NUREG/CR-5406

EGG-2569

Vol. 2

BWR Reactor Water Cleanup System

Flexible Wedge Gate Isolation

Valve Qualification and High

Energy Flow Interruption Test

Data Report

Prepared by K.G. DeWall, R. Steele, Jr.

Idaho National Engineering Laboratory

EG&G Idaho, Inc.

Prepared for

s U.S. Nuclear Regulatory Commission

- MMM=V
AVAILABILITY NOTICE

Availability of Reference Materials Cited in NRC Publications

Most documents cited In NRC publications will be available from one of the following sources:

1. The NRC Public Document Room, 2120 L Street, NW. Lower Level, Washington, DC 20555

2. The Superintendent of Documents, U.S. Government Printing Office, P.O. Box 37082, Washington,

DC 20013-7082

3. The National Technical nformation Service, Springfield, VA 22161

Although the listing that follows represents the majority of documents cited In NRC publications, It Is not

intended to be exhaustive.

Referenced documents available for Inspection and copying for a fee from the NRC Public Document Room

Include NRC correspondence and Internal NRC memoranda; NRC Office of Inspection and Enforcement

bulletins, circulars, Information notices, Inspection and investigation notices; Ucensee Event Reports; vendor reports and correspondence; Commission papers; and applicant and licensee documents and correspondence.

The following documents in the NUREG series are available for purchase from the GPO Sales Program:

formal NRC staff and contractor reports, NRC-sponsored conference proceedings, and NRC booklets and

brochures. Also available are Regulatory Guides, NRC regulations In the Code of Federal Regulations, and

Nuclear Regulatory Commission Issuances. l

Documents available from the National Technical Information Service Include NUREG series reports and

technical reports prepared by other federal agencies and reports prepared by the Atomic Energy Comrnmisslon, forerunner agency to the Nuclear Regulatory CommissIon.

Documents available from public and special technical libraries include all open literature Items, such as F

books, journal and periodical articles, and transactions. Federal Register notices, federal and state legislation, and congressional reports can usually be obtained from these libraries.

Documents such as theses, dissertations, foreign reports and translations, and non-NRC conference proceedings are available for purchase from the organization sponsoring the publication cited. [ Single copies of NRC draft reports are available free, to the extent of supply, upon written request to the

Office of Information Resources Management, Distribution Section, U.S. Nuclear Regulatory Commission,

Washington, DC 20555.

Copies of Industry codes and standards used In a substantive manner In the NRC regulatory process are i

maintained at the NRC Library, 7920 Norfolk Avenue, Bethesda, Maryland, and are available there for reference use by the public. Codes and standards are usually copyrighted and may be purchased from the

originating organization or, If they are American National Standards, from the American National Standards

Institute, 1430 Broadway, New York, NY 10018.

DISCLAIMER NOTICE

This report was prepared as an account of work sponsored by an agency of the United States Government.

Neitherthe United States Government nor any agency thereof, orany of their employees, makes any warranty,

expresed or implied, or assumes any legal liability of responsibility for any third party's use, or the results of

such use, of any information, apparatus, product or process disclosed in this report, or represents that its use

by such third party would not infringe privately owned rights.
NUREG/CR-5406

EGG-2569

Vol. 2

R1

BWR Reactor Water Cleanup System

Flexible Wedge Gate Isolation

Valve Qualification and High

Energy Flow Interruption Test

Data Report

Manuscript Completed: September 1989

Date Published: October 1989

Prepared by

K.G. DeWall, R. Steele, Jr.

Idaho National Engineering Laboratory

Managed by the U.S. Department of Energy

EG&G Idaho, Inc.

P. O. Box 1625

Idaho Falls, ID 83415

Prepared for

Division of Engineering

Division of Safety Issue Resolution

Office of Nuclear Regulatory Research

U.S. Nuclear Regulatory Commission

Washington, DC 20555

NRC FIN A6857, B5529
FOREWORD

The information contained in Volume II is the actual measured data from the gate valve test program described in

Volume I. They are provided here for those readers who wish to look at the data and form their own opinion on the

performance of the testvalves. Forthose readers who wish to do theirown analysis, the electronic datais available from

our DOE Office of Technology Transfer. Requests for the data can be made by calling (208) 5268318.

iii
CONTENTS

FOREWORD ......................................................................... iii

Figure 1. Simplified GJ-87 test loop showing configuration, lengths, and pipe sizes ..................... 2

Figure 2. Venturi flow meter calibration curve for converting the AP differential pressure measurement to

gallons per minute . ................................................................. 3

Table 1. Valve diagnostic equipment used for subcooled blowdown tests ............................. 4

Table 2. Test parameters measured during blowdown tests ......................................... 5

Table 3. Test step matrix for qualification and blowdown tests ..................................... 6

Table 4. Test steps and system pressure and temperature for each test performed ....................... 8

Test Data ........................................................................... 15

V
BWR REACTOR WATER CLEANUP SYSTEM

FLEXIBLE WEDGE GATE ISOLATION VALVE QUALIFICATION AND

HIGH ENERGY FLOW INTERRUPTION TEST

VOLUME II

DATA REPORT

Volume H presents the measured test data from the gate valve test program described in Volume I. Figure 1 shows the

testloopinschematicform andidentifiestheinstrumentlocation andnumbers. Figure 2convertsthe differentialpressure

measurement to gallons per minute. Table 1 outlines the test sequence performed on each valve and correlates the data

as itis presented here. The header on each plot defines the valve A orB, the test series number, and the test step number.

Table 2 lists the test parameters measured during blowdown tests, Table 3 lists the test step matrix for qualification and

blowdown tests, and Table 4 lists the test steps and system pressure and temperature for each of the tests performed.

1
Specimen

Blowdown

Bleed

................

10 In.] -

pipe *

: :.

; t.

I 6 In pin.

ppe

I

! 13.3 It.

10 ft.

e -

0 a elI.- 

Water tank

10 In.

pipe

20 ft.

-Flowmeter

BMG00265

Figure 1. Simplified GI-87 test loop showing configuration, lengths, and pipe sizes.

2
Venturi Flow Meter

18

16

1>

E

c,)

-.

14

12

10

8

6

4

2

0

0 10 20 30 40 50 60 70

Differential pressure (psid)

MGH02161

80

Figure 2. Venturi flow meter calibration curve for converting the AP differential pressure measurement to gallons per

minute.

3
-

Table 1. Valve diagnostic equipment used for subcooled blowdown tests

Valve Test Series Description Diagnostic Equipment'

A

A

A

A

A

A

A

A

A

A

A

1

3

2

4

6

5

7

9

8

10

11

Qualification test

Blowdown, 1000 psig, 4800F

Blowdown, 1000 psig, 530°F

Blowdown, 1000 psig, 400°F

Blowdown, 1400 psig, 5300F

Blowdown, 1400 psig, 580°F

Blowdown, 1400 psig, 4500F

Blowdown, 600 psig, 430°F

Blowdown, 600 psig, 480°F

Blowdown, 600 psig, 350°F

Blowdown, 1000 psig, 5300 F

Qualification test

Blowdown, 1000 psig, 530°F

Blowdown, 1400 psig, 580°F

Blowdown, 600 psig, 4800F

Blowdown, 1000 psig, 530°F

MCSA

MCSA

None

V-MODS

V-MODS

MOVATS

MOVATS

None

None

MAC, VOTES

MCSA

MCSA

MCSA, MOVATS

V-MODS

MAC

V-MODS

B

B

B

B

B

1

2

3

4

5

a MAC

MCSA

MOVATS

V-MODS

VOTES

Limitorque Motor Actuator Characterizer

ORNL Motor Current Signature Analysis

MOVATS, Inc. (M Analysis and lest System)

WYLE Laboratories Yalve Motor Qperator iagnostic System

Liberty Technology Yalve Operator lest & Evaluation System

4
Table 2. Test parameters measured during blowdown tests

Data X-Y

Transducer Measurement FM Tape Oscillograph Logger Plotter

Tl System water temperature X

T2 Test valve inlet water temperature X

T3 Test valve body temperature X

T4 Heating section water temperature X

T5 Load cell temperature X

Pl System water pressure X X X X

P2 Test valve inlet water pressure X X X

P3 Test valve outlet water pressure X X X

P4 Discharge section water pressure X X X

API Test valve differential pressure X X X

AP2 Venturi differential pressure X X X

AP3 Pump differential pressure X X

Il Actuator current X X

12 Actuator current X

I3 Actuator current X

El Actuator voltage X X

E2 Actuator voltage X

ST Valve stroke-LVDT X X X

LSl Open limit switch X X

LS2 Close limit switcha

TS Close torque switch X X

F Valve stem force X X X

Al Acutator acceleration Y X X

A2 Actuator acceleration X X

A3 Actuator acceleration Z X

A4 Valve body acceleration Y X X

A5 Valve body acceleration X X

A6 Valve body acceleration Z X

a. Control room light indicator only.

5
Table 3. Test step matrix for qualification and blowdown tests

Step Number Valve Cycle Description

Qualification tests (Test 1, Valves A and B)

1

2

3

4

5

6

7

8

9

10

11

12

13

14

15

16

17

18

19

20

21

22

23

24

25

26

O-+C

C-+ptO

ptO-4C-+O

O-C

C-oO

0-+C-40

0-+C-*.o

0-C-40

0-~C C-+O

O-C C-+O

0OoC

C-40

0-+C-+O

O-4C

C-+O

C-+O

O-+C

C-+O

O-+C

C0-*

Close valve at 2220 psig, cold

Seat leakage test

AP opening at 1700 psig, cold

Packing leakage test

Cycle valve at 0 psig, cold

Close valve at 2220 psig, cold

AP opening at 1700 psig, cold

Cycle valve at 0 psig, cold

Cycle valve at 0 psig, cold

Cycle valve at 0 psig, cold

Close valve at 2220 psig, cold

AP opening at 1700 psig, cold

Close valve at 2220 psig, cold

AP opening at 1700 psig, cold

Close valve at 2220 psig, cold

AP opening at 1700 psig, cold

Cycle valve at 0 psig, cold

Close valve at 1650 psig, 600°F

AP opening at 1650 psig, 600°F

Close valve at 1650 psig, 600°F

AP opening at 1650 psig, 600°F

Close valve at 1650 psig, 600°F

AP opening at 1650 psig, 600°F

Close valve at 1650 psig, 600°F

AP opening at 1650 psig, 600°F

close valve at 1650 psig, 600°F

6
Table 3. (continued)

Step Number Valve Cycle Description

Blowdown tests (Valve A, Tests 2-11, and Valve B, Tests 2-5)

.' 0

1

2

3

4

O-C-+O

O-+C

C-4o

O-4C

C-4O

O-4C

C -ptO

ptO-+C

C-+O

O-C-40

Cycle valve at test pressure and temperature

Close valve at test pressure and temperature

AP opening at test pressure and temperature

Close valve at 100 gpm, test pressure and

temperature

Open valve at 100 gpm, test pressure and

temperature

Blowdown at test pressure and temperature

Blowdown at test pressure and temperature

Blowdown at test pressure and temperature

Open valve at 0 psig and test temperature

Cycle valve at 0 psig and test temperature

5

6

7

8

9

Final cold testing (Valve A, Test 11, and Valve B, Test 5)

10

11

12

13

14

15

16

17

18

19

20

21

22

23

C-4O

O-C

C-+ptO

ptO-40

O-C

C-+O

O-C

C-+O

O-C

C-+O

O-C

C-4O

AP opening at 1000 psig, cold

Close valve at 1000 psig, cold

Seat leakage test

AP opening at 1000 psig, cold

Packing leakage test

Open valve at 1000 psig, cold

Close valve at 1000 psig, cold

AP opening at 1000 psig, cold

Close valve at 0 psig, cold

Open valve at 0 psig, cold

Close valve at 0 psig, cold

Open valve at 0 psig, cold

Close valve at 0 psig, cold

Open valve at 0 psig, cold

0 open

C close

Pt partial valve stroke

7
Table 4. Test steps and system pressure and temperature for each test performed

Test Test

Step Valve Pressure Temperature

Number Cycle (psig) (

0F) Remafs

Valve A, Test 1, Qualification test, 420 & 25188

1 O - C 2246 58

2 2246 58 Seat leakage test

3 C-ept 0 1706 59 APopening

4 1706 59 Packing leakage test

5 pt0o-C-+O 20 59

6 0 - C 2248 60

7 C - 0 1699 60 AP opening

8 O*C +O 25 60

9 O-C 0 25 60

10 0O C 24 61

11 o - C 2258 61

12 C .*O 1726 61 APopening

13 O - C 2258 61

14 C e 0 1701 61 AP opening

15 O - C 2254 61

16 C - 0 1723 61 AP opening

17 0 -C -0 17 62

18 O -C 1655 590

19 C- .0 1615 574 AP opening

20 O - C 1664 591

21 C - 0 1558 569 AP opening

22 0 - C 1679 586

23 C. 0 1573 560 AP opening

24 0o C 1653 583

25 C-+0 1510 563 AP opening

26&27 O-4C-40 1623 583

0 open

C close

Pt partial valve stroke

8
Table 4. (continued)

Step

Number

Valve

Cycle

Test Test

Pressure Temperature

(psig) (

0F) Remads

Valve A, Test 3, Blowdown test, 425/88

1 0 -4C

2 C-+0

3&4 0sCoO

S O-C

8&9 Co0eC+O

1121

1112

1110

1000

0

476

469

483

480

480

AP pening

Normal flow, 100 gpm

Blowdown, end with N2 flow

Valve A, Ilst 2, Blowdown test, 4/30/88

1

2

3&4

S

6&7

8&9

O-C

C-+O

0-+C-3*O

0-+C

C -ptO-4C

C-+O-C-iO

1170

1121

1095

1009

1041

15

540

514

510

524

505

404

AP opening

Normal flow, 100 gpm

Blowdown

Blowdown 0% open, end with N2

Valve A, test 4, Blowdown test, 5/3/88

1 O-C

2

3&4

5

7

8&9

C-O

0-+CO

0O+C

pt O- C

C-+O-C-+O

1029

1020

974

1071

1122

23

403

400

400

418

414

370

AP opening

Normal flow, 100 gpm

Blowdown 50% open

Blowdown 75% open

Valve A, Test 6, Blowdown test, 5/6/88

1

2

3&4

5

8&9

0O+C

C-+O

0-4CoO

C-~0-4C-+O

1430

1402

1408

1408

7

515

516

518

518

428

AP opening

Normal flow, 100 gpm

Blowdown, end with N2

9
Table 4. (continued)

Step

Number

Valve

Cycle

Test

Pressure

(psig)

Test

Temperature

(OF) Remars

Valve A, Test 5, Blowdown test, 5/11/88

I OC

2 C 0

3&4 C O

5 O-C

6&7 C-+ptO-+C

8&9 C-O-C -+ O

Valve A, Test 7, Blowdown test, 5/13/88

1 0-C

2 C O

3&4 O-C-4O

5 o0*C

6&7 C-*ptO-+C

8&9 C +C O

Valve A, Test 9, Blowdown test, 5/17/88

1 O C

2 C O

3&4 O-C-+O

5 O*C

8&9 C-+O--C-+O

Valve A, Tst 8, Blowdown test, 5/19/88

I O-C

2 C-+O

3&4 O+C O

5 O-C

6&7 C-+ptO-*C

8&9 C- O-C-+O

1558

1540

1600

1624

1535

7

1330

1356

1331

1431

1372

2

581

580

586

583

560

450

496

493

496

509

494

440

AP opening

Normal flow, 100 gpm

Blowdown 83% open

Blowdown 50% open

AP opening

Normal flow, 100 gpm

Blowdown

Blowdown 60% open, end on N2

AP opening

Normal flow, 100 gpm

Blowdown

AP opening

Normal flow, 100 gpm

Blowdown 75% open

Blowdown 75% open

684

612

618

645

6

443

438

452

451

435

694

674

655

590

655

5

486

483

482

488

460

446

10
Table 4. (continued)

Step

Number

Valve

Cycle

Test

Pressure

(psig)

Test

Temperature

('IF) Remarks

Valve A, Test 10, Blowdown test, 5/24/88

2 C -O

3&4 O-C-+O

5 0+

6&7 C-+ptO-+C

8&9 C+OeC+O

660

656

617

641

650

5

Valve A, Tests 11, Blowdown test, 5127 & 28/88

1 0 -C 980

2 C-+O 975

3&4 O-C-40 1000

5 0-C 1080

6&7 C-+ptO-+C 1080

8 C-+O 1020

9 O-C 7

354

352

357

367

355

351

507

502

524

524

497

486

393

AP opening

Normal flow, 100 gpm

Blowdown 75% open

Blowdown 50% open

AP opening

Normal flow, 100 gpm

Blowdown

Blowdown 36% open

AP opening

Final Cold Testing

10

11

12

13

14

15

16

17

18 19

20&21

22 & 23

C-+O

0O+C

C-eptO

ptO-4C

C-+O

O-C

C-+O

0-+C-+0

0+C-+O

0+C-+O

1080

1080

1080

1091

1081

1081

1078

1079

22

24

25

79

98

98

85

98

99

105

99

104

104

104

AP opening

Leakage test

AP opening

AP opening

AP opening

11
Table 4. (continued)

Test Test

Step Valve Pressure Temperature

Number Cycle (psig) (OF) Remaiks

Valve B, Test 1, Qualification test, 17, 8, & 13/88

1 O C 2161 77

2 2161 77 Seat leakage test

3 C-+ptO 1738 77 AP opening

4 1738 77 Packing leakage test

5 ptO-+C-O 1 75

6 O C 2233 75

7 C. 0 1708 75 AP opening

8 O C O 7 75

9 O C O 8 75

10 O CO 8 75

11 O -+ C 2355 75

12 C O 1685 75 AP opening

13 O C 2210 75

14 C 0o 1713 75 AP opening

15 O C 2170 75

16 C 0 1700 75 AP opening

17 O- C-oO 22 75

18 0 + C 1641 586

19 C-+ 1630 582 APopening

20 O - C 1616 579

21 C 4 0 1513 575 AP opening

22 O C 1694 570

23 C - 0 1593 570 AP opening

24 Oo0 C 1659 567

25 C ^ 0 1657 565 AP opening

26 O-C-+O 1739 573

12
Table 4. (continued)

Step

Number

Valve

Cycle

Test

Pressure

(Psig)

Test

Temperature

(°F) Remarks

Valve B, Test 2, Blowdown test, 6/14/88

1

2

3&4

5

6&7

8&9

O-+C

0-+C-40

C-*ptO.C

1109

1084

1125

987

1006

22

518

516

524

524

508

428

AP opening

Normal flow, 100 gpm

Blowdown

Blowdown 50% open, end with N2

Valve B, Test 3, Blowdown test, 6/17/88

1

2

3&4

5

6&7

8&9

O-+C

C-+o

O-C

C-+ptO-+C

C-+O-4C-+O

16703

1544

1529

1406

1492

23

583

579

575

563

557

495

AP opening

Normal flow, 100 gpm

Blowdown

Blowdown 40% open, end with N2

Valve B. Test 4, Blowdown test, 6/21/88

1

2

3&4

5

6&7

8&9

O-4C

C-+o

O-+C-+o

O-C

C-+ptO-+C

C-+O- >C-+O

734

749

733

631

634

30

497

493

491

493

488

276

AP opening

Normal flow, 100 gpm

Blowdown

Blowdown 50% open

13
Table 4. (continued)

Step

Number

Valve

Cycle

Test

Pressure

(psig)

Test

Temperature

(oF) Remarks

Valve B, Test 5, Blowdown test, 6/24 & 27/88

1

2

3&4

5

8

9

956

944

933

970

52

2

524

521

520

517

433

431

AP opening

Normal flow, 100 gpm

Blowdown, end on N2

Final Cold Testing

10

11

12

13

14

15

16

17

18 & 19

20 & 21

22 & 23

1033

1030

1030

982

984

997

1016

1036

17

18

18

82

86

86

83

87

85

88

85

84

86

86

AP opening

Leakage test

AP opening

AP opening

AP opening

14
2300

22501

.C

Co4 2200

VALVE A, TEST 1, STEP 1

* I * *I - I I I I * I . I I I I I I 

. ~ ~ . . . , .

215 1

2100 1

CF 10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 1

220D

2150

. 0

n~ 21001

2050

2000

0 10 20 30

TIME(SEC)

40

15
VALVE A, TEST 1, STEP 1

2300 . . . . . . . . . . . . . . . . . . . I I I

2250 F

.g2200

' 210

E 2100

2050 r

2000

2.2

2.0

' D 1.8

.

e 1.6

l 1.4

1.2

1.0

I . I I

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 1

a 10 20 30 40

TIME(SEC)

16
VALVE A, TEST 1, STEP 1

150

100

0"

. .

T 5D

I-_

El

m

I I I I . I

I -

-50 L

a 1 I I I I I I . I I . I I . * . a

10 20o 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 1

3

2

1

,c~.9

-

-1

-2

-3

17
30

20

U

E

° 10

0

VALVE A, TEST 1, STEP 1

I I I I I I I I I I I I I

I a I I I I I I I I I * I I I I * -10

4

a 10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 1

3

0

0 10 20 30

TIME(SEC)

18

40
VALVE A, TEST 1, STEP 1

25

20 :

3 15

10

T 5

0

I I I II I I I I I I I I I I I

I aI I I I . I I I a i * I I I i I -5 

0

600 -

500

400 

~300I

>; 200 

> 100I

D0

10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 1

-10

a 20

TIME(SEC)

40

.19
VALVE A, TEST STEP 1

500

400

En 300

'' 200

Q 100

0

. . .

v

I- - - I I I I I I I I I I I I

I * I *I * * -100 0 - - - - - - - - - - - - - - - - - - - 10 20 30 40

TIME(SEC)

VALVE A, TEST 1, STEP 1

2

1

En

(, 

N -1

I

2

=1-2

-3

0 40

20
VALVE A, TEST 1, STEP 1

4

23

I0

"I,,

-' -30000

-40000 

To

VALVE A, TEST 1, STEP 1

20

TIME(SEC)

40

21
VALVE A, TEST 1, STEP 3

2000

1800

.0

EL 1600

C-,'

V 1400

1200

1000

0

1500 

1000 _

.0

IT 500

5 0

-500 

5 10 15 20

TIME(SEC)

VALVE A, TEST 1 STEP 3

I * I S I * S S S I * S S S I S S I S

* S S S I * S I I 10

5

TIME(SEC)

22

15 20
VALVE A, TEST 1, STEP 3

1500 Iw~o

.an

EL

",d- 50

0

-500

I I5 I I I I a I I I I I I I I

* I *I * I 

0 5 1D

TIME(SEC)

15 20

VALVE A, TEST 1, STEP 3

65

64 

.m

' 63

<62

61

60

--- - I I I I I I I I I I I S I I I I 

10*% 

0 5 la

TIME(SEC)

23

15 20
VALVE A, TEST 1, STEP 3

2000

1500

c,

'Iii

CL

IA

1000

500

0

-500

0 5 10 15

TIME(SEC)

20

VALVE A, TEST 1, STEP 3

0.0

-o.

.' -1.0

t5 -1.5

-2.0

-2.5

-3.0

0 5 10 15

TIME(SEC)

20

24
VALVE A, TEST 1, STEP 3

30

20

2D

03FU

E.

0 a

* I . * * I S * I I

* S S I I * * * S I*I*II I I t I -la L

0 5 10

TIME(SEC)

15 20

VALVE A, TEST 1, STEP 3

a

6

.

4 

2

0 

a3

S v S S I I * S I S g S I

I

I . I I . . .

10 5 10

TIME(SEC)

25

15 20
VALVE A, TEST 1, STEP 3

20

~15

1a

0 5 10 15 20

TIME(SEC)

VALVE A, TEST 1, STEP 3

600 * * * * * , * * , 

500

400

200

>.100I

0

-100 , 0 5 10 15 20

TIME(SEC)

.26
VALVE A, TEST 1, STEP 3

500

,, 400

I5? 30 . 0

> 200

,. 100

-100

1.0

0.6

I-

. 0.6

A 0.4

: 0.2

0.0

10

TIME(SEC)

20

VALVE A, TEST 1, STEP 3

~~i 1 * I | { I -1 I 2 I I- - *- *

0 5 10

TIME(SEC)

15 20

21
VALVE A, TEST 1, STEP 3

0.4

l

I0.3

0.2

0.1

0.0 

-0.1 -

0 20

VALVE A, TEST 1, STEP 3

20000

10000

O 0

t -10000

-20000

-30000

-40000

a 10

TIME(SEC)

28

20
200

1501

on . _

EL

. .

C-4

VALVE A, TEST 1, STEP 5 , II I I I I * * I I I I 

I I I , I . . A I , I * * .

100

50

0

0 20 40

TIME(SEC)

60 80

200

150 

VALVE A, TEST 1, STEP 5 U U I 1 U U I 5 f I I I I

I I .I . I . . . , a . *

100 L

50

0

0 2D 40

TIME(SEC)

60 s0

-29
VALVE A, TEST 1 STEP 5

200

150 1

CP

.,

,I 10D

50

0

, I I I I

I I a I a I I I a I I a t

0 20 40

TIME(SEC)

60 80

VALVE A, TEST 1, STEP 5

58

56

0,

'D]

0L

- 54

52

. I I I I I I a I I I

* * * I * I * I 50

l 20 40

TIME(SEC)

60 so

30
40

20

*Sp 0 CL

CN -20

IA -40

VALVE A, TEST 1, STEP 5

* I I I I I I I I I I I 

-- - -L-- I . - . 1 - - - - I - - I 

-60 

-80 a 20 40

TIME(SEC)

60 80

VALVE A, TEST 1, STEP 5

3

2

-1

-2

-3

40

TIME(SEC)

s0

.31
VALVE A, TEST 1, STEP 5

30

20 in

E

a 10

-10

I I a I I . 4 I . I 

5 1 I * * S I . . I . .

0 20 40

TIME(SEC)

60 a0

VALVE A, TEST 1, STEP 5

6

5

E4

3

2

1

0

a 20 40 60

TME(SEC)

32

80
VALVE A, TEST 1, STEP 5

25

20

815

lo 

E 5

0 

-5

0

600 -

500 _

400

300_

200

100 i

I . I I . I 

r . . , I .. .I .I . I a 

20 40 60

TIME(SEC) 80

VALVE A, TEST 1, STEP 5

fn

IC) I

e)4i: IIIs I I i~~~ I I

0 II

-1D t

0

I , . . I I

40 20 40

TIME(SEC)

33

60 80
VALVE A, TEST 1, STEP 5

600

400

1* it

I I I

V)-

0

C-)

200

0 I-

-200

0

. . . ~ ~ ~ ~ ~~~~~I I . . . I . I I . . . I

20 40 60

TIME(SEC)

30

VALVE A, TEST 1, STEP 5

2.0

Q 1.5

i 1.0

5 0.5

0.0

0 20 40 60

TIME(SEC)

so

34
VALVE A, TEST 1, STEP 5

4

I-.

B3

2

1

To

I I I I I -I--i 1 - -1 I -I ~I

.1

. . , . . I .I . I . .

-1

0~ 20 40

TIME(SEC)

60 80

VALVE A, TEST 1, STEP 5

20000

0

-10000

-20000 --I

40

TIME(SEC)

35

80
2240

22301

.C' 2220

.

C4 2210

t 2200

2190

VALVE A, TEST 1 STEP 6 a I I I I I I I I I I I

-aa

I I I I I . . I I I . I I I I . I . . !31v r

0

2200

2180 

.0

E 2160

p4

To

En 2140 

2120-

2100 a'

10 20

TIME(SEC)

30 40

VALVE A, TEST 1 STEP 6

TIME(SEC)

36
VALVE A, TEST 1, STEP 6

2240

2220

. 2200

'd 2180

t 2160

I

I I I . . , I. . . . , I .I .I S

* S S S I * . a I * . * S I a a S

21401-

2120 L

0 10 20 30 40

TIME(SEC)

62

601

CP

.m

t:L

- e

N

VALVE A, TEST 1, STEP 6

I I I I I I I a I I I I I a I I I I a I 20- - . I I --- --

56

54

0 10 20

TIME(SEC)

37

4940
VALVE A, TEST 1, STEP 

120 . .. . . . . . . . . . . . . . . . . . . . . I I

100 :.

oP

0,

T

so

60

40

20

or.

-20 

l

I l I , .

I 10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 6

3

2

1

I.

0

-J

0

-1

-2

-3

0 20

TIME(SEC)

.38
VALVE A, TEST 1, STEP 6

30

20

In

E

To

, .

I * I . . . . * *II I I

S S S I II . ..

I I I I

I . .

0

-10 L0 10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 6 -.- I

0.41

I I I I I .I . I I I I

M#^VaI2

0.3 _ .a . - I I II Ia 

u 10 20

TIME(SEC)

39

30 40
VALVE A, TEST 1, STEP 6

25 . * * X i i ' * ' ' *o ' * ' * 

20

1

10

0 10 20 30 40

TIME(SEC)

VALVE At TEST 1, STEP 6

600

400

200

0

-200

0 10 20 30 40

40
VALVE A, TEST 1, STEP 6

600

SW

400

I.,I

-J

C)

300

200

100

0

-100

2

1

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 6

0

=1 -2

-3

20

TIME(SEC)

41
VALVE A, TEST 1, STEP 6

4. . . .S . . . . . . . . . . . . . .

(n 3

. 2

T I

w 

-

-1 

0

0..

. . I I I I 

a I I S I I I I I a * I I I I * * S

10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 6

S S X S I S . I g * S S I * S

-5000

E -10000

'' -15000

1 -2000

° -25000

-30000

-35000

-

_ .

. S I S I

I *_S I * I 

I I . . . . I. .

I 10 20

TIME(SEC)

30 40

42
VALVE A, TEST 1, STEP 7

1700

1600

.E C 500

c-4 1400

1300

1200

20

TIME(SEC)

40

VALVE A, TEST 1, STEP 7

1500 -. -. -. . -...----. . ---- .

100

.,-

e~* 500

o

* * * * I * I I I 

* * * * I * I * * I * -501

I 10 ' 20

TIME(SEC)

30 40

43
VALVE A, TEST 1, STEP 7

1500

1000

-0

.EL

-4 5W0

-500

0 20

TIME(SEC)

VALVE A, TEST 1, STEP 7

62

601

CL

.,

' 58

IA5

596

541 . . . , I a I p I I I a - p I I p -

C 10 20

TIME(SEC)

30 40

44
VALVE A, TEST 1, STEP 7

2DD

'DSD

C' 1DOD 15DD

1 00

-500

3 

2 

1 

I I I I I I I I - I -- -' --

I * * * I I I

I

I

. . . . . . . . . . . . . . . . . . .

10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 7

. -

.

0

-1

-2

-3

40

45
VALVE A, TEST 1, STEP 7

25

20 

rn

Ea

v15

10

5

I I . I I I I I I I r I 

a a a I a a a I a a a a I a a a a

a1

-5

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 7

0.5

0.41

a a I I I I I I I I I I I I 

* a a a I a a I a a I a a a 0.3

0 10 20

TIME(SEC)

30 40

46
VALVE A, TEST 1t STEP 7

25

20

la

15

1D

5

0

-5

a 10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 7

600

500

I-

'C400

30

200

10

I~~~~~ 

, . . , I . . . I , . . . .

0 

-10 I

Il . . . . . . . . . . . . . . . . . . I 10 20

TIME(SEC)

47

30 40
VALVE A, TEST 1, STEP 7

800

600 I-~~~

o 400

Cal

1 2o0

Oo

I I I I I I I I I I I II I I I I I

* I I I .I I . , I -200 

0

I . I I I

10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 7

2.0 . . . . . . . . . . . . . . . . . .

E 1.5

is 1.0

210

2 0.5

* . . , . . . , . .* 

* I * I I I . . ~ I I I I I 

. __

0.0 L

0 10 20

TIME(SEC)

30 40

48
VALVE A, TEST 1, STEP 7

0.2

> 0.1

I,,

aU 0.0

I U A L | | | tI |I l I l l I I

I I I a I 

-1.1 I

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 7

49
200

1501

on . _

C-4 ,U 100 .

0T

so

VALVE A, TEST 1, STEP 9

. a I I I I I I I I I I I * I

nI * S ~~I *I I I . S

93nn

20 40

TIME(SEC)

60 80

VALVE A, TEST 1, STEP 9 - -U150 

.2

S.

) 100

50 p * , , , S I , 

Ok

20 40

TIME(SEC)

60 80

50
VALVE A, TEST 1, STEP 9

200

150

1DD

50

10

40

TIME(SEC)

so

VALVE A, TEST 1, STEP 9

58

57

'7 56

AL

- 54

A 54

I

f

I I I I I I I I . , . i . I 

: 

53 

52r

a 20 40

TIME(SEC)

60 s0

*51
VALVE A, TEST 1, STEP 9

40

20

I I . . ,I I. 

'VI

.

d

0

-20 1-

-40 _.

