Name: Patricia Q. West

Title: Manager, Environmental, Energy Supp

Company: Progress Energy Florida, Inc.

Sign Date: 9/3/2010

Name: Michael Sussman, P.E.

Title: Project Manager

Company: Kleinfelder Southeast, Inc.

Sign Date: 9/3/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Progress Energy Florida Suwannee River Power Plant Unit 2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 17, 2011 Page 1 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Facility Information:

Progress Energy Florida, Inc. Suwannee Riv

4037 River Road

Live Oak FL 32060

Contact: Cary W. Hamilton

Phone:

Fax:

Email: cary.hamilton@pgnmail.com

Testing Company:

Kleinfleder Southeast Inc.

6200 Harris Technology Blvd.

Charlotte NC 28269

Contact:W. Quentin Best

Phone: 704-598-1049

Fax: 704-598-1050

Email: qbest@kleinfelder.com

Air Permit Number:

1210003-007-AV

Permitted Source ID/Name:

Suw Unit 1 Fossil Fuel Fired Steam Generator Unit No. 1

Permitted Maximum Process Rate:

450 million Btu/hr

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Industry/SCC/NAIS 221121 AFS #: 1212100003 FRS #: 110000909214

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Regulation Description Compound Limit Unit

ICR % H2O 0 percent(%)

ICR 1,2,3,4,6,7,8-HpCDD 0 ng/dscm corrected

ICR 1,2,3,4,6,7,8-HpCDD 0 lb/million BTU 

using O2

ICR 1,2,3,4,6,7,8-HpCDF 0 ng/dscm corrected

ICR 1,2,3,4,6,7,8-HpCDF 0 lb/million BTU 

using O2

ICR 1,2,3,4,7,8,9-HpCDF 0 ng/dscm corrected

ICR 1,2,3,4,7,8,9-HpCDF 0 lb/million BTU 

using O2

ICR 1,2,3,4,7,8-HxCDD 0 ng/dscm corrected

ICR 1,2,3,4,7,8-HxCDD 0 lb/million BTU 

using O2

ICR 1,2,3,4,7,8-HxCDF 0 ng/dscm corrected

ICR 1,2,3,4,7,8-HxCDF 0 lb/million BTU 

using O2

ICR 1,2,3,6,7,8-HxCDD 0 ng/dscm corrected

ICR 1,2,3,6,7,8-HxCDD 0 lb/million BTU 

using O2

ICR 1,2,3,6,7,8-HxCDF 0 ng/dscm corrected

ICR 1,2,3,6,7,8-HxCDF 0 lb/million BTU 

using O2

ICR 1,2,3,7,8,9-HxCDD 0 ng/dscm corrected

Thursday, February 17, 2011 Page 2 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

ICR 1,2,3,7,8,9-HxCDD 0 lb/million BTU 

using O2

ICR 1,2,3,4,6,7,8-HpCDF 0 ng/dscm corrected

ICR 1,2,3,7,8,9-HxCDF 0 lb/million BTU 

using O2

ICR 1,2,3,7,8-PeCDD 0 ng/dscm corrected

ICR 1,2,3,7,8-PeCDD 0 lb/million BTU 

using O2

ICR 1,2,3,7,8-PeCDF 0 ng/dscm corrected

ICR 1,2,3,7,8-PeCDF 0 lb/million BTU 

using O2

ICR 2,3,3',4,4',5,5'-HpCB 

(PCB189)

0 ng/dscm corrected

ICR 2,3,3',4,4',5,5'-HpCB 

(PCB189)

0 lb/million BTU 

using O2

ICR 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

0 ng/dscm corrected

ICR 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

0 lb/million BTU 

using O2

ICR 2,3,3',4,4'-PeCB (PCB105) 0 ng/dscm corrected

ICR 2,3,3',4,4'-PeCB (PCB105) 0 lb/million BTU 

using O2

ICR 2,3',4,4',5,5'-HxCB 

(PCB167)

0 ng/dscm corrected

ICR 2,3',4,4',5,5'-HxCB 

(PCB167)

