Revision 4.2 

10/28/09 

Air Pollution Control Operating Permit 

Minor Modification and Preconstruction Approval 

Permit Activity Number: BOP090002 Program Interest Number: 85455 

Mailing Address Plant Location 

LEON BRASOWSKI 

DIRECTOR OF ENV PERMITTING 

COVANTA WARREN ENERGY RESOURCE CO 

LP 

40 LANE RD 

Fairfield, NJ 07007-2615 

COVANTA WARREN ENERGY RESOURCE CO 

LP 

218 Mt Pisgah Ave 

Oxford Twp 

Warren County 

Initial Operating Permit Approval Date: September 13, 2004 

Minor Modification Approval Date: November 30, 2009 

Operating Permit Expiration Date: September 11, 2014 

This minor modification is approved and issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 26:2C-9.2). 

The equipment at the facility must be operated in accordance with the requirements of this permit. 

This approval, in response to your application, merges the provisions of the previously approved operating permit 

and the changes from this minor modification into a single comprehensive permit that replaces the one previously 

issued. This modification adds a requirement from 40CFR 60.58b(i)(8) and (9) which allows the maximum 

demonstrated particulate control device temperature at the control device inlet , as determined during dioxin/furan 

testing on one unit annually, to be applied to both units. 

Equipment at the facility referenced by this minor modification is not covered by the permit shield, pursuant to the 

provisions of N.J.A.C. 7:27-22.17. Pursuant to N.J.A.C. 7:27-22.33(e), this minor modification consists of both a 

preconstruction approval and operating permit approval. This operating permit does not include compliance 

schedules as part of the approved compliance plan. 

The permittee shall submit to the Department and to the EPA on forms provided by the Department, at the addresses 

given below, a periodic compliance certification, in accordance with N.J.A.C. 7:27-22.19 and the schedule for 

compliance certifications set forth in the compliance plan in this operating permit. The annual compliance 

certification reporting period will cover the calendar year ending December 31. The annual compliance 

certification is due to the Department and the EPA within 60 days after the end of each calendar year during 

which this permit was in effect. Forms provided by the Department can be found on the Department's website at: 

http://www.nj.gov/dep/enforcement/compliancecertsair.htm. 

The annual compliance certification report may also be considered as your six month deviation report for the period 

from July 1 through December 31 which is due by January 30 of each year, as required by paragraph 13 in Section 

F, General Provisions and Authorities, of this permit, if the annual compliance certification is submitted by January 

30. 

New Jersey Department of Environmental Protection United States Environmental Protection Agency, Region II 

Air & Environmental Quality Compliance & Enforcement Air Compliance Branch 

401 East State Street, P. O. Box 422 290 Broadway 

Trenton, New Jersey 08625-0422 New York, New York 10007-1866 

 

 Jon S. Corzine DEPARTMENT of ENVIRONMENTAL PROTECTION Mark N. Mauriello 

 Governor Acting Commissioner 

Environmental Regulation 

Bureau of Air Permits 

401 E. State Street, 2nd floor, P.O. Box 27 

Trenton, NJ 08625-0027
Revision 4.2 

10/28/09 

New Jersey Department of Environmental Protection 

Air and Environmental Quality Compliance & Enforcement 

Northern Regional Enforcement Office 

7 Ridgedale Avenue

Cedar Knolls, NJ 07927 

We are including two electronic files, PDF and RADIUS. The PDF file contains the complete operating permit for 

your facility. The RADIUS file contains the Facility Name, Location, and Contact Information; the Facility Specific 

Requirements (Compliance Plan) and Inventories; and any Compliance Schedules (if needed). Upon importing this 

information into your personal computer with RADIUS software, you will have up-to-date information in RADIUS 

format. RADIUS software, instructions, and help are available at the Department's website at 

www.state.nj.us/dep/aqpp. We also have an Operating Permit Help Line available from 9:00 AM to 4:00 PM daily, 

where you may speak to someone about any questions you may have. The Operating Permit Help Line number is 

609-633-8248. 

If, in your judgment, the Department is imposing any unreasonable condition of approval in this permit modification 

action, you may contest the Department’s decision on the modification and request an adjudicatory hearing pursuant 

to N.J.S.A. 52:14b-1 et seq. and N.J.A.C. 7:27-22.32(a). All requests for an adjudicatory hearing must be received 

in writing by the Department within 20 calendar days of the date you receive this letter. The request must contain 

the information requested in N.J.A.C. 7:27-1.32 and the information on the enclosed Administrative Hearing 

Request Checklist and Tracking Form. 

The permittee is responsible for submitting a timely and administratively complete operating permit renewal 

application. The application is considered timely if it is received at least 12 months before the expiration date of the 

operating permit. To be deemed administratively complete, an application for renewal of the operating permit shall 

include all of the information required by the application form for the renewal and the information required pursuant 

to N.J.A.C. 7:27-22.30(d). However, consistent with N.J.A.C. 7:27-22.30(c), the permittee is encouraged to submit 

the renewal application at least 15 months prior to expiration of the operating permit, so that the Department can 

notify the applicant of any deficiencies in the application. This will allow the permittee to correct any deficiencies, 

and to better ensure that the application is administratively complete by the renewal deadline. Only applications 

which are timely and administratively complete will be eligible for coverage by an application shield. The renewal 

application can be found at our website, http://www.state.nj.us/dep/aqpp/downloads/forms/OPRenewal.PDF. 

Permittees that are subject to Compliance Assurance Monitoring (CAM), pursuant to 40 CFR 64, shall develop a 

CAM Plan for modified equipment as well as existing sources. Details of the rule and guidance on how to prepare a 

plan can be found at EPA’s website: www.epa.gov/ttn/emc/cam.html. In addition, CAM Plans must be included as 

part of the permit renewal application. Permittees that do not submit a CAM Plan may have their modification 

applications denied, pursuant to N.J.A.C. 7:27-22.3. 

If you have any questions regarding this permit approval, please call your permit writer, Harry Baist, at (609) 633-

8235. 

Approved by: 

Yaso Sivaganesh 

Bureau of Air Permits 

Enclosure 

CC: S. Riva, USEPA Region II (CD containing final permit) 
Revision 4.2 

10/28/09 

Administrative Hearing Request Checklist and Tracking Form 

I. Document Being Appealed 

Name of the Facility 

Program Interest 

(PI) Number

Permit Activity 

Number

Issuance 

Date 

COVANTA WARREN ENERGY RESOURCE 

CO LP 

85455 BOP090002 

II. Contact Information 

Name of Person Requesting Hearing Name of Attorney (if applicable) 

Address: Address:

Telephone: Telephone:

III. Please include the following information as part of your request: 

A. The date the permittee received the permit decision, 

B. A copy of the document being appealed,

C. The legal and factual questions you are appealing; 

D. A statement as to whether or not you raised each legal and factual issues during the 

permit application process; 

E. Suggested revised or alternative permit conditions; 

F. An estimate of the time required for the hearing; 

G. A request, if necessary, for a barrier-free hearing location for physically disabled persons; 

H. A clear indication of any willingness to negotiate a settlement with the Department prior to 

the Departments processing of your hearing request to the Office of Administrative Law; 

Mail this form, completed, signed and dated with all of the information listed above, including attachment, 

to: 

1. New Jersey Department of Environmental Protection 

Office of Legal Affairs 

Attention: Adjudicatory Hearing Requests 

401 E. State Street, P.O. Box 402 

Trenton, New Jersey 08625 

2. Mr. Robert Esposito 

Air Quality Permitting Element 

New Jersey Department of Environmental Protection 

 401 E. State Street, 2nd Floor, P.O. Box 027 

Trenton, New Jersey 08625 

Phone: (609) 633-2829 

Signature Date 
Revision 4.2 

10/28/09 

Administrative Hearing Request Checklist and Tracking Form 

IV. If you are not the applicant but rather an interested person claiming to be aggrieved by the 

permit decision, please include the following information: 

1. The date you or your agent received notice of the permit decision (include a copy of that 

permit decision with your hearing request); 

2. Evidence that a copy of the request has been delivered to the applicant for the permit 

which is the subject of the permit decision; 

3. A detailed statement of which findings of fact and/or conclusion of law you are 

challenging; 

4. A description of your participation in any public hearings held in connection with the 

permit application and copies of any written comments you submitted; 

5. Whether you claim a statutory or constitutional right to a hearing, and, if you claim such a 

right, a reference to the applicable statute or explanation of how your property interests 

are affected by the permit decision; 

6. If the appeal request concerns a CAFRA permit decision, evidence that a copy of the 

request has been delivered to the clerks of the county and the municipality in which the 

project which is the subject of the permit decision is located; 

7. Suggested revised or alternative permit conditions; 

8. An estimate of the time required for the hearing; 

9. A request, if necessary, for a barrier-free hearing location for physically disabled persons; 

10. A clear indication of any willingness to negotiate a settlement with the Department prior to 

the Department’s transmittal of the hearing request to the Office of Administrative Law; 

Mail this form, completed, signed and dated with all of the information listed above, including attachment, 

to: 

1. New Jersey Department of Environmental Protection 

Office of Legal Affairs 

Attention: Adjudicatory Hearing Requests 

401 East State Street, P.O. Box 402 

Trenton, New Jersey 08625-0402 

 

2. Mr. Robert Esposito 

Air Quality Permitting Element 

New Jersey Department of Environmental Protection 

 401 E. State Street, 2nd Floor, P.O. Box 027 

Trenton, New Jersey 08625 

Phone: (609) 633-2829 

Signature Date 
Revision 4.2 

10/28/09 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

TABLE OF CONTENTS 

Section A

REASON FOR PERMIT 

Section B

DEFINITIONS 

Section C

POLLUTANT EMISSIONS SUMMARY 

Section D

POLLUTION PREVENTION REPORTING 

Section E

GENERAL PROVISIONS AND AUTHORITIES 

Section F

STATE-ONLY APPLICABLE REQUIREMENTS 

Section G

COMPLIANCE PLAN AND INVENTORIES
Revision 4.2 

10/28/09 

Section A 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

REASON FOR PERMIT 

The reason for issuance of this permit is to comply with the air pollution control permit provisions of Title V of the 

federal Clean Air Act, federal rules promulgated at 40 CFR 70, and state regulations promulgated at N.J.A.C. 7:27-

22, which requires the state to issue operating permits to major facilities and minor facilities that are in certain 

designated source categories. This is the operating permit for the facility listed on the cover page, which includes a 

minor modification which adds a requirement from 40CFR 60.58b(i)(8) and (9) which allows the maximum 

demonstrated particulate control device temperature at the control device inlet , as determined during dioxin/furan 

testing on one unit annually, to be applied to both units 

New Jersey has elected to integrate its Title I New Source Review (NSR) preconstruction permits with the new Title 

V operating permits instead of issuing separate permits. Consequently, the existing preconstruction permit 

provisions that were previously approved for this facility have been consolidated into this permit. This permit may 

also include applicable requirements for grandfathered sources. 

This permit action consolidates previously approved permit terms and conditions into one single permit for the 

facility. The New Jersey Department of Environmental Protection (Department) issues this operating permit 

authorizing the facility to operate equipment and air pollution control devices. In the operating permit application, 

the facility represented that it meets all applicable requirements of the federal Clean Air Act and the New Jersey Air 

Pollution Control Act codified at N.J.S.A. 26:2C. Based on an evaluation of the data contained in the facility’s 

application, the Department has approved this operating permit. 

This permit allows this facility to operate the equipment and air pollution control devices specified in this permit and 

emit up to a level specified for each source operation. The signatories named in the application are responsible for 

ensuring that the facility is operated in a manner consistent with this permit, its conditions, and applicable rules. 
Revision 4.2 

10/28/09 

Section B 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

DEFINITIONS 

The terms used in this permit are used consistent with the definitions at N.J.A.C. 7:27-1 and N.J.A.C. 7:27-22. Any 

terms defined in this section are not defined at N.J.A.C. 7:27-1 or N.J.A.C. 7:27-22, and are needed for clarifying 

the permit. 

“Permitting Authority” means the New Jersey Department of Environmental Protection (NJDEP). 

“The EPA,” or “the Administrator,” means the Administrator of the EPA or his designee. 

“M” preceding a unit of measure means one thousand. For example, “10 M gal.” means ten thousand gallons. 

“MM” preceding a unit of measure means one million. For example, “10 MM gal.” means ten million gallons. 

“Grandfathered” means, in reference to equipment or control apparatus, that construction, reconstruction, or 

modification occurred prior to enactment of N.J.S.A. 26:2C-9.2 on June 15, 1967, or prior to the subsequent 

applicable revisions to rules and regulations codified at N.J.A.C. 7:27-8 that occurred March 5, 1973, June 1, 1976, 

April 5, 1985, and October 31, 1994, and no construction, reconstruction, or modification of the equipment or 

control apparatus has occurred since. 

“Compliance Plan” means the applicable requirements, monitoring requirements, recordkeeping requirements, and 

submittal/action requirements detailed in Section J, Facility Specific Requirements, of the operating permit. 
Revision 4.2 

10/28/09 

Section C 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

POLLUTANT EMISSIONS SUMMARY

The following table indicates the facility’s Potential to Emit (PTE) emissions summary: 

Facility Total Potential to Emit 

(tons per year) 

Source Categories Primary Secondary 

VOC 

(total) 

NOx CO SO2 TSP 

(total) 

Other 

(total) 

PM10

(total) 

Pb HAPs 

(total) 

Emission Unit 

Summary 

15.0 301 307 175 26.5 NA 14.9 2.19 108 

Batch Process 

Summary 

NA NA NA NA NA NA NA NA NA 

Non-Source Fugitive 

Emissions1

NA NA NA NA NA NA NA NA NA 

Group 

Summary 

NA NA NA NA NA NA NA NA NA 

Total 

Emissions2

15.0 301 307 175 26.5 NA 14.9 2.19 108 

VOC Volatile Organic Compounds PM10 Particulates under 10 microns 

NOx Nitrogen Oxides Pb Lead 

CO Carbon Monoxide HAPs Hazardous Air Pollutants 

SO2 Sulfur Dioxide 

TSP Total Suspended Particulates 

Other Any other air contaminant regulated under the Federal Clean Air Act 

 

1

 Not applicable to this facility. 

2

 Total emissions from this facility do not include emissions from Insignificant Sources. 
Revision 4.2 

10/28/09 

Section C 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

POLLUTANT EMISSIONS SUMMARY

The following table indicates the facility’s hazardous air pollutants (HAP) emissions summary:3

HAP TPY 

Hydrogen Chloride 104. 

Hydrogen Fluoride 0.876 

H2SO4 & SO3 2.02 

Mercury 0.0407 

Arsenic 0.0175 

Beryllium 0.00350 

Cadmium 0.263 

Chromium 0.0876 

Lead 2.19 

Nickel 0.0350 

2,3,7,8 tetrachloro dibenzodioxin 0.00000876 

Polycyclic aromatic 

hydrocarbons (PAH) 

0.0368 

 

3

 Do not sum these values for the purpose of establishing a total HAP potential to emit. See previous page for the 

allowable total HAP emissions. 
Revision 4.2 

10/28/09 

Section D 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

POLLUTION PREVENTION REPORTING 

General Pollution Prevention conditions

The following evaluation requirements are included to track the facility’s progress in several critical areas identified 

in the National Environmental Performance Partnership System (NEPPS). Nitrogen Oxides (NOx) and Volatile 

Organic Compounds (VOC) are precursors to the air pollutant Ozone, for which New Jersey is non-attainment with 

the air quality standard for the protection of public health. The control of hazardous air pollutants (HAPs) is also a 

focus item for the next decade in order to minimize localized hot spots and general urban air toxics levels. 

Therefore, the Department is requiring evaluation of emission trends at 5-year intervals for major sources of these 

air contaminants. Also, as part of significant modification applications, proposed major increases of these air 

contaminants requires evaluation of pollution prevention and cross media effects. 

The evaluation of these trends requires no increased monitoring. Rather it utilizes existing monitoring data, as 

reported annually in Emission Statements (for NOx and VOC) and annual Release and Pollution Prevention Reports 

(for HAPs). The intent of this evaluation is to better utilize the existing data by having the company, the public and 

the Department review major source trends periodically, as part of the 5-year renewal review and public comment 

process. The Department requests that the facility-wide trends be presented on graphs for attachment to the public 

information document for the 5-year renewal. 

Pollution prevention includes changes that result in the reduction in use or generation of non-product output per unit 

of product. Cross media effects are practices that result in transferring the ultimate release or disposal of a 

contaminant from one environmental medium (e.g. air) to another environmental medium (e.g. water, solid or 

hazardous wastes). 

Information to include with the renewal application:

1. The facility will evaluate annual emission trends over the last five years for actual air contaminant 

emissions of Volatile Organic Compounds (VOC), Nitrogen Oxides (NOx), if the facility’s potential to 

emit VOC or NOx is greater than 25 tons per year, or any Hazardous Air Pollutants (HAP), for which the 

facility’s potential to emit is greater than 10 tons per year. The VOC and NOx emission data should reflect 

annual emission statement reports submitted pursuant to N.J.A.C. 7:27-21, and the HAP emissions data 

should reflect the annual Release and Pollution Prevention Report submitted pursuant to N.J.A.C. 7:1G-4 

and 5 and N.J.A.C. 7:1K-6. Although not required, the Department encourages the facility to explain the 

reason for any significant trend, including whether it is the result of cross media shifts (to air, water, or 

solid waste) and/or pollution prevention. Changes should be itemized for each emission unit (or process) 

with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton per year 

of any HAP. Also, show the net change for the facility. 

2. The facility will summarize annual potential to emit limits (allowable emissions) for VOC, NOx, and 

HAPs, which are subject to reporting under 1 above, for the last five years. Changes should be itemized for 

each emission unit (or process) with a potential to emit over five tons per year of VOC or NOx or a 

potential to emit over one ton per year of any HAP. Also, show the net change for the facility. 

3. The facility will summarize five-year trends in annual VOC, NOx, and HAP emissions, which are subject 

to reporting under 1 above, on a pound per unit of product basis, based on annual actual emissions and 

annual production over the five year period. Changes should be itemized for each emission unit (or 
Revision 4.2 

10/28/09 

process) with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton 

per year of any HAP. Also, show the net change for the facility. 

4. The facility will discuss five-year trends in actual air contaminant emissions of non-source VOC and HAP 

fugitives, which are subject to reporting under (1) above; explain measures taken to minimize such 

fugitives; and provide an explanation for any significant changes. 

Information to include with an application for a significant modification to this permit:

1. For any significant modifications, the facility is encouraged to explain any cross media shifts of VOC and 

HAP air contaminants as part of the significant modification application. If an explanation is provided, the 

facility should identify the pollutant and the specific environmental media to which the pollutant is 

anticipated to be transferred, whether it be from air to solid waste or water, or from water or solid waste to 

the air. 
Revision 4.2 

10/28/09 

Section E 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

GENERAL PROVISIONS AND AUTHORITIES 

Operating Permits

1. No permittee shall allow any air contaminant, including an air contaminant detectable by the sense of 

smell, to be present in the outdoor atmosphere in a quantity and duration which is, or tends to be, injurious 

to human health or welfare, animal or plant life or property, or which would unreasonably interfere with the 

enjoyment of life or property. This shall not include an air contaminant that occurs only in areas over 

which the permittee has exclusive use or occupancy. Conditions relative only to nuisance situations, 

including odors, are not considered Federally enforceable. [N.J.A.C. 7:27-22.16(g)8] 

2. Any deviation from operating permit requirements which results in a release of air contaminants shall be 

reported to the Department as follows: 

If the air contaminants are released in a quantity or concentration which poses a potential threat to public 

health, welfare or the environment or which might reasonably result in citizen complaints, the permittee 

shall report the release to the Department: 

i. Immediately on the Department hotline at 1-877-927-6337, pursuant to N.J.S.A. 26:2C-19(e); and 

ii. As part of the compliance certification required in N.J.A.C. 7:27-22.19(f). However, if the 

deviation is identified through source emissions testing, it shall be reported through the source 

emissions testing and monitoring procedures at N.J.A.C. 7:27-22.18(e)3; or 

If the air contaminants are released in a quantity or concentration which poses no potential threat to public 

health, welfare or the environment and which will not likely result in citizen complaints, the permittee shall 

report the release to the Department as part of the compliance certification required in N.J.A.C. 7:27-

22.19(f), except for deviations identified by source emissions testing reports, which shall be reported 

through the procedures at N.J.A.C. 7:27-22.18(e)3; or 

If the air contaminants are released in a quantity or concentration which poses no potential threat to public 

health, welfare or the environment and which will not likely result in citizen complaints, and the permittee 

intends to assert the affirmative defense afforded by N.J.A.C. 7:27-22.16(l), the violation shall be reported 

by 5:00 P.M. of the second full calendar day following the occurrence, or of becoming aware of the 

occurrence, consistent with N.J.A.C. 7:27-22.16(l). [N.J.A.C. 7:27-22.19(g)] 

3. The permittee shall comply with all conditions of the operating permit including the approved compliance 

plan. Any non-compliance with a permit condition constitutes a violation of the New Jersey Air Pollution 

Control Act N.J.S.A. 26:2C-1 et seq., or the CAA, 42 U.S.C. §7401 et seq., or both, and is grounds for 

enforcement action; for termination, revocation and reissuance, or for modification of the operating permit; 

or for denial of an application for a renewal of the operating permit. [N.J.A.C. 7:27-22.16(g)1] 

4. It shall not be a defense for the permittee in an enforcement action that it would have been necessary to halt 

or reduce the permitted activity in order to maintain compliance with the conditions of its operating permit. 

[N.J.A.C. 7:27-22.16(g)2] 
Revision 4.2 

10/28/09 

5. This operating permit may be modified, terminated, or revoked for cause by the EPA pursuant to 40 CFR 

70.7(g) and revoked or reopened and modified for cause by the Department pursuant to N.J.A.C. 7:27-

22.25. [N.J.A.C. 7:27-22.16(g)3] 

6. The permittee shall furnish to the Department, within a reasonable time, any information that the 

Department may request in writing to determine whether cause exists for modifying, revoking and 

reissuing, or terminating this operating permit; or to determine compliance with the operating permit. 

[N.J.A.C. 7:27-22.16(g)4] 

7. The filing of an application for a modification of an operating permit, or of a notice of planned changes or 

anticipated non-compliance, does not stay any operating permit condition. [N.J.A.C. 7:27-22.16(g)5] 

8. The operating permit does not convey any property rights of any sort, or any exclusive privilege. [N.J.A.C. 

7:27-22.16(g)6] 

9. Upon request, the permittee shall furnish to the Department copies of records required by the operating 

permit to be kept. [N.J.A.C. 7:27-22.16(g)7] 

10. The Department and its authorized representatives shall have the right to enter and inspect any facility 

subject to N.J.A.C. 7:27-22, or portion thereof, pursuant to N.J.A.C. 7:27-1.31. [N.J.A.C. 7:27-22.16(g)9] 

11. The permittee shall pay fees to the Department pursuant to N.J.A.C. 7:27. [N.J.A.C. 7:27-22.16(g)10] 

12. Each permittee shall maintain records of all source emissions testing or monitoring performed at the facility 

and required by the operating permit in accordance with N.J.A.C. 7:27-22.19. Records shall be maintained, 

for at least five years from the date of each sample, measurement, or report. Each permittee shall maintain 

all other records required by this operating permit for a period of five years from the date each record is 

made. At a minimum, source emission testing or monitoring records shall contain the information specified 

at N.J.A.C. 7:27-22.19(b). [N.J.A.C. 7:27-22.19(a) and N.J.A.C. 7:27-22.19(b)] 

13. In accordance with N.J.A.C. 7:27-22.19(c) and 22.19(d) 3, each permittee shall submit to the Department, 

on forms provided by the Department, a six month deviation report relating to testing and monitoring 

required by the operating permit, not including information for testing and monitoring which have other 

reporting schedules specified in the permit. Normally, stack testing reporting is submitted within 45 days 

of test completion and continuous monitoring reporting is done quarterly. The six month report must 

address other specified monitoring, including, but not limited to, continuous and periodic monitoring data 

required by this permit. (See column two and three entitled “Monitoring Requirement” and 

“Recordkeeping Requirement,” respectively, in the Facility Specific Requirements section of this permit.). 

