Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

1695 4254 Consumers Energy Consumers Energy Colegal owner CoOne EnergyJackson Plaza MI 49201

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

B.C. Cobb 151 N. Causeway Muskegon MI 49445 151 N. Causeway Muskegon MI 49445

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

TRUE FALSE TRUE FALSE FALSE TRUE FALSE TRUE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE FALSE Prompt Deviation reporting per ROP, Semi-annual ROP deviation reports No PART IFacility and Fuel InformationBoiler Information

Page 4
Facility_Information

mationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guida

Page 5
Facility_Information

 entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design g

Page 6
Facility_Information

on.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesi

Page 7
Facility_Information

fficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperatu

Page 8
Facility_Information

) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency 

Page 9
Facility_Information

 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temp

Page 10
Facility_Information

9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000F

Page 11
Facility_Information

sign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (200

Page 12
Facility_Information

 the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicab

Page 13
Facility_Information

009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous c

Page 14
Facility_Information

:12650Assumed subbituminous coal 

Page 15
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

1695 1 Project Engineer Corwin Holm5177881756 es clholmes@cmsenergy FALSE .com

1695 2 Sr. Environmental Planner Katie Cunningham 5177683468 kmcunningham@cmsenergy TRUE .com

Page 16
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

1695 bituminous 20 26.4 Applicabble to Unit 4 and Unit 5Assumed Bituminous coal btu/lb c

1695 subbituminous 80 73.6 Applicabble to Unit4 and Unit 5Assumed Bituminous coal btu/lb co

Page 17
facility_coal_utilized

Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800

Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800

Page 18
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

Page 19
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

Page 20
facility_other_materials

rcra_explain

Page 21
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

1695 4 Tangential firing Wet Bottomcoal 1378.3 1656 167

1695 5 Tangential firing Wet Bottomcoal 1378.3 1623 167.5

Page 22
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

156 89.33 83 2000 2024 1 1 FALSE

156 89.33 85.3 2000 2004 1 1 FALSE

Page 23
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 7585 67.18 N 2025 FALSE

FALSE 7745 73.48 N 2025 FALSE

Page 24
boiler_information

NOx_controlSO2_controlcombustion_additives

No Yes No

Yes Yes No

Page 25
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

1695 4 coal - bituminous2009 20 26.4

1695 4 coal - subbituminous 2009 80 73.6

1695 5 coal - bituminous2009 20 26.4

1695 5 coal - subbituminous 2009 80 73.6

Page 26
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

1695 5 Low NOx Burner 2/1/2001

Page 27
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

1695 4 Low Sulfur Coal 12/1/1985

1695 5 Low Sulfur Coal 12/1/1985

Page 28
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

Page 29
facility_units

facility_id unit_id

1695 Unit 4

1695 Unit 5

Page 30
unit_boilers

facility_id unit_id boiler_id

1695 Unit 4 4

1695 Unit 5 5

Page 31
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

1695 BCC4-ESPPM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 12/1/2000

1695 BCC5-ESPPM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 12/1/2000

Page 32
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

Page 33
facility_sampling_ports

facility_id sampling_port_id

1695 BCC4-Port

1695 BCC5-Port

Page 34
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

1695 BCC45- CombinedStack 650 20.8

Page 35
configurations

facility_id configuration_id

1695 BCCobb4-Conf

1695 BCCobb5-Conf

Page 36
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

1695 BCCobb4-Conf BCC45- CombinedStack 4 Stack

1695 BCCobb4-Conf BCC4-ESP 2 PM control

1695 BCCobb4-Conf BCC4-Port 3 Sampling Port

1695 BCCobb4-Conf Unit 4 1 Unit

1695 BCCobb5-Conf BCC45- CombinedStack 4 Stack

1695 BCCobb5-Conf BCC5-ESP 2 PM control

1695 BCCobb5-Conf BCC5-Port 3 Sampling Port

1695 BCCobb5-Conf Unit 5 1 Unit

Page 37
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

1695 BCCobb4-Conf PM (Filterable) Fderal - Title V Operating Permit 0.18 1 hour

1695 BCCobb4-Conf Sulur Dioxide (SO2) Federal - Title V Operating Permit 1.67 pound per million British Thermal Unit (lb/MMBtu) 30 days

1695 BCCobb5-Conf PM (Filterable) Fderal - Title V Operating Permit 0.18 1 hour

1695 BCCobb5-Conf Sulur Dioxide (SO2) Federal - Title V Operating Permit 1.67 pound per million British Thermal Unit (lb/MMBtu) 30 days

Page 38
configuration_pollutants1

avg_period_2emlimit_details test_methodemrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping

Limit Units= lbs per 1000 pounds exhaust gas, 50% excess air EPA Method 17 No not availableStack Testing, CAM Plan required Monitoring, Stack Test Results, monthly PM av

No not availableCEMs Operate and Maintain CEMs per P

limit units are: lb/1000 lbs exhaust gas, corrected to 50% excess air EPA Method 17 No not availableStack Testing, CAM Plan required Monitoring, Stack Test Results, monthly PM av

No not availableCEMs Operate and Maintain CEMs per P

Page 39
configuration_pollutants1

req_reporting

Stack Test Report Submission, promt deviation reporting, Quarterly EER for COMs, Semi-annual monitoring deviation and dow

Quarterly EER for CEMs, Semi-annual monitoring deviation and downtime.

