### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Friday, January 28, 2011 Page 1 of 22

### Facility Information:

J K Spruce
145 Navarro Street

San Antonio TX 78296 Contact:
Phone:
Fax:
Email: Testing Company:
Weston Solutions 1625 Pumphrey Ave

Auburn Al 36832 Contact: Greg Sims
Phone: 334-466-5600
Fax: 334-466-5660
Email: Gregory.Sims@WestonSolutions.com

Air Permit Number: Permitted Source ID/Name: JK Spruce Unit 1 BLR1
Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: See Attached Report Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
Stack 307 4728 2832 4 0 16 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Formaldehyde Method 0011 3 0 Stack 2,3,7,8-TCDD Method 23 3 0 Stack 1,2,3,7,8-PeCDD Method 23 3 0 Stack 1,2,3,4,7,8-HxCDD Method 23 3 0 Stack 1,2,3,6,7,8-HxCDD Method 23 3 0 Stack 1,2,3,7,8,9-HxCDD Method 23 3 0 Stack 1,2,3,4,6,7,8-HpCDD Method 23 3 0 Stack OCDD Method 23 3 0 Stack



### Friday, January 28, 2011 Page 2 of 22

### The following describes any modifications and/or deviations to the applicable test

methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. See attached report

2,3,7,8-TCDF Method 23 3 0 Stack 1,2,3,7,8-PeCDF Method 23 3 0 Stack 2,3,4,7,8-PeCDF Method 23 3 0 Stack 1,2,3,4,7,8-HxCDF Method 23 3 0 Stack 1,2,3,6,7,8-HxCDF Method 23 3 0 Stack 2,3,4,6,7,8-HxCDF Method 23 3 0 Stack 1,2,3,7,8,9-HxCDF Method 23 3 0 Stack 1,2,3,4,6,7,8-HpCDF Method 23 3 0 Stack 1,2,3,4,7,8,9-HpCDF Method 23 3 0 Stack OCDF Method 23 3 0 Stack 3,3',4,4'-TCB (PCB77) Method 23 3 0 Stack 3,4,4',5-TCB (PCB81) Method 23 3 0 Stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 0 Stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 0 Stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 0 Stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 0 Stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 0 Stack 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 0 Stack

2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 0 Stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 0 Stack 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 0 Stack

Total organic compounds

(TOC) as Propane Method 25A 3 0 Stack

Hydrogen Chloride Method 26A 3 0 Stack Hydrogen Fluoride Method 26A 3 0 Stack Antimony Method 29 3 0 Stack Selenium Method 29 3 0 Stack Arsenic Method 29 3 0 Stack Beryllium Method 29 3 0 Stack Cadmium Method 29 3 0 Stack Chromium Method 29 3 0 Stack Cobalt Method 29 3 0 Stack Manganese Method 29 3 0 Stack Nickel Method 29 3 0 Stack Lead Method 29 3 0 Stack Filterable Particulate Method 29 3 0 Stack Organic Condensible

Particulate Method 5/OTM-28 3 0 Stack

Filterable Particulate Method 5/OTM-28 3 0 Stack Inorganic (Aqueous)

Condensible Part. Method 5/OTM-28 3 0 Stack



### Friday, January 28, 2011 Page 3 of 22

### Sampling / Stack Data Results Summary



### Location Stack - Method 0011 Average
Run Number 1 2 3
Test Date 5/10/2010 5/11/2010 5/11/2010
Run Start Time 11:00:00 AM 8:00:00 AM 12:56:00 PM

Run Finish Time 3:12:00 PM 10:28:00 AM 4:26:00 PM

Net Run Time, minutes 128 128 128 Dry Gas Meter Volume Sampled, dscf 72.050 74.422 73.013 73.162 Moisture Content of Stack Gas, % 19.39 19.61 19.28 19.427 Moisture Saturation at Stack Gas Temperature, % 18.95 19.28 19.30 19.177 Carbon Dioxide, % 15 15 15 15.000 Oxygen, % 4.5 4.5 4.5 4.500 Average Stack Gas Temperature, °F 137.09 137.75 137.65 137.497 Dry Volumetric Flow Rate, dry scfm 1,220,732.0 1,235,113.6 1,221,128.6 1,225,658.06 7 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,773,777.5 1,804,003.6 1,789,507.4 1,789,096.16 7 Percent Isokinetic of Sampling Rate, % 98.5 100.6 99.8 99.633 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000
Fw 10640 10640 10640 10,640.000
Fc 1800 1800 1800 1,800.000