-60

-80 - . , . . I I I . I , . 2

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 1, STEP 9

2

1

._

Ji

0

-1

-2

-3

0 20 40 60

TIME(SEC)

s0

52
VALVE A, TEST 1, STEP 9

30 , I I I I . I I a I I I 

203

2

E

a 0

D'

-10 I I I I f a I -

0 20 40

TIME(SEC)

60 s0

VALVE A, TEST 1, STEP 9

2.0

1.5

10

. 1.0

a; 0.5

I I A I I, I I I I I I I

. * * . g , . . . I 0.01

i 20 40

TIME(SEC)

60 80

53
VALVE A, TEST 1, STEP 9

30 I - -- I s- I -- I - - I I - I I I - I 1 I~ j I - I ~ . -

25 .

g 20

t 15

to 10

O r-

-5 

O . . I _ . _ e.I I . ,I 

1 ~~20 40

TIME(SEC)

60 80

VALVE A, TEST 1, STEP 9

800

600

o 400 t

r- 6

2 o 

-

-200

10 20 40 60

TIME(SEC)

54

80
VALVE A, TEST 1, STEP 9

Sao

600

(n

I.-

o 400

.,

>1 200

C-)

0

-200

0

VALVE A, TEST 1, STEP 9

2

1

,

6

A -1

D: -2

__ -V I - I - I - - I -I - I I I I I I I I

* * ~ ~ * ~~~I I * I . I -3 L

1I 40 20 40

TIME(SEC)

.55

60 80
VALVE A, TEST 1, STEP 9

4

En

IT)

Li

3

2

1

0

L--' --- -- - I

I I 

-1 I I * I 

0 20 40 60

TIME(SEC)

so

VALVE A, TEST 1, STEP 9

20000

10000

. 0

M -10000

o -20000 - 3

-30000

I I I I a I I I I I a 

_______________________________________ I ______________________________________~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

* 1- - - - I * * 2 I . -40000

0 20 40

TIME(SEC)

56

60 80
VALVE A, TEST 1, STEP 12

1700

1600

.21

1500

C4

LO 1400

130

. . . .. . . , * S S I I I . I I I I I I

1200 S . . . , .I I I 

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 12

1500

1000

.0

to 5w

0

-500

0 40

TIME(SEC)

.57
VALVE A, TEST 1, STEP 12

1500

1000

(r3

0

tm

-500

c

62.0

.' 61.5

N 61.0

60.5

I, Ia I I , I I I I I I I I I I

9 | e I I I*** lL 

I

- - - - - - - - - - - - - - - - - - -

20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 12

10 20 30

TIME(SEC)

58

40
2000

1500

80

-o

VALVE A, TEST 1, STEP 12

I I I I I I i I I I a I I 

a I I I I , I I I I I I I I

3

1

2:

I

._C

-I:

-1

-2

-3

c

i

I

10 20

TIME(SEC)

40

VALVE A, TEST 1, STEP 12

20 30

TIME(SEC)

59

40
VALVE A, TEST 1, STEP 12

30

fn

-

E.

20

1D

D

. . , . . . , . . . I

h~~~~~ I_.

-10

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 12

2.0

1.5

1.0

0.5

0.0

I I I I I I I I 5 F 1- I UF

I I I I f I I * I I * I I I * * I

0 10 20

TIME(SEC)

30 40

60
VALVE A TEST 1, STEP 12

25

2D 

.3 15

10

5

* I I I I I I I I I I*aI g I I

I I I I I I I , I I

O

w

-5

0 1D 20

TIME(SEC)

30 19

VALVE A, TEST 1, STEP 12

600

500

Cu

IC:.

400

30

200

130

0

-100

20

TIME(SEC)

61
VALVE A, TEST 1, STEP 12

500

400

En 300

I-

* 200

0 100

0

-100

2.0

En 1.5

6 1.0

=0.5

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 12 I I . I I I I I I a I I I

0.0I

l 10 20

TIME(SEC)

30 40

62
VALVE A, TEST 1, STEP 12

0.4

*' 0.3

0.2

0.0

-0.1

30000

20000

IL 10000

0

9 -10D00

R -2000

-30000

-40000

VALVE A, TEST 1 STEP 12

0 10 20 30

TIME(SEC)

63

40
VALVE A, TEST 1, STEP 19

1600

1550

.10

C-4 1500

1450

1400

2000

1500

.0

2. 1000

CL

En 500

0 

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 1 STEP 19

64
VALVE A, TEST 1, STEP 19

2000

1500

1000

0

-500

4

2

0) .0.

Lo

<-2

D

I-5

-4

-6

VALVE A, TEST 1, STEP 19

40

65
VALVE A, TEST 1, STEP 19

2000

1500

cm

In

-J

w

A

1000

500

0

-500

0 20 30

TIME(SEC)

40

VALVE A, TEST 1, STEP 19

2

1

I.

I--

0

-1

-2

-3

a 20

TIME(SEC)

66
VALVE A, TEST 1 STEP 19

30

In

E

0

20

10

0

. I I I . I ... I I I 

a I a I  I I - I * - I I I * I I I *I -10

30

20

10

0

-10

0 ID 20

TIME(SEC)

30 40

VALVE A, TEST 1, STEP 19

0 10 20 30

TIME(SEC)

40

67
VALVE A, TEST 1, STEP 19

25

20

UI i 15

10

T 

a

-5

600

500

Q 400

X 300

; 200

> 100

0

-100

i

20

TIME(SEC)

VALVE A, TEST 1, STEP 19

I~ ~ I I 

II 

~~I I I

3 10 20

TIME(SEC)

30 40
VALVE A, TEST 1, STEP 19

600

500

En 400

I-

> 300

C-)

>. 100

0

-100

2.0

W2 1.5

I.

i 1.0 

5 0.5,

0.0 

C

0 2 I I I I 

I

1lO 20 31

TIME(SEC)

VALVE A, TEST 1, STEP 19

0 40

I I I I I * I I I I S. I 

10 20

TIME(SEC)

30 40

69
VALVE A, TEST 1, STEP 19

0.06

0.05

> 0.04

.

L'- 0.02

0 I-0.01

0.00

30000

20000

10000

i -10000

° -20000

0 20

TIME(SEC)

VALVE A, TEST 1, STEP 19

-30000

-40000

0

*70
VALVE A, TEST 2, STEP 1

1150

11401

.21

a

C14

,)

1130 

I I I I I I I I I I a I I ' 

1120 

1110

1100

0 10 20

TIME(SEC)

40

VALVE A, TEST 2, STEP 1

*LZUU.

1150 L

.0

EL

1100

I I I I I I I I I I I I I I I I I

I I I I I I , I I _ 

1050 

1000

0 10 20

TIME(SEC)

30 40

.71
VALVE A, TEST 2, STEP 1

1160 , . . . . . . . . . . . . . 1.. I I . . I . . I I I a I I I I I -1 ---I - U11501:

." 1140

0 1130

E10

In

1110

1100I

-

t t I I I a I a . I I . a a I

i 10 20

TIME(SEC)

30 40

i

VALVE A, TEST 2, STEP 1

0.0

'Z

. .

'- -0.5

-

-1.0

-1.5 40

72
300

200 

CL

. .

01

A~

VALVE A, TEST 2, STEP 1 , .I . . . , 

I . . . , . . . . , . . . . , . .

100 L

0

-100

a 10 20

TIME(SEC)

30 40

VALVE A, TEST 2, STEP 1

3

2

1

I.-

m

a

-1

-2

-3

a 20

TIME(SEC)

73
VALVE A, TEST 2, STEP 1

15

10

U,

FL 5 

E

a

T- 0 -

-5

-10

0

I I * I

I I . . . . I

10 20 30

TIME(SEC)

40

VALVE A, TEST 2, STEP 1

M*u.

15

10

5j

* p * I * I I I I I I I I I I I

I p p I I I p p I I I I I I

0 1

-5

-10 

a I 10 20

TIME(SEC)

30 40

.74
VALVE A, TEST 2, STEP 1

12

10

. 6

4

VALVE A, TEST 2, STEP 1

. ,

0

1000

600

600

400

200

0

-200

20

TIME(SEC)

75

40
VALVE A, TEST 2, STEP 1

600

400

-J

Is 0

0 

200

0

-200

0 10 20 30 TIME(SEC) 40

VALVE ATEST 2, STEP 1

1.5

Ln

, .

I1.0

0.5

0.0

-0.5

40

76
VALVE A, TEST 2, STEP 1

4-

f3 X

., -

Li

.- 1 _

o 0-

0

-10000

>: -20000

-30000

0

-40000

-50000

10 20 30

TIME(SEC)

40

VALVE A, TEST 2, STEP 1

20

TIME(SEC)

.77

40
VALVE A, TEST 2, STEP 2

1300

12501

.*' 1200

CN 150

1Cu F * I I I I I I I I I * i * * I i * * * I * * *

1050

1000

Cp Ui 2u

TIME(SEC)

30 40 50

VALVE A, TEST 2, STEP 2

1500

¢ 1000

to 0

C,,I

500

TIME(SEC)

78
VALVE A, TEST 2, STEP 2

1500

1000

.E

,.

*

5w

0

-500

-1000

To 50

VALVE A, TEST 2, STEP 2

15

10

.0

I

I0

. , p * I e p a a I a a a a I a a B I I * * i i

-5 1

-10

-15 

I 10 20 30

TIME(SEC)

40 50

79
VALVE A, TEST 2, STEP 2

.m0-

im1000

500

MD

400

20D

0

-200

TIME(SEC)

VALVE A, TEST 2, STEP 2

3

2

1

. 0

I-M -1

-2

-3

-4 30

TIME(SEC)

s0
20

15

VALVE A, TEST 2, STEP 2 I I I I I I I a a I P I I a i ,

E0

.

T

E

10

5

i

aI

o .

-5 :

0

I I I I .I I 2 I I . I I I I I. I I

10 20 30 40

TIME(SEC)

50

VALVE A, TEST 2, STEP 2

20

15

to

hl

t

ti

I

t

10

5

0

-5

0 10 20 30

TIME(SEC)

40 50

S1
VALVE A, TEST 2, STEP 2

20

15

10

0 10 20 30 40 50

TIME(SEC)

VALVE A, TEST 2, STEP 2

500I boo ,$i I

400I

300

>P. 200

0 10 20 30 40 50

TIME(SEC)

82
VALVE A, TEST 2, STEP 2

600

500 _

Lr 400 _

I-

> 300

! 200 _

> 100

0

-100

ri n

. . . .

. -

.. . . I I I

10 20 30 40

1IME(SEC)

50

VALVE A, TEST 2, STEP 2 YOUr

t2 1.5

r 1.0

I.-

2 1.5

0.0t

, I * I I a I I I I I . I a I I I I I I

-* ,* . . . . , . . . . , . . . . I . . .

I 10 20 30

TIME(SEC)

40 50

-83
2.0

1.5

1.0

LI

Cl 0.5

0.0

c

VALVE A, TEST 2, STEP 2 .I I I I 1 1 I .I I I * I I 

I - - - - - - - - - - - - - - - - - -10 20 30 40 50

TIME(SEC)

VALVE A, TEST 2, STEP 2

30000

ih u1Juu

0

? -10000

-20000

50

TIME(SEC)

84
1130

10801

.2"2.1060

C4

n 1040

VALVE A, TEST 2, STEP 3&4

I . I . i . . . . I . I I

1020

1000

0 20 40

TIME(SEC)

60 60

VALVE A, TEST 2, STEP 3&4

1130

1080

.17 1060

.

te3 1040

1020

1000

980

0 20 40 60

TIME(SEC)

80
VALVE A, TEST 2, STEP 3&4

11D0

1080

0,

.EL1060

..

L 1040

1020

1000

0 80

VALVE A, TEST 2 STEP 3&4

20

15 

0,10

.in

CL

.. 5

I-T 5

cl -5

I* I I I 

t. - '

I * * I * * a I a

-101

-15

a 20 40

TIME(SEC)

60 80

86
VALVE A, TEST 2, STEP 3&4

120

100

SP

Il

.m

.

80

60

40

20

0

-20

3

2 

IL

40

TIME(SEC)

s0

VALVE A, TEST 2, STEP 3&4

-

I.,

ts

0

-1

-2

-3

87
VALVE A, TEST 2, STEP 3&4

20

I I ~ ~ ~ ~ , I I 

15 -

FU

E

0

V- 5

T

0

-5 I I I I II I I

i

20

15

10

-5

-10

0 20 40 60 aC

TIME(SEC)

VALVE A, TEST 2, STEP 3&4

en~~~~ I : 

, , , 

0 20 40

TIME(SEC)

60 80

88
VALVE A, TEST 2, STEP 3&4

20

15

10

5

0

-5

0

800

20 40 60

TIME(SEC)

so

VALVE A, TEST 2, STEP 3&4

I * I I

600

II01

fILAITh

400

200

O _ I

-200 

0

. . . ~ ~ ~~~~~~~I l I . . . I I - -

40 20 40

TIME(SEC)

89

60 80
VALVE A, TEST 2, STEP 3&4

eoo

600

I - I . . . . .~~~~~~~ I

I

.

CS

400

200 : j~~~~~~~~~~~~~~~~~~~~~~~~~~~~ 0

-2,00

2.0 -

I a I - L I I a I I a I 

0 20 40 60

TIME(SEC) 40

VALVE A, TEST 2, STEP 3&4

2 1.5

0 1.0

A

2 0.5

0.0

80

90
VALVE A, TEST 2, STEP

4

iIP

2

I

0

, -- I I II, . - I I I' I .....

-1I

-2 1

CI 20 40 0

TIME(SEC)

60 8s

VALVE A, TEST 2 STEP 3&4

20000

10000

~~ 0

.. -10000

c -20000

-30000

-40000

-500o

40

TIME(SEC)

80

91
VALVE A, TEST 2, STEP 5

1400 

1200

v100

.

.. 800

C'J

e 600

X 400 

200

0

0D

10 20 T30 40

TIlME(SEC)

50

VALVE A, TEST 2, STEP 5

1500

1000

.21

.E.

1t1

500

0

-500

0 50

TIME(SEC)

92
VALVE A, TEST 2, STEP 5

1500 _

10o

500

0

-500 -

D 30 10 2 0

~IM(SC) 40

VALVE A, TEST 2, STEP 5

50

50

07

ITIME(SEC)

.93
VALVE A, TEST 2, STEP 5

12 0 0 . . . ..

1000

V, 800-/

.i i

600

400

200

0

-200 , .. . , . . . . , . . . , . . 0 10 20 30

TIME(SEC)

VALVE A, TEST 2, STEP 5

2

-1\

-2~~~~~~~~~

TIME(SEC)

.94
VALVE A, TEST 2, STEP 5

20 ,. . . . . . . . . ...... 

151

InU

E

Qa

,,

10

5

a a a . I . I . a I . a . a . a , I a a. a

. * L . . As . I . . . . I * * * I * * * .

0

-5

0 10 2n 30 40 50

TIME(SEC)

VALVE A, TEST 2, STEP 5

20

15

83hi

10

5

0

-5

5

TIME(SEC)

95
VALVE A, TEST 2, STEP 5

20

15

. .

10

5

. I I I I I I I I I I 1 . I I I I I I I I

. . . . . I . . . . . . . . . . . .

0

-5

cl 10 20 30 40 50

TIME(SEC)

VALVE A, TEST 2, STEP 5

600

400

CI I I I I I I I I . A d

He~~~pAW fI

I A I I 

200

0

-200 . . I . I . I . . I

0 20 30 40 50

TIME(SEC)

.96
VALVE A, TEST 2, STEP 5

B00

YEWI

.,

In

-

400

200

, I I I I . a I, * I ,I aI , a I I I . I

- S S I I I I I I I I I I I I * * i I I I I I *

0

-2001

0

2 

20 30

TIME(SEC)

40 50

VALVE A, TEST 2, STEP 5

U,

I1

a

-1

-2

-3

30

TIME(SEC)

SD

97
VALVE A, TEST 2, STEP 5

4

L')

IIJ*

3

2

1

0

-. I a I I I I I S I I I I a I I .

I I I I a I I I I I I I a I U I

-1 I

0 10 20 30

TIME(SEC)

40 50

VALVE A, TEST 2, STEP 5

-10000

S -20000

-30000

-40000:

0 10 20 30 40

TIME(SEC)

50

98
VALVE A, TEST 2, STEP 6&7

1200 _ _ . ,

100i ~~~~~~~~~~~~~~~~~~~~~~~~. E *D0

C.1 600

400

200

0

0 20 40 60

TIME(SEC)

VALVE A, TEST 2, STEP 6&7

100_ , , ,- , , * 1

800

.2' 600

I~)400

t 200

0

s0

0

99
VALVE A, TEST 2, STEP 6&7

500

400

*'3 300

'4- 200

I,

E100

0

-100

30,

B 20 40 60

TIME(SEC)

80

VALVE A, TEST 2, STEP 6&7

20F

oP

*1

. .

EJd~

* I * I * I I

a I I I 2 I I I I I a I a I 

-lot

-20 _ _

0 20 40

TIME(SEC)

.100

60 s0
VALVE A, TEST 2, STEP 6&7

1200

1000

M 800

~60 CL

IEd 400

200

0

VALVE A, TEST 2, STEP 6&7

. _

I.

-J

0

-1

-2

-3

80

101
VALVE A, TEST 2, STEP 6&7

20

151

L,

10 . lo E

0

r-5

0

- I I I I I I I I I I I

I I I I I I I I I I I I -5

20 -

I

20 40

TIME(SEC)

60 80

VALVE A, TEST 2, STEP 6&7

I I I I I * * -

15 [

e10

. .

5

I

11

I

0

-5 I I I I . I I I 

a 20 40

TIME(SEC)

60 30

102
VALVE A, TEST 2, STEP 6dc7

20

15

r 10

y 5

hi

I I I

_ I

l

.

-5 4 * . I I I I 

C

600

500

20 40 60 80

TIME(SEC)

VALVE A, TEST 2, STEP 6&7

I I I . p I I I I I I p I

I 

. I

I400

300

200

100

0

-100

v 20 40

TIME(SEC)

60 so

.103
VALVE A, TEST 2, STEP 6&7

800

Goo

o o

0 4WD , .

5: 20

Co

-200

I.- 

40

TIME(SEC)

80

VALVE A, TEST 2, STEP 6&7

I - - I

I I . . . .~~~~~~~~~~~~~

n 0.6

5 0.4

5 0.2 =3

I I I I . . I * a I I

k0.D

0 20 40

TIME(SEC)

so s0

104
VALVE A, TEST 2, STEP 6&7

4

En 3

.. 2

1

-1

a

I I I I I I I I I I I I I I

I I I I , , a I . , I I a a

2u 40

TIME(SEC)

60 80

VALVE A, TEST 2, STEP 6&7

40000

20000

0

-20DOO

-40000

40

TIME(SEC)

.105
VALVE A, TEST 2, STEP 8&9

0

-20

. _

40

CNt

1 -60

-80

-100

0,

60

TIME(SEC)

100

VALVE A, TEST 2, STEP 8&9 - ~ ~ - -~ - - - - - - - - - - -

I I * I | * * I * * 

-20 -

a -4

,cn

If -6 I- -Wv .

-80 _

-100 L

l

I I I I . I , 2 a I I a I 

I _ _ _

20 40 60

TIME(SEC)

80 100

106
VALVE A, TEST 2, STEP 8&9

0

-20

-40

-60

-80

-100

a 20 40 60 s0

TIME(SEC)

100

VALVE A, TEST 2, STEP 8&9

I

0

'6s -1

T -2

.- 3

-4

-5

100

TIME(SEC)

.107
VALVE A, TEST 2, STEP 8&9

20

10

l5

. 0

-10

-20

-30

a 20 40 60 80

TIME(SEC)

100

VALVE A, TEST 2, STEP 8&9

3

2

1

5-

-J

0

-1

-2

-3

0) 100 TIME(SEC)

108
VALVE A, TEST 2, STEP 8&9

20 I I I I . a , I a a I I I . I I I 

15L

U,

FLno a 10

v5

0

0

-

I I I . I . I 

I 20 40 60

TIME(SEC)

80 100

VALVE A, TEST 2 STEP 8&9

20

15

e 10

T 

0

-5

I

I

a 60

TIME(SEC)

.109
VALVE A, TEST 2, STEP 8&9

20

15

RI

e 10

t 5

0 I

-5

0 20 40 60 80

FIME(SEC)

VALVE A, TEST 2, STEP 8&9

600

500

aQ 4 0 0

8 300

I..

; 200

:> 100

0

-100

_

An d~~~~~I * I '

| I - I I I * I I I I I I

3 20 40 60 80 100

TIME(SEC)

*110
VALVE A, TEST 2, STEP 8&9

800

600

Io 400

. .

>~ 200

0

-200

2.0.

l 60

TIME(SEC)

100

VALVE A, TEST 2, STEP 8&9

I I I I I I 

sn 1.5

23to

6 1.0

I-

_ 0.5

0.0

-~~~~~~~~~~~~~~

-

I , , , I

60 0 20 40

TIME(SEC)

.111

s0 100
VALVE A, TEST 2, STEP 8&9

3.0

2.5

I--

8 2.0 >.

F 1.5

x 1.0

Lii

(3 0.5

0.0

-0.5

0

40000

20000

0 

-20000

0

-i

-40000

-60000

0

60

TIME(SEC)

100

VALVE A, TEST 2, STEP &9

20 40 60 so

TIME(SEC)

112

100
VALVE A, TEST 3, STEP 1

1100

1050

.0

CM4

) 950

L io

900

* I I I I * I 

_ | *| 9 9, Iwv t 

850 1

Cl 10 20

TIME(SEC)

30 40

VALVE A, TEST 3, STEP 1

1150

1100

1050

tr)

) 1DO

950

900

C

I I I I I I I I I 'I I I I

I I I I Ip ,I ,I .I I p I .a

10 20

TIME(SEC)

30 40

*113
VALVE A, TEST 3, STEP 1

1150

1100

oT'u

CL 1050 .

Lb 1010

950

900

. . .I . .I .I .

. . I I I . I . .I . I 

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 3, STEP 1

0.5

.1, 

d -0.5

T-

-1.0

a 40

114
VALVE A, TEST 3, STEP 1

0

-5

dEJ -15

I

-25

-30

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 3, STEP 1

30

20

ia

E

° 10

. 0.

_ . a I aa I I I i a I I I I

I a a I I I I I I I a , I a I a I -10

0 10 20

TIME(SEC)

30 40

115
VALVE A, TEST 3, STEP 1

30

U

C)

20

10

-10 6 20

TIME(SEC)

40

VALVE A, TEST 3, STEP 1

25

20

15

10

5

a

-5

0 20

TIME(SEC)

.116
VALVE A, TEST 3, STEP 1

600

500

I-2400D

** 300: In D

C 200

100

0

0

600 

VALVE A, TEST 3, STEP 1

I- 0C..

C-)

400

200

0

-200

0

-117
VALVE A, TEST 3 STEP 1

2.0 . . . I I

I,)

-

__

1.5

1.0

0.5

I 

0.0 I I I

4

I I

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 3 STEP 1

L')

LIi3

2

1

0

0 10 20 30

TIME(SEC)

40

118
VALVE A, TEST 3, STEP 1

20000 .. .. . , . .. . .. . , . . , 

10000

-10000

-20000

-30000

--'0000 I i *

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 3, STEP 2

.21

En 1040

1020

1000 f I a a I I I

0 20

TIME(SEC)

.119
VALVE A, TEST 3, STEP 2

1200 * * * * * * * * * * * * * * *

1000

.800i .2 aoo

"600

400

200

0 a p p I

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 3, STEP 2

1200 , , , , X , a * * 

1000

. 600

400

200

0 1

0 10 20 30 40

TIME(SEC)

*120
2

0

*ll]

° -2 .,

Ed

m

VALVE A, TEST 3, STEP 2

i i , . . . . , . . . .I 

-6 

-a

1200(

1000

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 3, STEP 2

cm

0m

IWo0

600

400

200

0

-200

20

TIME(SEC)

40

121
VALVE A, TEST 3, STEP 2

3.

2 

'S O

I

-1 

-2J

-1

-3 l

0

30 

40

VALVE A, TEST 3, STEP 2

25t

X 20

E

0.

105- 

T

0

-5

* * * I * * I * * I * *

* * * * I* I I I I I

0 0 20

TIME(SEC)

30 40

*122
VALVE A, TEST 3, STEP 2

30

20

E

t D

g3

. . . I I . I I *II I I

* I I I .* I I I * I 

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 3, STEP 2

25 - - - - - -T 

20 

1 j5

r10

0

I I . I . , I I I I 

I I I I I * p I I I I a I -5

0 10 20 I0

TIME(SEC)

30 4

123
VALVE A, TEST 3, STEP 2

MD0

600

Ul

400

200

5.

0

-200

I 1 U I I I I ' I I I I U - 1 5

U U U ~ I * I * I *

0 10 20 30 41

TIME(SEC)

VALVE A, TEST 3, STEP 2

Boo

I I I I I I I . I I * I I I i I I

600

Ln

Ino? 400

C.,

i~ 200

0

2l

-200 * I I U I p p I I I * * t P I I U I U

0o 10 20

TIME(SEC)

30 40

*124
VALVE A, TEST 3, STEP 2

2.0

1.5 L

cnI.-

FS

A1

5

=1

1.0 L

I S I | I i . * | I S S S S | . * * 

I I I , 1 , I I I, I -. . -

0.5 

o.o L

--0.5

I 1 20

TIME(SEC)

30 40

4

2

-2

VALVE A, TEST 3, STEP 2

* S S I I . I S . I I I I I I S I

. . . I I I . . . , . a a I I . . I -4

0 10 20

TIME(SEC)

30 40

125
VALVE A, TEST 3, STEP 2

30000

20000

0o

- 10000

R -20000

-30000

-40000

1200

40

1150 

. _

.

LUj

VALVE A, TEST 3, STEP 3&4 * , . ' , 

* I I I * * I * , I I * a 

11 I

1050

1000

0 20 40

TIME(SEC)

60 80

126
VALVE A, TEST 3, STEP 3&4

1200

1150

0E

' 1100

1050

1000

o 20 40 60 so

TIME(SEC)

VALVE A, TEST 3, STEP 3&4 1200 . . , , . ' ' ' 

1150

ct

m 1100 

1050

To

127
2

a

cm

-2

CEl

VALVE A, TEST 3, STEP 3&4

I I I I I I I I I

*1 I I a I I I I I1 f 

-4 .

-6

0 20 40

TIME(SEC)

60 so

VALVE A, TEST 3, STEP 3&4

so

0) 60 'i

. 402 

D 20

-20

-40

0

128
VALVE A, TEST 3, STEP 3&4

3

2

1

d0

a

-1

-2

-3

is

0 20 40 60

TIME(SEC)

a0

VALVE A, TEST 3, STEP 3&4

in

.

E

2D

10

0

-10

0 80

*129
VALVE A, TEST 3, STEP 3&4

30

I I I

20

a)

10

-10

25

AL~~~~~~~~~~~~~~~

.1

I . .

l 20 40 60 eC

TIME(SEC)

VALVE A, TEST 3, STEP 3&4 I~~ . .

I I I 

20 

8 15

.10

T5

r-

-5 

I

p . . , . . ,

20 40

TIME(SEC)

60 80

130
VALVE A, TEST 3, STEP 3&4

600

500

I0

400

300

200

100

18~~~~ i

AY~A#I M I

0

-100 tz.

0

p p I p I p I I I I I ,

20 40

TIME(SEC)

60 80

VALVE A, TEST 3, STEP 3&4

800

600

I-

-J

c

400

200

0

-200

0 20 40 60 80

TIME(SEC)

.131
VALVE A, TEST 3, STEP 3&4

2

i, 

¢ -I1

i -2

I * I I * I I * I II

I I I I -3

0 20 40

TIME(SEC)

60 80

VALVE A, TEST 3, STEP 3&4

4

3

. .

0

I2

lLU

B1

6o

I I I I I I I I I I I

I I4

. . . I I I I 7 0O

20 40

TIME(SEC) - 60 80

.132
VALVE A, TEST 3, STEP 3&4

20000 , a , . , *

10000

M-000

*2 -20000

0~~

-=D

-30000_

-4D000 I I I

0 20 40 60 8

TIME(SEC)

VALVE A, TEST 3, STEP 5

1200

1000

C- BD.0O 

600

400

0 10 20 30 40

TIME(SEC)

*133
VALVE A, TEST 3, STEP 

1500

1000

.P

, 

m3

500

0

0

1500 

1000 

VALVE A, TEST 3, STEP 5

0"

.S.

,d. 500

0

-500

20

TIME(SEC) 40

134
VALVE A, TEST 3 STEP 5

50

40

.

I

Ed

m

30

20

10

0

-10

0 10 20 30 TIME(SEC)

40

VALVE A, TEST 3, STEP 5

600

.

I400

20

0

-200

20

TIME(SEC)

40

*135
VALVE A, TEST 3, STEP 5

3

2

0 I.-

m

--J

-1

-2

a 10 20 30

TIME(SEC)

40

VALVE A, TEST 3, STEP 5

30

20

Un

E,.

~ 10

-10

- - - - p -I I I I I I I I I

I I I I I I I I I I I I I p p-A

0 10 20

TIME(SEC)

30 40

.136
VALVE A, TEST 3, STEP 5

30 . .. . . . . . . . . . . . . . . .

20

,,10

0 

-10

0

25

20

E 15 

t 10

T 5

a V

-5

. . . .

I I * I * I Il

I I a I I I & I . | . |

10 20 30

TIME(SEC)

40

VALVE A, TEST 3, STEP 5

20

TIME(SEC)

137
VALVE A, TEST 3, STEP 5

600

500

,, 400

. >.. 300

;: 200

m 100

-1o0

-100

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 3, STEP 5

600

500

,, 400

I-. 0 ~3

C1 200

> 100

0

-100

0

138
VALVE A, TEST 3, STEP 

2

-1

0

: -2

-3

| I I I I B I 5 9 I I

* I * * I L I * * I 1 I * . *

4

D 10 20 30 40

TIME(SEC)

- VALVE A, TEST 3 STEP 5

Q 3

2

E~ 1

I I * * * * I I

-. ,I . . . ... . , . -. . . , I . .

L

10 20

TIME(SEC)

30 40

*139
VALVE A, TEST 3, STEP 5

0

-10000

S -20000

-300

I I 

-40000

1000

500

F. I . . . , I I I I I I I . I I I a . .

10 20

TIME(SEC)

30 40

VALVE A, TEST 3, STEP &9

C.

Ca

a

I I I I I p 1 1 I I I

-500 

-1000

ci 20 40 60

TIME(SEC)

80 100

140
VALVE A, TEST 3, STEP 8&9

100

°-100

( -200

-300

.

_ I I I I * I I 

I I I * . * I I I I -400 .

0 20 40

TIME(SEC)

60 80 ioo

VALVE A, TEST 3, STEP 8&9

100

0

-100

10, ..

: -200

-300

-400

0

TIME(SEC)

141
VALVE A, TEST 3, STEP 8&9

4

2

C To

-2

Cd -4

-6

-8

200

0

CT)

-200

-400

TIME(SEC)

VALVE A, TEST 3, STEP &9

- - - -

I I I I I a I I I

-600 v-

-8001.

a 20 40 60

TIME(SEC)

80 100

.142
VALVE A, TEST 3, STEP 8&9

3

2

1

, e

:D

-J

0

-1

-2

-3

a 60

TIME(SEC)

100

VALVE A, TEST 3, STEP 8&9

30 I a I I 4 I T I I I _ a a I

20

tn

FU

E

" 10

. .

T

-10 I. I I . I I I I a I I I I

0 20 40 60

TIME(SEC)

80 1I

I0

0O

.143
VALVE A, TEST 3, STEP 8&9

30

20

0

10

-10

I I I I I I I

I I , I a I I t I I I I I a

0 20 40 60

TIME(SEC)

s0 100

VALVE A, TEST 3, STEP 8&9

25

20

1 15

10

5

0

-5

TIME(SEC)

144
VALVE A, TEST 3, STEP 8&9

600

500

1 400

I-

> 300

> 200

> 100

0

-100

0 100

TIME(SEC)

VALVE A, TEST 3, STEP 8&9

600

C,,

ti-

:- "

0

400

200

0

-200

0 1 60

TIME(SEC)

145
VALVE A, TEST 3, STEP 8&9

2.0

Q 1.5

T3 1.0

I0.5

0.01

4

e 2

I. 0

I.-2

I~

It

I I I II I* A I I I I

* * * I , a a I * * * I * a I I I a a

20 40 60 so

TIME(SEC)

100

VALVE A, TEST 3, STEP 8&9 . . . . . . . . . . . . . . . . . . . I I II 

I I I I I I I . . . I . I . . I. -4

0 20 40 60

TIME(SEC)

80 100

.146
VALVE A, TEST 4, STEP 1

1000

980

P- 960 D'AhM

I..'

1.4

a920

900

1000

TIME(SEC)

VALVE A, TEST 4, STEP 1

980 I

.0

E.,

to

960

* I * I a * I , I I I I I I I I I I I I I I I

940 

9201

900

0 10 20 30

TIME(SEC)

40 50

147
1500

1000

as

.,

VALVE A, TEST 4, STEP 1 ... , *** .. , , I * ' ' ' ' '.S

. .. 

500

a 

-500

-2 

a 10 20 30

TIME(SEC) 40 t

50

VALVE A TEST 4, STEP 1

-41

0P

ID-

-6 1 I44, * krI I . I . I . I * * I I I I I * 

-8 

-10

a 10 20 30 40 50

TIME(SEC)

.148
VALVE A, TEST 4, STEP 1

100 * I * * I I I I I I I - - - - - -

80 I

601 CL

.i

mo

401

* * I * } * I I I * . * I I * I I I * *

. . . I . . . . I . . . . I . . . . I . . . .

201

CI

-20

-401

CI 10 20 30

TIME(SEC)

40 50

VALVE A, TEST 4, STEP 1

2

1

a

I-.

m

0

-1

-2

0 30

TIME(SEC)

149
VALVE A, TEST 4, STEP 1

20

15

U,

n

10

K E o

0

- 5 T

a

20

15

: 10

0 l

-5

c

VALVE A, TEST 4, STEP 1 .

_ I a I a . I . I . I 

I I , I I I I I

I

I . . . . . . . . - - .- . - - . . .~~~~ - - I. -a -a a a a a a 

10

TIME(SEC)

-150

40 I50
VALVE A, TEST 4, STEP 1

20

15 :

t 10 

T 5 

0 

-5 -

600

500

TIME(SEC)

VALVE A, TEST 4, STEP 1

d400

300

200

100

.1 . , . I I * I . .. . . I .. 

:. .. . . . I . I . . . . I . . . ~~~.I . ,

0

-100

13I 10 20 30

TIME(SEC)

40 50

.151
VALVE A, TEST 4, STEP 1

Boo

600

I-.

