### Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

-down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg+2

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg0

### , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

-downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

### (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

### and , HgP, and Hg+2 

### . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

-down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please alsoEIA

Facility Code Facility Name Boiler ID

6085 SCHAHFER 14Control Device Configuraton

Listed (by

boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICRListed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICREIA

Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start TimeMeasured Value (ppm)

Test End Date Test End TimeBasis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) CO Emission Test ResultsTest Method Comments lb/mmBtu ppmdv @ 7% O2 Calculated Emission RateSteam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%)Flue Gas O2(%) Flue Gas Flow Rate (dscfm) Flue Gas CO2(%)Fuel Input Rate Fuel Type

Flue Gas Temperature (F) Fuel #1Units of Measure Measurement Method Fuel Input Rate Fuel #1Fuel Type Units of Measure Measurement Method Fuel #2Fuel Input Rate Fuel Type Units of Measure Fuel #3Measurement Method Fuel Input Rate Fuel Type Fuel #4Units of Measure Measurement Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 6085 SCHAHFER 14

Test End Date Run Number Test Start Date Test Start TimeMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Formaldehyde Emission Test Results Test End TimeTest Method

Comments lb/mmBtu ppmdv @ 7% O2 Total Heat Input (mmBtu/hr) Calculated Emission Rate Steam Output (1000 lb/hr)Fuel Input Rate Fuel Type Units of Measure Flue Gas Temperature (F) Fuel #1 Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Flue Gas Flow

Rate (dscfm)Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Fuel #2 Fuel #3Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Other Supporting Information Fuel #4EIA

Facility Code Facility Name Boiler ID 6085 SCHAHFER 14

1 4/6/2010 7:30 2 4/6/2010 10:20 3 4/6/2010 13:25 Run Number Test Start Date Test Start TimeMeasured Value (ppm) Basis (Wet or Dry)

4/6/2010 9:30 5.5 Wet 4/6/2010 12:20 24 Wet 4/6/2010 15:25 21 Wet Test End Date Test End Time Methane Emission Test ResultsTest Method Used Data Flag (ADL, BDL, DDL) Test Method Comments lb/mmBtu

U.S. EPA Method 18 ADL 0.00366 U.S. EPA Method 18 ADL 0.01577 U.S. EPA Method 18 ADL 0.01362 Methane Emission Test Results Calculated Emission Rateppmdv @ 7% O2

5.46 2890 4230 10.21 14.6 6.9 1046278 23.49 2890 4500 10.43 14.6 6.7 1046409 20.27 2890 4540 10.11 14.8 6.5 1046600 Flue Gas O2(%) Flue Gas

Flow Rate (dscfm) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas CO2(%)Fuel Input Rate Fuel Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure 309 4230 subbituminous MMBtu/hr gas fuel meter 318 4500 subbituminous MMBtu/hr gas fuel meter 323 4540 subbituminous MMBtu/hr gas fuel meter Flue Gas Temperat ure (F) Fuel #1 Fuel #2Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure Fuel #4 Fuel #3Measurement

Method Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 6085 SCHAHFER 14

Test End Date Run Number Test Start Date Test Start TimeMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Test End Time SO2Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments lb/mmBtu ppmdv @ 7% O2 Calculated Emission Rate Steam Output (1000 lb/hr)Fuel Input Rate Fuel Type Flue Gas O2(%) Flue Gas

Flow Rate (dscfm) Total Heat Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO2(%) Flue Gas Temperature (F) Fuel #1Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Fuel #1 Fuel #2 Fuel #3Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Fuel #3Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 6085 R M Schahfer 14

1A 4/28/2010 10:15 2A 4/28/2010 15:20 3A 4/29/2010 7:05

Run Number Test Start Date Test Start TimePlease note QA/QC documentation starting in Column "AI"

Measured Value (μg/dscm) Basis (Wet or Dry)

4/28/2010 12:15 1.4058 Dry 4/28/2010 17:20 1.1955 Dry 4/29/2010 9:05 1.5026 Dry

Test End Time Test End Date Total Vapor Phase Mercury Emission Test ResultsPlease note QA/QC documentation starting in Column "AI"

Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments (lb/mmBtu)

U.S. EPA Method 30B ADL 1.34E-06 2756.9 U.S. EPA Method 30B ADL 1.06E-06 2756.9 U.S. EPA Method 30B ADL 1.29E-06 2703.2 Total Vapor Phase Mercury Emission Test Results Steam Output (1000 lb/hr)Fuel Input Rate

4580 6.99 13.8 5.4 1012278 290 4580 4590 6.87 13.7 5.4 1007550 296 4590 4540 6.74 14.2 5 1009947 295 4540 Flue Gas Temperature (F) Flue Gas Moisture (%) Total Heat Input (mmBtu/hr) Flue Gas CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm)Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate

subbituminous

MMBtu/hr gas fuel meter subbituminous

MMBtu/hr gas fuel meter subbituminous

MMBtu/hr gas fuel meter Fuel #1 Fuel #2Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #3 Fuel #4QA /QC Documentation

Trap ID Section 1

Mass (ng) Section 2

Mass (ng) Total

Mass (ng) Initial

Spike (ng) Total NonSpike (ng)

66183 167 0.1 167.1 0 167.1 68152 138 0.7 138.7 0 138.7 68166 174 0.3 174.3 0 174.3 Other Supporting InformationSample

Volume (dscm) Volume

Difference (%) Volume Diff. Limit Breaktrough

(%) Breaktrough

Limit Concentration

(μg/dscm) Trap ID

0.1198 0.995843724 0.05988024 1.394824708 66734 0.1162 0.990622336 0.507246377 1.19363167 66729 0.1188 0.996644295 0.172413793 1.467171717 66783 ≤20% of field recovery test ≤ 10% of Section 1 Hg

mass for Hg conc. >1 μg/dscm: or ≤ 20% of Section Trap #1Section 1

Mass Section 2

Mass Total

Mass Initial

Spike Total NonSpike Sample

Volume Volume

Difference (%) Volume Diff. Limit

370 0.4 370.4 200 370.4 0.1203 0.120802087 340 0.4 340.4 200 340.4 0.1173 0.118410413 383 0.3 383.3 200 383.3 0.1192 0.119601347 ≤20% of field recovery test Trap #2Breaktrough (%) Breaktrough Limit Concentration

(μg/dscm) Abs. diff. RD (%) Limit C rec

0.108108108 3.078969244 1.684145 37.64466 99.8585 0.117647059 2.901960784 1.708329 41.7114 99.4903 0.078328982 3.215604027 1.748432 37.33752 1.000331 ≥10 % RD mass for Hg conc. >1 μg/dscm: or ≤20% RD or ≤0.2 μg/dscm abs.diff. for Hg conc. ≤1 ≤ 10% of Section 1 Hg mass for Hg conc. >1 μg/dscm: or ≤ 20% of Section 1 for Hg conc. ≤1 Measured Spike Recovery ( R ) Paired Trap Agreement (RD)R (%) by

Run Ravg(%) Limit

99.8 99.5 100.0 Average Recovery

, between 85 and 115% Measured Spike Recovery ( R )

99.7667EIA

Facility Code Facility Name Boiler ID 6085 SCHAHFER 14

Run Number Test Start Date Test Start TimeMeasured Hg 0Value (μg/dscm) Measured Hg +2Value (μg/dscm) Test End Time Test End DateMeasured Hg PValue

(μg/dscm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Total Vapor Phase Mercury Emission Test ResultsTest Method

Comments Total Mercury (lb/mmBtu) Steam Output

(1000 lb/hr) Total Heat

Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Flue Gas O2(%) Flue Gas

Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #2 Fuel #3Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Other Supporting Information Fuel #4EIA

Facility Code Facility Name Boiler ID 6085 SCHAHFER 14

Speciated Volatile Organic HAP Emission Data

Acetone 1 4/6/2010 Acetone 2 4/6/2010 Acetone 3 4/6/2010 Benzene 1 4/6/2010 Benzene 2 4/6/2010 Benzene 3 4/6/2010 Bromobenzene 1 4/6/2010 Bromobenzene 2 4/6/2010 Bromobenzene 3 4/6/2010 Bromochloromethane 1 4/6/2010 Bromochloromethane 2 4/6/2010 Bromochloromethane 3 4/6/2010 Bromodichloromethane 1 4/6/2010 Bromodichloromethane 2 4/6/2010 Bromodichloromethane 3 4/6/2010 Bromoform (tribromomethane) 1 4/6/2010 Bromoform (tribromomethane) 2 4/6/2010 Bromoform (tribromomethane) 3 4/6/2010 Bromomethane 1 4/6/2010 Bromomethane 2 4/6/2010 Bromomethane 3 4/6/2010 2-Butanone 1 4/6/2010 2-Butanone 2 4/6/2010 2-Butanone 3 4/6/2010 n-Butylbenzene 1 4/6/2010 n-Butylbenzene 2 4/6/2010 n-Butylbenzene 3 4/6/2010 sec-Butylbenzene 1 4/6/2010 sec-Butylbenzene 2 4/6/2010 sec-Butylbenzene 3 4/6/2010 tert-Butylbenzene 1 4/6/2010 tert-Butylbenzene 2 4/6/2010 tert-Butylbenzene 3 4/6/2010 Carbon disulfide 1 4/6/2010 Carbon disulfide 2 4/6/2010 Carbon disulfide 3 4/6/2010 Carbon tetrachloride 1 4/6/2010 Carbon tetrachloride 2 4/6/2010 Carbon tetrachloride 3 4/6/2010 Chlorobenzene 1 4/6/2010 Chlorobenzene 2 4/6/2010 Chlorobenzene 3 4/6/2010