0 lb/million BTU 

using O2

ICR 2,3,4,4',5-PeCB (PCB114) 0 ng/dscm corrected

ICR 2,3,4,4',5-PeCB (PCB114) 0 lb/million BTU 

using O2

ICR 2,3',4,4',5-PeCB (PCB118) 0 ng/dscm corrected

ICR 2,3',4,4',5-PeCB (PCB118) 0 lb/million BTU 

using O2

ICR 2',3,4,4',5-PeCB (PCB123) 0 ng/dscm corrected

ICR 2',3,4,4',5-PeCB (PCB123) 0 lb/million BTU 

using O2

ICR 2,3,4,6,7,8-HxCDF 0 ng/dscm corrected

ICR 2,3,4,6,7,8-HxCDF 0 lb/million BTU 

using O2

ICR 2,3,4,7,8-PeCDF 0 ng/dscm corrected

ICR 2,3,4,7,8-PeCDF 0 lb/million BTU 

using O2

ICR 2,3,7,8-TCDD 0 ng/dscm corrected

ICR 2,3,7,8-TCDD 0 lb/million BTU 

using O2

ICR 2,3,7,8-TCDF 0 ng/dscm corrected

ICR 2,3,7,8-TCDF 0 lb/million BTU 

using O2

ICR 2-Methylnaphthalene 0 ng/dscm corrected

ICR 2-Methylnaphthalene 0 lb/million BTU 

using O2

ICR 3,3',4,4',5,5'-HxCB 

(PCB169)

0 ng/dscm corrected

Thursday, February 17, 2011 Page 3 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

ICR 3,3',4,4',5,5'-HxCB 

(PCB169)

0 lb/million BTU 

using O2

ICR 3,3',4,4',5-PeCB (PCB126) 0 ng/dscm corrected

ICR 3,3',4,4',5-PeCB (PCB126) 0 lb/million BTU 

using O2

ICR 3,3',4,4'-TCB (PCB77) 0 ng/dscm corrected

ICR 3,3',4,4'-TCB (PCB77) 0 lb/million BTU 

using O2

ICR 3,4,4',5-TCB (PCB81) 0 ng/dscm corrected

ICR 3,4,4',5-TCB (PCB81) 0 lb/million BTU 

using O2

ICR Acenaphthene** 0 ug/dscm corrected

ICR Acenaphthene** 0 lb/million BTU 

using O2

ICR Acenaphthylene** 0 ug/dscm corrected

ICR Acenaphthylene** 0 lb/million BTU 

using O2

ICR Anthracene** 0 ug/dscm corrected

ICR Anthracene** 0 lb/million BTU 

using O2

ICR Antimony 0 lb/million BTU 

using O2

ICR Arsenic 0 lb/million BTU 

using O2

ICR Barium 0 lb/million BTU 

using O2

ICR Benzo(a)Anthracene* 0 ug/dscm corrected

ICR Benzo(a)Anthracene* 0 lb/million BTU 

using O2

ICR Benzo(a)Pyrene* 0 ug/dscm corrected

ICR Benzo(a)Pyrene* 0 lb/million BTU 

using O2

ICR Benzo(b)Fluoranthene* 0 ug/dscm corrected

ICR Benzo(b)Fluoranthene* 0 lb/million BTU 

using O2

ICR Benzo(e)Pyrene 0 ug/dscm corrected

ICR Benzo(e)Pyrene 0 lb/million BTU 

using O2

ICR Benzo(ghi)Perylene** 0 ug/dscm corrected

ICR Benzo(ghi)Perylene** 0 lb/million BTU 

using O2

ICR Benzo(k)Fluoranthene* 0 ug/dscm corrected

ICR Benzo(k)Fluoranthene* 0 lb/million BTU 

using O2

ICR Beryllium 0 lb/million BTU 

using O2

ICR Bromine 0 lb/million BTU 

using O2

ICR Cadmium 0 lb/million BTU 

using O2

ICR Carbon Monoxide 0 ppm corrected

ICR Carbon Monoxide 0 lb/million BTU 

using O2

Thursday, February 17, 2011 Page 4 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

ICR Chromium 0 lb/million BTU 

using O2

ICR Chrysene* 0 ug/dscm corrected

ICR Chrysene* 0 lb/million BTU 

using O2

ICR Co2 0 percent(%)

ICR Cobalt 0 lb/million BTU 

using O2

ICR Copper 0 lb/million BTU 

using O2

ICR Dibenzo(a,h)Anthracene* 0 ng/dscm corrected

ICR Dibenzo(a,h)Anthracene* 0 lb/million BTU 

using O2

ICR Filterable Particulate 0 lb/million BTU 

using O2

ICR Filterable PM2.5 0 lb/million BTU 

using O2

ICR Fluoranthene** 0 ug/dscm corrected

ICR Fluoranthene** 0 lb/million BTU 

using O2

ICR Fluorene** 0 ug/dscm corrected

ICR Fluorene** 0 lb/million BTU 

using O2

ICR Formaldehyde 0 ppm corrected

ICR Formaldehyde 0 lb/million BTU 

using O2

ICR Hydrogen Chloride 0 lb/million BTU 

using O2

ICR Hydrogen Fluoride 0 lb/million BTU 

using O2

ICR Indeno(1,2,3-cd)Pyrene* 0 ug/dscm corrected

ICR Indeno(1,2,3-cd)Pyrene* 0 lb/million BTU 

using O2

ICR Inorganic (Aqueous) 

Condensible Part.