Stack Test Report Submission, promt deviation reporting, Quarterly EER for COMs, Semi-annual monitoring deviation and dow

Quarterly EER for CEMs, Semi-annual monitoring deviation and downtime.

Page 40
configuration_pollutants1

annual monitoring deviation and downtime.

annual monitoring deviation and downtime.

Page 41
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

Page 42
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

Page 43
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

Page 44
control_technologies

feed_rate_units

Page 45
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

Page 46
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

Page 47
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

Page 48
control_costs

CBI

Page 49
misc_controls

facility_id misc_control_id control_description

Page 50
misc_control_configurations

facility_id misc_control_id configuration_id

Page 51
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

1695 BW 5/1/2009 98830.22 short tons (2000 lbs) coal MT

1695 BX 6/1/2009 146779.9 short tons (2000 lbs) coal MT

1695 BY 7/1/2009 97907.19 short tons (2000 lbs) coal MT

1695 BZ 8/1/2009 49565.93 short tons (2000 lbs) coal MT

1695 CA 9/1/2009 49892.19 short tons (2000 lbs) coal MT

1695 CB 10/1/2009 146156.1 short tons (2000 lbs) coal MT

1695 CC 11/1/2009 97113.78 short tons (2000 lbs) coal MT

1695 L 5/1/2009 52762.42 short tons (2000 lbs) coal WV

1695 M 6/1/2009 48515.85 short tons (2000 lbs) coal WV

1695 N 7/1/2009 24232 short tons (2000 lbs) coal WV

1695 O 8/1/2009 24926.03 short tons (2000 lbs) coal WV

1695 P 9/1/2009 24932.92 short tons (2000 lbs) coal WV

1695 Q 10/1/2009 25720.31 short tons (2000 lbs) coal WV

1695 R 11/1/2009 24920.87 short tons (2000 lbs) coal WV

Page 52
fuel_shipments

coal_seam shipment_method

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Ship

Page 53
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

1695 BW BCCobb4-Conf

1695 BW BCCobb5-Conf

1695 BX BCCobb4-Conf

1695 BX BCCobb5-Conf

1695 BY BCCobb4-Conf

1695 BY BCCobb5-Conf

1695 BZ BCCobb4-Conf

1695 BZ BCCobb5-Conf

1695 CA BCCobb4-Conf

1695 CA BCCobb5-Conf

1695 CB BCCobb4-Conf

1695 CB BCCobb5-Conf

1695 CC BCCobb4-Conf

1695 CC BCCobb5-Conf

1695 L BCCobb4-Conf

1695 L BCCobb5-Conf

1695 M BCCobb4-Conf

1695 M BCCobb5-Conf

1695 N BCCobb4-Conf

1695 N BCCobb5-Conf

1695 O BCCobb4-Conf

1695 O BCCobb5-Conf

1695 P BCCobb4-Conf

1695 P BCCobb5-Conf

1695 Q BCCobb4-Conf

1695 Q BCCobb5-Conf

1695 R BCCobb4-Conf

1695 R BCCobb5-Conf

Page 54
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

Page 55
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

Page 56
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Page 57
fuel_shipment_samples

analysis_copies

Page 58
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

Page 59
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

1695 BCC4 - 2006 PM Testing compliance Required Particulate testing per ROP 9/27/2006 No No

1695 BCC4 - 2009 PMTesting compliance Particulate Matter testing per ROP 9/2/2009 No No

1695 BCC4 - Hg CEMs Performance other Vendor Performance Guarentee RATA test for Hg CEMs to meet engineering study 1/30/2008 No No performance guarentees

1695 BCC5 - 2009 PM Testing compliance PM Testing requried by 9/1/2009 ROP No No

1695 BCC5 - Hg CEMs Performance Guarentee other Vendor Performance Guarentee RATA test for Hg CEMs to meet engineering study 1/29/2008 No No performance guarentees

