### Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

- down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg +2

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg 0

### , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

- downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

### (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

### and , HgP, and Hg+2 

### . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

- down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please alsoEIA

Facility Code Facility Name Boiler ID

130 Santee Cooper - Cross Unit #1Control Device Configuraton

Listed (by

boiler) in Question 16 (page 17) of the questionnaireEIA

Facility Code Facility Name Boiler ID 130 Santee Cooper - CrossUnit #1

Run 1 5/2/2010 15:10 5/2/2010 Run 2 5/3/2010 9:05 5/3/2010 Run 3 5/3/2010 13:10 5/3/2010 Test End Date Run Number Test Start Date Test Start TimeMe asured Value (ppm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) 18:18 0.01 Dry U.S. EPA Method 316 BDL 12:18 0.01 Dry U.S. EPA Method 316 BDL 16:16 0.01 Dry U.S. EPA Method 316 BDL Formaldehyde Emission Test Results Test End TimeTest Method

Comments lb/mmBtu ppmdv @ 7% O 2 [<14.6] 1.01E-05 0.01 4537.93 5855 [<13.9] 1.02E-05 0.01 4503.19 5834 [<13.7] 1.03E-05 0.01 4499 5833 Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr)Fuel Input Rate Fuel Type Units of Me asure 14.4 11.13 8.31 1615933 149 460.87 bitum inous lb/hour 14.5 11.2 8.35 1612383 149.7 459 bitum inous lb/hour 14.3 10.92 8.5 1628117 148.8 459 bitum inous lb/hour Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas Moisture (%) Flue Gas

CO 2(%) Flue Gas

O 2(%)Me asurement

Method Fuel Input

Rate Fuel Type Units of Measure Me asurement

Method Fuel Input

Rate Fuel Type Units of

Me asure Other Other Other Fuel #2 Fuel #3Me asurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Other Supporting Information Fuel #4EIA

Facility Code Facility Name Boiler ID 130 Santee Cooper - Cross Unit #1

Run 1 5/2/2010 15:10 Run 2 5/3/2010 9:05 Run 3 5/3/2010 13:10

Run Number Test Start Date Test Start TimeMeasured Value (ppm) Basis (Wet or Dry)

5/2/2010 17:20 12.5 Dry 5/3/2010 11:10 12.5 Dry 5/3/2010 15:18 11.4 Dry Methane Emission Test Results
Test End Date Test End TimeTest Method Used Data Flag (ADL, BDL, DDL) Test Method Comments lb/mmBtu

U.S. EPA Method 18 ADL 5.08E-03 U.S. EPA Method 18 ADL 5.08E-03 U.S. EPA Method 18 ADL 4.63E-03 Methane Emission Test Results Calculated Emission Rateppmdv @ 7% O 2

13.8 4537.93 5855 14.4 11.13 8.31 1615933 13.84 4503.19 5834 14.5 11.2 8.35 1612383 12.78 4499 5833 14.3 10.92 8.5 1628117 Flue Gas Flow Rate (dscfm) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas CO 2(%) Flue Gas

O 2(%)Fuel Input Rate Fuel Type Units of

Me asure Measurement

Method Fuel

Input Rate Fuel Type Units of

Me asure
149 460.87 bitum inous lb/hour Other 149.7 459 bitum inous lb/hour Other 148.8 459 bitum inous lb/hour Other Flue Gas Temperat ure (F) Fuel #1 Fuel #2Me asurement

Method Fuel

Input Rate Fuel Type Units of

Me asure Measurement

Method Fuel

Input Rate Fuel Type Units of

Me asure Fuel #4 Fuel #3Me asurement

Method Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 130 Santee Cooper - Cross Unit #1

Run 1 5/4/2010 10:48 Run 2 5/4/2010 17:15 Run 3 5/4/2010 19:30

Run Number Test Start Date Test Start TimePlease note QA/QC documentation starting in Column "AI"

Measured Value (μg/dscm) Basis (Wet or Dry)

5/4/2010 12:48 0.15 Dry 5/4/2010 19:16 0.14 Dry 5/4/2010 21:30 0.15 Dry Total Vapor Phase Mercury Emission Test Results

Test End Time Test End DatePlease note QA/QC documentation starting in Column "AI"

Test Method Used Data Flag (ADL, BDL, DDL) Test Method

Comments (lb/mmBtu)

U.S. EPA Method 30B ADL 1.52E-07 4514 U.S. EPA Method 30B ADL 1.44E-07 4493 U.S. EPA Method 30B ADL 1.55E-07 4508 Total Vapor Phase Mercury Emission Test Results Steam Output (1000 lb/hr)Fuel Input Rate

5855 12.9 11.08 8.32 1681900 147.8 460.8 5833 12.8 10.99 8.47 1652433 147.6 459 5853 12.2 10.88 8.58 1693683 147.9 460.7 Flue Gas Moisture (%) Total Heat Input (mmBtu/hr) Flue Gas CO 2(%) Flue Gas

