### Name: James Dudish

Title: Plant Manager Company: Gilberton Power Company Sign Date: 10/22/2010 Name: Stephen Schell Title: President Company:Air Analysis, LLC Sign Date: 10/22/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## Electricity Generating Unit ICR

Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Saturday, January 29, 2011 Page 1 of 12

### Electricity Generating Unit ICR 10/22/2010 Facility Information: John B. Rich Memorial Power Station 50 Eleanor Avenue

Frackville PA17931 Contact:James Dudish Phone:570 874 4456 Fax: 570 874 1644 Email: jdudish@culm2energy.com Testing Company: Air Analysis, LLC t/a SGF Consulting Services 189 Hausman Road

Lenhartsville PA19534 Contact:Stephen Schell Phone:610 756 3490 Fax: 610 756 3491 Email: Sschell@hughes.net

Air Permit Number: 54-00004 Permitted Source ID/Name: John B. Rich Memorial Power Station CFB1/CFB2 Permitted Maximum Process Rate:Max. Normal Operation Process Rate: 520 MMBtu/Hr Target Process Test Rate 90% of Maximum Load

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: The facility operates two circulating fluidized bed boilers used to produce steam and produce electricity from a common turbine. Each unit is rated at 520 Mmbtu/hr and fires waste anthracite coal. The exhaust from each boiler passes through an individual baghouse before entering a common stack. Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:4210700062 FRS #:110020578891

SCC / Description10102018 External Combustion Boilers - Electric Generation - Waste Coal - Circulating Fluidized Bed Combustion

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width CFB Comon Stack 102 1224 2244 2 102 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Flowrate Method 1 - 4 0 Throughout testing program CFB Comon Stack % H2O Method 1 - 4 0 During each test run CFB Comon Stack Carbon Monoxide Method 10 3 120 0 CFB Comon Stack



### Saturday, January 29, 2011 Page 2 of 12

### Electricity Generating Unit ICR 10/22/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

Custom Method 0010 3 120 0 Speciated SemiVOC HAPS CFB Comon Stack Formaldehyde Method 0011 3 120 0 CFB Comon Stack Total organic compounds

(TOC) as Propane Method 25A 3 120 0 CFB Comon Stack O2 Method 3A O2 0 During each test run CFB Comon Stack Co2 Method 3A CO2 0 During each test run CFB Comon Stack Custom Method 0031 3 120 0 Speciated VOC HAPS CFB Comon Stack Sulfur Dioxide Method 6C 3 120 0 CFB Comon Stack



### Saturday, January 29, 2011 Page 3 of 12

### Electricity Generating Unit ICR 10/22/2010 Sampling / Stack Data Results Summary 

### Location CFB Comon Stack - Method 10 Average Run Number 1 2 3 Test Date 8/3/2010 8/3/2010 8/3/2010 Run Start Time 7:10:00 AM 9:56:00 AM12:57:00 PM

Run Finish Time 9:09:00 AM 11:55:00 AM 2:58:00 PM

Carbon Dioxide, % 13.08 13.07 13.07 13.073 Oxygen, % 7.28 7.33 7.3 7.303 Dry Volumetric Flow Rate, dry scfm 279544 277980 281873 279,799.000 F-Factor, dscfm/MMBtu @ %O2 10278 10211 10275 10,254.667 Moisture, % 6.95 7.14 7.21 7.100 Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000



### Location CFB Comon Stack - Method 25A Average Run Number 1 2 3 Test Date 8/3/2010 8/3/2010 8/3/2010 Run Start Time 7:10:00 AM 9:56:00 AM12:57:00 PM

Run Finish Time 9:09:00 AM 11:55:00 AM 2:58:00 PM

Carbon Dioxide, % 7.28 13.07 13.07 11.140 Oxygen, % 13.08 7.33 7.3 9.237 Dry Volumetric Flow Rate, dry scfm 279544 277980 28487371,135,420.33 3 F-Factor, dscfm/MMBtu @ %O2 10278 10211 10275 10,254.667 Moisture, % 6.95 7.14 7.21 7.100 Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000



### Saturday, January 29, 2011 Page 4 of 12

### Electricity Generating Unit ICR 10/22/2010 Location CFB Comon Stack - Method 6C Average Run Number 1 2 3 Test Date 8/3/2010 8/3/2010 8/3/2010 Run Start Time 7:10:00 AM 9:56:00 AM12:57:00 PM

Run Finish Time 9:09:00 AM 11:55:00 AM 2:58:00 PM

Carbon Dioxide, % 13.08 13.07 13.07 13.073 Oxygen, % 7.28 7.33 7.3 7.303 Dry Volumetric Flow Rate, dry scfm 279544 277980 281.873 185,935.291 F-Factor, dscfm/MMBtu @ %O2 10278 10211 10275 10,254.667 Moisture, % 6.95 7.14 7.21 7.100 Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000



