Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

1606 1606 Mt. Tom Generating Company FirstLight Power Resources Services, LLC legal owner , LLC200 Northampton Street Holyoke MA 01040

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

Mount Tom200 Northampton Street Holyoke MA 01040 200 Northampton Street Holyoke MA 01040

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

No TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE FALSE Title V semi annual and annual reporting Yes other than Hg is reported through ECMPS to EPA (Region 1 Boston) No analysis provided for oil shipments because we have no data on H

Page 4
Facility_Information

ments because we have no data on HAPS or trace metals in oil (per guidance from RTI)RE coal shipments and analyses: analysis sup

Page 5
Facility_Information

hipments and analyses: analysis supplier and lab are same for shipments 1-5, remainder of shipments have no trace elements or HAP anal

Page 6
Facility_Information

have no trace elements or HAP analyses. Copies of coal analyses are not being provided with the ICR per guidance from J. Cole at RTI. All 

Page 7
Facility_Information

per guidance from J. Cole at RTI. All available, requested coal analysis data is entered in the ICR. 4 ports identified are in stack after a

Page 8
Facility_Information

4 ports identified are in stack after all controls ~150 ft above gradeStack velocity (68 ft/sec) is average of 12, flow-RATA runs in high loa

Page 9
Facility_Information

ge of 12, flow-RATA runs in high load range (measured in 2009)RE Unit control technology demonstrations: Turbosorp dry flue ga

Page 10
Facility_Information

emonstrations: Turbosorp dry flue gas desulfurization unit, for Hg and SO2 control, installed late in 2009 and is still undergoing commissionin

Page 11
Facility_Information

 and is still undergoing commissioning, O&M figure is as budgeted for 2010 (NOT 2009) and may not be representative of annual cost given 

Page 12
Facility_Information

e representative of annual cost given age of system.Notes re Emission test results:1) Flue gas flow for test results is SCFM wet

Page 13
Facility_Information

s flow for test results is SCFM wet2) Test of Oct 2005 was prior to SCR installa

Page 14
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

1606 1 Station Services Manager Richard Merchant 4135369563 richard.merchant@gdfsuezna.com TRUE

1606 2 EHS Specialist Milon Harris4135369571 milton.harris@gdfsuezna.com FALSE

Page 15
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

1606 bituminous 100 100 distillate oil used for start up only and not power generation

Page 16
facility_coal_utilized

 and not power generation

Page 17
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

1606 No.2 Fuel Oil (distillate) 100 100

Page 18
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

Page 19
facility_other_materials

rcra_explain

Page 20
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

1606 1 Wall firing - front firing Dry Bottomcoal 1480 1480 155

Page 21
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

143.6 89 89 2150 1950 1000 1000 FALSE 1000

Page 22
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 1000 7390 70.7 N TRUE

Page 23
boiler_information

NOx_controlSO2_controlcombustion_additives

Yes No No

Page 24
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

1606 1 coal - bituminous2007 100 100

1606 1 coal - bituminous2008 100 100

1606 1 coal - bituminous2009 100 100

Page 25
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

1606 1 Low NOx Burner 1/1/1995

Page 26
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

Page 27
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

Page 28
facility_units

facility_id unit_id

1606 1

Page 29
unit_boilers

facility_id unit_id boiler_id

1606 1 1

Page 30
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

1606 BH1 PM control Fabric Filter, pulse FALSE 12/1/2009

1606 ESP1 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 9/1/1982

1606 SCR1 NOx controlSelective Catalytic Reduction FALSE 6/1/2006 Ammonia

1606 TS1 SO2 controlCirculating Dry ScrubberFALSE 12/1/2009

Page 31
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

19

Lime yes

Page 32
facility_sampling_ports

facility_id sampling_port_id

1606 P1

1606 P2

1606 P3

1606 P4

Page 33
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

1606 STK1 370 13 68

Page 34
configurations

facility_id configuration_id

1606 1 current

Page 35
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

1606 1 current 1 1 Unit

1606 1 current BH1 5 PM control

1606 1 current ESP1 3 PM control

1606 1 current SCR1 2 NOx control

1606 1 current STK1 6 Stack

1606 1 current TS1 4 SO2 control

Page 36
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

1606 1 current Total Suspended Particulates (TSP) Federal - Title V Operating Permit 0.08 pound per million British Thermal Unit (lb/MMBtu) Continuous

