Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data fro

fuel burning power plants and which test methods were used to do so for cases where the test methods are not 

supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in t

if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 se

runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one 

one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet.

yellow are required. All cells that are shaded in green are populated using drop-down lists. You do not need to 

cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. 

resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls 

(example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksh

2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. 

spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission 

results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or c

family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter bot

Hg+2, or if the Ontario-Hydro Method was used, you would need to enter Hg0, HgP, and Hg

Volatile Organic HAP and Speciated Semi-Volatile Organic HAP worksheets allow you to use a drop

Constituent field to define as many records as needed to record each HAP that you have results for. General ins

follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample.

2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop-downs in the Fuel Type Selection 

You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more sa

then enter an input rate of zero. 

2. Please enter the unit of measure using the drop down provided.

3. Please enter the test method used to determine the fuel input rate.

4. Please provide any other information that you feel may be important in the Other Supporting Information fie

Emission Data
1. Some constituents ask for the emission rate results of each run in two different units of measure, while other

If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) 

ppmvd @ 7% O2(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both.

2. Please provide the test method used. This may or may not match the example given in the Test Method Used 

Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010).

3. Please provide any other information that you feel may be important in the Other Supporting Information fie

4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for p

enter these data.
nformation about emission data from fossil 

ses where the test methods are not currently 

nly be used if the method is not in the ERT or 

T. You must complete at least 3 separate 

sheet is intended to be used for one boiler of 

copies of this spreadsheet. Fields shaded in 

down lists. You do not need to populate 

rmation worksheet. Please name each 

nit_[BoilerID]_EmisTestMethods.xls 

ler on the Boiler Information worksheet. 

ent family required for this analysis. On each 

fuel input information, and emission test 

d depending on the constituent or constituent 

Mercury requires that you enter both Hg0 and 

, HgP, and Hg+2. However, both the Speciated 

low you to use a drop-down provided in the 

at you have results for. General instructions 

er Supporting Information field.

downs in the Fuel Type Selection field. 

fuel types entered in one or more samples, 

he Other Supporting Information field.
erent units of measure, while others do not. 

b/MMBtu (Pounds per million BTU) and 

, you are required to provide both.

mple given in the Test Method Used field. 

ethod (ex. U.S. EPA Method 0010).

he Other Supporting Information field.

 method you are entering data for please also 
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14
Control Device Configuraton

Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR
lectronic ICR
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time
Measured Value (ppm)

Test End Date Test End Time
Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

CO Emission Test Results
Test Method Comments lb/mmBtu ppmdv @ 7% O2

Calculated Emission Rate
Steam Output (1000 lb/hr) Total Heat Input 

(mmBtu/hr) Flue Gas Moisture (%)
Flue Gas O

2

 (%) Flue Gas Flow Rate 

(dscfm) Flue Gas CO2

 (%)
Fuel Input Rate Fuel Type

Flue Gas Temperature (F)

Fuel #1
Units of Measure Measurement Method Fuel Input Rate

Fuel #1
Fuel Type Units of Measure Measurement Method

Fuel #2
Fuel Input Rate Fuel Type Units of Measure

Fuel #3
Measurement Method Fuel Input Rate Fuel Type

Fuel #4
Units of Measure Measurement Method

Fuel #4

Other Supporting 

Information
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

Formaldehyde Emission Test Results

Test End Time
Test Method 

Comments lb/mmBtu ppmdv @ 7% O2

Total Heat Input 

(mmBtu/hr)

Calculated Emission Rate Steam Output (1000 

lb/hr)
Fuel Input 

Rate Fuel Type Units of Measure

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

Moisture (%)

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas Flow 

Rate (dscfm)
Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Fuel #2 Fuel #3
Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

1 4/6/2010 7:30

2 4/6/2010 10:20

3 4/6/2010 13:25

Run Number Test Start Date Test Start Time
Measured Value (ppm) Basis (Wet or Dry)

4/6/2010 9:30 5.5 Wet

4/6/2010 12:20 24 Wet

4/6/2010 15:25 21 Wet

Test End Date Test End Time

Methane Emission T
Test Method Used Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments lb/mmBtu

U.S. EPA Method 18 ADL 0.00366

U.S. EPA Method 18 ADL 0.01577

U.S. EPA Method 18 ADL 0.01362

Methane Emission Test Results Calculated Emission Rate
ppmdv @ 7% O2

5.46 2890 4230 10.21 14.6 6.9 1046278

23.49 2890 4500 10.43 14.6 6.7 1046409

20.27 2890 4540 10.11 14.8 6.5 1046600

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

lated Emission Rate

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)
Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Measurement 

Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

309 4230 subbituminous MMBtu/hr gas fuel meter

318 4500 subbituminous MMBtu/hr gas fuel meter

323 4540 subbituminous MMBtu/hr gas fuel meter

Flue Gas 

Temperat

ure (F)

Fuel #1 Fuel #2
Measurement 

Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Measurement 

Method

Fuel 

Input 

Rate

Fuel Type Units of 

Measure

Fuel #3 Fuel #4
Measurement 

Method

Other Supporting 

Information
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used Test End Time

SO2 Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments lb/mmBtu ppmdv @ 7% O

2

Calculated Emission Rate Steam Output 

(1000 lb/hr)
Fuel Input 

Rate Fuel Type

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

Flue Gas 

Temperature 

(F)

Fuel #1
Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type

Fuel #1 Fuel #2 Fuel #3
Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #3 Fuel #4
Other Supporting Information
EIA Facility Code Facility Name Boiler ID

6085 R M Schahfer 14

1A 4/28/2010 10:15

2A 4/28/2010 15:20

3A 4/29/2010 7:05

Run Number Test Start Date Test Start Time
Please note QA/QC documentation starting in Column "AI"

Measured Value 

(μg/dscm) Basis (Wet or Dry)

4/28/2010 12:15 1.4058 Dry

4/28/2010 17:20 1.1955 Dry

4/29/2010 9:05 1.5026 Dry

Test End Date Test End Time

Total Vapor Phase Mercury Em
 starting in Column "AI"

Test Method Used Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments (lb/mmBtu)

U.S. EPA Method 30B ADL 1.34E-06 2756.9

U.S. EPA Method 30B ADL 1.06E-06 2756.9

U.S. EPA Method 30B ADL 1.29E-06 2703.2

Total Vapor Phase Mercury Emission Test Results

Steam Output 

(1000 lb/hr)
Fuel Input Rate

4580 6.99 13.8 5.4 1012278 290 4580

4590 6.87 13.7 5.4 1007550 296 4590

4540 6.74 14.2 5 1009947 295 4540

Flue Gas 

Temperature (F)

Flue Gas 

Moisture 

(%)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

subbituminous MMBtu/hr gas fuel meter

subbituminous MMBtu/hr gas fuel meter

subbituminous MMBtu/hr gas fuel meter

Fuel #1 Fuel #2
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #3 Fuel #4
 QA/QC Documentation

Trap ID Section 1 

Mass (ng)

Section 2 

Mass (ng)

Total 

Mass (ng)

Initial 

Spike 

(ng)

Total NonSpike (ng)

66183 167 0.1 167.1 0 167.1

68152 138 0.7 138.7 0 138.7

68166 174 0.3 174.3 0 174.3

Other Supporting Information
Sample 

Volume 

(dscm)

Volume 

Difference (%)

Volume Diff. 

Limit

Breaktrough 

(%)

Breaktrough 

Limit

Concentration 

(μg/dscm) Trap ID

0.1198 0.995843724 0.05988024 1.394824708 66734

0.1162 0.990622336 0.507246377 1.19363167 66729

0.1188 0.996644295 ≤20% of field 0.172413793 1.467171717 66783

recovery test

≤ 10% of 

Section 1 Hg 

mass for Hg 

conc. >1 

μg/dscm: or ≤ 

20% of Section 

Trap #1
Section 1 

Mass

Section 2 

Mass

Total 

Mass

Initial 

Spike

Total NonSpikeSample 

Volume

Volume 

Difference (%)

Volume Diff. 

Limit

370 0.4 370.4 200 370.4 0.1203 0.120802087

340 0.4 340.4 200 340.4 0.1173 0.118410413

383 0.3 383.3 200 383.3 0.1192 0.119601347 ≤20% of field 

recovery test

Trap #2
Breaktrough (%) Breaktrough 

Limit

Concentration 

(μg/dscm) Abs. diff. RD (%) Limit Crec

0.108108108 3.078969244 1.684145 37.64466 99.8585

0.117647059 2.901960784 1.708329 41.7114 99.4903

0.078328982 3.215604027 1.748432 37.33752 1.000331

≥10 % RD mass 

for Hg conc. >1 

μg/dscm: or 

≤20% RD or ≤0.2 

μg/dscm abs.diff. 

for Hg conc. ≤1 

≤ 10% of Section 

1 Hg mass for 

Hg conc. >1 

μg/dscm: or ≤ 

20% of Section 1 

for Hg conc.≤1 

Paired Trap Agreement (RD) Measured Spik
R (%) by 

Run Ravg (%) Limit

99.8

99.5

100.0

Average 

Recovery, 

between 85 and 

115%

Measured Spike Recovery ( R )

99.7667
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time
Measured Hg

0

 Value 

(μg/dscm)

Measured Hg+2 Value 

(μg/dscm)

Test End Date Test End Time
Measured HgP

 Value 

(μg/dscm)

Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL)

Total Vapor Phase Mercury Emission Test Results
Test Method 

Comments

Total Mercury 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)

Flue Gas 

CO

2

 (%)
Fuel Input Rate Fuel Type Units of 

Measure

Measurement 

Method

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input Rate Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Speciated Volatile Organic HAP Emission Data