The six month reports for the testing and monitoring performed from January 1 through June 30, shall be 

reported by July 30 of the same calendar year; or from July 1 through December 31, shall be reported by 

January 30 of the following calendar year. Pursuant to N.J.A.C. 7:27-22.19(e), these six month reports 

shall clearly identify all deviations from operating permit requirements, the probable cause of such 

deviations, and any corrective actions taken. Any “None” listed in the Submittal/Action Requirement in 

the operating permit is not intended to override the six-month deviation report. The report shall be certified 

pursuant to N.J.A.C. 7:27-1.39 by a responsible official. Forms provided by the Department can be found 

on the Department's website at: http://www.nj.gov/dep/enforcement/compliancecertsair.htm [N.J.A.C. 

7:27-22.19(d) 3 and N.J.A.C. 7:27-22.19(e)] 

An annual compliance certification required by paragraph 2 above and required by N.J.A.C. 7:27-19(f) may 

also be considered as your six month deviation report for the period from July 1 through December 31 

which is due by January 30 of each year if the annual compliance certification is submitted by January 30. 

14. For emergencies (as defined at 40 CFR 70.6(g)(1)) that result in non-compliance with any promulgated 

federal technology-based standard such as NSPS, NESHAPS, or MACT, a federal affirmative defense is 

available, pursuant to 40 CFR 70. To assert a federal affirmative defense, the permittee must use the 

procedures set forth in 40 CFR 70. The affirmative defense provisions described in 15 below may not be 

applied to any situation that caused the Facility to exceed any federally delegated regulation, including but 

not limited to NSPS, NESHAP, or MACT. 
Revision 4.2 

10/28/09 

15. For situations other than those covered by 14 above, an affirmative defense is available for a violation of a 

provision or condition of the operating permit only if: 

i. The violation occurred as a result of an equipment malfunction, an equipment start-up or 

shutdown, or during the performance of necessary equipment maintenance; and 

ii. The affirmative defense is asserted and established as required by N.J.S.A. 26:2C-19.1 through 

19.5 and any implementing rules. [N.J.A.C. 7:27-22.16(l)] 

16. Each permittee shall meet all requirements of the approved source emissions testing and monitoring 

protocol during the term of the operating permit. N.J.A.C. 7:27-22.18(j)] 

The following paragraphs of this section are included for the permittee's convenience to remind them of their 

obligations with certain key applicable requirements. These paragraphs are not enforceable since they paraphrase 

areas of the operating permits rule. Also, these paragraphs do not reference all the applicable requirements with 

which the permittee must comply. 

17. Each owner and each operator of any facility, source operation, or activity to which this permit applies is 

responsible for ensuring compliance with all requirements of N.J.A.C. 7:27-22. If the owner and operator 

are separate persons, or if there is more than one owner or operator, each owner and each operator is jointly 

and severally liable for any fees due under N.J.A.C. 7:27-22, and for any penalties for violation of N.J.A.C. 

7:27-22. 

18. In the event of a challenge to any part of this operating permit, all other parts of the permit shall continue to 

be valid. 

19. The permittee shall ensure that no air contaminant is emitted from any significant source operation at a rate, 

calculated as the potential to emit, that exceeds the applicable threshold for reporting emissions set forth in 

the Appendix to N.J.A.C. 7:27-22, unless emission of the air contaminant is authorized by this operating 

permit. 

20. Consistent with the provisions of N.J.A.C. 7:27-22.3(e), the permittee shall ensure that all requirements of 

this operating permit are met. In the event that there are multiple emission limitations, monitoring, 

recordkeeping, and/or reporting requirements for a given source operation, the facility must comply with all 

requirements, including the most stringent. 

21. Consistent with the provisions of N.J.A.C. 7:27-22.9(c), the permittee shall use monitoring of operating 

parameters, where required by the compliance plan, as a surrogate for direct emissions testing or 

monitoring, to demonstrate compliance with applicable requirements. 

22. The permittee shall file a timely and complete application for: 

Administrative Amendments; 

Seven-Day-Notice changes; 

Minor Modifications; 

Significant Modifications; and 

Renewals. 

23. Process monitors must be operated at all times when the associated process equipment is operating except 

during outage time allowed by Department guidelines/procedures or as outlined in Technical Manual 1005. 

The permittee must keep a service log as required. 

 
Revision 4.2 

10/28/09 

Section F 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

STATE-ONLY APPLICABLE REQUIREMENTS 

N.J.A.C. 7:27-22.16(b)5 requires the Department to specifically designate as not being federally enforceable any 

permit conditions based only on applicable state requirements. The applicable state requirements to which this 

provision applies are listed in the table titled “State-Only Applicable Requirements.” 

STATE-ONLY APPLICABLE REQUIREMENTS 

The following applicable requirements are not federally enforceable: 

 SECTION SUBJECT ITEM ITEM # REF. #

 E --- 15 --- 

 G FC --- 3 

 G FC --- 9 

 G FC --- 16 
Revision 4.2 

10/28/09 

Section G 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

COMPLIANCE PLAN AND INVENTORIES 

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX 

• FACILITY SPECIFIC REQUIREMENTS (COMPLIANCE PLAN) 

• FACILITY PROFILE (ADMINISTRATIVE INFORMATION) 

• REASON FOR APPLICATION 

• NON-SOURCE FUGITIVE EMISSIONS 

• INSIGNIFICANT SOURCE EMISSIONS 

• EQUIPMENT INVENTORY 

• EQUIPMENT DETAILS 

• CONTROL DEVICE INVENTORY 

• CONTROL DEVICE DETAILS EMISSION POINT INVENTORY 

• EMISSION UNIT/BATCH PROCESS INVENTORY )

• SUBJECT ITEM GROUP INVENTORY 
Revision 4.2 

10/28/09 

Facility Name: COVANTA WARREN ENERGY RESOURCE CO LP 

Program Interest Number: 85455 

Permit Activity Number: BOP090002 

FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX 

Subject Item and Name Page Number

 Facility (FC): 

 FC 1 

Insignificant Sources (IS):

 IS1 – Heated Non-VOC Surface Cleaners (Parts Cleaners) using no VOCs, or HAPs. 6 

 IS2 - Kerosene, Diesel & Used Oil Storage Tanks (< 2,000 gallons) 7 

 IS5 - Equipment processing less than 50 lb/hr. 8 

 IS6 - Bins < 2,000 cu. ft. 9 

 IS8 - Cooling Tower 10 

 IS10 - Fuel oil storage Tanks > 10,000 gallons 11 

 IS20 – Urea Tank 13 

Group (GR):

 GR1 – Equipment Subject to Federal Regulations (E1, 2, 6, 8 & 13) 14 

Emission Units (U):

 U1 – Two 200 TPD MSW Incinerators 22 

 U2 – Ash Handling System 74 

 U3 – 1.85 MMBTU/hr Diesel Engine driven fire water pump 79 

 U4 – 2.12 MMBTU/hr Diesel Engine driven Emergency Generator 84 
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: FC

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 General Provisions: Defines numerous terms

used in N.J.A.C. 7:27. Specifies proceduresfor making confidentiality claims, certifyingapplications, reports, and other documentsto the Department, and requestingadjudicatory hearings and stays of theeffective date of departmental decisions.Also, provides provisions regardingapplicability, severability, and liberalconstruction of N.J.A.C. 7:27. [N.J.A.C.7:27- 1]

None. None. None.

2 Control and Prohibition of Open Burning:

Prohibits any person from open burning ofrubbish, garbage, trade waste, buildings,structures, leaves, other plant life andsalvage. Open burning of infested plant lifeor dangerous material may only beperformed with a permit from theDepartment. [N.J.A.C. 7:27- 2]

None. None. Obtain an 

occurrence [N.J.A.C. 

3 Prohibition of Air Pollution:

Notwithstanding compliance with othersubchapters of N.J.A.C. 7:27, no personshall suffer, allow, or permit to be emittedinto the outdoor atmosphere substances inquantities that result in air pollution asdefined at N.J.A.C. 7:27-5.1. Applicable toall facilities located in New Jersey.[N.J.A.C. 7:27- 5]

None. None. None.

4 Prevention and Control of Air Pollution

Control Emergencies: Requires that writtenStandby Plans, consistent with goodindustrial practice and safe operatingprocedures, be prepared for reducing theemission of air contaminants during periodsof an air pollution alert, warning, oremergency. Any person responsible for theoperation of a source of air contaminationnot set forth in Table 1 of N.J.A.C. 7:27-12is not required to prepare such a plan unlessrequested by the Department in writing.[N.J.A.C. 7:27-12]

None. None. Comply w

occurrence the Governwarning, oput the Stathe permitapplicable N.J.A.C. 7complied wpollution a[N.J.A.C. 

Page 1 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

5 Emission Offsets Rules. [N.J.A.C. 7:27-18] Other: When applying for minor/significant

modification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].

Comply woccurrence administraapplying fto N.J.A.Cmodificati7:27-22.24

6 Emissions Statements: Submit an annual

emission statement (if required)electronically to the NJDEP by May 15 ofeach year (or by mutually agreed upon date,but no later than June 15 of each year).[N.J.A.C. 7:27-21]

Other: The emission statement will be basedon monitoring, recording and recordkeepingof actual emissions, capture and controlefficiencies, process rate and operating datafor source operations with the potential toemit certain air contaminants. [N.J.A.C.7:27-21].

Other: The emission statement and allsupporting records shall be maintained onthe operating premises for a period of five(5) years from the due date of each emissionstatement. [N.J.A.C. 7:27-21].

Submit an Annually (15 or by anot later th[N.J.A.C. 

7 Compliance Certification: Submit annual

compliance certification for each applicablerequirement, pursuant to N.J.A.C.7:27-22.19(f), within 60 days after the endof each calendar year during which thispermit was in effect. [N.J.A.C. 7:27-22]

None. None. Submit an 

Annually tforms provdays after during whannual comperiod wilDecember DepartmenDepartmenhttp://wwwcomplianc [N.J.A.C

8 Prevention of Air Pollution from

Architectural Coatings and ConsumerProducts. [N.J.A.C. 7:27-23]

None. None. None.

9 Any operation of equipment which causes

off-property effects, including odors, orwhich might reasonably result in citizen'scomplaints shall be reported to theDepartment to the extent required by the AirPollution Control Act, N.J.S.A.26:2C-19(e). [N.J.S.A. 26:2C-19(e)]

Other: Observation of plant operations.[N.J.S.A. 26:2C-19(e)].

Other: Maintain a copy of all informationsubmitted to the Department. [N.J.S.A.26:2C-19(e)].

Notify by A person wcontaminawhich poshealth, wemight reasshall immeSuch notifthe Enviro927-6337. 

Page 2 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

10 Prevention of Significant Deterioration

(PSD). [40 CFR 52.21]

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].

Comply woccurrence permittee complete asignificant N.J.A.C. 7

11 National Emission Standards for Hazardous

Air Pollutants (NESHAPS) for Asbestos. [40 CFR 61]

Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].

Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].

Comply woccurrence comply wiwhen conddemolition 61]

12 Protection of Stratospheric Ozone:1) If the

permittee manufactures, transforms,destroys, imports, or exports a Class I orClass II substance, the permittee is subjectto all the requirements as specified at 40CFR 82, Subpart A; 2) If the permitteeperforms a service on motor "fleet" vehicleswhen this service involves an ozonedepleting substance refrigerant (or regulatedsubstance) in the motor vehicle airconditioner (MVAC), the permittee issubject to all the applicable requirements asspecified at 40 CFR 82, Subpart B. 3) Thepermittee shall comply with the standardsfor labeling of products containing ormanufactured with ozone depletingsubstances pursuant to 40 CFR 82, SubpartE. 4). The permittee shall comply with thestandards for recycling and emissionreductions of Class I and Class IIrefrigerants or a regulated substitutesubstance during the service, maintenance,repair, and disposal of appliances pursuantto 40 CFR 82, Subpart F, except as providedfor motor vehicle air conditioners (MVACs)in Subpart B. 5) The permittee shall beallowed to switch from any ozone depletingsubstance to any alternative that is listed inthe Significant New Alternative Program(SNAP) promulgated pursuant to 40 CFR82, Subpart G. [40 CFR 82]

Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].

Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].

Comply woccurrence comply wiF, and G. 

Page 3 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

13 Deviation Report: In accordance with

N.J.A.C. 7:27-22.19(c) and 22.19(d)3, thepermittee shall submit to the Department, onforms provided by the Department, acertified six-month deviation report relatingto testing and monitoring required by theoperating permit, not including informationfor stack emissions testing or continuousemissions monitoring which have otherreporting schedules specified in the permit(normally, stack test report is submittedwithin 45 days of test completion andcontinuous monitor reporting is donequarterly). Pursuant to N.J.A.C.7:27-22.19(e), the six-month report mustaddress other specified monitoring,including continuous and periodicmonitoring requirements found in column 2and 3, entitled "Monitoring Requirement"and "Recordkeeping Requirement,"respectively, of the Facility SpecificRequirements section of this permit. Thesesix-month reports shall clearly identify alldeviations from operating permitrequirements, the probable cause of suchdeviations, and any corrective actions orpreventive measures taken. If no deviationsoccurred, the report should say so. Any"None" listed in the Submittal/ActionRequirement in the Operating Permit is notintended to override the six-month deviationreport. [N.J.A.C. 7.27-22.19(d)3, N.J.A.C.7.27-22.19(e), and [N.J.A.C. 7:27-22.19(c)]

None. Other: The permittee shall maintain

deviation reports for a period of five yearsfrom the date each report is submitted to theDepartment. [N.J.A.C. 7:27-22.19(a)].

Submit a rschedule. specified tthe operatiJanuary 1 submitted year, and fshall be sufollowing submitted Office and N.J.A.C. 7official. Fcan be fouthe followhttp://wwwcomplianc [N.J.A.C. 

14 No person shall combust used oil except as

authorized pursuant to N.J.A.C. 7:27-20.[N.J.A.C. 7:27-20.2]

None. None. Comply w

occurrence oil) either pursuant tpermit issto N.J.A.Capplicable

Page 4 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

15 Prevention of Accidental Releases: Facilities

producing, processing, handling or storing achemical, listed in the tables of 40 CFR Part68.130, and present in a process in aquantity greater than the listed ThresholdQuantity, shall comply with 40 CFR 68. [40CFR 68]

Other: Comply with 40 CFR 68. [40 CFR68].

Other: Comply with 40 CFR 68. [40 CFR68].

Other (prowith 40 CFApplicable 

16 For equipment subject to CO2 Budget

Trading Program, comply with N.J.A.C.7:27C. [N.J.A.C. 7:27C]

Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].

Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].

Comply woccurrence 

Page 5 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: IS1 Heated Non-VOC Surface Cleaners (Parts Cleaners) that use cleaning solutions containing no VOCs, or HAP

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Cleaning solvents shall contain less than

five percent VOCs, HAPs or VOCs andHAPs combined. [N.J.A.C. 7:27-16.6(j)]

Other: Monitored by formulation datadetermined upon change in formulation ofsolution, confirm by MSDS.[N.J.A.C.7:27-22.16(o)].

Other: Recordkeeping by MSDS uponchange in formulation of solution. Log thedate of changing the formulation in alogbook or readily available computerfiles.[N.J.A.C. 7:27-22.16(o)].

None.

Page 6 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: IS2 Kerosene, Diesel & Used Oil Storage Tanks (< 2,000 gallons)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Sulfur Content in Fuel <= 0.3 % sulfur by

weight is maximum allowable sulfur contentin fuel oil by fuel oil type/viscosity allowedto be used in geographical zone (Zone 2 -Warren County). [N.J.A.C. 7:27- 9.2(b)]

Other: Check fuel sulfur content by suppliercertification on each change ofsupplier.[N.J.A.C. 7:27- 9.2(b)].

None. None.

Page 7 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: IS6 Bins (< 2,000 cubic feet)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The owner or operator shall not use this

emission unit in a manner which will causevisible emissions greater than 20 percentopacity, exclusive of condensed watervapor, for a period of three minutes in anyconsecutive 30-minute period. [N.J.A.C.7:27-6.2(d)] and. [N.J.A.C. 7:27- 6.2(e)]

None. None. None.

Page 8 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: IS8 Cooling tower

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The concentration in water of any TXS must

be less than 100 parts per billion by weightor the total concentration in the water ofVOC must be below 3,500 parts per billionby weight. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 9 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: IS10 Fuel Oil Storage Tank (> 10,000 gallons)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Sulfur Content in Fuel: If the tank contains

distillate fuel for use in Warren County NewJersey (Zone 2), the maximum allowablesulfur content is 0.3 percent by weight.[N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records once initially andper change of material. Check fuel sulfurcontent by supplier certification on eachchange of supplier. [N.J.A.C. 7:27-22.16(o)]

None. None.

2 The operating temperature shall not be

greater than 350 degrees F. [N.J.A.C.7:27-22.1]

None. None. None.

3 The vapor pressure of the liquid, excluding

the vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]

None. None. None.

4 The tank shall have no visible emissions,

exclusive of water vapor, to the outdooratmosphere. [N.J.A.C. 7:27-22.1]

None. None. None.

5 The tank shall not emit any air contaminants

which may cause an odor detectable outsidethe property boundaries of the facility.[N.J.A.C. 7:27-22.1]

None. None. None.

6 The tank shall not qualify for any

NESHAPS, MACT, or NSPS air pollutioncontrol standards, excluding the NSPSrequirements to maintain a record of thecontents of the tank, the period of storage ofthese contents, and the maximum true vaporpressure of the liquid stored. [N.J.A.C.7:27-22.1]

None. None. None.

7 The tank's potential to emit each TXS and

each HAP shall not exceed the de minimisreporting thresholds as specified in N.J.A.C.7:27-22, Appendix. [N.J.A.C. 7:27-22.1]

None. None. None.

8 The percentage by weight of all HAPs

collectively in the raw material stored in thetank shall be less than 1.0 percent. [N.J.A.C.7:27-22.1]

None. None. None.

Page 10 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 The owner or operator shall have readily

available upon Department request astatement certified in accordance withN.J.A.C. 7:27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank meets theapplicable requirements of Ref. #2 to #8above and (3) attests that the tank is incompliance with all other applicable State orfederal air pollution requirements. [N.J.A.C.7:27-22.1]

None. None. None.

Page 11 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: IS20 Urea Tank

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The material stored in the tank shall consist

of only water and urea and shall not containany VOCs or HAPs, based on theapplication for minor modification of theOperating Permit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 The tank shall not emit any air contaminants

which may cause an odor detectable outsidethe property boundaries of the facility.[N.J.A.C. 7:27-22.1]

None. None. None.

3 The vapor pressure of the liquid, excluding

the vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]

None. None. None.

4 The owner or operator shall have readily

available upon Department request astatement certified in accordance withN.J.A.C. 7:27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank meets theapplicable requirements of Ref. #1 to #2 and(3) attests that the tank is in compliance withall other applicable State or federal airpollution requirements. [N.J.A.C. 7:27-22.1]

None. None. None.

Page 12 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: IS21 kerosene fired Portable Space Heaters (10)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions except for a period no

longer that three minutes in any consecutive30-minute period. From BOP080001[N.J.A.C. 7:27-3.2(a)] and [N.J.A.C. 7:27-3.2(c)]

None. None. None.

2 The fuel for the ten portable space heaters is

limited to kerosene. [N.J.A.C.7:27-22.16(a)]

None. None. None.

Page 13 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Subject Item: GR1 Equipment Subject to Federal NSPS Regulations (E1, 2, 6, 8, 9 & 13)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): All requests, reports,applications, submittals, and othercommunications to the Administratorpursuant to Part 60 shall be submitted induplicate to the Regional Office of USEnvironmental Protection Agency. Submitinformation to: Region II, Director, Air andWaste Management Division, USEnvironmental Protection Agency, 21stFloor, 290 Broadway, New York, NY10007. [40 CFR 60.4(a)]

None. None. Submit a r

schedule tCFR 60. [

2 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): Copies of all informationsubmitted to EPA pursuant to 40 CFR Part60, must also be submitted to the NorthernRegional Enforcement Office of NJDEP at1259 Route 46, Parsippany, NJ 07054. [40CFR 60.4(b)]

None. None. Submit a r

schedule tEnforcemeby 40 CFR 

Page 14 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): The owner or operatorsubject to the provisions of 40 CFR Part 60shall furnish the Administrator writtennotification or, if acceptable to both theAdministrator and the owner or operator of asource, electronic notification, of anyphysical or operational change to an existingfacility which may increase the emission rateof any air pollutant to which a standardapplies, unless that change is specificallyexempted under an applicable subpart or insection 60.14(e). The notification shallinclude information describing the precisenature of the change, present and proposedemission control systems, productivecapacity of facility before and after thechange and the expected completion date ofthe change. Notification shall be postmarkedwithin 60 days or as soon as practicablebefore any change is commenced. TheAdministrator may request additionalrelevant information subsequent to thisnotice. [40 CFR 60.7(a)(4)]

None. None. Submit no

event to EEnforcemeby 40 CFR 

4 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): The owner or operatorshall maintain records of the occurrence andduration of any startup, shutdown, ormalfunction in the operation of an affectedfacility, any malfunction of air pollutioncontrol equipment or any periods duringwhich continuous monitoring system ormonitoring device is inoperative. [40 CFR60.7(b)]

None. Recordkeeping by manual logging of

parameter upon occurrence of event in alogbook. The records should be kept in apermanent form suitable for inspections. [40CFR 60.7(b)]

None.

Page 15 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

5 For equipment subject to NSPS CMS

requirements (E1 and E2): Each owner oroperator required to install a continuousmonitoring device shall submit an excessemissions and monitoring systemsperformance report (excess emissions aredefined in applicable subparts) and/or asummary report form (see section 60.7(d))to the Administrator semiannually, exceptwhen: more frequent reporting isspecifically required by an applicablesubpart; or the Administrator, on acase-by-case basis, determines that morefrequent reporting is necessary to accuratelyassess the compliance status of the source.All reports shall be postmarked by the 30thday following the end of each six-monthperiod. [40 CFR 60.7(c)]

None. Other: Written records of excess emissions

shall include the following information: (1)The magnitude of excess emissionscomputed in accordance with section60.13(h), any conversion factor(s) used, andthe date and time of commencement andcompletion of each time period and excessemissions. The process operating timeduring the reporting period. (2) Specificidentification of each period of excessemissions that occurs during startups,shutdowns, and malfunctions of the affectedfacility. The nature and cause of anymalfunction (if known), the corrective actiontaken or preventative measures adopted. (3)The date and time identifying each periodduring which the continuous monitoringsystem was inoperative except for zero andspan checks and the nature of the systemrepairs or adjustments. (4) When no excessemissions have occurred or the continuousmonitoring system(s) have not beeninoperative, repaired, or adjusted, suchinformation shall be stated in the report.[40CFR 60.7(c)].

Submit an Monitorin(EEMPR)30th day operformanpostmarkeend of eacshall be suAdministrEnforcemeformat spe40 CFR Pexcess eminformatiolisted undethis applic60.7(c)]

6 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): The owner or operatorshall maintain a file, suitable for inspection,of all monitoring measurements as indicatedin Recordkeeping Requirement column. [40CFR 60.7(f)]

None. Other: The file shall include all

measurements (including continuousmonitoring system, monitoring device, andperformance testing measurements), allcontinuous monitoring system performanceevaluations, all continuous monitoringsystem or monitoring device calibrationchecks, all adjustments/maintenanceperformed on these systems or devices, andall other information required by 40 CFRPart 60 recorded in a permanent formsuitable for inspection. [40 CFR 60.7(f)].

None.

7 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): The owner or operatorshall conduct performance tests and datareduced in accordance with the test methodsand procedures contained in each applicablesubpart, unless otherwise specified andapproved by the Administrator. [40 CFR60.8(b)]

None. None. None.

Page 16 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): Performance tests shall beconducted under conditions theAdministrator specifies to the plant operatorbased on representative performance of theaffected facility. Operations during periodsof startup, shutdown and malfunction shallnot constitute representative conditions forthe purpose of the performance test nor shallemissions in excess of the level of theapplicable emission limit be considered aviolation of the applicable emission limitunless otherwise specified in the applicablestandard. [40 CFR 60.8(c)]

None. None. None.

9 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): The owner or operatorshall provide the Administrator at least 30days prior notice of any performance testand shall provide adequate performancetesting facilities as specified in 40 CFR Part60.8(e). [40 CFR 60.8(d)]

None. None. None.