1695 BCC5-2006 PM Testing compliance PM Testing requried by 7/19/2006 ROP No No

Page 60
test_reports

deviation_reports

No

No

No

No

No

No

Page 61
test_report_configurations

facility_id report_id configuration_id

1695 BCC4 - 2006 PM Testing BCCobb4-Conf

1695 BCC4 - 2009 PMTesting BCCobb4-Conf

1695 BCC4 - Hg CEMs Performance BCCobb4-Conf

1695 BCC5 - 2009 PM Testing BCCobb5-Conf

1695 BCC5 - Hg CEMs Performance Guarentee BCCobb5-Conf

1695 BCC5-2006 PM Testing BCCobb5-Conf

Page 62
test_report_fuels

facility_id report_id fuel_id

1695 BCC4 - 2006 PM Testing coal

1695 BCC4 - 2009 PMTesting coal

1695 BCC4 - Hg CEMs Performance coal

1695 BCC5 - 2009 PM Testing coal

1695 BCC5 - Hg CEMs Performance Guarentee coal

1695 BCC5-2006 PM Testing coal

Page 63
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

Page 64
cem_data

facility_id time_periodcem_period_description

1695 2005-2009

Page 65
cem_data_pollutants1

facility_id time_periodpollutant_name

1695 2005-2009 Sulfur Dioxide (SO2)

1695 2005-2009 Nitrogen Oxide (NOx)

