Document headings vary by document type but may contain
                    the following: the agency or agencies that issued and signed a document
the number of the CFR title and the number of each part
                      the document amends, proposes to amend, or is directly
                      related to
the agency docket number / agency internal file number
the RIN which identifies each regulatory action listed in
                      the Unified Agenda of Federal Regulatory and Deregulatory
                      Actions See the
                    Document Drafting Handbook
                    for more details.
 Department of Energy [Case Number 2020-009; EERE-2020-BT-WAV-0025]
 AGENCY: Office of Energy Efficiency and Renewable Energy, Department of Energy.
 ACTION: Notification of petition for waiver and grant of an interim waiver; request for comments.
 SUMMARY: This document announces receipt of and publishes a petition for waiver and interim waiver from Heat Transfer Products Group (“HTPG”), which seeks a waiver for specified carbon dioxide (“CO2”) direct expansion unit cooler basic models from the U.S. Department of Energy (“DOE”) test procedure used to determine the efficiency of walk-in cooler and walk-in freezer refrigeration systems. DOE also gives notice of an Interim Waiver Order that requires HTPG to test and rate the specified CO2 direct expansion unit cooler basic models in accordance with the alternate test procedure set forth in the Interim Waiver Order. DOE solicits comments, data, and information concerning HTPG's petition and its suggested alternate test procedure so as to inform DOE's final decision on HTPG's waiver request.
 DATES: The Interim Waiver Order is effective on December 23, 2020. Written comments and information will be accepted on or before January 22, 2021.
 ADDRESSES: Interested persons are encouraged to submit comments using the Federal eRulemaking Portal at 
                        *http://www.regulations.gov.*
                         Alternatively, interested persons may submit comments, identified by case number “2020-009”, and Docket number “EERE-2020-BT-WAV-0025,” by any of the following methods: *Federal eRulemaking Portal: http://www.regulations.gov.*
                         Follow the instructions for submitting comments.
                    *Email: HTPG2020WAV0025@ee.doe.gov.*
                         Include Case No. 2020-009 in the subject line of the message.
                    *Postal Mail:*
                         Appliance and Equipment Standards Program, U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy, Building Technologies Office, Mail Stop EE-5B, Petition for Waiver Case No. 2020-009, 1000 Independence Avenue SW, Washington, DC 20585-0121. If possible, please submit all items on a compact disc (“CD”), in which case it is not necessary to include printed copies.
                    *Hand Delivery/Courier:*
                         Appliance and Equipment Standards Program, U.S. Department of Energy, Building Technologies Office, 950 L'Enfant Plaza SW, 6th floor, Washington, DC 20024. Telephone: (202) 287-1445. If possible, please submit all items on a CD, in which case it is not necessary to include printed copies. No telefacsimilies (“faxes”) will be accepted. For detailed instructions on submitting comments and additional information on this process, see the 
                        **SUPPLEMENTARY INFORMATION**
                         section of this document. *Docket:*
                         The docket, which includes 
                        **Federal Register**
                         notices, comments, and other supporting documents/materials, is available for review at 
                        *http://www.regulations.gov.*
                         All documents in the docket are listed in the 
                        *http://www.regulations.gov*
                         index. However, some documents listed in the index, such as those containing information that is exempt from public disclosure, may not be publicly available. The docket web page can be found at 
                        *http://www.regulations.gov/​docket?​D=​EERE-2020-BT-WAV-0025.*
                         The docket web page contains instruction on how to access all documents, including public comments, in the docket. See the 
                        **SUPPLEMENTARY INFORMATION**
                         section for information on how to submit comments through 
                        *http://www.regulations.gov.*
 FOR FURTHER INFORMATION CONTACT: Ms. Lucy deButts, U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy, Building Technologies Office, Mail Stop EE-5B, 1000 Independence Avenue SW, Washington, DC 20585-0121. Email: 
                        *AS_Waiver_Request@ee.doe.gov.* Michael Kido, U.S. Department of Energy, Office of the General Counsel, Mail Stop GC-33, Forrestal Building, 1000 Independence Avenue SW, Washington, DC 20585-0103. Telephone: (202) 586-8145. Email: 
                        *Michael.Kido@hq.doe.gov.*


SUPPLEMENTARY INFORMATION: DOE is publishing HTPG's petition for waiver in its entirety, pursuant to 10 CFR 431.401(b)(1)(iv).[1]
                    
