Name: Gregory D. Smith

Title: Plant Manager

Company: Public Service Company of New Mexi

Sign Date: 12/7/2010

Name: Karl G. Breuer

Title: Technical Report Writer

Company: Air Pollution Testing, Inc.

Sign Date: 6/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

San Juan Generating Station Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Saturday, February 26, 2011 Page 1 of 24
San Juan Generating Station Unit 1

12/7/2010

Facility Information:

San Juan Unit 1

6800 North County Road

Waterflow NM 87421

Contact: Rod Seagle

Phone: (598) 505-7529

Fax: (505) 598-7247

Email: rodney.seagle@pnmresources.com

Testing Company:

Air Pollution Testing, Inc.

5530 Marshall Street

Arvada CO 80002

Contact: Scott Bouchard

Phone: (303) 420-5949

Fax:

Email: sbouchard@airtest.net

Air Permit Number:

P062R1M1

Permitted Source ID/Name:

SJGS 1 San Juan Generating Station

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Coal fired generating unit burning subbituminuous coal. Controls include, Baghouse, Activated Carbon Injection, 

and an FGD.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000600868 FRS #: 110000600868

SCC / Description 10100222 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Subbituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Unit 1Stack 

House

255 0 0 0 8.47 4.23 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Unit 1Stack Hydrogen Chloride Method 26A 3 180 0

House

Unit 1Stack Hydrogen Fluoride Method 26A 3 180 0

House

Unit 1Stack Chromium Method 29 3 240 0

House

Saturday, February 26, 2011 Page 2 of 24
San Juan Generating Station Unit 1

12/7/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

No deviations were implemented as part of this test program.

Unit 1Stack Antimony Method 29 3 240 0

House

Unit 1Stack Cadmium Method 29 3 240 0

House

Unit 1Stack Cobalt Method 29 3 240 0

House

Unit 1Stack Lead Method 29 3 240 0

House

Unit 1Stack Manganese Method 29 3 240 0

House

Unit 1Stack Nickel Method 29 3 240 0

House

Unit 1Stack Selenium Method 29 3 240 0

House

Unit 1Stack Arsenic Method 29 3 240 0

House

Unit 1Stack Co2 Method 3A CO2 10 60 0

House

Unit 1Stack O2 Method 3A O2 10 60 0

House

Organic Condensible 

Particulate

Unit 1Stack Method 5/OTM-28 3 240 0

House

Inorganic (Aqueous) 

Condensible Part.

Unit 1Stack Method 5/OTM-28 3 240 0

House

Unit 1Stack Filterable Particulate Method 5/OTM-28 3 240 0

House

Unit 1Stack Total Particulate Method 5/OTM-28 3 240 0

House

Saturday, February 26, 2011 Page 3 of 24
San Juan Generating Station Unit 1

12/7/2010

Sampling / Stack Data Results Summary

Location Unit 1Stack House - Method 26A

Average

Run Number 1 2 3

Test Date 4/22/2010 4/23/2010 4/23/2010

Run Start Time 4:43:00 PM 8:04:00 

AM

3:07:00 PM

Run Finish Time 10:02:30 PM 2:34:30 PM 9:34:30 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 111.777 110.098 112.684 111.520

Moisture Content of Stack Gas, % 15.22 14.35 14.53 14.700

Moisture Saturation at Stack Gas Temperature, % 12.61 12.63 12.79 12.677

Carbon Dioxide, % 12.6 12.6 12.6 12.600

Oxygen, % 6.3 6.3 6.3 6.300

Average Stack Gas Temperature, °F 115.54 115.46 115.92 115.640

Dry Volumetric Flow Rate, dry scfm 841,455.0 824,415.9 855,684.8 840,518.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,303,573.6 1,282,081.4 1,334,215.9 1,306,623.63

3

Percent Isokinetic of Sampling Rate, % 103.8 104.4 102.9 103.700

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, February 26, 2011 Page 4 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Unit 1Stack House - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 5 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 1Stack House - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 6 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A CO2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 1Stack House - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 7 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 1Stack House - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 8 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A O2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 1Stack House - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Saturday, February 26, 2011 Page 9 of 24
San Juan Generating Station Unit 1

