Facility _Information facility _id utility

_code legal_owner_name

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 1695 4254 Consumers Energy Co Consumers Energy

Co legal ownerOne Energy Plaza Jackson MI 49201

Page 1Facility _Information plant_name

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip B.C. Cobb 151 N. Causeway Muskegon MI 49445 151 N. Causeway Muskegon MI 49445

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas TRUE FALSE TRUE FALSE FALSE TRUE FALSE TRUE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE Prompt Deviation reporting per ROP, Semi-annual ROP deviation reports No PART IFacility and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 4Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 5Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 6Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 7Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 8Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 9Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 10Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 11Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 12Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 13Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 14Facility _Information PART IFacility

and Fuel InformationBoiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and put correct temp in to the Notes section.Unit 4 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9153 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1054FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 983FUnit5 :Original design gross efficiency (HHV) 11,000 Btu/lbmPresent operating gross efficiency (HHV)9139 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1047FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 997FBoiler FuelsOnly the previous 12 months of data (2009) was requested in the hardcopy ICR from EPA; therefore, only 2009 data was completed.Applicable to Unit 4 and Unit 5 Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal

Page 15facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 1695 1 Project Engineer Corwin Holmes

5177881756 clholmes@cmsenergy.com FALSE 1695 2 Sr. Environmental Planner Katie Cunningham

5177683468 kmcunningham@cmsenergy.com TRUE

Page 16facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 1695 bituminous 20 26.4 Applicabble to Unit 4 and Unit 5Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800 1695 subbituminous 80 73.6 Applicabble to Unit4 and Unit 5Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800

Page 17facility _coal_utilized Applicabble to Unit 4 and Unit 5Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800 Applicabble to Unit4 and Unit 5Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800

Page 18facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type

Page 19facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 20facility _other_materials rcra_explain

Page 21boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 1695 4 Tangential firing Wet Bottom coal 1378.3 1656 167 1695 5 Tangential firing Wet Bottom coal 1378.3 1623 167.5

Page 22boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 156 89.33 83 2000 2024 1 1 FALSE 156 89.33 85.3 2000 2004 1 1 FALSE

Page 23boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 7585 67.18 N 2025 FALSE FALSE 7745 73.48 N 2025 FALSE

Page 24boiler_information

NOx_control

SO2_control

combustion_additives No Yes No Yes Yes No

Page 25boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 1695 4 coal - bituminous2009 20 26.4 1695 4 coal - subbituminous 2009 80 73.6 1695 5 coal - bituminous2009 20 26.4 1695 5 coal - subbituminous 2009 80 73.6

Page 26boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 1695 5 Low NOx Burner 2/1/2001

Page 27boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 1695 4 Low Sulfur Coal 12/1/1985 1695 5 Low Sulfur Coal 12/1/1985

Page 28boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 29facility _units facility _id unit_id 1695 Unit 4 1695 Unit 5

Page 30unit_boilers

facility _id unit_id boiler_id 1695 Unit 4 4 1695 Unit 5 5

Page 31facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 1695 BCC4-ESP PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 12/1/2000 1695 BCC5-ESP PM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 12/1/2000

Page 32facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 33facility _sampling_ports facility _id sampling_port_id 1695 BCC4-Port 1695 BCC5-Port

Page 34facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 1695 BCC45- CombinedStack 650 20.8

Page 35configurations

facility _id configuration_id 1695 BCCobb4-Conf 1695 BCCobb5-Conf

Page 36configuration_components

facility _id configuration_id

component_id

order component_type port_near 1695 BCCobb4-Conf

BCC45- CombinedStack

4 Stack 1695 BCCobb4-Conf

BCC4-ESP 2 PM control 1695 BCCobb4-Conf

BCC4-Port 3 Sampling Port 1695 BCCobb4-Conf

Unit 4 1 Unit 1695 BCCobb5-Conf

BCC45- CombinedStack

4 Stack 1695 BCCobb5-Conf

BCC5-ESP 2 PM control 1695 BCCobb5-Conf

BCC5-Port 3 Sampling Port 1695 BCCobb5-Conf

Unit 5 1 Unit

Page 37configuration_pollutants1

facility _id configuration_id

pollutant_name

permit_type_1

emlim it_1 emlim it_units_1 avg_period_1

emlim it_2 emlim it_units_2 1695 BCCobb4-Conf

PM (Filterable)