### Friday, January 28, 2011 Page 4 of 22

### Location Stack - Method 23 Average

Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location Stack - Method 25A Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Friday, January 28, 2011 Page 5 of 22

### Location Stack - Method 26A Average

Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location Stack - Method 29 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Friday, January 28, 2011 Page 6 of 22

### Location Stack - Method 5/OTM-28 Average

Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Friday, January 28, 2011 Page 7 of 22

### Emissions Summary



### Location: Stack - Method 0011 Compound: Formaldehyde Average RunNumber 1 2 3 Mass_mg 0.02 0.009 0.02 0.016 lb/mmBtuO2 7.63E-06 3.32E-06 7.53E-06 0.000 ppm 7.85E-03 3.42E-03 7.75E-03 0.006 ppm@7%O2 6.65E-03 2.90E-03 6.57E-03 0.005



### Location: Stack - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000069 0.0000000018 0.0000000019 0.000 lb/mmBtuO2 6.99E-13 1.83E-13 1.89E-13 0.000 ng/dscm 8.54E-04 2.24E-04 2.31E-04 0.000 ng/dscm@7%O2 7.61E-04 2.00E-04 2.06E-04 0.000


### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.000000032 0.0000000071 0.000000011 0.000 lb/mmBtuO2 3.24E-12 7.24E-13 1.09E-12 0.000 ng/dscm 3.96E-03 8.85E-04 1.34E-03 0.002 ng/dscm@7%O2 3.53E-03 7.89E-04 1.19E-03 0.002


### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000031 0.0000000024 0.0000000023 0.000 lb/mmBtuO2 3.14E-13 2.45E-13 2.29E-13 0.000 ng/dscm 3.84E-04 2.99E-04 2.79E-04 0.000 ng/dscm@7%O2 3.42E-04 2.66E-04 2.49E-04 0.000


### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000046 0.0000000022 0.0000000022 0.000 lb/mmBtuO2 4.66E-13 2.24E-13 2.19E-13 0.000 ng/dscm 5.70E-04 2.74E-04 2.67E-04 0.000 ng/dscm@7%O2 5.08E-04 2.44E-04 2.38E-04 0.000


### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000032 0.0000000034 0.000000011 0.000 lb/mmBtuO2 3.24E-13 3.47E-13 1.09E-12 0.000 ng/dscm 3.96E-04 4.24E-04 1.34E-03 0.001 ng/dscm@7%O2 3.53E-04 3.78E-04 1.19E-03 0.001



### Friday, January 28, 2011 Page 8 of 22

### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000047 0.0000000023 0.0000000029 0.000 lb/mmBtuO2 4.76E-13 2.34E-13 2.88E-13 0.000 ng/dscm 5.82E-04 2.87E-04 3.52E-04 0.000 ng/dscm@7%O2 5.19E-04 2.56E-04 3.14E-04 0.000


### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000038 0.0000000021 0.0000000068 0.000 lb/mmBtuO2 3.85E-13 2.14E-13 6.76E-13 0.000 ng/dscm 4.71E-04 2.62E-04 8.26E-04 0.001 ng/dscm@7%O2 4.20E-04 2.33E-04 7.36E-04 0.000


### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000044 0.0000000021 0.0000000025 0.000 lb/mmBtuO2 4.46E-13 2.14E-13 2.48E-13 0.000 ng/dscm 5.45E-04 2.62E-04 3.04E-04 0.000 ng/dscm@7%O2 4.86E-04 2.33E-04 2.71E-04 0.000


### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000035 0.0000000024 0.0000000022 0.000 lb/mmBtuO2 3.54E-13 2.45E-13 2.19E-13 0.000 ng/dscm 4.33E-04 2.99E-04 2.67E-04 0.000 ng/dscm@7%O2 3.86E-04 2.66E-04 2.38E-04 0.000


### Compound: 1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000055 0.0000000026 0.0000000022 0.000 lb/mmBtuO2 5.57E-13 2.65E-13 2.19E-13 0.000 ng/dscm 6.81E-04 3.24E-04 2.67E-04 0.000 ng/dscm@7%O2 6.07E-04 2.89E-04 2.38E-04 0.000


### Compound: 1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000063 0.0000000045 0.0000000062 0.000 lb/mmBtuO2 6.38E-13 4.59E-13 6.16E-13 0.000 ng/dscm 7.80E-04 5.61E-04 7.53E-04 0.001 ng/dscm@7%O2 6.95E-04 5.00E-04 6.71E-04 0.001


### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.0000047 0.0000044 0.0003 0.000 lb/mmBtuO2 4.76E-10 4.48E-10 2.98E-08 0.000



### Friday, January 28, 2011 Page 9 of 22ng/dscm 5.82E-01 5.48E-01 3.65E+01 12.543 ng/dscm@7%O2 5.19E-01 4.88E-01 3.25E+01 11.169


### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.0000056 0.0000056 0.0043 0.001 lb/mmBtuO2 5.67E-10 5.71E-10 4.27E-07 0.000 ng/dscm 6.93E-01 6.98E-01 5.23E+02 174.797 ng/dscm@7%O2 6.17E-01 6.22E-01 4.66E+02 155.746


### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.00049 0.00042 0.0083 0.003 lb/mmBtuO2 4.96E-08 4.28E-08 8.25E-07 0.000 ng/dscm 6.07E+01 5.23E+01 1.01E+03 374.333 ng/dscm@7%O2 5.41E+01 4.66E+01 9.00E+02 333.567


### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.0000055 0.0000055 0.0011 0.000 lb/mmBtuO2 5.57E-10 5.61E-10 1.09E-07 0.000 ng/dscm 6.81E-01 6.85E-01 1.34E+02 45.122 ng/dscm@7%O2 6.07E-01 6.10E-01 1.19E+02 40.072


### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.0000079 0.000023 0.00047 0.000 lb/mmBtuO2 8.00E-10 2.34E-09 4.67E-08 0.000 ng/dscm 9.78E-01 2.87E+00 5.71E+01 20.316 ng/dscm@7%O2 8.71E-01 2.56E+00 5.09E+01 18.110


### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.0015 0.0012 0.019 0.007 lb/mmBtuO2 1.52E-07 1.22E-07 1.89E-06 0.000 ng/dscm 1.86E+02 1.50E+02 2.31E+03 882.000 ng/dscm@7%O2 1.66E+02 1.34E+02 2.06E+03 786.667


### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.0000081 0.000015 0.00023 0.000 lb/mmBtuO2 8.20E-10 1.53E-09 2.29E-08 0.000 ng/dscm 1.00E+00 1.87E+00 2.79E+01 10.257 ng/dscm@7%O2 8.91E-01 1.67E+00 2.49E+01 9.154


### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3



### Friday, January 28, 2011 Page 10 of 22Mass_mg 0.0000000041 0.0000000024 0.0000000045 0.000 lb/mmBtuO2 4.15E-13 2.45E-13 4.47E-13 0.000 ng/dscm 5.08E-04 2.99E-04 5.47E-04 0.000 ng/dscm@7%O2 4.53E-04 2.66E-04 4.87E-04 0.000


### Compound: 2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000063 0.0000000043 0.0000000059 0.000 lb/mmBtuO2 6.38E-13 4.38E-13 5.86E-13 0.000 ng/dscm 7.80E-04 5.36E-04 7.17E-04 0.001 ng/dscm@7%O2 6.95E-04 4.78E-04 6.39E-04 0.001


