Name: Daniel R. Wilkus

Title: Director, Air Programs

Company: Westar Energy, Inc.

Sign Date: 8/24/2010

Name: Chuck Bruffey

Title: Program Director

Company: Shaw Environmental & Infrastructur

Sign Date: 8/17/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, February 11, 2011 Page 1 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Facility Information:

Tecumseh Energy Center

2nd & Dupont Road

Tecumseh KS 66542

Contact: Kevin McCarthy

Phone: 785-575-1838

Fax: 785-575-1838

Email: kevin.mccarthy@westarenergy.com

Testing Company:

Shaw Environmental and Infrastructure Inc.

5050 Section Avenue

Cincinnati OH 45212

Contact:Chuck Bruffey

Phone: 513-782-4890

Fax: 513-782-4807

Email:

Air Permit Number:

2017700030

Permitted Source ID/Name:

1252 Tecumseh Energy Center--Boiler 9

Permitted Maximum Process Rate:

78 Megawatts

Max. Normal Operation Process Rate:

78 Megawatts

Target Process Test Rate

78 Magwatts

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Boiler 9 is a tangential-fired dry-bottom coal fired boiler with ESP system for particulate control.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 2017700030 FRS #: 110000596524

SCC / Description 10100226 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom Tangential (Subbituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Boiler 9 Stack 138 0 0 0 228 744 4 20

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Boiler 9 Stack Flowrate Method 1 - 4 3 480 0

Boiler 9 Stack % H2O Method 1 - 4 3 480 0

Boiler 9 Stack 2,3,7,8-TCDD Method 23 3 480 0

Boiler 9 Stack 1,2,3,7,8-PeCDD Method 23 3 480 0

Boiler 9 Stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Boiler 9 Stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

ICR per Section 114 of CAA 0

Friday, February 11, 2011 Page 2 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

No modifications proposed.

Boiler 9 Stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Boiler 9 Stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Boiler 9 Stack OCDD Method 23 3 480 0

Boiler 9 Stack 2,3,7,8-TCDF Method 23 3 480 0

Boiler 9 Stack 1,2,3,7,8-PeCDF Method 23 3 480 0

Boiler 9 Stack 2,3,4,7,8-PeCDF Method 23 3 480 0

Boiler 9 Stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Boiler 9 Stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Boiler 9 Stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Boiler 9 Stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Boiler 9 Stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Boiler 9 Stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Boiler 9 Stack OCDF Method 23 3 480 0

Boiler 9 Stack Total Dioxins Method 23 3 480 0

Boiler 9 Stack Total Furans Method 23 3 480 0

Boiler 9 Stack 3,3',4,4'-TCB (PCB77) Method 23 0

Boiler 9 Stack 3,4,4',5-TCB (PCB81) Method 23 0

Boiler 9 Stack 2,3,3',4,4'-PeCB (PCB105) Method 23 0

Boiler 9 Stack 2,3,4,4',5-PeCB (PCB114) Method 23 0

Boiler 9 Stack 2,3',4,4',5-PeCB (PCB118) Method 23 0

Boiler 9 Stack 2',3,4,4',5-PeCB (PCB123) Method 23 0

Boiler 9 Stack 3,3',4,4',5-PeCB (PCB126) Method 23 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Boiler 9 Stack Method 23 0

Boiler 9 Stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 0

Boiler 9 Stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Boiler 9 Stack Method 23 0

Boiler 9 Stack Total PCBs Method 23 3 480 0

Boiler 9 Stack Total TEQ Method 23 3 480 0

Boiler 9 Stack Co2 Method 3A CO2 3 480 0

Boiler 9 Stack O2 Method 3A O2 3 480 0

Friday, February 11, 2011 Page 3 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Sampling / Stack Data Results Summary

Location Boiler 9 Stack - Method 23

Average

Run Number WT9-DF-1 WT9-DF-2 WT9-DF-3

Test Date 3/10/2010 3/11/2010 3/12/2010

Run Start Time 8:50:00 AM 8:53:00 

AM

8:15:00 AM

Run Finish Time 5:27:00 PM 5:17:00 PM 4:46:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 292.696 308.877 305.575 302.383