Fderal - Title V Operating Permit

0.18 1 hour 1695 BCCobb4-Conf

Sulur Dioxide (SO2)

Federal - Title V Operating Permit

1.67 pound per million British Thermal Unit (lb/MMBtu)

30 days 1695 BCCobb5-Conf

PM (Filterable)

Fderal - Title V Operating Permit

0.18 1 hour 1695 BCCobb5-Conf

Sulur Dioxide (SO2)

Federal - Title V Operating Permit

1.67 pound per million British Thermal Unit (lb/MMBtu)

30 days

Page 38configuration_pollutants1

avg_period_2

emlim it_details

test_method

emrate emrate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping Lim it Units= lbs per 1000 pounds exhaust gas, 50% excess air

EPA Method 17 No not available Stack Testing, CAM Plan required Monitoring, COMs

Stack Test Results, monthly PM average, CAM plan requriements No not available CEMs Operate and Maintain CEMs per Part 75 lim it units are: lb/1000 lbs exhaust gas, corrected to 50% excess air

EPA Method 17 No not available Stack Testing, CAM Plan required Monitoring, COMs

Stack Test Results, monthly PM average, CAM plan requriements No not available CEMs Operate and Maintain CEMs per Part 75

Page 39configuration_pollutants1

req_reporting Stack Test Report Submission, promt deviation reporting, Quarterly EER for COMs, Semi-annual monitoring deviation and downtime. Quarterly

EER for CEMs, Semi-annual monitoring deviation and downtime. Stack Test Report Submission, promt deviation reporting, Quarterly EER for COMs, Semi-annual monitoring deviation and downtime. Quarterly

EER for CEMs, Semi-annual monitoring deviation and downtime.

Page 40configuration_pollutants1 Stack Test Report Submission, promt deviation reporting, Quarterly EER for COMs, Semi-annual monitoring deviation and downtime. Stack Test Report Submission, promt deviation reporting, Quarterly EER for COMs, Semi-annual monitoring deviation and downtime.

Page 41control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 42control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 43control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 44control_technologies feed_rate_units

Page 45control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 46control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_name

Page 47control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investment

total_operating_costs

base_year

Page 48control_costs

CBI

Page 49misc_controls

facility _id misc_control_id

control_description

Page 50misc_control_configurations

facility _id misc_control_id

configuration_id

Page 51fuel_shipments

facility _id shipment_id

shipment_date

amount_received

amount_units

fuel_type state_country other_country

county 1695 BW 5/1/2009 98830.22 short tons (2000 lbs) coal MT 1695 BX 6/1/2009 146779.9 short tons (2000 lbs) coal MT 1695 BY 7/1/2009 97907.19 short tons (2000 lbs) coal MT 1695 BZ 8/1/2009 49565.93 short tons (2000 lbs) coal MT 1695 CA 9/1/2009 49892.19 short tons (2000 lbs) coal MT 1695 CB 10/1/2009 146156.1 short tons (2000 lbs) coal MT 1695 CC 11/1/2009 97113.78 short tons (2000 lbs) coal MT 1695 L 5/1/2009 52762.42 short tons (2000 lbs) coal WV 1695 M 6/1/2009 48515.85 short tons (2000 lbs) coal WV 1695 N 7/1/2009 24232 short tons (2000 lbs) coal WV 1695 O 8/1/2009 24926.03 short tons (2000 lbs) coal WV 1695 P 9/1/2009 24932.92 short tons (2000 lbs) coal WV 1695 Q 10/1/2009 25720.31 short tons (2000 lbs) coal WV 1695 R 11/1/2009 24920.87 short tons (2000 lbs) coal WV

