5A-i

APPENDIX 5A. ENGINEERING DATA

TABLE OF CONTENTS

5A.1 INTRODUCTION ........................................................................................................ 5A-1

5A.2 BASELINE SPECIFICATIONS .................................................................................. 5A-1

5A.3 LIGHTING CONFIGURATIONS ............................................................................... 5A-8

LIST OF TABLES

Table 5A.2.1 Baseline Design Options..................................................................................... 5A-2

Table 5A.2.2 Baseline Specifications....................................................................................... 5A-5

LIST OF FIGURES

Figure 5A.3.1 Lighting Configurations for VCT.RC.M......................................................... 5A-10

Figure 5A.3.2 Lighting Configurations for VCT.RC.L.......................................................... 5A-11

Figure 5A.3.3 Lighting Configurations for VCT.SC.M ......................................................... 5A-12

Figure 5A.3.4 Lighting Configurations for VCT.SC.L .......................................................... 5A-12

Figure 5A.3.5 Lighting Configurations for VCT.SC.I ........................................................... 5A-13

Figure 5A.3.6 Lighting Configurations for PD.SC.M ............................................................ 5A-13

Figure 5A.3.7 Lighting Configurations for VOP.RC.M......................................................... 5A-14

Figure 5A.3.8 Lighting Configurations for VOP.SC.M ......................................................... 5A-15

Figure 5A.3.9 Lighting Configurations for VOP.RC.L.......................................................... 5A-16

Figure 5A.3.10 Lighting Configurations for SVO.RC.M....................................................... 5A-17

Figure 5A.3.11 Lighting Configurations for SVO.SC.M ....................................................... 5A-18

Figure 5A.3.12 Lighting Configurations for SOC.RC.M....................................................... 5A-18
5A-1

APPENDIX 5A. ENGINEERING DATA

5A.1 INTRODUCTION

This appendix presents baseline specifications and detailed cost-efficiency results for 

each of the commercial refrigeration equipment classes directly analyzed in the engineering 

analysis (chapter 5 of the technical support document (TSD)).

5A.2 BASELINE SPECIFICATIONS

Table 5A.2.1 shows baseline design options for each of the commercial refrigeration 

equipment classes analyzed in the engineering analysis. All changes to cost and efficiency are 

measured relative to this level in the engineering analysis. Refer to chapter 5 of the TSD for 

details about each baseline technology.

Table 5A.2.2 shows baseline specifications (or case design specifications) for each of the 

commercial refrigeration equipment classes analyzed in the engineering analysis. These 

specifications include dimensions, numbers of components, temperatures, nominal power

ratings, and other case features that are necessary to calculate the energy consumption of each 

equipment class. In conjunction with baseline design option levels, the baseline specifications 

define the energy consumption and cost of the typical minimum technology equipment on the 

market.
5A-2

Table 5A.2.1 Baseline Design Optionsa

VOP.RC.M VOP.RC.L VOP.SC.M SVO.RC.M SVO.SC.M HZO.RC.M HZO.RC.L HZO.SC.M

Lighting for VOP, SVO, 

and SOC

T8 

Electronic

T8 

Electronic

T8 

Electronic

T8 

Electronic T8 Electronic - - -

Lighting for VCT and PD - - - - - - - -

Evaporator Coil Standard 

Coil

Standard 

Coil

Standard 

Coil

Standard 

Coil Standard Coil Standard Coil

Standard 

Coil

Standard 

Coil

Evaporator Fan Motors Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole

Case Insulation Standard Standard Standard Standard Standard Standard Standard Standard

Doors for VCT.XX.L/I - - - - - - - -

Doors for VCT/PD.XX.M - - - - - - - -

Doors for HCT.XX.L/I - - - - - - - -

Doors for HCT.XX.M - - - - - - - -

Doors for SOC.XX.L/I - - - - - - - -

Doors for SOC.XX.M - - - - - - - -

Condenser Coil Area 

(SC Only) - - Standard - Standard - - Standard

Condenser Fan Motors 

(SC only) - - Shaded Pole - Shaded Pole - - Shaded Pole

Compressor (SC only) - -

SingleSpeed 

Hermetic

- Single-Speed 

Hermetic - -

SingleSpeed 

Hermetic

Night Curtains None None None None None - - -

 a Equipment class designations consist of a combination—in sequential order separated by a period—of an equipment family code (VOP - vertical open, SVO -

semivertical open, HZO - horizontal open, VCT - vertical closed transparent, VCS - vertical closed solid, HCT - horizontal closed transparent, HCS - horizontal 

closed solid, SOC - service over counter, or PD – pull-down equipment), an operating mode code (RC - remote condensing or SC - self-contained), and a rating 

temperature code (M - medium temperature, L - low temperature, or I - ice-cream temperature). See chapter 3, Market and Technology Assessment, for a more 

detailed explanation of the equipment class terminology.
5A-3

Table 5A2.1 Cont.