Acetone 1 4/6/2010

Acetone 2 4/6/2010

Acetone 3 4/6/2010

Benzene 1 4/6/2010

Benzene 2 4/6/2010

Benzene 3 4/6/2010

Bromobenzene 1 4/6/2010

Bromobenzene 2 4/6/2010

Bromobenzene 3 4/6/2010

Bromochloromethane 1 4/6/2010

Bromochloromethane 2 4/6/2010

Bromochloromethane 3 4/6/2010

Bromodichloromethane 1 4/6/2010

Bromodichloromethane 2 4/6/2010

Bromodichloromethane 3 4/6/2010

Bromoform (tribromomethane) 1 4/6/2010

Bromoform (tribromomethane) 2 4/6/2010

Bromoform (tribromomethane) 3 4/6/2010

Bromomethane 1 4/6/2010

Bromomethane 2 4/6/2010

Bromomethane 3 4/6/2010

2-Butanone 1 4/6/2010

2-Butanone 2 4/6/2010

2-Butanone 3 4/6/2010

n-Butylbenzene 1 4/6/2010

n-Butylbenzene 2 4/6/2010

n-Butylbenzene 3 4/6/2010

sec-Butylbenzene 1 4/6/2010

sec-Butylbenzene 2 4/6/2010

sec-Butylbenzene 3 4/6/2010

tert-Butylbenzene 1 4/6/2010

tert-Butylbenzene 2 4/6/2010

tert-Butylbenzene 3 4/6/2010

Carbon disulfide 1 4/6/2010

Carbon disulfide 2 4/6/2010

Carbon disulfide 3 4/6/2010

Carbon tetrachloride 1 4/6/2010

Carbon tetrachloride 2 4/6/2010

Carbon tetrachloride 3 4/6/2010

Chlorobenzene 1 4/6/2010

Chlorobenzene 2 4/6/2010

Chlorobenzene 3 4/6/2010

Compound 

(use drop down to define for as many rows as 

needed)

Run Number Test Start Date
Chlorodibromomethane

1 4/6/2010

Chlorodibromomethane2 4/6/2010

Chlorodibromomethane3 4/6/2010

Chloroethane1 4/6/2010

Chloroethane2 4/6/2010

Chloroethane3 4/6/2010

Chloroform1 4/6/2010

Chloroform2 4/6/2010

Chloroform3 4/6/2010

Chloromethane1 4/6/2010

Chloromethane2 4/6/2010

Chloromethane3 4/6/2010

2-Chlorotoluene1 4/6/2010

2-Chlorotoluene2 4/6/2010

2-Chlorotoluene3 4/6/2010

4-Chlorotoluene1 4/6/2010

4-Chlorotoluene2 4/6/2010

4-Chlorotoluene3 4/6/2010

1,2-Dibromo-3-chloropropane1 4/6/2010

1,2-Dibromo-3-chloropropane2 4/6/2010

1,2-Dibromo-3-chloropropane3 4/6/2010

1,2-Dibromoethane1 4/6/2010

1,2-Dibromoethane2 4/6/2010

1,2-Dibromoethane3 4/6/2010

Dibromomethane1 4/6/2010

Dibromomethane2 4/6/2010

Dibromomethane3 4/6/2010

1,2-Dichlorobenzene1 4/6/2010

1,2-Dichlorobenzene2 4/6/2010

1,2-Dichlorobenzene3 4/6/2010

1,3-Dichlorobenzene1 4/6/2010

1,3-Dichlorobenzene2 4/6/2010

1,3-Dichlorobenzene3 4/6/2010

1,4-Dichlorobenzene (p-)1 4/6/2010

1,4-Dichlorobenzene (p-)2 4/6/2010

1,4-Dichlorobenzene (p-)3 4/6/2010

Dichlorodifluoromethane1 4/6/2010

Dichlorodifluoromethane2 4/6/2010

Dichlorodifluoromethane3 4/6/2010

1,1-Dichloroethane1 4/6/2010

1,1-Dichloroethane2 4/6/2010

1,1-Dichloroethane3 4/6/2010

1,2-dichloroethane1 4/6/2010

1,2-dichloroethane2 4/6/2010

1,2-dichloroethane3 4/6/2010

cis-1,2-Dichloroethene1 4/6/2010

cis-1,2-Dichloroethene2 4/6/2010

cis-1,2-Dichloroethene3 4/6/2010

trans-1,2-Dichloroethene1 4/6/2010
trans-1,2-Dichloroethene

2 4/6/2010

trans-1,2-Dichloroethene3 4/6/2010

1,1-Dichloroethene1 4/6/2010

1,1-Dichloroethene2 4/6/2010

1,1-Dichloroethene3 4/6/2010

1,2-Dichloropropane1 4/6/2010

1,2-Dichloropropane2 4/6/2010

1,2-Dichloropropane3 4/6/2010

1,3-Dichloropropane1 4/6/2010

1,3-Dichloropropane2 4/6/2010

1,3-Dichloropropane3 4/6/2010

2,2-Dichloropropane1 4/6/2010

2,2-Dichloropropane2 4/6/2010

2,2-Dichloropropane3 4/6/2010

cis-1,3-Dichloropropene1 4/6/2010

cis-1,3-Dichloropropene2 4/6/2010

cis-1,3-Dichloropropene3 4/6/2010

trans-1,3-Dichloropropene1 4/6/2010

trans-1,3-Dichloropropene2 4/6/2010

trans-1,3-Dichloropropene3 4/6/2010

1,1-Dichloropropene1 4/6/2010

1,1-Dichloropropene2 4/6/2010

1,1-Dichloropropene3 4/6/2010

Ethylbenzene1 4/6/2010

Ethylbenzene2 4/6/2010

Ethylbenzene3 4/6/2010

Hexachlorobutadiene1 4/6/2010

Hexachlorobutadiene2 4/6/2010

Hexachlorobutadiene3 4/6/2010

2-Hexanone1 4/6/2010

2-Hexanone2 4/6/2010

2-Hexanone3 4/6/2010

Isopropylbenzene1 4/6/2010

Isopropylbenzene2 4/6/2010

Isopropylbenzene3 4/6/2010

p-Isopropyltoluene1 4/6/2010

p-Isopropyltoluene2 4/6/2010

p-Isopropyltoluene3 4/6/2010

Methylene chloride1 4/6/2010

Methylene chloride2 4/6/2010

Methylene chloride3 4/6/2010

4-Methyl-2-pentanone1 4/6/2010

4-Methyl-2-pentanone2 4/6/2010

4-Methyl-2-pentanone3 4/6/2010

Napthalene1 4/6/2010

Napthalene2 4/6/2010

Napthalene3 4/6/2010

n-Propylbenzene1 4/6/2010

n-Propylbenzene2 4/6/2010
n-Propylbenzene

3 4/6/2010

Styrene1 4/6/2010

Styrene2 4/6/2010

Styrene3 4/6/2010

1,1,1,2-Tetrachloroethane1 4/6/2010

1,1,1,2-Tetrachloroethane2 4/6/2010

1,1,1,2-Tetrachloroethane3 4/6/2010

1,1,2,2-Tetrachloroethane1 4/6/2010

1,1,2,2-Tetrachloroethane2 4/6/2010

1,1,2,2-Tetrachloroethane3 4/6/2010

Tetrachlroethen1 4/6/2010

Tetrachlroethen2 4/6/2010

Tetrachlroethen3 4/6/2010

Toluene1 4/6/2010

Toluene2 4/6/2010

Toluene3 4/6/2010

1,2,3-Trichlorobenzene1 4/6/2010

1,2,3-Trichlorobenzene2 4/6/2010

1,2,3-Trichlorobenzene3 4/6/2010

1,2,4-Trichlorobenzene1 4/6/2010

1,2,4-Trichlorobenzene2 4/6/2010

1,2,4-Trichlorobenzene3 4/6/2010

1,1,1,-Trichloroethane1 4/6/2010

1,1,1,-Trichloroethane2 4/6/2010

1,1,1,-Trichloroethane3 4/6/2010

1,1,2-Trichloroethane1 4/6/2010

1,1,2-Trichloroethane2 4/6/2010

1,1,2-Trichloroethane3 4/6/2010

Trichloroethene1 4/6/2010

Trichloroethene2 4/6/2010

Trichloroethene3 4/6/2010

Trichlorofluoromethane1 4/6/2010

Trichlorofluoromethane2 4/6/2010

Trichlorofluoromethane3 4/6/2010

1,2,3-Trichloropropane1 4/6/2010

1,2,3-Trichloropropane2 4/6/2010

1,2,3-Trichloropropane3 4/6/2010

1,2,4-Trichlorobenzene1 4/6/2010

1,2,4-Trichlorobenzene2 4/6/2010

1,2,4-Trichlorobenzene3 4/6/2010

1,3,5-Trimethylbenzene1 4/6/2010

1,3,5-Trimethylbenzene2 4/6/2010

1,3,5-Trimethylbenzene3 4/6/2010

Vinyl chloride (chloroethene)1 4/6/2010

Vinyl chloride (chloroethene)2 4/6/2010

Vinyl chloride (chloroethene)3 4/6/2010

M-Xylene & p-Xylene1 4/6/2010

M-Xylene & p-Xylene2 4/6/2010

M-Xylene & p-Xylene3 4/6/2010
o-Xylene

1 4/6/2010

o-Xylene2 4/6/2010

o-Xylene3 4/6/2010



Measured Value 

(μg/m3)

8:05 AM 4/6/2010 9:50 AM [<52.9653]

10:20 AM 4/6/2010 12:05 PM [<81.2589]

1:25 PM 4/6/2010 3:15 PM 72.6081

8:05 AM 4/6/2010 9:50 AM [<1.3415]

10:20 AM 4/6/2010 12:05 PM [<2.0132]

1:25 PM 4/6/2010 3:15 PM [<1.7074]

8:05 AM 4/6/2010 9:50 AM [<0.2883]

10:20 AM 4/6/2010 12:05 PM [<0.2883]

1:25 PM 4/6/2010 3:15 PM [<0.2871]

8:05 AM 4/6/2010 9:50 AM [<0.4043]

10:20 AM 4/6/2010 12:05 PM [<0.4040]

1:25 PM 4/6/2010 3:15 PM [<0.4022]

8:05 AM 4/6/2010 9:50 AM [<0.1883]

10:20 AM 4/6/2010 12:05 PM [<0.1878]

1:25 PM 4/6/2010 3:15 PM [<0.1870]

