### Name: Patricia Q. West

Title: Manager, Environmental, Energy Supp Company: Progress Energy Florida, Inc. Sign Date: 9/3/2010 Name: Michael Sussman, P.E. Title: Project Manager Company:Kleinfelder Southeast, Inc. Sign Date: 9/3/2010 Permitted Facility Representative / Date Testing Company Representative / Date



## Progress Energy Florida Suwannee River Power Plant Unit 2 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Thursday, February 17, 2011 Page 1 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 Facility Information: Progress Energy Florida, Inc. Suwannee Riv 4037 River Road

Live Oak FL32060 Contact:Cary W. Hamilton Phone: Fax: Email:cary.hamilton@pgnmail.com Testing Company: Kleinfleder Southeast Inc. 6200 Harris Technology Blvd.

Charlotte NC28269 Contact:W. Quentin Best Phone:704-598-1049 Fax:704-598-1050 Email:qbest@kleinfelder.com

Air Permit Number: 1210003-007-AV Permitted Source ID/Name: Fossil Fuel Fired Steam Generator Unit No. 1 Suw Unit 1 Permitted Maximum Process Rate: 450 million Btu/hr Max. Normal Operation Process Rate: N/A Target Process Test Rate N/A Industry/SCC/NAIS221121 AFS #:1212100003 FRS #:110000909214

SCC / Description10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Regulation Description Compound Limit Unit ICR % H2O 0 percent(%) ICR 1,2,3,4,6,7,8-HpCDD 0 ng/dscm corrected ICR 1,2,3,4,6,7,8-HpCDD 0 lb/million BTU using O2 ICR 1,2,3,4,6,7,8-HpCDF 0 ng/dscm corrected ICR 1,2,3,4,6,7,8-HpCDF 0 lb/million BTU using O2 ICR 1,2,3,4,7,8,9-HpCDF 0 ng/dscm corrected ICR 1,2,3,4,7,8,9-HpCDF 0 lb/million BTU using O2 ICR 1,2,3,4,7,8-HxCDD 0 ng/dscm corrected ICR 1,2,3,4,7,8-HxCDD 0 lb/million BTU using O2 ICR 1,2,3,4,7,8-HxCDF 0 ng/dscm corrected ICR 1,2,3,4,7,8-HxCDF 0 lb/million BTU using O2 ICR 1,2,3,6,7,8-HxCDD 0 ng/dscm corrected ICR 1,2,3,6,7,8-HxCDD 0 lb/million BTU using O2 ICR 1,2,3,6,7,8-HxCDF 0 ng/dscm corrected ICR 1,2,3,6,7,8-HxCDF 0 lb/million BTU using O2 ICR 1,2,3,7,8,9-HxCDD 0 ng/dscm corrected



### Thursday, February 17, 2011 Page 2 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 ICR 1,2,3,7,8,9-HxCDD 0 lb/million BTU using O2 ICR 1,2,3,4,6,7,8-HpCDF 0 ng/dscm corrected ICR 1,2,3,7,8,9-HxCDF 0 lb/million BTU using O2 ICR 1,2,3,7,8-PeCDD 0 ng/dscm corrected ICR 1,2,3,7,8-PeCDD 0 lb/million BTU using O2 ICR 1,2,3,7,8-PeCDF 0 ng/dscm corrected ICR 1,2,3,7,8-PeCDF 0 lb/million BTU using O2 ICR 2,3,3',4,4',5,5'-HpCB (PCB189) 0 ng/dscm corrected

ICR 2,3,3',4,4',5,5'-HpCB (PCB189) 0 lb/million BTU using O2 ICR 2,3,3',4,4',5/2,3,3',4,4',5'- HxCB (PCBs156/157) 0 ng/dscm corrected

ICR 2,3,3',4,4',5/2,3,3',4,4',5'- HxCB (PCBs156/157) 0 lb/million BTU using O2 ICR 2,3,3',4,4'-PeCB (PCB105) 0 ng/dscm corrected ICR 2,3,3',4,4'-PeCB (PCB105) 0 lb/million BTU using O2 ICR 2,3',4,4',5,5'-HxCB (PCB167) 0 ng/dscm corrected

