Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 1745 1745 Detroit Edison Sam e legal ownerOne Energy Plaza Detroit MI 48226

Page 1Facility _Information plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip Trenton Channel Power Plant

4695 W . Jefferson Avenue

Trenton MI 48183 One Energy Plaza Detroit MI 48226

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 4Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 5Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 6Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 7Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 8Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 9Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 10Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 11Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 12Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 13Facility _Information Part I --The Trenton Channel High Pressure section is composed of 4 boilers (16-19) each of which can send steam to either of two main turbine generators. Emissions for all 4 boilers exhaust through their own Primary ESPs, with Boilers 16 &17 then passing through a combined secondary ESP, while Boilers 18 7 19 pass through the other secondary ESP. Both secondary ESPs exhaust into a single combined stack for all 4 boilers.ESP dates of installation: The year is correct, but the month is unknown so used June in each case.W hile each boiler has its own Boiler Information, the fuels for the HP section are monitored by a single control system, so all fuels information is for all 5 boilers combined.PM (Filterable) limits for all Trenton Channel boilers are lbs of particulate per 1000 lbs wet gas, corrected to 50% XS air as determined by EPA Method 5 or other MDNRE AQD approved methodSO2 limits are plant-wide mass limits of 151.36 tons per calendar day , and 55246.4 tons per calendar yearUnit

Page 14facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 1745 1 Principal Environm ental Engineer Wa yn e A. Rugenstein

3132357023

2488951060

rugensteinw@dteenergy .com

TRUE 1745 2 Supervisor - Environmental Mark J. Mullen

3138970298

3134024469

mu llenm @dteenergy .com

TRUE

Page 15facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 1745 bitum inous 41 50.2 1745 subbituminous 59 49.8

Page 16facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type 1745 No.2 Fuel Oil (distillate) 100 100

Page 17facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 18facility _other_materials rcra_explain

Page 19boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuel heat_input max_heat_input MW e_capacity 1745 16 Tangential firing We t Bottom coal 798 603 58 1745 17 Tangential firing We t Bottom coal 798 603 58 1745 18 Tangential firing Dry Bottom coal 798 603 58 1745 19 Tangential firing We t Bottom coal 798 603 58 1745 9A Tangential firing We t Bottom coal 4640 4045 540

Page 20boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 55 88.05 83.07 1550 1380 950 950 FALSE 55 88.05 83.07 1550 1380 950 950 FALSE 55 88.05 83.07 1550 1380 950 950 FALSE 55 88.05 83.07 1550 1380 950 950 FALSE 520 90.62 83.8 2990 2641 1000 1000 FALSE 1000

Page 21boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 7377 58.8 N FALSE FALSE 7073 59.3 N FALSE FALSE 7801 57.7 N FALSE FALSE 7159 58.6 N FALSE FALSE 1000 7835 78.4 N FALSE

Page 22boiler_information

NOx_control

SO2_control

combustion_additives No Yes Yes No Yes Yes No Yes Yes No Yes Yes Yes Yes Yes

Page 23boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 1745 16 coal - bituminous2007 39.8 49.4 1745 16 coal - bituminous2008 41 50.5 1745 16 coal - bituminous2009 44.4 53.8 1745 16 coal - subbituminous 2007 60.2 50.5 1745 16 coal - subbituminous 2008 59 49.2 1745 16 coal - subbituminous 2009 55.6 45.9 1745 16 oil - distillate 2007 100 0.1 1745 16 oil - distillate 2008 100 0.3 1745 16 oil - distillate 2009 100 0.3 1745 17 coal - bituminous2007 39.8 49.4 1745 17 coal - bituminous2008 41 50.5 1745 17 coal - bituminous2009 44.4 53.8 1745 17 coal - subbituminous 2007 60.2 50.5 1745 17 coal - subbituminous 2008 59 49.2 1745 17 coal - subbituminous 2009 55.6 45.9 1745 17 oil - distillate 2007 100 0.1 1745 17 oil - distillate 2008 100 0.3 1745 17 oil - distillate 2009 100 0.3 1745 18 coal - bituminous2007 39.8 49.4 1745 18 coal - bituminous2008 41 50.5 1745 18 coal - bituminous2009 44.4 53.8 1745 18 coal - subbituminous 2007 60.2 50.5 1745 18 coal - subbituminous 2008 59 49.2 1745 18 coal - subbituminous 2009 55.6 45.9 1745 18 oil - distillate 2007 100 0.1 1745 18 oil - distillate 2008 100 0.3 1745 18 oil - distillate 2009 100 0.3 1745 19 coal - bituminous2007 39.8 49.4 1745 19 coal - bituminous2008 41 50.5 1745 19 coal - bituminous2009 44.4 53.8 1745 19 coal - subbituminous 2007 60.2 50.5 1745 19 coal - subbituminous 2008 59 50.2 1745 19 coal - subbituminous 2009 55.6 45.9 1745 19 oil - distillate 2007 100 0.1 1745 19 oil - distillate 2008 100 0.3 1745 19 oil - distillate 2009 100 0.3 1745 9A coal - bituminous2007 41.5 51 1745 9A coal - bituminous2008 37.6 46.9 1745 9A coal - bituminous2009 34.2 43.4 1745 9A coal - subbituminous 2007 58.5 48.8 1745 9A coal - subbituminous 2008 62.4 53 1745 9A coal - subbituminous 2009 65.8 56.6 1745 9A oil - distillate 2007 100 0.2 1745 9A oil - distillate 2008 100 0.1 1745 9A oil - distillate 2009 100 0.1