8:05 AM 4/6/2010 9:50 AM [<1.4481]

10:20 AM 4/6/2010 12:05 PM [<1.4450]

1:25 PM 4/6/2010 3:15 PM [<1.4381]

8:05 AM 4/6/2010 9:50 AM [<6.0022]

10:20 AM 4/6/2010 12:05 PM [<6.7112]

1:25 PM 4/6/2010 3:15 PM [<4.1081]

8:05 AM 4/6/2010 9:50 AM [<14.3762]

10:20 AM 4/6/2010 12:05 PM [<14.3960]

1:25 PM 4/6/2010 3:15 PM [<14.3394

8:05 AM 4/6/2010 9:50 AM [<0.1445]

10:20 AM 4/6/2010 12:05 PM [<0.1443]

1:25 PM 4/6/2010 3:15 PM [<0.1437]

8:05 AM 4/6/2010 9:50 AM [<0.1443]

10:20 AM 4/6/2010 12:05 PM [<0.1443]

1:25 PM 4/6/2010 3:15 PM [<0.1436]

8:05 AM 4/6/2010 9:50 AM [<0.1588]

10:20 AM 4/6/2010 12:05 PM [<0.1587]

1:25 PM 4/6/2010 3:15 PM [<0.1580]

8:05 AM 4/6/2010 9:50 AM [<0.6272]

10:20 AM 4/6/2010 12:05 PM [<0.7098]

1:25 PM 4/6/2010 3:15 PM [<0.5448]

8:05 AM 4/6/2010 9:50 AM [<0.1831]

10:20 AM 4/6/2010 12:05 PM [<0.1925]

1:25 PM 4/6/2010 3:15 PM [<0.1821]

8:05 AM 4/6/2010 9:50 AM [<0.1446]

10:20 AM 4/6/2010 12:05 PM [<0.1444]

1:25 PM 4/6/2010 3:15 PM [<0.1533]

Test Start Time Test End Date Test End Time
8:05 AM 4/6/2010 9:50 AM [<0.2900]

10:20 AM 4/6/2010 12:05 PM [<0.2892]

1:25 PM 4/6/2010 3:15 PM [<0.2877]

8:05 AM 4/6/2010 9:50 AM [<0.8928]

10:20 AM 4/6/2010 12:05 PM [<0.8933]

1:25 PM 4/6/2010 3:15 PM [<0.8896]

8:05 AM 4/6/2010 9:50 AM [<0.1588]

10:20 AM 4/6/2010 12:05 PM [<0.1587]

1:25 PM 4/6/2010 3:15 PM [<0.1580]

8:05 AM 4/6/2010 9:50 AM [<24.7588]

10:20 AM 4/6/2010 12:05 PM [<30.4799]

1:25 PM 4/6/2010 3:15 PM [<12.7954]

8:05 AM 4/6/2010 9:50 AM [<0.1735]

10:20 AM 4/6/2010 12:05 PM [<0.1733]

1:25 PM 4/6/2010 3:15 PM [<0.1725]

8:05 AM 4/6/2010 9:50 AM [<0.2022]

10:20 AM 4/6/2010 12:05 PM [<0.2020]

1:25 PM 4/6/2010 3:15 PM [<0.2011]

8:05 AM 4/6/2010 9:50 AM [<1.8735]

10:20 AM 4/6/2010 12:05 PM [<1.8738]

1:25 PM 4/6/2010 3:15 PM [<1.8660]

8:05 AM 4/6/2010 9:50 AM [<0.2035]

10:20 AM 4/6/2010 12:05 PM [<0.2026]

1:25 PM 4/6/2010 3:15 PM [<0.2016]

8:05 AM 4/6/2010 9:50 AM [<0.3040]

10:20 AM 4/6/2010 12:05 PM [<0.3034]

1:25 PM 4/6/2010 3:15 PM [<0.3019]

8:05 AM 4/6/2010 9:50 AM [<0.2591]

10:20 AM 4/6/2010 12:05 PM [<0.2593]

1:25 PM 4/6/2010 3:15 PM [<0.2582]

8:05 AM 4/6/2010 9:50 AM [<0.2020]

10:20 AM 4/6/2010 12:05 PM [<0.2019]

1:25 PM 4/6/2010 3:15 PM [<0.2010]

8:05 AM 4/6/2010 9:50 AM [<0.2165]

10:20 AM 4/6/2010 12:05 PM [<0.2164]

1:25 PM 4/6/2010 3:15 PM [<0.2154]

8:05 AM 4/6/2010 9:50 AM [<0.6356]

10:20 AM 4/6/2010 12:05 PM [<1.0182]

1:25 PM 4/6/2010 3:15 PM [<0.9413]

8:05 AM 4/6/2010 9:50 AM [<0.1443]

10:20 AM 4/6/2010 12:05 PM [<0.1443]

1:25 PM 4/6/2010 3:15 PM [<0.1436]

8:05 AM 4/6/2010 9:50 AM [<0.2451]

10:20 AM 4/6/2010 12:05 PM [<0.2451]

1:25 PM 4/6/2010 3:15 PM [<0.2440]

8:05 AM 4/6/2010 9:50 AM [<0.1449]

10:20 AM 4/6/2010 12:05 PM [<0.1446]

1:25 PM 4/6/2010 3:15 PM [<0.1439]

8:05 AM 4/6/2010 9:50 AM [<0.2878]
10:20 AM 4/6/2010 12:05 PM [<0.2881]

1:25 PM 4/6/2010 3:15 PM [<0.2869]

8:05 AM 4/6/2010 9:50 AM [<0.2170]

10:20 AM 4/6/2010 12:05 PM [<0.2166]

1:25 PM 4/6/2010 3:15 PM [<0.2156]

8:05 AM 4/6/2010 9:50 AM [<0.2452]

10:20 AM 4/6/2010 12:05 PM [<0.2451]

1:25 PM 4/6/2010 3:15 PM [<0.2441]

8:05 AM 4/6/2010 9:50 AM [<0.2018]

10:20 AM 4/6/2010 12:05 PM [<0.2018]

1:25 PM 4/6/2010 3:15 PM [<0.2010]

8:05 AM 4/6/2010 9:50 AM [<0.1449]

10:20 AM 4/6/2010 12:05 PM [<0.1445]

1:25 PM 4/6/2010 3:15 PM [<0.1439]

8:05 AM 4/6/2010 9:50 AM [<0.2455]

10:20 AM 4/6/2010 12:05 PM [<0.2453]

1:25 PM 4/6/2010 3:15 PM [<0.2442]

8:05 AM 4/6/2010 9:50 AM [<0.1737]

10:20 AM 4/6/2010 12:05 PM [<0.1733]

1:25 PM 4/6/2010 3:15 PM [<0.1725]

8:05 AM 4/6/2010 9:50 AM [<0.1446]

10:20 AM 4/6/2010 12:05 PM [<0.0417]

1:25 PM 4/6/2010 3:15 PM [<0.0419]

8:05 AM 4/6/2010 9:50 AM [<0.1541]

10:20 AM 4/6/2010 12:05 PM [<0.1444]

1:25 PM 4/6/2010 3:15 PM [<0.1509]

8:05 AM 4/6/2010 9:50 AM [<0.3640]

10:20 AM 4/6/2010 12:05 PM [<0.3622]

1:25 PM 4/6/2010 3:15 PM [<0.3602]

8:05 AM 4/6/2010 9:50 AM [<0.9822]

10:20 AM 4/6/2010 12:05 PM [<0.9813]

1:25 PM 4/6/2010 3:15 PM [<0.9770]

8:05 AM 4/6/2010 9:50 AM [<0.1444]

10:20 AM 4/6/2010 12:05 PM [<0.1443]

1:25 PM 4/6/2010 3:15 PM [<0.1437]

8:05 AM 4/6/2010 9:50 AM [<0.1443]

10:20 AM 4/6/2010 12:05 PM [<0.1443]

1:25 PM 4/6/2010 3:15 PM [<0.1436]

8:05 AM 4/6/2010 9:50 AM 4.1016

10:20 AM 4/6/2010 12:05 PM 2.4281

1:25 PM 4/6/2010 3:15 PM 3.0405

8:05 AM 4/6/2010 9:50 AM [<14.3762]

10:20 AM 4/6/2010 12:05 PM [<14.3960]

1:25 PM 4/6/2010 3:15 PM [<14.3394]

8:05 AM 4/6/2010 9:50 AM [<1.4373]

10:20 AM 4/6/2010 12:05 PM [<1.4394]

1:25 PM 4/6/2010 3:15 PM [<1.4338]

8:05 AM 4/6/2010 9:50 AM [<0.1439]

10:20 AM 4/6/2010 12:05 PM [<0.1440]
1:25 PM 4/6/2010 3:15 PM [<0.1434]

8:05 AM 4/6/2010 9:50 AM [<0.2044]

10:20 AM 4/6/2010 12:05 PM [<0.1875]

1:25 PM 4/6/2010 3:15 PM [<0.2129]

8:05 AM 4/6/2010 9:50 AM [<0.1592]

10:20 AM 4/6/2010 12:05 PM [<0.1589]

1:25 PM 4/6/2010 3:15 PM [<0.1582]

8:05 AM 4/6/2010 9:50 AM [<0.4182]

10:20 AM 4/6/2010 12:05 PM [<0.4182]

1:25 PM 4/6/2010 3:15 PM [<0.4164]

8:05 AM 4/6/2010 9:50 AM [<0.1592]

10:20 AM 4/6/2010 12:05 PM [<0.1589]

1:25 PM 4/6/2010 3:15 PM [<0.1581]

8:05 AM 4/6/2010 9:50 AM [<0.4793]

10:20 AM 4/6/2010 12:05 PM [<0.4919]

1:25 PM 4/6/2010 3:15 PM [<0.4947]

8:05 AM 4/6/2010 9:50 AM [<0.2072]

10:20 AM 4/6/2010 12:05 PM [<0.1458]

1:25 PM 4/6/2010 3:15 PM [<0.1449]

8:05 AM 4/6/2010 9:50 AM [<0.2323]

10:20 AM 4/6/2010 12:05 PM [<0.2315]