Moisture Content of Stack Gas, % 10.56 10.64 10.60 10.600

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 12.3 12.4 12.6 12.433

Oxygen, % 5.8 5.4 5.6 5.600

Average Stack Gas Temperature, °F 282.50 285.20 276.00 281.233

Dry Volumetric Flow Rate, dry scfm 181,792.4 191,521.8 187,679.2 186,997.800

Actual Wet Volumetric Flue Gas Flow Rate, acfm 298,083.3 314,037.5 303,380.6 305,167.133

Percent Isokinetic of Sampling Rate, % 105.6 105.7 106.7 106.000

F-Factor, dscfm/MMBtu @ %O2 9647 9672 9671 9,663.333

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, February 11, 2011 Page 4 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Emissions Summary

Location: Boiler 9 Stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000000885 0.00000000813 0.0000000165 0.000

Elb/hr 7.27E-10 6.67E-10 1.34E-09 0.000

gr/dscf 4.67E-13 4.06E-13 8.33E-13 0.000

lb/mmBtuO2 8.90E-13 7.57E-13 1.57E-12 0.000

mg/dscm 1.07E-09 9.30E-10 1.91E-09 0.000

ng/dscm 1.07E-03 9.30E-04 1.91E-03 0.001

ng/dscm@7%O2 9.85E-04 8.34E-04 1.74E-03 0.001

pg/dscm 1.07E+00 9.30E-01 1.91E+00 1.303

pg/dscm@7%O2 9.85E-01 8.34E-01 1.74E+00 1.186

ppm 6.04E-11 5.26E-11 1.08E-10 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000647 0.0000000287 0.0000000945 0.000

Elb/hr 5.32E-09 2.35E-09 7.68E-09 0.000

gr/dscf 3.41E-12 1.43E-12 4.77E-12 0.000

lb/mmBtuO2 6.51E-12 2.67E-12 9.01E-12 0.000

mg/dscm 7.81E-09 3.28E-09 1.09E-08 0.000

ng/dscm 7.81E-03 3.28E-03 1.09E-02 0.007

ng/dscm@7%O2 7.19E-03 2.94E-03 9.90E-03 0.007

pg/dscm 7.81E+00 3.28E+00 1.09E+01 7.330

pg/dscm@7%O2 7.19E+00 2.94E+00 9.90E+00 6.677

ppm 4.59E-10 1.93E-10 6.42E-10 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000157 0.0000000208 0.000000026 0.000

Elb/hr 1.29E-09 1.71E-09 2.11E-09 0.000

gr/dscf 8.28E-13 1.04E-12 1.31E-12 0.000

lb/mmBtuO2 1.58E-12 1.94E-12 2.48E-12 0.000

mg/dscm 1.89E-09 2.38E-09 3.01E-09 0.000

ng/dscm 1.89E-03 2.38E-03 3.01E-03 0.002

ng/dscm@7%O2 1.74E-03 2.13E-03 2.73E-03 0.002

pg/dscm 1.89E+00 2.38E+00 3.01E+00 2.427

pg/dscm@7%O2 1.74E+00 2.13E+00 2.73E+00 2.200

ppm 1.11E-10 1.40E-10 1.77E-10 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000187 0.0000000145 0.00000003 0.000

Elb/hr 1.54E-09 1.19E-09 2.44E-09 0.000

gr/dscf 9.86E-13 7.24E-13 1.52E-12 0.000

lb/mmBtuO2 1.88E-12 1.35E-12 2.86E-12 0.000

mg/dscm 2.26E-09 1.66E-09 3.47E-09 0.000

Friday, February 11, 2011 Page 5 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

ng/dscm 2.26E-03 1.66E-03 3.47E-03 0.002

ng/dscm@7%O2 2.08E-03 1.49E-03 3.15E-03 0.002

pg/dscm 2.26E+00 1.66E+00 3.47E+00 2.463

pg/dscm@7%O2 2.08E+00 1.49E+00 3.15E+00 2.240

ppm 1.39E-10 1.02E-10 2.13E-10 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000124 0.0000000123 0.0000000237 0.000