10 For equipment subject to NSPS(E1, E2, E6,

E8, E9, and E13): Unless otherwisespecified in the applicable subpart, eachperformance test shall consist of threeseparate runs using the applicable testmethod. [40 CFR 60.8(f)]

None. None. None.

11 For equipment required to conduct NSPS

performance tests for standards other thanopacity (E1 and E2): Compliance withNSPS standards specified in this permit,other than opacity, shall be determined onlyby performance tests established by 40 CFR60.8, unless otherwise specified in NSPS.[40 CFR 60.11(a)]

None. None. None.

12 For equipment required to conduct visual

opacity tests (E1, E2, E6, E8, E9, and E13):The owner or operator shall demonstratecompliance with NSPS opacity standardsspecified in 40 CFR Part 60. [40 CFR60.11(e)(5)] & [40 CFR 60.11(b)]

Monitored by visual determination annually,based on 6 minute blocks. Testing shall beconducted using Reference Method 9 inAppendix A of NSPS, or any alternativemethod that is approved by theAdministrator, or continuous opacitymonitoring system (COMS) data results.[40 CFR 60.11(b)] &. [40 CFR 60.11(e)(5)]

Recordkeeping by manual logging ofparameter annually. The owner or operatorshall maintain records of opacity ofemissions based on Method 9 observations,or based on COM data. [40 CFR60.11(e)(2)]

Submit a roperator shobservatioAdministr

Page 17 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

13 For equipment subject to NSPS COM

requirements (E1 and E2 after November 6,2005): The owner or operator shalldemonstrate compliance with NSPS opacitystandards specified in 40 CFR Part 60. [40CFR 60.11(b)]

Monitored by continuous opacity monitorcontinuously, based on 6 minute blocks. [40CFR 60.11(b)]

Recordkeeping by strip chart, round chart ordata acquisition (DAS) system / electronicdata storage continuously. [40 CFR60.13(h)]

Submit a ragreed upoAdministrsubmit CoSystem (CperformanThe owner Administrdemonstraat least 30 required uconducted outlined in 60.11(e)(5

14 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): The NSPS opacitystandard shall apply at all times exceptduring periods of startup, shutdown,malfunctions and as otherwise specified inthis permit. [40 CFR 60.11(c)]

None. None. None.

15 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): At all times, includingperiods of start-up, shutdown, andmalfunction, owners and operators shall, tothe extent practicable, maintain and operateany affected facility including associated airpollution control equipment in a mannerconsistent with good air pollution controlpractice for minimizing emissions.Determination of whether acceptableoperating and maintenance procedures arebeing used will be based on informationavailable to the Administrator which mayinclude, but is not limited to, monitoringresults, opacity observations, review ofoperation and maintenance procedures, andinspection of the source. [40 CFR 60.11(d)]

None. None. None.

Page 18 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

16 For equipment subject to NSPS (E1, E2, E6,

E8, E9, and E13): No owner or operatorsubject to NSPS standards in Part 60, shallbuild, erect, install, or use any article,machine, equipment or process, the use ofwhich conceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to the atmosphere.[40 CFR 60.12]

None. None. None.

17 For equipment subject to NSPS CEM

requirements (E1 and E2): The owner oroperator shall perform zero and spanadjustments daily for continuous emissionmonitors and continuous opacity monitorsfollowing procedures outlined in 40 CFRPart 60.13(d)1 & 2. [40 CFR 60.13(d)]

None. None. None.

18 For equipment subject to NSPS COM

requirements (E1 and E2): Except forsystem breakdowns, repairs, calibrationchecks, and zero and span adjustments, allcontinuous opacity monitoring systems shallbe in continuous operation. They shallcomplete a minimum of one cycle ofsampling and analyzing for each successive10-second period and one cycle of datarecording for each successive 6-minuteperiod. [40 CFR 60.13(e)(1)]

None. None. None.

19 For equipment subject to NSPS CEM

requirements (E1 and E2): Except forsystem breakdowns, repairs, calibrationchecks, and zero and span adjustments, allcontinuous monitoring systems measuringemissions except opacity shall be incontinuous operation. They shall completea minimum of one cycle of operation(sampling, analyzing and data recording) foreach successive 15-minute period. [40 CFR60.13(e)(2)]

None. None. None.

Page 19 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

20 For equipment subject to NSPS CMS

requirements (E1 and E2): All continuousmonitoring systems or monitoring devicesshall be installed such that representativemeasurements of emissions or processparameters from the affected facility areobtained. Procedures for location ofcontinuous monitoring systems contained inthe applicable Performance Specifications ofAppendix B of 40 CFR Part 60 shall beused. [40 CFR 60.13(f)]

None. None. None.

21 For equipment subject to NSPS COM

requirements (E1 and E2): The owner oroperator shall reduce all continuousmonitoring systems for measuring opacitydata to 6-minute averages which shall becalculated from 36 or more data pointsequally spaced over each 6-minute period.Data recorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmetic orintegrated average of all data may be used.The data may be recorded in reduced ornonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]

None. None. None.

Page 20 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

22 For equipment subject to NSPS CEM

requirements (E1 and E2): The owner oroperator shall reduce all continuousmonitoring systems (other than opacity) datato 1-hour averages which shall be computedfrom four or more data points equallyspaced over each 1-hour period. Datarecorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmetic orintegrated average of all data may be used.The data may be recorded in reduced ornonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]

None. None. None.

23 For equipment subject to NSPS(E1, E2, E6,

E8, E9, and E13): Changes in time periodsfor submittal of information and postmarkdeadlines set forth in this subpart, may bemade only upon approval by theAdministrator and shall follow proceduresoutlined in 40 CFR Part 60.19. [40 CFR60.19]

None. None. None.

Page 21 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U1 Two nominal 274 TPD Municipal Solid Waste Combustors (with Carbon silo) subject to NSPS Eb, 40 CFR 60 

7:27-27

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Initial Performance Evaluation: Within 180

days after the date the facility has achievedfinal compliance with 40 CFR 62 SubpartFFF requirements, the initial performanceevaluation must be conducted. Ifperformance testing results are approved bythe Regional Enforcement Office and BTS,stack testing performed in 2006 prior toapproval of this operating permit shallsatifsfy this requirement.Final compliance shall be: Incorporate allprocess changes in the final control plansuch that all necessary process changes areoperating fully.This date is in lieu of the date for the initialperformance test specified in 40 CFR60.58b of subpart Eb.[40 CFR 60.58b(b)(3)], [40 CFR62.14108(a)(5)] & [40 CFR 62.14109(c)]

None. Recordkeeping by stack test results once

initially. Keep results of initial MACTPerformance test on site. [40 CFR 60.58b]

Submit a skeep resultest on site

2 STACK TESTING REQUIREMENTS: For

facilities demonstrating compliance with40CFR62, Subpart FFF standards, theowner or operator shall conduct aperformance test for opacity, particulatematter, cadmium, lead, mercury, hydrogenchloride, dioxin/furans, and fugitive ashemissions on an annual basis(no less than 9calendar months and no more than 15calendar months following the previousperformance test; and must complete 5performance tests in each 5-year calendarperiod). From BOP080004. [40CFR62.1409(a)] & [40 CFR 60.58(b)]

Monitored by stack emission testingannually, based on each of three Departmentvalidated stack test runs. [40 CFR60.58(b)(c)]

Recordkeeping by stack test resultsannually. [40 CFR 60.59(b)]

Stack Test and submischedule Swithin 90 CFR 60.58

OS Summary

Page 22 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 STACK TESTING REQUIREMENTS:

Conduct annual stack tests on eachmunicipal solid waste combustor todemonstrate compliance with the PSDemission limits for HCl. Upstream anddownstream tests shall be conductedsimultaneously (for HCl only). Testing forlead, cadmium, and ammonia slip is alsorequired annually. Testing must beconducted at worst-case permitted operatingconditions with regard to meeting theapplicable emission standards, but withoutcreating an unsafe condition. FromBOP080004. [N.J.A.C. 7:27-22.16(a)]

Monitored by stack emission testingannually, based on each of three Departmentvalidated stack test runs for HCl and theaverage of three 1-hour runs for cadmium,lead, and ammonia. [N.J.A.C.7:27-22.16(e)]

Recordkeeping by stack test resultsannually. All records shall be maintainedonsite in either paper copy orcomputer-readable format. [N.J.A.C.7:27-22.16(e)]

Submit a stesting shayear using tests, the p609-530-4acceptable than one ytest report90 days (pthe stack t7:27-22.19certified bprofessionhygienist.Test result[N.J.A.C. 

Page 23 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

4 PM-10:STACK TESTING: The owner or

operator shall conduct stack tests on eachmunicipal solid waste combustor todetermine compliance with the total PM-10emission limit (lb/hr.). Total PM-10 shallinclude both filterable and condensiblecatches from the tests. Testing must beconducted at worst-case permitted operatingconditions with regard to meeting theapplicable emission standards, but withoutcreating an unsafe condition. FromBOP080004.. [N.J.A.C. 7:27-22.16(a)]

Monitored by stack emission testing prior topermit renewal, based on each of threeDepartment validated stack test runs. Whenconducting stack emission testing, aminimum of three test runs shall beconducted. [N.J.A.C. 7:27-22.16(o)]

Recordkeeping by stack test results prior topermit renewal. Recordkeeping shall bedone through test reports pursuant toN.J.A.C. 7:27-22.19. [N.J.A.C.7:27-22.16(o)]

Submit a sapproved renewal of stack test pTechnical Trenton, Nto the expipermit.Within 30 permittee 609-530-4acceptable must be su(per PSD ptest pursuatest results licensed pindustrial For stack tmonths froOperating must be surenewal apprior to exTest resultneeded) [N[N.J.A.C. 

Page 24 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

5 TSP: STACK TESTING

REQUIREMENTS: Conduct acomprehensive stack test on each municipalsolid waste incinerator at least 18 monthsprior to the expiration of the approvedoperating permit to demonstrate compliancewith the particulate emission limits, by: i. Three test runs using a method approvedby Bureau of Testing Services; ii. One separate test run conducted usingEPA Reference Method 5 during whichboiler tube rapping is performed.Testing must be conducted at worst-casepermitted operating conditions with regardto meeting the applicable emissionstandards, but without creating an unsafecondition. From BOP080004.[N.J.A.C. 7:27-22.16(a)] and [N.J.A.C.7:27-22.16(e)]

TSP: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs conducted successively.Compliance with TSP emission limitspursuant to N.J.A.C. 7:27-22.16(e) shall bedetermined by the average of the three testruns indicated in (i) of the applicablerequirement, as required in thepreconstruction permit and 40 CFR60.54(b). Compliance with the limitstipulated under N.J.A.C. 7:27-22.16(e)when boiler tube rapping is performed shallbe determined by the test run indicated in(ii) of the applicable requirement. [N.J.A.C.7:27-22.16(a)] and. [N.J.A.C.7:27-22.16(e)]

TSP: Recordkeeping by stack test resultsevery 5 years. All records shall bemaintained onsite in either paper copy orcomputer-readable format. [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule (of this opetest protocServices (B08625 at lexpiration Within 30 permittee 609-530-4acceptable must be su(per PSD ptest pursuatest results licensed pindustrial For stack tmonths froOperating must be surenewal apprior to exTest resultneeded) [N[N.J.A.C. 

Page 25 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 STACK TESTING REQUIREMENTS:

Conduct stack tests on each municipal solidwaste incinerator to demonstrate compliancewith the mercury limits and the requirementsunder N.J.A.C. 7:27-27.4. Testing must beconducted at worst-case permitted operatingconditions with regard to meeting theapplicable emission standards, but withoutcreating an unsafe condition. FromBOP080004.[N.J.A.C. 7:27-27.4] and [N.J.A.C.7:27-22.16(a)]

Monitored by stack emission testingannually, based on the average of three testsconducted successively. The tests formercury shall consist of three sourceemission tests to measure mercury in the gasstream at the inlet of the air pollutioncontrol apparatus serving each combustionunit, and simultaneously perform threesource emission tests to measure mercury inthe gas stream at the exit of the controlapparatus. If source emission testing fails todemonstrate compliance with the applicablerequirement, then the frequency of sourcetesting shall increase to three sourceemission tests quarterly. There shall be atleast a 45 calendar day interval between thetesting performed for a given quarter and thetesting performed for the preceding quarter,unless a shorter period is approved by theDepartment. If compliance with theapplicable requirement is then achieved andmaintained during two consecutive years,the permittee may reduce the frequency ofsource emission testing to three sourceemission tests performed annually.[N.J.A.C. 7:27-27.4(c)] and. [N.J.A.C.7:27-22.16(e)]

Recordkeeping by stack test results annuallyor quarterly if required because of a failedstack test. All records shall be maintainedonsite in either paper copy orcomputer-readable format. [N.J.A.C.7:27-22.16(o)] and. [N.J.A.C.7:27-22.16(e)]

Submit a srequired bshall be peapproved psubmit a ceach test cdays (per Pthe compliChief, BT The test rJersey licecertified in7:27-27.4(

Page 26 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 STACK TESTING REQUIREMENTS:

Conduct stack tests on each municipal solidwaste combustor to demonstrate compliancewith the PSD emission limits forSO2(upstream and downstreamsimultaneously), nitrogen oxides, SO3 +H2SO4 (as converted and expressed asH2SO4), VOCs, Arsenic,Beryllium,Chromium, Nickel, polycyclicaromatic hydrocarbons (PAH) and 2,3,7,8TCDD and Benzo(A)Pyrene on one unit.Testing must be conducted at worst-casepermitted operating conditions with regardto meeting the applicable emissionstandards, but without creating an unsafecondition. From BOP080004.[N.J.A.C. 7:27-22.16(a)] & [N.J.A.C.7:27-22.16(e)]

Monitored by stack emission testing prior topermit renewal, based on the average ofthree Department validated stack test runsconducted successively. [N.J.A.C.7:27-22.16(e)]

Recordkeeping by stack test results every 5years , based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Submit a sapproved renewal of stack test pTechnical Trenton, Nto the expipermit.Within 30 permittee 609-530-4acceptable must be su(per PSD ptest pursuatest results licensed pindustrial For stack tmonths froOperating must be surenewal apprior to exTest resultneeded) [N[N.J.A.C. 

Page 27 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 STACK TESTING REQUIREMENTS:

Conduct stack tests on each municipal solidwaste incinerator to demonstrate compliancewith the 1-hour CO and HF emission limits.Testing must be conducted at worst-casepermitted operating conditions with regardto meeting the applicable emissionstandards, but without creating an unsafecondition. From BOP080004. [N.J.A.C.7:27-22.16(a)] and [N.J.A.C. 7:27-22.16(e)]

Monitored by stack emission testing onceinitially and every 5 years, based on any 60minute period by methods approved by theDepartment and EPA, based on thepreconstruction permit. Three stack testsmust be conducted successively on one unit.[N.J.A.C. 7:27-22.16(e)]

Recordkeeping by stack test results onceinitially and every 5 years , based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]

Submit a sapproved performed Operating approved pthe permit609-530-4acceptable one year ppermit. Stto BTS wiafter perfoN.J.A.C. 7must be ceprofessionhygienist.For stack tmonths froOperating must be surenewal apprior to exTest resultBTU, ppm 7:27-22.18

9 SO2 <= 2,000 ppmv from each emission

point, at standard conditions. This emissionlimit applies at all times, including startupand shutdown. [N.J.A.C. 7:27- 7.2(b)1]

None. None. None.

10 SO2 <= 900 lb/hr (in any 60-minute period)

from each emission point, based on thecalculation procedure at N.J.A.C.7:27-7.2(r). Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 7.2(b)2]

None. None. None.

11 SO2 <= 1,800 lb/hr from each emission

point, at any instant, based on thecalculation procedure at N.J.A.C.7:27-7.2(r). Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 7.2(b)2]

None. None. None.

Page 28 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

12 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 10 mg/ft^3 atstandard conditions from each emissionpoint. Emission limit applies at all times,including startup and shutdown. [N.J.A.C.7:27- 7.2(g)1]

None. None. None.

13 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 200 lb/hr in any60-minute period from each emission point,based on the calculation procedure atN.J.A.C. 7:27-7.2(r). Emission limit appliesat all times, including startup and shutdown.[N.J.A.C. 7:27- 7.2(g)2]

None. None. None.

14 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 400 lb/hr at anyinstant from each emission point, based onthe calculation procedure at N.J.A.C.7:27-7.2(r). Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 7.2(g)2]

None. None. None.

15 SO2 <= 1.5 lb/MMBTU. Maximum

emission rate from each incinerator, basedon Table 2 at N.J.A.C. 7:27-10.2(c) and thelocation of the facility (Warren County,Zone Two). Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27-10.2(c)]

None. None. None.

16 SO2 <= 1.2 lb/MMBTU gross heat input

determined as a 30-day rolling average foreach incinerator. Emission limit applies atall times, including startup and shutdown.[N.J.A.C. 7:27-10.3(c)4]

None. None. None.

17 Particulate Emissions <= 0.1 gr/dscf @ 12%

CO2 (including ash, excluding thecontribution of auxiliary fuel) for eachincinerator. Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27-11.3(a)4]

Particulate Emissions: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs during operation, using theNew Jersey test method for incinerators. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Other: See stack testing requirement atbeginning of U1, OS Summary (OS0.)[N.J.A.C. 7:27-22.16(o)].

None.

18 Opacity <= 1 Ringlemann Smoke Chart for

each incinerator. [N.J.A.C. 7:27-11.3(b)2ii]

None. None. None.

Page 29 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

19 The provisions of 7:27-11.3(b)(2) shall not

apply to: 1. Smoke emitted during thebuilding of a new fire, the shade orappearance of which is not greater thanNumber 2 of the Ringelmann smoke chartfor a period of three consecutive minutes;or ii. Emissions of such opacity within astack or chimney to a degree greater than theemission designated as Number 2 of theRingelmann smoke chart for a period notgreater than three consecutive minutes.[N.J.A.C. 7:27-11.3(b)3]

None. None. None.

20 No person shall cause, suffer, allow or

permit the emission of particles of unburnedwaste or ash from any common incineratoror from any special incinerator which areindividually large enough to be visible whilesuspended in the atmosphere. This appliesat all times, including startup and shutdown.[N.J.A.C. 7:27-11.3(c)]

None. None. None.

21 Odor: No person shall construct, install, use

or cause to be used any common incineratoror any special incinerator which will resultin odors being detectable by sense of smellin any area of human use or occupancy.This applies at all times, including startupand shutdown. [N.J.A.C. 7:27-11.3(d)]

None. None. None.

22 Any person responsible for the use of an

incinerator shall when ordered by theDepartment, provide the facilities andnecessary equipment for determining thedensity of smoke being discharged from astack or chimney and shall conduct suchsmoke tests using methods approved by theDepartment. [N.J.A.C. 7:27-11.3(e)1]

None. Other: All smoke test data shall be recorded

in a permanent log at such time intervals asspecified by the Department. Data shall bemaintained for a period of not less than oneyear and shall be available for review by theDepartment.[N.J.A.C. 7:27-11.3(e)1].

None.

Page 30 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

23 Any person responsible for the use of an

existing incinerator shall upon request of theDepartment provide such sampling facilitiesand testing facilities exclusive ofinstruments and sensing devices as may benecessary for the Department to determinethe nature and quantity of emissions fromsuch incinerators and shall during suchtesting operate the incinerator at a chargingrate of waste no less than the designedcapacity of the incinerator using materialsrepresentative of the types of wastesnormally burned. [N.J.A.C. 7:27-11.3(e)2]

None. None. None.

24 No person shall use or cause to be used any

incinerator unless all componentsconnected, or attached to, or serving theincinerator, including control apparatus arefunctioning properly and are in use, inaccordance with this permit. [N.J.A.C.7:27-11.5(c)]

None. None. None.

25 VOC (Total) <= 3.5 lb/hr. Maximum

uncontrolled emission rate from eachmunicipal solid waste combuster, based onthe Table 16A at N.J.A.C. 16.16. This limitapplies at all times, including startup andshutdown. [N.J.A.C. 7:27-16.16(d)]

None. None. None.

26 Opacity <= 10 % average during any

6-minute block period for each incineratorwhile firing fuel oil and/or MSW. Thisopacity limit from the preconstructionpermit applies at all times, including startupand shutdown. [N.J.A.C. 7:27-22.16(e)]

Opacity: Monitored by continuous opacitymonitor continuously, based on 6 minuteblocks , using USEPA referenced Method 9,or an equivalent method approved byUSEPA and the Department. [N.J.A.C.7:27-22.16(e)]

Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]

None.

27 Maximum Gross Heat Input <= 89

MMBTU/hr (HHV) of auxiliary fuel to eachof the municipal waste fired boilers, basedon the application for modification of theoperating permit. [N.J.A.C. 7:27-22.16(a)]

Other: Maximum rated heatcapacity.[N.J.A.C. 7:27-22.16(o)].

None. None.

28 The auxiliary fuel is limited to No. 2 Fuel

Oil. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 31 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

29 Records shall be kept for each unit to

accurately record the quantity of refusecharged hourly to each furnace. [N.J.A.C.7:27-22.16(a)] and [N.J.A.C. 7:27-22.16(e)]

Monitored by waste feed/charge ratemonitoring (solid) each hour duringoperation. [N.J.A.C. 7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storage each hourduring operation based on thepreconstruction (PSD) permit. Also, recordthe daily total steam production of eachincinerator and the hours of operation dailyin logbook or readily available computerfiles. [N.J.A.C. 7:27-22.16(o)]

None.

30 Maximum Steam Production Limit <=

255,600 lbs of steam per boiler in anydiscrete four - hour block period or <= to110 percent of the maximum demonstratedmunicipal waste combustor unit (hourlysteam) load as defined in 40 CFR 60.51b,whichever is more stringent based onapplication for significant modificationBOP050003. [N.J.A.C. 7:27-22.16(a)]

Monitored by integrated steam flow monitorcontinuously over a distinct four hour blockperiod. This monitor must meet therequirements at 40 CFR 60.58(i)(6).[N.J.A.C. 7:27-22.16(o)]

Recordkeeping by strip chart or dataacquisition (DAS) system continuously.[N.J.A.C. 7:27-22.16(o)]

None.

31 TSP <= 23.7 tons/yr is the combined total

maximum emission limit for all units, basedon the PSD permit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

32 PM-10 (Total) <= 12.09 tons/yr is the

combined total maximum emission limit forall units, from modification BOP070001.[N.J.A.C. 7:27-22.16(o)]

None. None. Other (pro

approved submit an within 30 Services hresults. [N

33 VOC (Total) <= 14.8 tons/yr is the

combined total maximum emission limit forall units, based on the operating permitapplication. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

34 CO <= 306.6 tons/yr is the combined total

maximum emission limit for all units, basedon the PSD permit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

35 SO2 <= 175.2 tons/yr is the combined total

maximum emission limit for all units, basedon the PSD permit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

36 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 5 tons/yr is thecombined total maximum emission limit forall units, based on the application for aminor modification to the operating permitBOP050003. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 32 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

37 HAPs (Total) <= 108 tons/yr is the

combined total maximum emission limit forall units, based on the PSD permit and theoperating permit application. [N.J.A.C.7:27-22.16(a)] and. [N.J.A.C.7:27-22.16(e)]

None. None. None.

38 HCl Emissions <= 104 tons/yr is the

combined total maximum emission limit forall units for this HAP, based on operatingpermit application. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

39 Hydrogen fluoride <= 0.876 tons/yr is the

combined total maximum emission limit forall units for this HAP, based on the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

40 Mercury Emissions <= 81.4 lb/yr is the

combined total maximum emission limit forall units for this HAP, based on 28ug/DSCM for each unit. [N.J.A.C.7:27-22.16(a)]

None. None. None.