Page 66
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

1695 BCC4 - 2006 PM Testing BCC4-Port No No

1695 BCC4 - 2009 PMTesting BCC4-Port No No

1695 BCC4 - Hg CEMs Performance BCC4-Port No No

1695 BCC5 - 2009 PM Testing BCC5-Port No No

1695 BCC5 - Hg CEMs Performance Guarentee BCC5-Port No No

1695 BCC5-2006 PM Testing BCC5-Port No No

Page 67
test_report_sampling

fg_fraction

Page 68
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

1695 BCC4 - 2006 PM Testing BCC4-Port 1 9/27/2006 9/27/2006 131 11.1

1695 BCC4 - 2006 PM Testing BCC4-Port 2 9/27/2006 9/27/2006 131 11.3

1695 BCC4 - 2006 PM Testing BCC4-Port 3 9/27/2006 9/27/2006 131 11.5

1695 BCC4 - 2006 PM Testing BCC4-Port average 9/27/2006 9/27/2006 131 11.3

1695 BCC4 - 2009 PMTesting BCC4-Port 1 9/2/2009 9/2/2009 168 10.4

1695 BCC4 - 2009 PMTesting BCC4-Port 2 9/2/2009 9/2/2009 168 10.4

1695 BCC4 - 2009 PMTesting BCC4-Port 3 9/2/2009 9/2/2009 168 10.4

1695 BCC4 - 2009 PMTesting BCC4-Port average 9/2/2009 9/2/2009 168 10.4

1695 BCC4 - Hg CEMs Performance BCC4-Port average 1/30/2008 1/31/2008

1695 BCC5 - 2009 PM Testing BCC5-Port 1 9/1/2009 9/1/2009 169 10.4

1695 BCC5 - 2009 PM Testing BCC5-Port 2 9/1/2009 9/1/2009 169 10.1

1695 BCC5 - 2009 PM Testing BCC5-Port 3 9/1/2009 9/1/2009 168 10

1695 BCC5 - 2009 PM Testing BCC5-Port average 9/1/2009 9/1/2009 169 10.2

1695 BCC5 - Hg CEMs Performance Guarentee BCC5-Port average 1/29/2008 1/31/2008

1695 BCC5-2006 PM Testing BCC5-Port 1 7/19/2006 7/19/2006 164 11.1

1695 BCC5-2006 PM Testing BCC5-Port 2 7/19/2006 7/19/2006 164 10.9

1695 BCC5-2006 PM Testing BCC5-Port 3 7/20/2006 7/20/2006 165 12.9

1695 BCC5-2006 PM Testing BCC5-Port average 7/19/2006 7/20/2006 164 11.6

Page 69
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

294760 dscfm 4.88 14.5 1

289864 dscfm 4.91 14.63 1

290691 dscfm 4.86 14.71 1

291772 dscfm 4.88 14.61 1

383821 dscfm 5.41 13.86 1

394508 dscfm 5.46 13.88 1

393167 dscfm 5.56 13.74 1

390499 dscfm 5.48 13.83 1

383114 dscfm 5.95 13.49 1

388111 dscfm 6.01 13.84 1

378823 dscfm 5.9 13.6 1

383349 dscfm 5.95 13.54 1

354903 dscfm 4.96 14.36 1

360572 dscfm 5.06 14.43 1

347759 dscfm 4.54 14.64 1

383349 dscfm 4.85 14.48 1

Page 70
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

17 flue gas temp=310 12062

17 flue gas temp=311F 12062

17 flue gas temp=311F 12062

Method 17 Flue Gas Temp was 310F 12062

17 flue gas temp=309F 111985

17 flue gas temp=313F

17 flue gas temp=314F 11985

Method 17 Flue gas temp was 312F 11985

30B

17 flue gas temp=307F 12368

17 flue gas temp=311F 12368

17 flue gas temp 12368

Method 17 Flue gas temperature was 310F. 12368

30B

17 flue gas temp=308

17 flue gas temp=308F 11953

17 flue gas temp=308F 12287

Method 17 Flue gas temp was 308F 12064

Page 71
sampling_runs

fuel_sulfur

Page 72
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

1695 BCC4 - 2006 PM Testing BCC4-Port 1 PM (Filterable) 0.0218 FALSE

1695 BCC4 - 2006 PM Testing BCC4-Port 2 PM (Filterable) 0.0252 FALSE

1695 BCC4 - 2006 PM Testing BCC4-Port 3 PM (Filterable) 0.0225 FALSE

1695 BCC4 - 2009 PMTesting BCC4-Port 1 PM (Filterable) 0.0714 FALSE

1695 BCC4 - 2009 PMTesting BCC4-Port 2 PM (Filterable) 0.1023 FALSE

1695 BCC4 - 2009 PMTesting BCC4-Port 3 PM (Filterable) 0.1271 FALSE

1695 BCC5 - 2009 PM Testing BCC5-Port 1 PM (Filterable) 0.0778 FALSE

1695 BCC5 - 2009 PM Testing BCC5-Port 2 PM (Filterable) 0.0852 FALSE

1695 BCC5 - 2009 PM Testing BCC5-Port 3 PM (Filterable) 0.0518 FALSE

1695 BCC5-2006 PM Testing BCC5-Port 1 PM (Filterable) 0.0898 FALSE

1695 BCC5-2006 PM Testing BCC5-Port 2 PM (Filterable) 0.1376 FALSE

1695 BCC5-2006 PM Testing BCC5-Port 3 PM (Filterable) 0.127 FALSE

1695 BCC4 - 2006 PM Testing BCC4-Port average PM (Filterable) 0.0232 TRUE

1695 BCC4 - 2009 PMTesting BCC4-Port average PM (Filterable) 0.1002 FALSE

1695 BCC4 - Hg CEMs Performance BCC4-Port average Total Mercury (Hgt) 2.089 FALSE

1695 BCC5-2006 PM Testing BCC5-Port average PM (Filterable) 0.1181 FALSE

1695 BCC5 - 2009 PM Testing BCC5-Port average PM (Filterable) 0.0716 FALSE

1695 BCC5 - Hg CEMs Performance Guarentee BCC5-Port average Total Mercury (Hgt) 1.181 FALSE

Page 73
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

37.98 pound per hour (lb/hr) FALSE 0.0267 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas

43.08 pound per hour (lb/hr) FALSE 0.0305 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas

38.77 pound per hour (lb/hr) FALSE 0.0272 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas

155.41 pound per hour (lb/hr) FALSE 0.0877 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas

228.02 pound per hour (lb/hr) FALSE 0.125 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas

280.67 pound per hour (lb/hr) FALSE 0.1559 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas

163.08 pound per hour (lb/hr) FALSE 0.0947 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas

179.75 pound per hour (lb/hr) FALSE 0.1027 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas

107.38 pound per hour (lb/hr) FALSE 0.0625 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas

187.18 pound per hour (lb/hr) FALSE 0.1102 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas

288.87 pound per hour (lb/hr) FALSE 0.1666 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas

269.6 pound per hour (lb/hr) FALSE 0.1589 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas

39.94 pound per hour (lb/hr) FALSE 0.0281 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas

221.37 pound per hour (lb/hr) FALSE 0.1228 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhaust gas

FALSE FALSE ug/wscm

248.55 pound per hour (lb/hr) FALSE 0.1452 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhaust gas

150.07 pound per hour (lb/hr) FALSE 0.0866 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhaust gas

FALSE FALSE ug/wscm

Page 74
sampling_run_pollutants1

run_pollutant_comment

lbs/1000lbs exhuast gas

lbs/1000lbs exhuast gas

lbs/1000lbs exhaust gas

lbs/1000 lbs exhuast gas

lbs/1000 lbs exhuast gas

lbs/1000 lbs exhuast gas

lbs/1000lbs exhaust gas

lbs/1000lbs exhaust gas

lbs/1000lbs exhaust gas

lbs/1000lbs exhaust gas

lbs/1000lbs exhaust gas

lbs/1000 lbs exhuast gas

lbs/1000 lbs exhuast gas

lbs/1000 lbs exhaust gas

lbs/1000 lbs exhaust gas

lbs/1000 lbs exhaust gas

Page 75
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

Page 76
sampling_run_fuel

fuel_conc_MDL

Page 77