1606 1 current Sulfur Dioxide (SO2) Federal - Title V Operating Permit 0.006 pound per Gigawatt hour (lb/GW 30 days h)

1606 1 current Total MercuryFederal - Title V Operating Permit (Hgt) 0.0075 pound per Gigawatt hour (lb/GW 24 hours h)

1606 1 current Carbon Monoxide (CO) Federal - Title V Operating Permit 200 parts per million by 24 hours volume (dry) (ppmvd)

1606 1 current Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.45 pound per million British Thermal Unit (lb/MMBtu) 24 hours

Page 37
configuration_pollutants1

avg_period_2emlimit_3 emlimit_units_3 avg_period_3emlimit_4 emlimit_units_4 avg_period_4emlimit_details test_method

SO2 limits are:3 lb/MWh as 12-month rollin

Hg limit is based upon State regulation: 0.0075 

NOx limit is 1.5 lb/MWh 12-month rolling avera

Page 38
configuration_pollutants1

emrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping req_reporting

0.04 pound per million British Thermal Unit (lb/MMBtu) No actual guarantee Recordkeeping, Title V Table 5:24) In accordance with approval 1

0.006 pound per Gigawatt hour (lb/GW No guaranteed min 95% reduction, 24 hr average measured at CEM and corrected to 3% O2 anh)Monitoring, Title V, Table 4:5) In accordance with the Acid Rain Program 40 CRecordkeeping, Title V, Table 5:1) In accordance with 40 CFR PaReporting, Title V Table 6:3) In accordance with Depa

0.0075 pound per Gigawatt hour (lb/GW Yes vendor would not guarantee, guaranteed rate entered to satisfy h)Monitoring Requirements, Title V, Table 4:26) In accordance with 310 CMR 7 completeness requirements 

200 parts per million by No volumno guaranteed rate, value entered to satisfy e (dry) (ppmvd) Monitoring, Title V Table 4:2) In accordance with Approval No. 1-B-94-011, th completeness requirement of ICR 

0.06 pound per million British Thermal Unit (lb/MMBtu) No less than or = 0.060 lb/MMBtu, 24-hr average

Page 39
configuration_pollutants1

24) In accordance with approval 1-P-05-031, Mt. Tom shall generate monthly reports in-house that document fuel use and compliance wit

ble 6:3) In accordance with Department Approval No. 1-B-90-099, MT. TOM shall submit SO2 emission reports for each calendar quarter 

26) In accordance with 310 CMR 7.29(5)(a)3.g.i, by January 1, 2008, Mt. Tom shall install, certify, and operate a Hg CEMS. Mt. Tom shall

nce with Approval No. 1-B-94-011, the programmable logic controller serving the CEMS shall be programmed to obtain readings from the NO

Page 40
configuration_pollutants1

ocument fuel use and compliance with the 12% per cargo and 9% per 12 rolling month ash limits. If any limits are exceeded, Mt. Tom shall n

on reports for each calendar quarter to verify compliance with the Massachusetts Acid Rain Law, 310 CMR 7.22. Said reports shall be subm

 operate a Hg CEMS. Mt. Tom shall:(i) submit a preliminary CEMS monitoring plan for Department approval at least 180 days prior to eq

mmed to obtain readings from the NOx and CO monitor at least every 10 seconds and compute 15-minute block averages as well as one ho

Page 41
configuration_pollutants1

 limits are exceeded, Mt. Tom shall notify the Department in writing no later than the 15th day of the following month.25) In accordance w

MR 7.22. Said reports shall be submitted by the 30th day of April, July, October, and January covering the previous calendar periods of Jan

approval at least 180 days prior to equipment installation;(ii) include the following information in the preliminary CEMS monitoring plan: so

te block averages as well as one hour averages as specified by 310 CMR 7.19(13)(b)9. Mt. Tom shall calculate the NOx emission rate usin