Elb/hr 1.02E-09 1.01E-09 1.93E-09 0.000

gr/dscf 6.54E-13 6.15E-13 1.20E-12 0.000

lb/mmBtuO2 1.25E-12 1.14E-12 2.26E-12 0.000

mg/dscm 1.50E-09 1.41E-09 2.74E-09 0.000

ng/dscm 1.50E-03 1.41E-03 2.74E-03 0.002

ng/dscm@7%O2 1.38E-03 1.26E-03 2.49E-03 0.002

pg/dscm 1.50E+00 1.41E+00 2.74E+00 1.883

pg/dscm@7%O2 1.38E+00 1.26E+00 2.49E+00 1.710

ppm 9.60E-11 9.02E-11 1.76E-10 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000161 0.0000000125 0.0000000259 0.000

Elb/hr 1.32E-09 1.03E-09 2.10E-09 0.000

gr/dscf 8.49E-13 6.25E-13 1.31E-12 0.000

lb/mmBtuO2 1.62E-12 1.16E-12 2.47E-12 0.000

mg/dscm 1.94E-09 1.43E-09 2.99E-09 0.000

ng/dscm 1.94E-03 1.43E-03 2.99E-03 0.002

ng/dscm@7%O2 1.79E-03 1.28E-03 2.72E-03 0.002

pg/dscm 1.94E+00 1.43E+00 2.99E+00 2.120

pg/dscm@7%O2 1.79E+00 1.28E+00 2.72E+00 1.930

ppm 1.20E-10 8.79E-11 1.84E-10 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000106 0.0000000313 0.0000000202 0.000

Elb/hr 8.71E-10 2.57E-09 1.64E-09 0.000

gr/dscf 5.59E-13 1.56E-12 1.02E-12 0.000

lb/mmBtuO2 1.07E-12 2.91E-12 1.93E-12 0.000

mg/dscm 1.28E-09 3.58E-09 2.33E-09 0.000

ng/dscm 1.28E-03 3.58E-03 2.33E-03 0.002

ng/dscm@7%O2 1.18E-03 3.21E-03 2.12E-03 0.002

pg/dscm 1.28E+00 3.58E+00 2.33E+00 2.397

pg/dscm@7%O2 1.18E+00 3.21E+00 2.12E+00 2.170

ppm 8.21E-11 2.30E-10 1.50E-10 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000185 0.0000000144 0.0000000297 0.000

Elb/hr 1.52E-09 1.18E-09 2.41E-09 0.000

gr/dscf 9.75E-13 7.19E-13 1.50E-12 0.000

Friday, February 11, 2011 Page 6 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

lb/mmBtuO2 1.86E-12 1.34E-12 2.83E-12 0.000

mg/dscm 2.23E-09 1.65E-09 3.43E-09 0.000

ng/dscm 2.23E-03 1.65E-03 3.43E-03 0.002

ng/dscm@7%O2 2.05E-03 1.48E-03 3.12E-03 0.002

pg/dscm 2.23E+00 1.65E+00 3.43E+00 2.437

pg/dscm@7%O2 2.05E+00 1.48E+00 3.12E+00 2.217

ppm 1.37E-10 1.01E-10 2.11E-10 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000154 0.0000000153 0.0000000294 0.000

Elb/hr 1.27E-09 1.25E-09 2.39E-09 0.000

gr/dscf 8.12E-13 7.64E-13 1.48E-12 0.000

lb/mmBtuO2 1.55E-12 1.42E-12 2.80E-12 0.000

mg/dscm 1.86E-09 1.75E-09 3.40E-09 0.000

ng/dscm 1.86E-03 1.75E-03 3.40E-03 0.002

ng/dscm@7%O2 1.71E-03 1.57E-03 3.09E-03 0.002

pg/dscm 1.86E+00 1.75E+00 3.40E+00 2.337

pg/dscm@7%O2 1.71E+00 1.57E+00 3.09E+00 2.123

ppm 1.19E-10 1.12E-10 2.18E-10 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000352 0.0000000356 0.000000014 0.000

Elb/hr 2.89E-09 2.92E-09 1.14E-09 0.000

gr/dscf 1.86E-12 1.78E-12 7.07E-13 0.000

lb/mmBtuO2 3.54E-12 3.31E-12 1.33E-12 0.000

mg/dscm 4.25E-09 4.07E-09 1.62E-09 0.000

ng/dscm 4.25E-03 4.07E-03 1.62E-03 0.003

ng/dscm@7%O2 3.91E-03 3.65E-03 1.47E-03 0.003

pg/dscm 4.25E+00 4.07E+00 1.62E+00 3.313

pg/dscm@7%O2 3.91E+00 3.65E+00 1.47E+00 3.010

ppm 2.87E-10 2.75E-10 1.09E-10 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000000932 0.00000000632 0.0000000477 0.000