Page 24boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 1745 9A Low NOx Burner 3/1/2001 1745 9A Overfire Air 3/1/2001

Page 25boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 1745 16 Low Sulfur Coal 7/1/1989 1745 17 Low Sulfur Coal 7/1/1989 1745 18 Low Sulfur Coal 7/1/1989 1745 19 Low Sulfur Coal 7/1/1989 1745 9A Low Sulfur Coal 7/1/1989

Page 26boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online 1745 16 Flue gas conditioning to control opacity (e.g., SO3 injection, ammonia, other) 7/1/1978 1745 17 Flue gas conditioning to control opacity (e.g., SO3 injection, ammonia, other) 7/1/1978 1745 18 Flue gas conditioning to control opacity (e.g., SO3 injection, ammonia, other) 7/1/1978 1745 19 Flue gas conditioning to control opacity (e.g., SO3 injection, ammonia, other) 1/1/1978 1745 9A Flue gas conditioning to control opacity (e.g., SO3 injection, ammonia, other) 6/1/2005 1745 9A Other (specify) NH3 injection 7/1/1987

Page 27facility _units facility _id unit_id 1745 9A 1745 HP

Page 28unit_boilers

facility _id unit_id boiler_id 1745 9A 9A 1745 HP 16 1745 HP 17 1745 HP 18 1745 HP 19

Page 29facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 1745 TC16/17-ESP2

PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1966 1745 TC16-ESP1

PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1948 1745 TC17-ESP1

PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1948 1745 TC18/19-ESP2

PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1966 1745 TC18-ESP1

PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1948 1745 TC19-ESP1

PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1948 1745 TC9A-ESP PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 6/1/1969

Page 30facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 31facility _sampling_ports facility _id sampling_port_id 1745 TC9A-Port 1745 TCHP-Port

Page 32facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 1745 TC9A-STK 16 561.5 140 1745 TCHP-STK 14.5 559 140

Page 33configurations

facility _id configuration_id 1745 TC16-Config 1745 TC17-Config 1745 TC18-Config 1745 TC19-Config 1745 TC9A-Config

Page 34configuration_components

facility _id configuration_id

component_id

order component_type port_near 1745 TC16-Config

HP 1 Unit 1745 TC16-Config

TC16/17-ESP2 3 PM control 1745 TC16-Config

TC16-ESP1 2 PM control 1745 TC16-Config

TCHP-Port 4 Sam pling Port next 1745 TC16-Config

TCHP-STK 5 Stack 1745 TC17-Config

HP 1 Unit 1745 TC17-Config

TC16/17-ESP2 3 PM control 1745 TC17-Config

TC17-ESP1 2 PM control 1745 TC17-Config

TCHP-Port 4 Sam pling Port next 1745 TC17-Config

TCHP-STK 5 Stack 1745 TC18-Config

HP 1 Unit 1745 TC18-Config

TC18/19-ESP2 3 PM control 1745 TC18-Config

TC18-ESP1 2 PM control 1745 TC18-Config

TCHP-Port 4 Sam pling Port next 1745 TC18-Config

TCHP-STK 5 Stack 1745 TC19-Config

HP 1 Unit 1745 TC19-Config

TC18/19-ESP2 3 PM control 1745 TC19-Config

TC19-ESP1 2 PM control 1745 TC19-Config

TCHP-Port 4 Sam pling Port next 1745 TC19-Config

TCHP-STK 5 Stack 1745 TC9A-Config

9A 1 Unit 1745 TC9A-Config

TC9A-ESP 2 PM control 1745 TC9A-Config

TC9A-Port 3 Sam pling Port next 1745 TC9A-Config

TC9A-STK 4 Stack

Page 35configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 1745 TC9A-Config

PM (Filterable)