HZO.SC.L VCT.RC.M VCT.RC.L VCT.SC.M VCT.SC.L VCT.SC.I VCS.SC.M VCS.SC.L VCS.SC.I

Lighting for VOP, 

SVO, and SOC - - - - - - - - -

Lighting for VCT and 

PD - T8 Electronic

T8 

Electronic

T8 

Electronic

T8 

Electronic

T8 

Electronic - - -

Evaporator Coil Standard Standard Standard Standard Standard Standard Standard Standard Standard

Evaporator Fan 

Motors Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded 

Pole

Case Insulation Standard Standard Standard Standard Standard Standard Standard Standard Standard

Doors for 

VCT.XX.L/I - - Standard - Standard Standard - - -

Doors for 

VCT/PD.XX.M - Standard - Standard - - - - -

Doors for 

HCT.XX.L/I - - - - - - - - -

Doors for 

HCT.XX.M - - - - - - - - -

Doors for 

SOC.XX.L/I - - - - - - - - -

Doors for SOC.XX.M - - - - - - - - -

Condenser Coil Area 

(SC Only) Standard - - Standard Standard Standard Standard Standard Standard

Condenser Fan 

Motors 

(SC only)

Shaded Pole - - Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded 

Pole

Compressor (SC 

only)

Single-Speed 

Hermetic - -

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

Night Curtains - - - - - - - - -
5A-4

Table 5A2.1 Cont.

HCT.SC.M HCT.SC.L HCT.SC.I HCS.SC.M HCS.SC.L SOC.RC.M PD.SC.M

Lighting for VOP, 

SVO, and SOC - - - - - - -

Lighting for VCT and 

PD - - - - - T8 Electronic

T8 

Electronic

Evaporator Coil - - - - - Standard Standard

Evaporator Fan 

Motors - - - - - Shaded Pole Shaded Pole

Case Insulation Standard Standard Standard Standard Standard Standard Standard

Doors for 

VCT.XX.L/I - - - - - - -

Doors for 

VCT/PD.XX.M - - - - - - Standard

Doors for 

HCT.XX.L/I - Standard Standard - - - -

Doors for HCT.XX.M Standard - - - - - -

Doors for 

SOC.XX.L/I - - - - - - -

Doors for SOC.XX.M - - - - - Standard -

Condenser Coil Area 

(SC Only) Standard Standard Standard Standard Standard - Standard

Condenser Fan 

Motors 

(SC only)

Shaded Pole Shaded Pole Shaded Pole Shaded Pole Shaded Pole - Shaded Pole

Compressor (SC only)