0 lb/million BTU 

using O2

ICR Lead 0 lb/million BTU 

using O2

ICR Magnesium 0 lb/million BTU 

using O2

ICR Manganese 0 lb/million BTU 

using O2

ICR Mercury 0 lb/million BTU 

using O2

ICR Naphthalene** 0 ug/dscm corrected

ICR Naphthalene** 0 lb/million BTU 

using O2

ICR Nickel 0 lb/million BTU 

using O2

ICR Nitrogen oxides (NOx) 0 ppm corrected

ICR Nitrogen oxides (NOx) 0 lb/million BTU 

using O2

ICR O2 0 percent(%)

ICR OCDD 0 ng/dscm corrected

Thursday, February 17, 2011 Page 5 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

ICR OCDD 0 lb/million BTU 

using O2

ICR OCDF 0 ng/dscm corrected

ICR OCDF 0 lb/million BTU 

using O2

ICR Organic Condensible 

Particulate

0 lb/million BTU 

using O2

ICR Other Di-CBs 0 ng/dscm corrected

ICR Other Di-CBs 0 lb/million BTU 

using O2

ICR Other Hepta-CBs 0 ng/dscm corrected

ICR Other Hepta-CBs 0 lb/million BTU 

using O2

ICR Other Hexa-CBs 0 ng/dscm corrected

ICR Other Hexa-CBs 0 lb/million BTU 

using O2

ICR Other HpCDD 0 ng/dscm corrected

ICR Other HpCDD 0 lb/million BTU 

using O2

ICR Other HpCDF 0 ng/dscm corrected

ICR Other HpCDF 0 lb/million BTU 

using O2

ICR Other HxCDD 0 ng/dscm corrected

ICR Other HxCDD 0 lb/million BTU 

using O2

ICR Other HxCDF 0 ng/dscm corrected

ICR Other HxCDF 0 lb/million BTU 

using O2

ICR Other Mono-CBs 0 ug/dscm corrected

ICR Other Mono-CBs 0 lb/million BTU 

using O2

ICR Other Nona-CBs 0 ng/dscm corrected

ICR Other Nona-CBs 0 lb/million BTU 

using O2

ICR Other Octa-CBs 0 ng/dscm corrected

ICR Other Octa-CBs 0 lb/million BTU 

using O2

ICR Other PeCDD 0 ng/dscm corrected

ICR Other PeCDD 0 lb/million BTU 

using O2

ICR Other PeCDF 0 ng/dscm corrected

ICR Other PeCDF 0 lb/million BTU 

using O2

ICR Other Penta-CBs 0 ng/dscm corrected

ICR Other Penta-CBs 0 lb/million BTU 

using O2

ICR Other TCDD 0 ng/dscm corrected

ICR Other TCDD 0 lb/million BTU 

using O2

ICR Other TCDF 0 ng/dscm corrected

ICR Other TCDF 0 lb/million BTU 

using O2

Thursday, February 17, 2011 Page 6 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

ICR Other Tetra-CBs 0 ng/dscm corrected

ICR Other Tetra-CBs 0 lb/million BTU 

using O2

ICR Other Tri-CBs 0 ng/dscm corrected

ICR Other Tri-CBs 0 lb/million BTU 

using O2

ICR Perylene 0 ug/dscm corrected

ICR Perylene 0 lb/million BTU 

using O2

ICR Phenanthrene** 0 ug/dscm corrected

ICR Phenanthrene** 0 lb/million BTU 

using O2

ICR Phosphorus (yellow or 

white)