                     DOE invites all interested parties to submit in writing by January 22, 2021, comments and information on all aspects of the petition, including the alternate test procedure. Pursuant to 10 CFR 431.401(d), any person submitting written comments to DOE must also send a copy of such comments to the petitioner. The contact information for the petitioner is Michael Straub, 
                    *mike.straub@htpg.com,*
                     201 Thomas French Dr., Scottsboro, AL 35769-7405. *Submitting comments via http://www.regulations.gov.*
                     The 
                    *http://www.regulations.gov*
                     web page will require you to provide your name and contact information. Your contact information will be viewable to DOE Building Technologies staff only. Your contact information will not be publicly viewable except for your first and last names, organization name (if any), and submitter representative name (if any). If your comment is not processed properly because of technical difficulties, DOE will use this information to contact you. If DOE cannot read your comment due to technical difficulties and cannot contact you for clarification, DOE may not be able to consider your comment. However, your contact information will be publicly viewable if you include it in the comment or in any documents attached to your comment. Any information that you do not want to be publicly viewable should not be included in your comment, nor in any document attached to your comment. If this instruction is followed, persons viewing comments will see only first and last names, organization names, correspondence containing comments, and any documents submitted with the comments. Do not submit to 
                    *http://www.regulations.gov*
                     information for which disclosure is restricted by statute, such as trade secrets and commercial or financial information (hereinafter referred to as Confidential Business Information (“CBI”)). Comments submitted through 
                    *http://www.regulations.gov*
                     cannot be claimed as CBI. Comments received through the website will waive any CBI claims for the information submitted. For information on submitting CBI, see the Confidential Business Information section. DOE processes submissions made through 
                    *http://www.regulations.gov*
                     before posting. Normally, comments 
                    ( print page 83928)
                    will be posted within a few days of being submitted. However, if large volumes of comments are being processed simultaneously, your comment may not be viewable for up to several weeks. Please keep the comment tracking number that 
                    *http://www.regulations.gov*
                     provides after you have successfully uploaded your comment. *Submitting comments via email, hand delivery/courier, or postal mail.*
                     Comments and documents submitted via email, hand delivery/courier, or postal mail also will be posted to 
                    *http://www.regulations.gov*. If you do not want your personal contact information to be publicly viewable, do not include it in your comment or any accompanying documents. Instead, provide your contact information on a cover letter. Include your first and last names, email address, telephone number, and optional mailing address. The cover letter will not be publicly viewable as long as it does not include any comments. Include contact information each time you submit comments, data, documents, and other information to DOE. If you submit via postal mail or hand delivery/courier, please provide all items on a CD, if feasible, in which case it is not necessary to submit printed copies. Faxes will not be accepted. Comments, data, and other information submitted to DOE electronically should be provided in PDF (preferred), Microsoft Word or Excel, WordPerfect, or text (ASCII) file format. Provide documents that are not secured, written in English and free of any defects or viruses. Documents should not contain special characters or any form of encryption and, if possible, they should carry the electronic signature of the author. *Campaign form letters.*
                     Please submit campaign form letters by the originating organization in batches of between 50 to 500 form letters per PDF or as one form letter with a list of supporters' names compiled into one or more PDFs. This reduces comment processing and posting time. *Confidential Business Information.*
                     According to 10 CFR 1004.11, any person submitting information that he or she believes to be confidential and exempt by law from public disclosure should submit via email, postal mail, or hand delivery/courier two well-marked copies: One copy of the document marked confidential including all the information believed to be confidential, and one copy of the document marked “non-confidential” with the information believed to be confidential deleted. Submit these documents via email or on a CD, if feasible. DOE will make its own determination about the confidential status of the information and treat it according to its determination. It is DOE's policy that all comments may be included in the public docket, without change and as received, including any personal information provided in the comments (except information deemed to be exempt from public disclosure). Signing Authority This document of the Department of Energy was signed on November 24, 2020, by Alexander N. Fitzsimmons, Deputy Assistant Secretary for Energy Efficiency, Energy Efficiency and Renewable Energy, pursuant to delegated authority from the Secretary of Energy. That document with the original signature and date is maintained by DOE. For administrative purposes only, and in compliance with requirements of the Office of the Federal Register, the undersigned DOE Federal Register Liaison Officer has been authorized to sign and submit the document in electronic format for publication, as an official document of the Department of Energy. This administrative process in no way alters the legal effect of this document upon publication in the 
                    **Federal Register**
                    . Signed in Washington, DC, on November 24, 2020. Treena V. Garrett, Federal Register Liaison Officer, U.S. Department of Energy.
 Case Number 2020-009 Interim Waiver Order I. Background and Authority The Energy Policy and Conservation Act, as amended (“EPCA”),[1]
                    
                     authorizes the U.S. Department of Energy (“DOE”) to regulate the energy efficiency of a number of consumer products and certain industrial equipment (42 U.S.C. 6291-6317). Title III, Part C [2]
                    
                     of EPCA (42 U.S.C. 6311-6316, as codified), added by the National Energy Conservation Policy Act, Public Law 95-619, sec. 441 (Nov. 9, 1978), established the Energy Conservation Program for Certain Industrial Equipment, which sets forth a variety of provisions designed to improve the energy efficiency for certain types of industrial equipment. Through amendments brought about by the Energy Independence and Security Act of 2007, Public Law  110-140, sec. 312 (Dec. 19, 2007), this equipment includes walk-in cooler and walk-in freezer (collectively, “walk-in”) refrigeration systems, the focus of this document (42 U.S.C. 6311(1)(G)). The energy conservation program under EPCA consists essentially of four parts: (1) Testing, (2) labeling, (3) Federal energy conservation standards, and (4) certification and enforcement procedures. Relevant provisions of EPCA include definitions (42 U.S.C. 6311), energy conservation standards (42 U.S.C. 6313), test procedures (42 U.S.C. 6314), labeling provisions (42 U.S.C. 6315), and the authority to require information and reports from manufacturers (42 U.S.C. 6316). The Federal testing requirements consist of test procedures that manufacturers of covered equipment must use as the basis for: (1) Certifying to DOE that their equipment complies with the applicable energy conservation standards adopted pursuant to EPCA (42 U.S.C. 6316(a); 42 U.S.C. 6295(s)), and (2) making representations about the efficiency of that equipment (42 U.S.C. 6314(d)). Similarly, DOE must use these test procedures to determine whether the covered equipment complies with relevant standards promulgated under EPCA. (42 U.S.C. 6316(a); 42 U.S.C. 6295(s)) Under 42 U.S.C. 6314, EPCA sets forth the criteria and procedures DOE is required to follow when prescribing or amending test procedures for covered equipment. EPCA requires that any test procedures prescribed or amended under this section must be reasonably designed to produce test results which reflect the energy efficiency, energy use or estimated annual operating cost of covered equipment during a representative average use cycle and requires that test procedures not be unduly burdensome to conduct (42 U.S.C. 6314(a)(2)). The test procedure for walk-in refrigeration systems is contained in the Code of Federal Regulations (“CFR”) at 10 CFR part 431, subpart R, appendix C, 
                    *Uniform Test Method for the Measurement of Net Capacity and AWEF of Walk-In Cooler and Walk-In Freezer Refrigeration Systems*
                     (“Appendix C”). Under 10 CFR 431.401, any interested person may submit a petition for waiver from DOE's test procedure requirements. DOE will grant a waiver from the test procedure requirements if DOE determines either that the basic model for which the waiver was requested contains a design characteristic that prevents testing of the basic model according to the prescribed test procedures, or that the prescribed 
                    ( print page 83929)
                    test procedures evaluate the basic model in a manner so unrepresentative of its true energy consumption characteristics as to provide materially inaccurate comparative data. 10 CFR 431.401(f)(2). A petitioner must include in its petition any alternate test procedures known to the petitioner to evaluate the performance of the equipment type in a manner representative of the energy consumption characteristics of the basic model. 10 CFR 431.401(b)(1)(iii). DOE may grant the waiver subject to conditions, including adherence to alternate test procedures specified by DOE. 10 CFR 431.401(f)(2). As soon as practicable after the granting of any waiver, DOE will publish in the 
                    **Federal Register**
                     a notice of proposed rulemaking to amend its regulations so as to eliminate any need for the continuation of such waiver. 10 CFR 431.401(l). As soon thereafter as practicable, DOE will publish in the 
                    **Federal Register**
                     a final rule to that effect. 
                    *Id.* The waiver process also provides that DOE may grant an interim waiver if it appears likely that the underlying petition for waiver will be granted and/or if DOE determines that it would be desirable for public policy reasons to grant immediate relief pending a determination on the underlying petition for waiver. 10 CFR 431.401(e)(2). Within one year of issuance of an interim waiver, DOE will either: (i) Publish in the 
                    **Federal Register**
                     a determination on the petition for waiver; or (ii) publish in the 
                    **Federal Register**
                     a new or amended test procedure that addresses the issues presented in the waiver. 10 CFR 431.401(h)(1). When DOE amends the test procedure to address the issues presented in a waiver, the waiver will automatically terminate on the date on which use of that test procedure is required to demonstrate compliance. 10 CFR 431.401(h)(2). II. HTPG's Petition for Waiver and Interim Waiver On July 6, 2020, HTPG filed a petition for waiver and interim waiver from the test procedure for walk-in refrigeration systems set forth at 10 CFR part 431, subpart R, appendix C (HTPG, No. 1 at p. 1 [3]
                    