Compound (use drop down to define for as many rows as

needed) Run Number Test Start DateChlorodibromomethane 1 4/6/2010

Chlorodibromomethane 2 4/6/2010 Chlorodibromomethane 3 4/6/2010 Chloroethane 1 4/6/2010 Chloroethane 2 4/6/2010 Chloroethane 3 4/6/2010 Chloroform 1 4/6/2010 Chloroform 2 4/6/2010 Chloroform 3 4/6/2010 Chloromethane 1 4/6/2010 Chloromethane 2 4/6/2010 Chloromethane 3 4/6/2010 2-Chlorotoluene 1 4/6/2010 2-Chlorotoluene 2 4/6/2010 2-Chlorotoluene 3 4/6/2010 4-Chlorotoluene 1 4/6/2010 4-Chlorotoluene 2 4/6/2010 4-Chlorotoluene 3 4/6/2010 1,2-Dibromo-3-chloropropane 1 4/6/2010 1,2-Dibromo-3-chloropropane 2 4/6/2010 1,2-Dibromo-3-chloropropane 3 4/6/2010 1,2-Dibromoethane 1 4/6/2010 1,2-Dibromoethane 2 4/6/2010 1,2-Dibromoethane 3 4/6/2010 Dibromomethane 1 4/6/2010 Dibromomethane 2 4/6/2010 Dibromomethane 3 4/6/2010 1,2-Dichlorobenzene 1 4/6/2010 1,2-Dichlorobenzene 2 4/6/2010 1,2-Dichlorobenzene 3 4/6/2010 1,3-Dichlorobenzene 1 4/6/2010 1,3-Dichlorobenzene 2 4/6/2010 1,3-Dichlorobenzene 3 4/6/2010 1,4-Dichlorobenzene (p-) 1 4/6/2010 1,4-Dichlorobenzene (p-) 2 4/6/2010 1,4-Dichlorobenzene (p-) 3 4/6/2010 Dichlorodifluoromethane 1 4/6/2010 Dichlorodifluoromethane 2 4/6/2010 Dichlorodifluoromethane 3 4/6/2010 1,1-Dichloroethane 1 4/6/2010 1,1-Dichloroethane 2 4/6/2010 1,1-Dichloroethane 3 4/6/2010 1,2-dichloroethane 1 4/6/2010 1,2-dichloroethane 2 4/6/2010 1,2-dichloroethane 3 4/6/2010 cis-1,2-Dichloroethene 1 4/6/2010 cis-1,2-Dichloroethene 2 4/6/2010 cis-1,2-Dichloroethene 3 4/6/2010 trans-1,2-Dichloroethene 1 4/6/2010trans-1,2-Dichloroethene 2 4/6/2010

trans-1,2-Dichloroethene 3 4/6/2010 1,1-Dichloroethene 1 4/6/2010 1,1-Dichloroethene 2 4/6/2010 1,1-Dichloroethene 3 4/6/2010 1,2-Dichloropropane 1 4/6/2010 1,2-Dichloropropane 2 4/6/2010 1,2-Dichloropropane 3 4/6/2010 1,3-Dichloropropane 1 4/6/2010 1,3-Dichloropropane 2 4/6/2010 1,3-Dichloropropane 3 4/6/2010 2,2-Dichloropropane 1 4/6/2010 2,2-Dichloropropane 2 4/6/2010 2,2-Dichloropropane 3 4/6/2010 cis-1,3-Dichloropropene 1 4/6/2010 cis-1,3-Dichloropropene 2 4/6/2010 cis-1,3-Dichloropropene 3 4/6/2010 trans-1,3-Dichloropropene 1 4/6/2010 trans-1,3-Dichloropropene 2 4/6/2010 trans-1,3-Dichloropropene 3 4/6/2010 1,1-Dichloropropene 1 4/6/2010 1,1-Dichloropropene 2 4/6/2010 1,1-Dichloropropene 3 4/6/2010 Ethylbenzene 1 4/6/2010 Ethylbenzene 2 4/6/2010 Ethylbenzene 3 4/6/2010 Hexachlorobutadiene 1 4/6/2010 Hexachlorobutadiene 2 4/6/2010 Hexachlorobutadiene 3 4/6/2010 2-Hexanone 1 4/6/2010 2-Hexanone 2 4/6/2010 2-Hexanone 3 4/6/2010 Isopropylbenzene 1 4/6/2010 Isopropylbenzene 2 4/6/2010 Isopropylbenzene 3 4/6/2010 p-Isopropyltoluene 1 4/6/2010 p-Isopropyltoluene 2 4/6/2010 p-Isopropyltoluene 3 4/6/2010 Methylene chloride 1 4/6/2010 Methylene chloride 2 4/6/2010 Methylene chloride 3 4/6/2010 4-Methyl-2-pentanone 1 4/6/2010 4-Methyl-2-pentanone 2 4/6/2010 4-Methyl-2-pentanone 3 4/6/2010 Napthalene 1 4/6/2010 Napthalene 2 4/6/2010 Napthalene 3 4/6/2010 n-Propylbenzene 1 4/6/2010 n-Propylbenzene 2 4/6/2010n-Propylbenzene 3 4/6/2010

Styrene 1 4/6/2010 Styrene 2 4/6/2010 Styrene 3 4/6/2010 1,1,1,2-Tetrachloroethane 1 4/6/2010 1,1,1,2-Tetrachloroethane 2 4/6/2010 1,1,1,2-Tetrachloroethane 3 4/6/2010 1,1,2,2-Tetrachloroethane 1 4/6/2010 1,1,2,2-Tetrachloroethane 2 4/6/2010 1,1,2,2-Tetrachloroethane 3 4/6/2010 Tetrachlroethen 1 4/6/2010 Tetrachlroethen 2 4/6/2010 Tetrachlroethen 3 4/6/2010 Toluene 1 4/6/2010 Toluene 2 4/6/2010 Toluene 3 4/6/2010 1,2,3-Trichlorobenzene 1 4/6/2010 1,2,3-Trichlorobenzene 2 4/6/2010 1,2,3-Trichlorobenzene 3 4/6/2010 1,2,4-Trichlorobenzene 1 4/6/2010 1,2,4-Trichlorobenzene 2 4/6/2010 1,2,4-Trichlorobenzene 3 4/6/2010 1,1,1,-Trichloroethane 1 4/6/2010 1,1,1,-Trichloroethane 2 4/6/2010 1,1,1,-Trichloroethane 3 4/6/2010 1,1,2-Trichloroethane 1 4/6/2010 1,1,2-Trichloroethane 2 4/6/2010 1,1,2-Trichloroethane 3 4/6/2010 Trichloroethene 1 4/6/2010 Trichloroethene 2 4/6/2010 Trichloroethene 3 4/6/2010 Trichlorofluoromethane 1 4/6/2010 Trichlorofluoromethane 2 4/6/2010 Trichlorofluoromethane 3 4/6/2010 1,2,3-Trichloropropane 1 4/6/2010 1,2,3-Trichloropropane 2 4/6/2010 1,2,3-Trichloropropane 3 4/6/2010 1,2,4-Trichlorobenzene 1 4/6/2010 1,2,4-Trichlorobenzene 2 4/6/2010 1,2,4-Trichlorobenzene 3 4/6/2010 1,3,5-Trimethylbenzene 1 4/6/2010 1,3,5-Trimethylbenzene 2 4/6/2010 1,3,5-Trimethylbenzene 3 4/6/2010 Vinyl chloride (chloroethene) 1 4/6/2010 Vinyl chloride (chloroethene) 2 4/6/2010 Vinyl chloride (chloroethene) 3 4/6/2010 M-Xylene & p-Xylene 1 4/6/2010 M-Xylene & p-Xylene 2 4/6/2010 M-Xylene & p-Xylene 3 4/6/2010o-Xylene 1 4/6/2010

o-Xylene 2 4/6/2010 o-Xylene 3 4/6/2010Measured Value (μg/m3) 8:05 AM 4/6/2010 9:50 AM 

### [<52.9653] 10:20 AM 4/6/2010 12:05 PM 

### [<81.2589] 1:25 PM 4/6/2010 3:15 PM 

### 72.6081 8:05 AM 4/6/2010 9:50 AM 

### [<1.3415] 10:20 AM 4/6/2010 12:05 PM 

### [<2.0132] 1:25 PM 4/6/2010 3:15 PM 

### [<1.7074] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2883] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2883] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2871] 8:05 AM 4/6/2010 9:50 AM 

### [<0.4043] 10:20 AM 4/6/2010 12:05 PM 

### [<0.4040] 1:25 PM 4/6/2010 3:15 PM 

### [<0.4022] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1883] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1878] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1870] 8:05 AM 4/6/2010 9:50 AM 

### [<1.4481] 10:20 AM 4/6/2010 12:05 PM 

### [<1.4450] 1:25 PM 4/6/2010 3:15 PM 

### [<1.4381] 8:05 AM 4/6/2010 9:50 AM 

### [<6.0022] 10:20 AM 4/6/2010 12:05 PM 

### [<6.7112] 1:25 PM 4/6/2010 3:15 PM 

### [<4.1081] 8:05 AM 4/6/2010 9:50 AM 

### [<14.3762] 10:20 AM 4/6/2010 12:05 PM 

### [<14.3960] 1:25 PM 4/6/2010 3:15 PM 

### [<14.3394 8:05 AM 4/6/2010 9:50 AM 

### [<0.1445] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1443] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1437] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1443] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1443] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1436] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1588] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1587] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1580] 8:05 AM 4/6/2010 9:50 AM 