Elb/hr 7.66E-10 5.18E-10 3.88E-09 0.000

gr/dscf 4.91E-13 3.16E-13 2.41E-12 0.000

lb/mmBtuO2 9.37E-13 5.88E-13 4.55E-12 0.000

mg/dscm 1.12E-09 7.23E-10 5.51E-09 0.000

ng/dscm 1.12E-03 7.23E-04 5.51E-03 0.002

ng/dscm@7%O2 1.03E-03 6.48E-04 5.01E-03 0.002

pg/dscm 1.12E+00 7.23E-01 5.51E+00 2.451

pg/dscm@7%O2 1.03E+00 6.48E-01 5.01E+00 2.229

ppm 7.94E-11 5.11E-11 3.89E-10 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.000000239 0.000000029 0.0000000214 0.000

Friday, February 11, 2011 Page 7 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Elb/hr 1.96E-08 2.38E-09 1.74E-09 0.000

gr/dscf 1.26E-11 1.45E-12 1.08E-12 0.000

lb/mmBtuO2 2.40E-11 2.70E-12 2.04E-12 0.000

mg/dscm 2.88E-08 3.32E-09 2.47E-09 0.000

ng/dscm 2.88E-02 3.32E-03 2.47E-03 0.012

ng/dscm@7%O2 2.65E-02 2.98E-03 2.24E-03 0.011

pg/dscm 2.88E+01 3.32E+00 2.47E+00 11.530

pg/dscm@7%O2 2.65E+01 2.98E+00 2.24E+00 10.573

ppm 1.75E-09 2.01E-10 1.50E-10 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000896 0.000000157 0.00000016 0.000

Elb/hr 7.36E-07 1.29E-08 1.30E-08 0.000

gr/dscf 4.72E-10 7.84E-12 8.08E-12 0.000

lb/mmBtuO2 9.01E-10 1.46E-11 1.52E-11 0.000

mg/dscm 1.08E-06 1.80E-08 1.85E-08 0.000

ng/dscm 1.08E+00 1.80E-02 1.85E-02 0.372

ng/dscm@7%O2 9.94E-01 1.61E-02 1.68E-02 0.342

pg/dscm 1.08E+03 1.80E+01 1.85E+01 372.167

pg/dscm@7%O2 9.94E+02 1.61E+01 1.68E+01 342.300

ppm 0.000

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000702 0.00000418 0.00000226 0.000

Elb/hr 5.77E-07 3.43E-07 1.84E-07 0.000

gr/dscf 3.70E-10 2.09E-10 1.14E-10 0.000

lb/mmBtuO2 7.06E-10 3.89E-10 2.15E-10 0.000

mg/dscm 8.47E-07 4.78E-07 2.61E-07 0.000

ng/dscm 8.47E-01 4.78E-01 2.61E-01 0.529

ng/dscm@7%O2 7.80E-01 4.29E-01 2.37E-01 0.482

pg/dscm 8.47E+02 4.78E+02 2.61E+02 528.667

pg/dscm@7%O2 7.80E+02 4.29E+02 2.37E+02 482.000

ppm 0.000

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000713 0.00000403 0.00000183 0.000

Elb/hr 5.86E-07 3.31E-07 1.49E-07 0.000

gr/dscf 3.76E-10 2.01E-10 9.24E-11 0.000

lb/mmBtuO2 7.17E-10 3.75E-10 1.74E-10 0.000

mg/dscm 8.60E-07 4.61E-07 2.12E-07 0.000

ng/dscm 8.60E-01 4.61E-01 2.12E-01 0.511

ng/dscm@7%O2 7.92E-01 4.13E-01 1.93E-01 0.466

pg/dscm 8.60E+02 4.61E+02 2.12E+02 511.000

pg/dscm@7%O2 7.92E+02 4.13E+02 1.93E+02 466.000

ppm 5.73E-08 3.07E-08 1.41E-08 0.000

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

Friday, February 11, 2011 Page 8 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.000000865 0.000000455 0.000000236 0.000