0

C-4

400

200

I a I I p I t I a I I I p p I p p * #

. I I_ 1 - , I I 

a

-200

2,

]

1

10 20 30

TIME(SEC)

40 50

VALVE A, TEST 4, STEP 1

E6

I1

0

-1

-2

-3

30

TIME(SEC)

50

.152
VALVE A, TEST 4, STEP 1

4

(I

Li

3

2

I

0

* * . . I p h p I . p p I I p * . p I . p p p

-1 

cI 10 20 30

TIME(SEC)

40 50

VALVE A, TEST 4, STEP 1

0 

-10000

> -200

-30000

-4DD

-400 00 

-50000

l

-

I p . . I . . . . I . . . I I . . . . *

' 2 30

-~~~ - ~~~~~~~~~. - - - - - - - I . I - I I I I I I I 

I 10 20 30

TIME(SEC)

153

40 50
VALVE A, TEST 4, STEP 2

1100

1050

.2 1000

C4 950

900 

so

800 

1500

1000

TIME(SEC)

.

CL

,,

VALVE At TEST 4, STEP 2

500 I* * . * * * * p * * . * * * . * * * * . I 

ol

-500 1

EI 10 20 30

TIME(SEC)

40 5io

154
1500

1000

.E

,-

500

0

VALVE A, TEST 4, STEP 2

* , . . | * . . . § . . . . I I I

* I I I I I I I I , * I * i , I i i a 

-500 

-10001

4: 10 20 30

TIME(SEC)

40 50

VALVE A, TEST 4, STEP 2

2

a

.c -2

0-

Ed -6

-8

-10

0 30

TIME(SEC)

155
VALVE A, TEST 4, STEP 2

1200

1000 I

800 as

. .

600

400

200

-. I . . I . . . . I . I . Ia I I I I I . I a I I 

* . . . I . . .a I a . . I . . . . I . . .

0

Ann ~-w I

0

I -,

10 20

TIME(SEC)

30 40 50

VALVE A, TEST 4, STEP 2

I-

-J

0

-1

-2

-3 

To 10 20 30 40

TIME(SEC)

50

156
VALVE A, TEST 4, STEP 2

20 I I . I I . . I I I I I I I I a I I I I I I

15L

U

E

0

10

.5

0

-5 

0

. . . . . . . . . . . . . . . . . . . .

10 20 30 40

TIME(SEC)

50

20

VALVE A, TEST 4, STEP 2

aI I , . I lI I I I I a II a

15 -

10

5

0

I1

I

-5 

0

I . . . . . . - . .. a - . . . I I . a I 1 . 2 I 0 I . . . . . . . . . . . .

TIME(SEC)

.157

I

50
VALVE A, TEST 4, STEP 2

20

15

10

5

0

-5

C

6CC

SOC

* I I I I I I I I I I I I I I I I I I a I I I

. I . . I , . I I I . * . a . I u a I * a

II 1D 20 30 4D0 5D

TIME(SEC)

VALVE A, TEST 4 STEP 2

Cl

I1Q

400

300

200

100

v v-- I I .I a I I I I * a I I . . 1 . I I 

: . I , II, .

01

-100

L 10 20 30

TIME(SEC)

158

40 50
VALVE A, TEST 4, STEP 2

800

600

U,

I0?

0!

400

200

0

-200

D 10 2D 30 4D

TIME(SEC)

50

VALVE A, TEST 4, STEP 2

2.0

$2 1.5

6 1.0

I--

M 0.5

0.0

. . I I . . . . I . . . . I . . . . I . . . .

A I I I I I I A 9 I I .- I -- -. 1 I. .

I 10 20 30 40 50

TIME(SEC)

.159
VALVE A, TEST 4, STEP 2

1.2 . . . . . . . . . . . - .f . - .x .E x . x . .

1.0

U,

Iii

0.8

0.6

0.4

.~~~~~~ , . . . . .

- A I

.. . . .,I . . .. ,I . . .. ,I .. .. I . .

0.2

0.0

--0.2 

0 . . . . . . . . . . . . . . . . . . . . . . . .

10 20 30

TIME(SEC)

40 50

VALVE A, TEST 4, STEP 2

20000

C

0

-J

TIME(SEC)

160
VALVE A, TEST 4 STEP 3&4

950

900

.91

.

C4 850

800

750

920

900

.m

0.

4~ 880

860

840

VALVE A, TEST 4 STEP 3&4

0 20 40 60

TIME(SEC)

.161

80
VALVE A, TEST 4, STEP 3&4

1000

950

.P

.

900

850

oo

0

VALVE A, TEST 4, STEP 3&4

-1.5

-2.0

0P

.5i

I.c

'- -2.5 -*

-

-3.0

-3.5

0 20 40 60

TIME(SEC)

s0
VALVE A, TEST 4, STEP 3&4

20

0

0P

.r_51

~-20 I. .

C A

-40

-60

2

0 

CI-

-1 1-

-2 

40

TIME(SEC)

so

VALVE A, TEST 4, STEP 3&4

-3

a 20 40 60

TIME(SEC)

163

80
VALVE A, TEST 4, STEP 3&4

20

21

tIJ

E0 o

-ID

-20

a 20 40 60 8D

TIME(SEC)

VALVE A, TEST 4, STEP 3&4

20

151

e10

5

-~~~~~~~~~~~~~~~~~~~~~

I

0 -

-8 I I I , I . I. I I , 

a 20 40

TIME(SEC)

60 80

164
VALVE A, TEST 4, STEP 3&4

20 . . . . . . .I . . .S

. , I I II I 

15L.

U,

t 10

S

0 .

-5 . . . I . I I . . , . .*

0 20 40

TIME(SEC)

60 80

VALVE A, TEST 4, STEP 3&4

800

600

LI

En2

-200 _

Io

20 40 60

TIME(SEC)

80

.165
VALVE A, TEST 4, STEP 3&4

800 I I I I I I I I I~~~~~~~ I I I .

6{

(I,

-j

o 4{

c.,

T 2f

I

-2[

2

1

i, 

0

I-- -11

-2

-3

D

Jo30

)D

Jo

* 1 I . . I . . I . I . I J0

20 40

TIME(SEC)

60 80

VALVE A, TEST 4, STEP 3&4

I I I I I I I I I I

* I I I a I * I * * 1

40 20 40

TIME(SEC)

166

60 80
VALVE A, TEST 4, STEP 3&4

4

en 3

2

(1)3

p 2

-1

C

I I I I I I I I , I I

I I Il I . I I I I I

20 40

TIME(SEC)

60 80

VALVE A, TEST 4, STEP 3&4

20000

10000 

0

-10000

-20000

-C3 -3000

-40000

S I 'I ' II 'I '- ' -

C._ I

* . . . , . * aI ,,I I -50000 

lI 20 40

TIME(SEC)

60 so

167
VALVE A, TEST 4, STEP 5

1200

1000

.2a

cs 800_

C,,

600-

400 

To 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 4, STEP 5

1500

100

m

, 

"I

500

0

-500 l

0

TIME(SEC)

168
VALVE A, TEST 4, STEP 5

1500

1000

500

-500

U 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 4, STEP 5

30

an 10la

CL

-10

I-2

A -20

TIME(SEC)

.169
VALVE A, TEST 4 STEP 5

1200 . I., .. , ...

1000

400

-200

-200 1 I a 1 ai a a I a a

0 5 10 15

TIME(SEC)

VALVE A, TEST 4, STEP 5

0.0

-0.5

-1.0

5 1.5-\

C -2.0

-2.5

-3.0

-3.5

D 5 10 15

20 25

25

TIME(SEC)

170
VALVE A, TEST 4, STEP 5

20

15

in

E

0

10

5

0

-5

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 4, STEP 5

20

15

_

r 10

T ~5

0

-5

15

TIME(SEC)

171
VALVE A, TEST 4, STEP 5

20

15

-5-

0

60

50

v_ 400

I-

-J

of 300

2Wa 

20

> 100

50

5 10 15

TIME(SEC)

20 25

VALVE A, TEST 4, STEP 5

I~~ h ' , .

II b ,i

A d I . I I

-100 I *I I I I I 1 , 1 I I I I I I .I I I I .I . .

0 5 10 15

TIME(SEC)

20 25

172
VALVE A, TEST 4, STEP 5

80 * * * I I I a # a * I I I I I I & I I I I

600

C,-)

'-

o 400

,I.

Cq

- 200

a

0

-200 l . I . . I I I I I I I I -

0 5 10 15 20

TIME(SEC)

25

VALVE A, TEST 4, STEP 5

0.8

W 0.6

S 0.4

9.-

2 0.2

0.0

0

TIME(SEC)

*173
VALVE A, TEST 4, STEP 5

3.0

2.5

.,

I-1d

,

Li

2.0

1.5

1.0

0.5

0.0

-0.5

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 4, STEP 5

0.

-10000

@ -20000

- -30000

-40000 

0o 25

TIME(SEC)

174
VALVE A, TEST 4, STEP 7

1600

14D

.2' 1200

m~ 1000

K800

60

400

ED

1500

100

VALVE A TEST 4, STEP 

. _

Eto

L.

500

a

175
VALVE A, TEST 4, STEP 5

1500

1000

0.

ok

A 

W00

0

-500

0

VALVE A, TEST 4, STEP 7

60

40

0P

T 20

A

0

-20

0 40

176
VALVE A, TEST 4, STEP 7

,

CA

1200

1000

80

600

400

200

0

-200

0 10 20

TIME(SEC)

40

VALVE A, TEST 4, STEP 7

2

1

-9 0

-

-2

-3

0 10 20 30

TIME(SEC)

177

40
VALVE A, TEST 4, STEP 7

20 Iu -I I I j I I - I I I I I I a I I I I I

15 -

ni

V

D. 10 E

a

.,5

is

-5 

0 - . . I I I I10 20 30

TIME(SEC)

40

VALVE A, TEST 4 STEP 7

20

I I I

15 -

10

. I

T5

- 5 I I I a I . . . . I I I I I

a 10 20

TIME(SEC)

30 40

178
VALVE At TEST 4, STEP 7

20 _

15

10 _

5 -

0 _

-5

600

500 

400 

I--

> 300

| 200

O:

> 100

0

-100

0

20

TIME(SEC)

40

VALVE A, TEST 4, STEP 7

I Ia I I

20

10 20

TIME(SEC)

179

30 40
800

600

VALVE A, TEST 4, STEP 7 a I I I I I I I I I I I I

1-

C-,

5

.

l

400

200

a . - -

-2{In . . . . ~~~~~~~~~~~~I I I . . .

0.8

V20.6

3 0.4

I-0.

2 0.2

0 10 20 30

TIME(SEC)

VALVE A, TEST 4, STEP 7

* I , , * * * * , * I 

to

0.0

a 10 20

TIME(SEC)

180

30 40
VALVE A, TEST 4, STEP 7

4

I.2 I1 2

0 I

-1

C

I ,I ,- ,- - ,I I 4 , =,Y

I I I I I I I I I 

I I a , II . I I

. . . , s . s~~~~~

I

- - I I I I.iiI I I I C I . . . I

10 20 30

TIME(SEC)

40

VALVE A, TEST 4, STEP 7

0

-10000

L. 

g -20000

- -30000

-40000

0 10 2D 30

TIME(SEC)

181

40
VALVE A, TEST 4 STEP 8&9

3D0

2500

2000 0O

ol

(na1500

. I . I I I I I I a I , I I

* S I I I I . S I . S

1000

500 1

a

-500

a 20 40

TIME(SEC)

60 a0

VALVE A, TEST 4 STEP &9

0

-50

.m

C4

LLI

-100

-150

-200

0 20 40 60

TIME(SEC)

182

80
VALVE A, TEST 4 STEP &9

0

-50L

0,

PO -10D

I

* 1 1,1 . .I. I I I I

* . I I *I I 

-150 -

-200

03 20 40

TIME(SEC)

60 s0

VALVE A, TEST 4 STEP 8&9

0

-210

0

.E. --40

c -60

-80

-100

40

TIME(SEC)

80

183
VALVE A, TEST 4 STEP &9

-2

I I! I. . t . . * * | * * -~~~~ .

JlI Y l n @a -11 ... 1 [j.,w~ "I' 7.1

tFT8g8qWH8l9g -Al~f*

-4

D. -6

< -8

I-

-lot-

-12 r I I l l

100

an

*0 50

I.

do

-80

20 40 60 at

TIME(SEC)

VALVE A, TEST 4 STEP &9

I . , .* 9 * . p 

40~~~~~~~~

U 20 40 TIME(SEC)

184

60 80
VALVE A, TEST 4 STEP &9

3

2

1

I-

-J 0

-1

-2

40

TIME(SEC)

80

VALVE A, TEST 4 STEP 8&9

20

I I I . .

15

U3 2

E

0

T

t,

10

5

L- 0o

-10 I I

40

0 20 40

TIME(SEC)

185

60 I

JE

30
VALVE A, TEST 4 STEP 8&9

20 I I I I I l I | 1 l I

15 -

e 10

. a

5

-s :

0

* . . , I . I I . . . , .I. I

20 40

TIME(SEC)

60 so

VALVE A, TEST 4 STEP 8&9

20

15

9 10

. .

-5

-10

0 20 40 60

TIME(SEC)

.186

so
VALVE A, TEST 4 STEP 8&9

600

500

, .

I-C.)

400

300

200

100

0o

-10D

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 4 STEP 8&9

800

600

I-

-J

0!

(I

400

200

0

-200 I . I I

20 40 60

0

TIME(SEC)

187

s0
VALVE A, TEST 4 STEP 8&9

2.0

L2 1.5

; 1.0

I--

2 0.5

0.0

I I I

I I I I I I I

a 20 40 60

TIME(SEC)

s0

VALVE A, TEST 4 STEP &9

4

En3

I--

d

'' 2

T 1

p O

E

I I I * I I I I I I I I I

[ * I I I -1 -

0 20 40

TIME(SEC)

60 so

-188
VALVE A, TEST 5, STEP 1

1500

1000 -

.9,

U1

.

C4 500

n

a L.

-500

200t

r)100c

500

I . . . .~~~~~~~~ l I . I

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 5 STEP 1

I ,, IIIIj 

I . I 

c _

0 10 20

TIME(SEC)

189

30 403
15DO

1000 

CL1

'I- 500

I0,

VALVE A, TEST 5, STEP 1 _ = -, . - - -,- --- I - - I m I

I . . . I . . . I I

0 

-500

0 10 20

TIME(SEC)

30

VALVE A, TEST 5, STEP 1

2

0

. .

e -2

C

Is.

-4

-6

To 40

190
150

100 1

0"

CL

.

> 50

0-

D

-50

VALVE A, TEST 5, STEP 1 I , I I I , . I I I * I I I p I

I . I I I . . . . I I I I I I I I I I

a 10 20

TIME(SEC)

30

VALVE A, TEST 5, STEP 1

4

2

C

0

-2

-4

40

20 40

TIME(SEC)
VALVE A, TEST 5, STEP 1

20

15

ul U

10

E

I.0

= 5

To :D

0

-5

20

15

Si

,.10

0

-5

20

TIME(SEC)

40

VALVE A, TEST 5, STEP 1

a 10 20 30

TIME(SEC)

.192

40
VALVE A, TEST 5, STEP 1

l0

8 L

16

4

2

To

I I I I I I I I I I I I I I I

-2

C 10 20

TIME(SEC)

30 40

VALVE A, TEST 5, STEP 1

600

500

,, 400

> 300

I..

r- 200

O O

C-)

>§ 100

lo

-100

0 10 20 30

TIME(SEC)

193

40
VALVE A, TEST 5, STEP 1

800 . . . . . . . . .~~~~~~I I

600 I:

Io 400

CM

1 200

C)

0

-200

c

0.8

0.6 

I

I I I . . . .

10 20 30

TIME(SEC)

40

VALVE A, TEST 5, STEP 1

tar

I--

0.4

9 0.2

2

' 03.0

I S I S I SI SISI I I I I

-0.2

a 10 20

TIME(SEC)

30 40

194
VALVE A, TEST 5, STEP 1

4

ILd

0

3t

2

1

0

a I I I * I* * i I I I

'1 $wj4> Afr9V aISwmiP

-1

a 10 20

TIME(SEC)

30 40

VALVE A, TEST 5, STEP 1

10000

a

-10000

9 -20000

*r -30000 0

-J

-40000

-50000

0 10 20 30

TIME(SEC)

40

195
VALVE A TEST 5, STEP 2

1500

1000 

.91

c"J 500

I,- Qn

EQ

r * , | | * * l 1 ' , ' l I . ' l I

I e , * I I * I I I * 

to

-rinn I

0

2000 -

1500 

.0

.

eO 1000

500 F

10 20

TIME(SEC)

30 40

VALVE A, TEST 5, STEP 2

196
VALVE A, TEST 5, STEP 2

1500

1000

.0

i.

LU

a00

a

-500

1 r

0 

0o

CL -1 L

CL -

-3

0 20

TIME(SEC)

40

VALVE AEST 5, STEP 2

-4

0 10 20 30

TIME(SEC)

197

40
VALVE A, TEST 5, STEP 2

1000

800

Ujs ok 600

S 400

Gj 200

0

-200

4 -

2-

0 m -

-j 

-2 -

-4 -

0o

20

TIME(SEC)

40

VALVE A, TEST 5, STEP 2

10 20 30

TIME(SEC)

-198

40
VALVE A, TEST 5, STEP 2

4

6

L

EU

E-

., I I I I I I I I I 

D I 10 20 30 40

TIME(SEC)

VALVE A, TEST 5, STEP 2

8I .

6

0

I I I I I I I I I I a I 

a . , . I , . , . I . a a a . I . a a

4- . I II 1 I I I 

I

-2 40 0 10 20

TIME(SEC)

199

30 4
VALVE A, TEST 5, STEP 2

a

6

4

. 2

, , , , I I I I I I -

.~~ ~ I . .I I I I. 0

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 5 STEP 2

600

400 

LO

,,

l

Cr 200

I I I I .I . . I . I . I .

0 1

-200

0 10 20

TIME(SEC)

30 40

200
VALVE A, TEST 5 STEP 2

600

600

Id)

IIN

0

400

200

0

-200

a 1o 20 30 TIME(SEC) 40

VALVE A, TEST 5, STEP 2

2.0

. .

J

.5

1.0

0.5

0.0

--0.5

20

TIME(SEC)

.201

40
VALVE A, TEST 5, STEP 2

0.3

LI

.I 

0

VALVE A, TEST 5, STEP 2

15000

0

-j

10000

5000

0

20

TIME(SEC)

202
1600

1580

.0

" 1560

C..

c) 1540

VALVE A, TEST 5, STEP 3&4

I I I 1 I & f I I I I j 

a a I I I I I I - i - I 

15201

1500

1800

D 20 40 60 BG

TIME(SEC)

VALVE A, TEST 5, STEP 3&4

17001

.21

" 1600

InI, I~

Id.

I I I I I I | r I | | I I I

2 . . I . . . I I I I I . . .I 1400 i

c~oI 20 40

TIME(SEC)

203

60 80
VALVE A, TEST 5, STEP 3&4

1600

1550

CP

.EL

- 1500

1450

1400

2,-

80

VALVE A, TEST 5, STEP 3&4

01

.in

XL -2

M -4

A

-B

I ., I I I .,,,I U I 

I . I . . I -8I

i 20 40

TIME(SEC)

60 8

204
VALVE A, TEST 5, STEP 3&4

80:_

a, 60

*.40

20

-20

-40 , , 0 20 40 60 80

TIME(SEC)

VALVE A, TEST 5, STEP 3&4

4 . * E * * * * 

2

-2

-4 . . I . . , I . . . | I .

0 20 40 610 8

TIME(SEC)

205
VALVE A, TEST 5, STEP 3&4

20 . .. . . . . . . . . . . . * I I I r r ~~~~~~I I I 

15L.

t 10

0

-5 : I I I I . I a I . , I . . I

20

15

: 10

I.

5

ao

3 20 40 60 8

TIME(SEC)

VALVE A, TEST 5, STEP 3&4

II I I I I

I I I I I , I I I I a _

1

-5

a 20 40

TIME(SEC)

206

60 so
VALVE A, TEST 5, STEP 3&4

600

500

-i, 400

> 300

200

0

100

0

I IJ94

I

I,

L-

-100 

a

-

I . . I I a , . I a I I I

I 20 40

TIME(SEC)

60 80

VALVE A, TEST 5, STEP 3&4

Bo0 . . . , .~~~~~~~~~~~~ I I

6w L

An

Io? 400

C)q

0

-200

0 .I . I . I . I L . I I I a a I I a a a I a a .

20 40

TIME(SEC)

60 80

207
VALVE A, TEST 5, STEP 3&4

2.0 . , I .I , I . I I I I I I

1.5

In

1.0

§ 0.5 En

- . 0.0 

-0.5 

I

I

I

__

L.e-

. . . I . I I . . S

20 40

TIME(SEC)

60 80

VALVE A, TEST 5, STEP 3&4

3.0

2.5

En

8 2.0

2I 1.5

x 1.0

w

Z30.5 ESD.

R _ _ i

I I I I I I 

0.0

-0.5 t

I 40 20 40

TIME(SEC)

208

60 so
VALVE A, TEST 5, STEP 3&4

2000

10000

V) 0

.. -10000

i-20000

4 -30000

-J

_ I I I I I I I 

_~~~. 

I

-40000:

-50000

cI I vo~~2 40

TIME(SEC)

0 so

VALVE A, TEST 5, STEP 5

2000 . .. ,, . a I 4. , , -. . . . I~~~~ I . . . . I . . .  I - - - - .

1500

.212.. 1000

1D 0.,

Li 500

LU0..

.

0

. . . I - . I . . . I -500 a I I I I I * I I I I _ -

0 5 10 15

TIME(SEC)

209

20 25 30
VALVE A, TEST 5, STEP 5

2000

1500

.0

EL

. .

en

1000

500

o 

0 5 10 15 20 25

TIME(SEC)

30

VALVE A, TEST 5, STEP 5

1500

1000

C,

0a

500

0

-500

a 30

210
30

20

0P

I-j

-

Li

m

10

0

VALVE A, TEST 5, STEP 5 , ~ ~ , . . . , . . . . , . .1 . . , . . .

i I I . I I 1I-I 1 I I~

-1DI

-inI

0

1500

1000

5 10 15

TIME(SEC)

20 25 30

VALVE A, TEST 5, STEP 5

cm

'i

.

IN

Ed

500

0

-500

TIME(SEC)

211
VALVE A, TEST 5, STEP 5

2

1

0

.e

-1

-2

-3

-4

20

15

15

TIME(SEC)

30

VALVE A, TEST 5, STEP 5

Un 2

PI

E

a

10

5

* , * * I I I I * I I I I 1 I II I I -, * I I I I

* * I * * * * I * * I * * * * I * * * I * *

0

-5 . . . . . . . . . . . . . . . . . . . . . . . . . . . . .

0 5 10 15

TIME(SEC)

20 25 30

212
VALVE A, TEST 5, STEP 5

20

15

t 10

T5

ao

-5

20

15

10 

t

T 5:

O.

0 5 10 15 20 25

TIME(SEC)

30

VALVE A, TEST 5, STEP 5

-5

0 5 10 15 20 25

TIME(SEC)

213

30
VALVE A, TEST 5, STEP 5

600 . . . . .. . . . . . . . . . . . . . . . .

500

VI

I0

400

300

200

100

I I I I A I , I I I .I I I I pI I I I

0

-100 I

a

6100 

5 10 15

TIME(SEC)

20 25 130

VALVE A, TEST 5, STEP 5

a I a I I I . I. . . I . . . I 

500

En

I0

CN4

I

400

300

200

100

0

-100 I

I: , . . I . I . , I I I I, I. I I a I I i I . I . . I I3 5 10 15

TIME(SEC)

20 25 30

214
VALVE A, TEST 5, STEP 5

1.0

0.8 

t2

2

0.6

0.4

0.2

0.0

* * | I * * i £ I * * * * | * * * * I i * * * | p ' * I

-0.2 

cI 5 10 15

TIME(SEC)

20 25 30

VALVE A, TEST 5 STEP 5

3.0

2.5

I-.

IPl

2.0

1.5

1.0

0.5

0.0

-0.5

To 15

TIME(SEC)

215
VALVE A, TEST 5, STEP 5

10000

oa_

-10000

-20000

-30000

-40000

-50000,.. ,.....,.. .,.....,. 0 5 10 15 20

TIME(SEC)

VALVE A, TEST 5, STEP 6&7

1500

1400

2.1300 .\,

t]1200

11D0

1000 . . . . . .a . . . , . . .

25 30

216
VALVE A, TEST 5 STEP 6&7

1000 . * * * X * * * X ' * ' * 

100 I I I .

~4DO

200

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 5 STEP 6&7

1000 * , , , I * * , * * * M * * 

8100

O0)600 

"I 400-

t 200 -

0

-20 . 4 

0 10 20O 30 40

217
VALVE A, TEST 5, STEP 6&7

CD

1

, .

o

15

10

5

01

-5

-15

40

VALVE A, TEST 5, STEP 6&7

1400

1200

Um100 0

BOB

-.,

El 600

400

200

20

TIME(SEC)

218

40
VALVE A, TEST 5, STEP 6&7

0

-1 

. G

,_ -2:

-3

-41

20

15

VALVE A, TEST 5, STEP 6&7

fn

EE

T

10

5

0

-5

0 10 20 30

TIME(SEC)

219

40
VALVE A, TEST 5, STEP 6&7

20

15

t 10

. .

0 

-5

20

15

t 10

T 5

Qa

I I I I I- I I I I I I

10 20 30 40

a a 2 2 I a I I a I I a I I a

I 10 20 30 40

TIME(SEC)

VALVE A, TEST 5, STEP &7

I I I a a a I I I T I a I 

-5 I I I

a 10 20

TIME(SEC)

220

40
VALVE A, TEST 5,TSTEP &7

600

500

U,

IQ.

400

300

200

100

I I I I . .l . I .I *

@ | § 2 I I I e 

0

-100

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 5 STEP 6&7

600 - - - - - - - - - - - - - - -

c,

In

C-)

500

400

300

200

* I I I A * * I 

L;

I ; | | I | 2 @ |~~~~~~~~~~

I

103

0

-100 . . . . . . . . . .

20 0 10 20

TIME(SEC)

221

30 40
VALVE A, TEST 5, STEP &7

2.0

m2 1.5

I.-

5 0.5

0.0

c

3

2

.- .

1

T w

I-

-11

C

I- - - I - I I ---v I I I I I 4 I 

* , , , I . . , , I . . 4 . I I

-I

_ 10 20

TIME(SEC)

30 40

VALVE A, TEST 5, STEP &7

40

222
VALVE A, TEST 5, STEP 6&7

40000

20000

IL

-J

a

-20000

-40000

-60000

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 5, STEP 8&9

200

150

.

m

CNq

-

EL

10

50

0

0 40

TIME(SEC)

223

80
200

1501

CLR

VALVE A, TEST 5, STEP 8&9 * .* I , I I I I S I A I

a I a I I I - I - I I I i I I I 

100 I

50

0

a3 20 40

TIME(SEC)

60 80

VALVE A, TEST 5, STEP 8&9

200

150

0P

(n 100

50

0

a 20 40 60 so

TIME(SEC)

224
VALVE A, TEST 5, STEP 8&9

M-2

0-

.,

-4

0 20 40 60 80

TIME(SEC)

VALVE A, TEST 5, STEP 8&9

8 . * * , * * * ''

d6 Kh

0)1+ F

O .. 

_0 .__. _ 

.225
VALVE A, TEST 5, STEP 8&9

150

loDD

0,

.1

0

0

I I I I a I I I I I I I & a 

I I * - I - ,2 t S I . * I I , 1 , S -50 

50

50

0

1?i 0m

0!-5

20 40

TIME(SEC)

60 80

VALVE A, TEST 5, STEP 8&9

. I I I I I I I I I I I U

* * I * I * S I * 

-100 

-150L

01I 20 40

TIME(SEC)

60 80

226
VALVE A, TEST 5, STEP 8&9

4

2

c

m

0

-2

-4

20

15

0 40

TIME(SEC)

VALVE A, TEST 5, STEP 8&9

In

m

E

0

T

10

5

a

-5

a 20 40 6

TIME(SEC)

.227

80
VALVE A, TEST 5, STEP 8&9

20

15 :

: 10

.,

0 

-5 -

0

20

15

10

. .

~~ 5

0o

I . I

a I I - - I I a I I . I I I . I

20 40 60

TIME(SEC)

s0

VALVE A, TEST 5, STEP 8&9

-5

0 20 40

TIME(SEC)

228

80
VALVE A, TEST 5, STEP 8&9

800

600

, 

It-,

400

200

I I I

t I I I a I I I - a- I - p-I 

Di

-200 '

800

6001

I 20 40

TIME(SEC)

60 80

VALVE A, TEST 5, STEP 8&9

cn

I-

-4

0

5~~

,,)

400

200

0

-200

0 20 40 60

TIME(SEC)

229

80
VALVE A, TEST 5, STEP &9

2.0

1.5

1.0

¢ 0.5

a 0.0

I 1 I I I I I I I

--0.5

4 -

23

TI1

LUJ

a

-1 -

I I I I .I I .I I I. 

a 20 40 60

TIME(SEC)

80

VALVE A, TEST 5, STEP 8&9

0

230
VALVE A, TEST 6, STEP 1

1400

1390

2. 1380

.,I

C14

CL370

1360

1350

1400

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 6, STEP 1

19 I

.,2. 1380

Lb 1370

S I I I I . . p p 20I . p p p I p p p p

13601.

1350*

a 10 20

TIME(SEC)

231

30 40
VALVE A, TEST 6, STEP 1

1450

0~

oo

.E.

U) 1420

1410

1400

0 

20

TIME(SEC)

VALVE A, TEST STEP 1 .~~ . . v , y . * * 

-21

am

.,

It~~~~~~~~~~~~~g,~~~~~~~~~~~

L~~,H,,4

.. . 7 . . . . , ..

-6 I

-8

0 10 20

TIME(SEC)

232

30 40
VALVE A, TEST 6, STEP 1

100 - . . .I * * I I 

BDL

.-

Di

AL

60 -

40 -

201-

-

-=20

0

3 -

2 

0

ts

ci 

-1

-2 

-3 

- I I I . . I I

W itvvM~v 

I . . . .

10 20

TIME(SEC)

-

30 40

VALVE A, TEST 6, STEP 1

20

TIME(SEC)

40

233
VALVE A, TEST 6, STEP 1

20 . . . . . . . . . . . . . . . . . . I . I I I H

15-

U,

10 E

0

=-5:

0=

-5

0

I I

10 20

TIME(SEC)

30 40

VALVE ATEST 6, STEP 1

20

15 -

Si

e 10

5

0

-5

I I I I I I I I I I I I I I I I I

I I a . I . . . . I . . I I I . . .

0 10 20

TIME(SEC)

.234

30 40
VALVE A, TEST 6, STEP 1

20

15

io

_ 10

t 5

ao

~I I 

* * , * I * I I * I I * * I

* * C _ I a a a I 

-5 . . . .

aI 10 20 30 40

TIME(SEC)

VALVE A, TEST 6, STEP 1

601I 

400

Ln

II0I

200

0

a . , a . I . .a a ~~~~~~I U1 I 1 I a a a a 

-200

0 10 20 TIME(SEC)

235

30 40
VALVE A, TEST 6, STEP 1

600

500

VI) 400

I-

° 300

-,,

>. 200

>. 100

0

| as r

X

-

-

-

-

, , I I a I I I I I I 

-100 . 0

2_

I

. . . . I . . I , . 1 . I 

10 20

TIME(SEC)

30 40

VALVE A, TEST 6, STEP 1

U,

0

I--

2

-3

0 10 20 30

TIME(SEC)

40

236
VALVE A, TEST 6, STEP 1

4.

E 2

T 1

-1

0I 20

TIME(SEC)

VALVE A, TEST 6, STEP 1

0

-10000

.. -20000

-30000

-C

I I a I I * I I I I . I I I I I 5 I I I I

-40000L.

-50000 I I I I I . I I I I I I I I

0 10 20

TIME(SEC)

30 40

237
VALVE A, TEST 6, STEP 2

1400

1390

,

.0.

Lb 1370

1360

1350

0

1500 -

*g) 1000_

.

500

20

TIME(SEC)

40

VALVE A, TEST 6, STEP 2

238
VALVE A, TEST 6, STEP 2

1500

.m 1000

9-. .

500

0

2-

0 

L -2 v

,, .

-6

-8 T

4D

VALVE A, TEST 6, STEP 2

10 20 30

TIME(SEC)

*239

40
VALVE A TEST 6, STEP 2

1500

1000

CL

In

,E.

Co

500

0

-500

a 20

TIME(SEC)

40

VALVE A, TEST 6, STEP 2

4

2

._

, -

In

0

-2

-4

20

TIME(SEC)

240
VALVE A, TEST 6, STEP 2

20

15

Up

2

Ez 10 E

0

V- 5

0

-5

20

0 20

TIME(SEC)

VALVE A, TEST 6, STEP 2

15

ba

e 10

5

I I I . , S I 7 I I I I I I

2 9 I I I i i I I I I i f I I t *

0

-5

0 10 20

TIME(SEC)

30 40

241
VALVE A, TEST , STEP 2

20

15

U3 w

t la

T 5

It

I I I I I I I S I S I I I I S

I S I I I I 1 e * S I * *

0 

- -- I

D

800

600

- - - - - - - - - - - - - - - - - - -

10 20 TIME(SEC) 30 40

VALVE A, TEST 6, STEP 2

E,

I-

-J

0

0-

400

200

0

-200

40

242
VALVE A, TEST 6, STEP 2

Bo

600

o 400

C-4

0-

-200-

0

ft 

- -1 -r ~~~~~~~~~~~I - A I I I I I^^ I ^ I I I I I 

I . . I I . . .