### [<0.6272] 10:20 AM 4/6/2010 12:05 PM 

### [<0.7098] 1:25 PM 4/6/2010 3:15 PM 

### [<0.5448] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1831] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1925] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1821] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1446] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1444] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1533] Test Start Time Test End Date Test End Time8:05 AM 4/6/2010 9:50 AM 

### [<0.2900] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2892] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2877] 8:05 AM 4/6/2010 9:50 AM 

### [<0.8928] 10:20 AM 4/6/2010 12:05 PM 

### [<0.8933] 1:25 PM 4/6/2010 3:15 PM 

### [<0.8896] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1588] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1587] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1580] 8:05 AM 4/6/2010 9:50 AM 

### [<24.7588] 10:20 AM 4/6/2010 12:05 PM 

### [<30.4799] 1:25 PM 4/6/2010 3:15 PM 

### [<12.7954] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1735] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1733] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1725] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2022] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2020] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2011] 8:05 AM 4/6/2010 9:50 AM 

### [<1.8735] 10:20 AM 4/6/2010 12:05 PM 

### [<1.8738] 1:25 PM 4/6/2010 3:15 PM 

### [<1.8660] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2035] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2026] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2016] 8:05 AM 4/6/2010 9:50 AM 

### [<0.3040] 10:20 AM 4/6/2010 12:05 PM 

### [<0.3034] 1:25 PM 4/6/2010 3:15 PM 

### [<0.3019] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2591] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2593] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2582] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2020] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2019] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2010] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2165] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2164] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2154] 8:05 AM 4/6/2010 9:50 AM 

### [<0.6356] 10:20 AM 4/6/2010 12:05 PM 

### [<1.0182] 1:25 PM 4/6/2010 3:15 PM 

### [<0.9413] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1443] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1443] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1436] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2451] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2451] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2440] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1449] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1446] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1439] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2878]10:20 AM 4/6/2010 12:05 PM 

### [<0.2881] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2869] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2170] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2166] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2156] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2452] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2451] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2441] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2018] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2018] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2010] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1449] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1445] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1439] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2455] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2453] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2442] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1737] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1733] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1725] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1446] 10:20 AM 4/6/2010 12:05 PM 

### [<0.0417] 1:25 PM 4/6/2010 3:15 PM 

### [<0.0419] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1541] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1444] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1509] 8:05 AM 4/6/2010 9:50 AM 

### [<0.3640] 10:20 AM 4/6/2010 12:05 PM 

### [<0.3622] 1:25 PM 4/6/2010 3:15 PM 

### [<0.3602] 8:05 AM 4/6/2010 9:50 AM 

### [<0.9822] 10:20 AM 4/6/2010 12:05 PM 

### [<0.9813] 1:25 PM 4/6/2010 3:15 PM 

### [<0.9770] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1444] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1443] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1437] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1443] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1443] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1436] 8:05 AM 4/6/2010 9:50 AM 

### 4.1016 10:20 AM 4/6/2010 12:05 PM 

### 2.4281 1:25 PM 4/6/2010 3:15 PM 

### 3.0405 8:05 AM 4/6/2010 9:50 AM 

### [<14.3762] 10:20 AM 4/6/2010 12:05 PM 

### [<14.3960] 1:25 PM 4/6/2010 3:15 PM 

### [<14.3394] 8:05 AM 4/6/2010 9:50 AM 

### [<1.4373] 10:20 AM 4/6/2010 12:05 PM 

### [<1.4394] 1:25 PM 4/6/2010 3:15 PM 

### [<1.4338] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1439] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1440]1:25 PM 4/6/2010 3:15 PM 

### [<0.1434] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2044] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1875] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2129] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1592] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1589] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1582] 8:05 AM 4/6/2010 9:50 AM 

### [<0.4182] 10:20 AM 4/6/2010 12:05 PM 

### [<0.4182] 1:25 PM 4/6/2010 3:15 PM 

### [<0.4164] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1592] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1589] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1581] 8:05 AM 4/6/2010 9:50 AM 

### [<0.4793] 10:20 AM 4/6/2010 12:05 PM 

### [<0.4919] 1:25 PM 4/6/2010 3:15 PM 

### [<0.4947] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2072] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1458] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1449] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2323] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2315] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2303] 8:05 AM 4/6/2010 9:50 AM 

### [<0.1454] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1448] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1440] 8:05 AM 4/6/2010 9:50 AM 

### [<1.4361] 10:20 AM 4/6/2010 12:05 PM 

### [<1.4388] 1:25 PM 4/6/2010 3:15 PM 

### [<1.4334] 8:05 AM 4/6/2010 9:50 AM 

### [<0.3170] 10:20 AM 4/6/2010 12:05 PM 

### [<0.3171] 1:25 PM 4/6/2010 3:15 PM 

### [<0.3158] 8:05 AM 4/6/2010 9:50 AM 

### [<0.3357] 10:20 AM 4/6/2010 12:05 PM 

### [<0.5133] 1:25 PM 4/6/2010 3:15 PM 

### [<0.4708] 8:05 AM 4/6/2010 9:50 AM 

### [<3.5897] 10:20 AM 4/6/2010 12:05 PM 

### [<3.5969] 1:25 PM 4/6/2010 3:15 PM 

### [<3.5833] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2160] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2161] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2152] 8:05 AM 4/6/2010 9:50 AM 

### [<0.2586] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2590] 1:25 PM 4/6/2010 3:15 PM 

### [<0.2580] 8:05 AM 4/6/2010 9:50 AM 

### [<0.3037] 10:20 AM 4/6/2010 12:05 PM 

### [<0.3032] 1:25 PM 4/6/2010 3:15 PM 

### [<0.3018] 8:05 AM 4/6/2010 9:50 AM 

### [<0.3117] 10:20 AM 4/6/2010 12:05 PM 

### [<0.2953] 1:25 PM 4/6/2010 3:15 PM 

### [<0.3275]8:05 AM 4/6/2010 9:50 AM 

### [<0.1519] 10:20 AM 4/6/2010 12:05 PM 

### [<0.1516] 1:25 PM 4/6/2010 3:15 PM 

### [<0.1581]Footnotes:

* Front half fraction contains filter, cyclone, and cartridge ** Back half fraction contains condensate, solvent, impingers

Basis Test Method Used Data Flag (ADL, BDL, DDL) Front Half Mass (ng) Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 2214.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 3390.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### ADL 3040.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 56.10 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 84.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 71.50 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 16.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 16.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 16.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 251.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 280.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 172.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 600.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 600.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 600.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 26.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 29.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 22.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 7.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 8.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.40Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 37.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 37.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 37.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 1036.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 1272.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 535.90 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 78.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 78.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 78.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 26.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 42.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 39.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.30 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 15.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 15.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 15.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 40.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 40.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 40.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### ADL 171.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### ADL 101.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### ADL 127.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 600.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 600.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 600.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.50 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 7.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.90 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 17.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 17.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 17.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 20.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 20.50 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 20.70 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 8.50 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 60.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 13.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 13.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 13.20 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 14.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 21.40 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### DLL 19.70 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 150.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 150.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 150.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 9.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 10.80 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 13.00 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 12.30 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 13.70Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.30 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.30 Dry U.S. EPA Method 0031 with SW-846 Method 8260B 