1:25 PM 4/6/2010 3:15 PM [<0.2303]

8:05 AM 4/6/2010 9:50 AM [<0.1454]

10:20 AM 4/6/2010 12:05 PM [<0.1448]

1:25 PM 4/6/2010 3:15 PM [<0.1440]

8:05 AM 4/6/2010 9:50 AM [<1.4361]

10:20 AM 4/6/2010 12:05 PM [<1.4388]

1:25 PM 4/6/2010 3:15 PM [<1.4334]

8:05 AM 4/6/2010 9:50 AM [<0.3170]

10:20 AM 4/6/2010 12:05 PM [<0.3171]

1:25 PM 4/6/2010 3:15 PM [<0.3158]

8:05 AM 4/6/2010 9:50 AM [<0.3357]

10:20 AM 4/6/2010 12:05 PM [<0.5133]

1:25 PM 4/6/2010 3:15 PM [<0.4708]

8:05 AM 4/6/2010 9:50 AM [<3.5897]

10:20 AM 4/6/2010 12:05 PM [<3.5969]

1:25 PM 4/6/2010 3:15 PM [<3.5833]

8:05 AM 4/6/2010 9:50 AM [<0.2160]

10:20 AM 4/6/2010 12:05 PM [<0.2161]

1:25 PM 4/6/2010 3:15 PM [<0.2152]

8:05 AM 4/6/2010 9:50 AM [<0.2586]

10:20 AM 4/6/2010 12:05 PM [<0.2590]

1:25 PM 4/6/2010 3:15 PM [<0.2580]

8:05 AM 4/6/2010 9:50 AM [<0.3037]

10:20 AM 4/6/2010 12:05 PM [<0.3032]

1:25 PM 4/6/2010 3:15 PM [<0.3018]

8:05 AM 4/6/2010 9:50 AM [<0.3117]

10:20 AM 4/6/2010 12:05 PM [<0.2953]

1:25 PM 4/6/2010 3:15 PM [<0.3275]
8:05 AM 4/6/2010 9:50 AM [<0.1519]

10:20 AM 4/6/2010 12:05 PM [<0.1516]

1:25 PM 4/6/2010 3:15 PM [<0.1581]



Footnotes:

* Front half fraction contains filter, cyclone, and cartridge

** Back half fraction contains condensate, solvent, impingers

Basis Test Method Used Data Flag (ADL, BDL, 

DDL) Front Half Mass (ng)

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 2214.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 3390.00

Dry U.S. EPA Method 0031 with SW ADL -846 Method 8260B 3040.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 56.10

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 84.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 71.50

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 16.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 16.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 16.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 251.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 280.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 172.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 600.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 600.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 600.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 26.20

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 29.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 22.80

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 7.60

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 8.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.40
Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 37.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 37.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 37.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 1036.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 1272.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 535.90

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 78.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 78.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 78.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 26.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 42.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 39.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00
Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.30

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 15.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 15.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 15.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 40.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 40.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 40.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW ADL -846 Method 8260B 171.00

Dry U.S. EPA Method 0031 with SW ADL -846 Method 8260B 101.00

Dry U.S. EPA Method 0031 with SW ADL -846 Method 8260B 127.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 600.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 600.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 600.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00
Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.50

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 7.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.90

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 17.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 17.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 17.40

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 20.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 20.50

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 20.70

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 8.50

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 60.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 13.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 13.20

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 13.20

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 14.00

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 21.40

Dry U.S. EPA Method 0031 with SW DLL -846 Method 8260B 19.70

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 150.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 150.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 150.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 9.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 10.80

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.60

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 13.00

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 12.30

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 13.70
Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.30

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.30

Dry U.S. EPA Method 0031 with SW BDL -846 Method 8260B 6.60



Back Half Mass (ng) Total Mass (ng) Test Method Comments lb/mmBtu

2.44 2216.44 [<4.748E-05]

1.24 3391.24 [<7.167E-05]

1.16 3041.16 6.344E-05

0.036 56.136 [<1.202E-06]

0.018 84.018 [<1.776E-06]

0.012 71.512 [<1.492E-06]

0.064 12.064 [<2.584E-07]

0.0312 12.0312 [<2.543E-07]

0.024 12.024 [<2.508E-07]

0.12 16.92 [<3.624E-07]

0.06 16.86 [<3.563E-07]

0.044 16.844 [<3.514E-07]

0.08 7.88 [<1.688E-07]

0.0396 7.8396 [<1.657E-07]

0.0308 7.8308 [<1.633E-07]

0.600 60.6 [<1.297E-06]

0.304 60.304 [<1.275E-06]

0.236 60.236 [<1.256E-06]

0.172 251.172 [<5.380E-06]

0.084 280.084 [<5.920E-06]

0.068 172.068 [<3.589E-06]

1.60 601.6 [<1.289E-05]

0.80 600.8 [<1.270E-05]

0.60 600.6 [<1.253E-05]

0.048 6.048 [<1.296E-07]

0.0232 6.0232 [<1.273E-07]

0.018 6.018 [<1.255E-07]

0.04 6.04 [<1.294E-07]

0.0208 6.0208 [<1.272E-07]

0.016 6.016 [<1.255E-07]

0.044 6.644 [<1.423E-07]

0.0216 6.6216 [<1.399E-07]

0.0164 6.6164 [<1.380E-07]

0.048 26.248 [<5.623E-07]

0.024 29.624 [<6.261E-07]

0.0184 22.8184 [<4.760E-07]

0.064 7.664 [<1.642E-07]

0.0332 8.0332 [<1.698E-07]

0.0256 7.6256 [<1.591E-07]

0.052 6.052 [<1.296E-07]

0.0252 6.0252 [<1.273E-07]

0.0192 6.4192 [<1.339E-07]

Calculated Emission Rate
0.136 12.136 [<2.600E-07]

0.068 12.068 [<2.551E-07]

0.052 12.052 [<2.514E-07]

0.16 37.36 [<8.003E-07]

0.08 37.28 [<7.879E-07]

0.06 37.26 [<7.772E-07]

0.044 6.644 [<1.423E-07]

0.022 6.622 [<1.400E-07]

0.0168 6.6168 [<1.380E-07]

0.080 1036.08 [<2.219E-05]

0.039 1272.0392 [<2.688E-05]

0.030 535.9304 [<1.118E-05]

0.060 7.26 [<1.555E-07]

0.030 7.2304 [<1.528E-07]

0.024 7.2236 [<1.507E-07]

0.060 8.46 [<1.812E-07]

0.030 8.4304 [<1.782E-07]

0.024 8.4236 [<1.757E-07]

0.400 78.4 [<1.679E-06]

0.200 78.2 [<1.653E-06]

0.156 78.156 [<1.630E-06]

0.116 8.516 [<1.824E-07]

0.056 8.456 [<1.787E-07]

0.044 8.444 [<1.761E-07]

0.120 12.72 [<2.725E-07]

0.060 12.66 [<2.676E-07]

0.044 12.644 [<2.637E-07]

0.044 10.844 [<2.323E-07]

0.022 10.8216 [<2.287E-07]

0.016 10.8164 [<2.256E-07]

0.052 8.452 [<1.811E-07]

0.026 8.4264 [<1.781E-07]

0.020 8.4204 [<1.756E-07]

0.060 9.06 [<1.941E-07]

0.030 9.03 [<1.908E-07]

0.023 9.0232 [<1.882E-07]

0.600 26.6 [<5.698E-07]

0.292 42.492 [<8.981E-07]

0.228 39.428 [<8.224E-07]

0.040 6.04 [<1.294E-07]

0.021 6.0208 [<1.272E-07]

0.016 6.016 [<1.255E-07]

0.056 10.256 [<2.197E-07]

0.028 10.228 [<2.162E-07]

0.022 10.2216 [<2.132E-07]

0.064 6.064 [<1.299E-07]

0.033 6.0332 [<1.275E-07]

0.026 6.0256 [<1.257E-07]

0.044 12.044 [<2.580E-07]
0.022 12.022 [<2.541E-07]

0.017 12.0168 [<2.507E-07]

0.080 9.08 [<1.945E-07]

0.040 9.04 [<1.911E-07]

0.031 9.0312 [<1.884E-07]

0.060 10.26 [<2.198E-07]

0.029 10.2292 [<2.162E-07]

0.023 10.2228 [<2.132E-07]

0.044 8.444 [<1.809E-07]

0.022 8.422 [<1.780E-07]

0.017 8.4168 [<1.756E-07]

0.064 6.064 [<1.299E-07]

0.032 6.0324 [<1.275E-07]

0.025 6.0252 [<1.257E-07]

0.072 10.272 [<2.200E-07]

0.036 10.236 [<2.163E-07]

0.028 10.228 [<2.133E-07]

0.068 7.268 [<1.557E-07]

0.034 7.2344 [<1.529E-07]

0.026 7.2264 [<1.507E-07]

0.052 6.052 [<1.296E-07]

0.026 6.0256 [<1.274E-07]

0.020 6.02 [<1.256E-07]

0.048 6.448 [<1.381E-07]

0.024 6.0244 [<1.273E-07]

0.019 6.3188 [<1.318E-07]

0.232 15.232 [<3.263E-07]

0.116 15.116 [<3.195E-07]

0.088 15.088 [<3.147E-07]

0.304 41.104 [<8.805E-07]

0.152 40.952 [<8.655E-07]

0.120 40.92 [<8.536E-07]

0.044 6.044 [<1.295E-07]

0.022 6.022 [<1.273E-07]

0.017 6.0168 [<1.255E-07]

0.040 6.04 [<1.294E-07]

0.021 6.0208 [<1.272E-07]

0.016 6.016 [<1.255E-07]

0.64 171.64 3.677E-06

0.332 101.332 2.142E-06

0.352 127.352 2.656E-06

1.600 601.6 [<1.289E-05]

0.800 600.8 [<1.270E-05]

0.600 600.6 [<1.253-05]

0.148 60.148 [<1.288E-06]

0.072 60.072 [<1.270E-06]

0.056 60.056 [<1.253E-06]

