Federal Register / Vol. 86, No. 44 / Tuesday, March 9, 2021 / Notices 13535 

–0.35′′ w.c. Once the external static 

pressure is set, do not adjust the test 

duct for the remainder of the test. 

Measure furnace fan electrical input 

power (EMax), fuel or electric resistance 

heat kit input energy (QIN, Max), external 

static pressure (ESPMax), steady-state 

efficiency for this setting (EffySS, Max) as 

specified in sections 11.2 and 11.3 of 

ASHRAE 103–2007, outlet air 

temperature (TMax,Out), and temperature 

rise (DTMax). 

(3) Representations. ECR may not 

make representations about the energy 

use of a basic model listed in paragraph 

(1) of this Order for compliance, 

marketing, or other purposes, unless the 

basic model has been tested in 

accordance with the provisions set forth 

in the Order and such representations 

fairly disclose the results of such 

testing. 

(4) This waiver shall remain in effect 

according to the provisions of 10 CFR 

430.27. 

(5) DOE issues this waiver on the 

condition that the statements, 

representations, and information 

provided by ECR are valid and on the 

condition that ECR makes no 

representation on any public-facing 

materials, including websites, marketing 

materials, product spec sheets, labels, 

nameplates, etc., that these basic models 

are designed to be installed in systems 

that provide both heating and cooling. If 

ECR makes any modifications to the 

controls or configurations of these basic 

models, such modifications will render 

the waiver invalid with respect to that 

basic model, and ECR will either be 

required to use the current Federal test 

method or submit a new application for 

a test procedure waiver. DOE may 

rescind or modify this waiver at any 

time if it determines the factual basis 

underlying the petition for waiver is 

incorrect, or the results from the 

alternate test procedure are 

unrepresentative of a basic model’s true 

energy consumption characteristics. 10 

CFR 430.27(k)(1). Likewise, ECR may 

request that DOE rescind or modify the 

waiver if ECR discovers an error in the 

information provided to DOE as part of 

its petition, determines that the waiver 

is no longer needed, or for other 

appropriate reasons. 10 CFR 

430.27(k)(2). 

(6) Granting of this waiver does not 

release ECR from the various 

certification requirements set forth at 10 

CFR part 429. 

Signing Authority 

This document of the Department of 

Energy was signed on March 4, 2021, by 

Kelly Speakes-Backman, Principal 

Deputy Assistant Secretary and Acting 

Assistant Secretary for Energy Efficiency 

and Renewable Energy, pursuant to 

delegated authority from the Secretary 

of Energy. That document with the 

original signature and date is 

maintained by DOE. For administrative 

purposes only, and in compliance with 

requirements of the Office of the Federal 

Register, the undersigned DOE Federal 

Register Liaison Officer has been 

authorized to sign and submit the 

document in electronic format for 

publication, as an official document of 

the Department of Energy. This 

administrative process in no way alters 

the legal effect of this document upon 

publication in the Federal Register. 

Signed in Washington, DC, on March 4, 

2021. 

Treena V. Garrett, 

Federal Register Liaison Officer, U.S. 

Department of Energy. 

[FR Doc. 2021–04866 Filed 3–8–21; 8:45 am] 

BILLING CODE 6450–01–P 

DEPARTMENT OF ENERGY 

Federal Energy Regulatory 

Commission 

[Docket No. EL21–56–000] 

Louisiana Public Service Commission, 

Arkansas Public Service Commission, 

Council of the City of New Orleans, 

Louisiana, v. System Energy 

Resources, Inc., Entergy Services, 

LLC, Entergy Operations, Inc., Entergy 

Corporation; Notice of Complaint 

Take notice that on March 2, 2021, 

pursuant to sections 206, 306, and 309 

of the Federal Power Act, 16 U.S.C. 

824e, 825e, and 825h and Rule 206 of 

the Federal Energy Regulatory 

Commission’s (Commission) Rules of 

Practice and Procedure, 18 CFR 385.206, 

Louisiana Public Service Commission, 

Arkansas Public Service Commission, 

and Council of The City of New Orleans, 

Louisiana (Complainants) filed a formal 

complaint against System Energy 

Resources, Inc. (SERI), Entergy Services, 

LLC, Entergy Operations, Inc., and 

Entergy Corporation, (collectively, 

Respondents) alleging that SERI has 

violated the obligation of prudent utility 

management in operating the Grand 

Gulf nuclear unit, resulting in large 

overcharges to its four affiliated 

customers, Entergy Arkansas, LLC, 

Entergy Louisiana, LLC, Entergy New 

Orleans, LLC, and Entergy Mississippi, 

LLC and their customers, pursuant to a 

Unit Power Sales Agreement, all as 

more fully explained in the complaint. 

The Complainants certify that copies 

of the complaint were served on the 

contacts listed for Respondents in the 

Commission’s list of Corporate Officials. 

Any person desiring to intervene or to 

protest this filing must file in 

accordance with Rules 211 and 214 of 

the Commission’s Rules of Practice and 

Procedure (18 CFR 385.211, 385.214). 

Protests will be considered by the 

Commission in determining the 

appropriate action to be taken, but will 

not serve to make protestants parties to 

the proceeding. Any person wishing to 

become a party must file a notice of 

intervention or motion to intervene, as 

appropriate. The Respondent’s answer 

and all interventions, or protests must 

be filed on or before the comment date. 

The Respondent’s answer, motions to 

intervene, and protests must be served 

on the Complainants. 

The Commission strongly encourages 

electronic filings of comments, protests 

and interventions in lieu of paper using 

the ‘‘eFiling’’ link at http://

www.ferc.gov. Persons unable to file 

electronically may mail similar 

pleadings to the Federal Energy 

Regulatory Commission, 888 First Street 

NE, Washington, DC 20426. Hand 

delivered submissions in docketed 

proceedings should be delivered to 

Health and Human Services, 12225 

Wilkins Avenue, Rockville, Maryland 

20852. 

In addition to publishing the full text 

of this document in the Federal 

Register, the Commission provides all 

interested persons an opportunity to 

view and/or print the contents of this 

document via the internet through the 

Commission’s Home Page (https://

www.ferc.gov/) using the ‘‘eLibrary’’ 

link. Enter the docket number excluding 

the last three digits in the docket 

number field to access the document. At 

this time, the Commission has 

suspended access to the Commission’s 

Public Reference Room, due to the 

proclamation declaring a National 

Emergency concerning the Novel 

Coronavirus Disease (COVID–19), issued 

by the President on March 13, 2020. For 

assistance, contact the Federal Energy 

Regulatory Commission at 

FERCOnlineSupport@ferc.gov, or call 

toll-free, (886) 208–3676 or TYY, (202) 

502–8659. 

Comment Date: 5:00 p.m. Eastern 

Time on March 22, 2021. 

Dated: March 3, 2021. 

Kimberly D. Bose, 

Secretary. 

[FR Doc. 2021–04852 Filed 3–8–21; 8:45 am] 

BILLING CODE 6717–01–P 


khammond on DSKJM1Z7X2PROD with NOTICES