41 Arsenic Emissions <= 0.0175 tons/yr is the

combined total maximum emission limit forall units for this HAP, based on the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

42 Beryllium Emissions <= 0.0035 tons/yr is

the combined total maximum emission limitfor all units for this HAP, based on the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

43 Cadmium Emissions <= 0.263 tons/yr is the

combined total maximum emission limit forall units for this HAP, based on the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

44 Chromium Emissions <= 0.0876 tons/yr is

the combined total maximum emission limitfor all units for this HAP, based on the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

45 Lead Emissions <= 2.19 tons/yr is the

combined total maximum emission limit forall units for this HAP, based on the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

46 Nickel Emissions <= 0.035 tons/yr is the

combined total maximum emission limit forall units for this HAP, based on the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 33 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

47 TCDD Emissions (2,3,7,8-) <= 0.00000876

tons/yr is the combined total maximumemission limit for all units for this HAP,based on the PSD permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

48 Polycyclic aromatic hydrocarbons (PAH) <=

0.0368 tons/yr is the combined totalmaximum emission limit for all units for thisHAP, based on the PSD permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

49 The facility shall install and operate a NOx

reduction control device (SNCR) to achievecompliance with NOx emission rates limitedby federal regulations at 40 CFR 62 SubpartFFF. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

50 NOx (Total) <= 298 tons/yr is the combined

total maximum emission limit for both units,based on the PSD permit and on 40 CFR 62,Subpart FFF. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

51 Ammonia <= 27.6 tons/yr is the combined

total maximum emission limit for both units,based on the application for the MinorModification of the Operating Permit.[N.J.A.C. 7:27-22.23]

Ammonia: Monitored by calculationsquarterly: once per quarter; quarters shallbegin on January 1, April 1, July 1, andOctober 1 of each year. [N.J.A.C.7:27-22.16(o)]

Ammonia: Recordkeeping by dataacquisition system (DAS) / electronic datastorage at the approved frequency(Quarterly), or by manual logging in alogbook, or other method acceptable to theDepartment. [N.J.A.C. 7:27-22.16(o)]

None.

52 Temperature at Reagent Injection Point >=

1,600 and Temperature at Reagent InjectionPoint <= 1,950 degrees F. [N.J.A.C.7:27-22.16(a)]

Temperature at Reagent Injection Point:Monitored by documentation ofconstruction once initially (based onengineering design). [N.J.A.C.7:27-22.16(a)]

Other: Retain documentation of constructionin permanent file.[N.J.A.C. 7:27-22.16(a)].

None.

53 NOx (Total): The permittee shall conduct

optimization tests (once initially) todetermine both the performance of theSNCR system and the optimized ureainjection rate versus NOx removalefficiency. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 34 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

54 Monitoring, Recording and Recordkeeping -

For each unit, continuous emission andopacity monitors and recorders shall be inoperation and accurately measure andrecord: the opacity of the stack gas andemission concentrations of carbonmonoxide, oxygen (at the stack andeconomizer exit), nitrogen oxides, hydrogenchloride (when required) and sulfur dioxide(inlet and outlet of acid gas controlequipment) and provide representative data,in accordance with the procedures submittedto and approved by the Department.Monitors must comply with EPAperformance and siting specifications,pursuant to 40 CFR Part 60, Appendix B.All continuous emission monitors, exceptthe opacity monitor, must comply with thequality assurance requirements outlines in40 CFR Part 60, Appendix F. [N.J.A.C.7:27-22.16(e)]

None. Recordkeeping by strip chart or data

acquisition (DAS) system continuously , ifthe stack test results exceeded the applicablerequirement. All continuous monitoringrecords shall then be maintained in a manneracceptable to the Regional EnforcementOfficer. [N.J.A.C. 7:27-22.16(e)]

None.

55 Each unit shall be equipped with continuous

monitors and recorders which shall beoperated to accurately record the:a. temperature at the baghouse inlet, andb. activated carbon volumetric feeder setting. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 35 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

56 The following shall be recorded in a

permanently bound log book or readilyaccessible computer memories:a. specific times of operation of each furnace;b. specific times of operation of the auxiliaryburners;c. removed in BOP080002.d. equipment malfunctions included in thispermit;e. exceedances of emission standardsdetermined by continuous monitoring;f. quantity of refuse charged hourly to eachfurnace The basis shall be steamproduction over a distinct four hour blockperiod and total steam for each calendarday), andg. amount of auxiliary fuel burned in theauxiliary burners, on a daily basis. [N.J.A.C. 7:27-22.16(a)] and [N.J.A.C.7:27-22.16(a)]

Monitored by waste feed/charge ratemonitoring (solid) each hour duringoperation The quantity of refuse chargedhourly to each furnace shall be calculated.Totalized steam production and MSWreceived (per truck scales) shall be recordeddaily and summed to determine the totalMSW received each month. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storage each monthduring operation or by manual logging in alogbook. [N.J.A.C. 7:27-22.16(e)]

None.

57 Start-up/ Shutdown Allowances - To obtain

start-up/shutdown allowances, the facilitymust:a. Maintain the equipment;b. Operate the equipment properly;c. Take steps to minimize emissions duringstart-up/shutdown/warm-up, and equipmentmaintenance periods;d. Identify and take steps to preventequipment malfunctions from occurring inthe future. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 36 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

58 Start-up and Shutdown Allowances -

i. The start-up period commences when theaffected incinerator begins the combustionof MSW, including continuous,semicontinuous, or batch feeding ofmunicipal solid waste (MSW) to thefurnace. The start-up period does notinclude any warm-up period when theaffected unit is combusting only auxiliaryfuel (fuel oil) and no MSW is beingcombusted. The duration of exemption fromemission limits during the start-up periodshall not exceed 3 hours.ii. The shutdown period commences whenthe feeding of MSW to the hopper isterminated as a result of a scheduledshutdown or malfunction. The shutdownperiod ends when MSW is no longercombusting on the grate. The duration ofexemption from emission limits during theshutdown period shall not exceed 3 hours.Malfunctions resulting in a shutdown of aunit shall be considered a shutdown, unlessoperation of the affected unit is resumedbefore the shutdown is completed.Resuming the operation of a unit before ashutdown is completed, if the shutdown isthe result of a malfunction, shall beconsidered a malfunction. [N.J.A.C. 7:27-22.16(e)]

Monitored by waste feed/charge ratemonitoring (solid) upon occurrence of event,based on an instantaneous determination.The occurrences of startups and shutdownsshall be monitored. [N.J.A.C. 7:27-22.16(e)]

Recordkeeping by production records uponoccurrence of event. The occurrences ofstartups and shutdowns shall be recorded.These records shall include the times whenthe startup started and ended and the timeswhen the shutdown started and ended. Allshutdowns due to a malfunction shall berecorded. These startup, shutdown andmalfunctions records shall be made readilyavailable via computer files or on hard copy.[N.J.A.C. 7:27-22.16(o)]

None.

Page 37 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

59 Carbon monoxide: Start-up and Shutdown

Allowances - The CO emission limitsspecified in this permit (see U1 OS1, OS2)shall not apply during periods, includingwarm-up periods, when no waste is burnedand fossil fuel is being combusted. Onlyauxiliary fuel (fuel oil) shall be combustedduring warm-up periods and no MSW shallbe combusted. The warm-up period beginsupon initiation of auxiliary fuel (fuel oil)combusted in the furnace and ends uponintroduction of MSW to the furnace. Theduration of exemption from CO emissionlimits shall not exceed 10 consecutive hoursper warm-up period. Operation of an oilburner for the purpose of refractory curingor other maintenance requirement shall notbe considered warmup. [N.J.A.C.7:27-22.16(e)]

Carbon monoxide: Monitored by wastefeed/charge rate monitoring (solid) uponoccurrence of event, based on aninstantaneous determination. Theoccurrences of startups and shutdowns shallbe monitored. [N.J.A.C. 7:27-22.16(e)]

Carbon monoxide: Recordkeeping byproduction records upon occurrence ofevent. The occurrences of startups andshutdowns shall be recorded. These recordsshall include the times when the startupstarted and ended and the times when theshutdown started and ended. All shutdownsdue to a malfunction shall be recorded.These startup, shutdown and malfunctionsrecords shall be made readily available viacomputer files or on hard copy. [N.J.A.C.7:27-22.16(o)]

None.

60 Requirements for Cessation of Waste

Charging:a. During periods of scrubbermalfunction, cessation of waste charging tothe affected furnace is required if annualscrubber downtime will exceed 2% ofannual operating time. (See otherrequirements at OS1 and OS2.)b. During a period of baghousemalfunction that requires a bypass of thebaghouse, cessation of waste charging to theaffected furnace is required before thebaghouse is bypassed.c. deleted in BOP080002.d. deleted in BOP080002.e. The charging of waste to the affectedfurnace shall cease when flue gas opacityexceeds 10% at any time, as measured bythe opacity monitor.f. The preceding conditions for cessationof waste charging do not supercede thestart-up and shutdown conditions specifiedin the conditions of this permit. [N.J.A.C.7:27-22.16(e)]

None. Other: Record each malfunction and its start

and end times. These malfunctions recordsshall be made readily available via computerfiles or on hard copy.[N.J.A.C.7:27-22.16(o)].

None.

Page 38 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

61 The permittee shall submit an Excess

Emissions and Monitoring SystemsPerformance Report to the Department forreview and approval.The permittee shall submit as an addendumto each semiannual Excess Emissions andMonitoring System Performance Report(EEMPR): (i) a CMS Excursion Sheet in theform approved by the Chief, NorthernRegional Office; and (ii) a summary, bypollutant, of the cumulative excursion hoursduring each 6-month period. This summaryshall include the total excursion hoursduring the 6-month period, the total of thesehours applied toward the annual excursionlimits specified in this permit, and therunning total excursion hours for the presentcalendar year. [N.J.A.C. 7:27-22.16(e)]

None. None. Submit an 

Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal to thapproval. 

62 Particulates Control Efficiency >= 99 %.

Minimum control efficiency for eachbaghouse (CD2 and CD5) from the PSDpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

63 The permittee shall conduct bag cleaning,

maintenance and replacement in eachbaghouse on a schedule necessary to achievethe required particulate removal efficiencyas specified by the manufacturer. [N.J.A.C.7:27-22.16(a)]

Monitored by visual determination annuallyduring the annual boiler outage and at othertimes necessary to achieve the requiredparticulate matter removal efficiency basedon baghouse differential pressure andCOMS data to determine the condition ofeach bag. From BOP080004. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by manual logging ofparameter upon occurrence of event in a logbook or by electronic data storage in readilyaccessible computer memory. The permitteeshall record each instance of bagmaintenance and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

64 MAINTENANCE OF THE EMISSION

CONTROLSThe facility shall maintain on-site anoperation, inspection and maintenance planfor the air pollution control and monitoringequipment and make it available to theDepartment. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

65 The facility shall not accept any beryllium

containing waste as defined at 40 CFR61.31(g). [N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 39 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

66 Mercury Emissions: The carbon injection

mercury control system on each MSWincinerator shall be operated to maintain theoptimized carbon feed rate based on an8-hour block average any time MSW iscombusted. From BOP080004. [N.J.A.C.7:27-22.16(a)]

None. None. None.

67 The gravimetric carbon feeder for each unit

shall monitor and record the carbon feedrate to confirm continuous compliance withthe optimized carbon feed rate based on an8-hour block average. From BOP08001.The gravimetric feed rate, vs. actual carbondelivery rate, shall be calibrated by actualmeasurements (collecting and weighing thecarbon delivered by the feeder) at least twicea year for each unit. Temporary diversionsof carbon during the calibrations for up toone hour for each calibration event do notapply to the requirement above (to maintainthe optimized feed rate any time MSW iscombusted.). [N.J.A.C. 7:27-22.16(a)]

Monitored by gravimetric monitoring daily.[N.J.A.C. 7:27-22.16(e)]

Recordkeeping by strip chart, dataacquisition (DAS) system, or other methodapproved by BTS daily in readily availablecomputer files or by manual logging in alogbook. [N.J.A.C. 7:27-22.16(o)]

None.

68 The activated carbon injection system for

mercury control shall be designed to reducea minimum of 80% of the emissions ofmercury, and be capable of reducing theconcentration of mercury in the flue gasfrom the MSW incinerator from 140ug/dscm (corrected to seven percent oxygen)to 28 ug/dscm (corrected to seven percentoxygen) or less after the control apparatus.[N.J.A.C. 7:27-27.4(a)]

None. None. None.

Page 40 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

69 The owner or operator of any MSW

incinerator that has a reagent based mercuryemision control system shall operate eachMSW incinerator at, or above, the optimizedreagent feed rate established in theoptimization tests and approved by theDepartment.The optimized carbon feed rate is 9.0pounds per hour based on an 8-hour blockaverage unless the Department approves arevised rate in subsequent optimizationtesting. From BOP080004.[N.J.A.C. 7:27-22.16(a)] and [N.J.A.C.7:27-27.4(k)]

Other: The total quantity of carbon actuallyused by the facility and by each unit shall bemonitored continuously, determined frombulk deliveries and storage silo inventorydifference.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter quarterly: once per quarter;quarters shall begin on January 1, April 1,July 1, and October 1 of each year.The following quarterly records must bemaintained:a. All bulk carbon deliveries during thequarter and storage silo inventory at the endof each calendar quarter;b. Total hours that waste is fed to eachunit, and total combined hours that waste isfed to both units;c. Required optimized quantity of carboncombined quarterly for both units calculatedas follows: Q =R x (Unit 1 hrs + Unit 2 hrs),where Q is the minimum required quarterlycarbon usage for the facility; R is the approved minimum hourlycarbon feed for each unit and Units 1-2 hrs is the total hours wasteis fed to each unit during thequarter.determined above;d. Total quantity of carbon actually used,determined from bulk deliveries and storagesilo inventory difference. [N.J.A.C.7:27-22.16(o)]

None.

70 Any owner or operator of a MSW

incinerator that submits to the Department areport of compliance testing, including alltest runs for a MSW incinerator shall havesuch report reviewed prior to submissionand certified by a registered professionalengineer or an industrial hygenist certifiedby the American Board of IndustrialHygiene. [N.J.A.C. 7:27-27.9(d)]

None. None. None.

71 Any owner or operator of a MSW

incinerator who submits to the Department areport of compliance testing, including alltest runs, shall certify that report. [N.J.A.C.7:27-27.9(f)]

None. None. None.

Page 41 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

72 The permittee shall calculate and maintain a

record of the annual emissions for allapplicable criteria pollutants, in tons peryear on a calendar year basis, for a period of5 years following resumption of regularoperations after approval of thismodification. If the actual emissions in thenext 5 years differ from the projectedpost-change emissions that were calculatedand submitted to US EPA on September 30,2005, the permittee must report the increaseto the Department and EPA within 60 daysafter the end of the year in accordance with40 CFR 52.21(r)6iii , from modificationBOP050003. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem each month during operation.Maintain emission and operating records forall applicable criteria pollutants. [N.J.A.C.7:27-22.16(o)]

Submit a rSubmit a rprojected freport sha (a) The number of  (b) The pursuant t52.21; and (c) Any or operato(e.g., an exdiffer from [40 CFR 5

73 See GR1for applicable requirements from

NSPS 40 CFR 60 Subpart A, GeneralProvisions. [40 CFR 60]

None. None. None.

74 OPERATOR TRAINING AND

CERTIFICATION:Each chief facility operator and shiftsupervisor must obtain and maintain acurrent provisional operator certificationfrom either the American Society ofMechanical Engineers (QRO-1-1994) or aState certification program. Compliance isrequired by November 6, 2006, or sixmonths after the operator is transferred to oris hired by the facility. [40 CFR 60.59b(d)]& [40 CFR 62.14104]

None. Other: The facility shall maintain the

following records for a period of five years:Records showing the names of the municipalwaste combustor chief facility operator, shiftsupervisors and control room operators whohave been fully certified or who areprovisionally certified by the AmericanSociety of Mechanical Engineers (ASME)or an equivalent State approved certificationprogram, including the dates of initial andrenewal and renewal certifications anddocumentation of current certification.Records showing the names of the municipalwaste combustor chief facility operator, shiftsupervisors and control room operators whohave completed the EPA municipal wastecombustor operator training course or aState approved equivalent course includingdocumentation of training completion.[40CFR 62.14104].

None.

Page 42 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

75 OPERATOR TRAINING AND

CERTIFICATION:Each chief facility operator and shiftsupervisor must complete full certificationor must have scheduled a full certificationexam with either the American Society ofMechanical Engineers (QRO-1-1994) or aState certification program. Each operatoror supervisor must be either certified orscheduled to take the certification exam byNovember 6, 2006, or six months after theoperator is transferred to or is hired by thefacility. [40 CFR 60.59b(d)] & [40 CFR62.14105(b)]

None. None. None.

76 The facility must not be operated unless one

of the following persons is on duty:- a fully certified chief facility operator;- a provisionally certified chief facilityoperator who is scheduled to take the fullcertification exam no later than 12 monthsafter November 6, 2005 ;- a fully certified shift supervisor; or- a provisionally certified shift supervisorwho is scheduled to take the fullcertification exam no later than November 6,2006. If one of the persons listed above mustleave the facility during their operating shift,a provisionally certified control roomoperator who is onsite may fulfill thisrequirement. [40 CFR 60.59b(d)] & [40CFR 62.14105(c)]

None. None. None.

77 A provisionally certified operator who is

newly promoted or recently transferred to ashift supervisor position or a chief facilityoperator position at the municipal wastecombustion unit may perform the duties ofthe certified chief facility operator orcertified shift supervisor without notice to,or approval by, the Administrator for up tosix months before taking the ASME QROcertification exam. [40 CFR 60.54(b)(c)(3)]

None. None. None.

Page 43 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

78 Each chief facility operator, shift supervisor

and control room operator at an affectedfacility must complete the EPA municipalwaste combustor operator training course orthe State municipal waste operator trainingcourse, except for chief facility operators,shift supervisors, and control room operatorswho have obtained full certification from theASME on or before November 6, 2005. Theemployees must complete the operatortraining course by November 6, 2006 or bythe date before an employee assumesoperating responsibilities.[40 CFR 60.59b(d)] & [40 CFR62.14105(d)]

None. None. None.

79 As further clarification to the preceding

"Stand-in" Provisions, a provisionallycertified control room operator can stand-infor a certified plant operator or shiftsupervisor when they are off site for periodsofa) up to twelve (12) hours withoutnotification to EPA, orb) from twelve (12) hours to two (2) weeksalso without notification to EPA (However,see recordkeeping requirement for this AR),orc) lastly, for more than two weeks againwithout notice to EPA in advance(However, see submittal requirement for thisAR). [40 CFR 62.14105(c)]

None. Other: The facility must record the periods

where the certified individuals are offsite formore than 12 hours and include thisinformation in the annual report specifiedat[40 CFR 62.14105].

Submit noevent. Whoff site for facility musubmit a ssummary tweeks follCFR 62.14

Page 44 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

80 OPERATING MANUAL:

By November 6, 2006, the facility mustdevelop and update on a yearly basis amanual that must, at a minimum, address thefollowing elements of municipal wastecombustor unit operation:- A summary of the applicable standardsof 40 CFR 62 Subpart FFF;- A description of basic combustiontheory applicable to a MWC unit;- Procedures for receiving, handling andfeeding MSW;- Procedures for MWC unit startup,shutdown and malfunction;- Procedures for maintaining propercombustion air supply levels;- Procedures for operating the MWC unitwithin the standards established under 40CFR 62 Subpart FFF;- Procedures for responding to periodicupset or off-specification conditions;- Procedures for minimizing particulatematter carryover;- Procedures for handling ash;- Procedures for monitoring MWC unitemissions;- Reporting and Recordkeepingprocedures. [40 CFR 60.59b(d)] & [40CFR 62.14105]

None. Other: The operating manual and records of

training must be available for inspection byUSEPA or the Department upon request.[40 CFR 60.59b(d)] &[40 CFR 62.14105].

None.

Page 45 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

81 TRAINING - OPERATING MANUAL

REVIEW:By November 6, 2006, the facility mustestablish a training program to review theoperating manual according to the schedulespecified below with each person who hasresponsibilities affecting the operation of thefacility, including but not limited to, chieffacility operators, shift supervisors, controlroom operators, ash handlers, maintenancepersonnel and crane/load handlers.Each person undergoing the operatingmanual review training shall do so no laterthan the dates specified below, whichever islater:- The date prior to the day the personassumes responsibilities affecting MWC unitoperation; or- The date 12 months after November 6,2005; or- Annually following the initial review.ACCESS TO OPERATING MANUAL:The operating manual must be kept in alocation readily accessible to each personrequired to undergo training. [40 CFR60.59b(d)] & [40 CFR 62.14105]

None. Other: The facility shall maintain records

showing the names of persons who havecompleted a review of the operating manualincluding the date of initial review andsubsequent annual reviews. [40 CFR60.59b(d)] &[40 CFR 62.14105].

None.

Page 46 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

82 SEMI-ANNUAL REPORT:

The facility shall submit a semi-annualreport if any emission limit or parameterdoes not meet the requirements specified inthis Operating Permit. This report shallinclude the following:a) Recorded data above the applicable limitsfor the average sulfur dioxide, nitrogenoxides, carbon monoxide, municipal wastecombustor unit load level, particulate mattercontrol device inlet temperature or opacitydata, - Reasons for such exceedances and - A description of the corrective actiontaken.b) If the results of the annual stack testsshow emissions above the limits specified inthis permit, a copy of the annual test reportdocumenting the emissions level and thecorrective action taken if the test reportindicates any particulate matter, opacity,cadmium, lead, mercury, dioxins/furans,hydrogen chloride or fugitive ash emissionlevels that were above applicable pollutantlimits.c) Identification of the calendar dates whenthe carbon feed rate was below the requiredfeed rate with reasons for such occurrencesand a description of corrective action takenand - Documentation of each quarter whentotal carbon usage at the municipal wastecombustion plant is less than the totalrequired quarterly usage of carbon.[40 CFR 60.59b(h)] & [40 CFR62.14109(a)]

None. Other: All semi-annual reports must be

maintained on site as a paper copy for aminimum of 5 years. [40 CFR 60.59b(h)]&[40 CFR 62.14109].

Submit a r31 and Julthe first hasubmitted The report calendar yFebruary 1 60.59b(h)] 

Page 47 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

83 ANNUAL REPORT:

An annual report shall be submitted, whichincludes the following:- A list of the particulate matter, opacity,cadmium, lead, mercury, dioxins/furans,hydrogen chloride and fugitive ash emissionlevels achieved during performance tests- A list of the highest emission levelrecorded for sulfur dioxide, nitrogendioxides, carbon monoxide, municipal wastecombustor load level and particulate mattercontrol device inlet temperature.- A list of the highest opacity level measured- The total number of days that the minimumnumber of hours of data for sulfur dioxide,nitrogen oxides, carbon monoxide,municipal waste combustor unit load level,particulate matter control device inlettemperature and carbon feed rate were notobtained for the calculation of the averageemissions concentrations or parameters.- The total number of hours that data forsulfur dioxide, nitrogen oxides, carbonmonoxide, municipal waste combustor unitload, particulate matter control device inlettemperature and carbon feed rate wereexcluded from the calculation of averageemissions concentrations or parameters. [40CFR 60.59b(g)] & [40 CFR 62.14109(a)]

None. Other: All annual reports must be

maintained on site as a paper copy for aminimum of 5 years. [40 CFR 60.59b(g)]&[40 CFR 62.14109].

Submit a rthe first fuby FebruaCFR 60.59

84 ANNUAL REPORT (continued):

-The facility shall also provide a summaryreport with the same data specified in theannual report for the preceding year in orderto provide the Administrator with asummary of the performance of the facilityover a 2 year period. This summary reportshall highlight any emission or parameterlevel that did not achieve the requiredemission or parameter limits.- The facility will also include a notificationof intent to begin reduced dioxin/furanperformance testing schedule as allowed in40 CFR 60.58(g)(5)(iii), i.e. NSPS SubpartEb. [40 CFR 60.59b(g)] & [40 CFR62.14109(a)]

None. Other: All annual reports must be

maintained on site as a paper copy for aminimum of 5 years. [40 CFR 60.59b(g)]&[40 CFR 62.14109].

Submit a rthe first fuby FebruaCFR 60.59

Page 48 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

85 REPORTING/RECORDKEEPING:

Maintain the records for a period of at leastfive years in accordance with 40 CFR60.59b(j). [40 CFR 62.14109(a)]

None. Other: Maintain records on paper copy or a

computer readable format for a period of atleast 5 years from the date of record. [40CFR 60.59b(j)] &[40 CFR 62.14109].

None.

Page 49 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

86 The standards under 40 CFR 62, Subpart

FFF apply at all times except during periodsof startup, shutdown, or malfunction.Duration of startup, shutdown, ormalfunction periods are limited to 3 hoursper occurrence. During periods of startup,shutdown, or malfunction, monitoring datashall be dismissed or excluded formcompliance calculations, but shall berecorded in accordance with the provisionsof 40 CFR 60.59b(d)](7). For the purposeof compliance with the carbon monoxideemission limits in 40CFR6053b(a), if a lossof boiling water level control or a loss ofcombustion air control is determined to be amalfunction, the duration of the malfunctionperiod is limited to 15 hours per occurence.During such periods of malfunction,monitoring data shall be dismissed orexcluded from compliance calculations, butshall be recorded and reported in accordancewith the provisions of 40CFR60.59(d)(7).During a loss of boiler water level control orloss of boiler or loss of combustion aircontrol malfunction periodas specified inparagraph(a)(1)(iii) of this section, a diluentcap of 14 percent for oxygen or 5 percent forcarbon dioxide may be used in the emissionscalculations for sulfur dioxide and nitrogenoxides.