### Saturday, January 29, 2011 Page 5 of 12

### Electricity Generating Unit ICR 10/22/2010 Emissions Summary

Process Run Data 

### Location: CFB Comon Stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 6.79E-02 6.00E-02 6.36E-02 0.064 ppm 5.92E+01 5.25E+01 5.54E+01 55.700 ppm@7%O2 6.04E+01 5.38E+01 5.66E+01 56.933


### Location: CFB Comon Stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 2.74E-03 9.82E-04 2.60E-03 0.002 ppm 8.71E-01 5.46E-01 1.44E+00 0.952 ppm@7%O2 1.55E+00 5.59E-01 1.47E+00 1.193



### Location: CFB Comon Stack - Method 6C Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 3.25E-01 3.33E-01 3.81E-01 0.346 ppm 1.24E+02 1.27E+02 1.45E+02 132.000 ppm@7%O2 1.27E+02 1.30E+02 1.48E+02 135.000



### Saturday, January 29, 2011 Page 6 of 12

### Electricity Generating Unit ICR 10/22/2010 Process Run Data



### Run Name Value UOM Comments Target Value 1 MegaWatt output 1733 MWh 0 

### 1 Steam Flow 695.99 klbs/hr 0 1 Anthracite Waste Coal Fuel Feed 1753 tons/day 0 1 Stack Temperature 0 F 0 

### 1 Stack Moisture 0 % 0 1 Stack O2 0 % 0 1 Stack CO2 0 % 0 

### 1 Heat Input 903.5 MMBtu/Hr Test Run 1 M0011 - 8/2/10 9:05-11:15 0

1 Stack Gas Flow 0 scfm 0 

### 2 MegaWatt output 1793 MWh 0 2 Steam Flow 677.45 klbs/hr 0 2 Anthracite Waste Coal Fuel Feed 1753 tons/day 0 

### 2 Stack Temperature 0 F 0 2 Stack Moisture 0 % 0 

### 2 Stack O2 0 % 0 2 Stack CO2 0 % 0 2 Heat Input 876.02 MMBtu/Hr 0 

### 2 Stack Gas Flow 0 scfm Test Run 2 M0011 - 8/2/2010 11:58-14:07 0

3 MegaWatt output 1766 MWh 0 

### 3 Steam Flow 705.41 klbs/hr 0 3 Anthracite Waste Coal Fuel Feed 1838 tons/day 0 3 Stack Temperature 0 F 0 

### 3 Stack Moisture 0 % 0 3 Stack O2 0 % 0 3 Stack CO2 0 % 0 

### 3 Heat Input 936.89 MMBtu/Hr 0 3 Stack Gas Flow 0 scfm Test Run 3 M0011, Test Run 1 M18, M25A, M6C & M10 - 8/3/10 7:01-9:12 0

4 MegaWatt output 1766 MWh 0



### Saturday, January 29, 2011 Page 7 of 12

### Electricity Generating Unit ICR 10/22/2010

APCD Run Data 4 Steam Flow 700.52 klbs/hr 0 

### 4 Anthracite Waste Coal Fuel Feed 1838 tons/day 0 4 Stack Temperature 0 F 0 4 Stack Moisture 0 % 0 

### 4 Stack O2 0 % 0 4 Stack CO2 0 % 0 4 Heat Input 934.53 MMBtu/Hr 0 

### 4 Stack Gas Flow 0 scfm Test Run 1 M0010 & M0031, Test Run 2 M18, M25A, M6C & M10 - 8/3/10 9:56- 11:55 0

5 MegaWatt output 1766 MWh 0 

### 5 Steam Flow 704.85 klbs/hr 0 5 Anthracite Waste Coal Fuel Feed 1838 tons/day 0 5 Stack Temperature 0 F 0 

### 5 Stack Moisture 0 % 0 5 Stack O2 0 % 0 5 Stack CO2 0 % 0 

### 5 Heat Input 929.03 MMBtu/Hr 0 5 Stack Gas Flow 0 scfm Test Run 2 M0010 & M0031, Test Run 3 M18, M25A, M6C & M10 - 8/3/10 12:57-15:20 0