### BDL 6.60Back Half Mass (ng) Total Mass (ng) Test Method Comments lb/mmBtu

2.44 2216.44 

### [<4.748E-05] 1.24 3391.24 

### [<7.167E-05] 1.16 3041.16 

### 6.344E-05 0.036 56.136 

### [<1.202E-06] 0.018 84.018 

### [<1.776E-06] 0.012 71.512 

### [<1.492E-06] 0.064 12.064 

### [<2.584E-07] 0.0312 12.0312 

### [<2.543E-07] 0.024 12.024 

### [<2.508E-07] 0.12 16.92 

### [<3.624E-07] 0.06 16.86 

### [<3.563E-07] 0.044 16.844 

### [<3.514E-07] 0.08 7.88 

### [<1.688E-07] 0.0396 7.8396 

### [<1.657E-07] 0.0308 7.8308 

### [<1.633E-07] 0.600 60.6 

### [<1.297E-06] 0.304 60.304 

### [<1.275E-06] 0.236 60.236 

### [<1.256E-06] 0.172 251.172 

### [<5.380E-06] 0.084 280.084 

### [<5.920E-06] 0.068 172.068 

### [<3.589E-06] 1.60 601.6 

### [<1.289E-05] 0.80 600.8 

### [<1.270E-05] 0.60 600.6 

### [<1.253E-05] 0.048 6.048 

### [<1.296E-07] 0.0232 6.0232 

### [<1.273E-07] 0.018 6.018 

### [<1.255E-07] 0.04 6.04 

### [<1.294E-07] 0.0208 6.0208 

### [<1.272E-07] 0.016 6.016 

### [<1.255E-07] 0.044 6.644 

### [<1.423E-07] 0.0216 6.6216 

### [<1.399E-07] 0.0164 6.6164 

### [<1.380E-07] 0.048 26.248 

### [<5.623E-07] 0.024 29.624 

### [<6.261E-07] 0.0184 22.8184 

### [<4.760E-07] 0.064 7.664 

### [<1.642E-07] 0.0332 8.0332 

### [<1.698E-07] 0.0256 7.6256 

### [<1.591E-07] 0.052 6.052 

### [<1.296E-07] 0.0252 6.0252 

### [<1.273E-07] 0.0192 6.4192 

### [<1.339E-07] Calculated Emission Rate0.136 12.136 

### [<2.600E-07] 0.068 12.068 

### [<2.551E-07] 0.052 12.052 

### [<2.514E-07] 0.16 37.36 

### [<8.003E-07] 0.08 37.28 

### [<7.879E-07] 0.06 37.26 

### [<7.772E-07] 0.044 6.644 

### [<1.423E-07] 0.022 6.622 

### [<1.400E-07] 0.0168 6.6168 

### [<1.380E-07] 0.080 1036.08 

### [<2.219E-05] 0.039 1272.0392 

### [<2.688E-05] 0.030 535.9304 

### [<1.118E-05] 0.060 7.26 

### [<1.555E-07] 0.030 7.2304 

### [<1.528E-07] 0.024 7.2236 

### [<1.507E-07] 0.060 8.46 

### [<1.812E-07] 0.030 8.4304 

### [<1.782E-07] 0.024 8.4236 

### [<1.757E-07] 0.400 78.4 

### [<1.679E-06] 0.200 78.2 

### [<1.653E-06] 0.156 78.156 

### [<1.630E-06] 0.116 8.516 

### [<1.824E-07] 0.056 8.456 

### [<1.787E-07] 0.044 8.444 

### [<1.761E-07] 0.120 12.72 

### [<2.725E-07] 0.060 12.66 

### [<2.676E-07] 0.044 12.644 

### [<2.637E-07] 0.044 10.844 

### [<2.323E-07] 0.022 10.8216 

### [<2.287E-07] 0.016 10.8164 

### [<2.256E-07] 0.052 8.452 

### [<1.811E-07] 0.026 8.4264 

### [<1.781E-07] 0.020 8.4204 

### [<1.756E-07] 0.060 9.06 

### [<1.941E-07] 0.030 9.03 

### [<1.908E-07] 0.023 9.0232 

### [<1.882E-07] 0.600 26.6 

### [<5.698E-07] 0.292 42.492 

### [<8.981E-07] 0.228 39.428 

### [<8.224E-07] 0.040 6.04 

### [<1.294E-07] 0.021 6.0208 

### [<1.272E-07] 0.016 6.016 

### [<1.255E-07] 0.056 10.256 

### [<2.197E-07] 0.028 10.228 

### [<2.162E-07] 0.022 10.2216 

### [<2.132E-07] 0.064 6.064 

### [<1.299E-07] 0.033 6.0332 

### [<1.275E-07] 0.026 6.0256 

### [<1.257E-07] 0.044 12.044 

### [<2.580E-07]0.022 12.022 

### [<2.541E-07] 0.017 12.0168 

### [<2.507E-07] 0.080 9.08 

### [<1.945E-07] 0.040 9.04 

### [<1.911E-07] 0.031 9.0312 

### [<1.884E-07] 0.060 10.26 

### [<2.198E-07] 0.029 10.2292 

### [<2.162E-07] 0.023 10.2228 

### [<2.132E-07] 0.044 8.444 

### [<1.809E-07] 0.022 8.422 

### [<1.780E-07] 0.017 8.4168 

### [<1.756E-07] 0.064 6.064 

### [<1.299E-07] 0.032 6.0324 

### [<1.275E-07] 0.025 6.0252 

### [<1.257E-07] 0.072 10.272 

### [<2.200E-07] 0.036 10.236 

### [<2.163E-07] 0.028 10.228 

### [<2.133E-07] 0.068 7.268 

### [<1.557E-07] 0.034 7.2344 

### [<1.529E-07] 0.026 7.2264 

### [<1.507E-07] 0.052 6.052 

### [<1.296E-07] 0.026 6.0256 

### [<1.274E-07] 0.020 6.02 

### [<1.256E-07] 0.048 6.448 

### [<1.381E-07] 0.024 6.0244 

### [<1.273E-07] 0.019 6.3188 

### [<1.318E-07] 0.232 15.232 

### [<3.263E-07] 0.116 15.116 

### [<3.195E-07] 0.088 15.088 

### [<3.147E-07] 0.304 41.104 

### [<8.805E-07] 0.152 40.952 

### [<8.655E-07] 0.120 40.92 

### [<8.536E-07] 0.044 6.044 

### [<1.295E-07] 0.022 6.022 

### [<1.273E-07] 0.017 6.0168 

### [<1.255E-07] 0.040 6.04 

### [<1.294E-07] 0.021 6.0208 

### [<1.272E-07] 0.016 6.016 

### [<1.255E-07] 0.64 171.64 

### 3.677E-06 0.332 101.332 

### 2.142E-06 0.352 127.352 

### 2.656E-06 1.600 601.6 

### [<1.289E-05] 0.800 600.8 

### [<1.270E-05] 0.600 600.6 

### [<1.253-05] 0.148 60.148 

### [<1.288E-06] 0.072 60.072 

### [<1.270E-06] 0.056 60.056 

### [<1.253E-06] 0.021 6.0208 

### [<1.290E-07] 0.010 6.0104 

### [<1.270E-07]0.008 6.008 

### [<1.253E-07] 0.052 8.552 

### [<1.832E-07] 0.025 7.8252 

### [<1.654E-07] 0.019 8.9192 

### [<1.860E-07] 0.064 6.664 

### [<1.428E-07] 0.033 6.6332 

### [<1.402E-07] 0.026 6.6256 

### [<1.382E-07] 0.100 17.5 

### [<3.749E-07] 0.052 17.452 

### [<3.688E-07] 0.039 17.4388 

### [<3.638E-07] 0.064 6.664 

### [<1.428E-07] 0.031 6.6312 

### [<1.401E-07] 0.024 6.624 

### [<1.382E-07] 0.056 20.056 

### [<4.296E-07] 0.029 20.5288 

### [<4.339E-07] 0.022 20.722 

### [<4.322E-07] 0.172 8.672 

### [<1.858E-07] 0.084 6.084 

### [<1.286E-07] 0.068 6.068 

### [<1.266E-07] 0.120 9.72 

### [<2.082E-07] 0.060 9.66 

### [<2.042E-07] 0.048 9.648 

### [<2.013E-07] 0.084 6.084 

### [<1.303E-07] 0.044 6.044 

### [<1.277E-07] 0.033 6.0332 

### [<1.258E-07] 0.096 60.096 

### [<1.287E-06] 0.048 60.048 

### [<1.269E-06] 0.037 60.0372 

### [<1.252E-06] 0.064 13.264 

### [<2.841E-07] 0.033 13.2332 

### [<2.797E-07] 0.026 13.2256 

### [<2.759E-07] 0.048 14.048 

### [<3.009E-07] 0.023 21.4232 

### [<4.528E-07] 0.018 19.718 

### [<4.113E-07] 0.220 150.22 

### [<3.218E-06] 0.112 150.112 

### [<3.173E-06] 0.084 150.084 

### [<3.131E-06] 0.038 9.038 

### [<1.936E-07] 0.019 9.0188 

### [<1.906E-07] 0.015 9.0148 

### [<1.880E-07] 0.021 10.8208 

### [<2.318E-07] 0.010 10.8104 

### [<2.285E-07] 0.008 10.808 

### [<2.254E-07] 0.108 12.708 

### [<2.722E-07] 0.052 12.652 

### [<2.674E-07] 0.040 12.64 

### [<2.637E-07] 0.044 13.044 

### [<2.794E-07] 0.022 12.322 

### [<2.604E-07] 0.017 13.7168 

### [<2.861E-07]0.056 6.356 

### [<1.362E-07] 0.028 6.328 

### [<1.337E-07] 0.022 6.6216 

### [<1.381E-07]ppmdv @ 7% O2



### [<2.214E-02] 2890 4230 10.21 

### [<3.348E-02] 2890 4500 10.43 

### 2.950E-02 2890 4540 10.11 

### [<4.169E-04] 2890 4230 10.21 

### [<6.169E-04] 2890 4500 10.43 

### [<5.159E-04] 2890 4540 10.11 

### [<4.457E-05] 2890 4230 10.21 

### [<4.394E-05] 2890 4500 10.43 

### [<4.315E-05] 2890 4540 10.11 

### [<7.586E-05] 2890 4230 10.21 

### [<7.473E-05] 2890 4500 10.43 

### [<7.336E-05] 2890 4540 10.11 

### [<2.790E-05] 2890 4230 10.21 

### [<2.744E-05] 2890 4500 10.43 

### [<2.693E-05] 2890 4540 10.11 

### [<1.391E-04] 2890 4230 10.21 

### [<1.368E-04] 2890 4500 10.43 

### [<1.343E-04] 2890 4540 10.11 

### [<1.535E-03] 2890 4230 10.21 

### [<1.692E-03] 2890 4500 10.43 

### [<1.021E-03] 2890 4540 10.11 

### [<4.840E-03] 2890 4230 10.21 

### [<4.778E-03] 2890 4500 10.43 

### [<4.693E-03] 2890 4540 10.11 

### [<2.614E-05] 2890 4230 10.21 

### [<2.574E-05] 2890 4500 10.43 

### [<2.526E-05] 2890 4540 10.11 

### [<2.610E-05] 2890 4230 10.21 

### [<2.572E-05] 2890 4500 10.43 

### [<2.526E-05] 2890 4540 10.11 

### [<2.872E-05] 2890 4230 10.21 

### [<2.829E-05] 2890 4500 10.43 

### [<2.778E-05] 2890 4540 10.11 

### [<2.000E-04] 2890 4230 10.21 

### [<2.231E-04] 2890 4500 10.43 

### [<1.689E-04] 2890 4540 10.11 

### [<2.890E-05] 2890 4230 10.21 

### [<2.995E-05] 2890 4500 10.43 

### [<2.793E-05] 2890 4540 10.11 

### [<3.119E-05] 2890 4230 10.21 

### [<3.070E-05] 2890 4500 10.43 

### [<3.213E-05] 2890 4540 10.11

Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%) Calculated Emission Rate

