- About NRC           - The Commission
      - Statutory Authority
      - Strategic Plan
      - Budget &  Performance
      - Organization & Functions
      - Locations
      - History
      - Values
      - Policymaking
      - Radiation Protection
      - Fire Protection
      - How We Regulate
      - Grants
      - Civil Rights
      -     
    - NuclearReactors           - Operating Reactor Locations
      - Reactor Quick Links
      - Power Reactors
      - Research and Test Reactors
      - Operating Reactors
      - Operator Licensing
      - New Reactors
      - Operator Licensing for New Reactors
      - Reactor Safety Research
      - Advisory Comm (ACRS)
      - Decommissioning of Nuclear Facilities
      -     
    - NuclearMaterials           - Fuel Cycle Facility Locations
      - Uranium Recovery Locations
      - Materials Quick Links
      - Special Nuclear Material
      - Source Material
      - Byproduct Material
      - Med, Academic & Ind Uses
      - Source Materials Facilities
      - Uranium Recovery
      - Fuel Cycle Facilities
      - Materials Transportation
      - Materials Research
      - Advisory Comm (ACMUI)
      - Decommissioning of Nuclear Facilities
      - Materials Environmental Reviews
      -     
    - RadioactiveWaste           - Waste Quick Links
      - Low-Level Waste
      - Waste Incidental to Reprocessing
      - Incidental Waste Criteria
      - High-Level Waste
      - Uranium Mill Tailings
      - LLW Disposal
      - HLW Disposal
      - Spent Fuel Storage
      - Spent Fuel Transport
      - Waste Research
      -     
    - NuclearSecurity           - Security Spotlight
      - NRC Responsibilities
      - Domestic Safeguards
      - Radioactive Material Security
      - Facility Protection
      - Nuclear Material Control
      - International Safeguards
      - Information Security
      - Emergency Preparedness
      - &;   
    - Public Meetings& Involvement           - Public Meeting Schedule
      - Commission	    Schedule
      - Conferences & Symposia
      - Documents for Comment
      - Brochures & Fact Sheets
      - Involving Stakeholders
      - Info Quality Guidelines
      - Rulemaking Process
      - Licensing
      - Enforcement
      - Hearing Process
      - Hearing Applications
      -     

```
				 UNITED STATES
			 NUCLEAR REGULATORY COMMISSION
		     OFFICE OF NUCLEAR REACTOR REGULATION
			 WASHINGTON, D.C.  20555-0001

				March 21, 1997


NRC INFORMATION NOTICE 97-11: CEMENT EROSION FROM CONTAINMENT SUBFOUNDATIONS
			      AT NUCLEAR POWER PLANTS


Addressees

All holders of operating licenses or construction permits for nuclear power
reactors.

Purpose

The U.S. Nuclear Regulatory Commission (NRC) is issuing this information
notice (IN) to alert addressees to information regarding the possible erosion
of cement from porous concrete subfoundations below the reactor building
basemats at some reactor sites.  It is expected that recipients will review
the information for applicability to their facilities and consider actions, as
appropriate, to monitor similar phenomena at their plants.  However,
suggestions contained in this information notice are not NRC requirements;
therefore, no specific action or written response is required.

Background

The containment structure at Millstone Nuclear Power Station Unit 3 (MNPS-3)
has a 3.05-meter [10-foot]-thick reinforced-concrete basemat founded on rock. 
Between the foundation rock surface and the underside of the basemat are
several layers of different materials.  These layers consist of (1) a 25.4-cm
[10-inch]-thick leveling layer of porous concrete made of coarse aggregates
and Portland cement, (2) a 0.16-cm [1/16th-inch]-thick butyl rubber
waterproofing membrane, (3) a 5.08-cm [2-inch]-thick Portland cement mortar
seal, (4) a second layer of 22.86-cm [9-inch]-thick porous concrete made of
coarse aggregates and calcium aluminate (high-alumina) cement, and (5) a thin
mortar seal (consisting of calcium aluminate cement and sand) on the top of
the upper layer of the porous concrete.  In the upper porous concrete layer,
15-cm [6-inch]-diameter porous concrete pipes are installed to collect and
drain ground water which may seep down along the periphery of the containment
wall.  The collected water drains into two sumps inside the Engineered Safety
Features (ESF) Building.

