).

(2) Not withstanding any contrary

provisions of appendix N of 10 CFR part

430, subpart B. the Goodman

Manufacturing Corporation shall be

permitted to test its PG and PGX series

rooftop furnaces on the basis of the test

procedure specified in 10 CFR part 430,

with modifications set forth below:

(i) Section 3.0 of appendix N is deleted

and replaced with the following

paragraph:

3.0 Test Procedure. Testing and

measurements shall be as specified in

section 9 in ANSI/ASHRAE 103-82 with

the exception of sections 9.2.2, 9.3.1, and

9.3.2, and the inclusion of the following

additional procedures:

(ii) Add a new paragraph 3.10 to

appendix N as follows:

3.10 Gas-and-Oil-Fueled Central

Furnaces. The following paragraph is in

lieu of the requirement specified in

section 9.3.1 of ANSI/ASHRAE 103-82.

After equilibrium conditions are

achieved following the cool-down test

and the required measurement

performed, turn on the furnaces and

measure the flue gas temperature, using

the thermocouple grid described above,

at 0.5 and 2.5 minutes after the main

burner(s) comes on. After the burner

start-up, delay the blower start-up by 1.5

minutes (t-), unless: (1) The furnace

employs a single motor to drive the

power burner and the indoor air

circulating blower, in which case the

burner and blower shall be started

together; or (2) the furnace is designed to

operate using an unvarying delay time

that is other than 1.5 minutes, in which

case the fan control shall be permitted

to start the blower; or (3) the delay time

results in the activities of a temperature

safety device which shuts off the burner,

in which case the fan control shall be

permitted to start the blower. In the

latter case, if the fan control is

adjustable, set it to start the blower at

the highest temperature. If the fan

control is permitted to start the blower,

measure time delay, (t-), using a stop

watch. Record the measured

temperatures. During the heat-up test for

oil-fueled furnaces, maintain the draft in

the flue pipe within ±0.01 inch of water

column of the manufacturer's

recommended on-period draft.

(iii) With the exception of the

modification set forth above, Goodman

Manufacturing Corporation shall comply

in all respects with the test procedures

specified in appendix N of 10 CFR part

430, subpart B.

(3) The Waiver shall remain in effect

from the date of issuance of this Order

until DOE prescribes final test

procedures appropriate to the PG and

PGX series rooftop furnaces

manufactured by Goodman

Manufacturing Corporation.

(4) This Waiver is based upon the

presumed validity of statements,

allegations, and documentary materials

submitted by the petitioner. This Waiver

may be revoked or modified at any time

upon a determination that the factual

basis underlying the petition is

incorrect.

(5) Effective October 15, 1991, this

Waiver supersedes the Interim Waiver

Granted Goodman Manufacturing

Corporation on April 26,1991. 56 FR

20421, May 3,1991, (Case No. F-030).

Issued in Washington. DC, October 3.1991.

J. Michael Davis,

Assistant Secretary. Conservation and

Renewal Energy.

)FR Doc. 91-24770 Filed 10-11-91; 8:45 am]

BILLING CODE 6450-01-M

CAS-RM-79-104 COMMENT 65