                    ). HTPG claims that the test conditions described in Table 15 and Table 16 of the Air-Conditioning, Heating, and Refrigeration Institute (“AHRI”) Standard 1250-2009, 
                    *Standard for Performance Rating of Walk-In Coolers and Freezers*
                     (“AHRI 1250-2009”) (for walk-in refrigerator unit coolers and freezer unit coolers tested alone, respectively), as incorporated by Appendix C with modification, cannot be achieved by the specified basic models and are not consistent with operation of HTPG's CO2
                     direct expansion unit coolers . HTPG stated that CO2
                     has a critical temperature of 87.8 °F,[4]
                    
                     and thus the required liquid inlet saturation temperature of 105 °F and the required liquid inlet subcooling temperature of 9 °F are not achievable, and that the test conditions should be more consistent with typical operating conditions for a transcritical CO2
                     booster system (HTPG, No. 1). The statements made by HTPG reference the difference in thermodynamic properties between CO2
                     and other refrigerants. At modest pressures (
                    *i.e.*
                     below the critical point), many substances transition from a solid to a liquid to a gas as temperature increases. For example, a pure substance like water transitions from liquid to steam at a specific temperature, 
                    *e.g.*
                     212 °F, at atmospheric pressure. As heat is added during a liquid to gas transition, the temperature remains constant and the substance coexists as both liquid and vapor. Continuing to add heat converts more of the liquid to vapor at a constant temperature. The reverse occurs when heat is removed. However, the transition temperature depends on the pressure—the higher the pressure, the higher the transition temperature. This is a key principle in refrigeration systems, which operate at two pressure levels associated with two temperatures. A refrigerant absorbs heat when it is at a low temperature and pressure, converting to gas and cooling the surrounding space. At high temperature and pressure, the refrigerant transitions to a liquid while releasing heat to the environment. A compressor is used to raise the low-pressure gas to a high pressure, and a throttle (pressure reduction device) is used to reduce the pressure once the refrigerant has been fully liquefied (condensed) at high pressure. All refrigerants have a “critical pressure” and an associated “critical temperature” above which liquid and vapor phases cannot coexist. Above this critical point, the refrigerant will be a gas and its temperature will increase or decrease as heat is added or removed. For all conventional refrigerants, the critical pressure is so high that it is never exceeded in typical refrigeration cycles. For example, R404A is a common refrigerant used in refrigeration systems that has a critical pressure of 540.8 psia [5]
                    