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

SingleSpeed 

Hermetic

-

SingleSpeed 

Hermetic

Night Curtains - - - - - - -
5A-5

Table 5A.2.2 Baseline Specifications

VOP.RC.M VOP.RC.L VOP.SC.M SVO.RC.M SVO.SC.M HZO.RC.M HZO.RC.L

Case Length (ft) 12 12 4 12 4 12 12

Case Gross Refrigerated Volume (ft3) 130.2 109.83 32 46.55 9.4 33 55

Case Total Display Area (ft2) 53.3 44.66 14.93 40 12.8 33 46

Number of Doors (#) 0 0 0 0 0 0 0

Single Door Area (ft2) 0 0 0 0 0 0 0

Non-Door Glass Area (ft2) 0 0 0 0 0 0 0

Non-Door Anti-Sweat Power (W) 0 600 0 50 100 50 200

Wall Area (ft2) 175.925 214 61 113.4 40.2 93.275 140

Insulation Thickness (in.) 1.5 2 1.5 1.5 1.5 1.5 2

Case Interior Surface Area (ft2) 130.225 118.5 47.5 72.5 21.3 48.35 82

Air Curtain Angle from Vertical (°) 8.5 7.28 6.05 47 57 82 90

Infiltrated Air Mass Flow (lb/hr) 860 530 300 590 220 250 140

Number of Bulbs in Conditioned Space (#) 12 0 4 9 3 0 0

Number of Bulbs Not in Conditioned Space (#) 9 9 3 6 2 0 0

Number of Ballasts in Conditioned Space (#) 0 0 0 0 0 0 0

Number of Ballasts Not in Conditioned Space (#) 7 3 3 5 2 0 0

Evaporator Fan Nominal Rated Wattage (W/fan) 9 9 6 9 6 9 6

Number of Evaporator Fans per Case (#) 6 14 2 4 1 4 4

Condenser Fan Nominal Rated Wattage (W/fan) 0 0 9 0 9 0 0

Number of Condenser Fans per Case (#) 0 0 3 0 1 0 0

Discharge Air Temperature (DAT) (F) 25 -10 25 25 25 25 -10

Baseline Evaporator Temperature (SET) (F) 15 -20 15 15 15 15 -20

Baseline Condenser Temperature (SCT) (F) 0 0 95 0 95 0 0

Compressor Oversize Multiplier 0 0 1.4 0 1.4 0 0

Defrost Mechanism (OFF, ELE, MAN) OFF ELE OFF OFF OFF ELE ELE

Defrost Time per Day (hr) 4.5 2 2.8 3 2.8 1 1

Defrost and Drain Heater Power (W) 0 8700 0 0 0 1000 3000

Condensate Pan Heater Power (W) 0 0 1500 0 1100 0 0
5A-6

Table 5A2.2 Cont.

HZO.SC.M HZO.SC.L VCT.RC.M VCT.RC.L VCT.SC.M VCT.SC.L VCT.SC.I

Case Length (ft) 4 4 12.725 12.74 4.5 4.5 4.3

Case Gross Refrigerated Volume (ft3) 7.5 7.4 142 133.5 49 49 48

Case Total Display Area (ft2) 12 12 65 65 20.7 20.7 26

Number of Doors (#) 0 0 5 5 2 2 2

Single Door Area (ft2) 0 0 13 13 10.35 10.35 13

Non-Door Glass Area (ft2) 4 4 0 0 0 0 0

Non-Door Anti-Sweat Power (W) 100 300 0 0 0 0 0

Wall Area (ft2) 54 52 204 200 73.02 73.02 77

Insulation Thickness (in.) 1.5 2 1.5 2 1.5 2 2.5

Case Interior Surface Area (ft2) 19.8 19.5 146.5 145 63.98 63.98 64

Air Curtain Angle from Vertical (°) 85 85 - - - - -

Infiltrated Air Mass Flow (lb/hr) 100 100 30 30 10.61 10.60 15

Number of Bulbs in Conditioned Space (#) 0 0 6 6 3 3 3

Number of Bulbs Not in Conditioned Space (#) 0 0 0 0 0 0 0

Number of Ballasts in Conditioned Space (#) 0 0 6 6 3 3 3

Number of Ballasts Not in Conditioned Space (#) 0 0 0 0 0 0 0

Evaporator Fan Nominal Rated Wattage (W/fan) 6 6 6 6 6 9 9

Number of Evaporator Fans per Case (#) 1 1 5 5 2 2 2

Condenser Fan Nominal Rated Wattage (W/fan) 6 6 0 0 6 6 6

Number of Condenser Fans per Case (#) 1 1 0 0 2 2 2

Discharge Air Temperature (DAT) (F) 25 -10 32 -5 25 -10 -20

Baseline Evaporator Temperature (SET) (F) 15 -20 27 -11 15 -20 -30

Baseline Condenser Temperature (SCT) (F) 95 95 0 0 95 95 95

Compressor Oversize Multiplier 1.4 1.4 0 0 1.4 1.4 1.4

Defrost Mechanism (OFF, ELE, MAN) ELE ELE OFF ELE OFF ELE ELE

Defrost Time per Day (hr) 1 1.5 1 1 1 1 1

Defrost and Drain Heater Power (W) 400 900 0 5000 0 1766.09 2580

Condensate Pan Heater Power (W) 300 400 0 0 0 200 200
5A-7

Table 5A2.2 Cont.