### Compound: 2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.0000000047 0.0000000028 0.0000000034 0.000 lb/mmBtuO2 4.76E-13 2.85E-13 3.38E-13 0.000 ng/dscm 5.82E-04 3.49E-04 4.13E-04 0.000 ng/dscm@7%O2 5.19E-04 3.11E-04 3.68E-04 0.000


### Compound: 2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000029 0.0000000067 0.0000000054 0.000 lb/mmBtuO2 2.94E-13 6.83E-13 5.37E-13 0.000 ng/dscm 3.59E-04 8.35E-04 6.56E-04 0.001 ng/dscm@7%O2 3.20E-04 7.44E-04 5.85E-04 0.001


### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.0000057 0.0000057 0.0000068 0.000 lb/mmBtuO2 5.77E-10 5.81E-10 6.76E-10 0.000 ng/dscm 7.06E-01 7.10E-01 8.26E-01 0.747 ng/dscm@7%O2 6.29E-01 6.33E-01 7.36E-01 0.666


### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.0000089 0.000008 0.0000087 0.000 lb/mmBtuO2 9.01E-10 8.15E-10 8.65E-10 0.000 ng/dscm 1.10E+00 9.97E-01 1.06E+00 1.052 ng/dscm@7%O2 9.80E-01 8.88E-01 9.44E-01 0.937


### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.0000079 0.0000068 0.0000085 0.000 lb/mmBtuO2 8.00E-10 6.93E-10 8.45E-10 0.000 ng/dscm 9.78E-01 8.47E-01 1.03E+00 0.952 ng/dscm@7%O2 8.71E-01 7.55E-01 9.18E-01 0.848



### Friday, January 28, 2011 Page 11 of 22

### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.0000077 0.0000085 0.000011 0.000 lb/mmBtuO2 7.80E-10 8.66E-10 1.09E-09 0.000 ng/dscm 9.53E-01 1.06E+00 1.34E+00 1.118 ng/dscm@7%O2 8.49E-01 9.44E-01 1.19E+00 0.994


### Compound: OCDD Average RunNumber 1 2 3 Mass_mg 0.0000000034 0.0000000039 0.0000000032 0.000 lb/mmBtuO2 3.44E-13 3.97E-13 3.18E-13 0.000 ng/dscm 4.21E-04 4.86E-04 3.89E-04 0.000 ng/dscm@7%O2 3.75E-04 4.33E-04 3.47E-04 0.000


### Compound: OCDF Average RunNumber 1 2 3 Mass_mg 0.0000000031 0.000000003 0.0000000038 0.000 lb/mmBtuO2 3.14E-13 3.06E-13 3.78E-13 0.000 ng/dscm 3.84E-04 3.74E-04 4.62E-04 0.000 ng/dscm@7%O2 3.42E-04 3.33E-04 4.12E-04 0.000



### Location: Stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 0.00E+00 1.40E-04 0.00E+00 0.000 ppm 0.00E+00 9.84E-02 0.00E+00 0.033 ppm@7%O2 0.00E+00 8.34E-02 0.00E+00 0.028



### Location: Stack - Method 26A Compound: Hydrogen Chloride Average RunNumber 1 2 3 Mass_mg 0.0874 0.12 0.0843 0.097 lb/mmBtuO2 6.67E-05 9.59E-05 6.61E-05 0.000 ppm 5.18E-02 7.39E-02 5.33E-02 0.060 ppm@7%O2 4.80E-02 6.89E-02 4.75E-02 0.055


### Compound: Hydrogen Fluoride Average RunNumber 1 2 3 Mass_mg 0.0732 0.068 0.0498 0.064 lb/mmBtuO2 5.59E-05 5.43E-05 3.90E-05 0.000 ppm 7.90E-02 7.63E-02 5.74E-02 0.071 ppm@7%O2 7.32E-02 7.12E-02 5.11E-02 0.065



### Location: Stack - Method 29 Compound: Antimony Average


### Friday, January 28, 2011 Page 12 of 22RunNumber 1 2 3 Mass_mg 0.0012 0.0012 0.0012 0.001 lb/mmBtuO2 2.54E-07 2.42E-07 2.44E-07 0.000 mg/dscm 2.98E-04 3.01E-04 3.04E-04 0.000 mg/dscm@7%O2 2.76E-04 2.63E-04 2.66E-04 0.000


### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.0012 0.0012 0.0012 0.001 lb/mmBtuO2 2.54E-07 2.42E-07 2.44E-07 0.000 mg/dscm 2.98E-04 3.01E-04 3.04E-04 0.000 mg/dscm@7%O2 2.76E-04 2.63E-04 2.66E-04 0.000


### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.0003 0.0003 0.0003 0.000 lb/mmBtuO2 6.34E-08 6.04E-08 6.10E-08 0.000 mg/dscm 7.45E-05 7.53E-05 7.60E-05 0.000 mg/dscm@7%O2 6.90E-05 6.58E-05 6.64E-05 0.000


### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.00075 0.00192 0.00068 0.001 lb/mmBtuO2 1.59E-07 3.86E-07 1.38E-07 0.000 mg/dscm 1.86E-04 4.82E-04 1.72E-04 0.000 mg/dscm@7%O2 1.72E-04 4.21E-04 1.50E-04 0.000


### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.00135 0.00124 0.0012 0.001 lb/mmBtuO2 2.85E-07 2.50E-07 2.44E-07 0.000 mg/dscm 3.35E-04 3.11E-04 3.04E-04 0.000 mg/dscm@7%O2 3.10E-04 2.72E-04 2.66E-04 0.000


### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.0003 0.0003 0.0003 0.000 lb/mmBtuO2 6.34E-08 6.04E-08 6.10E-08 0.000 mg/dscm 7.45E-05 7.53E-05 7.60E-05 0.000 mg/dscm@7%O2 6.90E-05 6.58E-05 6.64E-05 0.000


### Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 7 7 4 6.000 lb/mmBtuO2 1.48E-03 1.41E-03 8.13E-04 0.001 mg/dscm 1.74E+00 1.76E+00 1.01E+00 1.503 mg/dscm@7%O2 1.61E+00 1.54E+00 8.83E-01 1.344



### Friday, January 28, 2011 Page 13 of 22

### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.00177 0.00128 0.00158 0.002 lb/mmBtuO2 3.74E-07 2.58E-07 3.21E-07 0.000 mg/dscm 4.40E-04 3.21E-04 4.00E-04 0.000 mg/dscm@7%O2 4.08E-04 2.81E-04 3.50E-04 0.000


### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.00398 0.0027 0.00238 0.003 lb/mmBtuO2 8.41E-07 5.43E-07 4.84E-07 0.000 mg/dscm 9.89E-04 6.77E-04 6.03E-04 0.001 mg/dscm@7%O2 9.16E-04 5.92E-04 5.27E-04 0.001


### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 0.00588 0.00159 0.00395 0.004 lb/mmBtuO2 1.24E-06 3.20E-07 8.03E-07 0.000 mg/dscm 1.46E-03 3.99E-04 1.00E-03 0.001 mg/dscm@7%O2 1.35E-03 3.49E-04 8.74E-04 0.001


### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.0064 0.003 0.0035 0.004 lb/mmBtuO2 1.35E-06 6.04E-07 7.11E-07 0.000 mg/dscm 1.59E-03 7.53E-04 8.86E-04 0.001 mg/dscm@7%O2 1.47E-03 6.58E-04 7.75E-04 0.001



### Location: Stack - Method 5/OTM-28 Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 18.1 18.1 21.8 19.333 lb/mmBtuO2 3.98E-03 3.84E-03 4.81E-03 0.004 mg/dscm 4.68E+00 4.78E+00 5.99E+00 5.150 mg/dscm@7%O2 4.34E+00 4.18E+00 5.24E+00 4.587


### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber 1 2 3 Mass_mg 6.3 9.3 5.8 7.133 lb/mmBtuO2 1.39E-03 1.97E-03 1.28E-03 0.002 mg/dscm 1.63E+00 2.46E+00 1.59E+00 1.893 mg/dscm@7%O2 1.51E+00 2.15E+00 1.39E+00 1.683


