Name: Roger Burger

Title: Site Business Manager

Company: TES Filer City Station Limited Partner

Sign Date: 9/1/2010

Name: Mark Horne

Title: Principal

Company: Environemntal Partners, Inc.

Sign Date: 9/1/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Filer City Station Section 114 Test Program - Unit 1 Boiler

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 24, 2011 Page 1 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Facility Information:

TES Filer City Station. LP

700 Mee Street

Filer City MI 49634

Contact: Todd Guenthardt

Phone: 231-723-6573

Fax: 231-723-4766

Email: taguenthardt@cmsenergy.com

Testing Company:

Environmental Partners, Inc.

305 Hoover Boulevard

Suite 200

Holland MI 49423

Contact:Mark A, Horne, PE

Phone: 616-928-9128

Fax: 616-928-9126

Email: mark.horne@enviro-partners.com

Air Permit Number:

MI-ROP-N1685-2008a

Permitted Source ID/Name:

50835 EUBOILER01 (Boiler 1)

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Boilers 1 is a spreader-stoker boilers fed with coal and any of the following fuels: wood and wood waste, 

construction demolition material, petroleum coke, tire derived fuel (TDF). The boiler utilizes a dry scrubber and is 

followed by a baghouse filter for particulate matter (PM) and sulfur dioxide (SO2) emissions control.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 2610100072 FRS #: 110000412054

SCC / Description 10100204 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Spreader Stoker (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Boiler 1 76 0 0 0 152 608 6 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Boiler 1 Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Propane

Boiler 1 Method 25A 3 120 0

Boiler 1 Co2 Method 3A CO2 3 120 0

Boiler 1 O2 Method 3A O2 3 120 0

Boiler 2 Carbon Monoxide Method 10 3 480 0

Regulation Description Compound Limit Unit

N/A - Optional information not included. 0

Thursday, February 24, 2011 Page 2 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

See attached test report.

Boiler 2 2,3,7,8-TCDD Method 23 3 480 0

Boiler 2 1,2,3,7,8-PeCDD Method 23 3 480 0

Boiler 2 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Boiler 2 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Boiler 2 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Boiler 2 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Boiler 2 OCDD Method 23 3 480 0

Boiler 2 2,3,7,8-TCDF Method 23 3 480 0

Boiler 2 1,2,3,7,8-PeCDF Method 23 3 480 0

Boiler 2 2,3,4,7,8-PeCDF Method 23 3 480 0

Boiler 2 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Boiler 2 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Boiler 2 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Boiler 2 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Boiler 2 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Boiler 2 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Boiler 2 OCDF Method 23 3 480 0

Boiler 2 Other TCDD Method 23 3 480 0

Boiler 2 Other PeCDD Method 23 3 480 0

Boiler 2 Other HxCDD Method 23 3 480 0

Boiler 2 Other HpCDD Method 23 3 480 0

Boiler 2 Other TCDF Method 23 3 480 0

Boiler 2 Other PeCDF Method 23 3 480 0

Boiler 2 Other HxCDF Method 23 3 480 0

Boiler 2 Other HpCDF Method 23 3 480 0

Boiler 2 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Boiler 2 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Boiler 2 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Boiler 2 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Boiler 2 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Boiler 2 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Boiler 2 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Boiler 2 Method 23 3 480 0

Boiler 2 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Boiler 2 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Boiler 2 Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Boiler 2 Method 25A 3 480 0

Boiler 2 Co2 Method 3A CO2 3 480 0

Boiler 2 O2 Method 3A O2 3 480 0

Thursday, February 24, 2011 Page 3 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Sampling / Stack Data Results Summary

Location Boiler 1 - Method 1 - 4

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 

AM

12:05:00 PM

Run Finish Time 9:05:00 AM 11:15:00 

AM

1:25:00 PM

Net Run Time, minutes 80 80 80

Dry Gas Meter Volume Sampled, dscf 26.606 25.694 26.911 26.404

Moisture Content of Stack Gas, % 11.09 11.50 10.83 11.140

Moisture Saturation at Stack Gas Temperature, % 56.32 56.45 56.92 56.563

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Average Stack Gas Temperature, °F 183.38 183.50 183.88 183.587