VCS.SC.M VCS.SC.L VCS.SC.I HCT.SC.M HCT.SC.L HCT.SC.I HCS.SC.M

Case Length (ft) 4.5 4.5 4.3 3.8 3.8 3.42 4.2

Case Gross Refrigerated Volume (ft3) 49 49 48 8.83 8.83 10.2 7.03

Case Total Display Area (ft2) 0 0 0 7.656 7.656 5.12 0

Number of Doors (#) 2 2 2 2 2 2 1

Single Door Area (ft2) 10.35 10.35 13 3.828 3.828 2.56 7.03

Non-Door Glass Area (ft2) 0 0 0 0 0 0 0

Non-Door Anti-Sweat Power (W) 0 0 250 0 0 0 0

Wall Area (ft2) 73.02 73.02 77 34.75 34.75 36.77 27.50

Insulation Thickness (in.) 1.5 2 2.5 1.5 2 2.5 1.5

Case Interior Surface Area (ft2) 0 0 0 0 21.34 26.1 0

Air Curtain Angle from Vertical (°) - - - - - - -

Infiltrated Air Mass Flow (lb/hr) 10.61 10.60 15 2.25 2.25 3 2.49

Number of Bulbs in Conditioned Space (#) 0 0 0 0 0 0 0

Number of Bulbs Not in Conditioned Space (#) 0 0 0 0 0 0 0

Number of Ballasts in Conditioned Space (#) 0 0 0 0 0 0 0

Number of Ballasts Not in Conditioned Space (#) 0 0 0 0 0 0 0

Evaporator Fan Nominal Rated Wattage (W/fan) 6 9 9 0 0 0 0

Number of Evaporator Fans per Case (#) 2 2 2 0 0 0 0

Condenser Fan Nominal Rated Wattage (W/fan) 6 6 6 9 9 9 9

Number of Condenser Fans per Case (#) 2 2 2 1 1 1 1

Discharge Air Temperature (DAT) (F) 25 -10 -20 25 -10 -20 25

Baseline Evaporator Temperature (SET) (F) 15 -20 -30 15 -20 -30 15

Baseline Condenser Temperature (SCT) (F) 95 95 95 95 95 95 95

Compressor Oversize Multiplier 1.4 1.4 1.4 1.4 1.4 1.4 1.4

Defrost Mechanism (OFF, ELE, MAN) OFF ELE ELE OFF MAN MAN OFF

Defrost Time per Day (hr) 1 1 1 1 0 0 1

Defrost and Drain Heater Power (W) 0 1766.09 2580 0 0 0 0

Condensate Pan Heater Power (W) 0 200 200 0 0 0 0
5A-8

Table 5A2.1 Cont.

HCS.SC.L SOC.RC.M PD.SC.M

Case Length (ft) 4.2 12 2.5

Case Gross Refrigerated Volume (ft3) 7.03 66 27

Case Total Display Area (ft2) 0 51 11.6

Number of Doors (#) 2 6 1

Single Door Area (ft2) 3.125 3.5 11.6

Non-Door Glass Area (ft2) 0 30 0

Non-Door Anti-Sweat Power (W) 0 200 0

Wall Area (ft2) 27.5 84.6 57.58

Insulation Thickness (in.) 2 1.5 1.5

Case Interior Surface Area (ft2) 0 61.6 46.71

Air Curtain Angle from Vertical (°) - - -

Infiltrated Air Mass Flow (lb/hr) 2.49 15 5.89

Number of Bulbs in Conditioned Space (#) 0 15 2

Number of Bulbs Not in Conditioned Space (#) 0 0 0

Number of Ballasts in Conditioned Space (#) 0 0 1

Number of Ballasts Not in Conditioned Space (#) 0 5 0

Evaporator Fan Nominal Rated Wattage (W/fan) 0 9 6

Number of Evaporator Fans per Case (#) 0 4 1

Condenser Fan Nominal Rated Wattage (W/fan) 9 0 6

Number of Condenser Fans per Case (#) 1 0 1

Discharge Air Temperature (DAT) (F) -10 30 25

Baseline Evaporator Temperature (SET) (F) -20 20 15

Baseline Condenser Temperature (SCT) (F) 95 0 95

Compressor Oversize Multiplier 1.4 0 2

Defrost Mechanism (OFF, ELE, MAN) MAN ELE OFF

Defrost Time per Day (hr) 0 1.2 1

Defrost and Drain Heater Power (W) 0 1600 0

Condensate Pan Heater Power (W) 0 0 0

5A.3 LIGHTING CONFIGURATIONS

Lighting for use in cases with transparent doors functions differently than lighting for use 

in cases without doors. Cases with transparent doors typically display boxed merchandise, and 

only products on the front of the shelves are visible to the consumer. Therefore, the only portion 

of the display case that requires illumination is the area on the front surface of the case at the 

front of the shelves. Since this is only a limited area that requires lighting, light-emitting diodes 

(LEDs) offer an advantage over fluorescent lighting in vertical refrigerated cases with 

transparent doors because of the directional nature of LED lighting. 