None. None. None.

Page 50 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

Page 51 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

 [40 CFR 62.14100]

87 continued. The startup period commences

when the affected facility begins thecontinuous burning of municipal solid wasteand does not include any warmup periodwhen the affected facility is combustingfossil fuel or other nonmunicipal solid wastefuel, and no municipal solid waste is beingfed to the combustor. Continuous burning isthe continuous, semicontinuous, or batchfeeding of municipal solid waste forpurposes of waste disposal, energyproduction, or providing heat to thecombustion system in preparation for wastedisposal or energy production. The use ofmunicipal solid waste solely to providethermal protection of the grate or hearthduring the startup period when municipalsolid waste is not being fed to the grate isnot considered to be continuous burning.[40 CFR 60.59b(a)] & [40 CFR 62.14100]

None. None. None.

88 SO2 RATA Criteria: For sources that

haveactual inlet SO2 emissions less than100 ppmdv, the relative accuracy criteria forinlet SO2, CEMS should be no greater than20% of the mean value of the referencemethod test data in terms ofthe unitsof theemission standard, or 5 ppmvd absolutevalue of the mean difference between thereference method and the CEMS, whicheveris greater. [40 CFR 60.58(e)(12)]

Other: annual RATA[40 CFR 60.58(b)]. Other: RATA results annually.[40 CFR

60.58(b)].

None.

89 CO RATA Criteria: For affected facilities

subject to the 100 ppmdv carbon monoxidestandard, the relative accuracy criterion of 5ppmdv is calculated as the absolute value ofthe mean difference between the referencemethod and the continuous emissionsmonitoring systems. [40 CFR60.58(b)(i)(3)]

Other: Annual RATA[40 CFR 60.58(b)]. Other: RATA results annually.[40 CFR

60.58(b)].

None.

Page 52 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

90 At a minimum, valid continuous emissions

monitoring systems hourly averages shall beobtained for SO2, CO, NOx, baghouse inlettemperature and steam flow for at least 90percent of the operating hourss per calendarquarter and 95 percent of the operatinghours per calendar year that the affectedfacility is combusting municipal solid waste.Effective May 10, 2011, or by the finalcompliance date established in theforthcoming FIP, whichever is sooner. [40CFR 60.58(b)(e)(7)]

Monitored by continuous emissionmonitoring system continuously. [40 CFR60.58]

Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslyand CEMS maintenance/downtime records.[40 CFR 60.58(b)]

None.

91 The owner or operator shall develop a

QA/QC plan for all CEMS/COMS requiredby this permit. This QA/QC plan shallincorporate at a minimum those proceduresoutlined in 40 CFR, Part 60, Appendix Fand/or 40 CFR, Part 75, Appendix B forCEMS and those procedures outlined in 40CFR, Part 60, Appendix B, SpecificationOne and 40 CFR, Part 51, Proposed RM203 for COMS, published DepartmentTechnical Manuals or other proceduresapproved in writing by the Department. TheQA/QC plan shall designate a coordinatorfor the facility who is responsible to ensurethat the QA/QC plan is implemented. TheDepartment reserves the right to require theQA/QC plan to be revised at any time basedon the results of quarterly EEMPR reviews,inspections, audits or any other informationavailable to the Department. All proceduresoutlined in the QA/QC plan shall commenceupon the completion date of the PST. Allredundant CEMS/COMS must undergo theQA/QC procedure. [N.J.A.C. 7:27-22.16(a)]

Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis. [N.J.A.C.7:27-22.16(o)].

Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports. [N.J.A.C. 7:27-22.16(o)].

Submit a rOctober 3preceding begin on JOctober 1data shall reports anQA data mDepartmenthe QA/QC writing to the Bureau 7:27-22.16

Page 53 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U1 Two nominal 274 TPD Municipal Solid Waste Combustors (with Carbon silo) subject to NSPS Eb, 40 CFR 60 

7:27-27

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 9.38 lb/hr.

Maximum emission rate for each incineratorfrom the table at N.J.A.C. 7:27-6.2(a), basedon the Source gas flow of 72,260 ACFM at240 degrees F. Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 6.2(a)]

None. None. None.

2 Particulate Emissions <= 0.015 gr/dscf @

7% O2 in the stack gas of each incineratorexcluding periods of boiler tube cleaning,except during periods of start up andshut-down, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests conductedsuccessively using the approved method.(see beginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Particulate Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

3 Particulate Emissions <= 0.03 gr/dscf @ 7%

O2 in the stack gas of each incineratorincluding periods of boiler tube cleaning,except during periods of start up andshut-down, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Monitored by stackemission testing every 5 years, based on any60 minute period using the approvedmethod. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. [N.J.A.C. 

4 PM-10 (Total) <= 0.1 gr/dscf @ 12% CO2

in each stack flue for each incineratorexcluding the contribution of CO2 from thecombustion of auxiliary fuel, except duringperiods of start up and shut-down, frompreconstruction permit. ( PM shall includesolid and liquid particles, excluding water,collected in the "front half" and "back half"of the stack sampling train). [N.J.A.C.7:27-22.16(e)]

PM-10 (Total): Monitored by stack emissiontesting once initially, based on each of threeDepartment validated stack test runs duringoperation, using the New Jersey test methodfor incinerators. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

PM-10 (Total): Recordkeeping by stack testresults once initially. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

5 Particulate Emissions <= 2.7 lb/hr from each

unit except during periods of start up andshut-down, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests conducted insuccession, using EPA Method 5. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Particulate Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

OS1 89 MM BTU/hr Combustor #1 (E1) burning MSW and/or using No. 2 Fuel Oil with control by scrubber, car

baghouse and SNCR

Page 54 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 PM-10 (Total) <= 1.38 lb/hr , from

modification BOP070001. [N.J.A.C.7:27-22.16(a)]

PM-10 (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults prior to permit renewal (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

7 SO2 <= 50 ppmvd @ 7% O2 average

concentration in the stack gas of each unit ,as determined by continuous monitoring.When Oxygen is > 14 %, then raw SO2shall not be greater than 25 ppm. The 50 ppmdv @ 7% oxygen concentrationlimit shall not apply to a unit if the average3 hr concentration of SO2 in the stack gasfrom the unit is less than 20% of the averagethree-hour concentration at the inlet of theacid gas control scrubber as determined bycontinuous emission monitoring.The average 3-hour concentration of SO2 inthe stack gas shall never exceed 100 ppmvdon a dry basis corrected to 7% oxygen (drybasis), from preconstruction permit.The emission limitation applies at all timesexcept during start-up and shutdown.The emission limitation shall not applyduring periods of scrubber downtimebecause of malfunctions. The annualdowntime of each scrubbing system is to bethe shortest achievable and not exceed 2percent of the annual operating time of theassociated furnace. [N.J.A.C. 7:27-22.16(e)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average , starting and ending on thehour (from preconstruction permit.)Valid Data Capture Requirement: in orderfor a compliance averaging period to bevalid, it must be calculated based on aminimum of 65% valid data. (i.e. 2 hours ofdata would be required to calculate a valid3-hour rolling average.) From modificationBOP050003. [N.J.A.C. 7:27-22.16(a)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]

None.

8 SO2 <= 20 lb/hr from each unit except

during periods of start up and shut-down,from preconstruction permit. [N.J.A.C.7:27-22.16(e)]

SO2: Monitored by stack emission testingevery 5 years, based on the average of threetests (conducted successively ). (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

SO2: Recordkeeping by stack test resultsevery 5 years. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

Page 55 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 HCl Emissions <= 50 ppmvd @ 7% O2 in

the stack gas of each unit for any one hourperiod except for any 1-hour period duringwhich the average concentration of HCl(ppmv) in the stack gas is less than or equalto 10% of the average concentration of HCl(ppmv) at the inlet to the acid gas controlequipment except during periods of start upand shut-down, from preconstruction permit.Continuous emission monitoring of HCl todetermine compliance with this emissionlimit is required unless it is shown thatcontrol of SO2 to below 50 ppmdv alsocontrols HCl to below the 50 ppmv level.Continuous emission monitoring is requiredif annual tests show that the 50 ppmv HCllimit contained in the above permitrequirement is exceeded. [N.J.A.C.7:27-22.16(e)]

HCl Emissions: Monitored by stackemission testing annually, based on any 60minute period (see beginning of U1, OS0).Three 1-hour tests shall be conductedsimultaneously upstream and downstream ofthe acid gas control equipment. Testing maybe conducted on one unit. [N.J.A.C.7:27-22.16(e)]

HCl Emissions: Recordkeeping by stack testresults annually (see beginning of U1,OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. 

10 Hydrogen chloride <= 11.9 lb/hr from each

unit, from operating permit application,except during periods of start-up andshutdown. [N.J.A.C. 7:27-22.16(a)]

Hydrogen chloride: Monitored by stackemission testing annually, based on any 60minute period. (see beginning of U1, OS0).Testing may be conducted on one unit.[N.J.A.C. 7:27-22.16(e)]

Hydrogen chloride: Recordkeeping by stacktest results annually. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

11 Hydrogen fluoride <= 0.1 lb/hr from each

unit from preconstruction permit, exceptduring periods of start-up and shutdown.[N.J.A.C. 7:27-22.16(e)]

Hydrogen fluoride: Monitored by stackemission testing every 5 years, based on any60 minute period. (see beginning of U1,OS0). Testing may be conducted on oneunit. [N.J.A.C. 7:27-22.16(e)]

Hydrogen fluoride: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

12 Carbon monoxide <= 35 lb/hr from each

unit except during periods of start-up andshutdown, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Carbon monoxide: Monitored by stackemission testing every 5 years, based on any60 minute period. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Carbon monoxide: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

13 Carbon monoxide <= 400 ppmvd @ 7% O2

is the limit on the average concentration ofCO in the flue gas of each unit during anyblock 1-hour period beginning and endingon the hour, except during periods ofstart-up and shutdown, from thepreconstruction permit. When Oxygen is >14 %, then raw CO shall not be greater than200 ppm. [N.J.A.C. 7:27-22.16(e)]

Other: Monitored by continuous emissionmonitor continuously duringoperation.[N.J.A.C. 7:27-22.16(e)].

Carbon monoxide: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]

None.

Page 56 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

14 NOx (Total) <= 300 ppmvd @ 7% O2 is the

limit on the average concentration in the fluegas of each unit during any 3-hour period,based on a rolling 1-hour block exceptduring periods of start-up and shutdown,from preconstruction permit. WhenOxygen is > 14 %, then raw NOx shall notbe greater than 150 ppm. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average beginning and endingon the hour.Valid Data Capture Requirement: in orderfor a compliance averaging period to bevalid, it must be calculated based on aminimum of 65% valid data. (i.e. 2 hours ofdata would be required to calculate a valid3-hour block average.) From modificationBOP050003. [N.J.A.C. 7:27-22.16(a)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously [ N.J.A.C.7:27-19.13]and. [N.J.A.C. 7:27-22.16(e)]

None.

15 VOC (Total) <= 1.7 lb/hr as methane from

each unit except during periods of start-upand shutdown, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting every 5 years, based on the averageof three tests conducted successively. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

VOC (Total): Recordkeeping by stack testresults every 5 years. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

16 VOC (Total) <= 70 ppmvd @ 7% O2 is the

limit for any one hour period averageconcentration as methane in the flue gas ofeach unit except during periods of start-upand shutdown, from the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting every 5 years, based on any 60minute period. (see beginning of U1 OS0).[N.J.A.C. 7:27-22.16(e)]

VOC (Total): Recordkeeping by stack testresults every 5 years. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

17 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 0.57 lb/hr is thelimit on the sum of the emission rates ofH2SO4 and SO3 in the flue gas of each unitexcept during periods of start-up andshutdown, based on the application for aminor modification to the operating permitBOP050003. [N.J.A.C. 7:27-22.16(a)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing every 5 years, based on theaverage of three tests conducted on the sameunit. (see beginning of U1, OS0). Testingmay be conducted on one unit. [N.J.A.C.7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results every 5 years. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

18 Lead Emissions <= 0.25 lb/hr from each unit

except during periods of start-up andshutdown, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Lead Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

Lead Emissions: Recordkeeping by stacktest results upon occurrence of event. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. [N.J.A.C. 

Page 57 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

19 The Mercury emissions from each MSW

incinerator, shall comply with either of thetwo following alternatives, except duringperiods of start-up and shutdown, frompreconstruction permit:(a). Mercury emissions shall not exceed 28micrograms per dry standard cubic meter,corrected to 7% oxygen or(b). After January 3, 2006, Mercuryemissions shall not exceed 15 percent of themercury emissions in the effluent from theMSW incinerator, prior to the point ofinjection of activated carbon.Notwithstanding this provision, the emissionrate of mercury from each unit shall notexceed 0.05 pounds per hour based on theaverage value of 3 successive testsconducted on one unit.Compliance with the above mercuryconcentration limits of 28 micrograms perdry standard cubic meter at 7% oxygen shallbe based on the average of all source testsperformed in a calandar year.Compliance with the above mercuryremoval efficiency limits of (b) if quarterlytesting is required shall be based on theaverage of three source emission testsperformed during that quarter. [N.J.A.C.7:27-27.4(a) and N.J.A.C. 7:27-27.4(b)] and[N.J.A.C. 7:27-22.16(e)]

Monitored by stack emission testingannually, based on the average of three tests, or a method approved by the USEPA andthe Department. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Recordkeeping by stack test resultsannually. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. For compl28 microgpermittee year, the aaverage mcalendar dof the precFor complas specifiethe quarterwithin sixtof each caSubmit the quarterly a[N.J.A.C. 

20 Arsenic Emissions <= 0.002 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Arsenic Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Arsenic Emissions: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

21 Beryllium Emissions <= 0.0004 lb/hr per

unit except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Beryllium Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Beryllium Emissions: Recordkeeping bystack test results every 5 years. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

Page 58 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

22 Cadmium Emissions <= 0.03 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Cadmium Emissions: Monitored by stackemission testing annually, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Cadmium Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

23 Chromium Emissions <= 0.01 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Chromium Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Chromium Emissions: Recordkeeping bystack test results every 5 years. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

24 Nickel Emissions <= 0.004 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Nickel Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Nickel Emissions: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

25 Total 2,3,7,8 tetrachloro dibenzodioxin <=

0.000001 lb/hr is the limit on each unitexcept during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Monitored by stack emission testing every 5years, based on the average of three tests(successive) on one unit. (See stack testrequirements at the beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Recordkeeping by stack test results every 5years (see U1,OSO, Ref 1-6). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule epermit renRef 1-6). [

26 Polycyclic aromatic hydrocarbons (PAH) <=

0.0042 lb/hr is the limit in the flue gas fromeach unit except during periods of start-upand shutdown, from the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

Monitored by stack emission testing every 5years, based on the average of three testsconducted on one unit using a methodapproved by the Department. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Recordkeeping by stack test results every 5years. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

27 Opacity <= 10 % except during periods of

startup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.15165.[40 CFR 60.58b(e)] &. [40 CFR62.14103(a)]

Opacity: Monitored by continuous opacitymonitoring system continuously, based on 6minute blocks. The continuous opacitymonitoring system shall conform toPerformance Specification 1 in 40 CFR 60,appendix B. Also, perform annual opacityobservations using EPA Method 9. [40CFR 60.59b(d)] &. [40 CFR 62.14103(e)]

Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. All 6-minute opacity levelsshall be available for submittal or reviewonsite by an inspector. Also, maintainrecords of annual Method 9 opacityobservations on paper copy or computerreadable format. [40 CFR 60.59b(d)] &.[40 CFR 62.14103]

None.

28 NOx (Total) <= 36 lb/hr is the maximum

hourly emission limit, beginning November6, 2005, based on modification BOP050003.[N.J.A.C. 7:27-22.23]

NOx (Total): Monitored by stack emissiontesting every 5 years, based on the averageof three 1-hour tests conducted successively.(see beginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults every 5 years. (see beginning ofU1,OS0). [ N.J.A.C.7:27-19.13] and.[N.J.A.C. 7:27-22.16(o)]

None.

Page 59 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

29 Ammonia <= 3.1 lb/hr is the maximum

hourly emission limit, from BOP080004.[N.J.A.C. 7:27-22.16(a)]

Ammonia: Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runs.[N.J.A.C. 7:27-22.16(o)]

Ammonia: Recordkeeping by stack testresults annually. [N.J.A.C. 7:27-22.16(o)]

None.

30 Ammonia Slip <= 50 ppmvd @ 7% O2.

[N.J.A.C. 7:27-22.16(a)]

Ammonia Slip: Monitored by stack emissiontesting annually, based on the average ofthree 1-hour tests. See stack testrequirements at U1, OS Summary, Ref #1.[N.J.A.C. 7:27-22.16(a)]

Ammonia Slip: Recordkeeping by stack testresults annually. [N.J.A.C. 7:27-22.16(a)]

Stack Test and submischedule. requireme[N.J.A.C. 

31 Particulate Emissions <= 27 mg/dscm @ 7%

O2 from each MWC except during periodsof startup, shutdown, and malfunction.Startup, shutdown, and malfunctionexception is specified by 40 CFR62.14109(b). ***NEW*** On and afterApril 28, 2009, the emission limit forparticulate matter contained in the gasesdischarged to the atmosphere from adesignated facility is 25 milligrams per drystandard cubic meter, corrected to 7 percentoxygen. [40 CFR 60.33b(a)(1)(i)] &. [40CFR 62.14103(a)(1)]

Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the requirements at40 CFR 60.58b(c)(9). [40 CFR62.14109(b)]

Particulate Emissions: Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]

None.

32 Nitrogen oxides (NOx) <= 205 ppmvd @

7% O2 , 24-hour daily arithmetic average(midnight to midnight) from each MWCexcept during periods of startup, shutdown,and malfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). [40 CFR 62.14103(d)]

Nitrogen oxides (NOx): Monitored bycontinuous emission monitoring systemcontinuously, based on a 1 hour blockaverage. Monitor as specified at 40 CFR60.58b(h)(5). EPA Reference Method 19,section 4.1, shall be used for determiningthe 24-hour daily arithmetic averagenitrogen oxides emission concentration. [40CFR 62.14109(b)]

Nitrogen oxides (NOx): Recordkeeping bystrip chart or data acquisition (DAS) systemcontinuously. All 1-hour average nitrogenoxide concentrations shall be recorded andbe available for submittal or review onsiteby an inspector. This is as specified at 40CFR 60.59b(d)(2)(i)(C). [40 CFR62.15109(a)]

None.

33 Lead Emissions <= 0.44 mg/dscm @ 7% O2

from each MWC except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b).***NEW*** On and after April 28, 2009,the emission limit for lead contained in thegases discharged to the atmosphere from adesignated facility is 400 micrograms perdry standard cubic meter, corrected to 7percent oxygen. 40 CFR 60.33b(a)(4) &. [40CFR 62.14103(a)(2)]

Lead Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the Method 29requirements at 40 CFR 60.58b(d)(1). [40CFR 62.14109(b)]

Lead Emissions: Recordkeeping by stacktest results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]

None.

Page 60 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

34 Cadmium Emissions <= 0.04 mg/dscm @

7% O2 from each MWC except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). ***NEW*** On andafter April 28, 2009, the emission limit forcadmium contained in the gases dischargedto the atmosphere from a designated facilityis 35 micrograms per dry standard cubicmeter, corrected to 7 percent oxygen. [40CFR 60.33b(a)(2)(i) &. [40 CFR62.14103(a)(2)]

Cadmium Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring requirements are based on therequirements at 40 CFR 60.58b(d)(1). [40CFR 62.14109(b)]

Cadmium Emissions: Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]

None.

35 Mercury Emissions <= 0.08 mg/dscm @ 7%

O2 or 15 percent of the potential mercuryemission concentration (85-percentreduction by weight), corrected to 7%oxygen, whichever is less stringent, fromeach MWC except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b).***NEW*** On and after April 28, 2009,the emission limit for mercury contained inthe gases discharged to the atmosphere froma designated facility is 50 micrograms perdry standard cubic meter or 15 percent ofthe potential mercury emissionconcentration (85-percent reduction byweight), corrected to 7 percent oxygen,whichever is less stringent. [40 CFR60.33b(a)(3)] &. [40 CFR 62.14103(a)(3)]

Mercury Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the requirements of40 CFR 60.58b(d)(2). [40 CFR62.14109(b)]

Mercury Emissions: Recordkeeping by stacktest results annually. See stack testingrequirements in U1 OS0.. Recordkeeping isbased on the requirements at 40 CFR50.59b(d)(9)(i). [40 CFR 62.14109(a)]

None.

36 SO2 <= 29 ppmvd @ 7% O2 , or 25% of the

potential sulfur dioxide emissionconcentration (75 percent reduction byweight or volume) whichever is lessstringent, from each MWC except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). Compliance with thisemission limit is based on a 24-hour dailygeometric mean. [40 CFR 60.33b(b)(3)(i)]&. [40 CFR 62.14103(b)(1)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on adaily average (a 24-hour daily geometricaverage), or a daily geometric averagepercent reduction using EPA ReferenceMethod 19. This is based on the requirementat 40 CFR 60.58b(e)(4). [40 CFR62.14109(b)]

SO2: Recordkeeping by strip chart or dataacquisition (DAS) system continuously.The owner or operator shall maintainrecords of all 1-hour average sulfur dioxideemission concentrations. This is as specifiedat 40 CFR 60.59b(d)(2)(i)(B). [40 CFR61.14109(a)]

None.

Page 61 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

37 HCl Emissions <= 29 ppmvd @ 7% O2 or

5% of the potential hydrogen chlorideemission concentration (95 percentreduction by weight or volume) whichever isless stringent, from each MWC exceptduring periods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). [40 CFR60.33b(b)(3)(i)] &. [40 CFR62.14103(b)(2)]

HCl Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring, including detemining %reduction, is based on the requirements at 40CFR 60.58b(f). [40 CFR 62.14109(b)]

HCl Emissions: Recordkeeping by stack testresults annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]

None.

38 Dioxins/Furans (Total) <= 60 ng/dscm @

7% O2 , from each MWC except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b), 40 CFR 60.33b(c)(1)(i)and 40 CFR 60.58b(a)(1). [40 CFR62.14103(c)(1)]

Dioxins/Furans (Total): Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is as required at 40 CFR60.58b(h)(5), except as specified at 40 CFR62.14109(d)(1). [40 CFR 62.14109(b)] &.[40 CFR 62.14109(d)(1)]

Dioxins/Furans (Total): Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. This is asspecified at 40 CFR 60.59b(d)(9)(i). [40CFR 62.14109(a)]

None.

39 Dioxins/Furans (Total) <= 35 ng/dscm @

7% O2 ***NEW*** On and after April28, 2009, the emission limit for designatedfacilities that employ an electrostaticprecipitator-based emission control systemis 35 nanograms per dry standard cubicmeter (total mass), corrected to 7 percentoxygen. [40 CFR 60.33b(c)(1)(ii)]

Dioxins/Furans (Total): Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is as required at 40 CFR60.58b(h)(5), except as specified at 40 CFR62.14109(d)(1). [40 CFR 62.14109(b)] &.[40 CFR 62.14109(d)(1)]

Dioxins/Furans (Total): Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. This is asspecified at 40 CFR 60.59b(d)(9)(i). [40CFR 62.14109(a)]

None.

40 CO <= 100 ppmvd @ 7% O2 from each

MWC except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b), 40 CFR60.34b(a) and 40 CFR 60.58b(a)(1). [40CFR 62.14104(a)]

CO: Monitored by continuous emissionmonitoring system continuously, based on a1 hour block average which shall be used tocalcuate a 4-hour block average. Thecontinuous emission monitoring systemshall be operated according to PerformanceSpecification 4A in 40 CFR 60, appendix B.Monitoring is as specified at 40 CFR60.58b(i)(1), 40 CFR 60.58b(i)(3), and 40CFR 60.58b(i)(4). [40 CFR 62.14109(b)]

CO: Recordkeeping by strip chart or dataacquisition (DAS) system continuously. All1-hour average CO concentrations shall berecorded and available for submittal to theadministrator or review onsite by aninspector. This is as stated at 40 CFR60.59b(d)(2)(i)(D). [40 CFR62.14109(a)(1)]

None.