Page 52fuel_shipments

coal_seam shipment_method

Ship Ship Ship Ship Ship Ship Ship Ship Ship Ship Ship Ship Ship Ship

Page 53fuel_shipment_configurations

facility _id shipment_id

configuration_id 1695 BW BCCobb4-Conf 1695 BW BCCobb5-Conf 1695 BX BCCobb4-Conf 1695 BX BCCobb5-Conf 1695 BY BCCobb4-Conf 1695 BY BCCobb5-Conf 1695 BZ BCCobb4-Conf 1695 BZ BCCobb5-Conf 1695 CA BCCobb4-Conf 1695 CA BCCobb5-Conf 1695 CB BCCobb4-Conf 1695 CB BCCobb5-Conf 1695 CC BCCobb4-Conf 1695 CC BCCobb5-Conf 1695 L BCCobb4-Conf 1695 L BCCobb5-Conf 1695 M BCCobb4-Conf 1695 M BCCobb5-Conf 1695 N BCCobb4-Conf 1695 N BCCobb5-Conf 1695 O BCCobb4-Conf 1695 O BCCobb5-Conf 1695 P BCCobb4-Conf 1695 P BCCobb5-Conf 1695 Q BCCobb4-Conf 1695 Q BCCobb5-Conf 1695 R BCCobb4-Conf 1695 R BCCobb5-Conf

Page 54fuel_shipment_samples

facility _id shipment_id

sample_id amount_fuel amount_fuel_units

total_sulfur ash_content heating_value

hating_units

Page 55fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address

Page 56fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_name lab_address lab_city lab_state lab_zip analysis_copies

Page 57fuel_shipment_samples analysis_copies

Page 58fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 59test_reports

facility _id report_id report_typeother_type report_description report_begin_date

report_end_date

before_control

during_deviation 1695 BCC4 - 2006 PM Testing

compliance Required Particulate testing per ROP 9/27/2006 No No 1695 BCC4 - 2009 PMTesting

compliance Particulate Matter testing per ROP 9/2/2009 No No 1695 BCC4 - Hg CEMs Performance

other Vendor Performance Guarentee RATA test for Hg CEMs to meet engineering study performance guarentees 1/30/2008 No No 1695 BCC5 - 2009 PM Testing

compliance PM Testing requried by ROP 9/1/2009 No No 1695 BCC5 - Hg CEMs Performance Guarentee

other Vendor Performance Guarentee RATA test for Hg CEMs to meet engineering study performance guarentees 1/29/2008 No No 1695 BCC5-2006 PM Testing

compliance PM Testing requried by ROP 7/19/2006 No No

Page 60test_reports

deviation_reports No No No No No No

Page 61test_report_configurations

facility _id report_id configuration_id 1695 BCC4 - 2006 PM Testing

BCCobb4-Conf 1695 BCC4 - 2009 PMTesting

BCCobb4-Conf 1695 BCC4 - Hg CEMs Performance

BCCobb4-Conf 1695 BCC5 - 2009 PM Testing

BCCobb5-Conf 1695 BCC5 - Hg CEMs Performance Guarentee

BCCobb5-Conf 1695 BCC5-2006 PM Testing

BCCobb5-Conf

Page 62test_report_fuels

facility _id report_id fuel_id 1695 BCC4 - 2006 PM Testing

coal 1695 BCC4 - 2009 PMTesting

coal 1695 BCC4 - Hg CEMs Performance

coal 1695 BCC5 - 2009 PM Testing

coal 1695 BCC5 - Hg CEMs Performance Guarentee

coal 1695 BCC5-2006 PM Testing

coal

Page 63test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type

Page 64cem_data

facility _id time_period

cem_period_description 1695 2005-2009

Page 65cem_data_pollutants1

facility _id time_period

pollutant_name 1695 2005-2009 Sulfur Dioxide (SO2) 1695 2005-2009 Nitrogen Oxide (NOx)

Page 66test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 1695 BCC4 - 2006 PM Testing