10 20 30

TIME(SEC)

40

VALVE A, TEST , STEP 2 rZ.U ,

~2 1.5 

6 1.0 

I5 0.5 

0.

Cx 

I a I I I

* ~I I I I a I I I I I I I a a . - -

I 10 20

TIME(SEC)

30 40

243
0.3

Lo 0.2

I-0

0.1

L D.0

LUJ

o -0.1 I--

VALVE A, TEST 6, STEP 2

I ' I ' I I I I ' I I I 4 I I I I I 

_-

-

-02 _

0

I I I I I a I I . . * I . I I

10 20

TIME(SEC)

30 40

VALVE A, TEST 6 STEP 2

20000

10000

.- 0

=i -ioo

-20000

-30000

-40000

20

TIME(SEC)

244
VALVE A, TEST 6, STEP 3&

m-~~~~~~~~ 

6

so0

VALVE A, TEST 6, STE 3&

I~~ - i_r-S-EP 

so

245
VALVE A, TEST , STEP 3&4

1400

1380

0,

1360

.0.

(n 1340

1320

_ a I I I I A I a I I I 13001

D 20 40

TIME(SEC)

60 80

0

-2 1

0P .us

aD

m:

VALVE A, TEST 6, STEP 3&4

I I I , I I I a I I 

-6 

-8

0 20 40

TIME(SEC)

60 30

246
120

100 I

a, 80

'Lii

CL

*x 60

a 40

c 20

VALVE A, TEST 6, STEP 3&4

.. I I I I I I I I i

I I I I I I I I I I , I I I I -20

I 20 40

TIME(SEC)

60 SO

VALVE A, TEST 6, STEP 3&4

3

2

1

I- T 0

-2

-3

.247
VALVE A, TEST 6 STEP 3&4

20

15

. . * ,~~~~~~~~~~ I .I I * S

in

2

ES. 0

i0L

5

0 ~~~~~~~~~~~~~~~~~

-5 I I -

G -~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

l 20 40 50 80

TIME(SEC)

VALVE A, TEST 6 STEP 3&4

20 S .

I I . . I 

15

t 10

5

0u

-r

I l l HisW

a 20 40

TIME(SEC)

80

248
VALVE A, TEST 6, STEP 3&4

20

15

T0

I~ I I a I I I I II I I

l - -5 I I

20 40 60

TIME(SEC)

VALVE A, TEST 6, STEP 3&4

600

500

400

> 300

* 200

0 100

0

-100 80

249
VALVE A, TEST 6, STEP 3&4

ecu

600 I.

Io 400

C>.

- 200

0

0

-~~~~~~~~~~~~~~~~~~~~~

'I I

I I . , .

-2cin I I . . . I

2.0

Q 1.5

3 1.0

7 0.5

0.0

Jb

0 20 40 60

TIME(SEC)

VALVE A, TEST 6, STEP 3&4

, . I I . . . I . . . I . . . -

30

0 20 40

TIME(SEC)

250

60 so
VALVE A, TEST 6, STEP 3&4

4

w

3

2

1

0

-1

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 6, STEP 3&4

20000

10000

O 0

' -10000

2 -20000

9 -30000

-40000

-50000

0 20 40 60

TIME(SEC)

.251

80
VALVE A, TEST 6, STEP 5

1500 X i

a 500

E 

C,_

0 it 20 30 40

TIME(SEC)

VALVE A, TEST 6, STEP 5

1500 , . . . , . . . .

1000

-500

01

50

0 10 20 30 40

TIME(SEC)

252
VALVE A, TEST 6, STEP 

1500

1000

.B

U')

Soo

a

-500

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 6, STEP 5

40

30

CD

a-

(II

Cii

M

20

10

0

-10

-20

0 10 20 30

TIME(SEC)

.253

40
VALVE A, TEST 6, STEP 5

500 .. ., * .. . * . i * * a, * 

500

cr, 400

200

100

O~~~~~~~~~~~~~~~~~~ t 

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 6, STEP 5

3

-2

01- 

-3

-4

0 10 20 30 40

254
VALVE A, TEST 6, STEP 5

20

15

Ln

E

0

0

-5

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 8, STEP 5

20

151-

£CI 5

0

-5

I I S I I I IS I I I 

* * * * . I * I * I *

a 10 20

TIME(SEC)

30 40

255
VALVE A, TEST 6, STEP 5

20

15

10

5

0

-5 

601

501

I I I I I I i I I I I & I 

* * . . I , * I . I *.

0

0

10 20

TIME(SEC)

30 40

VALVE A, TEST 6, STEP 5

U,

IV)

400

300

200

100

O

-100

To 20

TIME(SEC)

40

256
VALVE A, TEST 6, STEP 5

800

600

V)

Io 400

: 200

C-)

0

-~~~~V1

I I I

-,,nnI -£ Lili -

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 6 STEP 5

2.0

1.5

1.0

N 0.5

-j 0.0

-0.5

II I U I I- I I I I 1'I 

i - ' -- -

i I

0 10 20 40

TIME(SEC)

257

30 19
VALVE A, TEST 6, STEP 5

3.0 _

2.5 I

; 2.0 _

I.

T3 1.'9:

T 1.0

wWI

D 0.5

0.0 

-0.5-

10000

10 20 30

TIME(SEC)

40

VALVE A, TEST 6, STEP 5

I I I I III I I I I I I I 

a 

~~~h T

-10000

D -20000 0

-30000

-40000

0

I . . I I . . I I I . l II

I

10 20

TIME(SEC)

30 40

258
VALVE A, TEST 6, STEP 8&9

a

-20

.21

& -40

tb -60

Lb-o

-80

-100

100,

) 20 40 60

TIME(SEC)

8o

VALVE A, TEST 6, STEP 8&9

I I I I I I I I I I I

so L0O

a 60

t L0

20

wo*** 2 ImAy~AwMwwvw

I I I f I a I . . I I I * I . a

a 20 40

TIME(SEC)

60 80

259
VALVE A, TEST 6, STEP 8&9

100

so

Cn

0 60

1 40

20

idN ,%Wm

40

TIME(SEC)

80

2

0

.0

CL -2

,I.

AL -4

a

VALVE A, TEST 6, STEP 8&9 , I I I , I I I I I . I I . .

I I I I I I I I _ I _ I 

-6 

-e 

0 20 40

TIME(SEC)

60 s0

260
150

100 I

T 50

I0

VALVE A, TEST 6, STEP 8&9 a I I I I I I I I I I I I

I I I II C5I 20 40

TIME(SEC)

60 80

VALVE A, TEST 6, STEP 8&9

2

I

.,

'- 0

Ia -1

-2

-3

-4

40

TIME(SEC)

80

261
VALVE A, TEST 6 STEP 8&9

20

15

E

a

nw

-5

20

15

10

5

a

-5

0 20 40 60

TIME(SEC)

s0

VALVE A, TEST 6, STEP &9

a 20 40 60

TIME(SEC)

262

80
VALVE A, TEST 6, STEP 8&9

20

15

10

. .D

925

0

-5

600

400

I0

40

TIME(SEC)

VALVE A, TEST 6, STEP 8&9

_j .

a I . aI . . I -200 40 0 20 40

TIME(SEC)

263

60 80
VALVE A, TEST 6, STEP 8&9

800

600 -

(n

Io 400

CM4

1 200

0

-200 I I I

0 20 40

TIME(SEC)

60 Bo

VALVE A, TEST 6, STEP 8&9

2.0

1.5

1.0

¢ 0.5

I -

0:, .0

I I a

-0.5 .

0

. I I I . I I I I I I a 1 

20 40 60

TIME(SEC)

264

s0
VALVE A, TEST 6, STEP 8&9

4

. .

ui

3

2

1

0

-1 L

0 20 40 60

TIME(SEC)

8s

VALVE A, TEST 6t STEP 8&9

0

-20000

-C

80

TIME(SEC)

:265
266
VALVE ATEST 7 STEP 1

1500

1000

.

C14 CLJSO5W0

03

I I I I I I I I , I I I I , I I I I

. . . . , . . . . , . .

0

-50D

0 10 20

TIME(SEC)

30 40

VALVE A TEST 7, STEP 1

2000

15DD _

.0

"' 1000

500

- * * * * I * I * 

* S S * I * * * S I * * S I * * Do 

o 10 20

TIME(SEC)

267

30 40
VALVE A, TEST 7, STEP 1

1500

1000

.M

,I- 500 a0

_ ' ' ' ' I ' ' ' ' I I I ' ' ' '

-500 . I I I . . . * I * * I I . . I

I) 10 20

TIME(SEC)

30 40

VALVE A, TEST 7 STEP 1

10

0

CP

1o

I0

-20

I . . . . . I . . . .

I I I I I I I t I I I I I I -30

0 10 20

TIME(SEC)

30 40

268
100

crP

EL

. .

I'

501

VALVE A, TEST 7 STEP 1

I . . . . I . . , . . . . , . . . S

0

-50

0 10 20

-: TIME(SEC)

30 40

VALVE A, TEST 7, STEP 1

4

2

0

-J

-2

-4

0 20

TIME(SEC)

* 269
VALVE A, TEST 7, STEP 1

20

15

in

10

K lo

E

0

0

-5

20,

VALVE A, TEST 7, STEP 1 . - - - - - - - - -_ -

15 

t 10

a

- 5

* .I I I I I I I I I 

* I I I~ ~ I i I a a I I I I I I f , 

a 10 20

TIME(SEC)

270

30 40
VALVE A, TEST 7, STEP 1

20

15

t 1

.

D 5

Ci0

-5

0

600

5W

,_1 41W Ln

1-

o 3D0

T 200

> Wc

-100

S I II I S I I a I * I I I I I I

* S S I * S I * I

iI,

.

10 20

TIME(SEC)

30 40

VALVE A, TEST 7, STEP 1

40

271
VALVE ATEST 7, STEP 1

600

500

ir, 400

I-. 0

5.300 

' 200

>~ 100

0

-100

C.

I I I I I i I I I I I I IT I

I~~~~ ~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~IA_

I I I I I I~~~~~~~~~~~~~~~

I 10 20

TIME(SEC)

30 40

VALVE A, TEST 7, STEP 1

2.D

U,.

,I

2i

1.5

1.0

0,5

0.0

-0.5

0 20

TIME(SEC)

272
VALVE A, TEST 7, STEP 1

2.5

~2.0

1.5

D 10 20 30 40

TIME(SEC)

VALVE A, TEST 7, STEP 1

I-- 

-0000F 2 

o-30000

0

-5 D , 0 , 4

0 10 20 30 40

TIME(SEC)

273
VALVE A, TEST 7, STEP 2

1500

1000

V)

500

U1

I I , I I I . . . I , 

. I I I * * s I I I I I I I I . -500 L

I 10 20

TIME(SEC)

30 40

VALVE A, TEST 7, STEP 2

2000

15D

.0

,E.

1000

500

0

0 20

TIME(SEC)

274
VALVE A, TEST 7, STEP 2

100

.9-

T 500

0

-500

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 7, STEP 2

.m00

us

CL

m -10

-20

-30.

0

a I I I a I I I I I I I I I

* I I I * * * I I * . . I I * * i I

:~~~ ~~~~~ I I

10 20

TIME(SEC)

30 40

275
VALVE A, TEST 7, STEP 2

1200

1000

CP 800

CL

.. 600

I 400

200

0

-200

4 -

2 

I 0 

I-o 

-2

-4 -

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 7, STEP 2

20

TIME(SEC)

40

276
VALVE A,: TEST 7,STEP 2 __rin

A, ------ ~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

15

Un

E

a V- 5

To

I I I * I I I * I I I

. . . *I . *I . I . I I . I I I I I I .I -5

{I 10 20 30 40

: TIME(SEC)

VALVE A, TEST 7, STEP 2

20

15

r 1D

£Ž 5

0

I I I I I * i I I I I I I I * a a

* , * * , , * * * i , v I , * * 

I~~~~~~~

. .. . ~ ~ ~ ~ ~ ~ ~ ~ ~ . ~ ~ ~~~~~~~~I I I I I -5rD 1D 2D - TIME(SEC)

277

30 4D
VALVE A, TEST 7, STEP 2

20

15

sJ

.

i

10

5

o I

-5 

600

500

to 400 -

. 0

;:* 200

> 100

0

-100

VALVE A, TEST 7, STEP 2

278
VALVE A, TEST 7, STEP 2

800

600

I

I-.

.

I0

400

200

0

I . I I I I I F I I . . .I , . .

I I I I i- I ' I. . I I I I I I . i-- *-L -200

2.0 ,

I 10 20

TIME(SEC)

30 40

VALVE A, TEST 7, STEP 2

=1

in.

1.5

1.0

* . . . I .II . I I I

I 

_

* . . . I e . . . I . . . I . .

0.5

0.0

-0.5 - - - - - - - - - - - - .- - - 0 10 20

TIME(SEC)

279

30 40
VALVE A,- TEST 7, STEP 2

1.0

LI)

ILI,

w.1

0.8

0.5

0.4

0.2

0.0

- . , II - , I * I I k . * I

I t I II I I I t I I I I I -0.2, I 10 20 30

TIME(SEC)

40

- VALVE A, TEST 7, STEP 2

20000

10000

i~ 0

-10000

M -20000

-j

-30000

-40000

20

TIME(SEC)

280
VALVE A, TEST 7, STEP 3&4

1500

1400

co

" 1300

C-l

t. 1200

1100

1000

2000

150

40

:- TIME(SEC)

.0

EL

-VALVE A, TEST 7 STEP 3&4

*' ' ' ' ' ' ' . : 

* I _p . , 

40 ~ ~ ~ ~ .

1000

500

0

a 20 40

: TIME(SEC)

281

60 80
VALVE A, TEST 7, STEP 3&4

1500

.0-

o

10 

. . . I I I I S I * I

I I I I I I I I I A a I a I I

20 40

TIME(SEC)

s0 80

VALVE A, TEST 7, STEP 3&4

aI

t

. .

'- -10

-20

-30

*~ ~ 5 ~ ~ * ~ S S | 3 5 I * S 

I I * I * * I a S S I a I a

40 0 20 40

TIME(SEC)

282

60 80
VALVE A, TEST 7 STEP 3&4

30

20

CL

'T 10

I-

-10

150

I I I I I I I I I I I 

-- I I I I . I I * I 

1 20 40 60 so

TIME(SEC)

VALVE A, TEST 7, STEP 3&4

loo1 cn

.0

I..- A SO

I

I I I I I I I I I I I

a

-50

0 20 40

TIME(SEC)

283

60 80
VALVE A, TEST 7, STEP 3&4

4

2

.S

a

-I

-2

-4.

a

20 

TIME(SEC)

VALVE A, TEST 7, STEP 3&4

15 -

Ul

l

10 E

0

I-5

To

rl-

* , , . , . - * * 

* . . , I I. , . I I . I I

-5

0 20 40

TIME(SEC)

60 80

284
VALVE A, TEST 7, STEP 3&4

20 , . . I , , . . . . I * * *

I 'I 1 I- I I I 

15L.

E 10

5

To

~~~~~~. . a , a I * * 1 I* -5 

OI 20 40

TIME(SEC)

60 80

VALVE A, TEST 7, STEP 3&4

20

15

t 10

T 2 5

a

-5

a 80

285
VALVE A, TEST 7, STEP 3&4

Boo

600

I200

. L_

-200

0 20 40 60 80

TIME(SEC)

VALVE A, TEST 7, STEP 3&4

800

600

-Jo400

C-)

0

-200 . . . , . . 0 20 40 60 An

TIME(SEC)

286
VALVE A, TEST 7, STEP 3&4

2.0

1.5

1.0

E 0.5 En

03(.0

S * S I I I I I I - - - - 1-- l 

0

I I

l 20 40 60

TIME(SEC)

a0

VALVE A, TEST 7, STEP 3&4

3.0

2.5

d 2.0

,I.

6 1.5

I8 0.5

O.5

-o.5

0 s0

287
VALVE A, TEST 7, STEP 3&4

20000 . . . * 

10000

MwoO I

~~ 0

' -10000

? -20W0

2 -30000

-40000

-50000

0 20 40 60

TIME(SEC)

VALVE A, TEST 7, STEP 5

1500 . . ,

1000

a0

-5M~ r 

80

0

TIME(SEC)

288
VALVE A TEST 7, STEP 5

2000

1500

.L

.

Uq

9-

Cn

1000

500

0

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 7 STEP 5

1500

.EL

. .

UT

(A

8K0Q

TIME(SEC)

289
VALVE A, TEST 7, STEP 5

20

10

CP

.Di

AL

I

, .

C:

0

-10

-20

-30 

0

150D

1000

TIME(SEC)

VALVE A, TEST 7, STEP 5

0cp

u0 

-500 

15

TIME(SEC)

25

290
VALVE A, TEST 7, STEP 5

2

I

0

rI-1

-2

-3

-4

TIME(SEC)

VALVE A, TEST 7, STEP 5

U'

M

E

0

20

15

10

5

0

-5 25

TIME(SEC)

291
VALVE A, TEST 7 STEP 5

20

0

15

~.a

!? 5

- :

0

15

10 

fn 5 

- 5

5 10 15 20 25

TIME(SEC)

VALVE A, TEST 7, STEP 5

25

TIME(SEC)

292
VALVE A, TEST 7, STEP 5

Soo

600

En

IC.)

400

200

0 

-200

600

500

I 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 7, STEP 5

I-

-J

0~

I-,

0

400

300

200

100

-~~ , . . . I . . . . I

-~~~~~~~~~~~

. ,. . I . . . . I . . . . I . . . . I

0 . . . . .

I 5 10 15 20 25

TIME(SEC)

293
VALVE A, TEST 7, STEP 5

1.0

En

I0.8

0.6

0.4

0.2

0.0

* , , , I * I I I I * I I I * I I I I

* I I I I . , , , I * . * * I p p p I I p * p -0.2

u 8 15 20 25

TIME(SEC)

VALVE A, TEST 7, STEP 5

4 I . . . I I I

IAI--

U,

w3

3

2

I

a

-1 l

l

I l l 5 10 I

TIME(SEC)

294

15 20 25
VALVE A, TEST 7, STEP 5

10000

I)n

-10000

$ -20000

-30000

-4DOO

-50000 . . I I I, I I 

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 7, STEP 6&7

I DD O 

CVJ 500

-500 . . 2 , , , , , , , , _

0 10 20 30 40

i

TIME(SEC)

295
VALVE A TEST 7, STEP 6&7

100)

800

to

n

-600

Lo 400

200

a

c

1500

1000

*I- 500

Id0

-500

40

VALVE A, TEST 7, STEP 6&7

20

TIME(SEC)

296
VALVE A, TEST 7, STEP 6&7

20

1D

.en 0

V -10

I-

-20

-30

-40

1500

5M CL

9 500 0 

40

VALVE A, TEST 7, STEP 6&7

40

297
VALVE A, TEST 7, STEP &7

1

D

.a -1

.

-3

-4

20

15

rU

Rm

E

0

T 5

.

-5

VALVE A, TEST 7, STEP 6&7

40

298
VALVE A, TEST 7, STEP 6&7

20

15

,, 10

5

0

-5 l

20 -

15

10

0

-5

VALVE A, TEST 7 STEP 6&7

20

TIME(SEC)

.299

40
VALVE A, TEST 7, STEP 6&7

600

500

to400

~300 

::: 200

:>: 100

0

-100

0

800 

Sa0 [

20

TIME(SEC)

40

VALVE A, TEST 7, STEP &7

In'3.

C.)

400

200

I

0

-200

20

TIME(SEC)

300

40
VALVE A, TEST 7, STEP 6&7

1.0

0.8I

LO

I-

§ 0.6

D 0.4

A 0.2

=i

0.0

S S S , I I I ,S I I I -0.2

4-

V) 3

.. 2

T 1

E o r

I-

-I L

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 7, STEP &7

20

TIME(SEC)

40

301
VALVE A, TEST 7, STEP 6&7

20000

! -20000

CJ -40000

-600

200

150

.0

cs' 100

50

0

'00

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 7 STEP 8&9

I I I I I ' I I * 

* S S S SI TI Lo 20 40

TiME(SEC)

60 so

302
VALVE A, TEST 7, STEP 8&9

60

50

.'340

to 30

LI,-

~20 

la 

0.

0

200

150

VALVE A, TEST 7 STEP 8&9

.0.

100)

50

a

.303
30

20

0D)

. .

Wa- 10L

VALVE A, TEST 7 STEP 8&9

I I I I 4 I I I p I I I

I I I I I I I I I I I I

0.

-10

40 I

20 40

TIME(SEC)

60 s0

VALVE A, TEST 7 STEP 8&9

p p p I I.I . . I I I I I I I

20

.

'M 0

S -20

i -40

D)

Lh|msell""zlsse.z*Es.9] M~~~~~~~~~t " .. ~~~~~~~~~~~~~ 

-60k

-80 E.

0

I I I I p I p * p I . I .

20 40

TIME(SEC)

s0

304
VALVE A, TEST 7 STEP 8&9

4

2

.-

-J

0

-2

-4

VALVE A, TEST 7 STEP 8&9

20

15

U,

.

E

0

10

5

0

-5

0 20 40 60

TIME(SEC)

305

80
VALVE A, TEST 7 STEP 8&9

20

15

: 10

CŽi 5

0

-5

20,

I

80

VALVE A, TEST 7 STEP 8&9 . . I I I a I I I 

1511

b 1a

. II

5? 

o M!

-5 

0

. . , . . . , .I . , . .

20 40

TIME(SEC)

306

60 80
VALVE A, TEST 7 STEP 8&9

600

500

-IC-)

400

300

200

10D

0

-100

0

VALVE A, TEST 7 STEP 8&9

S0

60

Ln

-

C.)

400

2D

0

-200

40

TIME(SEC)

80

307
VALVE A, TEST 7 STEP &9

2.0

I

1.5

1.0

0.5

0.0

-0.5

40

TIME(SEC)

VALVE A, TEST 7 STEP 8&9

4

is

.,

3

3

2

I

0

-1 40

T)E(SEC)

80

. . . .11 . - . . 0 

308
VALVE A, TEST 8, STEP 1

800

750

.2' 700

.

CI 650

600

II I I I I I I a I I 

550 L

500 LI~

0

800

600

El400 .

200

0

-200

10 20

TIME(SEC)

30 40

VALVE A, TEST 8, STEP 1

40

309
1400

1200 

C"

A

- 1000

I;

Si00

VALVE A, TEST 8, STEP 1

* . . . I . A I I I I I I . I a I I I

* * * S I * * * I * * * * I * * 

0

__ 

10 20

TIME(SEC)

30 40

VALVE A, TEST 8, STEP 1

401

.,

201

II I I I I I I I I j I I I I I I I I~ -I

I * ** I * I 

0

-20 . . . . . . . . . . . . . . . . . . . 0 10 20

TIME(SEC)

310

30 40
300

200

IElu Ci

100 1

VALVE A, TEST 8, STEP 1

0 -- ---* ---*-*- - I 

-100 

-200 

0 - - - - - - - - - - - - - - - - - - -

10 20

TIME(SEC)

30 40

VALVE A, TEST 8, STEP 1

4

2

._

., 0

-2

-4

0 10 20 30

TIME(SEC)

40

311
VALVE A TEST 8, STEP 1

20 r | T I g T I~~~~~~ r I I I 

15 _

tn

aloEa10 E

a

T .,

-5 I I I I I a I I I I I I I I 

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 8, STEP 1

20 a a i a * * ~ a a X - i * - aI g $ * I I * I I I

151-

810

0

2-

-5 I I I I . .I . . I I , . .Aa I 

0 10 20

TIME(SEC)

30 40

312
VALVE A, TEST 8, STEP 1

20

15 -

t 10

t? 5

To

. . . .I .. .I . I 

* . . . I . * I * I

-5 

lI 10 20

TIME(SEC)

30 40

VALVE A, TEST 8, STEP 1

600

zi- 400

> 300

T 200

i 100

313
VALVE A, TEST 8, STEP 1

800

In

o 400

1 200

0

0

-200

c

2.0 -

Q 1.5 "

i 1.0

9 0.5

0.0 -

0

I I I I * * I I I I I I I I I 

I I I L I I I I I I I * * t I I . . S

I 10 20

TIME(SEC)

30 40

VALVE A, TEST 8, STEP 1

10 20 30

TIME(SEC)

40

314
VALVE A, TEST 8, STEP 1

4.

83 

,

2 

To

w

s 1

0.

0 20

TIME(SEC)

40

VALVE A, TEST 8, STEP 1

0

-5000

F -10000

-15000

-20000 -2D

-25000

-30000

it

I~ ~ ~ ~ I, \ . . .~~~~~~~~~~~~~~~~~

I~~~~~~~~~~~~~~~~~~~~~~

I I I I :

10 20

TIME(SEC)

30 40

315
VALVE A, TEST 8, STEP 2

660

640

.2 620

Ce4 600

580

560

540

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 8, STEP 2

700

.2 600

: 500

W 400/

300

020:

0 10 20 30 40)

316
VALVE A, TEST 8, STEP 2

800

600

an

CEL

'I' 400

200

0

0

AM

. -2

<-4

fi -4

-6

-8

VALVE A, TEST 8, STEP 2

0 la 20 30

TIME(SEC)

40

317
VALVE A, TEST 8, STEP 2

600

500

a, 400

I.

AL

.. 300

eT 200

A 100

0

4-

2 _-

40

VALVE A, TEST 8, STEP 2

.

CJ

0

-2

-4

318
VALVE A, TEST 8, STEP 2

20 I * * I| 9 II I I I I I I I

1SL

i10

ry T5

0o

-5

20

15

10

C' 5

To

I I I I I i . I I I I I I I . .a S

a 10 20 30

TIME(SEC)

40

VALVE A, TEST 8, STEP 2

-5

a 10 20

TIME(SEC)

40

319
VALVE A, TEST 8, STEP 2

20

15

. 10

y95

0

I I I I I , aa * I * , . I .

I I I I I I I I I I I I I I -5

03 10 20

TIME(SEC)

30 40

VALVE A, TEST 8, STEP 2

600

500

-u 400

('-3

X 300

20

c100

.

0

-10

0 20

TIME(SEC)

320
VALVE A, TEST 8, STEP 2

W

CR

I1-i

o 41

'. 

>- 2

-21

2.0

(; 15

S 1.0

§ 0.5

C.o

Jo

30

Jo

40

VALVE A, TEST 8, STEP 2

.I I I I I I I I I I I I I I I I I

* S I S S * . . . I . . . . ~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~I .

I

10 20

TIME(SEC)

30 40

321
VALVE A, TEST 8, STEP 2

0.08

ewe 0.06

I-

-j

0

0.04

L 0.02

LU

ES0.00

-0.02

(

200C

1000

-100C

-2000

-3000

I I I I I I I I I I a I I I

. I I I I I I I I 

I0

0

0

0

10 20

TIME(SEC)

30 40

VALVE A, TEST 8, STEP 2

0

322
800

600

. .

04 400

O

VALVE A, TEST 8, STEP 3&4

a I I i i I I I I 

* a a I I I I I I I I I

200 L

0

1000

Up ~20 40 60 so

TIME(SEC)

VALVE A, TEST 8, STEP 3&4

800

.*2 600

PO 40D

tI)

U1 200 0E

I , I . I 

I * I * I

L-

-200

a 20 40

TIME(SEC)

60 80
VALVE A, TEST 8, STEP 3&4

600

400

CI 200

0

-20 .. ., 0 20 40 60 80

TIME(SEC)

VALVE A, TEST 8, STEP 3&4

2 . . . , . . , .

,, 2

a-

-6

-*8 . . . , . . . , , 

0 20 40 60 80

TIME(SEC)

324
VALVE A, TEST 8, STEP 3&4

120

100

En

'M

Io

E

LD

80

60

40

0

-20

0 20 40 6D

TIME(SEC)

80

VALVE A, TEST 8, STEP 3&4

4

2

0

-J

0

-2

-4

0 20 40 60

TIME(SEC)

.325

80
VALVE A, TEST , STEP 3&4

20 , .II . I I I I I I l I I 

15 

U'

10 E

0

T0 5

to

-5

20

15

: o

B

-59

. . , . . . , . . . , . .

0 20 40

TIME(SEC)

60 30

VALVE A, TEST 8, STEP 3&4

a I I I -

t I I I f I I I

40~~~~~~~~~~~~

I . . . . . .

0 20 40

TIME(SEC)

326

60 80
VALVE A, TEST , STEP 3&4

20

I . I . I .I I I I I I

151

t 1D

5

0

20 40 60 80

-5 

0

60C

50C

Vw 40C

> 30C

,.

r, 20D

- lo

-100

I l I 

I ~20 40 60 8D

TIME(SEC)

VALVE A, TEST 8, STEP 3&4

I)

I

I I I I II .I , I I . - I -. - . I 

I I ~ ~I f I

20 40

TIME(SEC)

60 80

327
VALVE A, TEST 8, STEP 3&4

800

600

tn

1-

o 400

,I.

2 200

0

-200

0

VALVE A, TEST 8, STEP 3&4

2.0

1.5

U)

1.0

A 0.5

I 0.0

-0.5

I I I I I I I I I

* . . ~ I I 

0 20 40

TIME(SEC)

60 80

328
VALVE A, TEST 8, STEP 3&4

4

En3

'' 2

n 1

w

001 --

* S * 5 I I I I I I I I I I I

* I I | 4 I S I || * I -1 l

0 20 40

TIME(SEC)

60 80

VALVE A, TEST 8, STEP 3&4

20000

10000

81 0m

-10000

< -20000

-30000

-4000000WO 20 40 60

TIME(SEC)

80

.329
VALVE A, TEST 8, STEP 5

800

600

.21

2 400

C4

En 200

-200

0 5 10 15 20 25 30

TIME(SEC)

VALVE A, TEST 8, STEP 

10O

800

600

400

200

0

0

330
VALVE A, TEST 8, STEP 5

800 ' ' r----. ' ,, . . | ' s * , ' ' ' ' ' ' ' ' '.*

600

00

v 200

0 5 10 15 20 25 30

TIME(SEC)

VALVE A, TEST 8, STEP 5

10:

-

-15 , , , ,

D 5 1 15 20 25 30

TIME(SEC)

331
VALVE A, TEST 8, STEP 5

600

400 cm

.u

I,

200

0

-200

1 

2

1 

15

TIME(SEC)

30

VALVE A, TEST 8, STEP 5

,

I-J

-1

-2

-3

-4

15

TIME(SEC)

30

332
VALVE A, TEST 8, STEP 5

20

15

, .1

T

10

5

C

-5

20

15

0 15

TIME(SEC)

VALVE A, TEST 8, STEP 5

I I I I I I I I I I I V F -I I I -I I | I 1 I I lI 

. 10

5

0

-5. I I I I 1 i I I I I I * I I I p 2 a I I 2 I I I I a I p

I 5 10 15

TIME(SEC)

20 25 30

333
VALVE A, TEST , STEP 5

20

15

e10

t 5

C

-5

600

500

sQ 400

> 300

T 200

0

-100

15

TIME(SEC)

VALVE A, TEST 8, STEP 5

15

TIME(SEC)

334
VALVE A, TEST 8, STEP 5

600

400

(n

I- 200

03

a I I I I I I I I I I I I I I I a I I I I I * I A I I I

-200 

lI 5 10 15

TIME(SEC)

20 25 30

VALVE A, TEST 8, STEP 5

0.8

Ln I.-

8

6

0*

1

5

=1

0.6

0.4

0.2

0.0

I I I i a I I I I I I a i I I I I I I I I I I 

I I I I I I I I a I I I I I I I I I I I I I t I I I I - A aJ -0.21

c

i 5 10 15

TIME(SEC)

20 25 30

335
VALVE A, TEST 8, STEP 5

4

cn

ill

0

I3

2

I

0)

-1

0 5 10 15 20 25

TIME(SEC)

30

VALVE A, TEST 8, STEP 5

15000 

O

,< -5000

''-10000_

-15000

¢

° -20000

-25000

-30000

To 15

TIME(SEC)

336
VALVE A, TEST STEP 6&7

800

60W

,CD

.J

400

200

* . * * 1 * f I I I I I I I j I I I I j I I I I I I I

* I * * I , , . I . . . . I . . . . I . . . . I . . .

-200

io

600 -

. 400

X 300

t 200 :

100

0

To

T

L

10 20 30

TIME(SEC)

40 50 60

VALVE A, TEST 8, STEP 6&7

337
VALVE A, TEST 8 STEP 6&7

BOB

600

..

lo

400

200

0

VALVE A, TEST 8 STEP 6&7

15

10

cm

a-

.0

.,

5

a

-5

-10

-15 

To 30

TIME(SEC)

'338
VALVE A, TEST 8 STEP &7

800

600

'{i

CL

400

200

0

1 

o ;

0 10 20 30 40 50

TIME(SEC)

60

VALVE A, TEST 8 STEP 6&7

I-

.-.

-1

-2

-3

-4

30

TIME(SEC)

60

339
VALVE A, TEST 8 STEP 6&7

20

15

U

E

0

TT

10

-5

-5 

20

20 -

15

10

5-

o 

-5

30

TIME(SEC)

VALVE A, TEST 8 STEP &7

30

TIME(SEC)

340

60
VALVE A, TEST 8 STEP 6&7

20 or

15

3 10_

T 5 

a

-5

a

60D

500

400

300

200

100

10 20 30 40 50

TIME(SEC)

60

VALVE A, TEST 8 STEP 6&7

In

I-.

0-

I I I I I I I I I I I 5 5 S I S I 5 S S S I 5 5 5 I 

5 -t 3 I I 5 I I I I I I I I a I I 3I I I a I I I 2 I , I 1 T 

0

-100

D 1D 20 30

TIME(SEC)

341

40 50 60
VALVE A, TEST 8 STEP 6&7

600

400

I-.