                     with an associated critical temperature of 161.7 °F. However, CO2
                     behaves differently, with a critical pressure of 1,072 psia associated with a much lower critical temperature of 87.8 °F. The refrigerant temperature must be somewhat higher than the ambient temperature in order to reject refrigeration cycle heat to the ambient environment. Ambient temperatures greater than 87.8 °F are common and the performance of many refrigeration and air conditioning systems are tested using a 95 °F ambient temperature, as indicated by the A test condition in AHRI 1250-2009 Section 5. At temperatures greater than the critical temperature, the CO2
                     refrigerant is in a supercritical state (
                    *i.e.*
                     a condition with pressure above the critical temperature) and heat is transferred to the environment. Since useful cooling is provided below the critical temperature, CO2
                     cycles are said to be transcritical. The transcritical nature of CO2
                     generally requires more complex refrigeration cycle design to approach the efficiency of traditional refrigerants (
                    *i.e.,*
                     R404A, R407A, R448A, etc.) during operation in high temperature conditions. To increase efficiency and prevent overheating, transcritical booster systems introduce (or use) multiple stages of compression and intercooling. CO2
                     is cooled in the gas cooler of a transcritical booster system, then expands through a high-pressure control valve and is delivered to a subcritical-pressure flash tank. In the flash tank, the refrigerant is in the subcritical phase and the liquid and vapor phases can be separated. A unit cooler in a CO2
                     booster system would be supplied with liquid refrigerant from the flash tank via expansion valves where the refrigerant is evaporated. The evaporated refrigerant is subsequently compressed up to gas cooler pressure to complete the cycle (HTPG, No. 2).
                    ( print page 83930) HTPG also requests an interim waiver from the existing DOE test procedure. DOE will grant an interim waiver if it appears likely that the petition for waiver will be granted, and/or if DOE determines that it would be desirable for public policy reasons to grant immediate relief pending a determination of the petition for waiver. 
                    *See*10 CFR 431.401(e)(2). Based on the assertions in the petition, absent an interim waiver, the prescribed test procedure is not appropriate for HTPG's CO2
                     direct expansion unit coolers and the test conditions are not achievable, since CO2
                     refrigerant has a critical temperature of 87.8 °F and the current DOE test procedure calls for a liquid inlet saturation temperature of 105 °F. The inability to achieve test conditions for the stated basic models would result in economic hardship from loss of sales stemming from the inability of the DOE test procedure to address the operating conditions of HTPG's equipment. III. Requested Alternate Test Procedure EPCA requires that manufacturers use the applicable DOE test procedures when making representations about the energy consumption and energy consumption costs of covered equipment (42 U.S.C. 6314(d)). Consistency is important when making representations about the energy efficiency of equipment, including when demonstrating compliance with applicable DOE energy conservation standards. Pursuant to 10 CFR 431.401, and after consideration of public comments on the petition, DOE may establish in a subsequent Decision and Order an alternate test procedure for the basic models addressed by the Interim Waiver Order. HTPG seeks to test and rate specific CO2
                     direct expansion unit cooler basic models with modifications to the DOE test procedure. HTPG's suggested approach specifies using modified liquid inlet saturation and liquid inlet subcooling temperatures—38°F and 5°F, respectively, for both walk-in refrigerator unit coolers and walk-in freezer unit coolers. Additionally, HTPG recommends that because the subject units are used in transcritical CO2
                     booster systems the calculations in AHRI 1250-2009 section 7.9 should be used to determine AWEF and net capacity for unit coolers matched to parallel rack systems as required under the DOE test procedure. This section of AHRI 1250-2009 is prescribed by the DOE test procedure for determining AWEF for all unit coolers tested alone (see 10 CFR part 431, subpart R, appendix C, section 3.3.1). Finally, HTPG also recommends that AHRI 1250-2009 Table 17, EER for Remote Commercial Refrigerated Display Merchandisers and Storage Cabinets, should be used to determine power consumption of CO2
                     direct expansion unit cooler systems as required under the DOE test procedure. IV. Interim Waiver Order DOE has reviewed HTPG's application, its suggested testing approach, industry materials regarding CO2
                     transcritical booster systems, and HTPG's consumer-facing materials, including websites and product specification sheets for the basic models listed in HTPG's petition. Based on this review, the suggested testing approach appears to allow for the accurate measurement of energy efficiency of the specified basic models, while alleviating the testing issues associated with HTPG's implementation of walk-in cooler and walk-in freezer testing for these basic models. Review of the CO2
                     refrigeration market confirms that the test conditions of the testing approach suggested by HTPG would be representative for operation of a unit cooler used in a transcritical CO2
                     booster system (HTPG, No. 4). CO2
                     that is cooled in the gas cooler of a transcritical booster system expands through a high-pressure control valve that delivers CO2
                     to a subcritical-pressure flash tank, where liquid and vapor phases of the refrigerant are separated. The liquid is then split and the unit coolers receive the refrigerant at the same condition, consistent with the use of the same liquid inlet saturation temperature for both the medium- and low-temperature systems in HTPG's suggested test approach. Calculations on other external CO2