BCC4-Port No No 1695 BCC4 - 2009 PMTesting

BCC4-Port No No 1695 BCC4 - Hg CEMs Performance

BCC4-Port No No 1695 BCC5 - 2009 PM Testing

BCC5-Port No No 1695 BCC5 - Hg CEMs Performance Guarentee

BCC5-Port No No 1695 BCC5-2006 PM Testing

BCC5-Port No No

Page 67test_report_sampling

fg_fraction

Page 68sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetime

unit_load net_generation fg_moisture_content 1695 BCC4 - 2006 PM Testing

BCC4-Port 1 9/27/2006 9/27/2006 131 11.1 1695 BCC4 - 2006 PM Testing

BCC4-Port 2 9/27/2006 9/27/2006 131 11.3 1695 BCC4 - 2006 PM Testing

BCC4-Port 3 9/27/2006 9/27/2006 131 11.5 1695 BCC4 - 2006 PM Testing

BCC4-Port average 9/27/2006 9/27/2006 131 11.3 1695 BCC4 - 2009 PMTesting

BCC4-Port 1 9/2/2009 9/2/2009 168 10.4 1695 BCC4 - 2009 PMTesting

BCC4-Port 2 9/2/2009 9/2/2009 168 10.4 1695 BCC4 - 2009 PMTesting

BCC4-Port 3 9/2/2009 9/2/2009 168 10.4 1695 BCC4 - 2009 PMTesting

BCC4-Port average 9/2/2009 9/2/2009 168 10.4 1695 BCC4 - Hg CEMs Performance

BCC4-Port average 1/30/2008 1/31/2008 1695 BCC5 - 2009 PM Testing

BCC5-Port 1 9/1/2009 9/1/2009 169 10.4 1695 BCC5 - 2009 PM Testing

BCC5-Port 2 9/1/2009 9/1/2009 169 10.1 1695 BCC5 - 2009 PM Testing

BCC5-Port 3 9/1/2009 9/1/2009 168 10 1695 BCC5 - 2009 PM Testing

BCC5-Port average 9/1/2009 9/1/2009 169 10.2 1695 BCC5 - Hg CEMs Performance Guarentee

BCC5-Port average 1/29/2008 1/31/2008 1695 BCC5-2006 PM Testing

BCC5-Port 1 7/19/2006 7/19/2006 164 11.1 1695 BCC5-2006 PM Testing

BCC5-Port 2 7/19/2006 7/19/2006 164 10.9 1695 BCC5-2006 PM Testing

BCC5-Port 3 7/20/2006 7/20/2006 165 12.9 1695 BCC5-2006 PM Testing

BCC5-Port average 7/19/2006 7/20/2006 164 11.6

Page 69sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 294760 dscfm 4.88 14.5 1 289864 dscfm 4.91 14.63 1 290691 dscfm 4.86 14.71 1 291772 dscfm 4.88 14.61 1 383821 dscfm 5.41 13.86 1 394508 dscfm 5.46 13.88 1 393167 dscfm 5.56 13.74 1 390499 dscfm 5.48 13.83 1 383114 dscfm 5.95 13.49 1 388111 dscfm 6.01 13.84 1 378823 dscfm 5.9 13.6 1 383349 dscfm 5.95 13.54 1 354903 dscfm 4.96 14.36 1 360572 dscfm 5.06 14.43 1 347759 dscfm 4.54 14.64 1 383349 dscfm 4.85 14.48 1

Page 70sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 17 flue gas temp=310 12062 17 flue gas temp=311F 12062 17 flue gas temp=311F 12062 Method 17 Flue Gas Temp was 310F 12062 17 flue gas temp=309F 111985 17 flue gas temp=313F 17 flue gas temp=314F 11985 Method 17 Flue gas temp was 312F 11985 30B 17 flue gas temp=307F 12368 17 flue gas temp=311F 12368 17 flue gas temp 12368 Method 17 Flue gas temperature was 310F. 12368 30B 17 flue gas temp=308 17 flue gas temp=308F 11953 17 flue gas temp=308F 12287 Method 17 Flue gas temp was 308F 12064

Page 71sampling_runs

fuel_sulfur

Page 72sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_name conc conc_units conc_ND conc_MDL 1695 BCC4 - 2006 PM Testing

