Dolan Chemical Laboratory 4001 Bixby Road Groveport, OH 43125 T: 614-836-4221, Audinet 210-4221 F: 614-836-4168, Audinet 210-4168 http://aepenv/labs 

### Water Analysis Form REP-703 Rev. 1, 11/2013



### Location: Amos Plant Report Date: 4/10/2014 Sample Number: 141150-001 Date Collected:04/02/2014 Date Received:4/3/2014 

### Trip Blank at 009 Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 0.64 0.5 TLT EPA 1631E-2002 0.2 04/08/2014 

### Sample Number: 141150-002 Date Collected: 04/02/2014 Date Received:4/3/2014 

### Field Blank at 009 Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 0.61 0.5 TLT EPA 1631E-2002 0.2 04/08/2014 

### Sample Number: 141150-003 Date Collected:04/03/2014 08:24 Date Received:4/3/2014 

### 003 Clarification Pond Discharge Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 6.34 2 TLT EPA 1631E-2002 0.8 04/08/2014 

### Sample Number: 141150-004 Date Collected: 04/03/2014 Date Received:4/3/2014 

### 003 Clarification Pond Discharge Duplicate Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 6.35 2 TLT EPA 1631E-2002 0.8 04/08/2014 

### Sample Number: 141150-005 Date Collected:04/02/2014 10:39 Date Received:4/3/2014 

## Quarrier Outlet #001 Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 3.30 2 TLT EPA 1631E-2002 0.8 04/09/2014 

### Sample Number: 141150-006 Date Collected: 04/02/2014 10:12 Date Received:4/3/2014 

### Quarrier Outlet #009 Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 2.51 2 TLT EPA 1631E-2002 0.8 04/09/2014 

### Sample Number: 141150-007 Date Collected:04/02/2014 Date Received:4/3/2014 

## Quarrier Outlet #009 Duplicate Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 2.33 2 TLT EPA 1631E-2002 0.8 04/09/2014 Amos Plant, 141150 Page 1 of 3

### Location: Amos Plant Report Date: 4/10/2014 Sample Number: 141150-008 Date Collected:04/02/2014 10:08 Date Received:4/3/2014 

### Quarrier Outlet #015 Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg < 0.8 2 TLT EPA 1631E-2002 0.8 04/09/2014 U 

### Sample Number: 141150-009 Date Collected: 04/03/2014 08:58 Date Received:4/3/2014 

### WWTP Inlet Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 302000 10000 TLT EPA 1631E-2002 4000 04/09/2014 

### Sample Number: 141150-010 Date Collected:04/03/2014 08:55 Date Received:4/3/2014 

## Primary Clarifier Outlet A Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 758 50 TLT EPA 1631E-2002 20 04/09/2014 

### Sample Number: 141150-011 Date Collected: 04/03/2014 08:47 Date Received:4/3/2014 

### Secondary Clarifier Outlet A Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 46.3 20 TLT EPA 1631E-2002 8 04/09/2014 

### Sample Number: 141150-012 Date Collected:04/03/2014 08:45 Date Received:4/3/2014 

## Secondary Clarifier Outlet B Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 44.1 20 TLT EPA 1631E-2002 8 04/09/2014 

### Sample Number: 141150-013 Date Collected:04/03/2014 08:49 Date Received:4/3/2014 

### WWTP Outlet Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 45.7 20 TLT EPA 1631E-2002 8 04/09/2014 

### Sample Number: 141150-014 Date Collected:04/03/2014 08:30 Date Received:4/3/2014 

## FGD Landfill Discharge to Pond Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 84.7 20 TLT EPA 1631E-2002 8 04/09/2014 

### Sample Number: 141150-015 Date Collected:04/03/2014 08:30 Date Received:4/3/2014 

### Recirculation Pond Outlet at Weir Units Parameter Result RL Analysis By Analysis Date/Time Method MDL Data Qual ng/L Mercury, Hg 4.14 1 TLT EPA 1631E-2002 0.4 04/09/2014

Amos Plant, 141150 Page 2 of 3

### Location: Amos Plant Report Date: 4/10/2014

THIS TEST REPORT RELATES ONLY TO THE ITEMS TESTED AND SHALL NOT BE REPRODUCED EXCEPT IN FULL WITHOUT WRITTEN APPROVAL OF THE LABORATORY. ALL TEST RESULTS MEET ALL OF THE REQUIREMENTS OF THE ACCREDITING AUTHORITY, UNLESS OTHERWISE NOTED. U: Analyte was analyzed and not detected at or above adjusted Method Detection Limit J: Analyte was positively identified, though the quantitation was below Reporting Limit. Brian Snyder, Chemist II Email bssnyder@aep.com Tel. 614-836-4224 Fax 614-836-4168 Audinet 210-4224

Amos Plant, 141150 Page 3 of 3