                     refrigeration system designs in the market indicate that the 38 °F liquid unit cooler inlet saturation temperature suggested by HTPG is representative of CO2
                     booster systems (HTPG, No. 2). Regarding use of the EER values in AHRI 1250-2009 Table 17 to determine the representative compressor power consumption for CO2
                     unit cooler systems, research into the performance of different configurations of CO2
                     booster systems shows that enhanced CO2
                     cycles (like those used in transcritical booster systems) can match conventional refrigerants in average annual efficiency (HTPG, No. 3). These data and studies help to justify the use of the EER values in AHRI 1250-2009 Table 17 for determining the power consumption of CO2
                     booster system evaporators, even though these EER values were initially established for conventional refrigerants. Consequently, DOE has determined that HTPG's petition for waiver likely will be granted. Furthermore, DOE has determined that it is desirable for public policy reasons to grant HTPG immediate relief pending a determination of the petition for waiver. For the reasons stated, it is 
                    *ordered*
                     that: (1) HTPG must test and rate the following CO2
                     direct expansion unit cooler basic models with the alternate test procedure set forth in paragraph (2). *Russell branded Basic Model Numbers:* RL6A041ADAF
RL6A041DDAF
RL6A052ADAF
RL6A052DDAF
RL6A066ADAF
RL6A066DDAFRL6A073ADAF
RL6A073DDAF
RL6A094ADAF
RL6A094DDAF
RL6A117ADAF
PL6A117DDAFRL6A130ADAF
RL6A130DDAF
RL6A141ADAF
RL6A141DDAF
RL6A161ADAF
RL6A161DDAFRL6A181ADAF
RL6A181DDAF
RL6A195ADAF
RL6A195DDAF
RL6A235ADAF
RL6A235DDAFRL6A260ADAF
RL6A260DDAF
RL6A295ADAF
RL6A295DDAF
RL6A330ADAF
RL6A330DDAFRL6A390ADAF
RL6A390DDAF
RL6E035DDAF
RL6E042DDAF
RL6E049DDAF
RL6E066DDAFRL6E077DDAF
RL6E090DDAF
RL6E105DDAF
RL6E121DDAF
RL6E142DDAF
RL6E162DDAFRL6E182DDAF
RL6E200DDAF
RL6E200EDAF
RL6E244DDAF
RL6E244EDAF
RL6E281DDAFRL6E281EDAF
RL4E027DDAF
RL4E032DDAF
RL4E038DDAF
RL4E051DDAF
RL4E064DDAFRL4E080DDAF
RL4E094DDAF
RL4E110DDAF
RL4E125DDAF
RL4E141DDAF
RL4E155DDAFRL4E155EDAF
RL4E195DDAF
RL4E195EDAF
RL4E230DDAF
RL4E230EDAFRM6A182ADAF
RM6A182DDAF
RM6A182FDAF
RM6A220ADAF
RM6A220DDAF
RM6A220FDAFRM6A276ADAF
RM6A276DDAF
RM6A276FDAF
RM6A370ADAF
RM6A370DDAF
RM6A370FDAFRM6A442ADAF
RM6A442DDAF
RM6A442FDAF
RM6A549ADAF
RM6A549DDAF
RM6A549FDAFRM6A658ADAF
RM6A658DDAF
RM6A658FDAF
RM6E153DDAF
RM6E153EDAF
RM6E153FDAFRM6E153GDAF
RM6E184DDAF
RM6E184EDAF
RM6E184FDAF
RM6E184GDAF
RM6E311DDAFRM6E311EDAF
RM6E311FDAF
RM6E311GDAF
RM6E374DDAF
RM6E374EDAF
RM6E374FDAFRM6E374GDAF
RM6E469EDAF
RM6E469FDAF
RM6E469GDAF
RM6E564EDAF
RM6E564FDAF( print page 83931)RM6E564GDAF
RM4E110DDAF
RM4E110EDAF
RM4E110FDAF
RM4E110GDAF
RM4E143DDAFRM4E143EDAF
RM4E143FDAF
RM4E143GDAF
RM4E232DDAF
RM4E232EDAF
RM4E232FDAFRM4E232GDAF
RM4E288DDAF
RM4E288EDAF
RM4E288FDAF
RM4E288GDAF
RM4E336EDAFRM4E336FDAF
RM4E336GDAF
RM4E419EDAF
RM4E419FDAF
RM4E419GDAFRV6A043ADAF
RV6A043DDAF
RV6A053ADAF
RV6A053DDAF
RV6A085ADAF
RV6A085DDAFRV6A106ADAF
RV6A106DDAF
RV6A129ADAF
RV6A129DDAF
RV6A158ADAF
RV6A158DDAFRV6A176ADAF
RV6A176DDAF
RV6A218ADAF
RV6A218DDAF
RV6A271ADAF
RV6A271DDAFRV6E043DDAF
RV6E053DDAF
RV6E085DDAF
RV6E106DDAF
RV6E129DDAF
RV6E158DDAFRV6E176DDAF
RV6E218DDAF
RV6E271DDAFASLA25048ADAF
ASLA25048DDAF
ASLA25061ADAF
ASLA25061DDAF
ASLA35073ADAF
ASLA35073DDAFASLA45098ADAF
ASLA45098DDAF
ASLA55122ADAF
ASLA55122DDAF
ASLA65158ADAF
ASLA65158DDAFASLE25048DDAF
ASLE25058DDAF
ASLE35070DDAF
ASLE45094DDAF
ASLE55117DDAF
ASLE65150DDAFRE6A041ADAF
RE6A041DDAF
RE6A070ADAF
RE6A070DDAF
RE6A084ADAF
RE6A084DDAFRE6A104ADAF
RE6A104DDAF
RE6A128ADAF
RE6A128DDAF
RE6A141ADAF
RE6A141DDAFRE6A169ADAF
RE6A169DDAF
RE6A204ADAF
RE6A204DDAF
RE6A258ADAF
RE6A258DDAFRE6E037DDAF
RE6E045DDAF
RE6E075DDAF
RE6E089DDAF
RE6E108DDAF
RE6E125DDAFRE6E137DDAF
RE6E182DDAF
RE6E221DDAF
RE6E278DDAF
RE4E037DDAF
RE4E075DDAFRE4E107DDAF
RE4E149DDAF
RE4E186DDAF
RE4E234DDAFRH6A031DDAF
RH6A031FDAF
RH6A043DDAF
RH6A043FDAF
RH6A052DDAF
RH6A052FDAFRH6A063DDAF
RH6A063FDAF
RH6A087DDAF
RH6A087FDAF
RH6A105DDAF
RH6A105FDAFRH6A132DDAF
RH6A132FDAF
RH6A156DDAF
RH6A156FDAF
RH6A175DDAF
RH6A175FDAFRH6A209DDAF
RH6A209FDAF
RH6E033DDAF
RH6E033EDAF
RH6E033FDAF
RH6E033GDAFRH6E044DDAF
RH6E044EDAF
RN6E044FDAF
RH6E044GDAF
RH6E053DDAF
RH6E053EDAFRH6E053FDAF
RH6E053GDAF
RH6E066DDAF
RH6E066EDAF
RH6E066FDAF
RH6E066GDAFRH6E089DDAF
RH6E089EDAF
RH6E089FDAF
RH6E089GDAF
RH6E109DDAF
RH6E109EDAFRH6E109FDAF
RH6E109GDAF
RH6E134DDAF
RH6E134EDAF
RH6E134FDAF
RH6E134GDAFRH6E163DDAF
RH6E163EDAF
RH6E163FDAF
RH6E163GDAF
RH6E199DDAF
RH6E199EDAFRH6E199FDAF
RH6E199GDAF
RH4E035DDAF
RH4E035EDAF
RH4E035FDAF
RH4E035GDAFRH4E044DDAF
RH4E044EDAF
RH4E044FDAF
RH4E044GDAF
RH4E071DDAF
RH4E071EDAFRH4E071FDAF
RH4E071GDAF
RH4E087DDAF
RH4E087EDAF
RH4E087FDAF
RH4E087GDAFRH4E107DDAF
RH4E107EDAF
RH4E107FDAF
RH4E107GDAF
RH4E131DDAF
RH4E131EDAFRH4E131FDAF
RH4E131GDAF
RH4E167DDAF
RH4E167EDAF
RH4E167FDAF
RH4E167GDAF
 (2) The HTPG basic models identified in paragraph (1) of this Interim Waiver Order shall be tested according to the test procedure for walk-in cooler and walk-in freezer refrigeration systems prescribed by DOE at 10 CFR part 431, subpart R, appendix C (“Appendix C”), except that the liquid inlet saturation temperature test condition and liquid inlet subcooling temperature test condition shall be modified to 38°F and 5°F, respectively, for both walk-in refrigerator unit coolers and walk-in freezer unit coolers, as detailed below. All other requirements of Appendix C and DOE's regulations remain applicable. In Appendix C, under section 3.1. 
                    *General modifications: Test Conditions and Tolerances,*
                     revise section 3.1.5., to read as follows: 3.1.5. Tables 15 and 16 shall be modified to read as follows: Table 15—Refrigerator Unit Cooler
Test description
Unit cooler
                             air entering 
                             dry-bulb, °F
Unit cooler
                             air entering 
                             relative 
                             humidity, %
Saturated
                             suction 
                             temp, °F
Liquid inlet
                             saturation 
                             temp, °F
Liquid inlet
                             subcooling 
                             temp, °F
Compressor 
                             capacity
Test objectiveOff Cycle Fan Power
35
<50