ICR 2,3',4,4',5,5'-HxCB (PCB167) 0 lb/million BTU using O2 ICR 2,3,4,4',5-PeCB (PCB114) 0 ng/dscm corrected ICR 2,3,4,4',5-PeCB (PCB114) 0 lb/million BTU using O2 ICR 2,3',4,4',5-PeCB (PCB118) 0 ng/dscm corrected ICR 2,3',4,4',5-PeCB (PCB118) 0 lb/million BTU using O2 ICR 2',3,4,4',5-PeCB (PCB123) 0 ng/dscm corrected ICR 2',3,4,4',5-PeCB (PCB123) 0 lb/million BTU using O2 ICR 2,3,4,6,7,8-HxCDF 0 ng/dscm corrected ICR 2,3,4,6,7,8-HxCDF 0 lb/million BTU using O2 ICR 2,3,4,7,8-PeCDF 0 ng/dscm corrected ICR 2,3,4,7,8-PeCDF 0 lb/million BTU using O2 ICR 2,3,7,8-TCDD 0 ng/dscm corrected ICR 2,3,7,8-TCDD 0 lb/million BTU using O2 ICR 2,3,7,8-TCDF 0 ng/dscm corrected ICR 2,3,7,8-TCDF 0 lb/million BTU using O2 ICR 2-Methylnaphthalene 0 ng/dscm corrected ICR 2-Methylnaphthalene 0 lb/million BTU using O2 ICR 3,3',4,4',5,5'-HxCB (PCB169) 0 ng/dscm corrected



### Thursday, February 17, 2011 Page 3 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 ICR 3,3',4,4',5,5'-HxCB (PCB169) 0 lb/million BTU using O2 ICR 3,3',4,4',5-PeCB (PCB126) 0 ng/dscm corrected ICR 3,3',4,4',5-PeCB (PCB126) 0 lb/million BTU using O2 ICR 3,3',4,4'-TCB (PCB77) 0 ng/dscm corrected ICR 3,3',4,4'-TCB (PCB77) 0 lb/million BTU using O2 ICR 3,4,4',5-TCB (PCB81) 0 ng/dscm corrected ICR 3,4,4',5-TCB (PCB81) 0 lb/million BTU using O2 ICR Acenaphthene** 0 ug/dscm corrected ICR Acenaphthene** 0 lb/million BTU using O2 ICR Acenaphthylene** 0 ug/dscm corrected ICR Acenaphthylene** 0 lb/million BTU using O2 ICR Anthracene** 0 ug/dscm corrected ICR Anthracene** 0 lb/million BTU using O2 ICR Antimony 0 lb/million BTU using O2 ICR Arsenic 0 lb/million BTU using O2 ICR Barium 0 lb/million BTU using O2 ICR Benzo(a)Anthracene* 0 ug/dscm corrected ICR Benzo(a)Anthracene* 0 lb/million BTU using O2 ICR Benzo(a)Pyrene* 0 ug/dscm corrected ICR Benzo(a)Pyrene* 0 lb/million BTU using O2 ICR Benzo(b)Fluoranthene* 0 ug/dscm corrected ICR Benzo(b)Fluoranthene* 0 lb/million BTU using O2 ICR Benzo(e)Pyrene 0 ug/dscm corrected ICR Benzo(e)Pyrene 0 lb/million BTU using O2 ICR Benzo(ghi)Perylene** 0 ug/dscm corrected ICR Benzo(ghi)Perylene** 0 lb/million BTU using O2 ICR Benzo(k)Fluoranthene* 0 ug/dscm corrected ICR Benzo(k)Fluoranthene* 0 lb/million BTU using O2 ICR Beryllium 0 lb/million BTU using O2 ICR Bromine 0 lb/million BTU using O2 ICR Cadmium 0 lb/million BTU using O2 ICR Carbon Monoxide 0 ppm corrected ICR Carbon Monoxide 0 lb/million BTU using O2 

### Thursday, February 17, 2011 Page 4 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 ICR Chromium 0 lb/million BTU using O2 ICR Chrysene* 0 ug/dscm corrected ICR Chrysene* 0 lb/million BTU using O2 ICR Co2 0 percent(%) ICR Cobalt 0 lb/million BTU using O2 ICR Copper 0 lb/million BTU using O2 ICR Dibenzo(a,h)Anthracene* 0 ng/dscm corrected ICR Dibenzo(a,h)Anthracene* 0 lb/million BTU using O2 ICR Filterable Particulate 0 lb/million BTU using O2 ICR Filterable PM2.5 0 lb/million BTU using O2 ICR Fluoranthene** 0 ug/dscm corrected ICR Fluoranthene** 0 lb/million BTU using O2 ICR Fluorene** 0 ug/dscm corrected ICR Fluorene** 0 lb/million BTU using O2 ICR Formaldehyde 0 ppm corrected ICR Formaldehyde 0 lb/million BTU using O2 ICR Hydrogen Chloride 0 lb/million BTU using O2 ICR Hydrogen Fluoride 0 lb/million BTU using O2 ICR Indeno(1,2,3-cd)Pyrene* 0 ug/dscm corrected ICR Indeno(1,2,3-cd)Pyrene* 0 lb/million BTU using O2 ICR Inorganic (Aqueous) Condensible Part. 0 lb/million BTU using O2 ICR Lead 0 lb/million BTU using O2 ICR Magnesium 0 lb/million BTU using O2 ICR Manganese 0 lb/million BTU using O2 ICR Mercury 0 lb/million BTU using O2 ICR Naphthalene** 0 ug/dscm corrected ICR Naphthalene** 0 lb/million BTU using O2 ICR Nickel 0 lb/million BTU using O2 ICR Nitrogen oxides (NOx) 0 ppm corrected ICR Nitrogen oxides (NOx) 0 lb/million BTU using O2 ICR O2 0 percent(%) ICR OCDD 0 ng/dscm corrected



