# Revision 4.3

1/19/10 

# Air Pollution Control Operating Permit

Minor Modification and Preconstruction Approval

Permit Activity Number: BOP090002 Program Interest Number: 55793

Mailing Address Plant Location

MICHAEL KISSEL

PLANT MGR

WHEELABRATOR GLOUCESTER CO LP

600 RT 130

West Deptford Twp, NJ 08093 WHEELABRATOR GLOUCESTER COMPANY

L P

600 Us Rt 130

Westville Boro

Gloucester County

Initial Operating Permit Approval Date: December 13, 2003

Minor Modification Approval Date: February 25, 2010

Operating Permit Expiration Date: December 11, 2013

This minor modification is approved and issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 26:2C-9.2).

The equipment at the facility must be operated in accordance with the requirements of this permit.

This approval, in response to your application, merges the provisions of the previously approved operating permit

and the changes from this minor modification into a single comprehensive permit that replaces the one previously

issued. This approval is for the proposed addition of non-ferrous metal separation and ash conditioning equipment

to Emission Unit U5 (ash handling in ash and metals loadout building) and the correction of an equipment

designation error in U4 and U5. The existing ash conditioning equipment in the ash conditioning area permitted as

Emission Unit U4 will then be used as backup or secondary equipment. A correction was made to the equipment

designation under OS1, U4. The equipment is E8 instead of E5, which is OS3 of U5. No other changes to U4 are

required. All emissions are less than de minimis emission levels and no changes to the compliance plan are required

Equipment at the facility referenced by this minor modification is not covered by the permit shield, pursuant to the

provisions of N.J.A.C. 7:27-22.17. Pursuant to N.J.A.C. 7:27-22.33(e), this minor modification consists of both a

preconstruction approval and operating permit approval. This operating permit does not include compliance

schedules as part of the approved compliance plan.

The permittee shall submit to the Department and to the EPA on forms provided by the Department, at the addresses

given below, a periodic compliance certification, in accordance with N.J.A.C. 7:27-22.19 and the schedule for

compliance certifications set forth in the compliance plan in this operating permit. The annual compliance

certification reporting period will cover the calendar year ending December 31. The annual compliance

certification is due to the Department and the EPA within 60 days af ter the end of each calendar year during

which this permit was in effect. Forms provided by the Department can be found on the Department's website at:

http://www.nj.gov/dep/enfor cement/compliancecertsair.htm

.

The annual compliance certification report may also be consid ered as your six month deviation report for the period

from July 1 through December 31 which is due by January 30 of each year, as required by paragraph 13 in Section

F, General Provisions and Authorities



# , of this permit, if the annual compliance certification is submitted by January

30. CHRIS CHRISTIE 

# D EPARTMENT 

# of E NVIRONMENTAL 

# P ROTECTION 

# BOB MARTIN

Governor Acting Commissioner

Division of Air Quality



# KIM GUADAGNO Bureau of Air Permits



# Lt. Governor 401 E. State Street, 2 nd 

# floor, P.O. Box 27

Trenton, NJ 08625-0027

# Revision 4.3

1/19/10 New Jersey Department of Environmental Protection United States Environmental Protection Agency, Region II

Air & Environmental Quality Compliance & Enforcement Air Compliance Branch

401 East State Street, P. O. Box 422 290 Broadway

Trenton, New Jersey 08625-0422 New York, New York 10007-1866

Air and Environmental Quality Compliance& Enforcementt

Southern Regional Enforcement Office

One Port Center, 2 Riverside Drive, Suite 201

Camden, NJ 08102

Air and Environmental Quality Compliance& Enforcement



# We are including two electronic files, PDF and RADIUS. The PDF file contains the complete operating permit for

your facility. The RADIUS file contains the Facility Name, Location, and Contact Information; the Facility Specific

Requirements (Compliance Plan) and Inventories; and any Compliance Schedules (if needed). Upon importing this

information into your personal computer with RADIUS software, you will have up-to-date information in RADIUS

format. RADIUS software, instructions, and help are available at the Department's website at

www.state.nj.us/dep/aqpp. We also have an Operating Permit Help Line available from 9:00 AM to 4:00 PM daily,

where you may speak to someone about any questions you may have. The Operating Permit Help Line number is

609-633-8248.