C4

I200

a

-200

a 10 20 30 40 50

TIME(SEC) 60

VALVE A, TEST 8 STEP 6&7

1.0 - .-. . -. .- -. .- . . . . . . . . . .

0.8

i

I

0.6

0.4

0.2

0.0

-0.2 _ 2 I I a a I I I a a T

ioI 10 20 30

TIME(SEC)

342

40 50 60
VALVE A, TEST 8 STEP 6&7

3

w

0

2

1

To

. c I a. . I I . I . I . I, I...

. . . . . . . . . . . . . . . I . . . . . . . _1 I _, -

0

20000

10000

- - - - - - - - - - - - - - - - - - - - - - - - - - - 10 20 30

TIME(SEC)

40 50 60

VALVE A, TEST 8 STEP 6&7

0

-J

0

-10000

-20000

-30WO 30

TIME(SEC)

343
VALVE A, TEST 8, STEP 8&9

100

50

.(

3;

S

,4

i!)

11

0

-50

-100

100

50

TIME(SEC)

VALVE A, TEST 8, STEP 8&9

.SP

rn

.I

41

0 ~~~~I I I I * I I I I I I *I 

-saL

-100

0 20 40

TIME(SEC)

60 30

*344
20

15

.1) ic:

EL

-5

-10

2

0

'DI]

"L -2

. .

0

io

I0

io

0

0

0

CL

VALVE A, TEST 8, STEP 8&9

* * I I I I I I 9 I a I I

1~~I 

I 20 40

TIME(SEC)

60 80

VALVE A, TEST 8, STEP 8&9

I I I I I I I I I I a I I I I

* S S 5 5 I I .*

-6

-8

cI

40

20 40

TIME(SEC)

345

60 f30
VALVE A, TEST 8, STEP 8&9

50

0

CCL

-50

-100

-150

4 r

a 20 40 60

TIME(SEC)

80

VALVE A, TEST 8, STEP 8&9

2

C

--J

0

-2

-4

a 20 40 60

TIME(SEC)

80

346
VALVE A, TEST 8, STEP 8&9

In

E

0

T

2D

10

0

-10

0 40

TIME(SEC)

VALVE A, TEST 8 STEP 8&9

T

20

10

0

-10

0 20 40 60

TIME(SEC)

347

s0
VALVE A, TEST 8, STEP 8&9

25 I . . I I * I 4 I * ~ I IT I I a I I I I

201.

15

I10

m 5 la C

-5-

600

500

n 400

8 3w

. 0

:> 100

0

-100

I a I II I I . . .I I . I

20 40

TIME(SEC)

60

VALVE A, TEST 8 STEP 8&9

40

TIME(SEC)

80

348
VALVE A, TEST 8, STEP 8&9

800

600

Ln

.-.

C.

400

200

I I I I I I I I I I I , I I I

I I I . I , I I . I I

0

-200

0 20 40

TIME(SEC)

60 80

VALVE A, TEST 8, STEP 8&9

2.0

ci

,I

1.5

1.0

0.5

0.0

-0.5

0 40

TIME(SEC)

349
VALVE A, TEST 8, STEP 8&9

3

8 2 

d .

T:

-11

-

-I

0

-

- I I II _ 

I I I I I I *IaIU I I I I

20 40

TIME(SEC)

60 80

VALVE A, TEST 8, STEP 8&9

20000

10000 

0

-10000

-20000

* I I I I SI I I I S

I a a I I I I I . I . . . -30000

0 20 40

TIME(SEC)

60 80

.350
VALVE A, TEST 9, STEP 1

80

600

CL 400

I..

CC& 200

I I I I I .I I . _ _ _ I _ .

S , . . .. . . . , . . . . I, . . .

Ok

-200

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 9, STEP 1

1000 .. . . . . . . . . . . . . . .a . .

BO

.0

a 600

0 D

C)) 400

I . . . I . * I .

I * * * * I * I

200 -

(I 

0 20 10 20D

TIME(SEC)

351

30 40
VALVE A, TEST 9,STEP1

400

0 2230

VALVE A TEST 9 STEP1

15

10 __i

0~~~~~~~~~~~~~~~4 -5t 

-10 A kD

0

352
150

1001

cm

.,

T 50

~50

0

VALVE A, TEST 9, STEP 1

.I I I I I I , I I .I I , I .

I I I I I I A I I I I * * p

10 20

TIME(SEC)

30 40

VALVE A, TEST 9, STEP 1

4

. _-

0

-2

-4

353
VALVE A, TEST 9, STEP 1

20

15

n1

E

K o

a

T- 5

To

0

-5

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 9, STEP 1

20

15

b

: 10

y 5

0

-5

* I I I I I I I I I I I I I I

- * * I I I I

0 10 20

TIME(SEC)

30 40

354
VALVE A, TEST 9, STEP 1

20

15

$;s10

. .m

T 25

0

-5

a 20

TIME(SEC)

VALVE A, TEST 9, STEP 1

600

500

(n 40D

U 300

T 200

Q 100

0

-100 _ I I I I I I p I _ 

20~~~~~~~~~~~~~~~~~~~7

D 1o 20

TIME(SEC)

.355

30 40
VALVE A, TEST 9, STEP 1

600

500

a, 400

I0

C> 200

* 100

0

-100

.