0.021 6.0208 [<1.290E-07]

0.010 6.0104 [<1.270E-07]
0.008 6.008 [<1.253E-07]

0.052 8.552 [<1.832E-07]

0.025 7.8252 [<1.654E-07]

0.019 8.9192 [<1.860E-07]

0.064 6.664 [<1.428E-07]

0.033 6.6332 [<1.402E-07]

0.026 6.6256 [<1.382E-07]

0.100 17.5 [<3.749E-07]

0.052 17.452 [<3.688E-07]

0.039 17.4388 [<3.638E-07]

0.064 6.664 [<1.428E-07]

0.031 6.6312 [<1.401E-07]

0.024 6.624 [<1.382E-07]

0.056 20.056 [<4.296E-07]

0.029 20.5288 [<4.339E-07]

0.022 20.722 [<4.322E-07]

0.172 8.672 [<1.858E-07]

0.084 6.084 [<1.286E-07]

0.068 6.068 [<1.266E-07]

0.120 9.72 [<2.082E-07]

0.060 9.66 [<2.042E-07]

0.048 9.648 [<2.013E-07]

0.084 6.084 [<1.303E-07]

0.044 6.044 [<1.277E-07]

0.033 6.0332 [<1.258E-07]

0.096 60.096 [<1.287E-06]

0.048 60.048 [<1.269E-06]

0.037 60.0372 [<1.252E-06]

0.064 13.264 [<2.841E-07]

0.033 13.2332 [<2.797E-07]

0.026 13.2256 [<2.759E-07]

0.048 14.048 [<3.009E-07]

0.023 21.4232 [<4.528E-07]

0.018 19.718 [<4.113E-07]

0.220 150.22 [<3.218E-06]

0.112 150.112 [<3.173E-06]

0.084 150.084 [<3.131E-06]

0.038 9.038 [<1.936E-07]

0.019 9.0188 [<1.906E-07]

0.015 9.0148 [<1.880E-07]

0.021 10.8208 [<2.318E-07]

0.010 10.8104 [<2.285E-07]

0.008 10.808 [<2.254E-07]

0.108 12.708 [<2.722E-07]

0.052 12.652 [<2.674E-07]

0.040 12.64 [<2.637E-07]

0.044 13.044 [<2.794E-07]

0.022 12.322 [<2.604E-07]

0.017 13.7168 [<2.861E-07]
0.056 6.356 [<1.362E-07]

0.028 6.328 [<1.337E-07]

0.022 6.6216 [<1.381E-07]



ppmdv @ 7% O2

[<2.214E-02] 2890 4230 10.21

[<3.348E-02] 2890 4500 10.43

2.950E-02 2890 4540 10.11

[<4.169E-04] 2890 4230 10.21

[<6.169E-04] 2890 4500 10.43

[<5.159E-04] 2890 4540 10.11

[<4.457E-05] 2890 4230 10.21

[<4.394E-05] 2890 4500 10.43

[<4.315E-05] 2890 4540 10.11

[<7.586E-05] 2890 4230 10.21

[<7.473E-05] 2890 4500 10.43

[<7.336E-05] 2890 4540 10.11

[<2.790E-05] 2890 4230 10.21

[<2.744E-05] 2890 4500 10.43

[<2.693E-05] 2890 4540 10.11

[<1.391E-04] 2890 4230 10.21

[<1.368E-04] 2890 4500 10.43

[<1.343E-04] 2890 4540 10.11

[<1.535E-03] 2890 4230 10.21

[<1.692E-03] 2890 4500 10.43

[<1.021E-03] 2890 4540 10.11

[<4.840E-03] 2890 4230 10.21

[<4.778E-03] 2890 4500 10.43

[<4.693E-03] 2890 4540 10.11

[<2.614E-05] 2890 4230 10.21

[<2.574E-05] 2890 4500 10.43

[<2.526E-05] 2890 4540 10.11

[<2.610E-05] 2890 4230 10.21

[<2.572E-05] 2890 4500 10.43

[<2.526E-05] 2890 4540 10.11

[<2.872E-05] 2890 4230 10.21

[<2.829E-05] 2890 4500 10.43

[<2.778E-05] 2890 4540 10.11

[<2.000E-04] 2890 4230 10.21

[<2.231E-04] 2890 4500 10.43

[<1.689E-04] 2890 4540 10.11

[<2.890E-05] 2890 4230 10.21

[<2.995E-05] 2890 4500 10.43

[<2.793E-05] 2890 4540 10.11

[<3.119E-05] 2890 4230 10.21

[<3.070E-05] 2890 4500 10.43

[<3.213E-05] 2890 4540 10.11

Steam Output (1000 

lb/hr)

Total Heat Input 

(mmBtu/hr) Flue Gas Moisture (%)