### Thursday, February 17, 2011 Page 5 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 ICR OCDD 0 lb/million BTU using O2 ICR OCDF 0 ng/dscm corrected ICR OCDF 0 lb/million BTU using O2 ICR Organic Condensible Particulate 0 lb/million BTU using O2 ICR Other Di-CBs 0 ng/dscm corrected ICR Other Di-CBs 0 lb/million BTU using O2 ICR Other Hepta-CBs 0 ng/dscm corrected ICR Other Hepta-CBs 0 lb/million BTU using O2 ICR Other Hexa-CBs 0 ng/dscm corrected ICR Other Hexa-CBs 0 lb/million BTU using O2 ICR Other HpCDD 0 ng/dscm corrected ICR Other HpCDD 0 lb/million BTU using O2 ICR Other HpCDF 0 ng/dscm corrected ICR Other HpCDF 0 lb/million BTU using O2 ICR Other HxCDD 0 ng/dscm corrected ICR Other HxCDD 0 lb/million BTU using O2 ICR Other HxCDF 0 ng/dscm corrected ICR Other HxCDF 0 lb/million BTU using O2 ICR Other Mono-CBs 0 ug/dscm corrected ICR Other Mono-CBs 0 lb/million BTU using O2 ICR Other Nona-CBs 0 ng/dscm corrected ICR Other Nona-CBs 0 lb/million BTU using O2 ICR Other Octa-CBs 0 ng/dscm corrected ICR Other Octa-CBs 0 lb/million BTU using O2 ICR Other PeCDD 0 ng/dscm corrected ICR Other PeCDD 0 lb/million BTU using O2 ICR Other PeCDF 0 ng/dscm corrected ICR Other PeCDF 0 lb/million BTU using O2 ICR Other Penta-CBs 0 ng/dscm corrected ICR Other Penta-CBs 0 lb/million BTU using O2 ICR Other TCDD 0 ng/dscm corrected ICR Other TCDD 0 lb/million BTU using O2 ICR Other TCDF 0 ng/dscm corrected ICR Other TCDF 0 lb/million BTU using O2 

### Thursday, February 17, 2011 Page 6 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 ICR Other Tetra-CBs 0 ng/dscm corrected ICR Other Tetra-CBs 0 lb/million BTU using O2 ICR Other Tri-CBs 0 ng/dscm corrected ICR Other Tri-CBs 0 lb/million BTU using O2 ICR Perylene 0 ug/dscm corrected ICR Perylene 0 lb/million BTU using O2 ICR Phenanthrene** 0 ug/dscm corrected ICR Phenanthrene** 0 lb/million BTU using O2 ICR Phosphorus (yellow or white) 0 lb/million BTU using O2 ICR Pyrene** 0 ug/dscm corrected ICR Pyrene** 0 lb/million BTU using O2 ICR Selenium 0 lb/million BTU using O2 ICR Silver 0 lb/million BTU using O2 ICR Sulfur Dioxide 0 ppm corrected ICR Sulfur Dioxide 0 lb/million BTU using O2 ICR Thallium 0 lb/million BTU using O2 ICR Total 16*/**PAH 0 ug/dscm corrected ICR Total 16*/**PAH 0 lb/million BTU using O2 ICR Total 7*PAH 0 ug/dscm corrected ICR Total 7*PAH 0 lb/million BTU using O2 ICR Total Dioxins 0 ng/dscm corrected ICR Total Dioxins 0 lb/million BTU using O2 ICR Total Furans 0 ng/dscm corrected ICR Total Furans 0 lb/million BTU using O2 ICR Total organic compounds (TOC) as Propane 0 ppm corrected

ICR Total organic compounds (TOC) as Propane 0 lb/million BTU using O2 ICR Total PCBs 0 ng/dscm corrected ICR Total PCBs 0 lb/million BTU using O2 ICR Total PM2.5 0 lb/million BTU using O2 ICR Total TEQ 0 ng/dscm corrected ICR Total TEQ 0 lb/million BTU using O2 ICR Zinc 0 lb/million BTU using O2 ICR Methane 0 ppm corrected 

### Thursday, February 17, 2011 Page 7 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Boiler No. 2 (E.U. ID No. -002) is a nominal 34.0 megawatt electric steam generator. The boiler is allowed to fireNo.2 fuel oil, No.6 fuel oil, “on specification” used oil, natural gas and a blend of fuel oil and natural gas. The “onspecification used oil is generally fired as blended fuel oil with either the No.2 fuel oil or No. 6 fuel oil. The boiler drives a turbine generator for electrical power and vents to its own stack. There is no air pollution equipment control devices associated with the boiler. Sampling Location Information:

Test Parameter Information: LocationRound

Duct Diam. Distance from upstream dist.Distance from

downstream dist.Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack Exit83.063 240 240 2 0 24 0 0

Target Parameter Test Method Number of

Test RunsTest Run

DurationSample

Points Comments Location2,3,7,8-TCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 Stack ExitOCDD Method 23 3 480 0 Stack Exit2,3,7,8-TCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0 Stack Exit2,3,4,7,8-PeCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0 Stack Exit2,3,4,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 Stack ExitOCDF Method 23 3 480 0 Stack ExitOther TCDD Method 23 3 480 0 Stack ExitOther PeCDD Method 23 3 480 0 Stack ExitOther HxCDD Method 23 3 480 0 Stack ExitOther HpCDD Method 23 3 480 0 Stack ExitOther TCDF Method 23 3 480 0 Stack ExitOther PeCDF Method 23 3 480 0 Stack ExitOther HxCDF Method 23 3 480 0 Stack ExitOther HpCDF Method 23 3 480 0 Stack ExitTotal Dioxins Method 23 3 480 0 Stack ExitTotal Furans Method 23 3 480 0 Stack Exit3,3',4,4'-TCB (PCB77) Method 23 3 480 0 Stack Exit ICR Methane 0 lb/million BTU using O2 ICR Hydrogen Cyanide 0 lb/million BTU using O2



### Thursday, February 17, 2011 Page 8 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

3,4,4',5-TCB (PCB81) Method 23 3 480 0 Stack Exit2,3,3',4,4'-PeCB (PCB105)Method 23 3 480 0 Stack Exit2,3,4,4',5-PeCB (PCB114)Method 23 3 480 0 Stack Exit2,3',4,4',5-PeCB (PCB118)Method 23 3 480 0 Stack Exit2',3,4,4',5-PeCB (PCB123)Method 23 3 480 0 Stack Exit3,3',4,4',5-PeCB (PCB126)Method 23 3 480 0 Stack Exit2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 Stack Exit

2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 0 Stack Exit3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 0 Stack Exit2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 Stack Exit
Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Exit



### Thursday, February 17, 2011 Page 9 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 Sampling / Stack Data Results Summary



### LocationStack Exit - Method 23 Average Run Number 1 2 3 Test Date 6/15/20106/21/2010 6/22/2010 Run Start Time 2:25:00 PM9:29:00 PM8:44:00 AM Run Finish Time 10:40:00 PM9:29:00 PM5:11:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 349.681 312.560 314.756 325.666 Moisture Content of Stack Gas, % 6.31 7.51 7.89 7.237 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 10.165 9.859 10.248 10.091 Oxygen, % 8.944 8.867 8.564 8.792 Average Stack Gas Temperature, °F 320.17 324.21 317.92 320.767 Dry Volumetric Flow Rate, dry scfm 100,401.595,132.2 95,897.197,143.600 Actual Wet Volumetric Flue Gas Flow Rate, acfm 158,185.7152,563.6 152,676.5154,475.267 Percent Isokinetic of Sampling Rate, % 100.7 99.4 99.3 99.800 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 17, 2011 Page 10 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 Emissions Summary



### Location:Stack Exit - Method 23 Compound:1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.00000000425 0.00000000389 0.00000000483 0.000 Elb/hr 1.61E-10 1.57E-10 1.95E-10 0.000 lb/mmBtuO2 4.30E-13 4.38E-13 5.27E-13 0.000 ng/dscm 4.29E-04 4.40E-04 5.42E-04 0.000 ng/dscm@7%O2 4.99E-04 5.08E-04 6.11E-04 0.001 

### Compound:1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.00000000317 0.00000000393 0.0000000028 0.000 Elb/hr 1.20E-10 1.58E-10 1.13E-10 0.000 lb/mmBtuO2 3.21E-13 4.42E-13 3.05E-13 0.000 ng/dscm 3.20E-04 4.44E-04 3.14E-04 0.000 ng/dscm@7%O2 3.72E-04 5.13E-04 3.54E-04 0.000 

### Compound:1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.00000000253 0.00000000279 0.00000000212 0.000 Elb/hr 9.61E-11 1.12E-10 8.54E-11 0.000 lb/mmBtuO2 2.56E-13 3.14E-13 2.31E-13 0.000 ng/dscm 2.56E-04 3.15E-04 2.38E-04 0.000 ng/dscm@7%O2 2.98E-04 3.64E-04 2.68E-04 0.000 

### Compound:1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.00000000242 0.00000000212 0.0000000019 0.000 Elb/hr 9.19E-11 8.54E-11 7.66E-11 0.000 lb/mmBtuO2 2.45E-13 2.39E-13 2.07E-13 0.000 ng/dscm 2.44E-04 2.40E-04 2.13E-04 0.000 ng/dscm@7%O2 2.84E-04 2.77E-04 2.40E-04 0.000 