### Compound: Organic Condensible Particulate Average RunNumber 1 2 3 Mass_mg 7 5.3 2.7 5.000



### Friday, January 28, 2011 Page 14 of 22

### Process Run Data lb/mmBtuO2 1.54E-03 1.12E-03 5.95E-04 0.001 mg/dscm 1.81E+00 1.40E+00 7.42E-01 1.317 mg/dscm@7%O2 1.68E+00 1.22E+00 6.49E-01 1.183



### Friday, January 28, 2011 Page 15 of 22

### Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 Gross Electric Output 0 MW 0

Run Name Value UOM Comments 

### 1 Coal Fuel Analysis 0 Btu/lb

Friday, January 28, 2011 Page 16 of 22

### Sampling / Stack Data Results Detail



### Location Stack - Method 0011 Average Run Number 1 2 3 Test Date 5/10/2010 5/11/2010 5/11/2010 Run Start Time 11:00:00 AM 8:00:00 AM 12:56:00 PM Run Finish Time 3:12:00 PM 10:28:00 AM 4:26:00 PM Net Traversing Points 32 32 31 Net Run Time, minutes 128 128 128 Nozzle Diameter, inches 0.21 0.21 0.21 0.210 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.99 0.99 0.99 0.990 Barometric Pressure, inches of Mercury 28.8 28.8 28.7 28.767 Average Orifice Meter Differential, inches H2O 1.14 1.21 1.18 1.177 Dry Gas Meter Volume Sampled, cubic feet 77.597 80.461 79.566 79.208 Average Dry Gas Meter Temperature, °F 83.47 85.66 88.06 85.730 Dry Gas Meter Volume Sampled, dscf 72.050 74.422 73.013 73.162 Total Moisture Liquid collected, g 368.1 385.6999999 99999 370.6 374.800

Volume of Water Vapor, standard cubic feet 17.33 18.15 17.44 17.640 Moisture Content of Stack Gas, % 19.39 19.61 19.28 19.427 Moisture Saturation at Stack Gas Temperature, % 18.95 19.28 19.30 19.177 Dry Mole Fraction 0.8105 0.8072 0.8072 0.808 Carbon Dioxide, % 15 15 15 15.000 Oxygen, % 4.5 4.5 4.5 4.500 Carbon Monoxide & Nitrogen, % 80.5 80.5 80.5 80.500 Fuel Factor 1.09 1.09 1.09 Dry Molecular Weight, lb/lb-Mole 30.58 30.58 30.58 30.580 Wet Molecular weight, lb/lb-Mole 28.28 28.21 28.15 28.213 Flue Gas Static Pressure, inches of H2O -0.9 -0.9 -0.9 -0.900 Absolute Flue Gas Pressure, inches of Mercury 28.73 28.73 28.63 28.697 Average Stack Gas Temperature, °F 137.09 137.75 137.65 137.497 Average Velocity Head, inches of H2O 0.8727238788 12058 0.899333939

655068 0.880131315

034659 0.884

Average Stack Gas Velocity, feet/second 57.51 58.49 58.02 58.007 Stack Cross-Sectional Area, square feet 514.049 514.049 514.049 514.049 Dry Volumetric Flow Rate, dry scfm 1,220,732.0 1,235,113.6 1,221,128.6 1,225,658.0 67 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,773,777.5 1,804,003.6 1,789,507.4 1,789,096.1 67 Percent Isokinetic of Sampling Rate, % 98.5 100.6 99.8 99.633 Percent Excess Air, % 26.9 26.9 26.9 26.900 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Round Duct Diameter, inches 307 307 307 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Friday, January 28, 2011 Page 17 of 22

### Location Stack - Method 23 Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, January 28, 2011 Page 18 of 22

### Location Stack - Method 25A Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, January 28, 2011 Page 19 of 22

### Location Stack - Method 26A Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, January 28, 2011 Page 20 of 22

### Location Stack - Method 29 Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, January 28, 2011 Page 21 of 22

### Location Stack - Method 5/OTM-28 Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, January 28, 2011 Page 22 of 22