6 MegaWatt output 1733 MWh 0 

### 6 Steam Flow 679.35 klbs/hr 0 6 Anthracite Waste Coal Fuel Feed 1936 tons/day 0 6 Stack Temperature 0 F 0 

### 6 Stack Moisture 0 % 0 6 Stack O2 0 % 0 6 Stack CO2 0 % 0 

### 6 Heat Input 914.98 MMBtu/Hr 0 6 Stack Gas Flow 0 scfm Test Run 3 M0010 & M0031 - 8/4/10 7:49-9:37 0

Target Value 

### Saturday, January 29, 2011 Page 8 of 12

### Electricity Generating Unit ICR 10/22/2010

Process Lab Run Data Run Name Value UOM Comments Target Value 

### 1 DRY LIMESTONE INJECTION 2068 lbs./hr 0 2 DRY LIMESTONE INJECTION 2068 lbs./hr 0 

### 3 DRY LIMESTONE INJECTION 1714 lbs./hr 0 4 DRY LIMESTONE INJECTION 1714 lbs./hr 0 5 DRY LIMESTONE INJECTION 1714 lbs./hr 0 

### 6 DRY LIMESTONE INJECTION 1995 lbs./hr 0 1 BAGHOUSE #1 6.36inches of H20 0 2 BAGHOUSE #1 6.36inches of H20 0 

### 3 BAGHOUSE #1 6.31 inches of H20 0 4 BAGHOUSE #1 6.31 inches of H20 0 5 BAGHOUSE #1 6.36inches of H20 0 

### 6 BAGHOUSE #1 6.3 inches of H20 0 1 BAGHOUSE #2 6.25inches of H2O 0 2 BAGHOUSE #2 6.22inches of H2O 0 

### 3 BAGHOUSE #2 6.32inches of H2O 0 4 BAGHOUSE #2 6.17inches of H2O 0 5 BAGHOUSE #2 6.3 inches of H2O 0 

### 6 BAGHOUSE #2 6.22inches of H2O 0

Saturday, January 29, 2011 Page 9 of 12

### Electricity Generating Unit ICR 10/22/2010 Sampling / Stack Data Results Detail 

### Location CFB Comon Stack - Method 10 Average Run Number 1 2 3 Test Date 8/3/2010 8/3/2010 8/3/2010 Run Start Time 7:10:00 AM9:56:00 AM12:57:00 PM Run Finish Time 9:09:00 AM11:55:00 AM 2:58:00 PM Carbon Dioxide, % 13.08 13.07 13.07 13.073 Oxygen, % 7.28 7.33 7.3 7.303 Fuel Factor 1.04 1.04 1.04 Dry Volumetric Flow Rate, dry scfm 279544 277980 281873279,799.000 F-Factor, dscfm/MMBtu @ %O2 10278 10211 1027510,254.667 Moisture, % 6.95 7.14 7.21 7.100 Analyzer Make Thermo Electron Thermo

Electron Thermo

Electron Analyzer Model 48C 48C 48C Analyzer Serial Number 48C-67476- 35648C-67476-

356 48C-67479-

356 Operating Range 260 260 260 260.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 1 2 3 2.000 Calibration Pre Zero Cylinder ID CC-133012 CC-133012 CC-133012 Calibration Pre Zero Cylinder Instrument Response 0.8 0.83 0.83 0.820 Calibration Pre Zero Cylinder Bias 0.27 0.28 0.28 0.277 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID CC-106987 CC-106987 CC-106987 Calibration Pre High Cylinder Instrument Response 126.4 126.6 126.4 126.467 Calibration Pre High Cylinder Bias 0.42 0.5 0.42 0.447 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID CC-133012 CC-133012 CC-133012 Calibration Post Zero Cylinder Instrument Response 0.83 0.83 0.8 0.820 Calibration Post Zero Cylinder Bias 0.28 0.28 0.27 0.277 Calibration Post Zero Cylinder Drift 0.01 0 0.01 0.007 Calibration Post High Cylinder ID CC-106987 CC-106987 CC-106987 Calibration Post High Cylinder Instrument Response 126.6 126.4 126.6 126.533 Calibration Post High Cylinder Bias 0.5 0.42 0.5 0.473 Calibration Post High Cylinder Drift 0.08 0.08 0.08 0.080 Cavg 60.46 53.72 56.6 56.927 Cavg Units ppmvd ppmvd ppmvd Cgas 59.225 52.5238 55.3922 55.714 Cgas Units ppmvd ppmvd ppmvd Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000 Cgasw 0 0 0 0.000 Cgasw Units