2.0-

~~~~~~~~~~~~~~I

I - - - - - - - - - - - - - - - 10 20

TIME(SEC)

30 40

VALVE A, TEST 9, STEP 1

Ln

I1.5

1.0

0.5

0.0

-0.50 10 20 30

TIME(SEC)

356

40
VALVE A, TEST 9, STEP 1

4

f) 3 e -

. 2

Lp1 is

R =

-1 

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 9, STEP 1

5000

0

~-500

' -10000

9 -15000

° -20000

-25000

-30000

i

I I I I I I I I S S S S 5 I I

It~~~~~~~~~~~~~~~~~~~~~~~~~~~~

~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~I-

:, . . . , . . . I a I I I I I

D1 10 20

TIME(SEC)

357

30 40
600

550

.,1a

"N SO

.uVALVE A, TEST 9, STEP 2

450

400

0

1000

VALVE A, TEST 9, STEP 2

-SP

a 600

U 400

358
VALVE A, TEST 9, STEP 2

800 . , . . . . , . . .

600

'd 4130

200

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 9, STEP 2

00 20 30 40

TIME(SEC)

.359
VALVE A, TEST 9 STEP 2

600

500

, 400

'Us

.. 300

I 200

9 100

0

-100

a 10 20 30

TIME(SEC)

40

VALVE A, TEST 9 STEP 2

4

2

I-

-J

a

-2

-4

0 40

.360
VALVE A, TEST 9, STEP 2

20 _

15 

en

E

V- 5 

0 .

-5

0

20

15

10 20 30

TIME(SEC)

40

VALVE A, TEST 9, STEP 2

to

9

_

D

10

5

0

-5

20

TIME(SEC)

361
VALVE A, TEST 9, STEP 2

20

15

10

5 

-5 

a 20 30

TIME(SEC)

40

VALVE A, TEST 9, STEP 2

600

500

. . . . . . . . . . . . . . . . .

En

C.. lp

400

300

200

100

orI

. ~~~ I I

0

-100 I . l l

0 10 20

TIME(SEC)

30 40

362
VALVE A, TEST 9, STEP 2

60

50

,x, 40

9 3D

9! 2D1

10

0

-10

2.0

1 1.5

1.0

0.5

0.0

I

0

I0

10

I0

0

a.

* . . S I * S I I I * 

. . . . I . . . . I . . . . I . . . .

I 10 20

TIME(SEC)

VALVE A, TEST 9, STEP 2

30 40

I I , I I I I I I I I I I I I '1I ' ' ' .

I - 1 2 2 I I I .-- I - -. - I A I I I I I I

20

TIME(SEC)

-363

30 40
VALVE A, TEST 9, STEP 2

0.3

EnI--

8

25

m

w

D

cl

c15

0.2 

0.1

0.0

-0.1 

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 9, STEP 2

20000

10000

LAL

.. 0

-10000

C

-20000

-30000

0

364
VALVE A, TEST 9, STEP 3&4

600

580

.21

LO 560

.,

A 540

520

500

c

1000

800

E 600

. .

c),400 ra

200

0

VALVE A, TEST 9, STEP 3&4

, , I I I I I I I

0 20 40

TIME(SEC)

365

60 80
VALVE A, TEST 9, STEP 3&4

800

600

.EL

ed 400

T

I. I . . I I I I . I , . .- I

200 

0

20.

0 20 40

TIME(SEC)

60 so

VALVE A, TEST 9, STEP 3&4

15 

CP10

.I

. -5

Cl: 

§ @~ I I .11,,I ,,,:

-10 

-15 t

lI 40 I . I I . p p I p I p

20 40

TIME(SEC)

366

60 E

I

I0
VALVE A, TEST 9, STEP 3&4

150

100

0P

.

.

CM4

I

ui

50

-50

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 9, STEP 3&4

4

2

. 0

-4

-2

-4

40

TIME(SEC)

367
VALVE A, TEST 9, STEP 3&4

20

15 :1

tn

12

E

T

25

0

I I a 1 I I I I I , I I I I

I

-5 L

a

I . I . . I , . , I I . . 1

20 40

TIME(SEC)

60 80

VALVE A, TEST 9, STEP 3&4

20

15

t 10

T5

0

-5

0 20 40 60

TIME(SEC)

368

80
VALVE A, TEST 9, STEP 3&4

20

15

10

, la

T5 I

0 r-

-5 L

0

600

500

Z-*- 400

X 300

r, 200

0, 1W

. . . ~ ~~ ~ ~~~~~~~~I I I . I . I . . I I i . I

20 40 60

TIME(SEC)

_

80

VALVE A, TEST 9, STEP 3&4

_ T ~~I I I I 1 1 r ~~~~~~~~~~~~~~

I

-100 

0

l . . ,~~~~~~~ I . . .

40 2D 40

TIME(SEC)

369

60 I-0
VALVE A, TEST 9, STEP 3&4

800

600

-

o 400

C4

0a

-200l

2.0

20 40 60

TIME(SEC)

80

VALVE A, TEST 9 STEP 3&4

=3

1.5

1.0

0.5

0.0

.51

20 40 60

TIME(SEC)

370

so
VALVE A, TEST 9, STEP 3&4

4

Im

E,

I3

2

I

0

-1

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 9, STEP 3&4

20000

Io :

0 

-10000 

-20000-

-30000

0

.371
VALVE A, TEST 9, STEP 5

800

613

400

vi 200

a

--200 F . , . . . , 

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 9 STEP 5

1000

8600

Il" 400

: 200

0

-200 : . . . . . . . . , . . , o 10 20 30 40

-372
VALVE A, TEST 9, STEP 5

1000

silo

.c 600

*Rt- 400

To -200

0

-200

41

a

VALVE A, TEST 9, STEP 5

CL

.

l

d.

C0

20

0

-20

20

TIME(SEC)

373

40
VALVE A, TEST 9, STEP 5

.IA

So

600

400

200

0

-200

a 10 20 30

TIME(SEC)

40

VALVE A, TEST 9, STEP 5

4

2

.-

.-. 0

-2

-4

0

374
VALVE A, TEST 9, STEP 5

20

15

~-

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 9, STEP 5

20 

15

-5 1 I0,40

o ~~10 _20 3040

TIME(SEC)

375
VALVE A, TEST 9, STEP 5

20

151

o

10

t 5

To

I * I * * * I I X

I . .I I I . . I I I I I . I -5

a 10 20 30 40

TIME(SEC)

VALVE A, TEST 9, STEP 5

6WC I 

500

U 4 0 0

I.-

;: 300 

200

> 100

0

-100

I I I I - j I

* * * * I * * I I

. . . .

I

,~~~~ - -

10 20

TIME(SEC)

30 40

376
VALVE A, TEST 9, STEP 5

600

400

C0 30

~200

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 9, STEP 5

2.0 ' ' ' ' e ' ' ' '

1.0

0.5<

D1 0.0

-0.5 2 i a I , I , 

0 20

TIME(SEC)

317
VALVE A, TEST 9, STEP 5

4 - - - I - - - I - - * I * * 

5Iw

2

1

0

I I I , I , , I I I 

-1 l 10 20

TIME(SEC)

30 40

VALVE A, TEST 9, STEP 5

5000

8 -5000

'' -10000

D -200

3 -20000

-2500

-30000

378
200

1501

07

C14 100

50

VALVE A, TEST 9, STEP 8&9

I f I I j I I I

I I.I , . I . I 0t

1000

800

.0

600

L 400

200

0

E

I

11

I

20 40

TIME(SEC)

60 80

VALVE A, TEST 9, STEP 8&9

20 40 60

TIME(SEC)

80

379
VALVE A, TEST 9, STEP 8&9

100

50

0"

U, 0

-50

-11

16

14

.6 12

A 10

Id a 

6 

4

C.

D0

VALVE A, TEST 9, STEP 8&9

. . . ,~~~~~~~~~~ I I

- Itant.1- 0-11 -11.yktlffl jiulibiL .- --.- )Lv,.

Spy

I

4 6 6 I a1 a a a a I 

vs "IMTII

74"#~~~~~~d . . . . . ,~~~~~~~~~~~~~~~~~~~~~~~~~~~~

20 40

TIME(SEC)

60 so

380
VALVE A, TEST 9, STEP 8&9

8

60

0"

'ax 40

CL

F 20

I-

-20

-40

0 20 40 60

TIME(SEC)

so

VALVE A, TEST 9, STEP 8&9

4

2

0

-J

-2

-4

40

TIME(SEC)

80

381
VALVE A, TEST 9, STEP 8&9

20

15

10 E

0

B. o

0

-5

0

I I I

I

Ll l

20 40

TIME(SEC)

60 80

VALVE A, TEST 9, STEP 8&9

20

15

: 10

5

, . .

I I I

7

To 

-5 1 1 . .I I 

0 20 40

TIME(SEC)

60 80

382
VALVE A, TEST 9, STEP 8&9

20

15

U, I 10

5

0

-5

0

600

500

40

TIME(SEC)

VALVE A, TEST 9, STEP 8&9

I0

400

300

200

I II * I * I I

I I I I t I I I , I I I a I

100

-100

l 20 40

TIME(SEC)

383

60 80
VALVE A, TEST 9, STEP 8&9

800 . r I r l I I rI

600 

En

0 400

t 200

0

I .Lt

-20i

2.0

( 1.5

6 1.0

0.0

I

o _

0 . . , . . . . . I , . a

20 40 60

TIME(SEC)

s0

VALVE A, TEST 9, STEP 8&9

I I I I I I a I I I I |I 

* I I I I I I I *

I 20 40

TIME(SEC)

60 so

-384
VALVE A, TEST 9, STEP 8&9

4

'' 2

5I 1

C: 0

-1 -

* . , | . . |I ,I I I I I I

20 40 so

TIME(SEC)

60

VALVE A, TEST 9, STEP 8&9

20000

2DDD

MOD

, .

-1OO0

*< -20W0

-J

-30000

-40000

16

I I I , I I I a I I I I

I.

I~~ , 

.~~~~ I I 

I 20 40

TIME(SEC)

60 s0

-385
386
VALVE A, TEST 10, STEP 1

800

600

. _

4 0 0

CQ2

ILtb 200

I I I

-200

BOB

600

EL 400

I,.

A) 200

a

-200

I . . . , . . . I I

0 10 20 30 4f

TIME(SEC)

VALVE A, TEST 10, STEP 1

a. . - -

, ,, ,, ,, , , 

0 10 20

TIME(SEC)

30 40

.387
VALVE A, TEST 10, STEP 1

Soo

600 

EP

400

, 200

I *

a a a a I I I I I I a a a

0

Afnn I

2

0 

.Ul 

'C- -2-

,I.

<-4

A I

a 10 20

TIME(SEC)

30 40

VALVE A, TEST 10, STEP 1 . - - - - - - - - - - - ' II I I I I Ia

I I I I I I I I I I I I I I A 

-6 L

-8

0 10 20

TIME(SEC)

30 40

.388
VALVE A, TEST 10, STEP 1

150

1001

CL

sT5s

Ed

0

I

I I I I I I I I I I I I I I I I I I

-mn I * a 6 0 I * . * I a * I a a a 0WU_

Io 10 20

TIME(SEC)

30 40

VALVE A, TEST 10, STEP 1

4

2

a

I-., 0

-2

-4

.389
VALVE A, TEST 10, STEP 1

U

E

0

Tj

. .

.

25

20 :

15

5

-5

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 10, STEP 1

30

40
VALVE A, TEST 10, STEP 1

25

20

E 15 

~.10

T 

5: 0 

-5

a

600

500

10 20 30

TIME(SEC)

40

VALVE A, TEST 10, STEP 1

C.)

400

300

20

D00

a

391
VALVE A, TEST 10, STEP 1

BUD

600 - -F- - IaIIIII

U-)

0 400

210

C)l D 0 

I I I I I I~~~~~~~~~~

-200 I . . . I L . I . I I . . .

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 10, STEP 1

2.0

1.5

EC

1.0

A 0.5

-0.5

392
VALVE A, TEST 10, STEP 1

> 2 Ri_

In1

10 20 30 40

TIME(SEC)

VALVE A, TEST 10, STEP 1

10000 * * * * , ! * I * , * . , , * 

F -10000

-20000

S -30000

-40000

-50000 ,a I ,I

0 10 20 30 40

TIME(SEC)

393
VALVE A, TEST 10, STEP 2

MO

600

4W

C, 200

d- l_ _ _

-~~~~~~~~~P 

I 

a I

-ronri

1 o

1000 

10 20

TIME(SEC)

30 40

VALVE A, TEST 10, STEP 2

800 I

600 . 4

cn 400

_ ~~I I I I I I I 

r-~ a- ~P -

. . . I I . . . I * . * I * 

200 

0

0 10 20

TIME(SEC)

30 40

*394
VALVE A, TEST 10, STEP 2

800

600

cP

.a-

' 400

200

0

2-

0

CL-2 -

III

-6

-8 -

0 40

VALVE A, TEST 10, STEP 2

20

TIME(SEC)

395
VALVE A, TEST 10, STEP 2

600 r .- . , I l l l l l X l l 

400 cm

,I

m

.T

.A

200

0

.I I I I I I I I I

I I I I I I I I I I I I I a I I I I -200

0 10 20

TIME(SEC)

,30 40

VALVE A, TEST 10, STEP 2

4

2

,-

>1

-J

0

-2

-4

0 40

396
VALVE A, TEST 10, STEP 2

25

20 

9 15 

t

10 

X s

0 -

-5

0

600

500

10 20 30

TIME(SEC)

40

VALVE A TEST 10, STEP 2

IC400

300

200

100

0

-Jm

0 10 20 30

TIME(SEC)

40

397
VALVE A, TEST 10, STEP 2

600

(/ 400

I.-

9 300

>. 200

s;. 100

VALVE A, TEST 10t STEP 2

2.0

-

=3

1.5

1.0

0.5

0.0

* . . . I .* . . , . . , I

I I I . I , I I f I I I I I I -0.5 

0 10 20

TIME (SEC)

398

.30 40
VALVE A, TEST 10, STEP 2

0.06 _

C,- 0.04

I-~~~

0.02 

Ln, 0.00

8 -0.02

-0.04

20000

0

A -2000

DOD

-40000

-60000

10 20 30

TIME(SEC)

40

VALVE A, TEST 10, STEP 2

40

.399
VALVE A, TEST 10, STEP 3&4

600 * S m I * S * T - I S S I 

500

.i 400

,,

Ce 300

LIa

E 200 a.

100

0 11

oo

Soo

.0

mO 400

a200

0

c

I

I

* S S I I , I X I I I I

20 40

TIME(SEC)

60 s0

VALVE A, TEST 10, STEP 3&4

S S S ~ ~~ I ~ a ~ ~ I I I a 

, ~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~1 -I -

I_ ~~~~~~I I I II LL L 1 I I L L

I

1

40 30

TIME(SEC)

400

60
600

5o

.o 400

*0- 300

t 200

VALVE A, TEST 10, STEP 3&4

. I I I a a a I a a I I I I I

100

0p20 40

TIME(SEC)

60 80

VALVE A, TEST 10, STEP 3&4

2

0

cm

cr -2

ICl

I I i I I I 

4I004I"IO

-41

-6 1

cI 20 40

TIME(SEC)

401

60 s0
VALVE A, TEST 10, STEP 3&4

120

NOD

ox 8B1

.m

.I

C:

601

* * I * I I 

* * * I * I I 

401

20

0

-20

a 20 40

TIME(SEC)

60 so

VALVE A, TEST 10, STEP 3&4

4

2

a

-J

a

-2

-4

0 80

402
VALVE A, TEST 10, STEP 3&4

30

20

0

E.

10

To

-10

0

VALVE A, TEST 10, STEP 3&4

30

20

I I S M I * * I

b3

v

10

y

 0 I

-10 I I I I I A . I . , I

0 20 40

TIME(SEC)

403

60 SD
VALVE A, TEST 10, STEP 3&4

25

20 

0

to

- -

0

. . . . . .~~~~~~~~

I' A

I I I 

I I

20 40

TIME(SEC)

60 so

VALVE A, TEST 10, STEP 3&4

600

500

,, 400

IT 200

C-)

>. 100

0

-100

404
VALVE A, TEST 10, STEP 3&4

800

600

Vd)

IO 400

;' 200

0

-200

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 10, STEP 3&4

2.0

1.5

1.0

0.5 .

-0.0

--0.5 

a

. , . . I . . 2 . 2 

20 40 60

20 4(0 60

TIME(SEC)

405

80
VALVE A, TEST 10, STEP 3&4

4-

fi2

¶ 1

80 -1 -

I I I I I I I I I - I - I - -F- F -

-I

. . | I I , I I 

20 40

TIME(SEC)

60 80

VALVE A, TEST 10, STEP 3&4

4D000

20000

a

-20000

-40000

-60000

0 40

TIME(SEC)

406y
VALVE A, TEST 10, STEP 5

1000

800

CL

I

C14

1

600

400

200

0

-200

TIME(SEC)

VALVE A, TEST 10, STEP 5

1000

80

n 600

En 400

200

0

0

TIME(SEC)

407
VALVE A, TEST 10, STEP 5

1000

800

600

400

200

0

-200

30

20

15

TIME(SEC)

30

VALVE A, TEST 10, STEP 5

'1

.,

VA

da

10

0

-10

-20

15

TIME(SEC)

408

30
VALVE A TEST 10, STEP 5

eoo

600

cm

.0

CL

. 400

200

0

-200

VALVE A, TEST 10, STEP 5

2

I

0

.-

-1

-2

-3

-4

0 6 la 15 20 25

TIME(SEC)

409

30
VALVE A, TEST 10, STEP 5

30 . . . . ....

20

I

E

-10

0 5 10 15 20

TIME(SEC)

VALVE A, TEST 10, STEP 5

30 * * . * .. , * ' ' ' ' ' .' 

20

10

-10 . ., I, 

D 10 15 202

25

2!5

TIME(SEC)

410
VALVE A, TEST 10, STEP 5

25 _

20

15

1 0

5

0

600

500

15

TIME(SEC)

25

VALVE A, TEST 10, STEP 5

400 ,.

I300

200

100

0

-100

0 5 10 15 20 25

TIME(SEC)

411
VALVE A, TEST 10, STEP 5

800

6100

I

IC4l

I)

400

200

0

-200

1.0

0.6

0 5 10 15TIME(SEC) 2D 25

VALVE A, TEST 10, STEP 5

tn

0.6

0.4

0.2

0.0

-0.2

25 TIME(SEC)

412
VALVE A, TEST 10, STEP 5

-1. , , I I I

2

LUJ

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 10, STEP 5

10000 .I I I I I 

0

-10000

-20000

< -30000

-40000

-5000 ,,,. .0@ § 

15

TIME(SEC)

25

413
VALVE A, TEST 10, STEP 6&7

800

600

.,

CqJ

400

200

a

-200

400 r

20

TIME(SEC)

VALVE A, TEST 10, STEP 6&7

300

.91

.

n 200

100

0

0 10 20 30

TIME(SEC)

40

414
VALVE A, TEST 10, STEP 6&7

400

300

.0

200 ..

LO 100

0K

a

-100

20

15 

ox10

CL_

5 :

I

D -5

-10

0 20

TIME(SEC)

VALVE A, TEST 10, STEP 6&7

40

415
VALVE A, TEST 10, STEP 6&7

Boo

600

,cP

CL

400

200

0

1.

0 .

-2

-3

-4.

0

40

VALVE A, TEST 10, STEP 6&7

10 20 30 40

TIME(SEC)

416
VALVE A, TEST 10, STEP &7

30

in

E

0

T

20

10

0

-10

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 10, STEP 6&7

30

20

10

j o

-101.

0 10 20 30

TIME(SEC)

417

40
VALVE A, TEST 10, STEP 15&7

25

20

15

10

5

a

-5

a 20

TIME(SEC)

VALVE A, TEST 10, STEP 6&7

600

500

cn

I0c)

400

300

200

10D

0

-100

0 10 20 30

TIME(SEC)

418

40
VALVE A, TEST 10, STEP 6&7

600

500 L

400 

9 300 

9! 200 

:o 100t

0

-100

0

I I I I I I I I I I I I I I I I

* . . I * I . . I 

10 20

TIME(SEC)

30

VALVE A, TEST 10, STEP &7

2.0

Lnf.-

T3

AI

E=1

1.5

1.0

0.5

0.0

-0.5

0 20

TIME(SEC)

40

419
VALVE A, TEST 10, STEP 6&7

4

CR

I,

Lii

3

2

1

0

-1

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 10, STEP 6&7

20000

. 0

m -20000

- -4000

20

TIME(SEC)

420
VALVE A, TEST 10, STEP 8a&

200

150

o)

.21

C%4 100

50

a

200

so

VALVE A, TEST 10, STEP 8&9

150

.E.

m 100

50

I - I I I a a I I I I I I 

I

. . I I I ~~II I . a p I I I I 0

0 20 40

TIME(SEC)

60 SO

421
VALVE A, TEST 10, STEP &9

200

150

.t

. .

4 100

50

so

2

0

0P

.m

m -2

< -4

I- -6

-8

c

VALVE A, TEST 10, STEP 8&9

I I I I I I I I I I I I .A 

I 20 40

TIME(SEC)

60 80

422
VALVE A, TEST 10, STEP 8&9

150

1o 1

0m

F 50

0

I I - - I I I I I I I I I a I

I I I I * -* I I a I I I a4 I I -50

0 20 40

TIME(SEC)

60 80

VALVE A, TEST 10, STEP 8&9

4

2

". 0

-2

-4

0

423
VALVE A, TEST 10, STEP 8&9

30 I I I I I S I

20

En

E

° 10 -I.

T

D

-10

I

l l - , . .I

30

1 20 40 60 80

TIME(SEC)

VALVE A, TEST 10, STEP 8&9 I I I I I I I I l I I I I I I

20

E

10

I

. l

I .I -10 I 

0 20 40

TIME(SEC)

60 80

424
VALVE A, TEST 10, STEP 8&9

25

I . I I I .

20D

015

.10

T; 5

g L-

-5 I- I I I I I I t I I I I I I I I

6C

I--

§ 4{

-2, 2C C~)

l0J 20 40 60 so

TIME(SEC)

VALVE A, TEST 10, STEP 8&9

zo. CD . + . , I e I hs 

-2C

0 20 40

TIME(SEC)

425

60 80
VALVE A, TEST 10, STEP 8&9

Boo

600

L,

I0

400

200

0

-200

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 10, STEP 8&9

2.0 T I

U,

I1.5

1.0

0.5

0.0

-0.5 I .. I I

so 20 40 60

0 20 4(0 60

TIME(SEC)

426

z
VALVE A, TEST 10, STEP 8&9

4

(n 3

I. 2

T 1

DL

I I * * I

I I I I . I I a a a I L a 

I I I I . I I I I . I I I I t -1

0 20 40

TIME(SEC)

60 80

VALVE A, TEST 10, STEP 8&9

40000

20000

0

-20000

-40000

-60000

40

TIME(SEC)

80

427
428
VALVE A, TEST 11, STEP 1

1000

800

.' 600

.

CJ 400

C,,

t 200

0

-200

I I * , I I I

* I I X I * I I

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 11, STEP 1

1200

1000

E 800

t 600

# 400

200

D

0

I I I I I I I I I I I i I I I

I I I I I f a I I I I I A A I *- i a- I

10 20

TIME(SEC)

429

30 40
VALVE A, TEST 11, STEP 1

1000

.C 600

'I- 400

E 200

0

-200

I ~~I *I * I *

I t I I I I I I I I I I I I I I d I 

0 *10 20

TIME(SEC)

30 40

15

101

.c, 5

V o

I -5

-10

VALVE A, TEST 11, STEP 1

. I I I I I I I I I I I_

I I I I I I I I I I * a I I I * * -15 I i 20 10 20

TIME(SEC)

430

30 40
VALVE A, TEST 11, STEP 1

100

SD I

.m CL 60

C4 40

i 20

C 0

I I I I I I I I I I I A I I I I I I I

-I - --t I I I 2 I a I I I I t~~~~~~~~~

-20 I

0

4 -

2

-2 

-4 

10 20

TIME(SEC)

30 40

VALVE A, TEST 11, STEP 1

431
VALVE A, TEST 11, STEP 1

25

2D

in 15

9S

.. 10

S

a a I _I I I I a I I a a 4 a I a 

. * * 1 .I I I I -5 ?

0 10 20

TIME(SEC)

30 440

VALVE A, TEST 11, STEP 1

30

20

10 

1Da 

-10

0

a a a I a a I a S a a a I a a

I , . . - , I I I I I I I , * -* . I i

10 20

TIME(SEC)

30 40

432
VALVE A, TEST 11, STEP 1

30

92v

20

10

0

I i I I I * I * * I * * I I I I * I

I I I I I I I I I . I I I f -10

80

600

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 11, STEP 1

.,

I400

200

0

-200

20

TIME(SEC)

433
VALVE A, TEST 11, STEP 1

80

600

(I)

I-

-JI

400

200

I . .I . .I . I . I .I .

f-

-~~~~~ I I.-. -

0

-200

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 11, STEP 1

2.0

Ln

1.5

l.a

a.s

0.0

-0.

0

434
VALVE A, TEST 11, STEP 1

4 -~ - ~ - - - - - - - - - - - - -. 

(n 3

. 2

1)

I I I I I I 

f I I . . I , I I , I -1

0 10 20

TIME(SEC)

30

I

40

VALVE A, TEST 11, STEP 1

10000

. . -1000

l -20000

-3000

-40000

20

TIME(SEC)

435

40
VALVE At TEST 11, STEP 2

1000

.,)

Cal

c 700

I I , I I , I I I I a I 4 I I I I I P

* I I I I * I I * t I I * i- - * I.- 

600 L

500 U

0 10 20

TIME(SEC)

30 40

VALVE A, TEST 11, STEP 2

1000

800

E2 600

.

C 400

en

E!~ 200

-200

0 20

TIME(SEC)

436
VALVE A, TEST 11, STEP 2

1200

1000

E 800 .

'T* 600

~400 

210

0

1000

800

c 600 

e1J- 400

LII

-z0

0

VALVE A, TEST 11, STEP 2

10 20 30

TIME(SEC)

437

40
VALVE A, TEST 11, STEP 2

10

5

C1~

*iok

, .

0 

-5

-10

-15

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 11, STEP 2

BO

600

D

.in

I. .

Cl

400

200

0

-200

0 10 20 30

TIME(SEC)

438

40
VALVE A, TEST 11, STEP 2

4

2

0 I.-

-2

-4

ao 40

VALVE A, TEST 11, STEP 2

30

20

U

E° 10 ., 

V- I

-10

0

* I I I I I I III I I I I I I

* I I I I i . , I i

10 20

TIME(SEC)

439

30 40
VALVE A TEST 11, STEP 2

30

20:

a]

10

D

-10

25.

I I* I I A I I a I I I I I I

p 2 a I I . * I I * . a I p . . .p

I 10 20

TIME(SEC)

30 40

VALVE A, TEST 11, STEP 2

20 

i15

0

-5

* p p I I I i I I I I 

-1

<~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~ I 

| t t s I I g L | I I 

0 10 20

TIME(SEC)

30 40

440
VALVE A, TEST 11, STEP 2

600

500

400

>300

T 200

0

-100*. . . .

0 10 20 30 40

TIME(SEC)

VALVE A, TEST 11, STEP 2

600 I 

V)40D

In

-J,

5D 300

~20D 

>100

0

0 10 20 30 40

TIME(SEC)

441
VALVE A, TEST 11, STEP 2

2.0

,,

1.5

1.0

-0.5 

0.

L- -I - I A 1 - f- I t A - I I I I I I I I I I I

i.D 10 20 30 4#

TIME(SEC)

VALVE A, TEST 11, STEP 2

0

0.2

I,

0.1

% * * . I * I I I I I I S I I I I I

* I I e I I . . S I * . . S I . . . S

0.0 

-0.1

0 10 20

TIME(SEC)

30

442
VALVE A, TEST 11, STEP 2

10000

-1DDD

-20000

-3000D , , , 0 10 20 30 40

TIME(SEC)

VALVE A, TEST 11, STEP 3&4

1000 , I 

800

*g 600t 

coJ 400

I IL -200

40

-200

0 20 40 60nB

TIME(SEC)

443
VALVE A, TEST 11, STEP 3&4

1500

1000

.0

W)

T 500

0

-500

0 20 40 60

TIME(SEC)

so

VALVE A, TEST 11, STEP 3&4

1000

800

ow

.

Q!-

o0

400

200

Pn - ,"I=1 . -- -,- 

I _ I 

I I I I I i I I , I I I - t t- * 

0

-2(0

a 20 40

TIME(SEC)

60 40

444
VALVE A, TEST 11. STEP 3&4

15

la

0n

Im

I..

r5

0

-5

-10

-15 80

VALVE A, TEST 11, STEP 3&4

120

100

80 e,

I60

40

20

0

-20

a 20 40 60 80

TIME(SEC)

445
VALVE A, TEST 11, STEP 3&4

4

2

I

a

-2

-4

30

40

TIME(SEC) so

VALVE A, TEST 11, STEP 3&4

tn

E

0

I..

T

20

10

a

-10

0 20 40 60 TIME(SEC)

so

446
VALVE A, TEST 11, STEP 3&4

30

20

.. 0

-10

25

0 20 40 60

TIME(SEC)

80

VALVE A, TEST 11, STEP 3&4 . . . . .

I I

201

~15

. 10

T 5

-I - I a I I* 

L

. . .~~~~~~~~~ . . I I I I

20 40

TIME(SEC)

60 so

447
VALVE A, TEST 11, STEP 3&4

600

500

En 400

300

> 200

. 100

0

I I I 

kbNIy

I I I

-100

0o

1 | . ~ ~ ~ ~~~I I I

20 40

TIME(SEC)

60 30

VALVE A, TEST 11, STEP 3&4

MOD L

U)

I0 400

CM4

z 200

0

-200

* I I I I I

I . . I . . . I . . . I . . .

0 2D 40

TIME(SEC)

60 80

448
VALVE A, TEST 11, STEP 3&4

2.0

1.5

En

I. 1.0

N 0.5

5

0.0

-0.5

4

an 3

'' 2

6 I

E l

-1

t

F

20 40 60

TIME(SEC)

s0

VALVE A, TEST 11, STEP 3&4 -I - ---- I-- . - 1 , I a I I I

K X * I I . I I L I I I* a -

40 20 40 30

TIME(SEC)

449

60 f
VALVE A, TEST 11, STEP 3&4

20000 _ _

10000

-20000

-30000

0 20 40 60 s0

TIME(SEC)

VALVE A, TEST 11, STEP 5

1500 . ., , . . .- . * 

1000

C64 500

-50 . 0 . 10 20 30 40

TIME(SEC)

4So
VALVE A, TEST 11, STEP 5

1500

1000

.L

.,

500

0

-500

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 11, STEP 5

1500

1000

500

a

-500

0 40

451
VALVE A, TEST 11, STEP 5

40

30

0

T

20

10

0

-10

-20

TIME(SEC)

VALVE A, TEST 11, STEP 5

0)

I.mIII

0:

1200

1000 

s0

600

400

200

0

-200

To 40

452
VALVE A, TEST 11, STEP 5

4

2

0

-2

-4

25

VALVE A, TEST 11, STEP 5

201

U i E215

E

~10 . l

t 5

I I I * I I I a I ' a I I I I I

* I I I I a * * * i * * * * I * * * a

. . . , I , , , , I , . . . I, 

0 1

-5 0 10 20

TIME(SEC)

30 40

453
VALVE A TEST 11, STEP 5

25

20 

E 15

10

94 5

I I I I I I

I I * * * I I S -

To 

_

-5 

25 -

20 i

E 15 -

lo 3 ID

5 I 

0 _

-5 -

S . . . I . . .

10 20 30

TIME(SEC)

40

VALVE A, TEST 11, STEP 5

40

454
VALVE A, TEST 11, STEP 5

800

600

U,,

4DO 

I-

, .

200

0-

-200

0

800

600

En

o 400

5 200

C-zo0

-200

10 20 30

TIME(SEC) 40

VALVE A, TEST 11, STEP 5

40

455
VALVE A, TEST 11, STEP 5

2.0

Lt2

-

1.5

1.0

0.5

0.0

-0.5

0

TIME(SEC)

VALVE A, TEST 11, STEP 5

4

3

.. 2

E~ 1

h]

o

-I- V I I I I I I I II I I I I

I

.~~~~~ I 

9 I I . I I

-1I

I

I 

1 10 20

TIME(SEC)

456

30 40
VALVE A, TEST 11, STEP 5

owo

0

10000

b -20000

-C

-J

-300w

-40000

1000

800

20

TIME(SEC)

40

VALVE A, TEST 11, STEP 6&7

.0

EL.

C-n

600

400

20D

0

-200

25

TIME(SEC)

457
VALVE A, TEST 11, STEP 6&7

.21

a 

1000

800

600

400

200

0

a 5 15 20 25

TIME(SEC)

VALVE A, TEST 11, STEP 6&7

.0

'A

CL

.,

300

600

400

200

0

-200

15

TIME(SEC)

458
VALVE A, TEST 11, STEP 6&7

CL

.

aAi

20

15

10

5

a

-5

-10

-15

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 11, STEP 6&7

1200

1000

.C 800

600

I.-N 400

20D

0

0 5 10 15 2D 25

TIME(SEC)

459
VALVE A, TEST 11, STEP &7

1

0

.-

-J

-1

-2

-3-

-4 

0 5 10 15

TIME(SEC)

20 25

VALVE A, TEST 11, STEP 6&7

30

En

EL

0

20

10

0

-10

25

TIME(SEC)

460
VALVE A, TEST 11, STEP 6&7

30 I I I I I . . I . I . . . I . . I

20 

b 1

-10

To

-10 

0

I I . I a . . I . a . I . I . I I I

5 10 15

TIME(SEC)

20 25

VALVE A, TEST 11, STEP 6&7

25 ,

20 

1 15

10

0

-5 - -8

15

TIME(SEC)

25

461
VALVE A, TEST 11, STEP 6&7

Soo

600

U,

IC)

400

200

0

-200

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 11, STEP &7

600 - I I I I I .I I I I I I I I I I I . I

500 1 vAjJxp9 1

I

to0

C"l

C)

400

300

200

100

0

-100

t

6.

I a I I I a I I I . I I I t I I I I a I

D 5 10

TIME(SEC)

15 20 25

462
VALVE A, TEST 11, STEP &7

0.8

II0.6 

0.4 

0.2 

0.0

-0.2

0 5 10 15 20

TIME(SEC)

25

VALVE A, TEST 11, STEP 6&7

3

is

2

1

a

I I I 4 * & I I I a; I I I I * IX 

-11 I I I , I , , , , I I I 

CI 5 10 15 20 25

TIME(SEC)

463
VALVE A, TEST 11, STEP 6&7

20000 * * * * * * * * * ' * ' ' ' ' * ' '

10000

~~ a

-10000 I

-20000

-30000

0 5 10 15 20 25

TIME(SEC)

VALVE A, TEST 11, STEP 8

1000

C4 40D\

200 ELDO

0

-200

0 10 20 30 40

464
VALVE A, TEST 11, STEP 8

1000

80

600

400

200

0

-200

o

600

20

TIME(SEC)

40

VALVE A, TEST 11, STEP 8

a.. .,

400

200

0

-200

0 10 20 30 TIME(SEC) 40

465
VALVE A, TEST 11, STEP 8

C"

,ii

, 

I20

15

10

5

a

-5

-1

-15

40

VALVE A, TEST 11, STEP 8

1200

Ioa

C, ena

600

I-1 400

8 200

-200

a 20

TIME(SEC)

466

40
VALVE A, TEST 11, STEP 8

4

2

-j

0

-2

-4

6

6,j

40

VALVE A, TEST 11, STEP 8

InU

E

04

§2

20

TIME(SEC)

467

40
VALVE A, TEST 11, STEP 8

a

a

a

I I I I I I I I I I

* I I I I * *I I I 

l 1 20

TIME(SEC)

30 40

VALVE A, TEST 1 STEP 8

a

6

S3

~2

a I I I I I I I I 1 1 I 5 

7 * * I * *I I I 

0 1

-2 

D

6

1I 10 20

TIME(SEC)

30 40

468
VALVE A, TEST 11, STEP 8

600

500

,-.

400

300

200

100

0

-100

800

600

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 11, STEP 8

I9!

4D0

200

0

-200

0 10 20 30

TIME(SEC)

469

40
VALVE A, TEST 11, STEP 8

2.0

1.5

vl

1.0

: 0.5

0.0

* . . . . . . . . . . . . I I I I ' ' ' I I ' ' ' I ' ' ' '

. , , I , I , I I I I I I I I I - - -0.5

0.06

v) 0.04 I--

J

*- 0.02

Up 0.00

Lii

a

$ -0.02

-0.04

0 10 20

T(ME(SEC)

30 40

VALVE A, TEST 11, STEP 8 I I I I I I I I I I a I . I ,I i .a

0 10 20

TIME(SEC)

470

30 40
VALVE A, TEST 11, STEP 8

15000

10010

IL 5000

1WOO

0

-5000

2 -10000

-15000

-20000

0 10 20 30

TIME(SEC)

40

VALVE A, TEST 11, STEP 9

100

8 to

.27

6 0

CM

in Lb140

I I I I I a I I I I a I I I I I I I I

* ~ ~ I I I t I S I S a I I I 

20

0

0 10 20

TIME(SEC)

30 40

471
VALVE A, TEST 11, STEP 9

100

80

C"

S.

fn

T(n

601

I I a I I I I I I * I I a I a *

* * I * * * * I * I I I* m r

40

201

oL0 10 20

TIME(SEC)

30 40

100

80D

CS

a 60

,I. I'l

(n 40

L

VALVE A, TEST 11, STEP 9 I I I I I I I I I I I I I I 

. I I . , I , I a 

20

0

0 10 20

TIME(SEC)

30 40

472
VALVE A, TEST 11, STEP 9

14 . . . . . . . . . . . . . . . , I I I 

12 -

0"

.p.

V- 8

Ic 

6

2

4L

0

I I I 1 2 1 1, . . . .

10 20 30

TIME(SEC)

40

40

30

.'B 20

R la

R10

-10

-20

VALVE A, TEST 11, STEP 9

I .I I . I I I I I , .. . I I I a*I-

:I I I I I I * i I I i I I a I I 

0 10 20

TIME(SEC)

30 40

473
VALVE A, TEST 11, STEP 9

15i

10 

C 5

I.-

-5 

-10 

0 10 20 30

TIME(SEC) 40

VALVE A, TEST 11, STEP 9

U

E

.a

10

4

B

4

2

0

0 10 20 30

TIME(SEC)

474

40
VALVE A, TEST 11, STEP 9

10

8

.I

6

4

2

VALVE A, TEST 11, STEP 9

10

8

hi

tj2

6

I I I I I I I 5 I I I I I I I

, I. - 'p I

-a I - I a I I I I I I I~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

4

2 

0

0 *10 20 I0

TIME(SEC)

30 4

475
VALVE A, TEST 11, STEP 9

Bo

600

8 400

It200

Q~

* * * I * * U U I U U I U I I U I U

I I U - I I I I I I I I I I I I

oL

-9nn I

nn

10 20

TiME(SEC)

30 40

VALVE A, TEST 11, STEP 9 --- I

4001

1-

0?

0~

200

--1 - -l I- I - -I I - - I I I~ ~ I ~ ~ a ~ ~ ~~~~~~~~~~ I a I I I

' I ' I a '' p I .. , I I . I I I

0 

-2001

-40

0 iD 20

TIME(SEC)

3D 40

476
VALVE A, TEST 11, STEP 9

2

I L

t

.. a

A -1 -

-2

-3

a

4

3 

- 2

E 1

0 o

-1

E

VALVE A TEST 11, STEP 9

I 1.. I I I I I ... I I I I I I I :

.I I i I_ I -A I -- I I

I

_ - - - - - - - -

10 20

TIME(SEC)

30 40

477
VALVE A, TEST 11, STEP 9

10000

0

., -10000

z -20000

-30000

-40000

1200

1000

800

.

600

C'4

400

X- 200

VALVE A, TEST 11, STEP 17

p p I I I I.I II p I . . I I I I I I I I I 20 I t I 

0 E

-200 C

0 10 20

TIME(SEC)

478

30 40
VALVE ATEST 11, STEP 17

1200

1000

.9 800

,2.

n 600

E~ 400

200

0

1200

1000

l DD 

800 

.. 600 

I 400

200

a0

* . . . I * I I * I I * I

* * , I * , , , . . .I , .I . . a

-

1 ~~~10 20

TIME(SEC)

30 40

VALVE A TEST 11, STEP 17

I * I - .I .

I I I .I .I .I . . . . . . . . . . I I I f 

-2D0 I

I 20 10 20

TIME(SEC)

419

30 40
VALVE A, TEST 11, STEP 17

2

a

.*1

.2

eA)

I I I I * I I I I I I I I I 

- I * * * Woe I I * * * I I * * * S

.~~~~ I I 

-41

-6

a 10 20

TIME(SEC)

30 40

VALVE A, TEST 11, STEP 17

1200

c, 8W0

600

< 400

200

a

I I I I I I I I I I I, I i I

-2001 * I I I p *I*I I I I I I I I I I I

cJ 10 20

TIME(SEC)

30 40

480
VALVE A, TEST 11, STEP 17

4

2

I-

-J

a

-2

-4

25

20

Dl

215

E

010 ,.

To

5

VALVE A, TEST 11, STEP 17

20

TIME(SEC)

481
VALVE A, TEST 11, STEP 17

,30

20

10

a 0

-10

25

VALVE A, TEST 11, STEP 17

20 

a 15

10

0

-5

* | * , I I * * e I , , , I _ 

a I I * , I I I I 

a 10 20

TIME(SEC)

30 40

482
VALVE A, TEST 11, STEP 17

6o

500

i 400

>. 300

C) 'I- 200

>~ 100

0

-110

So

BO0

600

20

TIME(SEC)

40

VALVE A, TEST 11, STEP 17

En

I-

-5

0~

0

400

200

-200 _

0o 40

483
VALVE A, TEST 11, STEP 17

2.0

Ln

I2

1.5

1.0

0.5

0.0

I I I I I I . I I I I I I I I I

-0.5 I I I I I I L - I I I p

I

) 10 20 30 4C

TIME(SEC)

VALVE A, TEST 11, STEP 17

0.1 . . . . . . . . . . . . . . . .

,,i II

0.01-

. . , . . . . I I

* p p p I I I a I I I p p p

10 20

TIME(SEC)

484

30 40
VALVE B TEST 1, STEP 1

2500

2000

. 3' 1500

.

1500

I I | II I I | I I 

* * * . * * * *Ig * I I I I I I I

0

-500

2500

2000

.2' 1500

K 1000

500

0 10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 1

I I I a I I I I I I I A I I I 

* a I I I I a I I I I I I I I I 

a

-5001

D 10 20

TIME(SEC)

30 40

485
VALVE B TEST 1, STEP 1

2500

2000

1500

1000

500

0 

-500

