Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

2594 2594 Oswego Harbor Power LLC NRG Oswego Harbor Power legal owner261 Washington Blvd Oswego NY 13126

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

Oswego Harbor Power 261 Washington Blvd Oswego NY 13126 261 Washington Blvd Oswego NY 13126

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

No FALSE TRUE TRUE FALSE FALSE FALSE TRUE TRUE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE FALSE Title V Semi-annual report No EPA Region 2Present operating gross efficiency for both boilers cannot be provided 

Page 4
Facility_Information

y for both boilers cannot be provided as it has not been done in over 10 years.For oil utilized information, No. 6 Fuel Oil versus natural ga

Page 5
Facility_Information

tion, No. 6 Fuel Oil versus natural gas percentages are calculated on a mmBtu basis only.No fuel oil has been received at this facility for 

Page 6
Facility_Information

 has been received at this facility for over 12 months.

Page 7
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

2594 1 Environmental Compliance Coordinator Marion Greenhalgh 31534923653155297019marion.greenhalgh@oswegopower.com TRUE

Page 8
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

Page 9
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

2594 No.6 Fuel Oil (residual or bunker C) 100 100

Page 10
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

Page 11
facility_other_materials

rcra_explain

Page 12
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

2594 5 Wall firing - front firing Dry Bottomfuel oil 7840 7840 871.43

2594 6 Wall firing - front firing Dry Bottomfuel oil 7840 7840 867.43

Page 13
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

839.75 90.27 2285 2285 1000 1000 FALSE 1000

835.75 90.27 2285 2285 1000 1000 FALSE 1000

Page 14
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 1000 209.72 1.06 N TRUE

FALSE 1000 174.04 0.86 Subpart D TRUE

Page 15
boiler_information

NOx_controlSO2_controlcombustion_additives

Yes No No

Yes No No

Page 16
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

2594 5 natural gas 2007 2.8

2594 5 natural gas 2008 5.8

2594 5 natural gas 2009 10.2

2594 5 oil - residual or bunker 2007 97.2

2594 5 oil - residual or bunker 2008 94.2

2594 5 oil - residual or bunker 2009 89.8

2594 6 natural gas 2007 2.8

2594 6 natural gas 2008 4.9

2594 6 natural gas 2009 5

2594 6 oil - residual or bunker 2007 97.2

2594 6 oil - residual or bunker 2008 95.1

2594 6 oil - residual or bunker 2009 95

Page 17
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

2594 5 Flue Gas Recirculation 6/1/1998

2594 5 Low Excess Air 6/1/1998

2594 5 Overfire Air 6/1/1998

2594 6 Flue Gas Recirculation 12/1/1979

2594 6 Low Excess Air 12/1/1979

2594 6 Overfire Air 12/1/1979

Page 18
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

Page 19
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

Page 20
facility_units

facility_id unit_id

2594 5

2594 6

Page 21
unit_boilers

facility_id unit_id boiler_id

2594 5 5

2594 6 6

Page 22
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

2594 5ESP PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 6/1/1975

2594 6ESP PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 12/1/1979

Page 23
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

Page 24
facility_sampling_ports

facility_id sampling_port_id

Page 25
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

2594 5ST 700 30 43

2594 6ST 700 24 60

Page 26
configurations

facility_id configuration_id

2594 5

2594 6

Page 27
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

2594 5 5 5 Unit

2594 5 5ESP 5 PM control

2594 5 5ST 5 Stack

2594 6 6 6 Unit

2594 6 6ESP 6 PM control

2594 6 6ST 6 Stack

Page 28
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

2594 5 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 1.6 pound per million British Thermal Unit (lb/MMBtu) 3 hours

2594 5 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 1/permit

2594 5 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.25 pound per million British Thermal Unit (lb/MMBtu) 24hr/month

2594 6 PM (Filterable) Fderal - Title V Operating Permit 0.1 pound per million British Thermal Unit (lb/MMBtu) 1/permit

2594 6 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.3 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.25 pound per million British Thermal U

2594 6 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 0.8 pound per million British Thermal Unit (lb/MMBtu) 3 hours

Page 29
configuration_pollutants1

avg_period_2emlimit_3 emlimit_units_3 avg_period_3emlimit_4 emlimit_units_4 avg_period_4emlimit_details test_method

24hr/month 0.2 pound per million British Thermal Unit (lb/MMBtu) 3 hours

Page 30
configuration_pollutants1

emrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping req_reporting

CEMS Per Part 75Quarterly EDR

Stack Test Stack Test Report Annual Stack Test Report

CEMS Per Part 75Quarterly EDR

Stack Test Stack Test Report Annual stack test report

CEMS Per Part 75Quarterly EDR

CEMS Per Part 75Quaterly EDR

Page 31
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

Page 32
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

Page 33
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

Page 34
control_technologies

feed_rate_units

Page 35
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

Page 36
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

Page 37
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

Page 38
control_costs

CBI

Page 39
misc_controls

facility_id misc_control_id control_description

Page 40
misc_control_configurations

facility_id misc_control_id configuration_id

Page 41
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

Page 42
fuel_shipments

coal_seam shipment_method

Page 43
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

Page 44
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

Page 45
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

Page 46
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Page 47
fuel_shipment_samples

analysis_copies

Page 48
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

Page 49
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

2594 TSP Testing\902324 compliance Once per permit term particulates test. 8/1/2006 8/2/2006 No No

Page 50
test_reports

deviation_reports

No

Page 51
test_report_configurations

facility_id report_id configuration_id

2594 TSP Testing\902324 5

2594 TSP Testing\902324 6

Page 52
test_report_fuels

facility_id report_id fuel_id

2594 TSP Testing\902324 Residual Fuel Oil

Page 53
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

2594 TSP Testing\902324 Residual Fuel Oil oil - residual or bunker 100 100

Page 54
cem_data

facility_id time_periodcem_period_description

2594 11:30-15:30

2594 11:59-16:26

Page 55
cem_data_pollutants1

facility_id time_periodpollutant_name

2594 11:30-15:30PM (Filterable)

2594 11:59-16:26PM (Filterable)

Page 56
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

2594 TSP Testing\902324 5ST No No

2594 TSP Testing\902324 6ST No No

Page 57
test_report_sampling

fg_fraction

Page 58
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

2594 TSP Testing\902324 5ST average 8/2/2006 8/2/2006 791.63 791.63 9.91

2594 TSP Testing\902324 6ST average 8/1/2006 8/1/2006 822 822 11.95

Page 59
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

1762020 dscfm 68 29.92 6.8 10.5 288

1524995 dscfm 68 29.92 3.4 12 300

Page 60
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

0 EPA Method 1, 2, 3, 4, 5

0 EPA Methods 1, 2, 3, 4, & 5

Page 61
sampling_runs

fuel_sulfur

Page 62
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

2594 TSP Testing\902324 5ST average PM (Filterable) 0.72 milligram per cubic meter (mg/m3) FALSE

2594 TSP Testing\902324 6ST average PM (Filterable) 0.901 milligram per cubic meter (mg/m3) FALSE

Page 63
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

168.033 pound per hour (lb/hr) FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE Measuring unit for concentration is 

182.107 pound per hour (lb/hr) FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration measuring units are 

Page 64
sampling_run_pollutants1

run_pollutant_comment

Measuring unit for concentration is really mg/dscf

Concentration measuring units are really mg/dscf

Page 65
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

Page 66
sampling_run_fuel

fuel_conc_MDL

Page 67