Page 42
configuration_pollutants1

wing month.25) In accordance with approval 1-P-05-031, Mt. Tom shall maintain coal certification, including coal supplier and % ash per 

the previous calendar periods of January through March, April through June, July through September, and October through December, resp

reliminary CEMS monitoring plan: source identification, source description, control technology description, the applicable regulations, the typ

calculate the NOx emission rate using the procedures specified in 40 CFR Part 75 Appendix F, Conversion Procedures.3) In accordance 

Page 43
configuration_pollutants1

ncluding coal supplier and % ash per shipment, and coal purchase records at the facility. These records shall be kept on site for five (5) year

nd October through December, respectively. For each fuel utilization facility that is part of the acid rain control plan, said reports shall contai

n, the applicable regulations, the type of monitor, a monitoring system flow diagram, a description of the data handling system, and a sample 

ion Procedures.3) In accordance with 310 CMR 7.19(13)(b)10., Mt. Tom shall operate its CEMS at all times that the emission unit is ope

Page 44
configuration_pollutants1

 shall be kept on site for five (5) years from date of record and shall be made available to the Department upon request.

control plan, said reports shall contain a monthly summary and a calendar year to date summary of:a.the type(s) of fuel burned;b.th

 data handling system, and a sample calculation demonstrating compliance with the emission limits using conversion factors from 40 CFR P

ll times that the emission unit is operating except for periods of CEMS calibration checks, zero span adjustment, reasonable maintenance, a

Page 45
configuration_pollutants1

nt upon request.

.the type(s) of fuel burned;b.the quantity of each fuel (gallons, tons, or cubic feet), the sulfur content of each fuel (pounds per million B

ng conversion factors from 40 CFR Part 60 or Part 75 or other proposed factors;(iii) submit for Department approval a CEMS certification 

ustment, reasonable maintenance, and periods of unexpected and unavoidable failure of the equipment. Notwithstanding such exceptions, 

Page 46
configuration_pollutants1

ent of each fuel (pounds per million Btu and percent by weight); and c.the average heating value (Btu per gallon, ton, or cubic foot) of e

tment approval a CEMS certification protocol at least 90 days prior to certification testing for the CEMS, and any proposed adjustment to the 

. Notwithstanding such exceptions, in all cases Mt. Tom shall obtain valid data for at least 75% of the hours per day, 75% of the days per m

Page 47
configuration_pollutants1

Btu per gallon, ton, or cubic foot) of each fuel burned.

 and any proposed adjustment to the certification testing at least seven days in advance; (iv) include the following information in the certif

ours per day, 75% of the days per month, and 90% of the hours per quarter during which the emission unit is operating. This requirement a

Page 48
configuration_pollutants1

the following information in the certificatio

unit is operating. This requirement applies to the monitoring of CO emissio

Page 49
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

1606 1 current TS1 1 Turbosorp DFGD Non-Demonstration Babcock Power, Inc. Daniel Douthright 5088543812

Page 50
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

5 Neponset St Worcester MA 01606 ######## powdered activated carbon or BPAC

Page 51
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

upstream of reactor and after ESP 90 2.5E-06 lb/MWh 95 5 lb/MMACF

Page 52
control_technologies

feed_rate_units

Page 53
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

1606 1 current TS1 1 bituminous

Page 54
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

1606 1 current TS1 1 Total Mercury (Hgt)

Page 55
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

1606 1 current TS1 1 Yes No 54000000 3600000 2009

Page 56
control_costs

CBI

FALSE

Page 57
misc_controls

facility_id misc_control_id control_description

1606 1 Emission controls include the following: use of low sulfur & low ash coal, SCR with ammonia injection fo

Page 58
misc_controls

coal, SCR with ammonia injection for NOx, ESP for particulate control, Turbosorp dry flue gas desulfurization system followed by a finishing 

Page 59
misc_controls

zation system followed by a finishing baghouse for PM control.