### [<3.380E-05] 2890 4230 10.21



### [<3.323E-05] 2890 4500 10.43 

### [<3.261E-05] 2890 4540 10.11 

### [<3.360E-04] 2890 4230 10.21 

### [<3.314E-04] 2890 4500 10.43 

### [<3.255E-04] 2890 4540 10.11 

### [<3.228E-05] 2890 4230 10.21 

### [<3.181E-05] 2890 4500 10.43 

### [<3.123E-05] 2890 4540 10.11 

### [<1.190E-02] 2890 4230 10.21 

### [<1.445E-02] 2890 4500 10.43 

### [<5.981E-03] 2890 4540 10.11 

### [<3.327E-05] 2890 4230 10.21 

### [<3.276E-05] 2890 4500 10.43 

### [<3.216E-05] 2890 4540 10.11 

### [<3.877E-05] 2890 4230 10.21 

### [<3.819E-05] 2890 4500 10.43 

### [<3.750E-05] 2890 4540 10.11 

### [<1.924E-04] 2890 4230 10.21 

### [<1.898E-04] 2890 4500 10.43 

### [<1.863E-04] 2890 4540 10.11 

### [<2.630E-05] 2890 4230 10.21 

### [<2.581E-05] 2890 4500 10.43 

### [<2.533E-05] 2890 4540 10.11 

### [<4.245E-05] 2890 4230 10.21 

### [<4.176E-05] 2890 4500 10.43 

### [<4.098E-05] 2890 4540 10.11 

### [<4.279E-05] 2890 4230 10.21 

### [<4.222E-05] 2890 4500 10.43 

### [<4.146E-05] 2890 4540 10.11 

### [<3.335E-06] 2890 4230 10.21 

### [<3.287E-05] 2890 4500 10.43 

### [<3.228E-05] 2890 4540 10.11 

### [<3.575E-05] 2890 4230 10.21 

### [<3.523E-05] 2890 4500 10.43 

### [<3.459E-05] 2890 4540 10.11 

### [<1.276E-04] 2890 4230 10.21 

### [<2.015E-04] 2890 4500 10.43 

### [<1.837E-04] 2890 4540 10.11 

### [<3.541E-05] 2890 4230 10.21 

### [<3.489E-05] 2890 4500 10.43 

### [<3.426E-05] 2890 4540 10.11 

### [<6.012E-05] 2890 4230 10.21 

### [<5.927E-05] 2890 4500 10.43 

### [<5.820E-05] 2890 4540 10.11 

### [<3.629E-05] 2890 4230 10.21 

### [<3.569E-05] 2890 4500 10.43 

### [<3.502E-05] 2890 4540 10.11 

### [<7.207E-05] 2890 4230 10.21

### [<7.112E-05] 2890 4500 10.43



### [<6.985E-05] 2890 4540 10.11 

### [<5.434E-05] 2890 4230 10.21 

### [<5.348E-05] 2890 4500 10.43 

### [<5.250E-05] 2890 4540 10.11 

### [<5.268E-05] 2890 4230 10.21 

### [<5.192E-05] 2890 4500 10.43 

### [<5.098E-05] 2890 4540 10.11 

### [<4.335E-05] 2890 4230 10.21 

### [<4.275E-05] 2890 4500 10.43 

### [<4.197E-05] 2890 4540 10.11 

### [<3.113E-05] 2890 4230 10.21 

### [<3.062E-05] 2890 4500 10.43 

### [<3.005E-05] 2890 4540 10.11 

### [<5.370E-05] 2890 4230 10.21 

### [<5.290E-05] 2890 4500 10.43 

### [<5.194E-05] 2890 4540 10.11 

### [<3.799E-05] 2890 4230 10.21 

### [<3.739E-05] 2890 4500 10.43 

### [<3.669E-05] 2890 4540 10.11 

### [<3.164E-05] 2890 4230 10.21 

### [<3.114E-05] 2890 4500 10.43 

### [<3.057E-05] 2890 4540 10.11 

### [<3.523E-05] 2890 4230 10.21 

### [<3.254E-05] 2890 4500 10.43 

### [<3.354E-05] 2890 4540 10.11 

### [<3.389E-05] 2890 4230 10.21 

### [<3.324E-05] 2890 4500 10.43 

### [<3.260E-05] 2890 4540 10.11 

### [<2.381E-04] 2890 4230 10.21 

### [<2.345E-04] 2890 4500 10.43 

### [<2.302E-04] 2890 4540 10.11 

### [<2.917E-05] 2890 4230 10.21 

### [<2.873E-05] 2890 4500 10.43 

### [<2.821E-05] 2890 4540 10.11 

### [<2.610E-05] 2890 4230 10.21 

### [<2.572E-05] 2890 4500 10.43 

### [<2.526E-05] 2890 4540 10.11 

### 1.172E-03 2890 4230 10.21 

### 6.842E-04 2890 4500 10.43 

### 8.449E-04 2890 4540 10.11 

### [<3.484E-03] 2890 4230 10.21 

### [<3.440E-03] 2890 4500 10.43 

### [<3.379E-03] 2890 4540 10.11 

### [<2.722E-04] 2890 4230 10.21 

### [<2.688E-04] 2890 4500 10.43 

### [<2.640E-04] 2890 4540 10.11 

### [<2.906E-05] 2890 4230 10.21 

### [<2.868E-05] 2890 4500 10.43

### [<2.817E-05] 2890 4540 10.11



### [<4.763E-05] 2890 4230 10.21 

### [<4.309E-05] 2890 4500 10.43 

### [<4.826E-05] 2890 4540 10.11 

### [<2.303E-05] 2890 4230 10.21 

### [<2.266E-05] 2890 4500 10.43 

### [<2.224E-05] 2890 4540 10.11 

### [<6.048E-05] 2890 4230 10.21 

### [<5.963E-05] 2890 4500 10.43 

### [<5.854E-05] 2890 4540 10.11 

### [<2.331E-05] 2890 4230 10.21 

### [<2.293E-05] 2890 4500 10.43 

### [<2.251E-05] 2890 4540 10.11 

### [<1.263E-04] 2890 4230 10.21 

### [<1.278E-04] 2890 4500 10.43 

### [<1.267E-04] 2890 4540 10.11 

### [<2.772E-05] 2890 4230 10.21 

### [<1.923E-05] 2890 4500 10.43 

### [<1.884E-05] 2890 4540 10.11 

### [<3.107E-05] 2890 4230 10.21 

### [<3.053E-05] 2890 4500 10.43 

### [<2.996E-05] 2890 4540 10.11 

### [<2.646E-05] 2890 4230 10.21 

### [<2.598E-05] 2890 4500 10.43 

### [<2.548E-05] 2890 4540 10.11 

### [<2.613E-04] 2890 4230 10.21 

### [<2.581E-04] 2890 4500 10.43 

### [<2.536E-04] 2890 4540 10.11 

### [<5.856E-05] 2890 4230 10.21 

### [<5.776E-05] 2890 4500 10.43 

### [<5.672E-05] 2890 4540 10.11 

### [<5.932E-05] 2890 4230 10.21 

### [<8.944E-05] 2890 4500 10.43 

### [<8.088E-05] 2890 4540 10.11 

### [<5.911E-04] 2890 4230 10.21 

### [<5.839E-04] 2890 4500 10.43 

### [<5.738E-04] 2890 4540 10.11 

### [<4.362E-05] 2890 4230 10.21 

### [<4.303E-05] 2890 4500 10.43 

### [<4.226E-05] 2890 4540 10.11 

### [<5.223E-05] 2890 4230 10.21 

### [<5.158E-05] 2890 4500 10.43 

### [<5.067E-05] 2890 4540 10.11 

### [<1.180E-04] 2890 4230 10.21 

### [<1.161E-04] 2890 4500 10.43 

### [<1.140E-04] 2890 4540 10.11 

### [<7.127E-05] 2890 4230 10.21 

### [<6.656E-05] 2890 4500 10.43 

### [<7.280E-05] 2890 4540 10.11

### [<3.473E-05] 2890 4230 10.21



### [<3.418E-05] 2890 4500 10.43 

### [<3.514E-05] 2890 4540 10.1114.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323

Flue Gas O2(%) Flue Gas Flow Rate (scfm) Flue Gas Temperature (F) Flue Gas CO2(%)14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 30914.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 31814.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323 14.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 32314.6 6.9 1046278 309 14.6 6.7 1046409 318 14.8 6.5 1046600 323Fuel Input Rate Fuel Type Units of Measure Measurement Method

4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation Fuel #14230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation 4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculation4230 subbituminous MMBtu/hr boiler efficiency calculation 4500 subbituminous MMBtu/hr boiler efficiency calculation 4540 subbituminous MMBtu/hr boiler efficiency calculationFuel Input Rate Fuel Type Units of Measure Measurement Method boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation Fuel #2boiler efficiency calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculationboiler efficiency calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculationboiler efficiency calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculation boiler efficiency

calculationboiler efficiency calculation boiler efficiency

calculation boiler efficiency

calculationFuel Input Rate Fuel Type Units of Measure Measurement Method Fuel #3Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel #4Other Supporting