alculated Emission Rate
[<3.380E-05] 2890 4230 10.21

[<3.323E-05] 2890 4500 10.43

[<3.261E-05] 2890 4540 10.11

[<3.360E-04] 2890 4230 10.21

[<3.314E-04] 2890 4500 10.43

[<3.255E-04] 2890 4540 10.11

[<3.228E-05] 2890 4230 10.21

[<3.181E-05] 2890 4500 10.43

[<3.123E-05] 2890 4540 10.11

[<1.190E-02] 2890 4230 10.21

[<1.445E-02] 2890 4500 10.43

[<5.981E-03] 2890 4540 10.11

[<3.327E-05] 2890 4230 10.21

[<3.276E-05] 2890 4500 10.43

[<3.216E-05] 2890 4540 10.11

[<3.877E-05] 2890 4230 10.21

[<3.819E-05] 2890 4500 10.43

[<3.750E-05] 2890 4540 10.11

[<1.924E-04] 2890 4230 10.21

[<1.898E-04] 2890 4500 10.43

[<1.863E-04] 2890 4540 10.11

[<2.630E-05] 2890 4230 10.21

[<2.581E-05] 2890 4500 10.43

[<2.533E-05] 2890 4540 10.11

[<4.245E-05] 2890 4230 10.21

[<4.176E-05] 2890 4500 10.43

[<4.098E-05] 2890 4540 10.11

[<4.279E-05] 2890 4230 10.21

[<4.222E-05] 2890 4500 10.43

[<4.146E-05] 2890 4540 10.11

[<3.335E-06] 2890 4230 10.21

[<3.287E-05] 2890 4500 10.43

[<3.228E-05] 2890 4540 10.11

[<3.575E-05] 2890 4230 10.21

[<3.523E-05] 2890 4500 10.43

[<3.459E-05] 2890 4540 10.11

[<1.276E-04] 2890 4230 10.21

[<2.015E-04] 2890 4500 10.43

[<1.837E-04] 2890 4540 10.11

[<3.541E-05] 2890 4230 10.21

[<3.489E-05] 2890 4500 10.43

[<3.426E-05] 2890 4540 10.11

[<6.012E-05] 2890 4230 10.21

[<5.927E-05] 2890 4500 10.43

[<5.820E-05] 2890 4540 10.11

[<3.629E-05] 2890 4230 10.21

[<3.569E-05] 2890 4500 10.43

[<3.502E-05] 2890 4540 10.11

[<7.207E-05] 2890 4230 10.21
[<7.112E-05] 2890 4500 10.43

[<6.985E-05] 2890 4540 10.11

[<5.434E-05] 2890 4230 10.21

[<5.348E-05] 2890 4500 10.43

[<5.250E-05] 2890 4540 10.11

[<5.268E-05] 2890 4230 10.21

[<5.192E-05] 2890 4500 10.43

[<5.098E-05] 2890 4540 10.11

[<4.335E-05] 2890 4230 10.21

[<4.275E-05] 2890 4500 10.43

[<4.197E-05] 2890 4540 10.11

[<3.113E-05] 2890 4230 10.21

[<3.062E-05] 2890 4500 10.43

[<3.005E-05] 2890 4540 10.11

[<5.370E-05] 2890 4230 10.21

[<5.290E-05] 2890 4500 10.43

[<5.194E-05] 2890 4540 10.11

[<3.799E-05] 2890 4230 10.21

[<3.739E-05] 2890 4500 10.43

[<3.669E-05] 2890 4540 10.11

[<3.164E-05] 2890 4230 10.21

[<3.114E-05] 2890 4500 10.43

[<3.057E-05] 2890 4540 10.11

[<3.523E-05] 2890 4230 10.21

[<3.254E-05] 2890 4500 10.43

[<3.354E-05] 2890 4540 10.11

[<3.389E-05] 2890 4230 10.21

[<3.324E-05] 2890 4500 10.43

[<3.260E-05] 2890 4540 10.11

[<2.381E-04] 2890 4230 10.21

[<2.345E-04] 2890 4500 10.43

[<2.302E-04] 2890 4540 10.11

[<2.917E-05] 2890 4230 10.21

[<2.873E-05] 2890 4500 10.43

[<2.821E-05] 2890 4540 10.11

[<2.610E-05] 2890 4230 10.21

[<2.572E-05] 2890 4500 10.43

[<2.526E-05] 2890 4540 10.11

1.172E-03 2890 4230 10.21

6.842E-04 2890 4500 10.43

8.449E-04 2890 4540 10.11

[<3.484E-03] 2890 4230 10.21

[<3.440E-03] 2890 4500 10.43

[<3.379E-03] 2890 4540 10.11

[<2.722E-04] 2890 4230 10.21

[<2.688E-04] 2890 4500 10.43

[<2.640E-04] 2890 4540 10.11

[<2.906E-05] 2890 4230 10.21

[<2.868E-05] 2890 4500 10.43
[<2.817E-05] 2890 4540 10.11

[<4.763E-05] 2890 4230 10.21

[<4.309E-05] 2890 4500 10.43

[<4.826E-05] 2890 4540 10.11

[<2.303E-05] 2890 4230 10.21

[<2.266E-05] 2890 4500 10.43

[<2.224E-05] 2890 4540 10.11

[<6.048E-05] 2890 4230 10.21

[<5.963E-05] 2890 4500 10.43

[<5.854E-05] 2890 4540 10.11

[<2.331E-05] 2890 4230 10.21

[<2.293E-05] 2890 4500 10.43

[<2.251E-05] 2890 4540 10.11

[<1.263E-04] 2890 4230 10.21

[<1.278E-04] 2890 4500 10.43

[<1.267E-04] 2890 4540 10.11

[<2.772E-05] 2890 4230 10.21

[<1.923E-05] 2890 4500 10.43

[<1.884E-05] 2890 4540 10.11

[<3.107E-05] 2890 4230 10.21

[<3.053E-05] 2890 4500 10.43

[<2.996E-05] 2890 4540 10.11

[<2.646E-05] 2890 4230 10.21

[<2.598E-05] 2890 4500 10.43

[<2.548E-05] 2890 4540 10.11

[<2.613E-04] 2890 4230 10.21

[<2.581E-04] 2890 4500 10.43

[<2.536E-04] 2890 4540 10.11

[<5.856E-05] 2890 4230 10.21

[<5.776E-05] 2890 4500 10.43

[<5.672E-05] 2890 4540 10.11

[<5.932E-05] 2890 4230 10.21

[<8.944E-05] 2890 4500 10.43

[<8.088E-05] 2890 4540 10.11

[<5.911E-04] 2890 4230 10.21

[<5.839E-04] 2890 4500 10.43

[<5.738E-04] 2890 4540 10.11

[<4.362E-05] 2890 4230 10.21

[<4.303E-05] 2890 4500 10.43

[<4.226E-05] 2890 4540 10.11

[<5.223E-05] 2890 4230 10.21

[<5.158E-05] 2890 4500 10.43

[<5.067E-05] 2890 4540 10.11

[<1.180E-04] 2890 4230 10.21

[<1.161E-04] 2890 4500 10.43

[<1.140E-04] 2890 4540 10.11

[<7.127E-05] 2890 4230 10.21

[<6.656E-05] 2890 4500 10.43

[<7.280E-05] 2890 4540 10.11
[<3.473E-05] 2890 4230 10.21

[<3.418E-05] 2890 4500 10.43

[<3.514E-05] 2890 4540 10.11



14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

Flue Gas O2 (%) Flue Gas Flow Rate 

(scfm)

Flue Gas Temperature 

(F) Flue Gas CO2

 (%)
14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309
14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318
14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323

14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323
14.6 6.9 1046278 309

14.6 6.7 1046409 318

14.8 6.5 1046600 323



Fuel Input Rate Fuel Type Units of Measure Measurement Method

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

Fuel #1
4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation
4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation
4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation

4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation
4230 subbituminous MMBtu/hr boiler efficiency calculation

4500 subbituminous MMBtu/hr boiler efficiency calculation

4540 subbituminous MMBtu/hr boiler efficiency calculation



Fuel Input Rate Fuel Type Units of Measure Measurement Method

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

Fuel #2
y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation
y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation
y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation

y calculation
y calculation

y calculation

y calculation



Fuel Input Rate Fuel Type Units of Measure Measurement Method

Fuel #3







Fuel Input Rate Fuel Type Units of Measure Measurement Method

Fuel #4







Other Supporting 

Information







EIA Facility Code Facility Name Boiler ID Footnotes:

6085 SCHAHFER 14 * Front Half Composite contains particulate filter, front half of the filter holder, and probe solvent rinses

** Back Half Composite contains XAD-2 resin tube, back half of the filter holder, and coil condenser solvent rinses

*** Condensate Composite contains condensate and Impinger contents and the glassware solvent rinses

Speciated Semi-Volatile Organic HAP Emission Data

Measured Value (μg/m3) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Front Half mass* (ng) Back Half mass* (ng) Condensate Mass*** (ng) Total Composite (ng) Test Method Comments lb/mmBtu ppmdv @ 7% O2 Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method

Acenaphthene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0709 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 70.00 32.00 25.00 127.00 6.358E-08 1.116E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Acenaphthene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.0932 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 88.00 42.00 32.00 162.00 8.354E-08 1.447E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Acenaphthene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.1246 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 130.00 35.00 50.00 215.00 1.106E-07 1.907E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Acenaphthylene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0087 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 2.40 12.00 1.20 15.60 7.936E-09 1.390E-06 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Acenaphthylene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.0070 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 2.90 7.90 1.40 12.20 6.291E-09 1.104E-06 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Acenaphthylene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.0082 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 4.30 8.10 1.80 14.20 7.308E-09 1.276E-06 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Anthracene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0380 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 32.00 18.00 18.00 68.00 3.459E-08 5.172E-06 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Anthracene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.0725 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 71.00 25.00 30.00 126.00 6.498E-08 9.735E-06 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Anthracene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.0812 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 94.00 14.00 32.00 140.00 7.205E-08 1.075E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (a) anthracene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0042] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 3.00 7.50 [<3.815E-09] [<4.454E-07] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (a) anthracene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0043] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 3.00 7.50 [<3.868E-09] [<4.524E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (a) anthracene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0043] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 3.00 7.50 [<3.860E-09] [<4.495E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (b) fluoranthene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0231 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 4.30 34.00 3.10 41.40 2.106E-08 2.224E-06 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (b) fluoranthene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0075] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 3.20 6.90 3.00 13.10 [<6.755E-09] [<7.149E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (b) fluoranthene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0094] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 3.30 10.00 3.00 16.30 [<8.389E-09] [<8.838E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (k) fluoranthene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0479] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.70 82.00 2.00 85.70 [<4.360E-08] [<4.605E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (k) fluoranthene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0493] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.70 82.00 2.00 85.70 [<4.419E-08] [<4.677E-06] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (k) fluoranthene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0497] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.70 82.00 2.00 85.70 [<4.410E-08] [<4.647E-06] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (ghi) perylene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0763] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 5.60 130.00 1.00 136.60 [<6.949E-08] [<6.702E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (ghi) perylene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0066] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 5.60 4.80 1.00 11.40 [<5.879E-09] [<5.681E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (ghi) perylene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0059] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 5.60 3.60 1.00 10.20 [<5.249E-09] [<5.050E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (a) pyrene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0168] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.90 26.00 2.20 30.10 [<1.531E-08] [<1.617E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (a) pyrene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0052] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.90 6.40 0.80 9.10 [<4.693E-09] [<4.966E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (a) pyrene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0064] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.90 8.40 0.80 11.10 [<5.713E-09] [<6.019E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (e) pyrene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0176] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 2.80 26.00 2.80 31.60 [<1.608E-08] [<1.698E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (e) pyrene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0064] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.80 5.60 2.80 11.20 [<5.776E-09] [<6.112E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Benzo (e) pyrene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0065] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.80 5.60 2.80 11.20 [<5.764E-09] [<6.073E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Chrysene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0077 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 3.50 8.80 1.40 13.70 6.969E-09 8.136E-07 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Chrysene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0080] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.50 11.00 1.40 13.90 [<7.168E-09] [<8.384E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Chrysene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.0059 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 4.60 4.10 1.50 10.20 5.249E-09 6.113E-07 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Dibenz (a,h) anthracene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0044] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.60 3.60 1.60 7.80 [<3.968E-09] [<3.799E-07] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Dibenz (a,h) anthracene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0045] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.60 3.60 1.60 7.80 [<4.022E-09] [<3.859E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Dibenz (a,h) anthracene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0045] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.60 3.60 1.60 7.80 [<4.014E-09] [<3.834E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Fluoranthene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.1781 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 160.00 100.00 59.00 319.00 1.623E-07 2.138E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Fluoranthene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.2336 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 210.00 120.00 76.00 406.00 2.094E-07 2.764E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Fluoranthene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.3130 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 300.00 120.00 120.00 540.00 2.779E-07 3.653E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Fluorene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.1346 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 120.00 77.00 44.00 241.00 1.226E-07 1.966E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Fluorene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.2048 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 160.00 140.00 56.00 356.00 1.836E-07 2.949E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Fluorene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.2313 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 230.00 80.00 89.00 399.00 2.053E-07 3.284E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Indeno(1,2,3-cd)pyrene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0148] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.50 23.00 2.00 26.50 [<1.348E-08] [<1.300E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Indeno(1,2,3-cd)pyrene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0033] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.50 2.30 2.00 5.80 [<2.991E-09] [<2.890E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Indeno(1,2,3-cd)pyrene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0031] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 1.80 2.00 5.30 [<2.728E-09] [<2.624E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

2-Methylnaphthalene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.1586 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 120.00 120.00 44.00 284.00 1.445E-07 2.708E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

2-Methylnaphthalene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.2336 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 150.00 200.00 56.00 406.00 2.094E-07 3.931E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

2-Methylnaphthalene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.2255 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 210.00 90.00 89.00 389.00 2.002E-07 3.743E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Naphthalene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.3306] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 97.00 460.00 35.00 592.00 [<3.012E-07] [<6.262E-05] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Naphthalene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.5776] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 110.00 850.00 44.00 1004.00 [<5.177E-07] [<1.079E-04] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Naphthalene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.3895] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 150.00 460.00 62.00 672.00 [<3.458E-07] [<7.173E-05] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Perylene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0034] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 1.60 6.10 [<3.103E-09] [<3.278E-07] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Perylene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0035] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 1.60 6.10 [<3.146E-09] [<3.329E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Perylene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0035] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 1.60 6.10 [<3.139E-09] [<3.308E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Phenanthrene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 1.0443 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 950.00 580.00 340.00 1870.00 9.513E-07 1.422E-04 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Phenanthrene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 1.3405 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 1200.00 700.00 430.00 2330.00 1.202E-06 1.800E-04 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Phenanthrene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 1.7390 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 1700.00 600.00 700.00 3000.00 1.544E-06 2.303E-04 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Pyrene1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0760] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 60.00 53.00 23.00 136.00 [<6.918E-08] [<9.116E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation

Pyrene2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0892] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 73.00 55.00 27.00 155.00 [<7.993E-08] [<1.055E-05] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation

Pyrene3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.1130] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 100.00 53.00 42.00 195.00 [<1.004E-07] [<1.319E-05] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation

Steam Output (1000 lb/hr) Total Heat Input 

(mmBtu/hr)