Page 60
misc_control_configurations

facility_id misc_control_id configuration_id

1606 1 1 current

Page 61
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

1606 1 1/1/2009 38807 short tons (2000 lbs) coal Other Colombia

1606 2 3/1/2009 35670 short tons (2000 lbs) coal Other Colombia

1606 3 4/1/2009 38400 short tons (2000 lbs) coal Other Colombia

1606 4 4/1/2009 39424 short tons (2000 lbs) coal Other Colombia

1606 5 7/1/2009 40115 short tons (2000 lbs) coal Other Colombia

1606 6 7/1/2009 7602 short tons (2000 lbs) coal WV

1606 7 8/1/2009 7715 short tons (2000 lbs) coal PA

1606 8 9/1/2009 7683 short tons (2000 lbs) coal PA

Page 62
fuel_shipments

coal_seam shipment_method

Barge

Barge

Barge

Barge

Barge

Pittsburgh Unit Train

Unit Train

Unit Train

Page 63
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

1606 1 1 current

1606 2 1 current

1606 3 1 current

1606 4 1 current

1606 5 1 current

1606 6 1 current

1606 7 1 current

1606 8 1 current

Page 64
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

1606 1 1 0.43 6.95 11369 Btu/lb

1606 2 1 0.46 7.72 11187 Btu/lb

1606 3 1 0.44 6.54 11511 Btu/lb

1606 4 1 0.49 7.92 11346 Btu/lb

1606 5 1 0.71 6.4 12196 Btu/lb

1606 6 1 3.09 8.75 13334 Btu/lb

1606 7 1 2.06 8.62 13994 Btu/gal

1606 8 1 2.13 8.73 13904 Btu/lb

Page 65
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

0.03 percent (dry) (%) contractual obligations Fuel supplierGlencore, LTD301 Tresser Blvd

0.03 percent (dry) (%) contractual obligations Fuel supplier

0.03 percent (dry) (%) contractual obligations Fuel supplier

0.03 percent (dry) (%) contractual obligations Fuel supplier

0.03 percent (dry) (%) contractual obligations Fuel supplier

contractual obligations Fuel supplier

contractual obligations Fuel supplier

contractual obligations Fuel supplier

Page 66
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Stamford CT 06901 Incolab Services Colombia LTDA. Km 2-25 Troncal del Caribe Via a Gaira Santa Marta, Magdalena, ColombiaNo

No

No

No

No

No

No

No

Page 67
fuel_shipment_samples

analysis_copies

Page 68
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

1606 1 1 Arsenic (As) parts per million (dry TRUE ) (ppm) 4

1606 1 1 Beryllium (Be) parts per million (dry TRUE ) (ppm) 2

1606 1 1 Cadmium (Cd) parts per million (dry TRUE ) (ppm) 2

1606 1 1 Chromium (Cr) 7 parts per million (dry FALSE) (ppm)

1606 1 1 Lead (Pb) 3 parts per million (dry TRUE ) (ppm) 4

1606 1 1 Manganese (Mn) 39 parts per million (dry FALSE) (ppm)

1606 1 1 Nickel (Ni) 7 parts per million (dry FALSE) (ppm)

1606 1 1 Selenium (Se) 3 parts per million (dry TRUE ) (ppm) 4

1606 2 1 Arsenic (As) parts per million (dry TRUE ) (ppm) 5

1606 2 1 Beryllium (Be) parts per million (dry TRUE ) (ppm) 2

1606 2 1 Cadmium (Cd) parts per million (dry TRUE ) (ppm) 2

1606 2 1 Chromium (Cr) 12 parts per million (dry FALSE) (ppm)

1606 2 1 Lead (Pb) parts per million (dry TRUE ) (ppm) 5

1606 2 1 Manganese (Mn) 63 parts per million (dry FALSE) (ppm)

1606 2 1 Mercury (Hg) 0.054 parts per million (dry FALSE) (ppm)

1606 2 1 Nickel (Ni) 10 parts per million (dry FALSE) (ppm)