InformationEIA Facility Code Facility Name Boiler ID Footnotes: 6085 SCHAHFER 14 * Front Half Composite contains particulate filter, front half of the filter holder, and probe solvent rinses ** Back Half Composite contains XAD-2 resin tube, back half of the filter holder, and coil condenser solvent rinses *** Condensate Composite contains condensate and Impinger contents and the glassware solvent rinses Speciated Semi-Volatile Organic HAP Emission Data

Measured Value (μg/m3) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Front Half mass* (ng) Back Half mass* (ng) Condensate Mass*** (ng) Total Composite (ng) Test Method Comments lb/mmBtu ppmdv @ 7% O2 Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Fuel Input Rate Fuel Type Units of Measure Measurement Method Acenaphthene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0709 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 70.00 32.00 25.00 127.00 6.358E-08 1.116E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Acenaphthene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.0932 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 88.00 42.00 32.00 162.00 8.354E-08 1.447E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Acenaphthene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.1246 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 130.00 35.00 50.00 215.00 1.106E-07 1.907E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Acenaphthylene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0087 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 2.40 12.00 1.20 15.60 7.936E-09 1.390E-06 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Acenaphthylene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.0070 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 2.90 7.90 1.40 12.20 6.291E-09 1.104E-06 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Acenaphthylene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.0082 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 4.30 8.10 1.80 14.20 7.308E-09 1.276E-06 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Anthracene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0380 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 32.00 18.00 18.00 68.00 3.459E-08 5.172E-06 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Anthracene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.0725 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 71.00 25.00 30.00 126.00 6.498E-08 9.735E-06 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Anthracene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.0812 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 94.00 14.00 32.00 140.00 7.205E-08 1.075E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Benzo (a) anthracene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0042] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 3.00 7.50 [<3.815E-09] [<4.454E-07] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Benzo (a) anthracene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0043] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 3.00 7.50 [<3.868E-09] [<4.524E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Benzo (a) anthracene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0043] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 3.00 7.50 [<3.860E-09] [<4.495E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Benzo (b) fluoranthene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0231 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 4.30 34.00 3.10 41.40 2.106E-08 2.224E-06 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Benzo (b) fluoranthene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0075] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 3.20 6.90 3.00 13.10 [<6.755E-09] [<7.149E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Benzo (b) fluoranthene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0094] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 3.30 10.00 3.00 16.30 [<8.389E-09] [<8.838E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Benzo (k) fluoranthene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0479] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.70 82.00 2.00 85.70 [<4.360E-08] [<4.605E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Benzo (k) fluoranthene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0493] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.70 82.00 2.00 85.70 [<4.419E-08] [<4.677E-06] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Benzo (k) fluoranthene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0497] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.70 82.00 2.00 85.70 [<4.410E-08] [<4.647E-06] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Benzo (ghi) perylene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0763] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 5.60 130.00 1.00 136.60 [<6.949E-08] [<6.702E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Benzo (ghi) perylene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0066] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 5.60 4.80 1.00 11.40 [<5.879E-09] [<5.681E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Benzo (ghi) perylene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0059] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 5.60 3.60 1.00 10.20 [<5.249E-09] [<5.050E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Benzo (a) pyrene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0168] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.90 26.00 2.20 30.10 [<1.531E-08] [<1.617E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Benzo (a) pyrene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0052] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.90 6.40 0.80 9.10 [<4.693E-09] [<4.966E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Benzo (a) pyrene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0064] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.90 8.40 0.80 11.10 [<5.713E-09] [<6.019E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Benzo (e) pyrene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0176] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 2.80 26.00 2.80 31.60 [<1.608E-08] [<1.698E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Benzo (e) pyrene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0064] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.80 5.60 2.80 11.20 [<5.776E-09] [<6.112E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Benzo (e) pyrene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0065] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.80 5.60 2.80 11.20 [<5.764E-09] [<6.073E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Chrysene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.0077 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 3.50 8.80 1.40 13.70 6.969E-09 8.136E-07 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Chrysene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0080] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.50 11.00 1.40 13.90 [<7.168E-09] [<8.384E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Chrysene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.0059 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 4.60 4.10 1.50 10.20 5.249E-09 6.113E-07 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Dibenz (a,h) anthracene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0044] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.60 3.60 1.60 7.80 [<3.968E-09] [<3.799E-07] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Dibenz (a,h) anthracene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0045] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.60 3.60 1.60 7.80 [<4.022E-09] [<3.859E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Dibenz (a,h) anthracene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0045] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 2.60 3.60 1.60 7.80 [<4.014E-09] [<3.834E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Fluoranthene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.1781 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 160.00 100.00 59.00 319.00 1.623E-07 2.138E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Fluoranthene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.2336 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 210.00 120.00 76.00 406.00 2.094E-07 2.764E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Fluoranthene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.3130 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 300.00 120.00 120.00 540.00 2.779E-07 3.653E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Fluorene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.1346 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 120.00 77.00 44.00 241.00 1.226E-07 1.966E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Fluorene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.2048 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 160.00 140.00 56.00 356.00 1.836E-07 2.949E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Fluorene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.2313 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 230.00 80.00 89.00 399.00 2.053E-07 3.284E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Indeno(1,2,3-cd)pyrene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0148] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.50 23.00 2.00 26.50 [<1.348E-08] [<1.300E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Indeno(1,2,3-cd)pyrene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0033] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 1.50 2.30 2.00 5.80 [<2.991E-09] [<2.890E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Indeno(1,2,3-cd)pyrene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0031] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 1.80 2.00 5.30 [<2.728E-09] [<2.624E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation 2-Methylnaphthalene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 0.1586 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 120.00 120.00 44.00 284.00 1.445E-07 2.708E-05 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation 2-Methylnaphthalene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 0.2336 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 150.00 200.00 56.00 406.00 2.094E-07 3.931E-05 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation 2-Methylnaphthalene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 0.2255 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 210.00 90.00 89.00 389.00 2.002E-07 3.743E-05 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Naphthalene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.3306] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 97.00 460.00 35.00 592.00 [<3.012E-07] [<6.262E-05] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Naphthalene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.5776] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 110.00 850.00 44.00 1004.00 [<5.177E-07] [<1.079E-04] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Naphthalene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.3895] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 150.00 460.00 62.00 672.00 [<3.458E-07] [<7.173E-05] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Perylene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0034] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 1.60 6.10 [<3.103E-09] [<3.278E-07] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Perylene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0035] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 1.60 6.10 [<3.146E-09] [<3.329E-07] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Perylene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.0035] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 1.50 3.00 1.60 6.10 [<3.139E-09] [<3.308E-07] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Phenanthrene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM 1.0443 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 950.00 580.00 340.00 1870.00 9.513E-07 1.422E-04 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Phenanthrene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM 1.3405 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 1200.00 700.00 430.00 2330.00 1.202E-06 1.800E-04 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Phenanthrene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM 1.7390 Dry U.S. EPA Method 0010 with SW-846 Method 8270C ADL 1700.00 600.00 700.00 3000.00 1.544E-06 2.303E-04 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Pyrene 1 4/6/2010 7:30 AM 4/6/2010 9:46 AM [<0.0760] Dry U.S. EPA Method 0010 with SW-846 Method 8270C DDL 60.00 53.00 23.00 136.00 [<6.918E-08] [<9.116E-06] 2890 4230 10.21 14.6 6.9 1046278 309 4230 subbituminous MMBtu/hr boiler efficiency calculation Pyrene 2 4/6/2010 10:20 AM 4/6/2010 12:41 PM [<0.0892] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 73.00 55.00 27.00 155.00 [<7.993E-08] [<1.055E-05] 2890 4500 10.43 14.6 6.7 1046409 318 4500 subbituminous MMBtu/hr boiler efficiency calculation Pyrene 3 4/6/2010 1:25 PM 4/6/2010 3:35 PM [<0.1130] Dry U.S. EPA Method 0010 with SW-846 Method 8270C BDL 100.00 53.00 42.00 195.00 [<1.004E-07] [<1.319E-05] 2890 4540 10.11 14.8 6.5 1046600 323 4540 subbituminous MMBtu/hr boiler efficiency calculation Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Fuel #4 Other Supporting Information Flue Gas O2(%) Flue Gas Flow Rate (scfm) Flue Gas Temperature (F) Fuel #1 Fuel #2 Fuel #3 Flue Gas Moisture (%) Flue Gas CO2(%) Compound (use drop down to define for as many rows as needed) Run Number Test Start Date Test Start Time Test End Date Test End Time Semi-Volatile Organic HAP Emission Test Results Calculated Emission RateEIA

Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

1 4/27/2010 8:45 4/27/2010 2 4/27/2010 12:00 4/27/2010 3 4/27/2010 15:25 4/27/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used

10:15 [<1.45E-04] Dry U.S. EPA Conditional Test Method 033 (CTM-033) 13:15 [<8.31E-05] Dry U.S. EPA Conditional Test Method 033 (CTM-033) 16:40 [<7.85E-05] Dry U.S. EPA Conditional Test Method 033 (CTM-033) Test End Time Hydrogen Cyanide Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments BDL [<1.45E-04] 2771.6 4384 17.4 14.3 BDL [<8.31E-05] 2771.6 4393 13.14 14.1 BDL [<7.85E-05] 2771.6 4416 13.78 14.2 Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate 5.4 886138 286 4384 subbituminous MMBtu/hr gas fuel meter 5.3 916325 293 4393 subbituminous MMBtu/hr gas fuel meter 5.5 908477 292 4416 subbituminous MMBtu/hr gas fuel meter Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas O2(%)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method [<208]