4 -

- - - - - - - - - - - - - - - - - - - - I II I I

I I I I I I I I I I I f I 

10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 1 . . . ~~. . . . . . . . . . . . . . . . I I . . . I .

2 -

'I .,

I

r- -2

-4

-6

-8

aY~~~~~~~~~.

MM1l1IW Ilna l -

.

. . . . I . . . I I

20

a 10 20

TIME(SEC)

486

30 40
VALVE B TEST 1, STEP 1

6w

50

'om 400

T 300

A 2D0

0

100

ao

a 10 20 30

TIME(SEC)

40

VALVE B TEST 1, STEP 1

3

2

I

I..

0

-1

-2

-3

20

TIME(SEC)

I487

40
VALVE B TEST 1 STEP 1

25 * * S - - -

20

U,

15

S.

E

0 10

-5

C

25

20

15

103 

0 

-5

* 0 5 0 I * I S I I g I I * * v I 

*I a t I I I I I

I1

10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 1 . . . ~ . ~~~. . . . . . . . . . . . . . I .I I I I 

I I I I I I I I I I t I I I I I I 

0 10 20

TIME(SEC)

30 40

488
VALVE B TEST 1, STEP 1

25

20 .

t 15 _

r : 10

lo 

0

-5

0

600 7-

5w

30 ~20

00

T 200

0

-100-

* * ~ I * I I * S I * 

* S * S I I a I I I I I I * I -t I

10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 1

20

TIME(SEC)

40

489
VALVE B TEST 1, STEP 1

400

300

. . . , I S S S I * S S S I

| . I I __

I W T W |I I I r w r T~~~~~~~~~~

En

I,.

I-

-J

200

100

0

I I I -100

2.0

I I I 

0 10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 1

. .

1.5

1.0

0.5

0.0

.I I I I I I . I . . .. I I .

I I L .1 a. I aI I I I I I a I a a- a - A- .L -0.5

0 10 20

TIME(SEC)

40

490
VALVE B TEST 1, STEP 1

0.5

I

w

a

m.

0.4

0.3

0.2

0.1

0.0

I~ ~ I ~ ~ a. I I . .

, , ,~~~~~~~~~~~A

-0.1 [

0 10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 1

5000

0

Hi

-J

-5000

-10000

-15000

-20000

0 10 20 30

TIME(SEC)

491

40
VALVE 8, TEST 1, STEP 3

2000

1500

.0

1000

I..

v 500

0

-500

0 5 10 15

TIME(SEC)

20

VALVE B, TEST 1, STEP 3

.0

rt

AL

100

60

40 

20 20 l

0 5 10 15

TIME(SEC)

492

20
VALVE B TEST 1, STEP 3

60

40

CP

C,,

20

I I I I I I I U I * 

* , U I , * U I * I I I *- * p 

a

-20

0 5 10

TIME(SEC)

15 2U

VALVE B TEST 1, STEP 3

15

4

.C3

of

-2

1

0

-1

20

493
VALVE B TEST 1, STEP 3

VP

0'

I2000

1500

1000

500

0

-500

20

VALVE B TEST 1, STEP 3

-j

0.5

0.0

-0.5

-1.0

-1.5

-2.0

-2.5

-3.0

494
VALVE B TEST 1, STEP 3

25

20

In

LI)15-

E

- 5

o

5 

0

25-

I I I I I I I I I I I I I a I * a 

I I a * * I * *

5 10

TIME(SEC)

15 20

VALVE B TEST 1, STEP 3

20D 

15

t10

B;5

0

-5

. . . . I , . I . , . I *

* S S S I * * * S I * * * S I * * * S

0 5 10

TIME(SEC)

15 20

495
VALVE , TEST 1 STEP 3

25

20

. .

15

10

5

0 

-8 

.... , .. I .I .I

* * * I * I * I

I

. . . . . . . . . . . . . . . . . . .

5 10

TIME(SEC)

15 20

VALVE B TEST 1, STEP 3

600

500

a,

IC.)

400

300

200

100

0

-100

496
VALVE B TEST 1, STEP 3

800

600

.,

I0

400

200

0

-200

20

VALVE B TEST 1, STEP 3

0.2 . . . . . I l I 

I-

=3

0.1

0.0

-0.1 . . . l 10 0 5 10

TIME(SEC)

497

15 20
VALVE B TEST 1, STEP 3

0.3 .. . . . . . . . . . . . . . . . . . I . I I I I 

t2

0

0.2 _

7

-

0.1 -

U.U L

-0.1 I I . . .

0 5 10

TIME(SEC)

15 20

VALVE B, TEST 1, STEP 3

5000

a

C0

0

-5000

-10000

-1500

0 5 10 15 20

TIME(SEC)

498
VALVE B TEST 1 STEP 5

2500

2000

.2' 1500

CX4 100

w 500

0o

-500

2500

2000

A" 1500

PL

.,I

RJ 500

0 

-500

a

.I

I

VALVE B TEST 1, STEP 5 - I I I I I 1 I I I 1 I 1 1 I I I I I I

I I I I I . p I p I p I I I I p p p I I . i p p I p p p p

I 10 20 30

TIME(SEC)

499

40 50 60
VALVE 8, TEST 1, STEP 5

2500

2000

* " 1500

I.

- 1000

500

CL

0

-500

2

0

cm

'17X

. .

E-2

I-

-4

-6

VALVE B TEST 1, STEP 5

500
VALVE B. TEST 1, STEP 5

6

v)

m

..

IaL. 2

-2

6D0

30

TIME(SEC)

60

VALVE B TEST 1, STEP 5

An

ICL

.A

400

200

0

-200 _

0

501
VALVE B TEST 1, STEP 5

3

2

1

. _

. 4

0

-1

-2

-3

-4

0

25 

60

VALVE B TEST 1, STEP 5

I I I I I . . . . I .. . . . Ir r , a I . ' I . -

201.

i 15

10

0

-5

E

.

I

,1 I I I I I I t I I , i * I I i * * I I * * I I I . . I I

10 20 30

TIME(SEC)

.502

40 50 60
VALVE B TEST 1, STEP 5

25 . .. . . . . ~ . . . . . . . . . . . . . . . . . . . .

- . . I . I . I I I I

20 

15

, 10

0

-5

L

r-

:. . . I I I . . . . . . . . . . . . . . . . . . . . . . . . . . . . .

10 20 30

TIME(SEC)

40 50 60

VALVE , TEST 1, STEP 5

25

20

.E

.

15

10

5

0

-5

a 10 20 30 40 50

TIME(SEC)

*503

60
VALVE B, TEST 1, STEP 5

600

400

I- C0

200

. . & i , . . r ,. Ia r I [ . I I .l . I l l I .

, .. I ... I . I ... I .. ,IIII . I I .

0 

-,3nn I

600

5w0

10 20 30

TIME(SEC)

40 50 60

VALVE B TEST 1, STEP 5

(n

I-

-A

I

0

400

3D

200

100

0

-100

504
VALVE B TEST 1, STEP 5

1.5

LV)

II

1.0

0.5

I * I I I I a U I I I I I I U U U I I I I U 

0.0 . . , ,,, . . , . I . . . , I . . . . I . . . . I . . .

-0.5

4

. . . . . . . . . . . . . . . . . . . . . . . . . . . . . 0 20 30

TIME(SEC)

40 50 60

VALVE B TEST 1, STEP 5

Ln

VIw

,3

2

1

0

-1

0 10 20 30 40 50

TIME(SEC)

60

505
VALVE B TEST 1, STEP 5

5000

0

.. -5000

-10000

-15000

2500

30

TIME(SEC)

60

VALVE B TEST 1, STEP 6

2000 

.27, 1500

.

C4 1000

500

0

I I I I I I I I I I I I * I I I I I I

-500 c I I I I I a I I I I 

I - - - - - - 10 20

TIME(SEC)

30 40

.506
VALVE B TEST 1, STEP 6

2500

2000

.2' 1500

.

: 1000

5

To

0

-500 

0

2500

2000

.m 1500

+ 1D0

500

0 

- g . I t I t 2 eII e I I e

10 20

TIME(SEC)

30 .940

VALVE B, TEST 1, STEP a I I I I I I A I I I I I I I I

* I I I I 2 m SA I 2 I 1 5 I I a . a I -5001:

01 10 20

TIME(SEC)

30 440

507
VALVE B TEST 1, STEP 6

2

a

0] . .P

-2

El

r I I I I I I I I I I

., vfwwhm",. rr

..Fly'll'toll'olti"iii4r,."

-4 

-6 I . . I I . . . .

0 10 20

TIME(SEC)

30 40

VALVE , TEST 1, STEP 6

800

SD

CP

.D.

400

200

0

0 10 20 30

TIME(SEC)

40

508
VALVE B TEST 1, STEP 6

3

2

1

-i

0

-1

-2

-3

To 40

VALVE B TEST 1 STEP 6

25

20

gu

P,

15

10

5

0

509
VALVE B TEST 1, STEP 6

25 .

20

b 15

: 10

I,

l

1 5

0

-5

25

20

1 15

10

T 5

0 j

40

VALVE B TEST 1 STEP 6 rI I I I I I I I I

I I I

'I

j

-5 5

0

I . . . I . I . I . I

10 20

TIME(SEC) 30 40

510
VALVE B TEST 1, STEP 6

600

500

f 400

> 300

T 200

0

> 100

a

-100

a 10 20 30 40

TIME(SEC)

VALVE B TEST 1, STEP 6

600

500

,, 400

9 300

9 200

C)

100

0

I I I I I I I I I I I 

I U U , I , , , , I I I I I I, t I -100 I

D 10 20

TIME(SEC)

511

30 40
VALVE B TEST 1, STEP 6

2.0

cno.-

8

3

e1

2 1

1.5

1.0

0.5

0.0

-0.50 40

VALVE B TEST 1, STEP 6

4

I

au

3

2

I

a

-1

0 20 TIME(SEC)

512
VALVE B TEST 1, STEP 6

5000

D

Ll

.. -5000

-ioooo 

-15000

-20000

2000

150O

1SD

1000

,I.

To

cj, 500

0

-500

0

i

20

TIME(SEC)

40

VALVE B, TEST 1, STEP 7

I a I I I I I I I I I I I I *

* I i a I * I S I t I I I I Ia- L

I 10 20

TIME(SEC)

*513

30 4u
VALVE B TEST 1, STEP 7

1500

1000

.0

. . W

To

I * I * . a I * . -500 - - - - - - - - - - - - - - - - - - - 0 10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 7

1500 - - - - - - - - - - - - - - - -

1000

.X

.,L

- 500

0

I a I . I I I I . 2I I I I I I I I I -500

0 10 20

TIME(SEC)

514

30 40
VALVE B, TEST 1, STEP 7

2

a

Ti

.m

' -2

-4

, I I

-6 

-8 a I I I I I I I I a I I I I I .

2000

150

D

m 1000

C500

I-L

0

-500

D 10 20 30 4C

TIME(SEC)

VALVE B TEST 1, STEP 7

_ ' ' ' I ' I I I I I a I ;a a 10 20

TIME(SEC)

30 40

515
VALVE B TEST 1, STEP 7

3-

2 _

1

.-

0 -

-I .

-2

-3

0

25 .

10 20 30

TIME(SEC)

40

VALVE B TEST 1, STEP 7

201.

InU15

E

0 10

T5

5

-5

* * * I I I I I I I I * I * I -

20 0 20

TIME(SEC)

516

30 40
VALVE B TEST 1, STEP 7

25 . . . . . . . . . . . . . . . . . .

20

b

.,

15

10

S

I I I I I

.,, 

-5

O 10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 7

25

20

__

.

15

1D

5

0

-5

10 10 20 30

TIME(SEC)

40

517
VALVE 8, TEST 1 STEP 7

600

500

(, 400

8 30

5 200

X 0

I >-~ 100 

a

-100 

a

600 _

500

En) 400 

9 30) Z

9! 20

IX 100 

0

-100

0

10 20 30

TIME(SEC) 40

VALVE , TEST 1, STEP 7

10 20 30 40

TIME(SEC)

*518
VALVE B TEST 1, STEP 7

2.0

,

,I

1.5

1.0

0.5

0.0

-0.5

0.06

0.04[

S * * * . . , I

* @ | | | t 2 9 t I * I * * 9~~~~~~~~~~

10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 7

(n

'' 0.02

En, 0.00

w

I- -002

-0.04

20

TIME(SEC)

40

519
VALVE B TEST 1, STEP 7

10000

5000

-j0

a)

-5000

-10000

-15000

-20000

0 20

TIME(SEC)

400

, ,

300 

.0

C-4

Ia200 

VALVE B TEST 1, STEP 8

* i I I a , I I , I I I I

I I I * S I t I I I I I

1

0

-100

0 20 40

TIME(SEC)

60 s0

520
VALVE B TEST 1, STEP 8

200

.2 10

.

n 50

-50

* . . , . . . , .I . I

* i I I I I I I I I I -100

I 20 40

TIME(SEC)

60 80

400

300

200

100

0

VALVE B TEST 1, STEP 8 * I I I I I I 

* I I ~I i * I I . I I * -100

0 20 40

TIME(SEC)

60 80

521
2

0

CP

il

VALVE B TEST 1 STEP 8 I I I . I I I I . I I I I

I I I , . . . , .I I I I I 

-2

-4L

-6

0 20 40

TIME(SEC)

60 8O

VALVE B, TEST 1, STEP 8

100

80 :

60 .0

.i

CL

401

I I I ,I I I a I I I I I I

I i I I I f I I a t I _. I S I

20 

0

-201

-40

0 20 40

TIME(SEC)

522

60 so
VALVE B TEST 1 STEP 8

3

2

1

._

-1

-2

-3

0 40

TIME(SEC)

VALVE B TEST 1 STEP 8

30

I I I I I I I I I I I I ,I 

20 wn

E

0o10

T

oI

-10 --

a

I . . , . . . , . . . I . . I

20 40

TIME(SEC)

523

60 80
VALVE B TEST 1, STEP 8

30

20

0

b

10

y

0

-10

25

a 20 40 60 TIME(SEC) 80

VALVE B TEST lo STEP 8

a I I I I I I I I I , I I I

201

15

10

5

a

-5 I I I . I , . I I . , I

0 20 40

TIME(SEC) 60 so

524
VALVE B TEST 1, STEP 8

80

600

(nIC.)

400

200

D

-200

800

6w

VALVE B TEST 1, STEP 8

I I . I I I I

cn

I--

-4

0

400

200

2O~

-200 W

To

t I

20 40 60

20 40 60

TIME(SEC)

525

I30
VALVE B TEST 1, STEP 8

2.0

1.5

I, 1.0

¢ 0.5

N-

-1 0.0

-0.5

I .I I I

I I I I I I I I I I I I I

20 40

TIME(SEC)

60 80

VALVE 8, TEST 1, STEP 8

4

cn 3

.. 2

T1

-

-1

0 20 40 60

TIME(SEC)

526

s0
VALVE B TEST 1 STEP 8

5000

a

.. -5000

-10000

-C

. .I . I I . I .

I I I * a I * a * I a 

I

-15000

-20000

0 20 40 60 SC

TIME(SEC)

VALVE , TEST 1 STEP 9

100 r . .

50

.2'

CM4

n

0t

I . . I ,I I 

* a1 I I I I a - - I ,- I a I I a a I 

-501.

-100 i

0 20 40

TIME(SEC)

*527

60 s0
100

50 

0E.2.

tr

U0

CVALVE B TEST 1 STEP 9

* I I I I I I I I * 

* * I * I I 

0

-5 L

-100I

0

4nn

20 40

TIME(SEC)

60 80

VALVE , TEST 1, STEP 9 .W- r

50 I

3

.0-

,,-

I

0o

.I I I I I I I I I I I

I I I I * *- I I *I I * -* L

-50 

-100

0 20 40

TIME(SEC)

528

60 80
VALVE , TEST 1, STEP 9

10

I

*c7e Di 

I0

I I I I I I I I I I aI

*- . I I I I I I , * I * -2

0 20 40

TIME(SEC)

60 so

100

50 

0P

'lil

..

AS

9!

VALVE B TEST 1, STEP 9

*~ ~~~~ , . . . , . . .I 

e A F~~~e~~rI I I * I 4 * I I * a p 

0

-50 

-100

0 20 40

TIME(SEC)

529

60 s0
VALVE B TEST 1, STEP 9

3

2

1

._

I.-

m

>i

0

-1

-2

-3

30 -

20

2D -

15

la-5

-5:

TIME(SEC)

VALVE B TEST 1, STEP 9

in

a

E

0

so

530
VALVE B TEST 1, STEP 9

30

, 

20

10

0

I I I I I a I I I I

-L 

.~~~~ I I -10

a 20 40

TIME(SEC)

60 80

VALVE B, TEST 1, STEP 9

25

20

.I.

15

10

5

0

-5

s0

TIME(<

531
VALVE B TEST 1, STEP 9

Boo

600

I400

1 200

0

II I I I

_lkAJ I

-200

800

600

g 400

C4

2

-200

I I I I I I . I

0 20 40 60 BC

TIME(SEC)

VALVE B TEST 1, STEP 9

I I I I I I I I 

I S I S I SI I I I I I

0 20 40

TIME(SEC)

60 so

532
VALVE B TEST 1, STEP 9

2

1

I--

-1

I2-2

-3

{

3.0

2.5

EnI

2.0

E 1.5

T 1.0

8 0.5

0.0

-0.5

0

I I I I I I I I I I I I

I 20 40

TIME(SEC)

60 80

VALVE , TEST 1 STEP 9

I I I I , I a I I ' a I I a I 

I I i

I 20 40

TIME(SEC)

533

60 80
VALVE B TEST 1, STEP 9

5000

0

iD

0

-5000

-10000

-15000

-20D00

a 20 40 60 TIME(SEC)

80

VALVE B TEST 1, STEP 12

1800

1600

.21

C4 1400

1200

1000

To 40

*534
VALVE B TEST 1, STEP 12

1500

.0

C150 ..

I 0 I 0 I 40

| | | * I I I e I I I I I I -- I - L

0

-50D

cI laD 20 30 40D

TIME(SEC)

VALVE B TEST 1, STEP 12

1500

1000

.EL

C,, 5 0 

I I I I I I 1 T I I

. . . . I . . * 1 I * * * * I I I -

-500 20 *1I 0 10 20

TIME(SEC)

535

30 49
VALVE B TEST 1 STEP 12

CL4

d 2

o -

0 10 20 30 40 TIME(SEC)

VALVE B TEST 1, STEP 12

0

-2

0-

-6

0 10 20 30 40

TIME(SEC)

536
VALVE B TEST 1 STEP 12

2000

1500

CL1100

'ER

< 500

So

E

0

-500

3

2

0

C-

-1

I , * * I I * * I . . I I 

I I I I I I I I I I * * I

I

10 20

TIME(SEC)

30 40

VALVE B TEST 1 STEP 12

-2

-3

0 10 20 30

TIME(SEC)

.537

40
VALVE BP TEST 1, STEP 12

25 . . . .

I I I

20 

E.

T

15

10

5

I: 4 I

0

-5 , . . . I . . C . I C C , . , I

{

30

25

g 20

t15

~I? 10

5

D 10 20 30 4C

TIME(SEC)

VALVE B TEST 1, STEP 12

C C C C C C C I * C C C I CI

0

-5

0 10 20

TIME(SEC)

538

30 40
VALVE B TEST 1, STEP 12

25 I I I I I I I I I [ T r r~~~~~~~~~~

20 :

15

10

T5

I _ 

-5 

G

, . . I ., , I I 

600

500

a2 400

> 300

200

> 100

1 10 20 30 40

TIME(SEC)

VALVE B TEST 1, STEP 12

1 - S S I , a S S , I S S S I * I t S

a

-inn

0o 10 20

TIME(SEC)

.539

30 40
VALVE B TEST 1, STEP 12

500

400

3001 

-J0

* 200

Ct) Cq100

0 

-100

c

2.0

mn 1.5

1.0

L2 .5

0.0

I I I I I I I I t I I I I I I I

I I I I

I

10 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 12 ft ft ft I I I , It I I I I I I I I 

i I --- -.-- -- . -I I I I 

10 20

TIME(SEC)

540

30 40
VALVE B TEST 1, STEP 12

O.Ds

En

I)

Lii

a

I0.06

0.04

0.02

D.D

-0.02

0

VALVE , TEST 1, STEP 12

10000

5000

ih 0

i -5000

f -10000

-15000

-20000

0 10 20 30

TIME(SEC)

541

40
VALVE B TEST 1, STEP 19

1600 , . M . . . , . .

1580

1560

u, 1540

1520

1500 . . , . . . . , . 0 10 20 31

TIME(SEC)

VALVE B TEST 1, STEP 19

1000

500

7 . 1, . , . . § @ , e 20

20

TIME(SEC)

*542
VALVE B TEST 1, STEP 19

2000

1500

CP

.E

,- 1000

50

0

10

B

20

TIME(SEC)

40

i

CL

. .

VALVE B. TEST 1, STEP 19

9 I a ~ I I I I I I I u I I I I 

I I I I I I I . . I I I I * I I I . i . .

_ .~~~~~~2 4'.

2

0

0 10 20

TIME(SEC)

.543

30 40
VALVE B TEST 1, STEP 19

2000

1500

on

.0

1000

T: 500 --

LU

D3

-500Jao 10 20 30

TIME(SEC)

40

VALVE B TEST 1, STEP 19

4

2

I._

--I

0

-2

-4

a 20

TIME(SEC)

544
VALVE B TEST 1, STEP 19

25

201.

U'

15

10

5

To

I I I I I I I I I I I I I I I I I I I

I I 

,30 ,

. . . . . . . . . . . . . . . . . . .

TO 20

TIME(SEC)

30 40

VALVE B TEST 1, STEP 19

,,

$

20

10

0

* I I I II I I I I 

* I I I I * * * - I I * * I I

§~~~ I I -10

0 20 10 20

TIME(SEC)

.545

30 40
VALVE B TEST 1 STEP 19

25

20

U15

i 15

10

-5

600

500

,,400

5 300

:> 100

0

TIME(SEC)

VALVE , TEST 1 STEP 19

I * I I

I I -T-

-100 t

0 I . . . I a a I I .I . . I 10 20

TIME(SEC)

546

30 40
VALVE B TEST 1, STEP 19

600

5o0

400

I--

-J

I0

300

200

100

0

-100

2.0

0 10 20 30

TIME(SEC)

40

VALVE B TEST 1, STEP 19

IV 1.5

6 1.0

I--

A

5 0.5

I I I I I I I I t I I I I I I 1

0.0 -,---J-~~~~~~~~~~~- I I 

0 10 20 40

TIME(SEC)

547

30 4
VALVE B. TEST 1, STEP 19

0.08

C1 0.06

I 0.04 

-0.02

w

o 0.00 

-0. 02 -

0

I - IW I I I I I I - I

I I . t I I . . . . t . . . .

10 20

TIME(SEC) ,30 40

VALVE B TEST 1, STEP 19

20000

-j

10000

D

-10000

* I \ I I S I SII I

-20000 

DII 10 20

TIME(SEC)

30 40

548
lij

10801

. c

A 1060

4

Lb 1040

EQ

VALVE B TEST 2, STEP 1 i a S I I I I a I * I I I I I 

I I I I I I I I . , I I I I I . . . I

I

1020 

1000

0 10 20

TIME(SEC)

30 49

I

.0

VALVE B TEST 2, STEP 1

11v0

1050

.CD

to 1000

950

900

20

TIME(SEC)

549
VALVE B TEST 2, STEP 1

1101

105{

.,-

e 1001

En

951

901

8

6

AL

.

2

a

C

)

3-

a 20

TIME(SEC)

VALVE B, TEST 2, STEP 1 -

r |I | I r r I I I * 

7 * I MI AIWI I t I t I I I I I

I I I s I | s i | N I I I 

D 10 20

TIME(SEC)

30 40

550
VALVE B TEST 2, STEP 1

100

80

so

'U! 60

F 40

S 20

0

-20

1

3-

2ID1OE5 -1.

-2

-3

-4

a

40

TIME(SEC)

VALVE B TEST 2, STEP 1

40

551
VALVE B TEST 2, STEP 1

25

20

U,

E 15

E

0 10

5

a

-5

0 10 20 30 TIME(SEC) 40

VALVE B TEST 2, STEP 1

a]

to

t

25

20

15

10

5

0

-5

20 TIME(SEC)

552

40
VALVE B TEST 2, STEP 1

25 _

20

15

10 1

co 5

-5

0

600

500

:. 300

I.

> 200

a 100

lo 

0

-lao

L

VALVE B TEST 2, STEP 1 I I I I I i I I I I I

I I I I I I I f I I I * I I I

I 10 20

TIME(SEC)

.553

30 40
VALVE B TEST 2, STEP 1

600 . . .. . . . . . . . . . . . . . .

500

. . . . I I . .

I

tn

I400

300

200

100

0

-100

0

- . . , . . . . I I

10 20 30

TIME(SEC)

40

VALVE B, TEST 2, STEP 1

2

I

I

a

-2

-2

-3

0 20

TIME(SEC)

40

-554
VALVE B TEST 2, STEP 1

4

ILiI

0

3

2

20 TIME(SEC)

40

VALVE B TEST 2, STEP 1

0

-5000

0

-J

-10000

-15000

-20000

-25000

.555
VALVE , TEST 2, STEP 2

1100

1080

.21

m- 1060

C14D CL

L'I 1040

1020

10D

0 20

TIME(SEC)

1500

. 1o

0-

E 500

0

VALVE B TEST 2, STEP 2 , , , I I I I I I I a S I I I I I I

. I . . I . . . I I . , I . I . . . .

0 10 20

TIME(SEC)

556

3D 40
VALVE B TEST 2, STEP 2

1500

.' 1000

.I.

C,, l

ciL 500

0

0 10 20 30

TIME(SEC)

40

VALVE B TEST 2, STEP 2

a

6

.0

I-4

AL

* I I I I I I I i I I I I I I I

I

I I I I I w I I I I i. I f I I 

2 1

01

t3 10 20

TIME(SEC)

30 40

.557
VALVE B TEST 2 STEP 2

.0

rL

Edi

Ci

1200

100a

800

600

400

200

0

-200

0 10 20 30

TIME(SEC) 40

VALVE B TEST 2, STEP 2

4

2

.-

8

0

-2

-4

558
25

VALVE B TEST 2, STEP 2 I I I I I I I I I I I I . . .

20 :

in

E 15

03

E

° 10 I.

5 ._ . _

-5 r . I I I I I . , I . . * I . . * I

2

gj

0 10 20 30 40

TIME(SEC)

VALVE B TEST 2, STEP 2

0 * - - * 1 __ 

,0

-

D 10 20

TIME(SEC)

30 4U

559
VALVE B TEST 2, STEP 2

25

201Z

U15 i 15

t

5

i

I I a a I I I 4 1 * I I I I I I

* , I * I I I * * I .I* , . I 5

10 20

TIME(SEC)

30 40

VALVE B TEST 2, STEP 2

600

500

Q 400

X 300

¢ 200

> 100

0

-100

0 40

560
VALVE B TEST 2, STEP 2

800

600

to)

I0

0,,

400

200

D0

-200

20

TIME(SEC)

40

VALVE B TEST 2, STEP 2

2.0

E:

1.5

1.0

0.5

I I I I I I I I I I I

0.0 0 I , . I I

0 10 20

TIME(SEC)

561

30 40
VALVE B TEST 2 STEP 2

0.08

VI S--

Ii

LI aj

0.06 I

0.04

0.02

I I I I I I i I I I . I I I I ' I

0.00 . . .I . . W. IM. 

-0.02 .~~~~~ ~ - - - - - -

0 10 20

TIME(SEC)

30 40

VALVE B TEST 2, STEP 2

20000

10000

0 

-10000

0

-j

-20000

-30000

a 20

TIME(SEC)

562
1200

115D

2.

C4 1100

ELLb

VALVE B TEST 2, STEP 3&4 * I I I I I I I I I

I I a I I - - , I I I I I I I * -- L

1050

1000 

4Ann

20 40

TIME(SEC)

60 80

VALVE B TEST 2, STEP 3&4 ITU 

130D01

'in

.

fn 1200

Ld

I I I I I I I I I I I I I I

. , , I , , a I II I 1000

0 20 40

TIME(SEC)

60 80

563
1400

1300 

CP

.9

0 1200

1100

1000

VALVE B, TEST 2, STEP 3&4

II I Ia I I I I I

I i I . I I I I I

a 20 40

TIME(SEC)

60

8

6

C,

vl 4

ELI

2

VALVE St TEST 2, STEP 3&4

I I i II a I I I I

0 I I I I I I i *II.I4

0 20 40

TIME(SEC)

564

60 80
VALVE B TEST 2, STEP 3&4

100

80

CL

, .n

iv

9!

w

m

60

40

20

0

-20

0 20 40 60 TIME(SEC) s0

VALVE B TEST 2, STEP 3&4

3

2

1

0

.

0

-1

-2

-3

0 20 40 60

TIME(SEC)

565

80
VALVE B. TEST 2, STEP 3&4 . I * S S S S j S S~~~~~~~~~~~~~~~~~~~~rrr YYYYYYYYYYYYY

30 .

20

2D

E

0 10

T

I I G I I I

a a I I , S I I I I . . .

a 20 40 60

TIME(SEC)

80

VALVE B TEST 2, STEP 3&4

30

25

1 20

15

. ID

5

0

-5

40

TIME(SEC)

80

566
VALVE B TEST 2, STEP 3&4

25

20

h 15 

la 

-5 -

0 

-5

a 40 

TIME(SEC)

VALVE B TEST 2 STEP 3&4

o

600

c-)

I0

400

200

0

-200

0

-567
VALVE B, TEST 2, STEP 3&4

800

600

VI

o 400

C14

- 200

C)

0

-200

0 20 40

TIME(SEC)

80

VALVE , TEST 2, STEP 3&4

2

1

.d, 

Al -1 -

2

a I I I I I I I i I & I I I I

* * I * * I * . _ _

.~ ~ I I -3 

]I 40 20 40

TIME(SEC)

568

60 80
VALVE B, TEST 2, STEP 3&4

4

( 3

.2

vplI

Lii

0 I- T

* * I I I * I

* I I I , * I I I I Im * -1

a 20 40

TIME(SEC)

60 80

VALVE B TEST 2, STEP 3&4

5000

cI

9 -5000

X -10000

*< -15000

-J

-20000

H * e I I , I I I _

a p * I I I I a a* I I -25000 t

0 20 40

TIME(SEC)

569

60 80
VALVE B. TEST 2, STEP 5

1600 , , , , I * * * , * * *

1400

.' 1200

4 1000

IL

En

R8 Boo 

600

0 10 20 30 40

TIME(SEC)

VALVE B. TEST 2, STEP 5

1500 ,, . , * a * * I ' ' ' * 

1000

I",500

0

40 TIME(SEC)

570
VALVE B TEST 2, STEP 5

1500

1000

.6

"d 500

To

-500

30

20

05

'T 10

EdI ci

( 20

TIME(SEC)

40

VALVE B TEST 2, STEP 5

L * * I S I S I I I I I a I I I I

S S I S ~ ~~I . . a I I I

aI

-10

0 10 20

TIME(SEC)

30 40

571
VALVE B TEST 2, STEP 5

1200

1000

C, 800 ' _

Ul

601

1 400

I-

-J

= 200

0

-200

0o 20

TIME(SEC)

40

VALVE B TEST 2, STEP 5

3

2

1

-J

0

-1

-2

-3

20

TIME(SEC)

572
VALVE B, TEST 2, STEP 5

25

20

In

12

l,CL

E

.

15

ia

5

0

-5

0 10 20

TIME(SEC)

VALVE B TEST 2, STEP 5

25

20

15

10

5

0

-5

0 10 210 30 TIME(SEC) 40

573
VALVE B TEST 2, STEP 5

30

20

10

o

-10

I . I . . I . I . . .

a I I I , I I I a I I I I I

D lo 20

TIME(SEC) 30 40

VALVE B TEST 2, STEP 5

600

500

Q 400

. 300

;: 200

C)

a. 100

0

-100

0 40

574
VALVE B TEST 2, STEP 5

600

500

I-

-J

400

300

200 

a

-100

0

2-

.- 1-7

I . I I I . . . I . I . .

10 20

TIME(SEC)

30 40

VALVE 8, TEST 2, STEP 5

tn

I.0

1

3-2

-3

20

TIME(SEC)

40

575
VALVE B TEST 2, STEP 5

en 3

4

-1, , , 

D 10 20 30 40

TIME(SEC)

VALVE B, TEST 2 STEP 5

-1000 _ 

. -000 

-2500D l

-25D0

-E f. . . . .,3 

20

TIME(SEC)

576

40
VALVE B. TEST 2. STEP 6&7

9000 - - U - . . - . , - , . .

OWE

C'% 700 a3-

E 600

500

400 , . . . , . . . . , . . . . 0 10 20 30

TIME(SEC)

VALVE B, TEST 2, STEP 6&7

5003

400

300

'~200

-100 : , . . . . . i .

577
VALVE B TEST 2, STEP 6&7

500

400

7 300

'- 200

E10

ico

0

-100

25

20

.

10

d 5 

Cl

0 10 20 30

TIME(SEC)

40

VALVE B, TEST 2 STEP 6&7 I I I I I I I I I I 

I I I I * I I * , I I I 

0 

_rl 

-%j 10 20

TIME(SEC)

30 40

578
VALVE B, TEST 2, STEP 6&7

1200

00

,I.

T: 600

400

VALVE B TEST 2, STEP 6&7

0

-1

C

I-

-2

-3

-4

0 10 20 30

TIME(SEC)

.579

40
VALVE B TEST 2, STEP 6&7

25

I I I 

201Z

En

E 15

E

0a10

5 D) o

0

-5 5 -

0~

I I I 

1o 20

TIME(SEC)

30 40

VALVE B, TEST 2, STEP 6&7

30

CM4

Hi

40

580
VALVE B, TEST 2, STEP 6&7

25 . . , . . . . . . . . . . . , I I I I

20 :

15

10

' 5 L ., __.S~~~~~~

D 

-5 

0

600

400

. . I 

10 20

TIME(SEC)

30 40

VALVE , TEST 2, STEP &7

IC,

200

0

-200 L

0 10 20 30

TIME(SEC)

40

581
VALVE B, TEST 2, STEP &7

800

600 -

I.

0

IN

C)

400

200

I , I , I * ,. I . I 

I I I I I I I . . . . . . . . . .

0

-200

0 10 20

TIME(SEC)

30 40

VALVE B TEST 2, STEP 61&7

0.5 I I U - - - - - - - - U 

0.4

I--

. 0.3:

0.2

,I

0.1

0.0o

(I

I I I I I I ,,.,,,,,.I

. . .-- , . .- . .- . . .

I

10 20

TIME(SEC)

582

30 40
VALVE B TEST 2, STEP 6&7

4

VI

ILil

u

0

3

2

1

0

* . . . I I I . I I . , I I

* * 5 4 I * S I * . S I * * I -1

a 10 20

TIME(SEC)

30 40

VALVE B TEST 2, STEP &7

20000

0 

-10000

0

-J

-2 0000-

-30000

,. O0

20

TIME(SEC) 40

583
VALVE B TEST 2 STEP 8&9

100

50

CM

U1

a

-50

-100

0 20 40 60

TIME(SEC)

so

VALVE B TEST 2, STEP 8&9

100

50

.0

, .

0

-50

-100

40

TIME(SEC)

584
VALVE B TEST 2, STEP 8&9

100

50

0P

, ui CL

10-

1"

0

-50

-100

10 

a 80

VALVE B TEST 2, STEP 8&9

I i I I I~~~~~I I I I I I

a

.1, CL 6

<4

Ed

m

Ewe0400 vhW6mm

a - - . .

- I I . .a - IS . .- ~~~~~~I I

a0 20 40

TIME(SEC)

60 so

585
VALVE , TEST 2, STEP 8&9

80

so

.us

.

yo

40

20

0

-20

-40

4

2

VALVE B TEST 2, STEP &9

a

--J

0

-2

-4

586
VALVE B, TEST 2, STEP 8&9

30

In

2

B_

E

T

20

10

a0

-10

l

I I I I a I I I I I I I I

1 2 6 I I a a I I I I . I I

I 20 40

TIME(SEC)

60 all

VALVE B TEST 2, STEP 8&9

30

20

10

0

.- 10

40

TIME(SEC)

587

80
VALVE B TEST 2, STEP 8&9

30 

20

10

-10 -

To

0

600 

40

TIME(SEC)

VALVE B TEST 2, STEP 8&9 I I I I I I I I I I I I

500

400

I-

;. 300

.,

> 200

>- 100

0

-100o 

^:2t

.. , 

I

I . I l

I 40 20 40

TIME(SEC)

588

60 so
VALVE B TEST 2, STEP 8&9

800

60D

LO

I0

C-4J

0

400

200

0

-200

80

VALVE B TEST 2, STEP 8&9

2.0

n6

6

AI

2-i

1.5

1.0

0.5

I ' I I

0.0 -- q I - I I t i I I I I I

0 20 40

TIME(SEC)

589

60 80
VALVE , TEST 2, STEP &9

4

u( 3

* 2

¶ 1

0 0

-1

I I . I I I I I I i I I I I I

I I I *iI I I , I * 1

0 20 40

TIME(SEC)

60 80

30000

20000

-1000

M -10000

-Joo

VALVE B TEST 2, STEP 8&9 I I I I I I I I I

* I I I I II -30000 F 20 40

TIME(SEC)

590

60 80
VALVE B TEST 3, STEP 1

1600 - - - - - - - - - - - - - - - - - - -

0,

I.

C4 150

14850

, . . . I .I I I

4Ann I I * * I * . I I I 

1700 ,

10 20

TIME(SEC)

30 40

VALVE B TEST 3, STEP 1

1650 

0,

,2.

mo 1600 0-

I I I I I & I I i I I I I I 1 I 

A o 0 %I , . . . . , . . . . , . . .

1 2 . . 1 . a I I I a . I I I I I I 2

1550 -

150 _

0 10 20

TIME(SEC)

591

30 40
1700

1650

.0

CL

N: 1600

a_

U")

VALVE B TEST 3, STEP 1 , I , I I I I I I I I ' '

I I * I1 I I .I I I a I I I I -. . I 

1550 

1nn

0

10 -

a

Ci

2

.Ul

CL 6 - I,.

0-

< 4 _

I :

2 

O 6

10 20

TIME(SEC) MU A40

VALVE B, TEST 3, STEP 1

10 20 30

TIME(SEC)

592

40
100

801

CDM 60 ,,.

c'4 40

-20

3

J2D1

- 0 .,

-1

VALVE B TEST 3, STEP 1 I . I ' I I I. , II

. I I I I I , I , I I I I rnM 0 10 20

TIME(SEC)

30

VALVE B TEST 3, STEP 1

-2

-3

-4

0 10 20 30

TIME(SEC)

.593

40
VALVE B TEST 3, STEP 1

30

25

in 20

E 15

V- 10

T

Of

I I I

0

-5 . ., , .

0 1D 20

TIME(SEC)

30 40

VALVE B TEST 3, STEP 1

30

25

g 2 0

115

T 10

t5

0

-5

20

TIME(SEC)

40

.594
VALVE B TEST 3, STEP 1

25

20

E15

10

in T 5

-5

0 10 20 30

TIME(SEC)

40

VALVE B TEST 3, STEP 1

600

400

9-

I~

Q200

I I I I I I I I I * p I I I I I I

0oi

-2001

cI 10 210

TIME(SEC)

595

3D 40
VALVE B, TEST 3, STEP 1

600

500

VM 400

° 300

I..

' 200

C.)

>. 100

0

-100 

0

2

*1

. o_

*- -

-3 -

I I I I I I i I I I I I t

* 8 , , , h | , , , 

10 20

TIME(SEC)

30 40

VALVE B, TEST 3, STEP 1

10 10 20 30

TIME(SEC)

40

596
VALVE , TEST 3, STEP 1

4

iLu

0

3

2

1

0

-1 _

0

D

-5000

-10000

I -15000

0

-j

10 20 30

TIME(SEC)

40

VALVE , TEST 3, STEP 1

I

I I I I , . , I.I . I ,

t I Ip I I I I I I I I I

-20000 

-25000

0~ 10 20

TIME(SEC)

.597

30 40
VALVE B TEST 3, STEP 2

1600

1550I

.s

,.

C- 1500

a I I I I I I I I I I I & I I T I a I

I I , , I , , , , I p p p I p I I I _ 

14503

1400

0 10 20

TIME(SEC)

30 40

VALVE B, TEST 3, STEP 2

2000

1500

. .

n 1000

500

0

20

TIME(SEC)

598
VALVE B TEST 3, STEP 2

2000

1500

.ELCD

1000

500

0

0 10 20 30

TIME(SEC)

40

VALVE B TEST 3 STEP 2

8

6

0,

.,

I4

II

Z5 _

I

I A I I I . I . i I I a I I

21

0

0 20

TIME(SEC)

599

30 40
VALVE B TEST 3, STEP 2

2000

1500

tN

0M

c3-

CL

,,I

1000

500

0

-500

1

3-

2 

.. _

- _

-2

-3

-4

20

TIME(SEC)

40

VALVE BA TEST 3, STEP 2

20

TIME(SEC)

40

600
VALVE B TEST 3, STEP 2

30 -~ - ~ - - - - - -

tn

Pi

C)

E

0

0

20

1D

0 * I I I I , * i I I i . * I I * .

-10 I I I I I I I I I, 

D 1I10 20 3A

TIME(SEC)

VALVE B TEST 3 STEP 2

30 40

25

20

B 15

10

cT 5

0

-5

20

TIME(SEC)

601
VALVE B TEST 3, STEP 2

25 _

20 

15

.10

o

ft .t .t .t , I I I I I I a I fI. 

I I f. I I I . I I . . t I . .

SC

0 10 20 30 40

TIME(SEC)

VALVE , TEST 3, STEP 2

DO

,,

IQ.

4

2C

-2'

a 20

TIME(SEC)

602

30 40
VALVE B TEST 3, STEP 2

8oo

600

En

1-

o 400

0 200

a

I I I I I * I I I . I

-2Cin . . . . I . . . I * .I I I . I 

2.0

t 1.5

6 1.0

5 0.5

0.0

J

0 10 20 30

TIME(SEC)

VALVE B, TEST 3, STEP 2

. , . , . | ~ ~ , I ' * 

. , , , , * ., ._ i . , , , , , . . .

to

) 10

TIME(SEC)

603

30 40
VALVE B TEST 3, STEP 2

1.5

I.

Lii

3

If

1.0

0.5

0.0

-0.5

c

I I I I I I I I l 4 X . 4 '

.I. j . . . . . . I . . . . I . . . .

I 10 20

TIME(SEC)

30 40

VALVE B TEST 3, STEP 2

20000

10000

0

-10000

0

-20000

-30000 ao 40

604
VALVE , TEST 3, STEP 3&4

1600

1550 

C)

I I I I I I I i I I I I I I I

I I I I I . L I . I I I I . I

1450 

14D 

1600

1550

. .

to 1500

4

0 20 40

TIME(SEC)

60 s0

VALVE B TEST 3, STEP 3&4

I a I I I I I I I -

_ I I I I I I I I I

14501 _ t _~~4

1400

0 2u 40

TIME(SEC)

605

60 so
160j

VALVE BP TEST STEP 3&4

Zs(

EL

1.!

M -OD 

'1450

1400

0

10 VALVE a, TEST 3 STEP 3&4

I

2

4

to

0

80

606
VALVE B. TEST 3, STEP 3&4

80

60

= 40

20

A 2D

0o

* * * I I , I I I I I I I {

II I I * I I * I * -20 .

_ _

0 20 40

TIME(SEC)

60 80

VALVE B TEST 3, STEP 3&4

3

2

I

9 O

m-1

-J

-2

-3

-4

0 20 4D 60

TIME(SEC)

80

607
VALVE B, TEST 3 STEP 3&4

25

20

in

E.

03

15

10

5

a

-5

0 20 40 60

TIME(SEC)

80

VALVE B, TEST 3, STEP 3&4

25

20

15

10

5

0

-5

0 20 40 60

TIME(SEC)

608

80
VALVE B TEST 3 STEP 3&4

25 I U i J I I j s I I * 

20 :

L- 15

io

10

1 .

0 o

-5 5