Elb/hr 7.11E-08 3.73E-08 1.92E-08 0.000

gr/dscf 4.56E-11 2.27E-11 1.19E-11 0.000

lb/mmBtuO2 8.70E-11 4.24E-11 2.25E-11 0.000

mg/dscm 1.04E-07 5.20E-08 2.73E-08 0.000

ng/dscm 1.04E-01 5.20E-02 2.73E-02 0.061

ng/dscm@7%O2 9.57E-02 4.66E-02 2.48E-02 0.056

pg/dscm 1.04E+02 5.20E+01 2.73E+01 61.100

pg/dscm@7%O2 9.57E+01 4.66E+01 2.48E+01 55.700

ppm 0.000

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000255 0.0000149 0.0000109 0.000

Elb/hr 2.10E-06 1.22E-06 8.86E-07 0.000

gr/dscf 1.34E-09 7.44E-10 5.50E-10 0.000

lb/mmBtuO2 2.56E-09 1.39E-09 1.04E-09 0.000

mg/dscm 3.08E-06 1.70E-06 1.26E-06 0.000

ng/dscm 3.08E+00 1.70E+00 1.26E+00 2.013

ng/dscm@7%O2 2.84E+00 1.52E+00 1.14E+00 1.833

pg/dscm 3.08E+03 1.70E+03 1.26E+03 2,013.333

pg/dscm@7%O2 2.84E+03 1.52E+03 1.14E+03 1,833.333

ppm 0.000

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.000016 0.00000899 0.0000000197 0.000

Elb/hr 1.31E-06 7.37E-07 1.60E-09 0.000

gr/dscf 8.44E-10 4.49E-10 9.95E-13 0.000

lb/mmBtuO2 1.61E-09 8.37E-10 1.88E-12 0.000

mg/dscm 1.93E-06 1.03E-06 2.28E-09 0.000

ng/dscm 1.93E+00 1.03E+00 2.28E-03 0.987

ng/dscm@7%O2 1.78E+00 9.24E-01 2.07E-03 0.902

pg/dscm 1.93E+03 1.03E+03 2.28E+00 987.427

pg/dscm@7%O2 1.78E+03 9.24E+02 2.07E+00 902.023

ppm 0.000

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000124 0.0000000123 0.0000000236 0.000

Elb/hr 1.02E-09 1.01E-09 1.92E-09 0.000

gr/dscf 6.54E-13 6.15E-13 1.19E-12 0.000

lb/mmBtuO2 1.25E-12 1.14E-12 2.25E-12 0.000

mg/dscm 1.50E-09 1.41E-09 2.73E-09 0.000

ng/dscm 1.50E-03 1.41E-03 2.73E-03 0.002

ng/dscm@7%O2 1.38E-03 1.26E-03 2.48E-03 0.002

pg/dscm 1.50E+00 1.41E+00 2.73E+00 1.880

pg/dscm@7%O2 1.38E+00 1.26E+00 2.48E+00 1.707

ppm 9.60E-11 9.02E-11 1.75E-10 0.000

Friday, February 11, 2011 Page 9 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000000938 0.00000000635 0.0000000184 0.000

Elb/hr 7.71E-10 5.21E-10 1.49E-09 0.000

gr/dscf 4.95E-13 3.17E-13 9.29E-13 0.000

lb/mmBtuO2 9.43E-13 5.91E-13 1.75E-12 0.000

mg/dscm 1.13E-09 7.26E-10 2.13E-09 0.000

ng/dscm 1.13E-03 7.26E-04 2.13E-03 0.001

ng/dscm@7%O2 1.04E-03 6.51E-04 1.94E-03 0.001

pg/dscm 1.13E+00 7.26E-01 2.13E+00 1.329

pg/dscm@7%O2 1.04E+00 6.51E-01 1.94E+00 1.210

ppm 8.00E-11 5.13E-11 1.50E-10 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000104 0.00000000787 0.0000000134 0.000

Elb/hr 8.54E-10 6.45E-10 1.09E-09 0.000

gr/dscf 5.48E-13 3.93E-13 6.77E-13 0.000

lb/mmBtuO2 1.05E-12 7.33E-13 1.28E-12 0.000

mg/dscm 1.25E-09 9.00E-10 1.55E-09 0.000

ng/dscm 1.25E-03 9.00E-04 1.55E-03 0.001

ng/dscm@7%O2 1.15E-03 8.07E-04 1.41E-03 0.001

pg/dscm 1.25E+00 9.00E-01 1.55E+00 1.233

pg/dscm@7%O2 1.15E+00 8.07E-01 1.41E+00 1.122

ppm 9.37E-11 6.72E-11 1.16E-10 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000459 0.00000000651 0.00000000916 0.000