The MNPS-3 licensee, Northeast Nuclear Energy Company (NNECO), identified the
issue of cement erosion from the porous concrete drainage system in 1987 upon
examination of the accumulated sludge in the two lower drain sumps in the ESF
Building.  The licensee's efforts  


9703190136 .                                                IN 97-11
							    March 21, 1997
							    Page 2 of 4


to follow up on and resolve this concern are documented in NRC Inspection
Reports 50-423/94-11 (accession number 9406060281) and 50-423/96-04 (accession
number 9606180450), dated May 27, 1994, and June 6, 1996, respectively.  The
main concern is the adequacy of the eroded porous media to transfer the
containment loads to the bedrock.  The unexpected erosion of the high-alumina
cement also gave rise to another concern regarding a potential for interaction
between the concrete of the foundation basemat that contains Portland cement
and the high-alumina cement of the subfoundation in the presence of
underground water.  

To address these concerns, the licensee performed strength tests on cores
obtained from mockup tests that simulated accelerated degradation of the
porous concrete.  The licensee concluded that the load-bearing capacity of the
porous concrete has not been compromised.  The licensee is continuing to
investigate the effects of continuous water flow on the time-dependent
degradation of porous concrete.  In response to a staff question on settlement
of the containment structure, NNECO has stated that, to date, no detectable
movement of the containment structure has been observed.  Furthermore, NNECO
has reported that the loss of cement as a result of erosion from porous
concrete is not significant.  

On the basis of a review of all the available information, it appears that
there is no immediate safety concern at MNPS-3 because only an insignificant
amount of cement is estimated to have possibly eroded from the porous concrete
subfoundation since the plant was built in 1975, and because no adverse
consequences of the cement erosion are either predicted or have been observed
at the plant.

Discussion

To address the question of whether there are other nuclear power plant sites
at which these types of conditions could exist, the staff reviewed the updated
Final Safety Analysis Reports (UFSARs) of 24 plants selected on the basis of
(1) the unique practice of the constructor or the architect and engineers
(A&Es) and (2) a sampling of A&Es.  The staff found that  12 reactor units had
subfoundation layers of porous concrete:  MNPS-3, North Anna Units 1 and 2,
Surry Units 1 and 2, Nine Mile Point Unit 2 (NMP-2), Maine Yankee,
FitzPatrick, Beaver Valley Units 1 and 2, Haddam Neck, and Perry.  Of these 12
plants, 3 have surveillance programs for monitoring cement erosion � MNPS-3,
NMP-2, and Maine Yankee.  Maine Yankee Inspection Report 50-309/95-08
(accession number 9505240167), dated May 16, 1995, shows that the containment
sump has been under surveillance since 1970 and that no sign of cement slurry
has been found.  The NMP-2 licensee has replied verbally that no calcium
aluminate has been found in the sump water sample and that its surveillance
findings will be documented in due course.  The staff has obtained the
following information from the licensees of the remaining nine plants
regarding the conditions at their plants:

      Virginia Electric & Power Company (VEPCO), the licensee of North Anna
      Units 1  and 2 and Surry Units 1 and 2, reported on November 5, 1996,
      that Type II, low-alkali, Portland cement (and not calcium aluminate
      cement) was used in the porous concrete at North Anna and Surry sites..                                                            
							    IN 97-11
							    March 21, 1997
							    Page 3 of 4


      At North Anna Unit 2, water samples taken recently from the basemat sump
      and from two domestic water wells at the plant site showed virtually no
      aluminum (less than  1 ppm) in the three locations.  Insignificant
      amounts of calcium and sulfate were noticed at the mat sump.  No
      detectable settlement of the containment basemat was noticed at North
      Anna Units 1 and 2.  
      
      At Surry Units 1 and 2, an external subsurface drainage system operates
      continuously to control groundwater level.  The Unit 1 valve pit area
      for the internal drainage system was dry; the Unit 2 area had a few
      centimeters of standing water apparently leaking in through a side wall. 