O 2(%) Flue Gas

Flow Rate (dscfm) Flue Gas

Temperature (F)Fuel Type Units of Me asure Me asurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate
bitum inous lb/hour Other bitum inous lb/hour Other bitum inous lb/hour Other Fuel #1 Fuel #2Fuel Type Units of Me asure Me asurement

Method Fuel Input

Rate Fuel Type Units of Measure Me asurement

Method Fuel #3 Fuel #4QA /QC Documentation

Trap ID Section 1

Mass (ng) Section 2

Mass (ng) Total

Mass (ng) Initial

Spike (ng) Total NonSpike (ng)
65824 33.3 2.9 36.2 0 36.2 65656 31.7 0 31.7 0 31.7 65806 33.5 0 33.5 0 33.5 Other Supporting InformationSample

Volume (dscm) Volume

Difference (%) Volume Diff. Limit Breaktrough

(%) Breaktrough

Limit Concentration

(μg/dscm) Trap ID

0.228827 0.672560493 8.708708709 0.158198115 65861 0.227214 1.493745984 0 0.139516051 65938 0.228775 1.249262376 0 0.146432084 65814 Trap #1

≤20% of field

recovery test ≤10% of Section 1 Hg

mass for HgSection 1

Mass Section 2

Mass Total

Mass Initial

Spike Total NonSpike Sample

Volume Volume

Difference (%) Volume Diff. Limit
31 0 31 0 31 0.227288 0.672560493 50.1 0.1 50.2 20 30.1 0.22382 1.493745984 35.7 0 35.7 0 35.7 0.225917 1.249262376 ≤20% of field recovery test Trap #2Breaktrough (%) Breaktrough Limit Concentration

(μg/dscm) Abs. diff. RD (%) Limit C rec

0 0.136390835 0.021807 7.402613 0.199600798 0.134483067 0.005033 1.836861 0.084771

0 0.158022637 0.011591 3.806987 ≥ 10 % RD mass for Hg conc. >1 μg/dscm: or ≤10% of Section 1 Hg mass for Hg conc. >1 Me asured Spike Recovery ( R ) Paired Trap Agreement (RD)R (%) by

Run Ravg(%) Limit

94.8 Average Recovery

, between 85 and Me asured Spike Recovery ( R )

94.8EIA

Facility Code Facility Name Boiler ID

130 Santee Cooper - Cross Unit #1

Run 1 5/2/2010 15:10 5/2/2010 Run 2 5/3/2010 9:05 5/3/2010 Run 3 5/3/2010 13:10 5/3/2010 Run Number Test Start Date Test Start Time Test End DateMe asured Value (ppm) Basis (Wet or Dry) Test Method Used
18:18 1.28E-02 Dry U.S. EPA Method 26A-Mod 12:18 1.35E-02 Dry U.S. EPA Method 26A-Mod 16:16 1.38E-02 Dry U.S. EPA Method 26A-Mod Test End Time Hydrogen Cyanide Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments BDL 1.97E-05 4537.93 5855 13.8 11.13 BDL 2.08E-05 4503.19 5834 14.1 11.2 BDL 2.15E-05 4499 5833 14 10.92 Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO 2(%) Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Input Rate Fuel Type Units of Me asure Me asurement

Method Fuel Input

Rate 8.31 1628000 147.3 460.87 bitum inous lb/hour Other 8.35 1641900 147.9 459 bitum inous lb/hour Other 8.5 1625050 146.9 459 bitum inous lb/hour Other Flue Gas Temperature (F) Fuel #1 Flue Gas O 2(%) Flue Gas

Flow Rate (dscfm)Fuel Type Units of Me asure Me asurement

Method Fuel Input Rate Fuel Type Units of Me asure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Me asure Me asurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 130 Santee Cooper - Cross Unit #1

Run 1 5/4/2010 7:45 Run 2 5/4/2010 12:45 Run 3 5/4/2010 17:15

Run Number Test Start Date Test Start TimeTotal Dissolved Solids (mg solids/liter) Total Suspended Solids (mg solids/liter)
5/4/2010 11:53 14500 647000 5/4/2010 16:54 15100 622000 5/4/2010 21:23 17700 618000

Test End Time Test End DateTest Method Used Data Flag (ADL, BDL, DDL)
Standard Methods of the Examination of W ater and W astewater Method 2540B ADL ADL ADL Constisuent Emission Test ResultsTest Method Comments Fuel Input Rate

4514 5855 1681900 147.8 460.8 4493 5833 1652433 147.6 459 4508 5853 1693683 147.9 460.7 Flue Gas Temperat ure (F) Flue Gas Flow Rate (dscfm) Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr)Fuel Type Units of Me asure Me asurement

Method Fuel Input Rate Fuel Type Units of Me asure Measurement

Method Fuel Input Rate

bitum inous lb/hour Other bitum inous lb/hour Other bitum inous lb/hour Other Fuel #1 Fuel #2Fuel Type Units of Me asure Me asurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel #3 Fuel #4Other Supporting Information