### Compound:1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.00000000316 0.00000000455 0.00000000254 0.000 Elb/hr 1.20E-10 1.83E-10 1.02E-10 0.000 lb/mmBtuO2 3.20E-13 5.12E-13 2.77E-13 0.000 ng/dscm 3.19E-04 5.14E-04 2.85E-04 0.000 ng/dscm@7%O2 3.71E-04 5.94E-04 3.21E-04 0.000 

### Compound:1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.00000000232 0.0000000022 0.00000000185 0.000 Elb/hr 8.81E-11 8.86E-11 7.46E-11 0.000



### Thursday, February 17, 2011 Page 11 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 lb/mmBtuO2 2.35E-13 2.48E-13 2.02E-13 0.000 ng/dscm 2.34E-04 2.49E-04 2.08E-04 0.000 ng/dscm@7%O2 2.72E-04 2.88E-04 2.34E-04 0.000 

### Compound:1,2,3,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.00000000243 0.00000000352 0.00000000198 0.000 Elb/hr 9.23E-11 1.42E-10 7.98E-11 0.000 lb/mmBtuO2 2.46E-13 3.96E-13 2.16E-13 0.000 ng/dscm 2.45E-04 3.98E-04 2.22E-04 0.000 ng/dscm@7%O2 2.85E-04 4.60E-04 2.50E-04 0.000 

### Compound:1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000026 0.00000000238 0.000000002 0.000 Elb/hr 9.87E-11 9.58E-11 8.06E-11 0.000 lb/mmBtuO2 2.63E-13 2.68E-13 2.18E-13 0.000 ng/dscm 2.63E-04 2.69E-04 2.24E-04 0.000 ng/dscm@7%O2 3.06E-04 3.11E-04 2.52E-04 0.000 

### Compound:1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.00000000177 0.00000000174 0.00000000133 0.000 Elb/hr 6.72E-11 7.01E-11 5.36E-11 0.000 lb/mmBtuO2 1.79E-13 1.96E-13 1.45E-13 0.000 ng/dscm 1.79E-04 1.97E-04 1.49E-04 0.000 ng/dscm@7%O2 2.08E-04 2.28E-04 1.68E-04 0.000 

### Compound:1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.00000000236 0.00000000219 0.00000000164 0.000 Elb/hr 8.96E-11 8.82E-11 6.61E-11 0.000 lb/mmBtuO2 2.39E-13 2.47E-13 1.79E-13 0.000 ng/dscm 2.38E-04 2.47E-04 1.84E-04 0.000 ng/dscm@7%O2 2.77E-04 2.85E-04 2.07E-04 0.000 

### Compound:1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.00000000587 0.00000000696 0.00000000302 0.000 Elb/hr 2.23E-10 2.80E-10 1.22E-10 0.000 lb/mmBtuO2 5.95E-13 7.84E-13 3.29E-13 0.000 ng/dscm 5.93E-04 7.86E-04 3.39E-04 0.001 ng/dscm@7%O2 6.89E-04 9.08E-04 3.82E-04 0.001 

### Compound:2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.0000000242 0.0000000142 0.0000000189 0.000 Elb/hr 9.19E-10 5.72E-10 7.62E-10 0.000



### Thursday, February 17, 2011 Page 12 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 lb/mmBtuO2 2.45E-12 1.60E-12 2.06E-12 0.000 ng/dscm 2.44E-03 1.60E-03 2.12E-03 0.002 ng/dscm@7%O2 2.84E-03 1.85E-03 2.39E-03 0.002 

### Compound:2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.000000296 0.000000183 0.000000223 0.000 Elb/hr 1.12E-08 7.37E-09 8.99E-09 0.000 lb/mmBtuO2 3.00E-11 2.06E-11 2.43E-11 0.000 ng/dscm 2.99E-02 2.07E-02 2.50E-02 0.025 ng/dscm@7%O2 3.48E-02 2.39E-02 2.82E-02 0.029 

### Compound:2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.000000595 0.00000041 0.000000424 0.000 Elb/hr 2.26E-08 1.65E-08 1.71E-08 0.000 lb/mmBtuO2 6.03E-11 4.62E-11 4.62E-11 0.000 ng/dscm 6.01E-02 4.63E-02 4.76E-02 0.051 ng/dscm@7%O2 6.99E-02 5.35E-02 5.36E-02 0.059 

### Compound:2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.00000011 0.0000000652 0.0000000795 0.000 Elb/hr 4.18E-09 2.62E-09 3.20E-09 0.000 lb/mmBtuO2 1.11E-11 7.34E-12 8.67E-12 0.000 ng/dscm 1.11E-02 7.37E-03 8.92E-03 0.009 ng/dscm@7%O2 1.29E-02 8.51E-03 1.01E-02 0.011 