0 lb/million BTU 

using O2

ICR Pyrene** 0 ug/dscm corrected

ICR Pyrene** 0 lb/million BTU 

using O2

ICR Selenium 0 lb/million BTU 

using O2

ICR Silver 0 lb/million BTU 

using O2

ICR Sulfur Dioxide 0 ppm corrected

ICR Sulfur Dioxide 0 lb/million BTU 

using O2

ICR Thallium 0 lb/million BTU 

using O2

ICR Total 16*/**PAH 0 ug/dscm corrected

ICR Total 16*/**PAH 0 lb/million BTU 

using O2

ICR Total 7*PAH 0 ug/dscm corrected

ICR Total 7*PAH 0 lb/million BTU 

using O2

ICR Total Dioxins 0 ng/dscm corrected

ICR Total Dioxins 0 lb/million BTU 

using O2

ICR Total Furans 0 ng/dscm corrected

ICR Total Furans 0 lb/million BTU 

using O2

ICR Total organic compounds 

(TOC) as Propane

0 ppm corrected

ICR Total organic compounds 

(TOC) as Propane

0 lb/million BTU 

using O2

ICR Total PCBs 0 ng/dscm corrected

ICR Total PCBs 0 lb/million BTU 

using O2

ICR Total PM2.5 0 lb/million BTU 

using O2

ICR Total TEQ 0 ng/dscm corrected

ICR Total TEQ 0 lb/million BTU 

using O2

ICR Zinc 0 lb/million BTU 

using O2

ICR Methane 0 ppm corrected

Thursday, February 17, 2011 Page 7 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Boiler No. 2 (E.U. ID No. -002) is a nominal 34.0 megawatt electric steam generator. The boiler is allowed to fire 

No.2 fuel oil, No.6 fuel oil, “on specification” used oil, natural gas and a blend of fuel oil and natural gas. The “onspecification used oil is generally fired as blended fuel oil with either the No.2 fuel oil or No. 6 fuel oil. The boiler 

drives a turbine generator for electrical power and vents to its own stack. There is no air pollution equipment control 

devices associated with the boiler.

Sampling Location Information:

Test Parameter Information:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 83.063 0 0 0 240 240 2 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 3 480 0

Stack Exit Other PeCDD Method 23 3 480 0

Stack Exit Other HxCDD Method 23 3 480 0

Stack Exit Other HpCDD Method 23 3 480 0

Stack Exit Other TCDF Method 23 3 480 0

Stack Exit Other PeCDF Method 23 3 480 0

Stack Exit Other HxCDF Method 23 3 480 0

Stack Exit Other HpCDF Method 23 3 480 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

ICR Methane 0 lb/million BTU 

using O2

ICR Hydrogen Cyanide 0 lb/million BTU 

using O2

Thursday, February 17, 2011 Page 8 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Thursday, February 17, 2011 Page 9 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 6/15/2010 6/21/2010 6/22/2010

Run Start Time 2:25:00 PM 9:29:00 PM 8:44:00 AM

Run Finish Time 10:40:00 PM 9:29:00 PM 5:11:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 349.681 312.560 314.756 325.666

Moisture Content of Stack Gas, % 6.31 7.51 7.89 7.237

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.165 9.859 10.248 10.091

Oxygen, % 8.944 8.867 8.564 8.792

Average Stack Gas Temperature, °F 320.17 324.21 317.92 320.767

Dry Volumetric Flow Rate, dry scfm 100,401.5 95,132.2 95,897.1 97,143.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 158,185.7 152,563.6 152,676.5 154,475.267

Percent Isokinetic of Sampling Rate, % 100.7 99.4 99.3 99.800

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 17, 2011 Page 10 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Emissions Summary

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000425 0.00000000389 0.00000000483 0.000

Elb/hr 1.61E-10 1.57E-10 1.95E-10 0.000

lb/mmBtuO2 4.30E-13 4.38E-13 5.27E-13 0.000

ng/dscm 4.29E-04 4.40E-04 5.42E-04 0.000

ng/dscm@7%O2 4.99E-04 5.08E-04 6.11E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000317 0.00000000393 0.0000000028 0.000

Elb/hr 1.20E-10 1.58E-10 1.13E-10 0.000

lb/mmBtuO2 3.21E-13 4.42E-13 3.05E-13 0.000

ng/dscm 3.20E-04 4.44E-04 3.14E-04 0.000

ng/dscm@7%O2 3.72E-04 5.13E-04 3.54E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000253 0.00000000279 0.00000000212 0.000

Elb/hr 9.61E-11 1.12E-10 8.54E-11 0.000

lb/mmBtuO2 2.56E-13 3.14E-13 2.31E-13 0.000

ng/dscm 2.56E-04 3.15E-04 2.38E-04 0.000

ng/dscm@7%O2 2.98E-04 3.64E-04 2.68E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000242 0.00000000212 0.0000000019 0.000