Fuel #4 Other Supporting 

Information Flue Gas O2 (%) Flue Gas Flow Rate (scfm) Flue Gas Temperature (F) Fuel #1 Fuel #2 Fuel #3 Flue Gas Moisture (%) Flue Gas CO2 (%) Compound (use drop down to define for as many rows as needed) Run Number Test Start Date Test Start Time Test End Date Test End Time Semi-Volatile Organic HAP Emission Test Results Calculated Emission Rate

EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

1 4/27/2010 8:45 4/27/2010

2 4/27/2010 12:00 4/27/2010

3 4/27/2010 15:25 4/27/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

10:15 [<1.45E-04] Dry U.S. EPA Conditional Test Method 033 (CTM-033)

13:15 [<8.31E-05] Dry U.S. EPA Conditional Test Method 033 (CTM-033)

16:40 [<7.85E-05] Dry U.S. EPA Conditional Test Method 033 (CTM-033)

Test End Time

Hydrogen Cyanide Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<1.45E-04] 2771.6 4384 17.4 14.3

BDL [<8.31E-05] 2771.6 4393 13.14 14.1

BDL [<7.85E-05] 2771.6 4416 13.78 14.2

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

5.4 886138 286 4384 subbituminous MMBtu/hr gas fuel meter

5.3 916325 293 4393 subbituminous MMBtu/hr gas fuel meter

5.5 908477 292 4416 subbituminous MMBtu/hr gas fuel meter

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

O2 (%)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

[<208]

[<124]

[<118]

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

Hydrogen Chloride Emission Test Results

Test End Time
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

 Test Results

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used Test End Time

Hydrogen Flouride Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

Test Results

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time
Measured NO (ppm) Test End Date Test End Time
Measured NO2

 (ppm) Basis (Wet or Dry) Test Method Used 

NOX Emission Test Results
Data Flag (ADL, BDL, DDL) Test Method Comments (lb/mmBtu)

Total NOX Calculated Emission Rate
ppmdv @ 7% O2

Flue Gas 

O2 (%)

 Calculated Emission Rate Steam Output 

(1000 lb/hr)

Total Heat Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)

Flue Gas 

CO2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time
Total Dissolved Solids 

(mg solids/liter)

Total Suspended Solids 

(mg solids/liter)

Test End Date Test End Time
Test Method Used Data Flag (ADL, 

BDL, DDL)

Constisuent Emission Test Results
Test Method Comments Fuel Input Rate

Flue Gas 

Flow Rate 

(dscfm)

Steam Output 

(1000 lb/hr)

Total Heat Input 

(mmBtu/hr)

Flue Gas 

Temperat

ure (F)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate

Fuel #1 Fuel #2
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #3 Fuel #4
Other Supporting Information





Fuel

anthracite

bituminous

subbituminous

lignite

coal refuse (culm or gob)

No.2 Fuel Oil (distillate)

No.6 Fuel Oil (residual or bunker C)

synfuel

petroleum coke

other

Relative to Control Device

Upstream

Downstream

Fuel Input Units of Measure

MMBtu/hr

standard cubic feet per minute (scfm)

gallon/minute

lb/hour

ton/day

Exhaust Flow Rate Units of Measure

acfm

dscfm

Exhaust Temperature Units of Measure

deg C

deg F

Test Method Used for Fuel Input Rate

F-Factor

gas fuel meter

boiler efficiency calculation

Other

CO Test Method

U.S. EPA Method 10A

U.S. EPA Method 10B

Formaldehyde Test Method
U.S. EPA Method 320

U.S. EPA Method 0011

U.S. EPA Method 316

CH4 Test Method

U.S. EPA Method 18

U.S. EPA Method 320

SO2 Test Method

U.S. EPA Method 6

Hg Test Method

U.S. EPA Method 30B

Speciated Volatile Organic HAP Method

U.S. EPA Method 0031 with SW-846 Method 8260B

U.S. EPA Method 0031/TO-15

Speciated Semi-Volatile Organic HAP Method

U.S. EPA Method 0010 with SW-846 Method 8270C

U.S. EPA Method 0010 with SW-846 Method 8270D

HCN Test Method

U.S. EPA Conditional Test Method 033 (CTM-033)

U.S. EPA Method 320

CARB 426

U.S. EPA Method 26A-Mod

O2/CO2 Test Method

U.S. EPA Method 3B

NOX Test Method

U.S. EPA Method 7

U.S. EPA Method 7A

U.S. EPA Method 7B

U.S. EPA Method 7C

U.S. EPA Method 7D

TDS/TSS Test Method

Standard Test Method for Filterable and Nonfilterable Matter in Water ASTM D5907

Standard Methods of the Examination of Water and Wastewater Method 2540B

Control Configuration

Listed (by boiler) in Question 16 (page 17) of the questionnaire
Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR

Hg Ontario Hydro Test Method

ASTM Method D6784

HCL Test Methods

U.S. EPA Method 320

U.S. EPA Method 26

HF Test Methods

U.S. EPA Method 320

U.S. EPA Method 26

Basis

Wet

Dry


Constituent CAS

Methyl chloride 74-87-3

1,1,2-Trichloroethane 79-00-5

1,1-Dimethylhydrazine 57-14-7

1,2-dichloroethane

1,2,4-Trichlorobenzene 120-82-1

1,2-Dibromo-3-chloropropane 96-12-8

1,2-Epoxybutane (1,2-butylene oxide) 106-88-7

1,2-Propyleneimine (2-methylaziridine) 75-55-8

1,3-Butadiene 106-99-0

1,3-Dichloropropene 542-75-6

1,3-Propane sultone 1120-71-4

1,4-Dichlorobenzene (p-) 106-46-7

1,4-Dioxane (1,4-Diethylene oxide) 123-91-1

2,2,4-Trimethyl pentane 540-84-1

2-Nitropropane 79-46-9

Acetaldehyde 75-07-0

Acetonitrile (cyanomethane) 75-05-8

Acetophenone 98-86-2

Acrolein (2-propenal) 107-02-8

Acrylamide 79-06-1

Acrylic acid 79-10-7

Acrylonitrile (2-propenenitrile) 107-13-1

Allyl chloride (3-chloropropene) 107-05-1

Aniline (aminobenzene) 62-53-3

Benzene 71-43-2

Benzyl chloride (a-chlorotoluene) 100-44-7

Beta-Propiolactone 57-57-8

Bis(2-Chloroethyl)ether 111-44-4

Bis(chloromethyl) ether 542-88-1

Bromoform (tribromomethane) 75-25-2

Carbon disulfide 75-15-0

Carbon tetrachloride 56-23-5

Carbonyl sulfide 463-58-1

Catechol (o-hydroxyphenol) 120-80-9

Chloroacetic acid 79-11-8

Chlorobenzene 108-90-7

Chloroform 67-66-3

Chloromethyl methyl ether 107-30-2

Chloroprene (2-chloro-1,3-butadiene) 126-99-8

Cresylic acid (cresol isomer mixture) 1319-77-3

Cumene (isopropylbenzene) 98-82-8

Diazomethane 334-88-3

Diethyl sulfate 64-67-5

Dimethyl sulfate 77-78-1

Dimethylcarbamyl chloride 79-44-7

Epichlorohydrin (1-chloro-2,3-epoxy

propane) 106-89-8

Ethyl acrylate 140-88-5

Ethyl carbamate (urethane) 51-79-6

Speciated Volatile Organic HAPs
Ethyl chloride 75-00-3

Ethylbenzene 100-41-4

Ethylene dibromide (1,2-dibromoethane) 106-93-4

Ethylene dichloride (1,2-dichloroethane) 107-06-2

Ethylene oxide 75-21-8

Ethyleneimine (aziridine) 151-56-4

Ethylidene dichloride (1,1-dichloroethane) 75-34-3

Formaldehyde 50-00-0

Hexachlorobutadiene 87-68-3

Hexachloroethane 67-72-1

Hexane 110-54-3

Isophorone 78-59-1

1, 1, 2, 2-Tetrachloroethane 79-34-5

Methanol 67-56-1

Methyl bromide 74-83-9.