Dry Volumetric Flow Rate, dry scfm 89,373.6 89,015.6 89,771.5 89,386.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 125,508.0 125,564.7 125,753.7 125,608.800

Percent Isokinetic of Sampling Rate, % 38.9 37.7 39.2 38.600

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Boiler 1 - Method 10

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 

AM

12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 

AM

2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Thursday, February 24, 2011 Page 4 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Location Boiler 1 - Method 25A

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 

AM

12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 

AM

2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.57768 5.5 5.4 5.493

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Boiler 1 - Method 3A CO2

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 

AM

12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 

AM

2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Thursday, February 24, 2011 Page 5 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Location Boiler 1 - Method 3A O2

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 

AM

12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 

AM

2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Thursday, February 24, 2011 Page 6 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Emissions Summary

Process Run Data

Location: Boiler 1 - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 5.34E-02 5.20E-02 5.00E-02 0.052

ppm 5.65E+01 5.94E+01 5.96E+01 58.500

ppm@7%O2 5.13E+01 5.36E+01 5.34E+01 52.767

Location: Boiler 1 - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 1.09E-03 1.88E-03 6.00E-04 0.001

ppm 7.35E-01 1.37E+00 4.54E-01 0.853

ppm@7%O2 6.67E-01 1.24E+00 4.07E-01 0.771

Thursday, February 24, 2011 Page 7 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Boiler 1 Heat Input Million Btus/million BTU using O2 413.52 F-Factor 

Calculation

0

2 Boiler 1 Heat Input Million Btus/million BTU using O2 441.34 F-Factor 

Calculation

0

3 Boiler 1 Heat Input Million Btus/million BTU using O2 470.11 F-Factor 

Calculation

0

Run Name Value UOM Comments

Target

Value

1 Boiler 1 DRY SCRUBBER 20.96gal lime slurry flow 0

2 Boiler 1 DRY SCRUBBER 21 gal lime slurry flow 0

3 Boiler 1 DRY SCRUBBER 21.13gal lime slurry flow 0

1 Boiler 1 BAGHOUSE 5.46inches of water column 0

2 Boiler 1 BAGHOUSE 5.27inches of water column 0

3 Boiler 1 BAGHOUSE 5.33inches of water column 0

Run Name Value UOM Comments

1 Boiler 1 Fuel F-Factor 9509

2 Boiler 1 Fuel F-Factor 8917

3 Boiler 1 Fuel F-Factor 8496

Thursday, February 24, 2011 Page 8 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Sampling / Stack Data Results Detail

Location Boiler 1 - Method 1 - 4

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 AM 12:05:00 PM

Run Finish Time 9:05:00 AM 11:15:00 AM 1:25:00 PM

Net Traversing Points 16 16 16

Net Run Time, minutes 80 80 80

Nozzle Diameter, inches 0.235 0.235 0.235 0.235

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.944 0.944 0.944 0.944

Barometric Pressure, inches of Mercury 29.25 29.25 29.25 29.250

Average Orifice Meter Differential, inches H2O 1.60 1.60 1.60 1.600

Dry Gas Meter Volume Sampled, cubic feet 28.450 27.730 29.240 28.473

Average Dry Gas Meter Temperature, °F 63.14 68.00 71.57 67.570

Dry Gas Meter Volume Sampled, dscf 26.606 25.694 26.911 26.404

Total Moisture Liquid collected, g 70.5 71 69.5 70.333

Volume of Water Vapor, standard cubic feet 3.32 3.34 3.27 3.310

Moisture Content of Stack Gas, % 11.09 11.50 10.83 11.140

Moisture Saturation at Stack Gas Temperature, % 56.32 56.45 56.92 56.563

Dry Mole Fraction 0.8891 0.885 0.8917 0.889

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Carbon Monoxide & Nitrogen, % 81.1232 81.144 81.138 81.135