      A minimum amount of leachate was observed in this area.  The settlement
      of the containment structures of both units at Surry were found to be
      less than 0.32 cm [1/8 inch], which is within the design values (1.27 cm 
      [1/2 inch]) for settlement.  

      The Haddam Neck plant (HNP) licensee, Northeast Utilities Services
      Company, reported on October 31, 1996, that Type II, low-alkali,
      Portland cement (and not calcium aluminate cement) was used in the
      porous concrete mix.  For the last   10 years at HNP, no slurry was
      found in the drainage water from the external containment sump during
      the monthly survey done for radiological concerns.  Reactor building
      settlement is not monitored; however, recent inspections inside the
      containment found no evidence of containment settlement and no
      indications of degradation of the concrete slab.

      The Perry nuclear power plant licensee, Cleveland Electric Illuminating
      Company, reported on November 4, 1996, that no cement slurry has been
      noted in the drainage and there has been no evidence of pea gravel in
      the drainage pipes or manholes.  The licensee has, however, reported
      that dissolved calcium carbonate is being carried to the drainage pipes
      and the sumps, where it is solidifying as a fine particulate which
      hardens into hard scale.  According to NRC Region III Inspection Report
      50-440/96-04 (accession number 9609030241) dated August 21, 1996, the
      licensee also discovered an accumulation of mineral deposits that
      clogged the pores of the porous concrete pipes and developed an
      effective method of clearing the clogged pipes.  The licensee plans to
      clear the remaining pipes.  No containment structure settlement has been
      observed at Perry.

      The Beaver Valley Power Station (BVPS) Units 1 and 2 licensee, Duquesne
      Light Company (DLC), reported on November 7, 1996, that neither of the
      two units has experienced drainage from the porous concrete layers below
      the basemat.   DLC further claims that such drainage is not expected at
      BVPS because of the plant's containment design features and the
      waterproof membrane that envelops the porous concrete layer, the
      containment mat foundation, and the exterior wall up to the plant grade
      level.  DLC has reported that the total observed settlement of the BVPS .                                                            
							    IN 97-11
							    March 21, 1997
							    Page 4 of 4


      containment structures compares favorably with the total predicted
      settlement, and that it has not noted any unusual conditions that were
      related to the porous concrete layers at BVPS Units 1 and 2.

      The James A. FitzPatrick nuclear power plant licensee, New York Power
      Authority (NYPA), reported on November 8, 1996, that the porous concrete
      subfoundation slab of 15.24-cm [6-inch] (minimum) thickness was
      constructed using Type II Portland cement.  This slab, laid between the
      basemat and the rock, is surrounded by engineered backfill.  On top of
      the backfill, a 30.48-cm [12-inch]-diameter porous concrete drainage
      pipe leading to a sump was laid with its invert level about  1.22 meters
      [4 feet] above the top of the porous concrete slab.  Any ground water
      seeping down along the sides of the reactor building collects in the
      sump and is pumped into the drainage system.  NYPA has not observed any
      cementitious slurry in the water samples being regularly collected from
      the drainage sump.  NYPA has also reported that the containment
      structure has not settled.

On the basis of this information and also on the basis of the staff's
preliminary assessments of MNPS-3 and NMP-2, the staff finds that there is no
immediate generic or plant-specific safety concern related to the porous
concrete subfoundations below the containment basemat at nuclear power plants. 
However, the NRC staff is continuing to evaluate the potential long-term
impact of erosion of high-alumina cement at MNPS-3.  

This information notice requires no specific action or written response.  If
you have any questions about the information in this notice, please contact
one of the technical contacts listed below or the appropriate project manager.


					  signed by M.M. Slosson

				    Thomas T. Martin, Director
				    Division of Reactor Program Management
				    Office of Nuclear Reactor Regulation

Technical contacts:  R. Pichumani, NRR          
		     (301) 415-2734       
		     E-mail:  [email protected]

		     H. Ashar, NRR
		     (301) 415-2851
		     E-mail:  [email protected]
```