1606 2 1 Selenium (Se) parts per million (dry TRUE ) (ppm) 5

1606 3 1 Arsenic (As) parts per million (dry TRUE ) (ppm) 5

1606 3 1 Beryllium (Be) parts per million (dry TRUE ) (ppm) 2

1606 3 1 Cadmium (Cd) parts per million (dry TRUE ) (ppm) 2

1606 3 1 Chromium (Cr) 11 parts per million (dry FALSE) (ppm)

1606 3 1 Lead (Pb) parts per million (dry TRUE ) (ppm) 4

1606 3 1 Manganese (Mn) 41 parts per million (dry FALSE) (ppm)

1606 3 1 Mercury (Hg) 0.06 parts per million (dry FALSE) (ppm)

1606 3 1 Nickel (Ni) 10 parts per million (dry FALSE) (ppm)

1606 3 1 Selenium (Se) parts per million (dry TRUE ) (ppm) 4

1606 4 1 Arsenic (As) parts per million (dry TRUE ) (ppm) 4

1606 4 1 Beryllium (Be) parts per million (dry TRUE ) (ppm) 2

1606 4 1 Cadmium (Cd) parts per million (dry TRUE ) (ppm) 2

1606 4 1 Chromium (Cr) 14 parts per million (dry FALSE) (ppm)

1606 4 1 Lead (Pb) parts per million (dry TRUE ) (ppm) 4

1606 4 1 Manganese (Mn) 35 parts per million (dry FALSE) (ppm)

1606 4 1 Mercury (Hg) 0.052 parts per million (dry FALSE) (ppm)

1606 4 1 Nickel (Ni) 14 parts per million (dry FALSE) (ppm)

1606 4 1 Selenium (Se) parts per million (dry TRUE ) (ppm) 4

1606 5 1 Arsenic (As) 5 parts per million (dry FALSE) (ppm)

1606 5 1 Beryllium (Be) parts per million (dry TRUE ) (ppm) 2

1606 5 1 Cadmium (Cd) parts per million (dry TRUE ) (ppm) 2

1606 5 1 Chromium (Cr) 8 parts per million (dry FALSE) (ppm)

1606 5 1 Lead (Pb) parts per million (dry TRUE ) (ppm) 4

1606 5 1 Manganese (Mn) 28 parts per million (dry FALSE) (ppm)

1606 5 1 Mercury (Hg) 0.055 parts per million (dry FALSE) (ppm)

1606 5 1 Nickel (Ni) 8 parts per million (dry FALSE) (ppm)

1606 5 1 Selenium (Se) parts per million (dry TRUE ) (ppm) 4

Page 69
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

1606 Hg CEM certification 2008 compliance as above ######## ######## No No

1606 Hg CEMS certification 2009 compliance as above 12/7/2009 ######## No No

1606 Hg emissions 2006 other company initiated ######## No No

1606 Hg emissions Jan. 2007 compliance 1/23/2007 1/25/2007 No No

1606 Hg emissions Sept 2007 compliance 9/5/2007 No No

1606 Jan 2008 initial Hg CEMS certification compliance as above 1/24/2008 2/5/2008 No No

1606 Oct 2006 compliance compliance ######## ######## No No

1606 Turbosorp - initial compliance test compliance demonstration of control efficiencies and compliance with emission limits ######## No No