Compressor Off
Measure fan input power during compressor off cycle.Refrigeration Capacity Suction A
35
<50
25
38
5
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.**Note:**
                         Superheat to be set according to equipment specification in equipment or installation manual. If no superheat specification is given, a default superheat value of 6.5 °F shall be used. The superheat setting used in the test shall be reported as part of the standard rating.
 Table 16—Freezer Unit Cooler
Test description
Unit cooler
                             air entering 
                             dry-bulb, °F
Unit cooler
                             air entering 
                             relative 
                             humidity, %
Saturated
                             suction 
                             temp, °F
Liquid inlet
                             saturation 
                             temp, °F
Liquid inlet
                             subcooling 
                             temp, °F
Compressor 
                             capacity
Test objectiveOff Cycle Fan Power
−10
<50



Compressor Off
Measure fan input power during compressor off cycle.Refrigeration Capacity Suction A
−10
<50
−20
38
5
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.Defrost
−10
Various



Compressor Off
Test according to Appendix C Section C11.**Note:**
                         Superheat to be set according to equipment specification in equipment or installation manual. If no superheat specification is given, a default superheat value of 6.5 °F shall be used. The superheat setting used in the test shall be reported as part of the standard rating.
 
 
 (3) 
                    *Representations.*
                     HTPG may not make representations about the energy efficiency of a basic model listed in paragraph (1) of this Interim Waiver Order for compliance, marketing, or other purposes unless the basic model has been tested in accordance with the provisions set forth in this alternate test procedure and such representations fairly disclose the results of such testing. (4) This Interim Waiver Order shall remain in effect according to the provisions of 10 CFR 431.401. (5) This Interim Waiver Order is issued on the condidion that the statements and representations provided by HTPG are valid. If HTPG makes any modifications to the controls or configurations of a basic model subject to this Interim Waiver Order, such modifications will render the waiver invalid with respect to that basic model, and HTPG will either be required to use the current Federal test method or submit a new application for a test procedure waiver. DOE may rescind or modify this waiver at any time if it determines the factual basis underlying the petition for the Interim Waiver Order is incorrect, or the results from the alternate test procedure are unrepresentative of the basic model's true energy consumption characteristics. 10 CFR 431.401(k)(1). Likewise, HTPG may request that DOE rescind or modify the Interim Waiver Order if HTPG discovers an error in the information provided to DOE as part of its petition, determines that the interim waiver is no longer needed, or for other appropriate reasons. 10 CFR 431.401(k)(2). (6) Issuance of this Interim Waiver Order does not release HTPG from the applicable requirements set forth at 10 CFR part 429. DOE makes decisions on waivers and interim waivers for only those basic models specifically set out in the petiion, not future models that may be manufactured by the petitioner. HTPG may submit a new or amended petition for waiver and rerquest for grant of interim waiver, as appropriate, for additional basic models of CO2
                     direct expansion unit coolers. Alternatively, if appropriate, HTPG may rerquest that DOE extend the scope of a waiver or an interim waiver to include additional basic models employing the same technology as the basic model(s) set forth in the original petition consistent with 10 CFR 431.401(g). Signed in Washington, DC, on November 24, 2020. Alexander N. Fitzsimmons, Deputy Assistant Secretary for Energy Efficiency,  Energy Efficiency and Renewable Energy.
 
 
  July 6, 2020 The design characteristics constituting the grounds for the Waiver and Interim Waiver Application: Appendix C to Subpart R of Part 431—Uniform Test Method for the Measurement of Net Capacity and AWEF of Walk-in Cooler and Walk-in Freezer Refrigeration Systems specifies that unit coolers tested alone use the test procedures described in AHRI 1250-2009. Table 15 and Table 16 of AHRI 1250-2009 are as follows:( print page 83934) Table 15—Refrigerator Unit Cooler
Test description
Unit cooler
                             air entering 
                             dry-bulb, °F
Unit cooler
                             air entering 
                             relative 
                             humidity, %
Saturated
                             suction 
                             temp, °F
Liquid inlet
                             saturation 
                             temp, °F
Liquid inlet
                             subcooling 
                             temp, °F
Compressor 
                             capacity
Test objectiveOff Cycle Fan Power
35
<50



Compressor Off
Measure fan input power during compressor off cycle.Refrigeration Capacity Suction A
35
<50
25
105
9
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.Refrigeration Capacity Suction B
35
<50
20
105
9
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.
 Table 16—Freezer Unit Cooler
Test description
Unit cooler air entering dry-bulb, °F
Unit cooler air entering relative 
                             humidity, %
Saturated suction temp, °F
Liquid inlet saturation temp, °F
Liquid inlet subcooling temp, °F
Compressor 
                             capacity
Test objectiveOff Cycle Fan Power
−10
<50



Compressor Off
Measure fan input power during compressor off cycle.Refrigeration Capacity Suction A
−10
<50
−20
105
9
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.Refrigeration Capacity Suction B
−10
<50
−26
105
9
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.Defrost
−10
Various