Elb/hr 9.19E-11 8.54E-11 7.66E-11 0.000

lb/mmBtuO2 2.45E-13 2.39E-13 2.07E-13 0.000

ng/dscm 2.44E-04 2.40E-04 2.13E-04 0.000

ng/dscm@7%O2 2.84E-04 2.77E-04 2.40E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000316 0.00000000455 0.00000000254 0.000

Elb/hr 1.20E-10 1.83E-10 1.02E-10 0.000

lb/mmBtuO2 3.20E-13 5.12E-13 2.77E-13 0.000

ng/dscm 3.19E-04 5.14E-04 2.85E-04 0.000

ng/dscm@7%O2 3.71E-04 5.94E-04 3.21E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000232 0.0000000022 0.00000000185 0.000

Elb/hr 8.81E-11 8.86E-11 7.46E-11 0.000

Thursday, February 17, 2011 Page 11 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

lb/mmBtuO2 2.35E-13 2.48E-13 2.02E-13 0.000

ng/dscm 2.34E-04 2.49E-04 2.08E-04 0.000

ng/dscm@7%O2 2.72E-04 2.88E-04 2.34E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000243 0.00000000352 0.00000000198 0.000

Elb/hr 9.23E-11 1.42E-10 7.98E-11 0.000

lb/mmBtuO2 2.46E-13 3.96E-13 2.16E-13 0.000

ng/dscm 2.45E-04 3.98E-04 2.22E-04 0.000

ng/dscm@7%O2 2.85E-04 4.60E-04 2.50E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000026 0.00000000238 0.000000002 0.000

Elb/hr 9.87E-11 9.58E-11 8.06E-11 0.000

lb/mmBtuO2 2.63E-13 2.68E-13 2.18E-13 0.000

ng/dscm 2.63E-04 2.69E-04 2.24E-04 0.000

ng/dscm@7%O2 3.06E-04 3.11E-04 2.52E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000177 0.00000000174 0.00000000133 0.000

Elb/hr 6.72E-11 7.01E-11 5.36E-11 0.000

lb/mmBtuO2 1.79E-13 1.96E-13 1.45E-13 0.000

ng/dscm 1.79E-04 1.97E-04 1.49E-04 0.000

ng/dscm@7%O2 2.08E-04 2.28E-04 1.68E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000236 0.00000000219 0.00000000164 0.000

Elb/hr 8.96E-11 8.82E-11 6.61E-11 0.000

lb/mmBtuO2 2.39E-13 2.47E-13 1.79E-13 0.000

ng/dscm 2.38E-04 2.47E-04 1.84E-04 0.000

ng/dscm@7%O2 2.77E-04 2.85E-04 2.07E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000587 0.00000000696 0.00000000302 0.000

Elb/hr 2.23E-10 2.80E-10 1.22E-10 0.000

lb/mmBtuO2 5.95E-13 7.84E-13 3.29E-13 0.000

ng/dscm 5.93E-04 7.86E-04 3.39E-04 0.001

ng/dscm@7%O2 6.89E-04 9.08E-04 3.82E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000242 0.0000000142 0.0000000189 0.000

Elb/hr 9.19E-10 5.72E-10 7.62E-10 0.000

Thursday, February 17, 2011 Page 12 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

lb/mmBtuO2 2.45E-12 1.60E-12 2.06E-12 0.000

ng/dscm 2.44E-03 1.60E-03 2.12E-03 0.002

ng/dscm@7%O2 2.84E-03 1.85E-03 2.39E-03 0.002

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000296 0.000000183 0.000000223 0.000

Elb/hr 1.12E-08 7.37E-09 8.99E-09 0.000

lb/mmBtuO2 3.00E-11 2.06E-11 2.43E-11 0.000

ng/dscm 2.99E-02 2.07E-02 2.50E-02 0.025

ng/dscm@7%O2 3.48E-02 2.39E-02 2.82E-02 0.029

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000595 0.00000041 0.000000424 0.000

Elb/hr 2.26E-08 1.65E-08 1.71E-08 0.000

lb/mmBtuO2 6.03E-11 4.62E-11 4.62E-11 0.000

ng/dscm 6.01E-02 4.63E-02 4.76E-02 0.051

ng/dscm@7%O2 6.99E-02 5.35E-02 5.36E-02 0.059

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.00000011 0.0000000652 0.0000000795 0.000