Page 62 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

41 FUGITIVE ASH EMISSIONS: The facility

must not cause to be discharged to theatmosphere visible emissions of combustionash from an ash conveying system(including conveyor transfer points) inexcess of 5 percent of the observation period(i.e., 9-min. per 3-hour period), except asprovided below: The emission limit specified above does notcover visible emissions discharged insidebuildings or enclosures of ash conveyingsystems; however, the emission limitspecified above does cover visible emissionsdischarged to the atmosphere from buildingsor enclosures of ash conveying systems. The provisions specified above do notapply during maintenance and repair ofboilers or ash conveying systems.40 CFR 60.59b(d)& [40 CFR 62.14106]

Monitored by visual determination annually,based on the average of three testsCompliance with fugitive ash emissionlimits shall be based on a series of three onehour observations, performed annually,using EPA Reference Method 22. [40 CFR60.59b(d)]&. [40 CFR 62.14106]

Other: Maintain records of annual method22 results along with all supportingcalculations. [40 CFR 60.59b(d)]&[40CFR 62.14106].

None.

Page 63 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

42 No owner or operator of an affected facility

shall cause it to operate at a load levelgreater than 110 percent of the maximumdemonstrated municipal waste combustorunit load as defined in 40 CFR 60.51b, or a4-hour steam production limit of 255,604lbs, whichever is more restrictive except: (1)During the annual dioxin/furan performancetest and the 2 weeks preceding that test, nomunicipal waste combustor unit load limitpursuant to NSPS Subpart Eb is applicable;(2)The municipal waste combustor unit loadlimit pursuant to NSPS Subpart Eb may bewaived in accordance with permissiongranted by the Administrator or delegatedState regulatory authority for the purpose ofevaluating system performance, testing newtechnology or control technologies,diagnostic testing, or related activities forthe purpose of improving facilityperformance or advancing the state-of-theart for controlling facility emissions. This isas stated at 40 CFR 60.53b(b).N.J.A.C. 7:27-22.16(a) & [40 CFR60.59b(d)]

Other: The owner or operator shall operate asteam or feedwater flow meter on acontinuous basis, as required at 40 CFR60.58(i)(6)(i). Steam (or feed water flow)flow calculations as required under 40 CFR60.58(i)(6)(i) shall be in accordance withASME PTC 4.1-1964 (Reaffirmed 1991),Power test codes : Test Code for SteamGenerating Units (with 1968 and 1969Addenda). For design, construction,installation, calibration, and use of nozzlesand orifices required in 40 CFR60.58(i)(6)(ii), proceed in accordance withthe recommendations in ASME InterimSupplement 19.5 on Instruments andApparatus: Application, Part II of FluidMeters, 6th Edition (1971).[40 CFR60.59b(d)].

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [40 CFR 60.59b(d)]

None.

Page 64 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

43 The temperature at the particulate control

device inlet shall not exceed the maximumdemonstrated particulate matter controldevice temperature as defined in 40 CFR60.51b by more than 17 degrees Celsius,except: (1) During the annual dioxin/furanperformance test the 2 weeks preceding theannual dioxin/furan performance test, noparticulate matter control device temperaturelimitations pursuant to NSPS Subpart Eb areapplicable; (2) The particulate matter controldevice temperature limits pursuant to NSPSSubpart Eb may be waived in accordancewith permission granted by theAdministrator or delegated State regulatoryauthority for the purpose of evaluationsystem performance, testing new technologyor control technologies, diagnostic testing,or related activities for the purpose ofimproving facility performance or advancingthe state-of the-art for controlling facilityemissions. This is based on the requirementat 40 CFR 60.53b(c). [40 CFR 60.59b(d)]

Monitored by temperature instrumentcontinuously, based on a 1 hour blockaverage which shall be used to calculate4-hour block arthithmetic avarages. [40 CFR60.59b(d)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. All 4-hour block arithmetictemperature averages shall be computed andrecorded and be available for submittal tothe Administrator or review onsite by aninspector. [40 CFR 60.59b(d)(6)]

None.

44 If a subsequent dioxin/furan performance

test is being performed on only one affectedfacility at the MSW plant, as provided inparagraph (g)(5)(iii) of this section, theowner or operator may elect to apply thesame maximum particulate matter controldevice temperature from the tested facilityfor all the similarly designed and operatedfacilities at the MWC plant. [40 CFR60.58(b)(i)(8)]

None. None. None.

Page 65 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

45 During operation, the carbon injection

system operating parameter(s) that are theprimary indicator(s) of the carbon mass feedrate (e.g., screw feeder setting) must equalor exceed the level established duringperformance tests for mercury anddioxin/furan emissions. During the annualdioxin/furan or mercury performance test,no limit is applicable for average carbonmass feed rate if the limit is waived inaccordance with permission granted by theAdministrator for the purpose of evaluatingsystem performance, testing new controltechnology, or related activities for thepurpose of improving facility performanceor advancing the state-of-the-art forcontrolling facility emissions. [40 CFR60.59b(d)] & [40 CFR 62.14103(c)]

Other: Monitored by carbon feed rate in8-hour block averages as required at 40CFR 62 Subpart FFF. [40 CFR 60.59b(d)]&[40 CFR 62.14103].

Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslyThe facility shall record the average carbonmass feed rate (in kg/hr or lb/hr) estimatedfor each hour of operation. Also, the facilityshall record the dates where the carbon feedrate is less than the levels established by theperformance tests for mercury anddioxins/furans. [40 CFR 60.59b(d)] &. [40CFR 62.14103]

None.

46 Pneumatic injection pressure or othercarbon

injection system indicator shall be used toprovide additional verification ofpropercarboninjection system operation. Thecarbon injection system operationalindicatorused to provide additionalverification of carboninjection systemoperation, including basis for selecting theindicator and operating responseto theindicator alarm, shall be included insection(e)(6) of the site-specific operatingmanual required under 40CFR 60.54b(e).This is effective May 10, 2011 or by thefinal compliance date established intheforthcoming FIP, whichever is sooner.[40 CFR 60.58(b)(m)(4)]

Other: instantaneous visual or audible alarmto alert the operatorof a potentialinterruption in the carbon feedrate thatwould not normallybe indicated bydirectmonitoring ofcarbon mass feedrate.[N.J.A.C. 7:27-22.16(o)].

None. None.

Page 66 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U1 Two nominal 274 TPD Municipal Solid Waste Combustors (with Carbon silo) subject to NSPS Eb, 40 CFR 60 

7:27-27

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 EMERGENCY MALFUNCTION:This

means any sudden and unavoidable failureto the equipment or control apparatus tooperate in a normal manner. Malfunctionsthat are caused entirely or in part byimproperly designed equipment, lack ofpreventative maintenance, careless orimproper operation, operator error, or anypreventable upset condition or preventableequipment or control apparatus breakdownshall not be considered emergencymalfunctions. In any enforcementproceeding, the Permittee seeking toestablish the occurrence of an emergencymalfunction has the burden of proof.[N.J.A.C. 7:27-22.16(e)]

None. None. Submit a r

schedule. emission lemergency submit a wRegional Ethe second incident. This prel A deschow it resu A desccorrect the contravent A descminimize curtailmen This provPermittee Departmencontaminawhich poshealth, wemight resuto N.J.S7:27-22.16

2 EMERGENCY MALFUNCTION:

The Department will review the EmergencyMalfunction asserted by the facility. If theDepartment deems that any EmergencyMalfuntion was asserted incorrectly, theDepartment will reject the claim and takeappropriate enforcement action. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS2 Combustor #1 under emergency malfunction, OS4 Combustor #2 under emergency malfunction

Page 67 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 EMERGENCY MALFUNCTION:

The Department will review the EmergencyMalfunction asserted by the facility. If theDepartment deems that any EmergencyMalfuntion was asserted incorrectly, theDepartment will reject the claim and takeappropriate enforcement action. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 EMERGENCY MALFUNCTION:

At the request of the Northern RegionalEnforcement Office, a telephonednotification to the NJDEP hotline mayreplace the 2-day written notfficationproviding the same information is providedin the telephone notification. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 EMERGENCY MALFUNCTION:

To obtain malfunction allowances, thefacility must:a. Maintain the equipment;b. Operate the equipment properly;c. Take steps to minimize emissionsduring malfunction periods;d. Identify and take steps to preventmalfunctions from occuring in future; ande. Report malfunctions in accordance withthe reporting requirements of this permit.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 68 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 EMERGENCY MALFUNCTION:

 Within thirty days of an emergencymalfunction, the Permittee shall submit tothe Department certified information whichidentifies the contravention and includes thefollowing: Copies of relevant operating dataincluding but not limited to continuousmonitoring data or portions of logbooksthat show the malfunction to be sudden andunavoidable. Relevant data shall include at aminimum data recorded one hour before,during, and one hour after the malfunction. List of the actions taken to prevent thepotential for the malfunction from occuringin the future. Certification in accordance withN.J.A.C. 7:27-1.39 that the malfunction didnot occur as a result of: improperly designedequipment, lack of preventativemaintenance, careless or improperoperation, or operator error, and certificationthat the information contained in thepreliminary notice is correct. If theinformation submitted in the preliminarynotice is inaccurate, a certified revision ofthe notice shall be submitted. [N.J.A.C.7:27-22.16(e)]

None. None. None.

7 EMERGENCY MALFUNCTION:

The duration of emission excursions causedby malfunctions shall not exceed thefollowing limits per occurence and percentof operating time:SO2 180min. 2% / calendar yearCO 60min 0.2% / calendar yearNOx 180min 2% / calendaryear [N.J.A.C. 7:27-22.16(e)]

Monitored by continuous emission monitorupon occurrence of event (and hour timemonitor). [N.J.A.C. 7:27-22.16(e)]

Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. Data may beperiodically printed and maintained reliablyin a log book on site. [N.J.A.C.7:27-22.16(o)]

None.

Page 69 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 EMERGENCY MALFUNCTION:

Neither the time , nor the emissions, duringthe periods of emergency malfunctionsmeeting the above criteria shall be used inthe calculation of emission levels forcomparison to allowable emission limits.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

9 EMERGENCY MALFUNCTION:

Malfunctions resulting in an excursion of anemission limit with an averaging time of lessthan or equal to one hour shall be deemed tohave occured during the entire applicableaveraging time of that emission limit.Malfunction resulting in an excursion of anemission limit with an averaging time ofgreater than one hour shall be deemed tohave occured only during the hours of themalfunction. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

10 EMERGENCY MALFUNCTION:

Any visible emission caused by amalfunction shall not exceed an average of10% opacity in any 60 minute block period,as determined by the continuous emissionmonitoring equipment or USEPA ReferenceMethod 9. [N.J.A.C. 7:27-22.16(e)]

Monitored by continuous opacity monitorupon occurrence of event, based on 6 minuteblocks. [N.J.A.C. 7:27-22.16(e)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]

None.

Page 70 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U1 Two nominal 274 TPD Municipal Solid Waste Combustors (with Carbon silo) subject to NSPS Eb, 40 CFR 60 

7:27-27

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 9.38 lb/hr.

Maximum emission rate for each incineratorfrom the table at N.J.A.C. 7:27-6.2(a), basedon the Source gas flow of 72,260 ACFM at240 degrees F. Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 6.2(a)]

None. None. None.

2 Particulate Emissions <= 0.015 gr/dscf @

7% O2 in the stack gas of each incineratorexcluding periods of boiler tube cleaning,except during periods of start up andshut-down, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests conductedsuccessively using the approved method.(see beginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Particulate Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

3 Particulate Emissions <= 0.03 gr/dscf @ 7%

O2 in the stack gas of each incineratorincluding periods of boiler tube cleaning,except during periods of start up andshut-down, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Monitored by stackemission testing every 5 years, based on any60 minute period using the approvedmethod. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. [N.J.A.C. 

4 PM-10 (Total) <= 0.1 gr/dscf @ 12% CO2

in each stack flue for each incineratorexcluding the contribution of CO2 from thecombustion of auxiliary fuel, except duringperiods of start up and shut-down, frompreconstruction permit. ( PM shall includesolid and liquid particles, excluding water,collected in the "front half" and "back half"of the stack sampling train). [N.J.A.C.7:27-22.16(e)]

PM-10 (Total): Monitored by stack emissiontesting once initially, based on each of threeDepartment validated stack test runs duringoperation, using the New Jersey test methodfor incinerators. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

PM-10 (Total): Recordkeeping by stack testresults once initially. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

5 Particulate Emissions <= 2.7 lb/hr from each

unit except during periods of start up andshut-down, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Particulate Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests conducted insuccession, using EPA Method 5. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Particulate Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

OS3 89 MM BTU/hr Combustor #2 (E2) burning MSW and/or using No. 2 Fuel Oil with control by scrubber, car

baghouse and SNCR

Page 71 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 PM-10 (Total) <= 1.38 lb/hr , from

modification BOP070001. [N.J.A.C.7:27-22.16(a)]

PM-10 (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults prior to permit renewal (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

7 SO2 <= 50 ppmvd @ 7% O2 average

concentration in the stack gas of each unit ,as determined by continuous monitoring.When Oxygen is > 14 %, then raw SO2shall not be greater than 25 ppm. The 50 ppmdv @ 7% oxygen concentrationlimit shall not apply to a unit if the average3 hr concentration of SO2 in the stack gasfrom the unit is less than 20% of the averagethree-hour concentration at the inlet of theacid gas control scrubber as determined bycontinuous emission monitoring.The average 3-hour concentration of SO2 inthe stack gas shall never exceed 100 ppmvdon a dry basis corrected to 7% oxygen (drybasis), from preconstruction permit.The emission limitation applies at all timesexcept during start-up and shutdown.The emission limitation shall not applyduring periods of scrubber downtimebecause of malfunctions. The annualdowntime of each scrubbing system is to bethe shortest achievable and not exceed 2percent of the annual operating time of theassociated furnace. [N.J.A.C. 7:27-22.16(e)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average , starting and ending on thehour (from preconstruction permit.)Valid Data Capture Requirement: in orderfor a compliance averaging period to bevalid, it must be calculated based on aminimum of 65% valid data. (i.e. 2 hours ofdata would be required to calculate a valid3-hour rolling average.) From modificationBOP050003. [N.J.A.C. 7:27-22.16(a)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]

None.

8 SO2 <= 20 lb/hr from each unit except

during periods of start up and shut-down,from preconstruction permit. [N.J.A.C.7:27-22.16(e)]

SO2: Monitored by stack emission testingevery 5 years, based on the average of threetests (conducted successively ). (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

SO2: Recordkeeping by stack test resultsevery 5 years. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

Page 72 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 HCl Emissions <= 50 ppmvd @ 7% O2 in

the stack gas of each unit for any one hourperiod except for any 1-hour period duringwhich the average concentration of HCl(ppmv) in the stack gas is less than or equalto 10% of the average concentration of HCl(ppmv) at the inlet to the acid gas controlequipment except during periods of start upand shut-down, from preconstruction permit.Continuous emission monitoring of HCl todetermine compliance with this emissionlimit is required unless it is shown thatcontrol of SO2 to below 50 ppmdv alsocontrols HCl to below the 50 ppmv level.Continuous emission monitoring is requiredif annual tests show that the 50 ppmv HCllimit contained in the above permitrequirement is exceeded. [N.J.A.C.7:27-22.16(e)]

HCl Emissions: Monitored by stackemission testing annually, based on any 60minute period (see beginning of U1, OS0).Three 1-hour tests shall be conductedsimultaneously upstream and downstream ofthe acid gas control equipment. Testing maybe conducted on one unit. [N.J.A.C.7:27-22.16(e)]

HCl Emissions: Recordkeeping by stack testresults annually (see beginning of U1,OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. 

10 Hydrogen chloride <= 11.9 lb/hr from each

unit, from operating permit application,except during periods of start-up andshutdown. [N.J.A.C. 7:27-22.16(a)]

Hydrogen chloride: Monitored by stackemission testing annually, based on any 60minute period. (see beginning of U1, OS0).Testing may be conducted on one unit.[N.J.A.C. 7:27-22.16(e)]

Hydrogen chloride: Recordkeeping by stacktest results annually. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

11 Hydrogen fluoride <= 0.1 lb/hr from each

unit from preconstruction permit, exceptduring periods of start-up and shutdown.[N.J.A.C. 7:27-22.16(e)]

Hydrogen fluoride: Monitored by stackemission testing every 5 years, based on any60 minute period. (see beginning of U1,OS0). Testing may be conducted on oneunit. [N.J.A.C. 7:27-22.16(e)]

Hydrogen fluoride: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

12 Carbon monoxide <= 35 lb/hr from each

unit except during periods of start-up andshutdown, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Carbon monoxide: Monitored by stackemission testing every 5 years, based on any60 minute period. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Carbon monoxide: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

13 Carbon monoxide <= 400 ppmvd @ 7% O2

is the limit on the average concentration ofCO in the flue gas of each unit during anyblock 1-hour period beginning and endingon the hour, except during periods ofstart-up and shutdown, from thepreconstruction permit. When Oxygen is >14 %, then raw CO shall not be greater than200 ppm. [N.J.A.C. 7:27-22.16(e)]

Other: Monitored by continuous emissionmonitor continuously duringoperation.[N.J.A.C. 7:27-22.16(e)].

Carbon monoxide: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]

None.

Page 73 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

14 NOx (Total) <= 300 ppmvd @ 7% O2 is the

limit on the average concentration in the fluegas of each unit during any 3-hour period,based on a rolling 1-hour block exceptduring periods of start-up and shutdown,from preconstruction permit. WhenOxygen is > 14 %, then raw NOx shall notbe greater than 150 ppm. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average beginning and endingon the hour.Valid Data Capture Requirement: in orderfor a compliance averaging period to bevalid, it must be calculated based on aminimum of 65% valid data. (i.e. 2 hours ofdata would be required to calculate a valid3-hour block average.) From modificationBOP050003. [N.J.A.C. 7:27-22.16(a)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously [ N.J.A.C.7:27-19.13]and. [N.J.A.C. 7:27-22.16(e)]

None.

15 VOC (Total) <= 1.7 lb/hr as methane from

each unit except during periods of start-upand shutdown, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting every 5 years, based on the averageof three tests conducted successively. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

VOC (Total): Recordkeeping by stack testresults every 5 years. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

16 VOC (Total) <= 70 ppmvd @ 7% O2 is the

limit for any one hour period averageconcentration as methane in the flue gas ofeach unit except during periods of start-upand shutdown, from the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting every 5 years, based on any 60minute period. (see beginning of U1 OS0).[N.J.A.C. 7:27-22.16(e)]

VOC (Total): Recordkeeping by stack testresults every 5 years. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

17 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 0.57 lb/hr is thelimit on the sum of the emission rates ofH2SO4 and SO3 in the flue gas of each unitexcept during periods of start-up andshutdown, based on the application for aminor modification to the operating permitBOP050003. [N.J.A.C. 7:27-22.16(a)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing every 5 years, based on theaverage of three tests conducted on the sameunit. (see beginning of U1, OS0). Testingmay be conducted on one unit. [N.J.A.C.7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results every 5 years. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

18 Lead Emissions <= 0.25 lb/hr from each unit

except during periods of start-up andshutdown, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Lead Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

Lead Emissions: Recordkeeping by stacktest results upon occurrence of event. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. [N.J.A.C. 

Page 74 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

19 The Mercury emissions from each MSW

incinerator, shall comply with either of thetwo following alternatives, except duringperiods of start-up and shutdown, frompreconstruction permit:(a). Mercury emissions shall not exceed 28micrograms per dry standard cubic meter,corrected to 7% oxygen or(b). After January 3, 2006, Mercuryemissions shall not exceed 15 percent of themercury emissions in the effluent from theMSW incinerator, prior to the point ofinjection of activated carbon.Notwithstanding this provision, the emissionrate of mercury from each unit shall notexceed 0.05 pounds per hour based on theaverage value of 3 successive testsconducted on one unit.Compliance with the above mercuryconcentration limits of 28 micrograms perdry standard cubic meter at 7% oxygen shallbe based on the average of all source testsperformed in a calandar year.Compliance with the above mercuryremoval efficiency limits of (b) if quarterlytesting is required shall be based on theaverage of three source emission testsperformed during that quarter. [N.J.A.C.7:27-27.4(a) and N.J.A.C. 7:27-27.4(b)] and[N.J.A.C. 7:27-22.16(e)]

Monitored by stack emission testingannually, based on the average of three tests, or a method approved by the USEPA andthe Department. (see beginning of U1,OS0). [N.J.A.C. 7:27-22.16(e)]

Recordkeeping by stack test resultsannually. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. For compl28 microgpermittee year, the aaverage mcalendar dof the precFor complas specifiethe quarterwithin sixtof each caSubmit the quarterly a[N.J.A.C. 

20 Arsenic Emissions <= 0.002 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Arsenic Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Arsenic Emissions: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

21 Beryllium Emissions <= 0.0004 lb/hr per

unit except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Beryllium Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Beryllium Emissions: Recordkeeping bystack test results every 5 years. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

Page 75 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

22 Cadmium Emissions <= 0.03 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Cadmium Emissions: Monitored by stackemission testing annually, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Cadmium Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

23 Chromium Emissions <= 0.01 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Chromium Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Chromium Emissions: Recordkeeping bystack test results every 5 years. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

24 Nickel Emissions <= 0.004 lb/hr per unit

except during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Nickel Emissions: Monitored by stackemission testing every 5 years, based on theaverage of three tests (successive) on oneunit. (See stack test requirements at thebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Nickel Emissions: Recordkeeping by stacktest results every 5 years. (see beginning ofU1, OS0). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

25 Total 2,3,7,8 tetrachloro dibenzodioxin <=

0.000001 lb/hr is the limit on each unitexcept during periods of start-up andshutdown, from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Monitored by stack emission testing every 5years, based on the average of three tests(successive) on one unit. (See stack testrequirements at the beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Recordkeeping by stack test results every 5years (see U1,OSO, Ref 1-6). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule epermit renRef 1-6). [

26 Polycyclic aromatic hydrocarbons (PAH) <=

0.0042 lb/hr is the limit in the flue gas fromeach unit except during periods of start-upand shutdown, from the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

Monitored by stack emission testing every 5years, based on the average of three testsconducted on one unit using a methodapproved by the Department. (seebeginning of U1, OS0). [N.J.A.C.7:27-22.16(e)]

Recordkeeping by stack test results every 5years. (see beginning of U1, OS0).[N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule. [N.J.A.C. 

27 Dioxins/Furans (Total) <= 30 ng/dscm @

7% O2 , except during periods of start-up,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.15165.40 CFR 60.59b(d), 40 CFR 60.53a(b) &.[40 CFR 62.14103(c)(2)]

Dioxins/Furans (Total): Monitored by stackemission testing annually, based on theaverage of three tests (see U1,OSO, Ref1-6.) If these municipal waste combustionunits have demonstrated levels ofdioxins/furans emissions less than or equalto 15 nanograms per dry standard cubicmeter (total mass) for 2 consecutive years,the facility may choose to conduct annualstack tests for dioxins/furans emissions ononly one municipal waste combustion unitper year. [40 CFR 60.59b(d)] &. [40 CFR62.14103]

Dioxins/Furans (Total): Recordkeeping bystack test results annually. (see beginning ofU1, OS0) [40 CFR 60.59b(d)] &. [40 CFR62.14103]

Stack Test and submischedule (7:27-22.16

Page 76 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

28 Cadmium Emissions <= 0.04 mg/DSCM

corrected to 7% oxygen except duringperiods of start-up, shutdown, andmalfunction. On May 10, 2011, or by thefinal compliance date established in theforthcoming FIP, whichever is sooner,Cadmium emissions<=0.035mg/dscm@7%O2 except during periods of start-up,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40CFR 62.15165.[40 CFR 60.59b(d)] &. [40 CFR62.14103(a)]

Cadmium Emissions: Monitored by stackemission testing annually, based on theaverage of three tests. (see beginning of U1,OS0) [40 CFR 60.59b(d)] &. [40 CFR62.14103]

Cadmium Emissions: Recordkeeping bystack test results annually. (see beginning ofU1, OS0) [40 CFR 60.59b(d)] &. [40 CFR62.14103]

Stack Test and submischedule. [N.J.A.C. 