As part of the engineering analysis for the 2009 final rule, the U.S. Department of Energy 

(DOE), with input from manufacturers and other stakeholders, developed lighting configurations 

for cases with transparent doors. DOE has retained these configurations as part of this analysis, 

and has further developed additional configurations for equipment classes not covered in the 

2009 rulemaking. For the VCT equipment family, DOE assumed one fluorescent bulb on each 

mullion and a fluorescent bulb on each end of the case. There are two different types of LED 

lighting used in cases with transparent doors. A center mullion lighting fixture is used between 

doors and is designed to have half of the LED emitters directed toward one door and half of the 

LED chips directed toward the other door. An end mullion lighting fixture has half the light 
5A-9

output, cost, and power consumption of a center mullion lighting fixture. The LED emitters in an 

end mullion lighting fixture are all directed toward the one door next to which they are located. 

Therefore, two end mullion lighting fixtures are the approximately equivalent to a single center 

mullion lighting fixture with regard to cost, light output, and power consumption. DOE modeled 

the LED lighting for the VCT equipment family using a center mullion lighting fixture and 

assumed one center mullion lighting fixture per door. Illustrative front views of the lighting 

configurations for both fluorescent and LED lighting for the VCT equipment family are shown in

Figure 5A.3.1 through Figure 5A.3.6. The red strips represent a fluorescent bulb inside the 

refrigerated volume, the blue strips represent an LED center mullion lighting fixture inside the 

refrigerated volume, and the green strips represent an LED end mullion lighting fixture inside the 

refrigerated volume.
5A-10

Figure 5A.3.1 Lighting Configurations for VCT.RC.M

Bulb In =

LED In = Center Mullion

1/2 LED In = End Mullion (one on either end of case, resulting in the

 equivalent of a single center mullion)

VCT.RC.M

Lighting Type: Fluorescent

Case Length [ft]:12.7

Bulb Length [ft]: 5

Bulbs In: 6

Bulbs Out: 0

VCT.RC.M

Lighting Type: LED

Case Length [ft]:12.7

Bulb Length [ft]: 5

LEDs In: 5

LEDs Out: 0
5A-11

VCT.RC.L

Lighting Type: Fluorescent

Case Length [ft]: 12.7

Bulb Length [ft]: 5

Bulbs In: 6

Bulbs Out: 0

VCT.RC.L

Lighting Type: LED

Case Length [ft]: 12.7

Bulb Length [ft]: 5

LEDs In: 5

LEDs Out: 0

Figure 5A.3.2 Lighting Configurations for VCT.RC.L
5A-12

Figure 5A.3.3 Lighting Configurations for VCT.SC.M

Figure 5A.3.4 Lighting Configurations for VCT.SC.L

VCT.SC.L

Lighting Type: LED

Case Length [ft]: 4.5

Bulb Length [ft]: 5

LEDs In: 2

LEDs Out: 0

VCT.SC.L

Lighting Type: Fluorescent

Case Length [ft]: 4.5

Bulb Length [ft]: 5

Bulbs In: 3

Bulbs Out: 0

VCT.SC.M

Lighting Type: Fluorescent

Case Length [ft]: 4.5

Bulb Length [ft]: 5

Bulbs In: 3

Bulbs Out: 0

VCT.SC.M

Lighting Type: LED

Case Length [ft]: 4.5

Bulb Length [ft]: 5

LEDs In: 2

LEDs Out: 0
5A-13

Figure 5A.3.5 Lighting Configurations for VCT.SC.I

Figure 5A.3.6 Lighting Configurations for PD.SC.M

For equipment classes without doors (i.e., VOP, SVO, SOC, and HZO equipment 

families), merchandise throughout the entire refrigerated volume is visible to the consumer.

Therefore, the entire refrigerated volume must be illuminated.b For this application, the 

directionality characteristic of LED lighting tends to be less effective than fluorescent lighting,

which outputs light in all directions surrounding the bulb. In the 2009 final rule, DOE developed 

 b DOE assumes that the HZO equipment family does not contain any lighting because the ambient light of the store 

provides adequate illumination of the displayed merchandise.