BCC4-Port 1 PM (Filterable) 0.0218 FALSE 1695 BCC4 - 2006 PM Testing

BCC4-Port 2 PM (Filterable) 0.0252 FALSE 1695 BCC4 - 2006 PM Testing

BCC4-Port 3 PM (Filterable) 0.0225 FALSE 1695 BCC4 - 2009 PMTesting

BCC4-Port 1 PM (Filterable) 0.0714 FALSE 1695 BCC4 - 2009 PMTesting

BCC4-Port 2 PM (Filterable) 0.1023 FALSE 1695 BCC4 - 2009 PMTesting

BCC4-Port 3 PM (Filterable) 0.1271 FALSE 1695 BCC5 - 2009 PM Testing

BCC5-Port 1 PM (Filterable) 0.0778 FALSE 1695 BCC5 - 2009 PM Testing

BCC5-Port 2 PM (Filterable) 0.0852 FALSE 1695 BCC5 - 2009 PM Testing

BCC5-Port 3 PM (Filterable) 0.0518 FALSE 1695 BCC5-2006 PM Testing

BCC5-Port 1 PM (Filterable) 0.0898 FALSE 1695 BCC5-2006 PM Testing

BCC5-Port 2 PM (Filterable) 0.1376 FALSE 1695 BCC5-2006 PM Testing

BCC5-Port 3 PM (Filterable) 0.127 FALSE 1695 BCC4 - 2006 PM Testing

BCC4-Port average PM (Filterable) 0.0232 TRUE 1695 BCC4 - 2009 PMTesting

BCC4-Port average PM (Filterable) 0.1002 FALSE 1695 BCC4 - Hg CEMs Performance

BCC4-Port average Total Mercury (Hgt) 2.089 FALSE 1695 BCC5-2006 PM Testing

BCC5-Port average PM (Filterable) 0.1181 FALSE 1695 BCC5 - 2009 PM Testing

BCC5-Port average PM (Filterable) 0.0716 FALSE 1695 BCC5 - Hg CEMs Performance Guarentee

BCC5-Port average Total Mercury (Hgt) 1.181 FALSE

Page 73sampling_run_pollutants1

emission_rate

emission_rate_units

emission_rate_ND

emission_rate_MDL

emission_factor

emission_factor_units

emission_factor_ND

emission_factor_MDL

run_pollutant_comment 37.98 pound per hour (lb/hr)

FALSE 0.0267 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 43.08 pound per hour (lb/hr)

FALSE 0.0305 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 38.77 pound per hour (lb/hr)

FALSE 0.0272 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 155.41 pound per hour (lb/hr)

FALSE 0.0877 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas 228.02 pound per hour (lb/hr)

FALSE 0.125 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas 280.67 pound per hour (lb/hr)

FALSE 0.1559 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas 163.08 pound per hour (lb/hr)

FALSE 0.0947 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 179.75 pound per hour (lb/hr)

FALSE 0.1027 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 107.38 pound per hour (lb/hr)

FALSE 0.0625 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 187.18 pound per hour (lb/hr)

FALSE 0.1102 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 288.87 pound per hour (lb/hr)

FALSE 0.1666 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 269.6 pound per hour (lb/hr)

FALSE 0.1589 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas 39.94 pound per hour (lb/hr)

FALSE 0.0281 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas 221.37 pound per hour (lb/hr)

FALSE 0.1228 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhaust gas FALSE FALSE ug/wscm 248.55 pound per hour (lb/hr)

FALSE 0.1452 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhaust gas 150.07 pound per hour (lb/hr)

FALSE 0.0866 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhaust gas FALSE FALSE ug/wscm

Page 74sampling_run_pollutants1 run_pollutant_comment lbs/1000lbs exhuast gas lbs/1000lbs exhuast gas lbs/1000lbs exhaust gas lbs/1000 lbs exhuast gas lbs/1000 lbs exhuast gas lbs/1000 lbs exhuast gas lbs/1000lbs exhaust gas lbs/1000lbs exhaust gas lbs/1000lbs exhaust gas lbs/1000lbs exhaust gas lbs/1000lbs exhaust gas lbs/1000 lbs exhuast gas lbs/1000 lbs exhuast gas lbs/1000 lbs exhaust gas lbs/1000 lbs exhaust gas lbs/1000 lbs exhaust gas

Page 75sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 76sampling_run_fuel fuel_conc_MDL

Page 77