Elb/hr 3.77E-09 5.34E-10 7.44E-10 0.000

gr/dscf 2.42E-12 3.25E-13 4.63E-13 0.000

lb/mmBtuO2 4.62E-12 6.06E-13 8.73E-13 0.000

mg/dscm 5.54E-09 7.44E-10 1.06E-09 0.000

ng/dscm 5.54E-03 7.44E-04 1.06E-03 0.002

ng/dscm@7%O2 5.10E-03 6.67E-04 9.63E-04 0.002

pg/dscm 5.54E+00 7.44E-01 1.06E+00 2.448

pg/dscm@7%O2 5.10E+00 6.67E-01 9.63E-01 2.243

ppm 4.35E-10 5.85E-11 8.32E-11 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000771 0.000000109 0.0000000266 0.000

Elb/hr 6.33E-09 8.94E-09 2.16E-09 0.000

gr/dscf 4.07E-12 5.45E-12 1.34E-12 0.000

lb/mmBtuO2 7.75E-12 1.01E-11 2.54E-12 0.000

mg/dscm 9.30E-09 1.25E-08 3.07E-09 0.000

ng/dscm 9.30E-03 1.25E-02 3.07E-03 0.008

ng/dscm@7%O2 8.56E-03 1.12E-02 2.79E-03 0.008

pg/dscm 9.30E+00 1.25E+01 3.07E+00 8.290

pg/dscm@7%O2 8.56E+00 1.12E+01 2.79E+00 7.517

Friday, February 11, 2011 Page 10 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

ppm 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.000000028 0.0000000337 0.0000000242 0.000

Elb/hr 2.30E-09 2.76E-09 1.97E-09 0.000

gr/dscf 1.48E-12 1.68E-12 1.22E-12 0.000

lb/mmBtuO2 2.82E-12 3.14E-12 2.31E-12 0.000

mg/dscm 3.38E-09 3.85E-09 2.80E-09 0.000

ng/dscm 3.38E-03 3.85E-03 2.80E-03 0.003

ng/dscm@7%O2 3.11E-03 3.45E-03 2.54E-03 0.003

pg/dscm 3.38E+00 3.85E+00 2.80E+00 3.343

pg/dscm@7%O2 3.11E+00 3.45E+00 2.54E+00 3.033

ppm 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000261 0.0000000435 0.000000456 0.000

Elb/hr 2.14E-09 3.57E-09 3.70E-08 0.000

gr/dscf 1.38E-12 2.17E-12 2.30E-11 0.000

lb/mmBtuO2 2.62E-12 4.05E-12 4.35E-11 0.000

mg/dscm 3.15E-09 4.97E-09 5.27E-08 0.000

ng/dscm 3.15E-03 4.97E-03 5.27E-02 0.020

ng/dscm@7%O2 2.90E-03 4.46E-03 4.79E-02 0.018

pg/dscm 3.15E+00 4.97E+00 5.27E+01 20.273

pg/dscm@7%O2 2.90E+00 4.46E+00 4.79E+01 18.420

ppm 0.000

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000282 0.000000047 0.000000875 0.000

Elb/hr 2.32E-09 3.85E-09 7.11E-08 0.000

gr/dscf 1.49E-12 2.35E-12 4.42E-11 0.000

lb/mmBtuO2 2.84E-12 4.37E-12 8.34E-11 0.000

mg/dscm 3.40E-09 5.37E-09 1.01E-07 0.000

ng/dscm 3.40E-03 5.37E-03 1.01E-01 0.037

ng/dscm@7%O2 3.13E-03 4.82E-03 9.18E-02 0.033

pg/dscm 3.40E+00 5.37E+00 1.01E+02 36.590

pg/dscm@7%O2 3.13E+00 4.82E+00 9.18E+01 33.250

ppm 0.000

Compound: OCDD

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.000000136 0.0000000942 0.000000115 0.000