12/7/2010

Emissions Summary

Location: Unit 1Stack House - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.437 0.428 0.341 0.402

lb/mmBtuO2 1.21E-04 1.20E-04 9.34E-05 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.889 0.872 0.693 0.818

lb/mmBtuO2 2.45E-04 2.44E-04 1.90E-04 0.000

Location: Unit 1Stack House - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.00048 0.000617 0.000475 0.001

mg/dscm 1.18E-04 1.47E-04 1.10E-04 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00015 0.000355 0.000185 0.000

mg/dscm 3.68E-05 8.45E-05 4.28E-05 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0012 0.00119 0.00106 0.001

mg/dscm 2.94E-04 2.83E-04 2.45E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.00839 0.02382 0.022 0.018

mg/dscm 2.06E-03 5.67E-03 5.09E-03 0.004

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.003 0.0025 0.0045 0.003

mg/dscm 7.35E-04 5.95E-04 1.04E-03 0.001

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0048 0.00486 0.0055 0.005

mg/dscm 1.18E-03 1.16E-03 1.27E-03 0.001

Saturday, February 26, 2011 Page 10 of 24
San Juan Generating Station Unit 1

12/7/2010

Process Run Data

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0124 0.0202 0.0369 0.023

mg/dscm 3.04E-03 4.81E-03 8.54E-03 0.005

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0064 0.02485 0.0119 0.014

mg/dscm 1.57E-03 5.92E-03 2.75E-03 0.003

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.00086 0.00052 0.00052 0.001

mg/dscm 2.11E-04 1.24E-04 1.20E-04 0.000

Location: Unit 1Stack House - Method 5/OTM-28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 16.1 13.3 23.6 17.667