If, in your judgment, the Department is imposing any unreasonable condition of approval in this permit modification

action, you may contest the Department’s decision on the modification and request an adjudicatory hearing pursuant

to N.J.S.A. 52:14b-1 et seq. and N.J.A. C. 7:27-22.32(a). All requests for an adjudicatory hearing must be received

in writing by the Department within 20 calendar days of the date you receive this letter. The request must contain

the information requested in N.J.A.C. 7:27-1.32 and the information on the enclosed Administrative Hearing

Request Checklist and Tracking Form.

The permittee is responsible for submitting a timely and administratively complete operating permit renewal

application. The application is considered timely if it is received at least 12 months before the expiration date of the

operating permit. To be deemed administratively complete, an application for renewal of the operating permit shall

include all of the information required by the application form for the renewal and the information required pursuant

to N.J.A.C. 7:27-22.30(d). However, consistent with N.J.A.C. 7:27-22.30(c), the permittee is encouraged to submit

the renewal application at least 15 months prior to expiration of the operating permit, so that the Department can

notify the applicant of any deficiencies in the application. This will allow the permittee to correct any deficiencies,

and to better ensure that the application is administratively complete by the renewal deadline. Only applications

which are timely and administratively complete will be eligible for coverage by an application shield. The renewal

application can be found at our website, http://www.state.nj.us/dep/aqpp/downloads/forms/OPRenewal.PDF

.

Permittees that are subject to Compliance Assurance Monitoring (CAM), pursuant to 40 CFR 64, shall develop a

CAM Plan for modified equipment as well as existing sources. Details of the rule and guidance on how to prepare a

plan can be found at EPA’s website: www.epa.gov/ttn/emc/cam.html . In addition, CAM Plans must be included as

part of the permit renewal application. Permittees that do not submit a CAM Plan may have their modification

applications denied, pursuant to N.J.A.C. 7:27-22.3.

If you have any questions regarding this permit approval, please call your permit writer, Harry Baist, at (609) 633-

8235.

Approved by:

Yaso Sivaganesh

Bureau of Air Permits

Enclosure

CC: S. Riva, USEPA Region II (CD containing final permit)

# Revision 4.3

1/19/10 

# Administrative Hearing Request **Checklist and Tracking Form**

**I. Document Being Appealed**

**Name of the Facility Program Interest** 

**(PI) Number Permit Activity** 

**Number Issuance** 

**Date**

**WHEELABRATOR GLOUCESTER**

**COMPANY L P 55793 BOP090002** 

**II. Contact Information**

**Name of Person Requesting Hearing Name of Attorney (if applicable)**

**Address: Address:** 

**Telephone: Telephone:** 

**III. Please include the following information as part of your request:**

A. The date the permittee received the permit decision,

B. One printed and two PDF (or scanned) copies of the document being appealed saved on

two CDs – for submitting to address 1 below;

A PDF (or scanned) copy of all documents being submitted to the Office of Legal Affairs

saved on a CD – for submitting to address 2 below **;** C. The legal and factual questions you are appealing;

D. A statement as to whether or not you raised each legal and factual issues during the

permit application process;

E. Suggested revised or alternative permit conditions;

F. An estimate of the time required for the hearing;

G. A request, if necessary, for a barrier-free hearing location for physically disabled persons;

H. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Departments processing of your hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 E. State Street, P.O. Box 402

Trenton, New Jersey 08625-0402

2. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625-0027

Phone: (609) 633-2829

**Signature Date**

# Revision 4.3

1/19/10 

# Administrative Hearing Request **Checklist and Tracking Form**

**IV. If you are not the applicant but rather an interested person claiming to be aggrieved by the**

**permit decision, please include the following information:**

1. The date you or your agent received notice of the permit decision (include a copy of that

permit decision with your hearing request);

2. Evidence that a copy of the request has been delivered to the applicant for the permit

which is the subject of the permit decision;

3. A detailed statement of which findings of fact and/or conclusion of law you are

challenging;

4. A description of your participation in any public hearings held in connection with the

permit application and copies of any written comments you submitted;

5. Whether you claim a statutory or constitutional right to a hearing, and, if you claim such a

right, a reference to the applicable statute or explanation of how your property interests

are affected by the permit decision;

6. If the appeal request concerns a CAFRA permit decision, evidence that a copy of the

request has been delivered to the clerks of the county and the municipality in which the

project which is the subject of the permit decision is located;