Elb/hr 1.12E-08 7.73E-09 9.34E-09 0.000

gr/dscf 7.17E-12 4.71E-12 5.81E-12 0.000

lb/mmBtuO2 1.37E-11 8.77E-12 1.10E-11 0.000

mg/dscm 1.64E-08 1.08E-08 1.33E-08 0.000

ng/dscm 1.64E-02 1.08E-02 1.33E-02 0.014

ng/dscm@7%O2 1.51E-02 9.69E-03 1.21E-02 0.012

Friday, February 11, 2011 Page 11 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

pg/dscm 1.64E+01 1.08E+01 1.33E+01 13.500

pg/dscm@7%O2 1.51E+01 9.69E+00 1.21E+01 12.297

ppm 8.58E-10 5.63E-10 6.95E-10 0.000

Compound: OCDF

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.000000113 0.0000000474 0.0000001 0.000

Elb/hr 9.28E-09 3.89E-09 8.12E-09 0.000

gr/dscf 5.96E-12 2.37E-12 5.05E-12 0.000

lb/mmBtuO2 1.14E-11 4.41E-12 9.53E-12 0.000

mg/dscm 1.36E-08 5.42E-09 1.16E-08 0.000

ng/dscm 1.36E-02 5.42E-03 1.16E-02 0.010

ng/dscm@7%O2 1.25E-02 4.86E-03 1.05E-02 0.009

pg/dscm 1.36E+01 5.42E+00 1.16E+01 10.207

pg/dscm@7%O2 1.25E+01 4.86E+00 1.05E+01 9.287

ppm 7.39E-10 2.94E-10 6.26E-10 0.000

Compound: Total Dioxins

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000020215 0.00000015467 0.0000001776 0.000

Elb/hr 1.66E-08 1.27E-08 1.44E-08 0.000

gr/dscf 1.07E-11 7.73E-12 8.97E-12 0.000

lb/mmBtuO2 2.03E-11 1.44E-11 1.69E-11 0.000

mg/dscm 2.44E-08 1.77E-08 2.05E-08 0.000

ng/dscm 2.44E-02 1.77E-02 2.05E-02 0.021

ng/dscm@7%O2 2.25E-02 1.59E-02 1.86E-02 0.019

pg/dscm 2.44E+01 1.77E+01 2.05E+01 20.867

pg/dscm@7%O2 2.25E+01 1.59E+01 1.86E+01 19.000

ppm 0.000

Compound: Total Furans

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.00000024532 0.00000012012 0.00000024553 0.000

Elb/hr 2.02E-08 9.85E-09 1.99E-08 0.000

gr/dscf 1.29E-11 6.00E-12 1.24E-11 0.000

lb/mmBtuO2 2.47E-11 1.12E-11 2.34E-11 0.000

mg/dscm 2.96E-08 1.37E-08 2.84E-08 0.000

ng/dscm 2.96E-02 1.37E-02 2.84E-02 0.024

ng/dscm@7%O2 2.72E-02 1.23E-02 2.58E-02 0.022

pg/dscm 2.96E+01 1.37E+01 2.84E+01 23.900

pg/dscm@7%O2 2.72E+01 1.23E+01 2.58E+01 21.767

ppm 0.000

Compound: Total PCBs

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000659 0.000033 0.0000168 0.000

Elb/hr 5.41E-06 2.71E-06 1.36E-06 0.000

gr/dscf 3.47E-09 1.65E-09 8.48E-10 0.000

lb/mmBtuO2 6.63E-09 3.07E-09 1.60E-09 0.000

mg/dscm 7.95E-06 3.77E-06 1.94E-06 0.000

Friday, February 11, 2011 Page 12 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Process Run Data

ng/dscm 7.95E+00 3.77E+00 1.94E+00 4.553

ng/dscm@7%O2 7.32E+00 3.38E+00 1.76E+00 4.153

pg/dscm 7.95E+03 3.77E+03 1.94E+03 4,553.333

pg/dscm@7%O2 7.32E+03 3.38E+03 1.76E+03 4,153.333

ppm 0.000

Compound: Total TEQ

Average

RunNumber WT9-DF-1 WT9-DF-2 WT9-DF-3

Mass_mg 0.0000000493 0.0000000418 0.0000000527 0.000

Elb/hr 4.05E-09 3.43E-09 4.28E-09 0.000

gr/dscf 2.60E-12 2.09E-12 2.66E-12 0.000

lb/mmBtuO2 4.96E-12 3.89E-12 5.02E-12 0.000

mg/dscm 5.95E-09 4.78E-09 6.09E-09 0.000

ng/dscm 5.95E-03 4.78E-03 6.09E-03 0.006

ng/dscm@7%O2 5.48E-03 4.29E-03 5.53E-03 0.005

pg/dscm 5.95E+00 4.78E+00 6.09E+00 5.607

pg/dscm@7%O2 5.48E+00 4.29E+00 5.53E+00 5.100

ppm 0.000

Friday, February 11, 2011 Page 13 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Gross Load 77 Megawatts

