Editorial Note on Part 75
Editorial Note: The provisions of this part marked [Statutory Provision] appear in Title III of the Federal Coal Mine Health and Safety Act of 1969.

§ 75.1912 Fire suppression systems for permanent underground diesel fuel storage facilities. ( a ) The fire suppression system required by § 75.1903 shall be an automatic multipurpose dry chemical type (ABC) fire suppression system listed or approved as an engineered dry chemical extinguishing system by a nationally recognized independent testing laboratory and appropriate for installation at a permanent underground diesel fuel storage facility. ( 1 ) Alternate types of fire suppression systems shall be approved in accordance with § 75.1107-13 of this part.
( 2 ) The system shall be installed in accordance with the manufacturer's specifications and the limitations of the listing or approval.
( 3 ) The system shall be installed in a protected location or guarded to prevent physical damage from routine operations.
( 4 ) Suppressant agent distribution tubing or piping shall be secured and protected against damage, including pinching, crimping, stretching, abrasion, and corrosion.
( 5 ) Discharge nozzles shall be positioned and aimed for maximum fire suppression effectiveness in the protected areas. Nozzles must also be protected against the entrance of foreign materials such as mud, coal dust, and rock dust.
( b ) The fire suppression system shall provide automatic fire detection and automatic fire suppression for all areas within the facility.
( c ) Audible and visual alarms to warn of fire or system faults shall be provided at the protected area and at a surface location which is continually monitored by a person when personnel are underground. In the event of a fire, personnel shall be warned in accordance with the provisions set forth in § 75.1502.
( d ) The fire suppression system shall deenergize all power to the diesel fuel storage facility when actuated except that required for automatic enclosure and alarms.
( e ) Fire suppression systems shall include two manual actuators located as follows: ( 1 ) At least one within the fuel storage facility; and
( 2 ) At least one a safe distance away from the storage facility and located in intake air, upwind of the storage facility.
( f ) The fire suppression system shall remain operational in the event of electrical system failure.
( g ) Electrically operated detection and actuation circuits shall be monitored and provided with status indicators showing power and circuit continuity. If the system is not electrically operated, a means shall be provided to indicate the functional readiness status of the detection system.
( h ) Each fire suppression system shall be tested and maintained in accordance with the manufacturer's recommended inspection and maintenance program and as required by the nationally recognized independent testing laboratory listing or approval, and be visually inspected at least once each week by a person trained to make such inspections.
( i ) *Recordkeeping.* Persons performing inspections and tests of fire suppression systems under paragraph (h) shall record when a fire suppression system does not meet the installation or maintenance requirements of this section. ( 1 ) The record shall include the facility whose fire suppression system did not meet the installation or maintenance requirements of this section, the defect found, and the corrective action taken.
( 2 ) Records are to be kept manually in a secure manner not susceptible to alteration or recorded electronically in a secured computer system that is not susceptible to alteration.
( 3 ) Records shall be maintained at a surface location at the mine for one year and made available for inspection by an authorized representative of the Secretary and miners' representatives.
( j ) All miners normally assigned to the active workings of the mine shall be instructed about the hazards inherent to the operation of the fire suppression systems and, where appropriate, the safeguards available for each system.
[61 FR 55527, Oct. 25, 1996; 70 FR 36347, June 23, 2005]