Elb/hr 4.18E-09 2.62E-09 3.20E-09 0.000

lb/mmBtuO2 1.11E-11 7.34E-12 8.67E-12 0.000

ng/dscm 1.11E-02 7.37E-03 8.92E-03 0.009

ng/dscm@7%O2 1.29E-02 8.51E-03 1.01E-02 0.011

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000371 0.0000000315 0.0000000269 0.000

Elb/hr 1.41E-09 1.27E-09 1.08E-09 0.000

lb/mmBtuO2 3.76E-12 3.55E-12 2.93E-12 0.000

ng/dscm 3.75E-03 3.56E-03 3.02E-03 0.003

ng/dscm@7%O2 4.36E-03 4.11E-03 3.40E-03 0.004

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000155 0.00000103 0.00000112 0.000

Elb/hr 5.89E-08 4.15E-08 4.51E-08 0.000

lb/mmBtuO2 1.57E-10 1.16E-10 1.22E-10 0.000

ng/dscm 1.57E-01 1.16E-01 1.26E-01 0.133

ng/dscm@7%O2 1.83E-01 1.34E-01 1.42E-01 0.153

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000283 0.00000000893 0.0000000227 0.000

Elb/hr 1.07E-09 3.60E-10 9.15E-10 0.000

Thursday, February 17, 2011 Page 13 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

lb/mmBtuO2 2.87E-12 1.01E-12 2.48E-12 0.000

ng/dscm 2.86E-03 1.01E-03 2.55E-03 0.002

ng/dscm@7%O2 3.33E-03 1.17E-03 2.87E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000013 0.00000000212 0.00000000102 0.000

Elb/hr 4.94E-11 8.54E-11 4.11E-11 0.000

lb/mmBtuO2 1.32E-13 2.39E-13 1.11E-13 0.000

ng/dscm 1.31E-04 2.40E-04 1.14E-04 0.000

ng/dscm@7%O2 1.52E-04 2.77E-04 1.28E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000852 0.00000000971 0.0000000046 0.000

Elb/hr 3.24E-10 3.91E-10 1.85E-10 0.000

lb/mmBtuO2 8.63E-13 1.09E-12 5.02E-13 0.000

ng/dscm 8.61E-04 1.10E-03 5.16E-04 0.001

ng/dscm@7%O2 1.00E-03 1.27E-03 5.81E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000026 0.00000000224 0.00000000136 0.000

Elb/hr 9.87E-11 9.02E-11 5.48E-11 0.000

lb/mmBtuO2 2.63E-13 2.52E-13 1.48E-13 0.000

ng/dscm 2.63E-04 2.53E-04 1.53E-04 0.000

ng/dscm@7%O2 3.06E-04 2.92E-04 1.72E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000194 0.0000000176 0.00000000853 0.000

Elb/hr 7.37E-10 7.09E-10 3.44E-10 0.000

lb/mmBtuO2 1.96E-12 1.98E-12 9.30E-13 0.000

ng/dscm 1.96E-03 1.99E-03 9.57E-04 0.002

ng/dscm@7%O2 2.28E-03 2.30E-03 1.08E-03 0.002

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000000862 0.00000000844 0.0000000087 0.000

Elb/hr 3.27E-10 3.40E-10 3.51E-10 0.000

lb/mmBtuO2 8.73E-13 9.50E-13 9.49E-13 0.000

ng/dscm 8.71E-04 9.54E-04 9.76E-04 0.001

ng/dscm@7%O2 1.01E-03 1.10E-03 1.10E-03 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.00000000834 0.00000000695 0.00000000596 0.000

Elb/hr 3.17E-10 2.80E-10 2.40E-10 0.000

Thursday, February 17, 2011 Page 14 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

lb/mmBtuO2 8.45E-13 7.82E-13 6.50E-13 0.000

ng/dscm 8.42E-04 7.85E-04 6.69E-04 0.001

ng/dscm@7%O2 9.79E-04 9.07E-04 7.54E-04 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000000973 0.0000000706 0.0000000462 0.000

Elb/hr 3.70E-09 2.84E-09 1.86E-09 0.000

lb/mmBtuO2 9.85E-12 7.95E-12 5.04E-12 0.000

ng/dscm 9.83E-03 7.98E-03 5.18E-03 0.008

ng/dscm@7%O2 1.14E-02 9.22E-03 5.84E-03 0.009

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.00000000588 0.00000000602 0.00000000589 0.000