### Compound:2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.0000000371 0.0000000315 0.0000000269 0.000 Elb/hr 1.41E-09 1.27E-09 1.08E-09 0.000 lb/mmBtuO2 3.76E-12 3.55E-12 2.93E-12 0.000 ng/dscm 3.75E-03 3.56E-03 3.02E-03 0.003 ng/dscm@7%O2 4.36E-03 4.11E-03 3.40E-03 0.004 

### Compound:2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.00000155 0.00000103 0.00000112 0.000 Elb/hr 5.89E-08 4.15E-08 4.51E-08 0.000 lb/mmBtuO2 1.57E-10 1.16E-10 1.22E-10 0.000 ng/dscm 1.57E-01 1.16E-01 1.26E-01 0.133 ng/dscm@7%O2 1.83E-01 1.34E-01 1.42E-01 0.153 

### Compound:2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.0000000283 0.00000000893 0.0000000227 0.000 Elb/hr 1.07E-09 3.60E-10 9.15E-10 0.000



### Thursday, February 17, 2011 Page 13 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 lb/mmBtuO2 2.87E-12 1.01E-12 2.48E-12 0.000 ng/dscm 2.86E-03 1.01E-03 2.55E-03 0.002 ng/dscm@7%O2 3.33E-03 1.17E-03 2.87E-03 0.002 

### Compound:2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000013 0.00000000212 0.00000000102 0.000 Elb/hr 4.94E-11 8.54E-11 4.11E-11 0.000 lb/mmBtuO2 1.32E-13 2.39E-13 1.11E-13 0.000 ng/dscm 1.31E-04 2.40E-04 1.14E-04 0.000 ng/dscm@7%O2 1.52E-04 2.77E-04 1.28E-04 0.000 

### Compound:2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.00000000852 0.00000000971 0.0000000046 0.000 Elb/hr 3.24E-10 3.91E-10 1.85E-10 0.000 lb/mmBtuO2 8.63E-13 1.09E-12 5.02E-13 0.000 ng/dscm 8.61E-04 1.10E-03 5.16E-04 0.001 ng/dscm@7%O2 1.00E-03 1.27E-03 5.81E-04 0.001 

### Compound:2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.0000000026 0.00000000224 0.00000000136 0.000 Elb/hr 9.87E-11 9.02E-11 5.48E-11 0.000 lb/mmBtuO2 2.63E-13 2.52E-13 1.48E-13 0.000 ng/dscm 2.63E-04 2.53E-04 1.53E-04 0.000 ng/dscm@7%O2 3.06E-04 2.92E-04 1.72E-04 0.000 

### Compound:2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000194 0.0000000176 0.00000000853 0.000 Elb/hr 7.37E-10 7.09E-10 3.44E-10 0.000 lb/mmBtuO2 1.96E-12 1.98E-12 9.30E-13 0.000 ng/dscm 1.96E-03 1.99E-03 9.57E-04 0.002 ng/dscm@7%O2 2.28E-03 2.30E-03 1.08E-03 0.002 

### Compound:3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.00000000862 0.00000000844 0.0000000087 0.000 Elb/hr 3.27E-10 3.40E-10 3.51E-10 0.000 lb/mmBtuO2 8.73E-13 9.50E-13 9.49E-13 0.000 ng/dscm 8.71E-04 9.54E-04 9.76E-04 0.001 ng/dscm@7%O2 1.01E-03 1.10E-03 1.10E-03 0.001 

### Compound:3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.00000000834 0.00000000695 0.00000000596 0.000 Elb/hr 3.17E-10 2.80E-10 2.40E-10 0.000



### Thursday, February 17, 2011 Page 14 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 lb/mmBtuO2 8.45E-13 7.82E-13 6.50E-13 0.000 ng/dscm 8.42E-04 7.85E-04 6.69E-04 0.001 ng/dscm@7%O2 9.79E-04 9.07E-04 7.54E-04 0.001 

### Compound:3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.0000000973 0.0000000706 0.0000000462 0.000 Elb/hr 3.70E-09 2.84E-09 1.86E-09 0.000 lb/mmBtuO2 9.85E-12 7.95E-12 5.04E-12 0.000 ng/dscm 9.83E-03 7.98E-03 5.18E-03 0.008 ng/dscm@7%O2 1.14E-02 9.22E-03 5.84E-03 0.009 

### Compound:3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.00000000588 0.00000000602 0.00000000589 0.000 Elb/hr 2.23E-10 2.42E-10 2.37E-10 0.000 lb/mmBtuO2 5.96E-13 6.78E-13 6.42E-13 0.000 ng/dscm 5.94E-04 6.80E-04 6.61E-04 0.001 ng/dscm@7%O2 6.91E-04 7.86E-04 7.45E-04 0.001 