Methyl chloroform (1,1,1-trichloroethane) 71-55-6

Methyl ethyl ketone (2-butanone) 78-93-3

Methyl iodide 74-88-4

Methyl isobutyl ketone (hexone) 108-10-1

Methyl isocyanate 624-83-9

Methyl methacrylate 80-62-6

Methyl tert-butyl ether 1634-04-4

Methylene chloride 75-09-2

Methylhydrazine 60-34-4

m-Xylene 108-38-3

N,N-Dimethylaniline 100-23-2

N,N-Dimethylformamide 68-12-2

Nitrobenzene 98-95-3

N-Nitrosodimethylamine 62-75-9

N-Nitrosomorpholine 59-89-2

N-Nitroso-N-methylurea 684-93-5

o-Cresol 95-48-7

o-Xylene 95-47-6

Phenol 108-95-2

Phosgene 75-44-5

Propionaldehyde 123-38-6

Propylene dichloride (1,2-dichloropropane) 78-87-5

Propylene oxide 75-56-9 

p-Xylene 106-42-3

Styrene 100-42-5

Styrene oxide 96-09-3

sec-Butylbenzene

Tetrachloroethylene 127-18-4

Toluene 108-88-3

Trichloroethylene 79-01-6

Triethylamine 121-44-8

Vinyl acetate 108-05-04

Vinyl bromide 593-60-2

Vinyl chloride (chloroethene) 75-01-4

Vinylidene chloride 75-35-4

Xylenes (isomer & mixtures) 1330-20-7
lectronic ICR







Speciated Semi-volatile Organic HAPs

Constituent CAS

2-Methylnaphthalene 91-57-6

Acenaphthene 83-32-9

Acenaphthylene 208-96-8

Anthracene 120-12-7

Benzo(a)anthracene 56-55-3

Benzo(a)pyrene 50-32-8

Benzo(b)fluoranthene 205-99-2

Benzo(e)pyrene 192-97-2

Benzo(g,h,i)perylene 191-24-2

Benzo(k)fluoranthene 207-08-9

Chrysene 218-01-9

Dibenzo(a,h)anthracene 53-70-3

Fluoranthene 206-44-0

Fluorene 86-73-7

Indeno(1,2,3-cd)pyrene 193-39-5

Naphthalene 91-20-3

Perylene 77392-71-3

Phenanthrene 85-01-8

Pyrene 129-00-0

Acetophenone 98-86-2

2-Acetylaminofluorene 53-96-3

1-Acetyl-2-thiourea 591-08-2

Aldrin 309-00-2

2-Aminoanthraquinone 117-79-3

Aminoazobenzene 60-09-3

4-Aminobiphenyl 92-67-1

3-Amino-9-ethylcarbazole 132-32-1

Anilazine 101-05-3

Aniline 62-53-3

o-Anisidine 90-04-0

Aramite 140-57-8

Aroclor 1016 12674-11-2

Aroclor 1221 11104-28-2

Aroclor 1232 11141-16-5

Aroclor 1242 53469-21-9

Aroclor 1248 12672-29-6

Aroclor 1254 11097-69-1

Aroclor 1260 11096-82-5

Azinphos-methyl 86-50-0

Barban 101-27-9

Benzidine 92-87-5

Benzoic acid 65-85-0

p-Benzoquinone 106-51-4

Benzyl alcohol 100-51-6

α-BHC 319-84-6

β-BHC 319-85-7

δ-BHC 319-86-8
γ-BHC (Lindane) 58-89-9

Bis(2-chloroethoxy)methane 111-91-1

Bis(2-chloroethyl) ether 111-44-4

Bis(2-chloroisopropyl) ether 39638-32-9

Bis(2-ethylhexyl) phthalate 117-81-7

4-Bromophenyl phenyl ether 101-55-3

Bromoxynil 1689-84-5

Butyl benzyl phthalate 85-68-7

Captafol 2425-06-1

Captan 133-06-2

Carbaryl 63-25-2

Carbofuran 1563-66-2

Carbophenothion 786-19-6

Chlordane (NOS) 57-74-9

Chlorfenvinphos 470-90-6

4-Chloroaniline 106-47-8

Chlorobenzilate 510-15-6

5-Chloro-2-methylaniline 95-79-4

4-Chloro-3-methylphenol 59-50-7

3-(Chloromethyl)pyridine hydrochloride 6959-48-4

1-Chloronaphthalene 90-13-1

2-Chloronaphthalene 91-58-7

2-Chlorophenol 95-57-8

4-Chloro-1,2-phenylenediamine 95-83-0

4-Chloro-1,3-phenylenediamine 5131-60-2

4-Chlorophenyl phenyl ether 7005-72-3

Coumaphos 56-72-4

p-Cresidine 120-71-8

Crotoxyphos 7700-17-6

2-Cyclohexyl-4,6-dinitro-phenol 131-89-5

4,4'-DDD 72-54-8

4,4'-DDE 72-55-9

4,4'-DDT 50-29-3

Demeton-O 298-03-3

Demeton-S 126-75-0

Diallate (cis or trans) 2303-16-4

2,4-Diaminotoluene 95-80-7

Dibenz(a,j)acridine 224-42-0

Dibenzofuran 132-64-9

Dibenzo(a,e)pyrene 192-65-4

1,2-Dibromo-3-chloropropane 96-12-8

Di-n-butyl phthalate 84-74-2

Dichlone 117-80-6

1,2-Dichlorobenzene 95-50-1

1,3-Dichlorobenzene 541-73-1

1,4-Dichlorobenzene 106-46-7

3,3'-Dichlorobenzidine 91-94-1

2,4-Dichlorophenol 120-83-2

2,6-Dichlorophenol 87-65-0

Dichlorovos 62-73-7
Dicrotophos 141-66-2

Dieldrin 60-57-1

Diethyl phthalate 84-66-2

Diethylstilbestrol 56-53-1

Diethyl sulfate 64-67-5

Dimethoate 60-51-5

3,3'-Dimethoxybenzidine 119-90-4

Dimethylaminoazobenzene 60-11-7

7,12-Dimethylbenz(a)-anthracene 57-97-6

3,3'-Dimethylbenzidine 119-93-7

α,α-Dimethylphenethylamine 122-09-8

2,4-Dimethylphenol 105-67-9

Dimethyl phthalate 131-11-3

1,2-Dinitrobenzene 528-29-0

1,3-Dinitrobenzene 99-65-0

1,4-Dinitrobenzene 100-25-4

4,6-Dinitro-2-methylphenol 534-52-1

2,4-Dinitrophenol 51-28-5

2,4-Dinitrotoluene 121-14-2

2,6-Dinitrotoluene 606-20-2

Dinocap 39300-45-3

Dinoseb 88-85-7

Diphenylamine 122-39-4

5,5-Diphenylhydantoin 57-41-0

1,2-Diphenylhydrazine 122-66-7

Di-n-octyl phthalate 117-84-0

Disulfoton 298-04-4

Endosulfan I 959-98-8

Endosulfan II 33213-65-9

Endosulfan sulfate 1031-07-8

Endrin 72-20-8

Endrin aldehyde 7421-93-4

Endrin ketone 53494-70-5 X X ND X X 53494-70-5

EPN 2104-64-5

Ethion 563-12-2

Ethyl carbamate 51-79-6

Ethyl methanesulfonate 62-50-0

Famphur 52-85-7

Fensulfothion 115-90-2

Fenthion 55-38-9

Fluchloralin 33245-39-5

2-Fluorobiphenyl (surr) 321-60-8

2-Fluorophenol (surr) 367-12-4

Heptachlor 76-44-8

Heptachlor epoxide 1024-57-3

Hexachlorobenzene 118-74-1

Hexachlorobutadiene 87-68-3

Hexachlorocyclopentadiene 77-47-4

Hexachloroethane 67-72-1

Hexachlorophene 70-30-4

Hexachloropropene 1888-71-7

Hexamethylphosphoramide 680-31-9

Hydroquinone 123-31-9

Isodrin 465-73-6
Isophorone 78-59-1

Isosafrole 120-58-1

Kepone 143-50-0

Leptophos 21609-90-5

Malathion 121-75-5

Maleic anhydride 108-31-6

Mestranol 72-33-3

Methapyrilene 91-80-5

Methoxychlor 72-43-5

3-Methylcholanthrene 56-49-5

4,4'-Methylenebis (2-chloroaniline) 101-14-4

4,4'-Methylenebis(N,N-dimethylaniline) 101-61-1

3-Methylphenol & 4-Methylphenol

2-Methylnaphthalene

Methyl methanesulfonate 66-27-3

Methyl parathion 298-00-0

2-Methylphenol 95-48-7

3-Methylphenol 108-39-4

4-Methylphenol 106-44-5

Mevinphos 7786-34-7

Mexacarbate 315-18-4

Mirex 2385-85-5

Monocrotophos 6923-22-4

Naled 300-76-5

Naphthalene

1,4-Naphthoquinone 130-15-4

1-Naphthylamine 134-32-7

2-Naphthylamine 91-59-8

Nicotine 54-11-5

5-Nitroacenaphthene 602-87-9

2-Nitroaniline 88-74-4

3-Nitroaniline 99-09-2

4-Nitroaniline 100-01-6

5-Nitro-o-anisidine 99-59-2

Nitrobenzene 98-95-3

4-Nitrobiphenyl 92-93-3

Nitrofen 1836-75-5

2-Nitrophenol 88-75-5

4-Nitrophenol 100-02-7

5-Nitro-o-toluidine 99-55-8

Nitroquinoline-1-oxide 56-57-5

N-Nitrosodi-n-butylamine 924-16-3

N-Nitrosodiethylamine 55-18-5

N-Nitrosodimethylamine 62-75-9

N-Nitrosodiphenylamine 86-30-6

N-Nitrosodi-n-propylamine 621-64-7

N-Nitrosomethylethylamine 10595-95-6

N-Nitrosomorpholine 59-89-2

N-Nitrosopiperidine 100-75-4

N-Nitrosopyrrolidine 930-55-2

Octamethyl pyrophosphoramide 152-16-9

4,4'-Oxydianiline 101-80-4

2,2-oxybis(1-Chloro-propane)

Parathion 56-38-2

Pentachlorobenzene 608-93-5
Pentachloronitrobenzene 82-68-8

Pentachlorophenol 87-86-5

Phenacetin 62-44-2

Phenenthrene

Phenobarbital 50-06-6

Phenol 108-95-2

1,4-Phenylenediamine 106-50-3

Phorate 298-02-2

Phosalone 2310-17-0

Phosmet 732-11-6

Phosphamidon 13171-21-6

Phthalic anhydride 85-44-9

Pyrene

Pyridine

2-Picoline (2-Methylpyridine) 109-06-8

Piperonyl sulfoxide 120-62-7

Pronamide 23950-58-5

Propylthiouracil 51-52-5

Resorcinol 108-46-3

Safrole 94-59-7

Strychnine 57-24-9

Sulfallate 95-06-7

Terbufos 13071-79-9

1,2,4-Tetrachlorobenzene

1,2,4,5-Tetrachlorobenzene 95-94-3

2,4,5-Tetrachlorophenol 58-90-2

2,4,6-Tetrachlorophenol

Tetrachlorvinphos 961-11-5

Tetraethyl dithiopyrophosphate 3689-24-5

Tetraethyl pyrophosphate 107-49-3

Thionazine 297-97-2

Thiophenol (Benzenethiol) 108-98-5

Toluene diisocyanate 584-84-9

o-Toluidine 95-53-4

Toxaphene 8001-35-2

1,2,4-Trichlorobenzene 120-82-1

2,4,5-Trichlorophenol 95-95-4

2,4,6-Trichlorophenol 88-06-2

Trifluralin 1582-09-8

2,4,5-Trimethylaniline 137-17-7

Trimethyl phosphate 512-56-1

1,3,5-Trinitrobenzene 99-35-4

Tris(2,3-dibromopropyl) phosphate 126-72-7

Tri-p-tolyl phosphate 78-32-0

O,O,O-Triethyl phosphorothioate 126-68-1