[<124] [<118] Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Hydrogen Chloride Emission Test Results Test End TimeData Flag (ADL,

BDL, DDL) Test Method

Comments Calculated

Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO2(%) Hydrogen Chloride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Flue Gas Temperature (F) Fuel #1 Flue Gas O2(%) Flue Gas

Flow Rate (dscfm)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID

6085 SCHAHFER 14

Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Test End Time Hydrogen Flouride Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments Hydrogen Flouride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas CO2(%) Flue Gas

O2(%)Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel #2 Fuel #3Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 6085 SCHAHFER 14

Run Number Test Start Date Test Start TimeMeasured NO (ppm)

Test End Date Test End TimeMeasured NO2(ppm) Basis (Wet or Dry) Test Method Used NOXEmission Test ResultsData Flag (ADL, BDL, DDL) Test Method Comments (lb/mmBtu) Total NOXCalculated Emission Rateppmdv @ 7% O2 Flue Gas O2(%) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 6085 SCHAHFER 14

Run Number Test Start Date Test Start TimeTotal Dissolved Solids (mg solids/liter) Total Suspended Solids (mg solids/liter) Test End Time Test End DateTest Method Used Data Flag (ADL, BDL, DDL) Constisuent Emission Test ResultsTest Method Comments Fuel Input Rate Flue Gas Flow Rate (dscfm) Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr) Flue Gas Temperat ure (F)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel #1 Fuel #2Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel #3 Fuel #4Other Supporting InformationFuel

anthracite bitum inous subbituminous lignite

coal refuse (culm or gob) No.2 Fuel Oil (distillate) No.6 Fuel Oil (residual or bunker C) synfuel petroleum coke other

Relative to Control Device Upstream Downstream

Fuel Input Units of Measure MMBtu/hr standard cubic feet per minute (scfm) gallon/m inute lb/hour ton/day

Exhaust Flow Rate Units of Measure acfm dscfm

Exhaust Temperature Units of Measure deg C deg F

Test Method Used for Fuel Input Rate F-Factor gas fuel meter boiler efficiency

calculation Other

CO Test Method U.S. EPA Method 10A U.S. EPA Method 10B

Formaldehyde Test MethodU.S. EPA Method 320

U.S. EPA Method 0011 U.S. EPA Method 316

CH4 Test Method U.S. EPA Method 18 U.S. EPA Method 320

SO2 Test Method U.S. EPA Method 6

Hg Test Method U.S. EPA Method 30B

Speciated Volatile Organic HAP M ethod U.S. EPA Method 0031 with SW -846 Method 8260B U.S. EPA Method 0031/TO-15

Speciated Semi-Volatile Organic HAP M ethod U.S. EPA Method 0010 with SW -846 Method 8270C U.S. EPA Method 0010 with SW -846 Method 8270D

HCN Test Method U.S. EPA Conditional Test Method 033 (CTM-033) U.S. EPA Method 320 CARB 426 U.S. EPA Method 26A-Mod

O2/CO2 Test Method U.S. EPA Method 3B

NOX Test Method U.S. EPA Method 7 U.S. EPA Method 7A U.S. EPA Method 7B U.S. EPA Method 7C

U.S. EPA Method 7D

TDS/TSS Test Method Standard Test Method for Filterable and Nonfilterable Matter in W ater ASTM D5907 Standard Methods of the Examination of W ater and W astewater Method 2540B

Control Configuration 

### Listed (by boiler) in Question 16 (page 17) of the questionnaire

### Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR

Hg Ontario Hydro Test Method ASTM Method D6784

HCL Test Methods U.S. EPA Method 320 U.S. EPA Method 26

HF Test Methods U.S. EPA Method 320 U.S. EPA Method 26

Basis Wet DryConstituent CAS Methyl chloride 74-87-3 1,1,2-Trichloroethane 79-00-5 1,1-Dimethylhydrazine 57-14-7 1,2-dichloroethane 1,2,4-Trichlorobenzene 120-82-1 1,2-Dibromo-3-chloropropane 96-12-8 1,2-Epoxybutane (1,2-butylene oxide) 106-88-7 1,2-Propyleneim ine (2-methylaziridine) 75-55-8 1,3-Butadiene 106-99-0 1,3-Dichloropropene 542-75-6 1,3-Propane sultone 1120-71-4 1,4-Dichlorobenzene (p-) 106-46-7 1,4-Dioxane (1,4-Diethylene oxide) 123-91-1 2,2,4-Trimethyl pentane 540-84-1 2-Nitropropane 79-46-9 Acetaldehyde 75-07-0 Acetonitrile (cyanom ethane) 75-05-8 Acetophenone 98-86-2 Acrolein (2-propenal) 107-02-8 Acrylam ide 79-06-1 Acrylic acid 79-10-7 Acrylonitrile (2-propenenitrile) 107-13-1 Allyl chloride (3-chloropropene) 107-05-1 Aniline (am inobenzene) 62-53-3 Benzene 71-43-2 Benzyl chloride (a-chlorotoluene) 100-44-7 Beta-Propiolactone 57-57-8 Bis(2-Chloroethyl)ether 111-44-4 Bis(chloromethyl) ether 542-88-1 Bromoform (tribromomethane) 75-25-2 Carbon disulfide 75-15-0 Carbon tetrachloride 56-23-5 Carbonyl sulfide 463-58-1 Catechol (o-hydroxyphenol) 120-80-9 Chloroacetic acid 79-11-8 Chlorobenzene 108-90-7 Chloroform 67-66-3 Chloromethyl m ethyl ether 107-30-2 Chloroprene (2-chloro-1,3-butadiene) 126-99-8 Cresylic acid (cresol isomer mixture) 1319-77-3 Cumene (isopropylbenzene) 98-82-8 Diazom ethane 334-88-3 Diethyl sulfate 64-67-5 Dim ethyl sulfate 77-78-1 Dim ethylcarbamyl chloride 79-44-7 Epichlorohydrin (1-chloro-2,3-epoxy propane) 106-89-8 Ethyl acrylate 140-88-5 Ethyl carbamate (urethane) 51-79-6 Speciated Volatile Organic HAPsEthyl chloride 75-00-3 Ethylbenzene 100-41-4 Ethylene dibrom ide (1,2-dibromoethane) 106-93-4 Ethylene dichloride (1,2-dichloroethane) 107-06-2 Ethylene oxide 75-21-8 Ethyleneim ine (aziridine) 151-56-4 Ethylidene dichloride (1,1-dichloroethane) 75-34-3 Formaldehyde 50-00-0 Hexachlorobutadiene 87-68-3 Hexachloroethane 67-72-1 Hexane 110-54-3 Isophorone 78-59-1 1, 1, 2, 2-Tetrachloroethane 79-34-5 Methanol 67-56-1 Methyl bromide 74-83-9. Methyl chloroform (1,1,1-trichloroethane) 71-55-6 Methyl ethyl ketone (2-butanone) 78-93-3 Methyl iodide 74-88-4 Methyl isobutyl ketone (hexone) 108-10-1 Methyl isocyanate 624-83-9 Methyl m ethacrylate 80-62-6 Methyl tert-butyl ether 1634-04-4 Methylene chloride 75-09-2 Methylhydrazine 60-34-4 m-Xylene 108-38-3 N,N-Dimethylaniline 100-23-2 N,N-Dimethylformamide 68-12-2 Nitrobenzene 98-95-3 N-Nitrosodimethylam ine 62-75-9 N-Nitrosomorpholine 59-89-2 N-Nitroso-N-methylurea 684-93-5 o-Cresol 95-48-7 o-Xylene 95-47-6 Phenol 108-95-2 Phosgene 75-44-5 Propionaldehyde 123-38-6

Propylene dichloride (1,2-dichloropropane) 78-87-5 Propylene oxide 75-56-9 p-Xylene 106-42-3 Styrene 100-42-5 Styrene oxide 96-09-3 sec-Butylbenzene Tetrachloroethylene 127-18-4 Toluene 108-88-3 Trichloroethylene 79-01-6 Triethylam ine 121-44-8 Vinyl acetate 108-05-04 Vinyl bromide 593-60-2 Vinyl chloride (chloroethene) 75-01-4 Vinylidene chloride 75-35-4 Xylenes (isomer & mixtures) 1330-20-7

### Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICRSpeciated Semi-volatile Organic HAPs

Constituent CAS 2-Methylnaphthalene 91-57-6 Acenaphthene 83-32-9 Acenaphthylene 208-96-8

Anthracene 120-12-7 Benzo(a)anthracene 56-55-3 Benzo(a)pyrene 50-32-8 Benzo(b)fluoranthene 205-99-2 Benzo(e)pyrene 192-97-2 Benzo(g,h,i)perylene 191-24-2 Benzo(k)fluoranthene 207-08-9 Chrysene 218-01-9 Dibenzo(a,h)anthracene 53-70-3 Fluoranthene 206-44-0 Fluorene 86-73-7 Indeno(1,2,3-cd)pyrene 193-39-5 Naphthalene 91-20-3 Perylene 77392-71-3 Phenanthrene 85-01-8 Pyrene 129-00-0 Acetophenone 98-86-2 2-Acetylam inofluorene 53-96-3 1-Acetyl-2-thiourea 591-08-2 Aldrin 309-00-2 2-Aminoanthraquinone 117-79-3 Am inoazobenzene 60-09-3 4-Aminobiphenyl 92-67-1 3-Amino-9-ethylcarbazole 132-32-1 Anilazine 101-05-3 Aniline 62-53-3 o-Anisidine 90-04-0 Aramite 140-57-8 Aroclor 1016 12674-11-2 Aroclor 1221 11104-28-2 Aroclor 1232 11141-16-5 Aroclor 1242 53469-21-9 Aroclor 1248 12672-29-6 Aroclor 1254 11097-69-1 Aroclor 1260 11096-82-5 Azinphos-m ethyl 86-50-0 Barban 101-27-9 Benzidine 92-87-5 Benzoic acid 65-85-0 p-Benzoquinone 106-51-4 Benzyl alcohol 100-51-6