### Compound:OCDD Average RunNumber 1 2 3 Mass_mg 0.0000000284 0.0000000166 0.0000000315 0.000 Elb/hr 1.08E-09 6.68E-10 1.27E-09 0.000 lb/mmBtuO2 2.88E-12 1.87E-12 3.44E-12 0.000 ng/dscm 2.87E-03 1.88E-03 3.53E-03 0.003 ng/dscm@7%O2 3.34E-03 2.17E-03 3.98E-03 0.003 

### Compound:OCDF Average RunNumber 1 2 3 Mass_mg 0.00000000824 0.00000000862 0.00000000849 0.000 Elb/hr 3.13E-10 3.47E-10 3.42E-10 0.000 lb/mmBtuO2 8.35E-13 9.71E-13 9.26E-13 0.000 ng/dscm 8.32E-04 9.74E-04 9.53E-04 0.001 ng/dscm@7%O2 9.67E-04 1.13E-03 1.07E-03 0.001 

### Compound:Other HpCDD Average RunNumber 1 2 3 Mass_mg 0.00000000824 0.00000000389 0.00000000825 0.000 Elb/hr 3.13E-10 1.57E-10 3.32E-10 0.000 lb/mmBtuO2 8.35E-13 4.38E-13 9.00E-13 0.000 ng/dscm 8.32E-04 4.40E-04 9.26E-04 0.001 ng/dscm@7%O2 9.67E-04 5.08E-04 1.04E-03 0.001 

### Compound:Other HpCDF Average RunNumber 1 2 3 Mass_mg 0.00000000612 0.00000000393 0.00000000593 0.000 Elb/hr 2.32E-10 1.58E-10 2.39E-10 0.000



### Thursday, February 17, 2011 Page 15 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 lb/mmBtuO2 6.20E-13 4.42E-13 6.47E-13 0.000 ng/dscm 6.18E-04 4.44E-04 6.65E-04 0.001 ng/dscm@7%O2 7.18E-04 5.13E-04 7.49E-04 0.001 

### Compound:Other HxCDD Average RunNumber 1 2 3 Mass_mg 0.00000000244 0.00000000235 0.0000000027 0.000 Elb/hr 9.27E-11 9.46E-11 1.09E-10 0.000 lb/mmBtuO2 2.47E-13 2.65E-13 2.94E-13 0.000 ng/dscm 2.46E-04 2.66E-04 3.03E-04 0.000 ng/dscm@7%O2 2.86E-04 3.07E-04 3.41E-04 0.000 

### Compound:Other HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000124 0.0000000188 0.0000000105 0.000 Elb/hr 4.71E-10 7.57E-10 4.23E-10 0.000 lb/mmBtuO2 1.26E-12 2.12E-12 1.15E-12 0.000 ng/dscm 1.25E-03 2.12E-03 1.18E-03 0.002 ng/dscm@7%O2 1.45E-03 2.45E-03 1.33E-03 0.002 

### Compound:Other PeCDD Average RunNumber 1 2 3 Mass_mg 0.00000000236 0.00000000219 0.00000000164 0.000 Elb/hr 8.96E-11 8.82E-11 6.61E-11 0.000 lb/mmBtuO2 2.39E-13 2.47E-13 1.79E-13 0.000 ng/dscm 2.38E-04 2.47E-04 1.84E-04 0.000 ng/dscm@7%O2 2.77E-04 2.85E-04 2.07E-04 0.000 

### Compound:Other PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000441 0.0000000544 0.0000000278 0.000 Elb/hr 1.67E-09 2.19E-09 1.12E-09 0.000 lb/mmBtuO2 4.47E-12 6.12E-12 3.03E-12 0.000 ng/dscm 4.45E-03 6.15E-03 3.12E-03 0.005 ng/dscm@7%O2 5.17E-03 7.10E-03 3.52E-03 0.005 

### Compound:Other TCDD Average RunNumber 1 2 3 Mass_mg 0.0000000026 0.00000000224 0.00000000136 0.000 Elb/hr 9.87E-11 9.02E-11 5.48E-11 0.000 lb/mmBtuO2 2.63E-13 2.52E-13 1.48E-13 0.000 ng/dscm 2.63E-04 2.53E-04 1.53E-04 0.000 ng/dscm@7%O2 3.06E-04 2.92E-04 1.72E-04 0.000 

### Compound:Other TCDF Average RunNumber 1 2 3 Mass_mg 0.000000159 0.000000134 0.0000000682 0.000 Elb/hr 6.04E-09 5.39E-09 2.75E-09 0.000



### Thursday, February 17, 2011 Page 16 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Process Run Data lb/mmBtuO2 1.61E-11 1.51E-11 7.44E-12 0.000 ng/dscm 1.61E-02 1.51E-02 7.65E-03 0.013 ng/dscm@7%O2 1.87E-02 1.74E-02 8.62E-03 0.015 