PD.SC.M

Lighting Type: LED

Case Length [ft]: 2.5

Bulb Length [ft]: 5

LEDs In: 1

LEDs Out: 0

PD.SC.M

Lighting Type: Fluorescent

Case Length [ft]: 2.5

Bulb Length [ft]: 5

Bulbs In: 2

Bulbs Out: 0

VCT.SC.I

Lighting Type: Fluorescent

Case Length [ft]: 4.3

Bulb Length [ft]: 5

Bulbs In: 3

Bulbs Out: 0

VCT.SC.I

Lighting Type: LED

Case Length [ft]: 4.3

Bulb Length [ft]: 5

LEDs In: 2

LEDs Out: 0
5A-14

case lighting configurations for these classes as well. Based on discussions with LED 

refrigerated display case lighting manufacturers and comments from commercial refrigeration 

equipment manufacturers, DOE determined that there are two different types of LED luminaries 

used in this equipment. A shelf light is used to illuminate merchandise close to it. Due to the 

directionality of the light output from an LED luminary, DOE assumes that two shelf lights are 

used per shelf to provide the desired illumination throughout an entire shelf: one on the front of 

the shelf and one midway under the shelf. A canopy light is typically located on the canopy of a 

display case. A canopy light has effectively twice the light output, cost, and power consumption 

of a shelf light and is typically is used to provide additional illumination of the product in the 

bottom well of the display case. DOE modeled the LED lighting for the VOP, SVO, and SOC 

equipment families, in the engineering analysis, using a shelf light. DOE also assumed that the 

number of LED lighting fixtures per shelf would have to be doubled from what was assumed for 

fluorescent lighting to provide adequate illumination for the merchandise displayed on each 

shelf. Illustrative cross-sections of lighting configurations for both fluorescent and LED lighting 

for the VOP, SVO, and SOC equipment families are shown in Figure 5A.3.7 through Figure 

5A.3.12. The green circles represent a bulb or LED inside the refrigerated volume and the red 

circles represent a bulb or LED outside the refrigerated volume.

Bulb/LED In =

Bulb/LED Out =

VOP.RC.M VOP.RC.M

Lighting Type: Fluorescent Lighting Type: LED

Case Length [ft]: 12 Case Length [ft]: 12

Bulb Length [ft]: 4 LED Length [ft]: 4

Bulbs In: 12 LEDs In: 24

Bulbs Out: 9 LEDs Out: 9

Figure 5A.3.7 Lighting Configurations for VOP.RC.M
5A-15

VOP.SC.M VOP.SC.M

Lighting Type: Fluorescent Lighting Type: LED

Case Length [ft]: 4 Case Length [ft]: 4

Bulb Length [ft]: 4 LED Length [ft]: 4

Bulbs In: 4 LEDs In: 8

Bulbs Out: 3 LEDs Out: 3

Figure 5A.3.8 Lighting Configurations for VOP.SC.M
5A-16

VOP.RC.L VOP.RC.L

Lighting Type: Fluorescent Lighting Type: LED

Case Length [ft]: 12 Case Length [ft]: 12

Bulb Length [ft]: 4 LED Length [ft]: 4

Bulbs In: 0 LEDs In: 0

Bulbs Out: 9 LEDs Out: 9

Figure 5A.3.9 Lighting Configurations for VOP.RC.L
5A-17

SVO.RC.M SVO.RC.M

Lighting Type: Fluorescent Lighting Type: LED

Case Length [ft]: 12 Case Length [ft]: 12

Bulb Length [ft]: 4 LED Length [ft]: 4

Bulbs In: 9 LEDs In: 18

Bulbs Out: 6 LEDs Out: 6

Figure 5A.3.10 Lighting Configurations for SVO.RC.M
5A-18

SVO.SC.M SVO.SC.M

Lighting Type: Fluorescent Lighting Type: LED

Case Length [ft]: 4 Case Length [ft]: 4

Bulb Length [ft]: 4 LED Length [ft]: 4

Bulbs In: 3 LEDs In: 6

Bulbs Out: 2 LEDs Out: 2

Figure 5A.3.11 Lighting Configurations for SVO.SC.M

SOC.RC.M SOC.RC.M

Lighting Type: Fluorescent Lighting Type: LED

Case Length [ft]: 12 Case Length [ft]: 12

Bulb Length [ft]: 4 LED Length [ft]: 4

Bulbs In: 15 LEDs In: 18

Bulbs Out: 0 LEDs Out: 0

Figure 5A.3.12 Lighting Configurations for SOC.RC.M