29 Lead Emissions <= 0.44 mg/DSCM

corrected to 7% O2 except during periodsof start-up, shutdown, and malfunction. OnMay 10, 2011, or by the final compliancedate established in the forthcoming FIP,whichever is sooner, Leademissions<=0.40mg/dscm@7% O2 exceptduring periods of start-up, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by40CFR 62.15165.[40 CFR 60.59b(d)] &. [40 CFR62.14103(a)]

Lead Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. (seebeginning of U1, OS0) [40 CFR 60.59b(d)]&. [40 CFR 62.14103]

Lead Emissions: Recordkeeping by stacktest results upon occurrence of event. (seebeginning of U1, OS0) [40 CFR60.59b(d)] &. [40 CFR 62.14103]

Stack Test and submischedule. [N.J.A.C. 

30 Mercury Emissions <= 0.08 mg/DSCM

corrected to 7% oxygen or 15 percent of thepotential mercury emission concentration(85-percent reduction by weight), whicheveris less stringent except during periods ofstart-up, shutdown, and malfunction. OnMay 10, 2011, or by the final compliancedate established in the forthcoming FIP,whichever is sooner, mercuryemissions<=0.050mg/dscm@7% O2 exceptduring periods of start-up, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by40CFR 62.15165.[40 CFR 60.59b(d)] &. [40 CFR62.14103(a)]

Mercury Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. (seebeginning of U1, OS0) [40 CFR 60.59b(d)]&. [40 CFR 62.14103]

Mercury Emissions: Recordkeeping by stacktest results upon occurrence of event. (seebeginning of U1, OS0) [40 CFR 60.59b(d)]&. [40 CFR 62.14103]

Stack Test and submischedule. [N.J.A.C. 

Page 77 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

31 Opacity <= 10 % except during periods of

startup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.15165.[40 CFR 60.58b(e)] &. [40 CFR62.14103(a)]

Opacity: Monitored by continuous opacitymonitoring system continuously, based on 6minute blocks. The continuous opacitymonitoring system shall conform toPerformance Specification 1 in 40 CFR 60,appendix B. Also, perform annual opacityobservations using EPA Method 9. [40CFR 60.59b(d)] &. [40 CFR 62.14103(e)]

Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. All 6-minute opacity levelsshall be available for submittal or reviewonsite by an inspector. Also, maintainrecords of annual Method 9 opacityobservations on paper copy or computerreadable format. [40 CFR 60.59b(d)] &.[40 CFR 62.14103]

None.

32 Particulate Emissions <= 27 mg/DSCM

except during periods of startup, shutdown,and malfunction. On May 10, 2011, or bythe final compliance date established in theforthcoming FIP, whichever is sooner,Particulate emissions<=0.25mg/dscm@7%O2 except during periods of start-up,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.15165.[40 CFR 60.59b(d)] &. [40 CFR62.14103(a)]

Other: See stack testing requirements (seebeginning of U1, OS0). [40 CFR60.59b(d)] &[40 CFR 62.14103].

Other: See stack testing requirements (seebeginning of U1, OS0). [40 CFR60.59b(d)] &[40 CFR 62.14103].

Stack Test and submischedule (7:27-22.16

33 HCl Emissions <= 29 ppmvd @ 7% O2 or

5% of the potential hydrogen chlorideemission concentration (95 percentreduction by weight or volume) whichever isless stringent except during periods ofstart-up, shutdown, and malfunction.Startup, shutdown, and malfunctionexception is specified by 40CFR 62.15165.[40 CFR 60.59b(d)] &. [40 CFR62.14103(b)]

HCl Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. (seebeginning of U1, OS0) [40 CFR 60.59b(d)]&. [40 CFR 62.14103]

HCl Emissions: Recordkeeping by stack testresults upon occurrence of event. (seebeginning of U1, OS0) [40 CFR 60.59b(d)]&. [40 CFR 62.14103]

Stack Test and submischedule. [N.J.A.C. 

Page 78 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

34 Nitrogen oxides (NOx) <= 205 ppmvd @

7% O2 , 24-hour daily arithmetic average(midnight to midnight) except duringperiods of start-up, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by40CFR 62.15165.[40 CFR 60.58b(h)] &. [40 CFR62.14103(d)]

Nitrogen oxides (NOx): Monitored bycontinuous emission monitoring systemcontinuously, based on a 1 hour blockaverage. EPA Reference Method 19,section 4.1, shall be used for determiningthe 24-hour daily arithmetic averagenitrogen oxides emission concentration.Valid Data Capture Requirement: in orderfor a compliance averaging period to bevalid, it must be calculated based on aminimum of 75% valid data. (i.e. 18 hoursof data would be required to calculate avalid 24-hour average.) From modificationBOP050003.[40 CFR 60.59b(d)] &. [40 CFR 62.14103]

Nitrogen oxides (NOx): Recordkeeping bystrip chart, data acquisition (DAS) system,or other method approved by BTScontinuously. All 1-hour average nitrogenoxide concentrations shall be recorded andbe available for submittal or review onsiteby an inspector. [40 CFR 60.59b(d)] &.[40 CFR 62.14103]

None.

35 NOx (Total) <= 36 lb/hr is the maximum

hourly emission limit, beginning November6, 2005, based on modification BOP050003.[N.J.A.C. 7:27-22.23]

NOx (Total): Monitored by stack emissiontesting every 5 years, based on the averageof three 1-hour tests conducted successively.(see beginning of U1, OS0). [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults every 5 years. (see beginning ofU1,OS0). [ N.J.A.C.7:27-19.13] and.[N.J.A.C. 7:27-22.16(o)]

None.

36 Ammonia <= 3.1 lb/hr is the maximum

hourly emission limit, from BOP080004.[N.J.A.C. 7:27-22.16(a)]

Ammonia: Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runs.[N.J.A.C. 7:27-22.16(o)]

Ammonia: Recordkeeping by stack testresults annually. [N.J.A.C. 7:27-22.16(o)]

None.

37 Ammonia Slip <= 50 ppmvd @ 7% O2.

[N.J.A.C. 7:27-22.16(a)]

Ammonia Slip: Monitored by stack emissiontesting annually, based on the average ofthree 1-hour tests. See stack testrequirements at U1, OS Summary, Ref #1.[N.J.A.C. 7:27-22.16(a)]

Ammonia Slip: Recordkeeping by stack testresults annually. [N.J.A.C. 7:27-22.16(a)]

Stack Test and submischedule. requireme[N.J.A.C. 

Page 79 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

38 SO2 <= 29 ppmvd @ 7% O2 or 25% of the

potential sulfur dioxide emissionconcentration (75 percent reduction byweight or volume) whichever is lessstringent except during periods of start-up,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40CFR 62.15165.[40 CFR 60.58b(e)(4)] &. [40 CFR62.14103(b)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on adaily average (a 24-hour daily geometricaverage), or a daily geometric averagepercent reduction using EPA ReferenceMethod 19.Valid Data Capture Requirement: in orderfor a compliance averaging period to bevalid, it must be calculated based on aminimum of 75% valid data. (i.e. 18 hoursof data would be required to calculate avalid 24-hour average.) From modificationBOP050003.[40 CFR 60.59b(d)] &. [40 CFR 62.14103]

SO2: Recordkeeping by strip chart, dataacquisition (DAS) system, or other methodapproved by BTS continuously. The owneror operator shall maintain records of all1-hour average sulfur dioxide emissionconcentrations. [40 CFR 60.59b(d)] &. [40CFR 61.14103]

None.

39 CO <= 100 ppmvd @ 7% O2 except during

periods of start-up, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by40CFR 62.15165.[40 CFR 60.58b(i)] &. [40 CFR62.14104(a)]

CO: Monitored by continuous emissionmonitoring system continuously, based on a1 hour block average which shall be used tocalculate a 4-hour block average. Thecontinuous emission monitoring systemshall be operated according to PerformanceSpecification 4A in 40 CFR 60, appendix B.Valid Data Capture Requirement: in orderfor a compliance averaging period to bevalid, it must be calculated based on aminimum of 75% valid data. (i.e. 3 hours ofdata would be required to calculate a valid4-hour block average.) From modificationBOP050003.40 CFR 60.58b(i)]. [40 CFR 62.14104]

CO: Recordkeeping by strip chart, dataacquisition (DAS) system, or other methodapproved by BTS continuously. All 1-houraverage CO concentrations shall be recordedand available for submittal to theadministrator or review onsite by aninspector. [40 CFR 60.58b(i)]. [40 CFR62.14104]

None.

Page 80 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

40 FUGITIVE ASH EMISSIONS: The facility

must not cause to be discharged to theatmosphere visible emissions of combustionash from an ash conveying system(including conveyor transfer points) inexcess of 5 percent of the observation period(i.e., 9-min. per 3-hour period), except asprovided below: The emission limit specified above does notcover visible emissions discharged insidebuildings or enclosures of ash conveyingsystems; however, the emission limitspecified above does cover visible emissionsdischarged to the atmosphere from buildingsor enclosures of ash conveying systems. The provisions specified above do notapply during maintenance and repair ofboilers or ash conveying systems.40 CFR 60.59b(d)& [40 CFR 62.14106]

Monitored by visual determination annually,based on the average of three testsCompliance with fugitive ash emissionlimits shall be based on a series of three onehour observations, performed annually,using EPA Reference Method 22. [40 CFR60.59b(d)]&. [40 CFR 62.14106]

Other: Maintain records of annual method22 results along with all supportingcalculations. [40 CFR 60.59b(d)]&[40CFR 62.14106].

None.

Page 81 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

41 No owner or operator of an affected facility

shall cause it to operate at a load levelgreater than 110 percent of the maximumdemonstrated municipal waste combustorunit load as defined in 40 CFR 60.51b, or a4-hour steam production limit of 255,604lbs, whichever is more restrictive except: (1)During the annual dioxin/furan performancetest and the 2 weeks preceding that test, nomunicipal waste combustor unit load limitpursuant to NSPS Subpart Eb is applicable;(2)The municipal waste combustor unit loadlimit pursuant to NSPS Subpart Eb may bewaived in accordance with permissiongranted by the Administrator or delegatedState regulatory authority for the purpose ofevaluating system performance, testing newtechnology or control technologies,diagnostic testing, or related activities forthe purpose of improving facilityperformance or advancing the state-of-theart for controlling facility emissions. This isas stated at 40 CFR 60.53b(b).N.J.A.C. 7:27-22.16(a) & [40 CFR60.59b(d)]

Other: The owner or operator shall operate asteam or feedwater flow meter on acontinuous basis, as required at 40 CFR60.58(i)(6)(i). Steam (or feed water flow)flow calculations as required under 40 CFR60.58(i)(6)(i) shall be in accordance withASME PTC 4.1-1964 (Reaffirmed 1991),Power test codes : Test Code for SteamGenerating Units (with 1968 and 1969Addenda). For design, construction,installation, calibration, and use of nozzlesand orifices required in 40 CFR60.58(i)(6)(ii), proceed in accordance withthe recommendations in ASME InterimSupplement 19.5 on Instruments andApparatus: Application, Part II of FluidMeters, 6th Edition (1971).[40 CFR60.59b(d)].

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [40 CFR 60.59b(d)]

None.

Page 82 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

42 The temperature at the particulate control

device inlet shall not exceed the maximumdemonstrated particulate matter controldevice temperature as defined in 40 CFR60.51b by more than 17 degrees Celsius,except: (1) During the annual dioxin/furanperformance test the 2 weeks preceding theannual dioxin/furan performance test, noparticulate matter control device temperaturelimitations pursuant to NSPS Subpart Eb areapplicable; (2) The particulate matter controldevice temperature limits pursuant to NSPSSubpart Eb may be waived in accordancewith permission granted by theAdministrator or delegated State regulatoryauthority for the purpose of evaluationsystem performance, testing new technologyor control technologies, diagnostic testing,or related activities for the purpose ofimproving facility performance or advancingthe state-of the-art for controlling facilityemissions. This is based on the requirementat 40 CFR 60.53b(c). [40 CFR 60.59b(d)]

Monitored by temperature instrumentcontinuously, based on a 1 hour blockaverage which shall be used to calculate4-hour block arthithmetic avarages. [40 CFR60.59b(d)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. All 4-hour block arithmetictemperature averages shall be computed andrecorded and be available for submittal tothe Administrator or review onsite by aninspector. [40 CFR 60.59b(d)(6)]

None.

43 During operation, the carbon injection

system operating parameter(s) that are theprimary indicator(s) of the carbon mass feedrate (e.g., screw feeder setting) must equalor exceed the level established duringperformance tests for mercury anddioxin/furan emissions. During the annualdioxin/furan or mercury performance test,no limit is applicable for average carbonmass feed rate if the limit is waived inaccordance with permission granted by theAdministrator for the purpose of evaluatingsystem performance, testing new controltechnology, or related activities for thepurpose of improving facility performanceor advancing the state-of-the-art forcontrolling facility emissions. [40 CFR60.59b(d)] & [40 CFR 62.14103(c)]

Other: Monitored by carbon feed rate in8-hour block averages as required at 40CFR 62 Subpart FFF. [40 CFR 60.59b(d)]&[40 CFR 62.14103].

Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslyThe facility shall record the average carbonmass feed rate (in kg/hr or lb/hr) estimatedfor each hour of operation. Also, the facilityshall record the dates where the carbon feedrate is less than the levels established by theperformance tests for mercury anddioxins/furans. [40 CFR 60.59b(d)] &. [40CFR 62.14103]

None.

Page 83 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

44 Pneumatic injection pressure or othercarbon

injection system indicator shall be used toprovide additional verification ofpropercarboninjection system operation. Thecarbon injection system operationalindicatorused to provide additionalverification of carboninjection systemoperation, including basis for selecting theindicator and operating responseto theindicator alarm, shall be included insection(e)(6) of the site-specific operatingmanual required under 40CFR 60.54b(e).This is effective May 10, 2011 or by thefinal compliance date established intheforthcoming FIP, whichever is sooner.[40 CFR 60.58(b)(m)(4)]

Other: instantaneous visual or audible alarmto alert the operatorof a potentialinterruption in the carbon feedrate thatwould not normallybe indicated bydirectmonitoring ofcarbon mass feedrate.[N.J.A.C. 7:27-22.16(o)].

None. None.

Page 84 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U1 Two nominal 274 TPD Municipal Solid Waste Combustors (with Carbon silo) subject to NSPS Eb, 40 CFR 60 

7:27-27

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 0.5 lb/hr is the

maximum allowable rate based on 0.02grains per SCF of stack gas flow. [N.J.A.C.7:27- 6.2(a)]

None. None. None.

2 The owner or operator shall not use this

emission unit in a manner which will causevisible emissions greater than 20 percentopacity, exclusive of condensed watervapor, for a period of three minutes in anyconsecutive 30-minute period. [N.J.A.C.7:27-6.2(d)] and. [N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 The owner or operator shall use this

emission unit in a manner which will causeno visible emissions exclusive of condensedwater vapor. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 The carbon particulate emissions shall be

controlled by a baghouse. [N.J.A.C.7:27-22.16(e)]

None. None. None.

5 The owner or operator shall inspect and

maintain the baghouse particulate filter andreplace the bags on a schedule necessary toachieve the required particulate controlefficiency as specified by the manufacturer.[N.J.A.C. 7:27-22.16(a)]

Monitored by visual determination annually(or after every fourth delivery, whichevercomes first) of the condition of the bags.[N.J.A.C. 7:27-22.16(o)]

Recordkeeping by manual logging ofparameter upon occurrence of event.Record each inspection and maintenanceevent in a logbook or readily accessiblecomputer memory. [N.J.A.C. 7:27-22.16(o)]

None.

6 Total Throughput <= 6,667 ft^3 per year of

carbon, from the operating permitapplication. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 The method of bag cleaning shall be pulse

jet, from operating permit application.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

8 TSP <= 0.084 lb/hr , from preconstruction

permit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

9 PM-10 (Total) <= 0.084 lb/hr , from

preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

OS5 Filling Carbon silo (E4) with emissions controlled by Baghouse (CD8)

Page 85 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

10 Pressure Drop Across the Baghouse >= 3

and Pressure Drop Across the Baghouse <=5 inches w.c. , from operating permitapplication. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

11 The bags shall be constructed of polyester

fabric. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

12 The number of bags shall be 25. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

13 The filtration area shall be at least 230 sq. ft.

[N.J.A.C. 7:27-22.16(e)]

None. None. None.

14 Particulates Control Efficiency >= 99 %.

[N.J.A.C. 7:27-22.16(e)]

None. None. None.

15 Air-to-Cloth Ratio <= 3 ACFM/sq.ft..

[N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 86 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U2 Ash Handling SystemOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The owner or operator shall not use this

emission unit in a manner which will causevisible emissions greater than 20 percentopacity, exclusive of condensed watervapor, for a period of three minutes in anyconsecutive 30-minute period. [N.J.A.C.7:27-6.2(d)] and. [N.J.A.C. 7:27- 6.2(e)]

Monitored by visual determination eachmonth during operation. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by other recordkeepingmethod (provide description) each monthduring operation Keep report ofobservations in file. The owner or operatorshall manually log in a logbook orelectronically record (in a computer, DAS orelectronic operating system). [N.J.A.C.7:27-22.16(o)]

None.

2 The owner or operator shall use this

emission unit in a manner which will causeno visible emissions exclusive of condensedwater vapor. [N.J.A.C. 7:27-22.16(e)]

Monitored by visual determination eachmonth during operation, based on aninstantaneous determination. Forcompliance with the opacity standard, thepermittee shall conduct visual opacityinspections during daylight hours. Visualinspections shall consist of a visual surveyto identify if the stack has visible emissions,(other than condensed water vapor), greaterthan the prescribed standard. If visibleemissions are observed, the permittee shalldo the following:(1) Verify that the equipment and/or controldevice causing the emission is operatingaccording to manufactures specificationsand the operating permit compliance plan.If the equipment or control device is notoperating properly, the permittee shall takecorrective action immediately to eliminatethe excess emissions. The permittee mustreport any permit violations to NJDEPpursuant to N.J.A.C. 7:27-22.19.(2) If the corrective action taken in step (1)does not correct the opacity problem within24 hours, the applicant shall perform acheck via a certified opacity reader, inaccordance with N.J.A.C. 7:27B-2. Suchtest shall be conducted each day untilcorrective action is taken to successfullycorrect the opacity problem. [N.J.A.C.7:27-22.16(o)]

Other: The owner or operator shall manuallylog in a logbook or electronically record (ina computer, DAS or electronic operatingsystem) daily and retain the followingrecords:(1) Date and time of inspection;(2) Emission Point number;(3) Operational status of equipment:(4) Observed results and conclusions:(5) Description of corrective action taken ifneeded;(6) Date and time opacity problem wassolved, if applicable;(7) N.J.A.C. 7:27B-2 results if conducted;and(8) Name of person(s) conducting inspection.[N.J.A.C. 7:27-22.16(a)].

None.

OS Summary

Page 87 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 TSP <= 2.63 tons/yr is annual emission

limit, from application for operating permit.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 PM-10 (Total) <= 2.63 tons/yr is annual

emission limit, from application foroperating permit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 The owner or operator shall not use this

emission unit in a manner which will causevisible emissions for more than 5 percent ofhourly observation period. Table 2 ofSubpart JJJ [40 CFR 62.15160]

Monitored by visual determination annually,based on the average of three 1-hour tests.This requirement becomes applicable afterthe effective date of federal regulations 40CFR 62, Subpart JJJ. [40 CFR 62]

Other: Keep report of annual observations infile.[40 CFR 62.15300].

None.

Page 88 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U2 Ash Handling SystemOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 0.5 lb/hr is the

maximum allowable particulate emissionrate based on .02 grains per scf. [N.J.A.C.7:27- 6.2(a)]

None. None. None.

2 TSP <= 0.4 lb/hr is the maximum emission

rate, from preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 PM-10 (Total) <= 0.4 lb/hr is the maximum

emission rate, from application for operatingpermit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Particulates Control Efficiency >= 99 % by

weight. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 The permittee shall conduct cartridge

maintenance and replacement at each filteron a schedule necessary to achieve therequired particulate removal efficiency asspecified by the manufacturer. [N.J.A.C.7:27-22.16(a)]

Other: The owner or operator shall performa visual inspection of the control deviceevery month and repair or replace anydefective or malfunctioningcomponents.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter upon occurrence of event. Thepermittee shall record each instance ofcartridge maintenance and cartridgereplacement in a logbook or in readilyavailable computer files. [N.J.A.C.7:27-22.16(o)]

None.

6 The filter shall contain 1 cartridge. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

7 The total filter area of the cartridge shall be

=> 244 sq. ft., from the application for theoperating permit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 The fabric of the cartridge shall be Cotton

having a woven weave and sateen finish,from application for the operating permit.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

9 Pressure Drop >= 3 and Pressure Drop <= 5

inches w.c. across the filter. [N.J.A.C.7:27-22.16(a)]

None. None. None.

10 Inlet Temperature to Baghouse <= 100

degrees F. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS1 Fly ash conveyor & surge bin (E6) venting to Cartridge Filter (CD9)

Page 89 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U2 Ash Handling SystemOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 0.5 lb/hr is the

maximum allowable particulate emissionrate based on .02 grains per scf. [N.J.A.C.7:27- 6.2(a)]

None. None. None.

2 TSP <= 0.1 lb/hr is the maximum emission

rate, from preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 PM-10 (Total) <= 0.1 lb/hr is the maximum

emission rate, from application for operatingpermit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Particulates Control Efficiency >= 99 % by

weight. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 The permittee shall conduct cartridge

maintenance and replacement at each filteron a schedule necessary to achieve therequired particulate removal efficiency asspecified by the manufacturer. [N.J.A.C.7:27-22.16(a)]

Other: The owner or operator shall performa visual inspection of the control deviceevery month and repair or replace anydefective or malfunctioningcomponents.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter upon occurrence of event. Thepermittee shall record each instance ofcartridge maintenance and cartridgereplacement in a logbook or in readilyavailable computer files. [N.J.A.C.7:27-22.16(o)]

None.

6 The filter shall contain 1 cartridge. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

7 The total filter area of the cartridge shall be

=> 12.8 sq. ft., from the application for theoperating permit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 The fabric of the cartridge shall be natural

and man-made fibers, from application forthe operating permit. [N.J.A.C.7:27-22.16(a)]

None. None. None.

9 Pressure Drop >= 0.13 and Pressure Drop

<= 0.22 inches w.c. across the filter.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

10 Inlet Temperature to Baghouse: shall be

outdoor ambient. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS2 Combustor ash and Fly ash Mixing operation (E12), venting to Cartridge Filter (CD10)

Page 90 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U2 Ash Handling SystemOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 4.76 lb/hr is the

maximum allowable particulate emissionrate based on .02 grains per scf. [N.J.A.C.7:27- 6.2(a)]

None. None. None.

2 TSP <= 0.1 lb/hr is the maximum emission

rate, from preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 PM-10 (Total) <= 0.1 lb/hr is the maximum

emission rate, from application for operatingpermit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Particulates Control Efficiency >= 99 % by

weight. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 The permittee shall conduct cartridge

maintenance and replacement at each filteron a schedule necessary to achieve therequired particulate removal efficiency asspecified by the manufacturer. [N.J.A.C.7:27-22.16(a)]

Other: The owner or operator shall performa visual inspection of the control deviceevery month and repair or replace anydefective or malfunctioningcomponents.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter upon occurrence of event. Thepermittee shall record each instance ofcartridge maintenance and cartridgereplacement in a logbook or in readilyavailable computer files. [N.J.A.C.7:27-22.16(o)]

None.

6 Each filter (of two) shall contain 14

cartridges. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

7 The total filter area of the cartridge shall be

=> 12.8 sq. ft., from the application for theoperating permit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 The fabric of the cartridge shall be natural

and man-made fibers, from application forthe operating permit. [N.J.A.C.7:27-22.16(a)]

None. None. None.

9 Pressure Drop >= 0.13 and Pressure Drop

<= 0.22 inches w.c. across the filter.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS3 Ash storage & Truck Loading (E13), Exhaust Fan (EF-9)/ Cartridge Filter (CD11) & Exhaust Fan (EF-10)/ C

Page 91 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U3 1.847 MMBTU/hr Diesel Engine driven Pump for Fire ProtectionOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Smoke emissions from stationary internal

combustion engines no greater than 20%opacity, exclusive of visible condensedwater vapor, for more than 10 consecutiveseconds. [N.J.A.C. 7:27- 3.5]

None. None. None.