Elb/hr 2.23E-10 2.42E-10 2.37E-10 0.000

lb/mmBtuO2 5.96E-13 6.78E-13 6.42E-13 0.000

ng/dscm 5.94E-04 6.80E-04 6.61E-04 0.001

ng/dscm@7%O2 6.91E-04 7.86E-04 7.45E-04 0.001

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000284 0.0000000166 0.0000000315 0.000

Elb/hr 1.08E-09 6.68E-10 1.27E-09 0.000

lb/mmBtuO2 2.88E-12 1.87E-12 3.44E-12 0.000

ng/dscm 2.87E-03 1.88E-03 3.53E-03 0.003

ng/dscm@7%O2 3.34E-03 2.17E-03 3.98E-03 0.003

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000824 0.00000000862 0.00000000849 0.000

Elb/hr 3.13E-10 3.47E-10 3.42E-10 0.000

lb/mmBtuO2 8.35E-13 9.71E-13 9.26E-13 0.000

ng/dscm 8.32E-04 9.74E-04 9.53E-04 0.001

ng/dscm@7%O2 9.67E-04 1.13E-03 1.07E-03 0.001

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000824 0.00000000389 0.00000000825 0.000

Elb/hr 3.13E-10 1.57E-10 3.32E-10 0.000

lb/mmBtuO2 8.35E-13 4.38E-13 9.00E-13 0.000

ng/dscm 8.32E-04 4.40E-04 9.26E-04 0.001

ng/dscm@7%O2 9.67E-04 5.08E-04 1.04E-03 0.001

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000612 0.00000000393 0.00000000593 0.000

Elb/hr 2.32E-10 1.58E-10 2.39E-10 0.000

Thursday, February 17, 2011 Page 15 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

lb/mmBtuO2 6.20E-13 4.42E-13 6.47E-13 0.000

ng/dscm 6.18E-04 4.44E-04 6.65E-04 0.001

ng/dscm@7%O2 7.18E-04 5.13E-04 7.49E-04 0.001

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000244 0.00000000235 0.0000000027 0.000

Elb/hr 9.27E-11 9.46E-11 1.09E-10 0.000

lb/mmBtuO2 2.47E-13 2.65E-13 2.94E-13 0.000

ng/dscm 2.46E-04 2.66E-04 3.03E-04 0.000

ng/dscm@7%O2 2.86E-04 3.07E-04 3.41E-04 0.000

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000124 0.0000000188 0.0000000105 0.000

Elb/hr 4.71E-10 7.57E-10 4.23E-10 0.000

lb/mmBtuO2 1.26E-12 2.12E-12 1.15E-12 0.000

ng/dscm 1.25E-03 2.12E-03 1.18E-03 0.002

ng/dscm@7%O2 1.45E-03 2.45E-03 1.33E-03 0.002

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000236 0.00000000219 0.00000000164 0.000

Elb/hr 8.96E-11 8.82E-11 6.61E-11 0.000

lb/mmBtuO2 2.39E-13 2.47E-13 1.79E-13 0.000

ng/dscm 2.38E-04 2.47E-04 1.84E-04 0.000

ng/dscm@7%O2 2.77E-04 2.85E-04 2.07E-04 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000441 0.0000000544 0.0000000278 0.000

Elb/hr 1.67E-09 2.19E-09 1.12E-09 0.000

lb/mmBtuO2 4.47E-12 6.12E-12 3.03E-12 0.000

ng/dscm 4.45E-03 6.15E-03 3.12E-03 0.005

ng/dscm@7%O2 5.17E-03 7.10E-03 3.52E-03 0.005

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000026 0.00000000224 0.00000000136 0.000

Elb/hr 9.87E-11 9.02E-11 5.48E-11 0.000

lb/mmBtuO2 2.63E-13 2.52E-13 1.48E-13 0.000

ng/dscm 2.63E-04 2.53E-04 1.53E-04 0.000

ng/dscm@7%O2 3.06E-04 2.92E-04 1.72E-04 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000159 0.000000134 0.0000000682 0.000

Elb/hr 6.04E-09 5.39E-09 2.75E-09 0.000

Thursday, February 17, 2011 Page 16 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Process Run Data

lb/mmBtuO2 1.61E-11 1.51E-11 7.44E-12 0.000

ng/dscm 1.61E-02 1.51E-02 7.65E-03 0.013

ng/dscm@7%O2 1.87E-02 1.74E-02 8.62E-03 0.015

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.00000004894 0.00000003397 0.0000000512 0.000