Fuel Factor 1.15 1.15 1.15

Dry Molecular Weight, lb/lb-Mole 30.35 30.36 30.37 30.360

Wet Molecular weight, lb/lb-Mole 28.98 28.94 29.03 28.983

Flue Gas Static Pressure, inches of H2O -0.62 -0.61 -0.58 -0.603

Absolute Flue Gas Pressure, inches of Mercury 29.20 29.21 29.21 29.207

Average Stack Gas Temperature, °F 183.38 183.50 183.88 183.587

Average Velocity Head, inches of H2O 1.1245921984

9035

1.124304222

82917

1.130493960

20472

1.126

Average Stack Gas Velocity, feet/second 66.40 66.43 66.53 66.453

Stack Cross-Sectional Area, square feet 31.503 31.503 31.503 31.503

Dry Volumetric Flow Rate, dry scfm 89,373.6 89,015.6 89,771.5 89,386.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 125,508.0 125,564.7 125,753.7 125,608.800

Percent Isokinetic of Sampling Rate, % 38.9 37.7 39.2 38.600

Percent Excess Air, % 35.2 34.5 33.7 34.467

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Round Duct Diameter, inches 76 76 76

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Thursday, February 24, 2011 Page 9 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Location Boiler 1 - Method 10

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 AM 12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 AM 2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Fuel Factor 1.15 1.15 1.15

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Analyzer Make TECO TECO TECO

Analyzer Model 48C 48C 48C

Analyzer Serial Number

Operating Range

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 31 32 33 32.000

Calibration Pre Zero Cylinder ID Zero Zero Zero

Calibration Pre Zero Cylinder Instrument Response 0 -0.2 0.2 0.000

Calibration Pre Zero Cylinder Bias -0.2 -0.4 0 -0.200

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CO Mid CO Mid CO Mid

Calibration Pre High Cylinder Instrument Response 51 50.7 51 50.900

Calibration Pre High Cylinder Bias -0.3 -0.6 -0.3 -0.400

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Zero Zero

Calibration Post Zero Cylinder Instrument Response -0.2 0.2 -0.3 -0.100

Calibration Post Zero Cylinder Bias -0.4 0 -0.5 -0.300

Calibration Post Zero Cylinder Drift 0.2 0.4 0.5 0.367

Calibration Post High Cylinder ID CO Mid CO Mid CO Mid

Calibration Post High Cylinder Instrument Response 50.7 51 50.5 50.733

Calibration Post High Cylinder Bias -0.6 -0.3 -0.8 -0.567

Calibration Post High Cylinder Drift 0.3 0.3 0.5 0.367

Cavg 55.6 58.4 58.5 57.500

Cavg Units ppmvd ppmvd ppmvd

Cgas 56.5199 59.4 59.6 58.507

Cgas Units ppmvd ppmvd ppmvd

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw

Thursday, February 24, 2011 Page 10 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Location Boiler 1 - Method 25A

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 AM 12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 AM 2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.57768 5.5 5.4 5.493