Compressor Off
Test according to Appendix C Section C11.
 CO2
                     refrigerant has a critical temperature of 87.8 °F thus the liquid inlet saturation temperature of 105 °F and the liquid inlet subcooling temperature of 9 °F as specified in Table 15 and Table 16 are not achievable.
                The test condition values need to be more in line with typical operating conditions for a transcritical CO2
                     booster system. *Basic Models on which the Waiver and Interim Waiver is being requested (All Russell Brand):* RL6A041ADAF
RL6A041DDAF
RL6A052ADAF
RL6A052DDAF
RL6A066ADAF
RL6A066DDAFRL6A073ADAF
RL6A073DDAF
RL6A094ADAF
RL6A094DDAF
RL6A117ADAF
PL6A117DDAFRL6A130ADAF
RL6A130DDAF
RL6A141ADAF
RL6A141DDAF
RL6A161ADAF
RL6A161DDAFRL6A181ADAF
RL6A181DDAF
RL6A195ADAF
RL6A195DDAF
RL6A235ADAF
RL6A235DDAFRL6A260ADAF
RL6A260DDAF
RL6A295ADAF
RL6A295DDAF
RL6A330ADAF
RL6A330DDAFRL6A390ADAF
RL6A390DDAF
RL6E035DDAF
RL6E042DDAF
RL6E049DDAF
RL6E066DDAFRL6E077DDAF
RL6E090DDAF
RL6E105DDAF
RL6E121DDAF
RL6E142DDAF
RL6E162DDAFRL6E182DDAF
RL6E200DDAF
RL6E200EDAF
RL6E244DDAF
RL6E244EDAF
RL6E281DDAFRL6E281EDAF
RL4E027DDAF
RL4E032DDAF
RL4E038DDAF
RL4E051DDAF
RL4E064DDAFRL4E080DDAF
RL4E094DDAF
RL4E110DDAF
RL4E125DDAF
RL4E141DDAF
RL4E155DDAFRL4E155EDAF
RL4E195DDAF
RL4E195EDAF
RL4E230DDAF
RL4E230EDAFRM6A182ADAF
RM6A182DDAF
RM6A182FDAF
RM6A220ADAF
RM6A220DDAF
RM6A220FDAFRM6A276ADAF
RM6A276DDAF
RM6A276FDAF
RM6A370ADAF
RM6A370DDAF
RM6A370FDAFRM6A442ADAF
RM6A442DDAF
RM6A442FDAF
RM6A549ADAF
RM6A549DDAF
RM6A549FDAFRM6A658ADAF
RM6A658DDAF
RM6A658FDAF
RM6E153DDAF
RM6E153EDAF
RM6E153FDAFRM6E153GDAF
RM6E184DDAF
RM6E184EDAF
RM6E184FDAF
RM6E184GDAF
RM6E311DDAFRM6E311EDAF
RM6E311FDAF
RM6E311GDAF
RM6E374DDAF
RM6E374EDAF
RM6E374FDAFRM6E374GDAF
RM6E469EDAF
RM6E469FDAF
RM6E469GDAF
RM6E564EDAF
RM6E564FDAFRM6E564GDAF
RM4E110DDAF
RM4E110EDAF
RM4E110FDAF
RM4E110GDAF
RM4E143DDAFRM4E143EDAF
RM4E143FDAF
RM4E143GDAF
RM4E232DDAF
RM4E232EDAF
RM4E232FDAFRM4E232GDAF
RM4E288DDAF
RM4E288EDAF
RM4E288FDAF
RM4E288GDAF
RM4E336EDAFRM4E336FDAF
RM4E336GDAF
RM4E419EDAF
RM4E419FDAF
RM4E419GDAFRV6A043ADAF
RV6A043DDAF
RV6A053ADAF
RV6A053DDAF
RV6A085ADAF
RV6A085DDAFRV6A106ADAF
RV6A106DDAF
RV6A129ADAF
RV6A129DDAF
RV6A158ADAF
RV6A158DDAFRV6A176ADAF
RV6A176DDAF
RV6A218ADAF
RV6A218DDAF
RV6A271ADAF
RV6A271DDAFRV6E043DDAF
RV6E053DDAF
RV6E085DDAF
RV6E106DDAF
RV6E129DDAF
RV6E158DDAFRV6E176DDAF
RV6E218DDAF
RV6E271DDAFASLA25048ADAF
ASLA25048DDAF
ASLA25061ADAF
ASLA25061DDAF
ASLA35073ADAF
ASLA35073DDAFASLA45098ADAF
ASLA45098DDAF
ASLA55122ADAF
ASLA55122DDAF
ASLA65158ADAF
ASLA65158DDAFASLE25048DDAF
ASLE25058DDAF
ASLE35070DDAF
ASLE45094DDAF
ASLE55117DDAF
ASLE65150DDAFRE6A041ADAF
RE6A041DDAF
RE6A070ADAF
RE6A070DDAF
RE6A084ADAF
RE6A084DDAFRE6A104ADAF
RE6A104DDAF
RE6A128ADAF
RE6A128DDAF
RE6A141ADAF
RE6A141DDAFRE6A169ADAF
RE6A169DDAF
RE6A204ADAF
RE6A204DDAF
RE6A258ADAF
RE6A258DDAFRE6E037DDAF
RE6E045DDAF
RE6E075DDAF
RE6E089DDAF
RE6E108DDAF
RE6E125DDAFRE6E137DDAF
RE6E182DDAF
RE6E221DDAF
RE6E278DDAF
RE4E037DDAF
RE4E075DDAFRE4E107DDAF
RE4E149DDAF
RE4E186DDAF
RE4E234DDAFRH6A031DDAF
RH6A031FDAF
RH6A043DDAF
RH6A043FDAF
RH6A052DDAF
RH6A052FDAFRH6A063DDAF
RH6A063FDAF
RH6A087DDAF
RH6A087FDAF
RH6A105DDAF
RH6A105FDAF( print page 83935)RH6A132DDAF
RH6A132FDAF
RH6A156DDAF
RH6A156FDAF
RH6A175DDAF
RH6A175FDAFRH6A209DDAF
RH6A209FDAF
RH6E033DDAF
RH6E033EDAF
RH6E033FDAF
RH6E033GDAFRH6E044DDAF
RH6E044EDAF
RN6E044FDAF
RH6E044GDAF
RH6E053DDAF
RH6E053EDAFRH6E053FDAF
RH6E053GDAF
RH6E066DDAF
RH6E066EDAF
RH6E066FDAF
RH6E066GDAFRH6E089DDAF
RH6E089EDAF
RH6E089FDAF
RH6E089GDAF
RH6E109DDAF
RH6E109EDAFRH6E109FDAF
RH6E109GDAF
RH6E134DDAF
RH6E134EDAF
RH6E134FDAF
RH6E134GDAFRH6E163DDAF
RH6E163EDAF
RH6E163FDAF
RH6E163GDAF
RH6E199DDAF
RH6E199EDAFRH6E199FDAF
RH6E199GDAF
RH4E035DDAF
RH4E035EDAF
RH4E035FDAF
RH4E035GDAFRH4E044DDAF
RH4E044EDAF
RH4E044FDAF
RH4E044GDAF
RH4E071DDAF
RH4E071EDAFRH4E071FDAF
RH4E071GDAF
RH4E087DDAF
RH4E087EDAF
RH4E087FDAF
RH4E087GDAFRH4E107DDAF
RH4E107EDAF
RH4E107FDAF
RH4E107GDAF
RH4E131DDAF
RH4E131EDAFRH4E131FDAF
RH4E131GDAF
RH4E167DDAF
RH4E167EDAF
RH4E167FDAF
RH4E167GDAF
 *Specific Requirement sought to be waived*
                    —Petitioning for a waiver and interim waiver to exempt CO2
                     Direct Expansion Unit Coolers in Medium and Low Temperature application from being tested to the current test procedure. The prescribed test procedure is not appropriate for these products for the reasons stated previously (liquid inlet saturation temperature and liquid inlet subcooling temperature test condition values are not appropriate for a transcritical CO2
                     booster system application). *List of manufacturers of all other basic models marketing in the United States and known to the petitioner to incorporate similar design characteristics*
                    — Manufacturer: Heatcraft Refrigeration Products Manufacturer: Keeprite Refrigeration Manufacturer: Hussmann/Krack Refrigeration *Proposed alternate test procedure:* 1. Utilize the test procedure as outlined in Appendix C to Subpart R of Part 431—Uniform Test Method for the Measurement of Net Capacity and AWEF of Walk-in Cooler and Walk-in Freezer Refrigeration Systems with the exception of modifying the test conditions in Table 15 and 16 for liquid inlet saturation temperature and liquid inlet subcooling temperature as noted below. In addition, per Appendix C to Subpart R of 431 use the calculations in AHRI 1250 section 7.9 to determine AWEF and net capacity for unit coolers matched to parallel rack systems. Use AHRI 1250 Table 17, EER for Remote Commercial Refrigerated Display Merchandisers and Storage Cabinets to determine the power consumption of the system. Table 15—Refrigerator Unit Cooler
Test description
Unit cooler air entering dry-bulb, °F
Unit cooler air entering relative 
                             humidity, %
Saturated suction temp, °F
Liquid inlet saturation temp, °F
Liquid inlet subcooling temp, °F
Compressor 
                             capacity
Test objectiveOff Cycle Fan Power
35
<50