Page 70
test_reports

deviation_reports

No

No

No

No

No

No

No

No

Page 71
test_report_configurations

facility_id report_id configuration_id

1606 Hg CEM certification 2008 1 current

1606 Hg CEMS certification 2009 1 current

1606 Hg emissions Sept 2007 1 current

1606 Jan 2008 initial Hg CEMS certification 1 current

1606 Turbosorp - initial compliance test 1 current

Page 72
test_report_fuels

facility_id report_id fuel_id

1606 Hg CEM certification 2008 coal

1606 Hg CEMS certification 2009 coal

1606 Hg emissions 2006 coal

1606 Hg emissions Jan. 2007 coal

1606 Hg emissions Sept 2007 coal

1606 Jan 2008 initial Hg CEMS certification coal

1606 Oct 2006 compliance coal

1606 Turbosorp - initial compliance test coal

Page 73
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

1606 Hg CEM certification 2008 coal coal - bituminous 100 100

1606 Hg CEMS certification 2009 coal coal - bituminous 100 100

1606 Hg emissions 2006 coal coal - bituminous 100 100

1606 Hg emissions Jan. 2007 coal coal - bituminous 100 100

1606 Hg emissions Sept 2007 coal coal - bituminous 100 100

1606 Jan 2008 initial Hg CEMS certification coal coal - bituminous 100 100

1606 Oct 2006 compliance coal coal - bituminous 100 100

1606 Turbosorp - initial compliance test coal coal - bituminous 100 100

Page 74
cem_data

facility_id time_periodcem_period_description

1606 01/25/2008 to present Hg CEM certified Jan. 2008 as required by Mass. DEP

Page 75
cem_data_pollutants1

facility_id time_periodpollutant_name

1606 01/25/2008 to present Total Mercury (Hgt)

Page 76
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

1606 Hg CEM certification 2008 STK1 No No

1606 Hg CEMS certification 2009 STK1 No No

1606 Hg emissions 2006 STK1 No No

1606 Hg emissions Jan. 2007 STK1 No No

1606 Hg emissions Sept 2007 STK1 No No

1606 Jan 2008 initial Hg CEMS certification STK1 No No

1606 Oct 2006 compliance STK1 No No

1606 Turbosorp - initial compliance test STK1 No No

Page 77
test_report_sampling

fg_fraction

Page 78
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

1606 Hg CEM certification 2008 STK1 average ######## ######## 149 139

1606 Hg CEMS certification 2009 STK1 average 12/7/2009 ######## 148 135

1606 Hg emissions 2006 STK1 average ######## ########

1606 Hg emissions Jan. 2007 STK1 average 1/23/2007 1/25/2007 150

1606 Hg emissions Sept 2007 STK1 average 9/5/2007 9/5/2007

1606 Jan 2008 initial Hg CEMS certification STK1 average 1/24/2008 2/5/2008 149 139 6.3

1606 Oct 2006 compliance STK1 average ######## ######## 145 135 7.5

1606 Turbosorp - initial compliance test STK1 1 1/20/2009 1/20/2009 155 143

1606 Turbosorp - initial compliance test STK1 2 1/20/2009 1/20/2009 155 143

1606 Turbosorp - initial compliance test STK1 3 1/19/2009 1/19/2009 155 143

1606 Turbosorp - initial compliance test STK1 4 1/20/2009 1/20/2009 155 143

Page 79
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

68 29.92

68 29.92

68 29.92

444000 dscfm 68 29.92 7.7 11.8 298

7.73 11.79

7.684 11.818

11.941

11.701

Page 80
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

30.03

coal 155 8.95 13266

coal 155 8.6 13366

Page 81
sampling_runs

fuel_sulfur

1.16

1.58

Page 82
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

1606 Hg emissions 2006 STK1 average Total Mercury (Hgt)1.92 microgram per dry FALSE standard cubic meter (

1606 Hg emissions Jan. 2007 STK1 average Total Mercury (Hgt) 1.796 microgram per dry FALSE standard cubic meter (

1606 Hg emissions Sept 2007 STK1 average Total Mercury (Hgt) 2.407 microgram per dry FALSE standard cubic meter (

1606 Hg emissions Sept 2007 STK1 average Particulate-bound Mercury 0.03 microgram per dry (Hgp) FALSE standard cubic meter (

1606 Jan 2008 initial Hg CEMS certification STK1 average Total Mercury (Hgt)1.43 microgram per dry FALSE standard cubic meter (

1606 Hg CEM certification 2008 STK1 average Total Mercury (Hgt) 1.829 microgram per dry FALSE standard cubic meter (

1606 Hg CEMS certification 2009 STK1 average Total Mercury (Hgt)0.17 microgram per dry FALSE standard cubic meter (

1606 Turbosorp - initial compliance test STK1 1 Total Suspended Particulates (TSP)FALSE

1606 Turbosorp - initial compliance test STK1 1 PM (Filterable) FALSE

1606 Turbosorp - initial compliance test STK1 1 PM (Condensable) FALSE

1606 Turbosorp - initial compliance test STK1 2 Sulfur Dioxide (SO2) 26.08 parts per million by FALSE volume (dry) (ppmvd)