Elb/hr 1.86E-09 1.37E-09 2.06E-09 0.000

lb/mmBtuO2 4.96E-12 3.82E-12 5.58E-12 0.000

ng/dscm 4.94E-03 3.84E-03 5.75E-03 0.005

ng/dscm@7%O2 5.74E-03 4.44E-03 6.48E-03 0.006

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.00000023546 0.00000022428 0.00000012846 0.000

Elb/hr 8.94E-09 9.03E-09 5.18E-09 0.000

lb/mmBtuO2 2.38E-11 2.53E-11 1.40E-11 0.000

ng/dscm 2.38E-02 2.53E-02 1.44E-02 0.021

ng/dscm@7%O2 2.77E-02 2.92E-02 1.62E-02 0.024

Thursday, February 17, 2011 Page 17 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Residual Oil Burned 1000 Gallons/million BTU using O2 2251.9 0 Method 23 Run1

1 Average Heat Inpt 374.8 Million Btu/hr 0

1 Average Steam Output 312.7 1000 lb steam/hr 0

2 Residual Oil Burned 1000 Gallons/million BTU using O2 2306 0 Method 23 Run 2

2 Average Heat Inpt 357.4 Million Btu/hr 0

2 Average Steam Output 312.7 1000 lb steam/hr 0

3 Residual Oil Burned 1000 Gallons/million BTU using O2 2310.1 0 Method 23 Run 3

3 Average Heat Inpt 369.3 Million Btu/hr 0

3 Average Steam Output 312.6 1000 lb steam/hr 0

Run Name Value UOM Comments

Target

Value

1 NA 0 0

Run Name Value UOM Comments

1 Ash Content 0 Percent

1 Sulfur Content 0 Percent

1 BTU Content 0 BTU

1 Carbon Content 0 Percent

1 Hyrdrogen Content 0 Precent

1 Nitrogen Content 0 Present

Thursday, February 17, 2011 Page 18 of 19
Progress Energy Florida Suwannee River Power Plant Unit 2

9/3/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 6/15/2010 6/21/2010 6/22/2010

Run Start Time 2:25:00 PM 9:29:00 PM 8:44:00 AM

Run Finish Time 10:40:00 PM 9:29:00 PM 5:11:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.223 0.218 0.218 0.220

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.015 1.015 1.015 1.015

Barometric Pressure, inches of Mercury 29.92 29.93 30.03 29.960

Average Orifice Meter Differential, inches H2O 1.89 1.55 1.59 1.677

Dry Gas Meter Volume Sampled, cubic feet 364.905 323.827 325.951 338.228

Average Dry Gas Meter Temperature, °F 101.85 97.54 99.19 99.527

Dry Gas Meter Volume Sampled, dscf 349.681 312.560 314.756 325.666

Total Moisture Liquid collected, g 500.1 539.4 573 537.500

Volume of Water Vapor, standard cubic feet 23.54 25.39 26.97 25.300

Moisture Content of Stack Gas, % 6.31 7.51 7.89 7.237

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9369 0.9249 0.9211 0.928

Carbon Dioxide, % 10.165 9.859 10.248 10.091

Oxygen, % 8.944 8.867 8.564 8.792

Carbon Monoxide & Nitrogen, % 80.891 81.274 81.188 81.118

Fuel Factor 1.18 1.22 1.20

Dry Molecular Weight, lb/lb-Mole 29.98 29.93 29.98 29.963

Wet Molecular weight, lb/lb-Mole 29.22 29.03 29.03 29.093

Flue Gas Static Pressure, inches of H2O 0.4 0.44 0.38 0.407

Absolute Flue Gas Pressure, inches of Mercury 29.95 29.96 30.06 29.990

Average Stack Gas Temperature, °F 320.17 324.21 317.92 320.767

Average Velocity Head, inches of H2O 1.0675869796

6159

0.981916302

217567

0.994717820

700524

1.015

Average Stack Gas Velocity, feet/second 70.06 67.57 67.62 68.417

Stack Cross-Sectional Area, square feet 37.631 37.631 37.631 37.631

Dry Volumetric Flow Rate, dry scfm 100,401.5 95,132.2 95,897.1 97,143.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 158,185.7 152,563.6 152,676.5 154,475.267

Percent Isokinetic of Sampling Rate, % 100.7 99.4 99.3 99.800

Percent Excess Air, % 72.1 70.4 66.5 69.667

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 83.063 83.063 83.063

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 17, 2011 Page 19 of 19