Compressor Off
Measure fan input power during compressor off cycle.Refrigeration Capacity Suction A
35
<50
25
38
5
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.
 Table 16—Freezer Unit Cooler
Test description
Unit cooler air entering dry-bulb, °F
Unit cooler air entering relative 
                             humidity, %
Saturated suction temp, °F
Liquid inlet saturation temp, °F
Liquid inlet subcooling temp, °F
Compressor 
                             capacity
Test objectiveOff Cycle Fan Power
−10
<50



Compressor Off
Measure fan input power during compressor off cycle.Refrigeration Capacity Suction A
−10
<50
−20
38
5
Compressor On
Determine Net Refrigeration Capacity of Unit Cooler.Defrost
−10
Various



Compressor Off
Test according to Appendix C Section C11.
 *Success of the application for Waiver and interim Waiver will:*
                     Ensure that manufacturers of CO2
                     Direct Expansion Unit Coolers in Medium and Low Temperature application can continue to participate in the market. *What economic hardship and/or competitive disadvantage is likely to result absent a favorable determination on the Application for Waiver and Interim Waiver*
                    —Economic hardship will be loss of sales due to not meeting the DOE requirements set forth. *Conclusion:* Heat Transfer Products Group respectfully requests that DOE grant this petition for a Waiver and Interim Waiver from DOE's current requirement to test CO2
                     direct expansion unit coolers. /s/ Michael Straub, Director, Engineering and Product Development.


# Footnotes

1.
    
                         The petition did not identify any of the information contained therein as confidential business information. Back to Citation
 1.
    
                         All references to EPCA in this document refer to the statute as amended through America's Water Infrastructure Act of 2018, Public Law 115-270 (Oct. 23, 2018). Back to Citation
 2.
    
                         For editorial reasons, upon codification in the U.S. Code, Part C was redesignated as Part A-1. Back to Citation
 3.
    
                         A notation in the form “HTPG, No.1” identifies a written submission: (1) Made by HTPG; and (2) recorded in document number 1 that is filed in the docket of this petition for waiver (Docket No. EERE-2020-BT-WAV-0025) and available at 
                        *http://www.regulations.gov/​docket?​D=​EERE-2020-BT-WAV-0025*. Back to Citation
 4.
    
                         The test procedure specifies the unit cooler refrigerant inlet condition in terms of a saturation temperature (the temperature at which it completes the condensation process in a condenser) and the subcooling temperature (additional reduction in temperature lower than the specified saturation temperature). For CO2, the critical temperature above which there cannot exist separate liquid and gas phases is below the saturation condition specified in the test procedure, hence the specified condition cannot be achieved. Back to Citation
 5.
    
                         Absolute pressure is the pressure measured relative to a complete vacuum; “psia” represents the absolute pressure in pounds per square inch. Back to Citation


BILLING CODE 6450-01-P BILLING CODE 6450-01-C [FR Doc. 2020-26322 Filed 12-22-20; 8:45 am]