2 The engine emissions, exclusive of visible

condensed water vapor, shall not exceed anOpacity <= 10 %. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 TSP <= 1.11 lb/hr is the maximum

particulate emission limit from thecombustion of fuel based on rated heat inputof the source. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

4 Sulfur Content in Fuel <= 0.3 % sulfur by

weight is maximum allowable sulfur contentin fuel oil by fuel oil type/viscosity andgeographical zone (Zone 2 - WarrenCounty). [N.J.A.C. 7:27- 9.2(b)]

Other: Check fuel sulfur content by suppliercertification on each change of supplieroreach change of formulation.[N.J.A.C. 7:27-9.2(b)].

Other: Keep records of suppliercertification showing fuel sulfur content oneach change of supplier and each change offormulation.[N.J.A.C. 7:27- 9.2(b)].

None.

5 Engine fuel limited to Diesel fuel. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

6 The engine shall be limited to a Maximum

Gross Heat Input <= 1.847 MMBTU/hr.[N.J.A.C. 7:27-22.16(e)]

Other: Fuel burner rated capacity.[N.J.A.C.7:27-22.16(o)].

None. None.

OS Summary

Page 92 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 The emergency generator shall be located at

the facility and produce mechanical orthermal energy, or electrical powerexclusively for use at the facility. Thisemergency generator shall be operated only:1. During the performance of normal testingand maintenance procedures, asrecommended in writing by themanufacturer and/or as required in writingby a Federal or State law or regulation,2. When there is power outage or theprimary source of mechanical or thermalenergy fails because of an emergency, or3. When there is a voltage reduction issuedby PJM and posted on the PJM internetwebsite (www.pjm.com) under the"emergency procedures" menu. [N.J.A.C. 7:27-19.1]

Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]

Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem, the following information:1. For each time the emergency generator isspecifically operated for testing ormaintenance: i. The reason for its operation; ii. The date(s) of operation and the startup and shut down time; iii. The total operating time for testing ormaintenance based on the generator's hourmeter; and iv. The name of the operator; and2. If a voltage reduction is the reason for theuse of the emergency generator, a copy ofthe voltage reduction notification from PJMor other documentation of the voltagereduction.[N.J.A.C. 7:27-19.11].

None.

Page 93 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 This emergency generator shall not be used:

1. For normal testing and maintenance ondays when the Department forecasts airquality anywhere in New Jersey to be"unhealthy for sensitive groups,""unhealthy," or "very unhealthy" as definedin the EPA's Air Quality Index athttp://airnow.gov/, as supplemented oramended and incorporated herein byreference, unless required in writing by aFederal or State law or regulation.Procedures for determining the air qualityforecasts for New Jersey are available at theDepartment's air quality permitting web siteathttp://www.state.nj.us/dep/aqpp/aqforecast;and2. As a source of energy or power after theprimary energy or power source has becomeoperable again. If the primary energy orpower source is under the control of theowner or operator of the emergencygenerator, the owner or operator shall makea reasonable, timely effort to repair theprimary energy or power source. [N.J.A.C. 7:27-19.2(d)]

None. None. None.

9 The Permittee shall, once per month, record

the total operating time from the generator'shour meter. [N.J.A.C. 7:27-19.11]

Monitored by hour/time monitorcontinuously . [N.J.A.C. 7:27-22.16(o)]

Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem the total operating time from thegenerator's hour meter. Once per month.[N.J.A.C. 7:27-19.11].

None.

Page 94 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

10 Hours of Operation <= 60 hr/yr. The

Permittee shall comply with the above hourper year limit for normal testing andmaintenance. [N.J.A.C. 7:27-22.16(a)]

Hours of Operation: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Other: The Permittee shall record thefollowing in either a logbook or computerdata system each time the emergencygenerator is operated for testing andmaintenance:1. The reason for its operation;2. The date(s) of operation and the start upand shut down time;3. The total operating time for testing ormaintenance based on the generator's hourmeter; and4. The name of the operator.[N.J.A.C. 7:27-19.11].

None.

11 NOx (Total) <= 0.246 tons/yr is the annual

emission limit, based on the fuel usage limit.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

12 All other emissions shall be below reporting

thresholds. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 95 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U3 1.847 MMBTU/hr Diesel Engine driven Pump for Fire ProtectionOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 VOC (Total) <= 0.64 lb/hr , from

preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

2 NOx (Total) <= 8.19 lb/hr , from

preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 CO <= 1.76 lb/hr , from preconstruction

permit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 SO2 <= 0.536 lb/hr based on heat input,

from application for operating permit.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 TSP <= 0.58 lb/hr , from preconstruction

permit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 PM-10 (Total) <= 0.58 lb/hr , from

preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

OS1 Firing Diesel fuel

Page 96 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U4 2.115 MMBTU/hr Diesel Engine driven Emergency Generator for Water Supply Pump

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Smoke emissions from stationary internal

combustion engines no greater than 20%opacity, exclusive of visible condensedwater vapor, for more than 10 consecutiveseconds. [N.J.A.C. 7:27- 3.5]

None. None. None.

2 The engine emissions, exclusive of visible

condensed water vapor, shall not exceed anOpacity <= 10 %. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 TSP <= 1.27 lb/hr is the particulate emission

limit from the combustion of fuel based onrated heat input of the source. [N.J.A.C.7:27- 4.2(a)]

None. None. None.

4 Sulfur Content in Fuel <= 0.3 % sulfur by

weight is maximum allowable sulfur contentin fuel oil by fuel oil type/viscosity andgeographical zone (Zone 2 - WarrenCounty). [N.J.A.C. 7:27- 9.2(b)]

Other: Check fuel sulfur content by suppliercertification on each change of supplieroreach change of formulation.[N.J.A.C. 7:27-9.2(b)].

Other: Keep records of suppliercertification showing fuel sulfur content oneach change of supplier and each change offormulation.[N.J.A.C. 7:27- 9.2(a)].

None.

5 Engine fuel limited to Diesel fuel. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

6 The engine shall be limited to a Maximum

Gross Heat Input <= 2.115 MMBTU/hr(HHV). [N.J.A.C. 7:27-22.16(e)]

None. None. None.

OS Summary

Page 97 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 The emergency generator shall be located at

the facility and produce mechanical orthermal energy, or electrical powerexclusively for use at the facility. Thisemergency generator shall be operated only:1. During the performance of normal testingand maintenance procedures, asrecommended in writing by themanufacturer and/or as required in writingby a Federal or State law or regulation,2. When there is power outage or theprimary source of mechanical or thermalenergy fails because of an emergency, or3. When there is a voltage reduction issuedby PJM and posted on the PJM internetwebsite (www.pjm.com) under the"emergency procedures" menu. [N.J.A.C. 7:27-19.1]

Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]

Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem, the following information:1. For each time the emergency generator isspecifically operated for testing ormaintenance: i. The reason for its operation; ii. The date(s) of operation and the startup and shut down time; iii. The total operating time for testing ormaintenance based on the generator's hourmeter; and iv. The name of the operator; and2. If a voltage reduction is the reason for theuse of the emergency generator, a copy ofthe voltage reduction notification from PJMor other documentation of the voltagereduction.[N.J.A.C. 7:27-19.11].

None.

Page 98 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 This emergency generator shall not be used:

1. For normal testing and maintenance ondays when the Department forecasts airquality anywhere in New Jersey to be"unhealthy for sensitive groups,""unhealthy," or "very unhealthy" as definedin the EPA's Air Quality Index athttp://airnow.gov/, as supplemented oramended and incorporated herein byreference, unless required in writing by aFederal or State law or regulation.Procedures for determining the air qualityforecasts for New Jersey are available at theDepartment's air quality permitting web siteathttp://www.state.nj.us/dep/aqpp/aqforecast;and2. As a source of energy or power after theprimary energy or power source has becomeoperable again. If the primary energy orpower source is under the control of theowner or operator of the emergencygenerator, the owner or operator shall makea reasonable, timely effort to repair theprimary energy or power source. [N.J.A.C. 7:27-19.2(d)]

None. None. None.

9 The Permittee shall, once per month, record

the total operating time from the generator'shour meter. [N.J.A.C. 7:27-19.11]

Monitored by hour/time monitorcontinuously . [N.J.A.C. 7:27-22.16(o)]

Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem the total operating time from thegenerator's hour meter. Once per month.[N.J.A.C. 7:27-19.11].

None.

Page 99 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

10 Hours of Operation <= 60 hr/yr. The

Permittee shall comply with the above hourper year limit for normal testing andmaintenance. [N.J.A.C. 7:27-22.16(a)]

Hours of Operation: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Other: The Permittee shall record thefollowing in either a logbook or computerdata system each time the emergencygenerator is operated for testing andmaintenance:1. The reason for its operation;2. The date(s) of operation and the start upand shut down time;3. The total operating time for testing ormaintenance based on the generator's hourmeter; and4. The name of the operator.[N.J.A.C. 7:27-19.11].

None.

11 NOx (Total) <= 0.328 tons/yr is the annual

emission limit, based on the fuel usage limit.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

12 All other emissions shall be below reporting

thresholds. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 100 of 101
New Jersey Department of Environmental Protection

Facility Specific Requirements

COVANTA WARREN ENERGY RESOURCE CO LP (85455) BOP090002

Emission Unit: U4 2.115 MMBTU/hr Diesel Engine driven Emergency Generator for Water Supply Pump

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 VOC (Total) <= 0.86 lb/hr based on heat

input, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 NOx (Total) <= 10.93 lb/hr based on heat

input, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 CO <= 2.34 lb/hr based on heat input, from

preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

4 SO2 <= 0.61 lb/hr , from application for

operating permit. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 TSP <= 0.78 lb/hr based on heat input, from

preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. None. None.

6 PM-10 (Total) <= 0.78 lb/hr based on heat

input, from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

OS1 Firing Diesel fuel

Page 101 of 101
COVANTA WARREN ENERGY RESOURCE CO LP (85455) Date: 11/30/2009

BOP090002

New Jersey Department of Environmental Protection

Facility Profile (General)

Municipal Solid Waste Incineration 4953 

4931 

State Plane Coordinates:

X-Coordinate:

Y-Coordinate:

Units:

Datum:

Source Org.:

Source Type:

County: Industry:

Location

Description: Primary SIC:

Secondary SIC:

Warren

Mailing

Address:

Street

Address:

218 MOUNT PISGAH AVE

OXFORD, NJ 07863

218 MOUNT PISGAH AVE

OXFORD, NJ 07863

Facility Name (AIMS): COVANTA WARREN ENERGY RESOURCE Facility ID (AIMS): 85455

NAICS:

Page 1 of 3
COVANTA WARREN ENERGY RESOURCE CO LP (85455) Date: 11/30/2009

BOP090002

New Jersey Department of Environmental Protection

Facility Profile (General)

(908) 453-3763 x 

( ) - x 

vcamporine@covantaenergy.com

Covanta Warren Energy Resource Co. L.P.

Victor Camporine

Environmental Specialist

(908) 453-2195 x 218 Mount Pisgah Avenue

Oxford, NJ 07863

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: Air Permit Information Contact

(908) 453-3763 x 

( ) - x 

Covanta Warren Energy Resource Co. L.P.

Victor Camporine

(908) 453-2195 x 218 Mount Pisgah Avenue

Oxford, NJ 07863

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: BOP - Operating Permits

(732) 968-5279 x 

( ) - x 

lubbert@rtpenv.com

RTP Environmental Associates, Inc.

Brian L. Lubbert

Senior Scientist / Project Manager

(732) 968-9600 x 239 US Highway 22 East

Green Brook, NJ 08812

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Private

NJ EIN:

Contact Type: Consultant

Page 2 of 3
COVANTA WARREN ENERGY RESOURCE CO LP (85455) Date: 11/30/2009

BOP090002

New Jersey Department of Environmental Protection

Facility Profile (General)

(908) 453-3763 x 

( ) - x 

Covanta Warren Energy Resource Co. L.P.

Howard Otinsky, Jr.

Facility Manager

(908) 453-2195 x2220 218 Mount Pisgah Avenue

Oxford, NJ 07863

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: On-Site Manager

( ) - x 

( ) - x 

Covanta Energy

( ) - x 

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

LP

NJ EIN:

Contact Type: Owner (Current Primary)

(908) 453-3763 x 

( ) - x 

Covanta Warren Energy Resource Co. L.P.

Craig E. Durr

Facility Manager

(908) 453-2195 x2220 218 Mount Pisgah Avenue

Oxford, NJ 07863

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: Responsible Official

Page 3 of 3
COVANTA WARREN ENERGY RESOURCE CO LP (85455)

BOP090002

New Jersey Department of Environmental Protection

Reason for Application

Date:11/30/2009

 Permit Being Modified

Permit Class: BOP Number:80003

Description

of Modifications:

This modification adds a requirement from 40CFR 60.58b(i)(8) and (9) which allows the

maximum demonstrated particulate control device temperature at the control device inlet ,

as determined during dioxin/furan testing on one unit annually, to be applied to both units.

Page 1 of 1
COVANTA WARREN ENERGY RESOURCE CO LP (85455)

BOP090002

New Jersey Department of Environmental Protection

Non-Source Fugitive Emissions

FG

 NJID

Description of 

Activity Causing

Emission

Location 

Description

Reasonable Estimate of Emissions (tpy)

VOC

(Total)

NOx CO SO TSP

(Total)

PM-10 Pb H

(

FG1 Material Handling and

ManufacturingOperations

All outdoor areas 0.000 0.000 0.000 0.000 2.000 2.000 0.000 

FG2 Architectual Coating Facility equipment and

structures

1.000 0.000 0.000 0.000 0.000 0.000 0.000 

Total 1.000 0.000 0.000 0.000 2.000 2.000 0.000 

Page 1 of 1
COVANTA WARREN ENERGY RESOURCE CO LP (85455)

BOP090002

New Jersey Department of Environmental Protection

Insignificant Source Emissions 

IS

 NJID

Source/Group

Description

Equipment Type Location 

Description

Estimate of Emissions (tpy

VOC

(Total)

NOx CO SO TSP PM-10 

IS1 Heated Non-VOC

Surface Cleaners (PartsCleaners) that usecleaning solutionscontaining no VOCs, orHAPs

Cleaning Machine (OpenTop: Cold)

Machine shop,(west end)

0.000 0.000 0.000 0.000 0.000 

IS2 Kerosene, Diesel &

Used Oil Storage Tanks(< 2,000 gallons)

Storage Vessel North side of ash

storage buildingand inside andoutside fire pumproom

0.000 0.000 0.000 0.000 0.000 

IS3 Sulfuric Acid Storage

tank (< 10,000 gallons)

Storage Vessel 0.000 0.000 0.000 0.000 0.000 

IS6 Bins (< 2,000 cubic

feet)

Storage Vessel 0.000 0.000 0.000 

IS8 Cooling tower Other Equipment cooling towers 0.000 0.000 0.000 0.000 1.340 1.340 IS10 Fuel Oil Storage Tank

(> 10,000 gallons)

Storage Vessel South side

IncineratorBuilding

0.000 0.000 0.000 0.000 0.000 

IS11 Pebble Lime storage

bin (< 2,000 cu. ft.)

Storage Vessel 0.000 0.000 0.000 0.000 0.160 0.160 

IS20 Urea Tank Storage Vessel SNCR SystemIS21 kerosene fired Portable

Space Heaters (10)

Fuel CombustionEquipment (Other)

portable

Total 0.000 0.000 0.000 0.000 1.500 1.500 

Page 1 of 1
Equip.

NJID

Facility's 

Designation

Equipment

Description

Equipment Type Certificate

Number

Install

Date

GrandFathered L

(S

New Jersey Department of Environmental Protection

Equipment Inventory

BOP090002COVANTA WARREN ENERGY RESOURCE CO LP (85455) 

E1 07-4 Incine1 Incinerator Unit #1 Incinerator 076910 (PCP960004) 6/13/1986 No 4/1E2 07-4 Incine2 Incinerator Unit #2 Incinerator 076910 (PCP960004) 6/13/1986 No 4/1E4 Carbon Silo Carbon silo Storage Vessel 129793 (PCP960010) 10/10/1995 No E6 Fly Ash Conv Fly ash conveyor & surge bin Manufacturing and 85197 (PCP960003) 6/30/1988 No 

Materials HandlingEquipment

E8 Fly Ash Cond Combustor ash and Fly ash 98485 (PCP960008) 2/27/1990 No 

Mixing / Handling System

Manufacturing andMaterials HandlingEquipment

E9 Non Ferrous Non Ferrous system Manufacturing and 10/1/2008 No 

Materials HandlingEquipment

E10 Ferrous Ferrous ssytem Manufacturing and 2/27/1990 No 

Materials HandlingEquipment

E13 Ash St Conv Ash storage conveyor/truck 98486 (PCP960009) 2/27/1990 No 

loading

Manufacturing andMaterials HandlingEquipment

E15 15-09 Fire P Diesel engine driven pump for 85198 (PCP960006) 7/12/1988 No 

Fire protection

Stationary ReciprocatingEngine

E16 15-26 WaterS Diesel emergency generator for 85555 (PCP960007) 7/12/1988 No 

Water supply pump

Stationary ReciprocatingEngine

Page 1 of 1
COVANTA WARREN ENERGY RESOURCE CO LP (85455) Da

New Jersey Department of Environmental Protection

Control Device Inventory

CD

 NJID

Facility's 

Designation

Description CD Type Install

Date

GrandFathered Last Mod. (Since 1968) 

BOP090002

CD1 SprayDryer#1 Spray Dryer - Unit 1 Scrubber (Other) 7/3/1988 NoCD2 Baghouse #1 Baghouse - Unit 1 Particulate Filter 7/3/1988 No

(Baghouse)

CD3 Carbon injection/mercury

control-Unit 1

Carbon Inj#1 Adsorber 1/1/1996 No

CD4 SprayDryer#2 Spray Dryer - Unit 2 Scrubber (Other) 7/3/1988 NoCD5 Baghouse #2 Baghouse - Unit 2 Particulate Filter 7/3/1988 No

(Baghouse)

CD6 Carbon injection/mercury

control-Unit 2

Carbon Inj#2 Adsorber 1/1/1996 No

CD8 VF-4 CarboBH Fabric Filter for Carbon Silo Particulate Filter 1/1/1996 No

(Baghouse)

CD9 Cartridge Filter for Ash Surge

Bin

09-25 BinS C Particulate Filter 7/3/1988 No 4/15/1992

(Cartridge)

CD10 Cartridge Filter for Ash Mixing

Building Exhaust

EF-7 Mix C Particulate Filter 10/3/1989 No

(Cartridge)

CD11 Cartridge Filter for Ash Storage

Building East Exhaust

EF-9 EStor C Particulate Filter 10/3/1989 No

(Cartridge)

CD12 Cartridge Filter for Ash Storage

Building West Exhaust

EF-10 WSto C Particulate Filter 10/3/1989 No

(Cartridge)

CD13 SNCR #1 SNCR Control System Selective Non-Catalytic 10/31/2005 No

Reduction

CD14 SNCR #2 SNCR Control System Selective Non-Catalytic 10/31/2005 No

Reduction

Page 1 of 1
COVANTA WARREN ENERGY RESOURCE CO LP (85455) 

New Jersey Department of Environmental Protection

Emission Points Inventory

PT

 NJID

Facility's 

Designation

Description Config. Equiv.

Diam.

(in.)

Height

(ft.)

Dist. to

Prop.

Line (ft)

Exhaust Temp. (deg. F) Exhaust V

Avg. Min. Max. Avg. Mi

BOP090002

PT1 07-4 Stack 1 Combustor 1 stack Round 48 250 240 240.0 320.0 37PT2 07-4 Stack 2 Combustor 2 stack Round 48 250 240 240.0 320.0 37PT4 VF-4 Carbo V Carbon silo vent from filter Rectangle 12 50 200 70.0 70.0 70.0 PT6 09-25 Ash V Ash surge bin vent from filter Rectangle 12 36 165 70.0 70.0 70.0 PT7 EF-7 Mix Ex Ash mixing building exhaust

fan filter vent

Square 17 26 175 70.0 70.0 70.0 1,500.0 1

PT8 EF-9 EStorEx Ash storage building east

exhaust fan filter vent

Rectangle 36 26 125 70.0 70.0 70.0 14,000.0 14

PT9 EF-10 WStorX Ash storage building west

exhaust fan filter vent

Rectangle 36 26 125 70.0 70.0 70.0 14,000.0 14

PT10 15-09 Fire IC engine for Fire protection

pump

Round 6 16 260 70.0 70.0 1,026.0 

PT11 15-26 Water IC engine for Water supply

system

Round 8 20 17 70.0 70.0 965.0 1

Page 1 of 1
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

COVANTA WARREN ENERGY RESOURCE CO LP (85455)BOP090002

U 1 Incinerators Two nominal 274 TPD Municipal Solid Waste Combustors (with Carbon silo) subject to NSPS Eb, 40 CFR 60 Subpar

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 07-4 C1-Norm 89 MM BTU/hr

Combustor #1 (E1)burning MSW and/orusing No. 2 Fuel Oil withcontrol by scrubber,carbon adsorption,baghouse and SNCR

Normal - SteadyState

E1 CD1 (P)

CD13 (P)CD2 (S)CD3 (T)

PT1 7,446.0 8,760.0 

OS2 07-4 C1-Malf Combustor #1 under

emergency malfunction

Malfunction E1 CD1 (P)

CD13 (P)CD2 (S)CD3 (T)

PT1 0.0 500.0 

OS3 07-4 C2-Norm 89 MM BTU/hr

Combustor #2 (E2)burning MSW and/orusing No. 2 Fuel Oil withcontrol by scrubber,carbon adsorption,baghouse and SNCR

Normal - SteadyState

E2 CD14 (P)

CD4 (P)CD5 (S)CD6 (T)

PT2 7,446.0 8,760.0 

OS4 07-4 C2-Malf Combustor #2 under

emergency malfunction

Malfunction E2 CD14 (P)

CD4 (P)CD5 (S)CD6 (T)

PT2 0.0 500.0 

OS5 Carbon Op Filling Carbon silo (E4)

with emissions controlledby Baghouse (CD8)

Normal - SteadyState

E4 CD8 (P) PT4 8,322.0 8,760.0 

Page 1 of 3
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

COVANTA WARREN ENERGY RESOURCE CO LP (85455)BOP090002

U 2 Ash System Ash Handling System

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 09-25 Fly ash conveyor & surge

bin (E6) venting toCartridge Filter (CD9)

Normal - SteadyState

E6 CD9 (P) PT6 8,322.0 8,760.0 

OS2 EF-7 Combustor ash and Fly

ash Mixing operation(E12), venting toCartridge Filter (CD10)

Normal - SteadyState

E8 CD10 (P) PT7 8,322.0 8,760.0 

OS3 EF-9/10 Ash storage & Truck

Loading (E13), ExhaustFan (EF-9)/ CartridgeFilter (CD11) & ExhaustFan (EF-10)/ CartridgeFilter (CD12)

Normal - SteadyState

E13 CD11 (P)

CD12 (P)

PT8 PT9 

8,322.0 8,760.0 

OS4 Nonferrous Non Ferrous Recovery

System E9

Normal - SteadyState

E9 PT8 

PT9 

8,322.0 8,760.0

OS5 Ferrous Ferrous Recovery System

E10

Normal - SteadyState

E10 PT8 

PT9 

8,322.0 8,760.0

Page 2 of 3
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

COVANTA WARREN ENERGY RESOURCE CO LP (85455)BOP090002

U 3 15-09 FiPump 1.847 MMBTU/hr Diesel Engine driven Pump for Fire Protection

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 15-09 F Engi Firing Diesel fuel Normal - Steady

State

E15 PT10 2.0 500.0 

U 4 15-26 WtrGen 2.115 MMBTU/hr Diesel Engine driven Emergency Generator for Water Supply Pump

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 15-26 Engine Firing Diesel fuel Normal - Steady

State

E16 PT11 2.0 500.0 

Page 3 of 3
New Jersey Department of Environmental Protection

Subject Item Group Inventory

Group NJID: GR1 NSPS Regulat

Members: Type ID OS Step 

E E 1E E 13E E 2E E 6E E 8

Formal Reason(s) for Group/Cap:

9 Other

Other (explain): Common NSPS regulations

Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group: Operating Circumstances:

Page 1 of 1