lb/mmBtuO2 3.53E-03 2.76E-03 5.02E-03 0.004

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 12.2 8 7.4 9.200

lb/mmBtuO2 2.68E-03 1.66E-03 1.57E-03 0.002

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 6.6 7.7 19.9 11.400

lb/mmBtuO2 1.45E-03 1.60E-03 4.23E-03 0.002

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 34.9 29 50.9 38.267

lb/mmBtuO2 7.65E-03 6.02E-03 1.08E-02 0.008

Saturday, February 26, 2011 Page 11 of 24
San Juan Generating Station Unit 1

12/7/2010

Process Run Data

APCD Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 3556 mmBtu/hr 3550

1 Load 352 Mw 355

1 Steam Output 2216 klbs/hr 2250

1 Moisture 11.4 % 14

1 Stack Flow 834322 dscfm 850000

1 Stack Temperature 120 Deg F 116

1 Coal Flow Rate 358693 lbs/hr 340000

1 CO2 12.9 % 12.6

1 O2 6.5 % 6.3

2 Heat Input 3611 mmBtu/hr 3550

2 Load 355 Mw 355

2 Steam Output 2234 klbs/hr 2250

2 Moisture 11.4 % 14

2 Stack Flow 842391 dscfm 850000

2 Stack Temperature 120 Deg F 116

2 Coal Flow Rate 358431 lbs/hr 340000

2 CO2 13 % 12.6

2 O2 6.4 % 6.3

3 Heat Input 3604 mmBtu/hr 3550

3 Load 355 Mw 355

3 Steam Output 2235 klbs/hr 2250

3 Moisture 11.6 % 14

3 Stack Flow 842365 dscfm 850000

3 Stack Temperature 121 Deg F 116

3 Coal Flow Rate 364885 lbs/hr 340000

3 CO2 13 % 12.6

3 O2 6.4 % 6.3

Run Name Value UOM Comments

Target

Value

1 ACTIVATED CARBON ADSORPTION 0.15ACI Feed Rate #/macf 0.15

2 ACTIVATED CARBON ADSORPTION 0.15ACI Feed Rate #/macf 0.15

3 ACTIVATED CARBON ADSORPTION 0.15ACI Feed Rate #/macf 0.15

Saturday, February 26, 2011 Page 12 of 24
San Juan Generating Station Unit 1

12/7/2010

Process Lab Run Data

1 BAGHOUSE 99.99Removal Efficiency 99.99

2 BAGHOUSE 99.99Removal Efficiency 99.99

3 BAGHOUSE 99.99Removal Efficiency 99.99

1 SPRAY SCRUBBER 94.4Removal Efficiency 90

2 SPRAY SCRUBBER 94.4Removal Efficiency 90

3 SPRAY SCRUBBER 94.4Removal Efficiency 90

Run Name Value UOM Comments

1 Scrubber TDS 51180 mg/l

1 Scurbber TSS 1E+05 mg/l

1 Scrubber Delta Pressure 0.423 "H2O

1 Scrubber Liquor Flow Rate 16.84 gal/min

2 Scrubber TDS 47020 mg/l

2 Scurbber TSS 1E+05 mg/l

2 Scrubber Delta Pressure 0.752 "H2O

2 Scrubber Liquor Flow Rate 13.87 gal/min

3 Scrubber TDS 46730 mg/l

3 Scurbber TSS 1E+05 mg/l

3 Scrubber Delta Pressure 0.752 "H2O

3 Scrubber Liquor Flow Rate 13.87 gal/min

Saturday, February 26, 2011 Page 13 of 24
San Juan Generating Station Unit 1

12/7/2010

Sampling / Stack Data Results Detail

Location Unit 1Stack House - Method 26A

Average

Run Number 1 2 3

Test Date 4/22/2010 4/23/2010 4/23/2010

Run Start Time 4:43:00 PM 8:04:00 AM 3:07:00 PM

Run Finish Time 10:02:30 PM 2:34:30 PM 9:34:30 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.215 0.215 0.215 0.215

Pitot Tube Coefficient 0.82 0.82 0.82 0.820

Dry Gas Meter Calibration Factor 0.993 0.993 0.993 0.993

Barometric Pressure, inches of Mercury 24.19 24.1 24.1 24.130

Average Orifice Meter Differential, inches H2O 1.61 1.52 0.97 1.367

Dry Gas Meter Volume Sampled, cubic feet 140.529 138.143 142.651 140.441

Average Dry Gas Meter Temperature, °F 75.54 72.35 76.21 74.700

Dry Gas Meter Volume Sampled, dscf 111.777 110.098 112.684 111.520

Total Moisture Liquid collected, g 426.3 391.9 407.1 408.433

Volume of Water Vapor, standard cubic feet 20.07 18.45 19.16 19.227

Moisture Content of Stack Gas, % 15.22 14.35 14.53 14.700

Moisture Saturation at Stack Gas Temperature, % 12.61 12.63 12.79 12.677

Dry Mole Fraction 0.8739 0.8737 0.8721 0.873

Carbon Dioxide, % 12.6 12.6 12.6 12.600

Oxygen, % 6.3 6.3 6.3 6.300

Carbon Monoxide & Nitrogen, % 81.1 81.1 81.1 81.100

Fuel Factor 1.16 1.16 1.16

Dry Molecular Weight, lb/lb-Mole 30.27 30.27 30.27 30.270

Wet Molecular weight, lb/lb-Mole 29.19 29.03 29.01 29.077

Flue Gas Static Pressure, inches of H2O -1.35 -1.35 -1.35 -1.350

Absolute Flue Gas Pressure, inches of Mercury 24.09 24.00 24.00 24.030

Average Stack Gas Temperature, °F 115.54 115.46 115.92 115.640

Average Velocity Head, inches of H2O 0.9329561069

93732

0.894203231

557659

0.967142024

669266

0.931

Average Stack Gas Velocity, feet/second 61.26 60.25 62.70 61.403

Stack Cross-Sectional Area, square feet 354.656 354.656 354.656 354.656

Dry Volumetric Flow Rate, dry scfm 841,455.0 824,415.9 855,684.8 840,518.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,303,573.6 1,282,081.4 1,334,215.9 1,306,623.6

33

Percent Isokinetic of Sampling Rate, % 103.8 104.4 102.9 103.700

Percent Excess Air, % 0.0 0.0 0.0 0.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 255 255 255

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, February 26, 2011 Page 14 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, February 26, 2011 Page 15 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 16 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 17 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 18 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A CO2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 19 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 20 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 21 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 22 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 3A O2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 23 of 24
San Juan Generating Station Unit 1

12/7/2010

Location Unit 1Stack House - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, February 26, 2011 Page 24 of 24