### Compound:Total Dioxins Average RunNumber 1 2 3 Mass_mg 0.00000004894 0.00000003397 0.0000000512 0.000 Elb/hr 1.86E-09 1.37E-09 2.06E-09 0.000 lb/mmBtuO2 4.96E-12 3.82E-12 5.58E-12 0.000 ng/dscm 4.94E-03 3.84E-03 5.75E-03 0.005 ng/dscm@7%O2 5.74E-03 4.44E-03 6.48E-03 0.006 

### Compound:Total Furans Average RunNumber 1 2 3 Mass_mg 0.00000023546 0.00000022428 0.00000012846 0.000 Elb/hr 8.94E-09 9.03E-09 5.18E-09 0.000 lb/mmBtuO2 2.38E-11 2.53E-11 1.40E-11 0.000 ng/dscm 2.38E-02 2.53E-02 1.44E-02 0.021 ng/dscm@7%O2 2.77E-02 2.92E-02 1.62E-02 0.024



### Thursday, February 17, 2011 Page 17 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1Residual Oil Burned 2251.9 1000 Gallons/million BTU using O2Method 23 Run1 0 

### 1Average Heat Inpt 374.8Million Btu/hr 0 1Average Steam Output 312.71000 lb steam/hr0 2Residual Oil Burned 2306 1000 Gallons/million BTU using O2Method 23 Run 2 0 

### 2Average Heat Inpt 357.4Million Btu/hr 0 2Average Steam Output 312.71000 lb steam/hr0 3Residual Oil Burned 2310.1 1000 Gallons/million BTU using O2Method 23 Run 3 0 

### 3Average Heat Inpt 369.3Million Btu/hr 0 3Average Steam Output 312.61000 lb steam/hr0



### Run Name Value UOM Comments Target Value 1NA 0 0

Run Name ValueUOM Comments 

### 1Ash Content 0Percent 1Sulfur Content 0Percent 1BTU Content 0 BTU 

### 1Carbon Content 0Percent 1Hyrdrogen Content 0Precent 1Nitrogen Content 0Present



### Thursday, February 17, 2011 Page 18 of 19

### Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010 Sampling / Stack Data Results Detail



### LocationStack Exit - Method 23 Average Run Number 1 2 3 Test Date 6/15/20106/21/20106/22/2010 Run Start Time 2:25:00 PM9:29:00 PM8:44:00 AM Run Finish Time 10:40:00 PM9:29:00 PM5:11:00 PM Net Traversing Points 48 48 48 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.223 0.218 0.218 0.220 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.015 1.015 1.015 1.015 Barometric Pressure, inches of Mercury 29.92 29.93 30.03 29.960 Average Orifice Meter Differential, inches H2O 1.89 1.55 1.59 1.677 Dry Gas Meter Volume Sampled, cubic feet 364.905 323.827 325.951338.228 Average Dry Gas Meter Temperature, °F 101.85 97.54 99.19 99.527 Dry Gas Meter Volume Sampled, dscf 349.681 312.560 314.756325.666 Total Moisture Liquid collected, g 500.1 539.4 573537.500 Volume of Water Vapor, standard cubic feet 23.54 25.39 26.97 25.300 Moisture Content of Stack Gas, % 6.31 7.51 7.89 7.237 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00100.000 Dry Mole Fraction 0.9369 0.9249 0.9211 0.928 Carbon Dioxide, % 10.165 9.859 10.248 10.091 Oxygen, % 8.944 8.867 8.564 8.792 Carbon Monoxide & Nitrogen, % 80.891 81.274 81.188 81.118 Fuel Factor 1.18 1.22 1.20 Dry Molecular Weight, lb/lb-Mole 29.98 29.93 29.98 29.963 Wet Molecular weight, lb/lb-Mole 29.22 29.03 29.03 29.093 Flue Gas Static Pressure, inches of H2O 0.4 0.44 0.38 0.407 Absolute Flue Gas Pressure, inches of Mercury 29.95 29.96 30.06 29.990 Average Stack Gas Temperature, °F 320.17 324.21 317.92320.767 Average Velocity Head, inches of H2O 1.0675869796 61590.981916302

2175670.994717820

700524 1.015
Average Stack Gas Velocity, feet/second 70.06 67.57 67.62 68.417 Stack Cross-Sectional Area, square feet 37.631 37.631 37.631 37.631 Dry Volumetric Flow Rate, dry scfm 100,401.5 95,132.2 95,897.197,143.600 Actual Wet Volumetric Flue Gas Flow Rate, acfm 158,185.7152,563.6 152,676.5154,475.267 Percent Isokinetic of Sampling Rate, % 100.7 99.4 99.3 99.800 Percent Excess Air, % 72.1 70.4 66.5 69.667 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 83.063 83.063 83.063 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Thursday, February 17, 2011 Page 19 of 19