### Saturday, January 29, 2011 Page 10 of 12

### Electricity Generating Unit ICR 10/22/2010 Location CFB Comon Stack - Method 25A Average Run Number 1 2 3 Test Date 8/3/2010 8/3/2010 8/3/2010 Run Start Time 7:10:00 AM9:56:00 AM12:57:00 PM Run Finish Time 9:09:00 AM11:55:00 AM 2:58:00 PM Carbon Dioxide, % 7.28 13.07 13.07 11.140 Oxygen, % 13.08 7.33 7.3 9.237 Fuel Factor 1.07 1.04 1.04 Dry Volumetric Flow Rate, dry scfm 279544 277980 28487371,135,420.3 33 F-Factor, dscfm/MMBtu @ %O2 10278 10211 1027510,254.667 Moisture, % 6.95 7.14 7.21 7.100 Analyzer Make JUM JUM JUM Analyzer Model VE-7 VE-7 VE-7 Analyzer Serial Number Operating Range 15 15 15 15.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 4 5 6 5.000 Calibration Pre Zero Cylinder ID CC-133012 CC-133012 CC-133012 Calibration Pre Zero Cylinder Instrument Response 0.14 0.13 0.15 0.140 Calibration Pre Zero Cylinder Bias 0 0 0 0.000 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID CC-98752 CC-98752 CC-98752 Calibration Pre High Cylinder Instrument Response 6.18 6.26 6.15 6.197 Calibration Pre High Cylinder Bias 0 0 0 0.000 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID CC-133012 CC-133012 CC-133012 Calibration Post Zero Cylinder Instrument Response -0.17 -0.14 -0.1 -0.137 Calibration Post Zero Cylinder Bias -2.07 -1.8 -1.67 -1.847 Calibration Post Zero Cylinder Drift 2.07 1.8 1.67 1.847 Calibration Post High Cylinder ID CC-98752 CC-98752 CC-98752 Calibration Post High Cylinder Instrument Response 5.91 5.99 5.95 5.950 Calibration Post High Cylinder Bias -1.8 -1.8 -1.33 -1.643 Calibration Post High Cylinder Drift 1.8 1.8 1.33 1.643 Cavg 0.8 0.51 1.36 0.890 Cavg Units ppmvw ppmvw ppmvw Cgas 0.8715 0.5456 1.4399 0.952 Cgas Units ppmvd ppmvd ppmvd Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000 Cgasw 0.8109653465 346540.506598694

9429041.336107883

81743 0.885 Cgasw Units ppmvw ppmvw ppmvw



### Saturday, January 29, 2011 Page 11 of 12

### Electricity Generating Unit ICR 10/22/2010 Location CFB Comon Stack - Method 6C Average Run Number 1 2 3 Test Date 8/3/2010 8/3/2010 8/3/2010 Run Start Time 7:10:00 AM9:56:00 AM12:57:00 PM Run Finish Time 9:09:00 AM11:55:00 AM 2:58:00 PM Carbon Dioxide, % 13.08 13.07 13.07 13.073 Oxygen, % 7.28 7.33 7.3 7.303 Fuel Factor 1.04 1.04 1.04 Dry Volumetric Flow Rate, dry scfm 279544 277980 281.873185,935.291 F-Factor, dscfm/MMBtu @ %O2 10278 10211 1027510,254.667 Moisture, % 6.95 7.14 7.21 7.100 Analyzer Make Bovar Bovar Bovar Analyzer Model 721M 721M 721M Analyzer Serial Number VD-721M8519-1 VD-721M8519-1 VD-721M8519-1 Operating Range 260 260 260 260.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 7 8 9 8.000 Calibration Pre Zero Cylinder ID CC-133012 CC-133012 CC-133012 Calibration Pre Zero Cylinder Instrument Response 1.7 1.9 0.92 1.507 Calibration Pre Zero Cylinder Bias 0.64 0.72 0.34 0.567 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID CC-114119 CC-114119 CC-114119 Calibration Pre High Cylinder Instrument Response 119.6 121.7 121.1 120.800 Calibration Pre High Cylinder Bias -2.42 -1.62 -1.85 -1.963 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID CC-133012 CC-133012 CC-133012 Calibration Post Zero Cylinder Instrument Response 1.9 0.92 0.97 1.263 Calibration Post Zero Cylinder Bias 0.72 0.34 0.36 0.473 Calibration Post Zero Cylinder Drift 0.08 0.38 0.02 0.160 Calibration Post High Cylinder ID CC-114119 CC-114119 CC-114119 Calibration Post High Cylinder Instrument Response 121.7 121.1 120.9 121.233 Calibration Post High Cylinder Bias -1.62 -1.85 -1.92 -1.797 Calibration Post High Cylinder Drift 0.8 0.236.999999999 99998E-02 0.367 Cavg 118.19 122.04 138.42 126.217 Cavg Units ppmvd ppmvd ppmvd Cgas 124.0775 127.3758 145.0842 132.179 Cgas Units ppmvd ppmvd ppmvd Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000 Cgasw 0 0 0 0.000 Cgasw Units



### Saturday, January 29, 2011 Page 12 of 12