0

I .I I . . I -8

20 40 30

TIME(SEC)

60 I

VALVE B TEST 3, STEP 3&4

600

400

Ln

. 200

0 0

80

609
VALVE B TEST 3 STEP 3&4

600

400

U)

-J

0

** 200

C"4

0

-200

2 -

I

1 :.

(,

I-

-2

-3

-

I I I I I I I I I I 

I 20 40 30

TIME(SEC)

60

VALVE B TEST 3, STEP 3&4

40

TIME(SEC)

80

610
VALVE B TEST 3 STEP 3&4

4

(13

.2

T 1 LI

D

LI- -- - .- - .F 1 - F I --- ' :- 

-I [

0

500(

{

-5001

-10001

K -1500

C)

-2000{

I I I

20 40 60 80

TIME(SEC)

VALVE B TEST 3, STEP 3&4

D ; , , . , .,) 

)E1 

)F 

)~~~-' _ 

-2500{ 0 20 40

TIME(SEC)

60 bu

611
VALVE B, TEST 3, STEP 5

1600

1400

.0

Ca

CL 0~j

EL)

1200

1000

aco

0 10 20 30

TIME(SEC)

40

VALVE B TEST 3, STEP 5

1500

1000

.0

I

500

0

612
VALVE B TEST 3, STEP 5

1500

1000

LU'M,- 500

0

-500 20

TIME(SEC)

VALVE B TEST 3, STEP 5

40

30

0z

0F .,

a- V20

10

0

-10

10 10 20 30

TME(SEC)

613

40
VALVE , TEST 3, STEP 5

1500

1000

0,

.

IEdD~

500

0

-500

a 10 2'0 30 TIME(SEC) 40

VALVE B, TEST 3, STEP 5

3

2

1

.,

a

-J

0

-1

-2

-3

40

614
VALVE B TEST 3, STEP 5

25

20 :

Dn Pi15

E

= 10

5

* S S I * * * I * * * * I

* * * *~ ~ I ~~ I I I * * * * 1 g 1 * -5 

0

20 -

15 

10

- 5 

0 

-5

To

10 20

TIME(SEC)

30 40

VALVE B TEST 3, STEP 5 . . V- I - I I I I I I I I I I a I . I[

I

* . . .I I I I I I I I . I I . . I 

10 20

TIME(SEC)

30 40

615
VALVE B TEST 3, STEP 5

20

15

U3

10

.,5

I I I I I I I I

a t=

-5 

0

800

600

I I I

10 20 30 40

TIME(SEC)

VALVE B TEST 3, STEP 5 ' ' ' 

cn

I400

200

0

-200

u 10 20

TIME(SEC)

30 40

616
VALVE B TEST 3, STEP 5

600 | * * * , * | * * * , 

500

400

I-I 

>.300

a 200

-100,,,. , . . . . 0 10 20 30 40

TIME(SEC)

VALVE B TEST 3, STEP 5

I

I-2

0 lo 20 30 40

617
VALVE B TEST 3, STEP 5

4

1n 3

'' 2

LU3

a

20

I a I I I I I I I * I * I

a I I I a I I I I * * a I I -1

0 10 20

TIME(SEC)

30 40

VALVE B TEST 3 STEP 5

a

-5000

t -10000

0

-I -15000

-20000

618
VALVE B TEST 3, STEP 6&7

1500

1400

.2"

- 1300

U 1200

1100

1000

0 5 10 15 20 25

TIME(SEC)

VALVE B TEST 3, STEP 6&7

.m

.r,

to

8D

600

'400

200

0

-200

0 25

TIME(SEC)

619
VALVE B TEST 3, STEP 6&7

Boo

600

0n

.EL

.I.

400

200

0

-200

20 -

15

3 10

..

-5 -

5

To

0 15

TIME(SEC)

VALVE B, TEST 3, STEP 6&7

5 10 is 20 25

TIME(SEC)

.620
VALVE B TEST 3, STEP 6&7

1600

1400

0" *a1 1200

,I.

1000

dj D Boo O

600

400

-0.5

-1.0

c= -1.5

8 -2.0.

-2.5

-3.0

J 5 10 15 20

TIME(SEC)

25

VALVE B TEST 3, STEP 8&7

25

TIME(SEC)

621
VALVE B TEST 3, STEP 6&7

30

tn

Pa.

T

20

10

r I . I I . . . . I . . I I .

-10 L

0

30 -

20 

t 10 

.: .

. . . . I . I .

5 10 15 20 25

TIME(SEC)

VALVE B, TEST 3, STEP 6&7

TIME(SEC)

622
VALVE B TEST 3, STEP 6&7

25 .4 , II I I I I .I I . I -I. . . a 

201-

15

10

5

0

-5 l

0

.I . I I I . I . I I I I i I I I I I I I I

5 10 15

TIME(SEC)

20 25

VALVE B TEST 3, STEP 6&7

60

500

I .

C400

300

200

100

yvYk)4

* . * . . * * * * . * . . * . . , .

0

-100

]I 5 10 15

TIME(SEC)

623

20 25
VALVE B TEST 3, STEP 6&7

600 . . . .   . . . . . . . . . I . . . .- I - I . .. .

L,

I

0

500

400

300

200

100

- . . . . I . . 0 I . . . . I . . . , I .. .

. . . . . . . . . . . . . . . . . . . . . . . .

5 10 15

TIME(SEC)

20 25

VALVE B TEST 3, STEP &7

. . . . . . 0.4

m 0.3

5 0.2

20. i

0.0

* * * * I * * . .f I . I I I I I . , I I I I I 

0 5 10 15

TIME(SEC)

20 25

624
VALVE B TEST 3, STEP 6&7

4

LO

To

3

2

I

0

I I I I I I I I I I I I I I I I

-, * * I * * I * * I * I - I I-.-

0

15000

10000

5 10 15 20 25

TIME(SEC)

VALVE B TEST 3, STEP &7

Lii

C-,

0

-J

5000

0

-5000

-10000

-15000

-20DO0

0 25

TIME(SEC)

625
100

501

.9,

. Ca

C-4

VALVE B TEST 3, STEP 8&9 4 . I . , , I I I I I . I

I I I I I I I_ 

01

-50 L

-100

D 20 40

TIME(SEC)

60 so

VALVE B TEST 3, STEP 8&9

100

50

.,D 0

X _5

to'* -50

En

-100

-150

-200

40

TIME(SEC)

626
VALVE B TEST 3 STEP &9

100

50

' ao

I..

*0i -50

-100

I I I I

-i50 E

-200 

I 20 40

TIME(SEC)

60 so

VALVE B TEST 3, STEP 8&9

10

a

.0

6 I..

;E4

* S I I I I

I I I I L p-I *2 I I 5- 5 I I I S 

2

0

cI 20 40

TIME(SEC)

627

60 80
VALVE B TEST 3 STEP 8&9

40

20

. I 

UL9b.1e, ~ *..-

mnlrllllllmi ... .. --. -8 

u_.1 

*jvi 0

~-20

-0

EJ-40

.. - El-''.'-I irm,, ....... .. 

a61 -- I . I I I I I I I I . I I

20 40

TIME(SEC)

60 so

VALVE , TEST 3 STEP 8&9

3

2

1

.-

.,

0

-1

-2

-3

-4

a 40

TIME(SEC)

628
VALVE B TEST 3, STEP 8&9

25 I I . I 

20k.

In

2! 15

E

010

5

-5

0

30 

I I I I I - I . I . . I

20 40

TIME(SEC)

60 s0

VALVE B TEST 3, STEP 8&9

I I I I I I I a I i .

20

ig

10

-10

'1

I I I I I I I I I I I I . I I

0 20 40

TIME(SEC)

60

629
VALVE B TEST 3, STEP 8&9

25 I I I I I.I I I I I I I I

20 

B 15

.. 10

5

To

-5 

0

S . S .I . . I I I

20 40

TIME(SEC)

60 80

VALVE B TEST 3, STEP 8&9

600

5W

(, 400

8 ;.. 3300

T 200

I 1 >* 100

0

-100

a

630
VALVE B TEST 3, STEP 8&9

800

600

U,

I-

-J

C-.'

I

400

200

0

VALVE B TEST 3, STEP 8&9

2.0

6 1.5

6 1.1D

I.-

, 0.5

0.0

0 20 40 60 TIME(SEC) 80

631
VALVE B, TEST 3 STEP 8&9

4

V3

.2

T 1

3

ESo

I I I

Ji

. .

-it

0

| . . ~ ~ ~~~~~~~I I l

20 40 60

TIME(SEC)

a0

VALVE B TEST 3, STEP 8&9

5000

0

F -5000

-10000

< -15000

-20000

I I I I I I I I I I - r 1 

,~~~~ 

-25000 

0I 40 20 40

TIME(SEC)

632

_ _

0 a0
VALVE B TEST 4, STEP 1

wo

900 i

.m

VI 700

600

I I I I I I I I I I I I I 

I I I I I e I a I I I I I I

40 500 

0 10 20

TIME(SEC)

30

VALVE B TEST 4, STEP 1

1000

90

.

U) 700

600

500

D 40

633
VALVE B TEST 4, STEP 1

1000

903I

CP00Boo

En 700

I I I I I , I I * I 

, . . . , . . . . , . . . . , . . .t

600

rnn I

a

6

0~

*oI

-

.m

CL

4 

3 10 20

TIME(SEC)

30 40

VALVE B TEST 4, STEP 1

I I S I I . I , , , , 1 , I , I , ,

-I I I I . . . I . I .1 I , . . I I 

2 

0

0 10 20

TIME(SEC)

30 40

634
VALVE B TEST 4, STEP 1

100

ED I

o" 60

.. 40

20

m -

Cl 0

I

I I I I I I I I I I I I I a I S S I I

I * I I 

I

-20

-A I

3

2 

I 

I.

-1

-2

-3

-4

. . . . . . . . . . . . . . . . . . .

10 20

TIME(SEC)

30 40

VALVE B, TEST 4, STEP 1

20

TIME(SEC)

635

40
VALVE B. TEST 4, STEP 1

30

25 -

ui 20

0

r- 10

T

* * I . * i , . I

I I I -5 .

0

25

20

G 15

10

10 20

TIME(SEC)

30 40

VALVE B TEST 4, STEP 1

I .I * , * .* I * , I * I * I * , I * * I *e U

D ~

-5

0 10 20 TIME(SEC)

30 40

636
VALVE B TEST 4, STEP 1

25

20 :

ff 15

T 5

I I , I I I I I I

I . . . I I I I I I . . I . . I 

o p-

-5 L

600

400

10 20

TIME(SEC)

30 40

VALVE B, TEST 4, STEP 1

C.) 200

0

-200 40

637
VALVE , TEST 4, STEP 1

600

So

,,, 4Dw

8 300

I-

-J

~. 30

g! 200

g 100

o

I I I I I i I I I I I a I I -4 I I I

I

- I 

q4w",

Ow

-1

I

. . . . I . . . . I . . . . I . . . . -100

cl 10 20

TIME(SEC)

30 40

VALVE B TEST 4, STEP 1

2

-1

A -2

I - -- I I I I 4 I I I I I I I I 

- *~ ~~~ I * ~ ~~ I ** I *

-3 

C1 . . . . . . . . . . . . . . . . . . . 10 20

TIME(SEC)

30 40

638
VALVE B TEST 4, STEP 1

4 - - - - - - - - - - - - - - - - - -

En 2

L~1

6 O

* S S S I * * * S I a a * I * * S S -1 

To 10 20

TIME(SEC)

30 40

VALVE B, TEST 4, STEP 1

5000

lh -sow

g -15000

-J

-20000

-25000 C1

a I I I I I I I I I I :

L S S S I I I I I I I I I I t a

i0 10 20

TIME(SEC)

30 49

639
800

700

.m3 600

.

(N4 500

E 400 EL

VALVE B, TEST 4, STEP 2

: : 

: 

300

200

0 40

1000

800

E 600

t 400

200

E

10 20

TIME(SEC)

30 4

VALVE B, TEST 4, STEP 2

40

640
VALVE B TEST 4, STEP 2

1000

80

600

( 400

200

0

0 10 20 30

TIME(SEC)

VALVE B TEST 4, STEP 2

10

8

0"C 6

rd. .

-: 4

I I I J II I I I I I g 

, , , .I . I 2 l i ' * ' ' .

40

40

2 

n I

0 10 20

TIME(SEC)

30 A

641
VALVE B TEST 4, STEP 2

800

600

of

.Ij

.

I-

-Jd

Lu

400

200

0

-200

3 

2 

1r

a 20

TIME(SEC)

VALVE B TEST 4 STEP 2

C

I-J

0

-1

-2

-3

-4

40

642
VALVE B TEST 4, STEP 2

25

201

In

2 15

E

~10 ,.

5

I I I I I I I I I A I I I I I 

. . . .. . I . . I1 . . :

...- ,,,,,,,,

-5 1 4 10 20

TIME(SEC)

30 49

VALVE B TEST 4, STEP 2

30

20

10.

-10

0

* I p p ~ ~ ~ ~~I I I 4 I I I I I I p I p 

I . . . . . . . . 20 . . . . .

t I I I I I I I I I I I 

I 10 20

TIME(SEC)

643

30 40
VALVE B TEST 4, STEP 2

25

20

9 15

,,10

a

- -

5

To 10 20 30

TIME(SEC)

40

VALVE B TEST 4, STEP 2

600

400

I I - I -F

4e i"

- - I -

2-

I~

200

0

-200 L

I

l l I 

10 20

TIME(SEC)

30 40
VALVE B TEST 4, STEP 2

600 - o - - - f - - -|*|

500

,,, 400

I-

>-300

5~ 200

lot)

> 10

I. . . . . I . . . . I . . . .

I I I II I , , I , , i * * -100

I 10 20

TIME(SEC)

30 40

2.0

VALVE B TEST 4, STEP 2

I I I I I I I I I ' ' ' .

f 1.5

1.0

5 0.5

0.0 --i -- E - I-------or . | I - -- --- I I I 

0 10 20

TIME(SEC)

30 40

645
VALVE B TEST 4, STEP 2

0.2

In

w

. ,

To

0.1 _

0.01-

a . . , , . I I , . . . , II.

I I I I I I . I I I I . . I I t a 

-0.1 -

-02

0 10 20

TIME(SEC)

30 40

VALVE B, TEST 4, STEP 2

20000

10000

0

-10000

-20000

-30000 20

TIME(SEC)

40

646
800

750

.E

70

VALVE B TEST 4, STEP 3&4

. . . I I I I I I I I I I

* * I * * ~~II I * * I *

650 1

600

800

750

. .

to 700

650

600

20 40

TIME(SEC)

60

VALVE B, TEST 4, STEP 3&4

40

TIME(SEC)

80

647
VALVE B TEST 4, STEP 3&4

ago

750

Cn

.EL

'0- 700

650

600

In

40

TIME(SEC)

40

VALVE B TEST 4, STEP 3&4

I 

0)

.D.

C}

Ir0-

Iiii

Cd

6 

I * * I * I a r- * l 

I I I I . . I , . . l , , p

4

2

0 20 40

TIME(SEC)

648

60 40
VALVE B TEST 4, STEP 3&4

100

80

rl 60 CL

9 40

i 20

0

-20

a 40

TIME(SEC)

so

VALVE B TEST 4, STEP 3&4

3

2

1

.-

t -1

-2

-3

-4

0 80

649
VALVE Li, TEST 4, STEP 3&4

25

20

tn

E 15

E

=10

,,

5

To

-5

0 40

TIME(SEC)

VALVE B TEST 4, STEP 3&4

30

20

a]

10

0a

I I I I I I I I 

* U U * aI I a U I I -10 40 0 20 40

TIME(SEC)

650

60 so
VALVE B TEST 4, STEP 3&4

25

20

L15

10

5

To

I I I S 5 4 * 1 I I S S S I a

I . . . I . .I , I SI -5 

aI 20 40

TIME(SEC)

60 s0

VALVE B TEST 4, STEP 3&4

600

400

In

C 200

C.)

. II I.

I . I I Ia3

-200

a 20 40

TIME(SEC)

60 80

651
VALVE B TEST 4, STEP 3&4

600

500

E,) 400

I0

>. 300 _

' 200

CD,

>. 100

0

-100

0

2 -

1 -

- _ . o 

-

1 -2 -

-3

0

V I I I~~~~~~~~~~~~~~~~~~~~~ I I , . a I a I I

I I , . I . I I I I I I

20 40

TIME(SEC)

60 s0

VALVE B TEST 4 STEP 3&4

20 40 60

TIME(SEC)

so

652
VALVE B, TEST 4, STEP 3&4

3.0

2.5

U,

-

Ui

a

2.0

1.5

1.0

0.5

0.0

- I I IIIIj I I I I I

-

, a I I I I . I . . a I I -0.5 

0 20 40

TIME(SEC)

60 80

VALVE B TEST 4, STEP 3&4

10000

5000

-J

0

-5000

-1000

-15000

-20000

-25000

653
-

VALVE , TEST 4, STEP 5

1000

900

. 7

En 700

600

500

0 10 20 30

TIME(SEC)

40

VALVE B TEST 4, STEP 5

1000

800

.E.

6D

400

200

0

-200

0 20

TIME(SEC)

.654
VALVE B TEST 4, STEP 5

100t .I * * * * I I I I I U 

800I

.O 600

V* 400

0)

200

0

-200 , . . . . . , . . . , . 0 10 20 30

TIME(SEC)

VALVE B TEST 4, STEP 5

25 , , * , 

20

.cp 15

- 0 10 20 30 40

TIME(SEC)

655
VALVE B, TEST 4, STEP 5

800

600

cm

.in

CL

0d.,

400

200

0

-200

3

2:

20

TIME(SEC)

40

VALVE B TEST 4, STEP 5

1

-

m

-J

0

-1

-2

-3

-4

0 10 20 30

TIME(SEC)

40

656
VALVE B TEST 4, STEP 5

25

20

U'

E

To

15

10

5

0

-.5

a 20

TIME(SEC)

40

VALVE B TEST 4, STEP 5

25

20

E 15

10

C1 5

0

-5 0 10 20 30

TIME(SEC)

657

40
VALVE B TEST 4 STEP 5

25 * I I I I * | I 5 I I I I 5 I I I I 

20F.

i 15

10

T 5

A;

* I I I I . I * I I I I * I I I

L~~~~~ I 

-5 

0 10 20

TIME(SEC) 30 40

VALVE B TEST 4, STEP 5

600

500

En 400 

I-6= 300

| 200

C)

>I' 100

-100' 0

0

I I I .I I . I I I I a I

* * * , * * * , . . . . , . . , 

10 20

TIME(SEC)

30 40

658
VALVE B TEST 4, STEP 5

600

.500:

400 

In

0. 300

C. 200

0

,i 100

0

-100

2 -

1 

2 I

X I

.. 0 

-1 -

-2

-3 -

* I I I I I A I I I & I I I I 

* . . , . . . . , . , . . , I a p p ':

.~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~7

:---, I - - - . - - :LI

--r

-L

10 20

TIME(SEC)

30 40

VALVE B TEST 4, STEP 5

40

659
VALVE B TEST 4, STEP 5

4

II, I

U.1,

ui

.

3S

3

2

I

0

.II.1 I filkm I L _ X _ - ------ _ fiul . ,_`UTrfJ 

-1 L

a

5000

0

l l l 20 30 10 20 30

TIME(SEC)

VALVE , TEST 4, STEP 5

40

I.

0

-J

-5000

-10000

-15000

-20000

20

TIME(SEC)

660'
VALVE B, TEST 4, STEP 6&7

800

700

.0

..

C4 600 

500_

400D

o

0

400

300

.L

a 200 ,,

(, 100

CL

0

-100

0o

10 20 30 TIME(SEC) 40

VALVE B TEST 4, STEP 6&7

661
VALVE B TEST 4, STEP 6&7

400

300

200

100

0

-100

0 10 20 30

TIME(SEC)

40

VALVE B TEST 4, STEP 6&7

0P

r20

15

10

5

0

-5

20

TIME(SEC)

662

40
VALVE B TEST 4, STEP 6&7

800

700

CP5 600

T Soo

I-

~400

300

200

-1

-2

-3

-4

VALVE B, TEST 4, STEP 6&7

20

TIME(SEC)

663
VALVE B, TEST 4, STEP 6&7

30

20

U,

E

a 10

T

-10

t

30

20

, .10

Iu

0

I p I p p p .p I P I F I I C I I

I I - I I I q I I I I I i I

-- 9m I _HAo 3 10 2u 4

TIME(SEC) MU

VALVE B, TEST 4, STEP 7

664
VALVE B TEST 4, STEP 6&7

25

20

t 15

10

0i

-5

0

VALVE B TEST 4, STEP 6&7

600 I , I I I I I * * * I | S S I

500

V, 40 0

X 300

T 200

0 i > 100

0

-10

0

- . . . , I . . . . , I

10 20

TIME(SEC)

30 40

665
VALVE B TEST 4, STEP 6&7

600

500

..... . . . . . . . . . . . . .~~ ~~~~~~~~~~

. . . . I . . . I I

. . .. U .-- I .t.

311 l ri I r r r r 1I

I0

5-,

I

4oo

300

200

100

0

-100 I . . . . I . I 

0 10 20

TIME(SEC)

30 40

VALVE B TEST 4, STEP &7

0.5

II-

=3.

0.4

0.3

0.2

0.1

* . . . I * I * * * I * *

* p p p I p p p p I p p p P I . p p p

0.0

0 10 20

TIME(SEC)

30 40

666
VALVE B TEST 4, STEP 6&7

4 I I I I I I I . . , . . . . , . .

I -I - - I

w

0

3

2

1

a

4ULVAIkILL

-1 . . l I , . . . . a ,. . I

. _ ' ' _'_ ' ' ' ' ' ' ' ' T~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

u 1D 20

TIME(SEC)

30 40

VALVE B TEST 4, STEP 6&7

20000

-

10000

0

-10000

-2000

4667
VALVE B TEST 4, STEP &9 100

50

.2)

. .

C14

4

En

0

-50

-100

a 20 40 60

TIME(SEC)

so

VALVE B, TEST 4, STEP 8&9

100

50

.0

.

En

a

-50

-10

a

668
VALVE B TEST 4, STEP 8&9

100

oP

.A

a

-50

-100

10 r

0 40

TIME(SEC)

s0

VALVE B TEST 4, STEP 8&9

I I I I I Ia I I

a

W" P o.55..z.-

- rr-M VP P. - k. .. 

0, .m

I,.

0 

2 -

0 U . . I I .

0 20 40

TIME(SEC)

60 s0

669
VALVE B TEST 4, STEP 8&9

150

l l

100 _

CP'Z

CL

, .

-

Ad

5o L

0

w_- p~vimvN -.1 boo

-50 I I I 

0 20 40

TIME(SEC)

60 sO

VALVE B TEST 4, STEP 8&9

2

1

I-

-J

0

-1

-2

-3

-4

To 40

TIME(SEC)

670
VALVE B TEST 4, STEP 8&9

30

20

UL

E

0 10

-10

a 40

TIME(SEC)

VALVE B TEST 4, STEP 8&9

251.

E 20

v 15

-5

I I I I I I I I I I j I I I

I I I I I * I I * I

0 20 40

TIME(SEC)

6D 80

671
VALVE B TEST 4, STEP 8&9

25

20

. 15

10

5

a

-5

0 20 40 60

TIME(SEC)

s0

VALVE B TEST 4, STEP 8&9

600

50

C.)

400

,300

200

100

. , I I I I I --9 I

0

-100 I - . . . . . . .~~~ I - -I -I I I I I

0 20 40

TIME(SEC)

60 80

672
VALVE B TEST 4, STEP 8&9

600

500 1~~~~~~~~~~~~~~~~~~~~ I I

Un

I-

-J0

, .

400

3w

200

100

0

-100:

0

2 II I I a a I I I I I . . . .

20 40

TIME(SEC)

60

VALVE B TEST 4, STEP 8&9

2.0

a 1.5

,I.

6 1.0

5 0.5

0.0

0

0 40

TIME(SEC)

4673
VALVE B TEST 4, STEP 8&9

4-

VI 3

2

T 1 - *..

E o:

-1

0

20000

TIME(SEC)

VALVE B TEST 4, STEP 8&9

10000

0

-1000

--Iu- - I I I I I I I

I . . I . I 

-20000 1

-30000 1

cI 20 40

TIME(SEC)

60 so

614
1000

950 L

0'

c"J 900

In

, .

VALVE B, TEST 5, STEP 1

k- w %A JI ~ ~ ~ ~ I- -

... .0 20 30 40'''

__ I L l f i L L L

850 

800

ID 1D 20 30 40

TIME(SEC)

VALVE B TEST 5, STEP 1

1000

950

.,E

m 900

I

* I I ~ ~ ~ ~ I-~ T I I U -

* . . . I , , 4 . I . . . . I , * . 4

850 

B00 

lI 10 20

TIME(SEC)

30 40

675
VALVE , TEST 5, STEP 1

1000

9501

an

wJ- 900 a.

a.,

p I I I I * I 5 I I I I I

I I - I I . i I I I I , - I I I a 

_U I

850

B0

0 40

10

a

.0

CL 6

-

IL

10 M TIME(SEC) MJU

VALVE , TEST 5, STEP 1 a I I I I I . I I * I * . I 5 . I I

I I I I I , , * p I . a I I I I.

2 

0

a 10 20

TIME(SEC)

676

30 40
120

100 

1, 80

*u 60

Cj

T 40

E2D 20

0

VALVE B, TEST 5, STEP 1

N * * , , , p , p , , I 

-nn F * 1p * I I I * * I * * * * I I I 

0

3

2

10 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 1

1

8 -1

-2

-3

-4

2D

TIME(SEC)

677
VALVE B TEST 5, STEP 1

25

201

Up

2 15

E.

0

I . . . I I I . I

I a t 2 I I I I I I i * I * I I * * -5 .

0

25

20

E 15

10

l : 5 5

0 

-5

10 20 TIME(SEC) 30 40

VALVE B, TEST 5, STEP 1

40

678
VALVE B TEST 5, STEP 1

25

20 

9101

9 0

I I I I I I a & I I I I I I I I I

- , , , I I I I , , , , I t I I -5 

aI 20

TIME(SEC)

40

VALVE B TEST 5, STEP 1

600

400

-

-. 200

0_

a a a I I g I I -I .I a I I I

a I t I I I -. -, - I I I I I I L 2 | 9

0

-200

0 10 20

TIME(SEC)

30 40

679
VALVE B TEST 5, STEP 1

800

600

Io 400

1!200

0

-200

a 10 20 30

TIME(SEC)

40

VALVE B TEST 5, STEP 1

2

1

-

-1 -2

-3

20

TIME(SEC)

680

40
4

3

2

1

TU

0

IVALVE B TEST 5, STEP 1 L. I I. , I. . ....

_ a I I I I I I I I I , I I ..., 

I 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 1

0.

-5000

.. -100o

2 -15000

-20000 

-25000

To 10 20 30

TIME(SEC)

681

40
VALVE B TEST 5, STEP 2

1000 , , , 

950

C- 850 9100a r___, 

80

0 10 20 30 40

TIME(SEC)

VALVE B, TEST 5 STEP 2

1000 . . , 

800

2600

~400

200

0 . ,, I . . . . I 4 0 

0 10 2,0_ 30 40

TIME(SEC)

682
VALVE B TEST 5, STEP 2

,moo

600

- 400

200

0

6

I-

.,

r-4 

2

0

1

20

TIME(SEC)

40

VALVE B TEST 5, STEP 2

a I I I I I - i I I I I I I I -- . i , I

I 10 20

TIME(SEC)

30 40

683
VALVE B TEST 5, STEP 2

0

AL

i,

loDD

800

600

400

200

0

-200

0 10 20 30

TIME(SEC)

40

VALVE B, TEST 5, STEP 2

3

2

I

.G

c-1

-J

-2

-3

-4

0

684
VALVE B TEST 5, STEP 2

30

20

UI

03

E.

0 10

0

. . , . . . . I . . , I.

. . , .I . I . . . . I -10

a 10 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 2

25

20

15

10

5 5

20

TIME(SEC)

685
VALVE B TEST 5, STEP 2

25

20 

0 15

D 10

T 

I I I I I I I I a I I I I I I I I I :

I a a_ 

-r 5

0

600

500

g 400

: 300

I.

: 200

0

g 100

lo'

0

-100

10 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 2

a 10 20 30

TIME(SEC)

40

686
VALVE B TEST 5, STEP 2

600

500

En 400

IO 300

C 200

>100

0

-100

t

2.0

v 1.5

6 1.0

_0.5

0.0

. . ' ' 'I ' . ' I ' ' . ' I ' .

Ia

I

*10 20

TIME(SEC)

30 4

VALVE B TEST 5, STEP 2

40

TIME(SEC)

487
VALVE B TEST 5, STEP 2

0.2

0 10 20 30 40

TIME(SEC)

VALVE B TEST 5, STEP 2

20000A__ 

I-I

0

-20000

30000_,,,

0 10 20 30 40

TIME(SEC)

688
1000

9501

CL

,.

C4 900

n

VALVE B, TEST 5, STEP 3&4

' * ,. . , I I ., A 

, 4 4 . . . I I I I

853 1

BOB

c

1000 -

I 20 40

TIME(SEC)

60 80

VALVE B, TEST 5, STEP 3&4

95D 

,

. .

K 9DD

tL

Ln

I I I I II

I i I p I I p I , i I I g

I I 1- I I I 

850 1.

800F1

I 20 40

TIME(SEC)

689

60 80
VALVE B TEST 5, STEP 3&4

1000

950 

. 9

..

It 900

* . . I I I I

I I I I , * I I I *1I - I - 1 -

850 

8s0

a

6

0P

.G.

I4

T

Cl

2

0 20 40

TIME(SEC)

60 so

VALVE B, TEST 5, STEP 3&4

1~ ~~ ~~~~ I .I I I I I I I I I

I - I I I I I I I 

0

0 20 40

TIME(SEC)

60 80

690
1D0

S0

0,

an 60

T 40

El 20

To

VALVE B TEST 5, STEP 3&4

' ' ' ' ' ' ' ' ' ' ' ' ' '

* . , . . . . . . .a -20 

0

3-

2

1

C O .0

8 -1

-2

-3

-4-

20 40

TIME(SEC)

60 80

VALVE B TEST 5, STEP 3&4

40

TIME(SEC)

691
VALVE B TEST 5, STEP 3&4

25

20

U'

2L

Ea

T

15

10

5

0

-5

0 40

TIME(SEC)

VALVE B TEST 5, STEP 3&4

25

20

15

**10 I..

54 

0

-5

0 20 40 60

TIME(SEC)

692

s0
VALVE B TEST 5, STEP 3&4

30

T

203

*10

0 

-10

600

500

,, 400

> 300

>~ 200

0

> 100

0

-100

0

VALVE B TEST 5, STEP 3&4

40 TIME(SEC)

,693

80
VALVE B, TEST 5, STEP 3&4

800

600

I--J

o 400

! 200

0

-200

0

VALVE , TEST 5, STEP 3&4

2

1

('3

-1

I-

-2

-3

0 20 40 60

TIME(SEC)

694

so
VALVE B TEST 5, STEP 3&4

0 ~~20 40 60 8D

TIME(SEC)

VALVE B TEST 5, STEP 3&4

-25000:

4200

40

TIME(SEC)

695
VALVE B TEST 5, STEP 5

1100 * , , a * , -* * 

1000

' 9003

700

600

500 , , , 

0 10 20 30 40

TIME(SEC)

VALVE B, TEST 5, STEP 5

12003 * * * * ' * * ' * * * , * * 

1000

800

,,600

400

200

0-

-200 . , , 0 10 20 30 40

TIME(SEC)

696
VALVE , TEST 5, STEP 5

1200 ' ' ' ' I ' ' ' * 

1200

10'0

.600

400

CL 200

0

-200 

-20 ID10 20 30 40

TIME(SEC)

VALVE B TEST 5, STEP 5

40 * * * * ' X 

30

13

20

0

0 10 20 30 40

TIME(SEC)

697
VALVE B, TEST 5, STEP 8&9

25

I I I

20 :

15

l0

5

a ii I.._ I

-5 l I 

0 20 40

TIME(SEC)

60 so

VALVE B TEST 5, STEP 8&9

600

50

U,

C-

:'

400

300

200

100

I . I . , . I I

. I . I , , I a I , I,

0

-100

0 20 40

TIME(SEC)

60

698
VALVE B TEST 5, STEP 8&9

800

600

En

..

400

200

0

-200

0 20 40 60

TIME(SEC)

l

VALVE B TEST 5, STEP &9

2.0

(1 1.5

I.-

is 1.0

5 0.5

I I , . , I a I I I I

. - . , , . , . , , , . I . . . . . .

so

80

0.0 

0 20 40

TIME(SEC)

,699

60 I
VALVE B TEST 5, STEP 5

1000

BoO

0)

. .

JL

600

400

200

0

40

VALVE B TEST 5, STEP 5

3

2

1

..

D

>i

a

-1

-2

-3

-4

0 10 20 30

TIME(SEC)

.700

40
VALVE B TEST 5, STEP 5

25

20 :

U

2 15

EL

. 10ID

5

a

I I I a I I I I I I I I I I I 

* ' ' ' I I I -5 

0 - - - - - -10 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 5

25

20

15

10

5 

0 

-5

0 10 20 30

TIME(SEC)

701

40
VALVE B TEST 5, STEP 5

30

20

10

0

I I I

-10 I I I

a

600

500

,, 400

, 300

T 200

> 100

0

10 20 30 40

TIME(SEC)

VALVE B TEST 5, STEP 5

l , , , l _ 

-100

0 10 20

TIME(SEC)

30 40

702
VALVE B TEST 5, STEP 5

600

50

Ln

I-

-J

400

300

200

100

p 5 p 5 5 I S I j I I p p i * * p

. a p a I p 0 5 p I a I p a I , . , P

0

2 -

10 20 10

TIME(SEC)

30 49

VALVE B TEST 5, STEP 5

f n6

Al

5

=1

I

0

-1

-2

-3

20

TIME(SEC)

703
VALVE B, TEST 5, STEP 5

3.0 . . . . . . . . . . . . . . . .~~ . .

2.5

I--

>' 2.0 -

1i 1.5

LU 1.0

'- 0.5

0.0

0

0

-5000

-10000

> -15000

-20000

r T T § | T II I

toI . , . I I I I. .I.. L ,. 

I I I I I I I .I 

IM!I2- . .- -- .. [IIu I -

i I I I . I I . I I I .

10 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 5

20

TIME(SEC)

40

704
VALVE B TEST 5, STEP 8&9

400

300

.0

200

En 100

-100

300

200

00

0

cn

-100

3

VALVE B TEST 5 STEP 8&9

* .I I I l I I I ' ' .

* S S I , * S I * S I * S I

I 20 40

TIME(SEC)

705

60 80
VALVE , TEST 5, STEP 8&9

300 . . . ,

200

- 100 . . . , . . . ,,

0 20 40 60 80

TIME(SEC)

VALVE B, TEST 5, STEP 8&9

10

8::

Am 

6_

2

0 20 40 60 80

TIME(SEC)

706
250

200 

Cn .Ul

C,

CIEd

CD

150

100

VALVE B. TEST S. STEP 8&9

I L 

* I . . . I * p * 9 * * *

0

-50

0

3

2

1r

20 40

TIME(SEC)

60

VALVE B, TEST 5, STEP 8&9

80

so

I-

--J

a

-1

-2

-3

-4

40

TIME(SEC)

*707
VALVE B TEST 5, STEP 8&9

25

20

En

2 15 

E

a010 

0

-5

0 20 40 60

TIME(SEC) so

VALVE B TEST 5, STEP 8&9

.a I I I I I 

20

10

Il l

%fl

-10 U | | I I , 40 U I I a U 

0 20 40 TIME(SEC)

.708

60 80
VALVE B TEST 5, STEP 8&9

4

3

., 2

a1

* . . . * I I I

n4 . I . . I I , , '

0

30000

20000

20 40

TIME(SEC)

60 so

VALVE B TEST 5, STEP 8&9

01

-J

1000

0

-10000

-20000

-30000

0 20 40 60

TIME(SEC)

s0

.709
VALVE B TEST 5, STEP 17

1000

aC, .' 920

8860 -

EL

E~ 9200

8800

1200

400

BO

.2)

., 600

1 400

0

-200

20 30

TIME(SEC)

40

VALVE , TEST 5, STEP 17

I , , II II I I I 

I I I I i tI I t a t a I a a 5

a 10 20

TIME(SEC)

30 40

710
VALVE B TEST 5, STEP 17

1200

1000

BOB

.cp

((3I 40D

~-D

~-200

0

-200

6-

_I I I I I I a onII 

) 10 2u

TIME(SEC)

"aU 40

VAVLE B TEST 5, STEP 17

12

CP

CL 0.6

aff 0.6

40

711
VALVE , TEST 5, STEP 17

1200

1000

c

'in

.,

Bo0

600

400

200

* * ~~~~~~~~I *I I I *

I I I . I . . . I I I . . *

0

-200

0 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 17

3

2

1

0

,_j

0

-1

-2

-3

-4

0

.712
VALVE B TEST 5, STEP 17

25

20

Ul

15

03

E

0 1

5

a . I - I I I I I I I I I I I 

* I I * * I II I I -s 5 0 10 20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 17

25

20

E15

10

5

I

* I I * j I I I I I I II I I I I & I

-5 * e I , I , , a , I I I I * l

0 10 20

TIME(SEC)

713

30 40
VALVE B TEST 5, STEP 17

25

20

0 15

-5

600

500

~,,400

300

. .

20-

C) 6 100

50

. , 5 , A I ' I ' ' ' ' ' :

I * , I I_ , * I I a I , 

I

I

I

I

20

TIME(SEC)

30 40

VALVE B TEST 5, STEP 17

-100 0 10 20

TIME(SEC)

40

714
VALVE B TEST 5, STEP 17

600

50

n) 400

9 300

" 200

i 100

0

-100

0 10 20 30

TIME(SEC)

40

VALVE B TEST 5, STEP 17

2.0

in 1.5

E 1.0

, 0.5

I , I I I I I I I I 

- - I 0.0

0 10 20

TIME(SEC)

30 40

715
VALVE B TEST 5, STEP 17

0.05 ' ' ' ' | ' ' * ' | '

) 0.04

0.03

E 0.02

o~~~~~oo ~ ~ , , , 

0 10 20 30 40

TIME(SEC)

VALVE B TEST 5, STEP 17

20000 ' * * * * . * * .

10000

0

-10000

-20000

-3X00 ,0 .. 20 0 10 20 30X

TIME(SEC)

716
NRC FU 335 U S. NUCLE&R REGULATORY COMMISSION I.REPORT NUMBER

Ga91 Ftl Vd b NRC Ad Ve.S. , Ar.. NRCM 1102. "~~~~~~~~~~~~~~~~~~~~~~~~~ Addsndum Nu-tw. I ony I

RCt07, 2BIBLIOGRAPHIC DATA SHEET NUREG/CR-5406

e insrtions n the rse NUREG/CR-5406

2. TITLE AND SUBTITLE EGG-2569 Vol. 2

BWR Reactor Water Cleanup System Flexible Wedge Gate Isolation

Valve Qualification and High Energy Flow Interruption Test 3. IATEREPORTPUIESHEO

. *8~~~~~~~~~~~~~~~~~ONT*4 | R

Data Report October 1989

4. FIN OR GRANT NUMBER

A6857 and B5529

5. AUTHOR(S) 6. TYPE OF REPORT

Kevin G. DeWall Technical

Robert Steele, Jr. 7. PERIOD COVERED f5ffi*W'e

S. PER FORMI1NG ORGAN IZATION -NAME AND ADDR ESS11s Rxc.,orVieo lOfKf 0e Region .SNFr RurevCnriondmtgdlnifento pe awne end mwlin addW.&J

Idaho National Engineering Laboratory

EG&G Idaho, Inc.

P.O. Box 1625

Idaho Falls, ID 83415

9. SPONSORING ORGANIZATION -NAME AND ADDRESS ffRCr. y Sen 'Se o abo., WConcroP A*m NRC OWfion. OMCe or Aeso.. U.S MVCfe' Rf ulmso1V C.niion.

-a miing iddnZL).

Division of Engineering and Division of Safety Issue Resolution

Office of Nuclear Regulatory Research

U.S. Nuclear Regulatory Commission

Washington, DC 20555

10. SUPPLEMENTARY NOTES

I1. ABSTRACT 120 od or t l

This report presents the measured data and the analyses performed to date on the fll-scale high-energy

qualification and flow interruption gate valve testing to develop technical insights for the United States Nuclear

Regulatory Commission USNRC) effort regarding Gcneric Issue 87 (GI-87). The research was sponsored by the

USNRO and conducted by researchers from the Idaho National Engineering Laboratory. We tested two 6-in., 900-lb

class valve assemblies, which represent a significant percentage oftbe reactor water cleanup isolation valves installed in

plantapplications. These valves were modified before testing by adding ahigh temperature load cell in the valve stems,

which allowed the direct measurement of valve stem thrust during both opening and closing valve cycles.

Instrumentation installed in the low loop and on the valve assemblies measured the important valve and system test

responses. Additionally, during the testprogram, all of the currentlypopularmotor operated valve diagnostic test systems

monitored the perfonnance of the valves. Initially the valves were subjected to the hydraulic and Icakage qualification

tests defined in ANSI B16.41 and then to flow interruption and reopening valve tests at boiling water ra.IoT primary

system water temperature and pressure conditions with downstream line break flows. For the two valves tested, results

show that (a) the disc factor used in current industry motor operator sizing equations underpredicts actual valve thrust

requirements at all high temperature loadings, and for one valve design the equations may require an additional term to

account fornonlinearperformance, (b)the thrusts required to close the valves were sensitive to the fluid temperature, and

(c) the results of testing at lower pressures, temperatures, and flows cannot be extrapolated to design basis pressures,

temperatures, and flows for valve designs that have not exhibited linear performance behavior during design basis

- rototyical testing.th 1.AALBIT AEE0 12. tdT WUhDUtb4.ha-ra1n S Qhlu wor1* 6ar000s.s ilar wiff ssistrehtgAn Ah 0c~ w #inomrd 1. AVAILABILt tAIEME 1

valve testing Unlimited

BWR reactor water cleanup 14. SECURIIYCLASSIFICAIOCJ

Generic Issue 87 (GI-87) fr1T 0,00

Unclassified

IIrni Repotj

Unclassified

15 NUMBER OF PAGES

IS. PRICE

NRC foRM 35 (491
UNITED STATES

NUCLEAR REGULATORY COMMISSION

WASHINGTON, D.C. 20555

SPECIAL FOURTH-CLASS A. POSTAGE e FEES PAID

USNRC

PERMIT No. G-87

OFFICIAL BUSINESS

PENALTY FOR PRIVATE USE. *300