1606 Turbosorp - initial compliance test STK1 3 Total Mercury (Hgt) 0.096 microgram per dry FALSE standard cubic meter (

1606 Turbosorp - initial compliance test STK1 4 Total Mercury (Hgt) 0.022 microgram per dry FALSE standard cubic meter (

1606 Oct 2006 compliance STK1 average PM (Filterable) FALSE

1606 Oct 2006 compliance STK1 average PM (Condensable) FALSE

1606 Oct 2006 compliance STK1 average Nitrogen Oxide (NOx) FALSE

1606 Oct 2006 compliance STK1 average Sulfur Dioxide (SO2) FALSE

1606 Oct 2006 compliance STK1 average Carbon Monoxide (CO) 150 parts per million by FALSE volume (dry) (ppmvd)

Page 83
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

FALSE 1.86 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

FALSE 1.726 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

FALSE 2.247 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

FALSE 0.025 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

FALSE FALSE

FALSE FALSE

FALSE FALSE

FALSE 0.0059 pound per million British Thermal Unit (lb/MMBtu) FALSE 3 run average on Jan. 20, 2010, m

FALSE 0.0055 pound per million British Thermal Unit (lb/MMBtu) FALSE 3 run average, measured in stack, 

FALSE 0.0004 pound per million British Thermal Unit (lb/MMBtu) FALSE 3 run average, measured in stack, 

FALSE 0.066 pound per million British Thermal Unit (lb/MMBtu) FALSE measured in stack, average of 3 ru

FALSE 0.09 pound per trillion British Thermal Unit (lb/1012Btu) FALSE average of 3 runs on Jan. 19, 201

FALSE 0.021 pound per trillion British Thermal Unit (lb/1012Btu) FALSE average of 3 runs, Jan. 20, 2010, m

14.6 pound per hour (lb/hr) FALSE FALSE

20.4 pound per hour (lb/hr) FALSE FALSE

FALSE 0.08 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE 0.758 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE at 3% O2

Page 84
sampling_run_pollutants1

run_pollutant_comment

3 run average on Jan. 20, 2010, measured in stack

3 run average, measured in stack, January 20, 2010

3 run average, measured in stack, Jan. 20, 2010

measured in stack, average of 3 runs on Jan. 20, 2010

average of 3 runs on Jan. 19, 2010, measured in stack, WITHOUT PAC injection

average of 3 runs, Jan. 20, 2010, measured in stack, WITH PAC injection

Page 85
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

1606 Turbosorp - initial compliance test STK1 3 Antimony (Sb) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 3 Arsenic (As) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 3 Barium (Ba) 42 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Beryllium (Be) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 3 Cadmium (Cd) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 3 Chloride (Cl) 300 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Chromium (Cr) 11 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Cobalt (Co) 3 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Copper (Cu) 8 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Lead (Pb) 5 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Manganese (Mn) 23 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Mercury (Hg) 0.06 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Molybdenum (Mo) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 3 Nickel (Ni) 10 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 3 Selenium (Se) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 3 Vanadium (V) 25 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Antimony (Sb) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 4 Arsenic (As) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 4 Barium (Ba) 34 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Beryllium (Be) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 4 Cadmium (Cd) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 4 Chloride (Cl) 400 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Chromium (Cr) 11 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Cobalt (Co) 3 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Copper (Cu) 7 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Lead (Pb) 6 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Manganese (Mn) 26 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Mercury (Hg) 0.08 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Molybdenum (Mo) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 4 Nickel (Ni) 8 parts per million (dry FALSE) (ppm)

1606 Turbosorp - initial compliance test STK1 4 Selenium (Se) parts per million (dry TRUE ) (ppm) 2

1606 Turbosorp - initial compliance test STK1 4 Vanadium (V) 24 parts per million (dry FALSE) (ppm)

Page 86
sampling_run_fuel

fuel_conc_MDL

Page 87