2 Gross Load 77.1 Megawatts

3 Gross Load 77.1 Megawatts

1 Steam Flow Rate 561.6 1000 lb/h 0

2 Steam Flow Rate 556.3 1000 lb/h 0

3 Steam Flow Rate 560.7 1000 lb/h 0

1 Gross Unit heat Rate 9942.3 BTU/KWh 0

2 Gross Unit heat Rate 9940.9 BTU/KWh 0

3 Gross Unit heat Rate 9834.9 BTU/KWh 0

Run Name Value UOM Comments

Target

Value

1 ELECTROSTATIC PRECIPITATOR 0 0

Friday, February 11, 2011 Page 14 of 15
Westar Energy Tecumseh Energy Center Boiler 9 Dioxin/Furan HAP Test Program

8/24/2010

Sampling / Stack Data Results Detail

Location Boiler 9 Stack - Method 23

Average

Run Number WT9-DF-1 WT9-DF-2 WT9-DF-3

Test Date 3/10/2010 3/11/2010 3/12/2010

Run Start Time 8:50:00 AM 8:53:00 AM 8:15:00 AM

Run Finish Time 5:27:00 PM 5:17:00 PM 4:46:00 PM

Net Traversing Points 20 20 20

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.246 0.246 0.246 0.246

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.977 0.977 0.977 0.977

Barometric Pressure, inches of Mercury 28.71 28.84 28.88 28.810

Average Orifice Meter Differential, inches H2O 1.22 1.31 1.26 1.263

Dry Gas Meter Volume Sampled, cubic feet 307.320 314.173 311.770 311.088

Average Dry Gas Meter Temperature, °F 61.35 47.45 49.65 52.817

Dry Gas Meter Volume Sampled, dscf 292.696 308.877 305.575 302.383

Total Moisture Liquid collected, g 734.5 781.4 769.7 761.867

Volume of Water Vapor, standard cubic feet 34.57 36.78 36.23 35.860

Moisture Content of Stack Gas, % 10.56 10.64 10.60 10.600

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8944 0.8936 0.894 0.894

Carbon Dioxide, % 12.3 12.4 12.6 12.433

Oxygen, % 5.8 5.4 5.6 5.600

Carbon Monoxide & Nitrogen, % 81.9 82.2 81.8 81.967

Fuel Factor 1.23 1.25 1.21

Dry Molecular Weight, lb/lb-Mole 30.20 30.20 30.24 30.213

Wet Molecular weight, lb/lb-Mole 28.91 28.90 28.94 28.917

Flue Gas Static Pressure, inches of H2O -0.31 -0.31 -0.31 -0.310

Absolute Flue Gas Pressure, inches of Mercury 28.69 28.82 28.86 28.790

Average Stack Gas Temperature, °F 282.50 285.20 276.00 281.233

Average Velocity Head, inches of H2O 0.4956109662

52861

0.550390358

361974

0.521541759

292242

0.523

Average Stack Gas Velocity, feet/second 47.83 50.39 48.68 48.967

Stack Cross-Sectional Area, square feet 103.869 103.869 103.869 103.869

Dry Volumetric Flow Rate, dry scfm 181,792.4 191,521.8 187,679.2 186,997.800

Actual Wet Volumetric Flue Gas Flow Rate, acfm 298,083.3 314,037.5 303,380.6 305,167.133

Percent Isokinetic of Sampling Rate, % 105.6 105.7 106.7 106.000

Percent Excess Air, % 36.7 33.1 35.0 34.933

F-Factor, dscfm/MMBtu @ %O2 9647 9672 9671 9,663.333

Round Duct Diameter, inches 138 138 138

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, February 11, 2011 Page 15 of 15