Fuel Factor 1.15 1.15 1.15

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Analyzer Make JUM JUM JUM

Analyzer Model VE-7 VE7 VE7

Analyzer Serial Number

Operating Range

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 41 42 43 42.000

Calibration Pre Zero Cylinder ID Zero Zero Zero

Calibration Pre Zero Cylinder Instrument Response -0.2 -0.3 -0.3 -0.267

Calibration Pre Zero Cylinder Bias 0 -0.1 -0.1 -0.067

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID VOC Mid VOC Mid VOC Mid

Calibration Pre High Cylinder Instrument Response 51 50.9 50.7 50.867

Calibration Pre High Cylinder Bias 0 -0.1 -0.3 -0.133

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Zero Zero

Calibration Post Zero Cylinder Instrument Response -0.3 -0.3 -0.1 -0.233

Calibration Post Zero Cylinder Bias -0.1 -0.1 0.1 -0.033

Calibration Post Zero Cylinder Drift 0.1 0 0.2 0.100

Calibration Post High Cylinder ID VOC Mid VOC Mid VOC Mid

Calibration Post High Cylinder Instrument Response 50.9 50.7 50.6 50.733

Calibration Post High Cylinder Bias -0.1 -0.3 -0.4 -0.267

Calibration Post High Cylinder Drift 0.1 0.2 0.1 0.133

Cavg 0.4 0.9 0.2 0.500

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.7354 1.3665 0.4543 0.852

Cgas Units ppmvd ppmvd ppmvd

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0.6538085937

5

1.209393346

37965

0.405113077

679449

0.756

Cgasw Units ppmvw ppmvw ppmvw

Thursday, February 24, 2011 Page 11 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Location Boiler 1 - Method 3A CO2

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 AM 12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 AM 2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Fuel Factor 1.15 1.15 0

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1440C 1440C 1440C

Analyzer Serial Number

Operating Range

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 81 82 83 82.000

Calibration Pre Zero Cylinder ID Zero Zero Zero

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CO2 Mid CO2 Mid CO2 Mid

Calibration Pre High Cylinder Instrument Response 12 12 11.9 11.967

Calibration Pre High Cylinder Bias 0.42 0.42 0 0.280

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Zero Zero

Calibration Post Zero Cylinder Instrument Response 0 0 0.1 0.033

Calibration Post Zero Cylinder Bias 0 0 0.42 0.140

Calibration Post Zero Cylinder Drift 0 0 0.42 0.140

Calibration Post High Cylinder ID CO2 Mid CO2 Mid CO2 Mid

Calibration Post High Cylinder Instrument Response 12 11.9 12 11.967

Calibration Post High Cylinder Bias 0.42 0 0.42 0.280

Calibration Post High Cylinder Drift 0 0 0.42 0.140

Cavg 13.3 13.3 13.4 13.333

Cavg Units %vd %vd %vd

Cgas 13.3 13.3556 13.4622 13.373

Cgas Units %vd %vd %vd

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 24, 2011 Page 12 of 13
Filer City Station Section 114 Test Program - Unit 1 Boiler

9/1/2010

Location Boiler 1 - Method 3A O2

Average

Run Number 1 2 3

Test Date 6/10/2010 6/10/2010 6/10/2010

Run Start Time 7:45:00 AM 9:55:00 AM 12:05:00 PM

Run Finish Time 9:45:00 AM 11:55:00 AM 2:05:00 PM

Carbon Dioxide, % 13.3 13.356 13.462 13.373

Oxygen, % 5.5768 5.5 5.4 5.492

Fuel Factor 1.15 1.15 1.15

Dry Volumetric Flow Rate, dry scfm 89387.1 89015.6 89758 89,386.900

F-Factor, dscfm/MMBtu @ %O2 9534 8869 8559 8,987.333

Moisture, % 11.09 11.5 10.83 11.140

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1440C 1440C 1440C

Analyzer Serial Number

Operating Range

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 61 62 63 62.000

Calibration Pre Zero Cylinder ID Zero Zero Zero

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID O2 Mid O2 Mid O2 Mid

Calibration Pre High Cylinder Instrument Response 12.1 12 12 12.033

Calibration Pre High Cylinder Bias 0.4 0 0 0.133

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Zero Zero

Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID O2 Mid O2 Mid O2 Mid

Calibration Post High Cylinder Instrument Response 12 12 12 12.000

Calibration Post High Cylinder Bias 0 0 0 0.000

Calibration Post High Cylinder Drift 0.41 0 0 0.137

Cavg 5.6 5.5 5.4 5.500

Cavg Units %vd %vd %vd

Cgas 5.5768 5.5 5.4 5.492

Cgas Units %vd %vd %vd

Fuel Type

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 24, 2011 Page 13 of 13