Fderal - Title V Operating Permit

0.15 1745 TC9A-Config

Sulfur Dioxide (SO2)

Federal - Title V Operating Permit

1.67 pound per million British Thermal Unit (lb/MMBtu)

30 days 1745 TC16-Config

PM (Filterable)

Fderal - Title V Operating Permit

0.19 1745 TC16-Config

Sulfur Dioxide (SO2)

Federal - Title V Operating Permit

1.67 pound per million British Thermal Unit (lb/MMBtu)

30 days 1745 TC17-Config

PM (Condensable)

Federal - Title V Operating Permit

0.19 1745 TC17-Config

Sulfur Dioxide (SO2)

Federal - Title V Operating Permit 1745 TC18-Config

PM (Filterable)

Fderal - Title V Operating Permit

0.19 1745 TC18-Config

Sulfur Dioxide (SO2)

Federal - Title V Operating Permit 1745 TC19-Config

PM (Filterable)

Fderal - Federal Operating Permit

0.19 1745 TC19-Config

Sulfur Dioxide (SO2)

Federal - Title V Operating Permit

Page 36configuration_pollutants1

avg_period_2

em lim it_details

test_method

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping See Notes See Notes --Opacity COMS per 49CFR75--Continue monitoring, logging, and ESP operating data --Records kept per 40CFR75--Continuous monitoring, logging and reports of ESP operating data--Record CAM exceedances, inspections, corrective actions, probable causes, and problem resolution--Maintain fuel use and sulfur content records See Notes for SO2 emission limits See Notes --CEMS per 49CFR75--Continue monitoring, logging, and ESP operating data --Records kept per 40CFR75--Record CAM exceedances, inspections, corrective actions, probable causes, and problem resolution--Maintain fuel use and sulfur content records See Notes for Units

EPA Method 15 or other method approved by MDNRE AQD See Notes Sam e as Unit 9A Sam e as Unit 9A See Notes for SO2 limits See Notes Sam e as Unit 9A Sam e as Unit 9A See Notes See Notes Sam e as Unit 9A Sam e as Unit 9A See Notes for SO2 limits See Notes Sam e as Unit 9A Sam e as Unit 9A See Notes See Notes Sam e as Unit 9A Sam e as Unit 9A See Notes for SO2 limits See Notes Sam e as Unit 9A Sam e as Unit 9A See Notes See NoresASee Notes Sam e as Unit 9A

Sam e as Unit 9A See Notes for SO2 limits See Notes Sam e as Unit 9A Sam e as Unit 9A

Page 37configuration_pollutants1

req_reporting --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system Sam e as Unit 9A Sam e as Unit 9A Sam e as Unit 9A Sam e as Unit 9A Sam e as Unit 9A Sam e as Unit 9A Sam e as Unit 9A Sam e as Unit 9A

Page 38configuration_pollutants1 --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system

Page 39configuration_pollutants1 --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system

Page 40configuration_pollutants1 --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system --Quarterly

XS emissions reports to MDNRE and USEPA--CEMS/COMS reports per 40CFR75--Semi-Annual monitoring and deviations reports--Annual Certification of Compliance Annual Report--Semi-annual CAM summaries of exceedances, inspections, corrective actions, probable causes, and resolution--Annual reporting of emissions using MDNRE MAERS system

Page 41control_technologies

facility _id configuration_id

component_id

control_id project_title project_type vendor_name

vndor_contact

vendor_phone

Page 42control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 43control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 44control_technologies feed_rate_units

Page 45control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 46control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 47control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 48control_costs

CBI

Page 49mi sc_controls

facility _id mi sc_control_id

control_description 1745 1 No

Page 50mi sc_control_configurations

facility _id mi sc_control_id

configuration_id

Page 51fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county

Page 52fuel_shipments

coal_seam shipment_method

Page 53fuel_shipment_configurations

facility _id shipment_id

configuration_id

Page 54fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units

Page 55fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address

Page 56fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies

Page 57fuel_shipment_samples analysis_copies

Page 58fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 59test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation

Page 60test_reports

deviation_reports

Page 61test_report_configurations

facility _id report_id configuration_id

Page 62test_report_fuels

facility _id report_id fuel_id

Page 63test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type

Page 64cem_data

facility _id tim e_period

cem_period_description

Page 65cem_data_pollutants1

facility _id tim e_period

pollutant_nam e

Page 66test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent

Page 67test_report_sampling

fg_fraction

Page 68sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content

Page 69sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature

Page 70sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value

Page 71sampling_runs

fuel_sulfur

Page 72sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL

Page 73sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment

Page 74sampling_run_pollutants1 run_pollutant_comment

Page 75sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 76sampling_run_fuel fuel_conc_MDL

Page 77