α-BHC 319-84-6 β-BHC 319-85-7 δ-BHC 319-86-8γ-BHC (Lindane) 58-89-9

Bis(2-chloroethoxy)methane 111-91-1 Bis(2-chloroethyl) ether 111-44-4 Bis(2-chloroisopropyl) ether 39638-32-9 Bis(2-ethylhexyl) phthalate 117-81-7 4-Bromophenyl phenyl ether 101-55-3 Bromoxynil 1689-84-5 Butyl benzyl phthalate 85-68-7 Captafol 2425-06-1 Captan 133-06-2 Carbaryl 63-25-2 Carbofuran 1563-66-2 Carbophenothion 786-19-6 Chlordane (NOS) 57-74-9 Chlorfenvinphos 470-90-6 4-Chloroaniline 106-47-8 Chlorobenzilate 510-15-6 5-Chloro-2-methylaniline 95-79-4 4-Chloro-3-methylphenol 59-50-7 3-(Chloromethyl)pyridine hydrochloride 6959-48-4 1-Chloronaphthalene 90-13-1 2-Chloronaphthalene 91-58-7 2-Chlorophenol 95-57-8 4-Chloro-1,2-phenylenediam ine 95-83-0 4-Chloro-1,3-phenylenediam ine 5131-60-2 4-Chlorophenyl phenyl ether 7005-72-3 Coumaphos 56-72-4 p-Cresidine 120-71-8 Crotoxyphos 7700-17-6 2-Cyclohexyl-4,6-dinitro-phenol 131-89-5 4,4'-DDD 72-54-8 4,4'-DDE 72-55-9 4,4'-DDT 50-29-3 Demeton-O 298-03-3 Demeton-S 126-75-0 Diallate (cis or trans) 2303-16-4

2,4-Diaminotoluene 95-80-7 Dibenz(a,j)acridine 224-42-0 Dibenzofuran 132-64-9 Dibenzo(a,e)pyrene 192-65-4 1,2-Dibromo-3-chloropropane 96-12-8

Di-n-butyl phthalate 84-74-2 Dichlone 117-80-6 1,2-Dichlorobenzene 95-50-1 1,3-Dichlorobenzene 541-73-1 1,4-Dichlorobenzene 106-46-7 3,3'-Dichlorobenzidine 91-94-1 2,4-Dichlorophenol 120-83-2 2,6-Dichlorophenol 87-65-0 Dichlorovos 62-73-7Dicrotophos 141-66-2

Dieldrin 60-57-1 Diethyl phthalate 84-66-2 Diethylstilbestrol 56-53-1 Diethyl sulfate 64-67-5 Dim ethoate 60-51-5 3,3'-Dimethoxybenzidine 119-90-4 Dim ethylam inoazobenzene 60-11-7 7,12-Dimethylbenz(a)-anthracene 57-97-6 3,3'-Dimethylbenzidine 119-93-7 α,α-Dimethylphenethylam ine 122-09-8 2,4-Dimethylphenol 105-67-9 Dim ethyl phthalate 131-11-3 1,2-Dinitrobenzene 528-29-0 1,3-Dinitrobenzene 99-65-0 1,4-Dinitrobenzene 100-25-4 4,6-Dinitro-2-methylphenol 534-52-1 2,4-Dinitrophenol 51-28-5 2,4-Dinitrotoluene 121-14-2 2,6-Dinitrotoluene 606-20-2 Dinocap 39300-45-3 Dinoseb 88-85-7 Diphenylam ine 122-39-4 5,5-Diphenylhydantoin 57-41-0 1,2-Diphenylhydrazine 122-66-7 Di-n-octyl phthalate 117-84-0 Disulfoton 298-04-4 Endosulfan I 959-98-8 Endosulfan II 33213-65-9 Endosulfan sulfate 1031-07-8 Endrin 72-20-8 Endrin aldehyde 7421-93-4 Endrin ketone 53494-70-5 X X ND X X 53494-70-5 EPN 2104-64-5 Ethion 563-12-2 Ethyl carbamate 51-79-6 Ethyl m ethanesulfonate 62-50-0 Famphur 52-85-7 Fensulfothion 115-90-2 Fenthion 55-38-9 Fluchloralin 33245-39-5 2-Fluorobiphenyl (surr) 321-60-8 2-Fluorophenol (surr) 367-12-4 Heptachlor 76-44-8 Heptachlor epoxide 1024-57-3 Hexachlorobenzene 118-74-1 Hexachlorobutadiene 87-68-3 Hexachlorocyclopentadiene 77-47-4 Hexachloroethane 67-72-1 Hexachlorophene 70-30-4 Hexachloropropene 1888-71-7 Hexamethylphosphoramide 680-31-9 Hydroquinone 123-31-9 Isodrin 465-73-6Isophorone 78-59-1

Isosafrole 120-58-1 Kepone 143-50-0 Leptophos 21609-90-5 Malathion 121-75-5 Maleic anhydride 108-31-6 Mestranol 72-33-3 Methapyrilene 91-80-5 Methoxychlor 72-43-5 3-Methylcholanthrene 56-49-5 4,4'-Methylenebis (2-chloroaniline) 101-14-4 4,4'-Methylenebis(N,N-dimethylaniline) 101-61-1 3-Methylphenol & 4-Methylphenol 2-Methylnaphthalene Methyl m ethanesulfonate 66-27-3 Methyl parathion 298-00-0 2-Methylphenol 95-48-7 3-Methylphenol 108-39-4 4-Methylphenol 106-44-5 Mevinphos 7786-34-7 Mexacarbate 315-18-4 Mirex 2385-85-5 Monocrotophos 6923-22-4 Naled 300-76-5 Naphthalene 1,4-Naphthoquinone 130-15-4 1-Naphthylam ine 134-32-7 2-Naphthylam ine 91-59-8 Nicotine 54-11-5 5-Nitroacenaphthene 602-87-9 2-Nitroaniline 88-74-4 3-Nitroaniline 99-09-2 4-Nitroaniline 100-01-6 5-Nitro-o-anisidine 99-59-2 Nitrobenzene 98-95-3 4-Nitrobiphenyl 92-93-3 Nitrofen 1836-75-5 2-Nitrophenol 88-75-5 4-Nitrophenol 100-02-7 5-Nitro-o-toluidine 99-55-8 Nitroquinoline-1-oxide 56-57-5 N-Nitrosodi-n-butylam ine 924-16-3 N-Nitrosodiethylam ine 55-18-5 N-Nitrosodimethylam ine 62-75-9 N-Nitrosodiphenylam ine 86-30-6 N-Nitrosodi-n-propylam ine 621-64-7 N-Nitrosomethylethylam ine 10595-95-6 N-Nitrosomorpholine 59-89-2 N-Nitrosopiperidine 100-75-4 N-Nitrosopyrrolidine 930-55-2 Octamethyl pyrophosphoramide 152-16-9 4,4'-Oxydianiline 101-80-4 2,2-oxybis(1-Chloro-propane) Parathion 56-38-2 Pentachlorobenzene 608-93-5Pentachloronitrobenzene 82-68-8

Pentachlorophenol 87-86-5 Phenacetin 62-44-2 Phenenthrene Phenobarbital 50-06-6 Phenol 108-95-2 1,4-Phenylenediam ine 106-50-3 Phorate 298-02-2 Phosalone 2310-17-0 Phosmet 732-11-6 Phosphamidon 13171-21-6 Phthalic anhydride 85-44-9 Pyrene Pyridine 2-Picoline (2-Methylpyridine) 109-06-8 Piperonyl sulfoxide 120-62-7 Pronamide 23950-58-5 Propylthiouracil 51-52-5 Resorcinol 108-46-3 Safrole 94-59-7 Strychnine 57-24-9 Sulfallate 95-06-7 Terbufos 13071-79-9 1,2,4-Tetrachlorobenzene 1,2,4,5-Tetrachlorobenzene 95-94-3 2,4,5-Tetrachlorophenol 58-90-2 2,4,6-Tetrachlorophenol Tetrachlorvinphos 961-11-5 Tetraethyl dithiopyrophosphate 3689-24-5 Tetraethyl pyrophosphate 107-49-3 Thionazine 297-97-2 Thiophenol (Benzenethiol) 108-98-5 Toluene diisocyanate 584-84-9 o-Toluidine 95-53-4 Toxaphene 8001-35-2 1,2,4-Trichlorobenzene 120-82-1 2,4,5-Trichlorophenol 95-95-4 2,4,6-Trichlorophenol 88-06-2 Trifluralin 1582-09-8 2,4,5-Trimethylaniline 137-17-7 Trimethyl phosphate 512-56-1 1,3,5-Trinitrobenzene 99-35-4 Tris(2,3-dibromopropyl) phosphate 126-72-7 Tri-p-tolyl phosphate 78-32-0 O,O,O-Triethyl phosphorothioate 126-68-1