7. Suggested revised or alternative permit conditions;

8. An estimate of the time required for the hearing;

9. A request, if necessary, for a barrier-free hearing location for physically disable persons;

10. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Department’s transmittal of the hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 East State Street, P.O. Box 402

Trenton, New Jersey 08625-0402

2. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625

Phone: (609) 633-2829

**Signature Date**

# Revision 4.3

1/19/10 

# Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

TABLE OF CONTENTS

Section A

REASON FOR PERMIT

Section B

DEFINITIONS

Section C

POLLUTANT EMISSIONS SUMMARY

Section D

POLLUTION PREVENTION REPORTING

Section E

GENERAL PROVISIONS AND AUTHORITIES

Section F

STATE-ONLY APPLICABLE REQUIREMENTS

Section G

COMPLIANCE PLAN AND INVENTORIES

# Revision 4.3

1/19/10 

# Section A

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

REASON FOR PERMIT

The reason for issuance of this permit is to comply with the air pollution control permit provisions of Title V of the

federal Clean Air Act, federal rules promulgated at 40 CFR 70, and state regulations promulgated at N.J.A.C. 7:27-

22, which requires the state to issue operating permits to major facilities and minor facilities that are in certain

designated source categories. This is the operating permit for the facility listed on the cover page, which includes a

minor modification for the addition of non-ferrous metal separation and ash conditioning equipment to Emission

Unit U5 (ash handling in ash and metals loadout building) and the correction of an equipment designation error in

U4 and U5. The existing ash conditioning equipment in the ash conditioning area permitted as Emission Unit U4

will then be used as backup or s econdary equipment. A correction was ma de to the equipment designation under

OS1, U4. The equipment is E8 instead of E5, which is OS3 of U5. No other changes to U4 are required. All

emissions are less than de minimis emission levels and no changes to the compliance plan are required

New Jersey has elected to integrate its Title I New Source Review (NSR) preconstruction permits with the new Title

V operating permits instead of issuing separate permits. Consequently, the existing preconstruction permit

provisions that were previously approved for this facility have been consolidated into this permit. This permit may

also include applicable requirements for grandfathered sources.

This permit action consolidates previously approved permit terms and conditions into one single permit for the

facility. The New Jersey Department of Environmental Protection (Department) issues this operating permit

authorizing the facility to operate equipment and air pollution control devices. In the operating permit application,

the facility represented that it meets all applicable requirements of the federal Clean Air Act and the New Jersey Air

Pollution Control Act codified at N.J.S.A. 26:2C. Based on an evaluation of the data contained in the facility’s

application, the Department has approved this operating permit.

This permit allows this facility to operate the equipment and air pollution control devices specified in this permit and

emit up to a level specified for each source operation. The signatories named in the application are responsible for

ensuring that the facility is operated in a manner consistent with this permit, its conditions, and applicable rules.

# Revision 4.3

1/19/10 

# Section B

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

DEFINITIONS

The terms used in this permit are used consistent with the definitions at N.J.A.C. 7:27-1 and N.J.A.C. 7:27-22. Any

terms defined in this section are not defined at N.J.A.C. 7:27-1 or N.J.A.C. 7:27-22, and are needed for clarifying

the permit.

“Permitting Authority” means the New Jersey Department of Environmental Protection (NJDEP).

“The EPA,” or “the Administrator,” means the Administrator of the EPA or his designee.

“M” preceding a unit of measure means one thousand. For example, “10 M gal.” means ten thousand gallons.

“MM” preceding a unit of measure means one million. For example, “10 MM gal.” means ten million gallons.

“Grandfathered” means, in reference to equipment or co ntrol apparatus, that construction, reconstruction, or

modification occurred prior to enactment of N.J.S.A. 26:2C-9.2 on June 15, 1967, or prior to the subsequent

applicable revisions to rules and regulations codified at N.J.A.C. 7:27-8 that occurred March 5, 1973, June 1, 1976,

April 5, 1985, and October 31, 1994, and no construction, reconstruction, or modification of the equipment or

control apparatus has occurred since.

“Compliance Plan” means the applicable requirements, mo nitoring requirements, record keeping requirements, and

submittal/action requirements detailed in Section G, Facility Specific Requirements, of the operating permit.

# Revision 4.3

1/19/10 

# Section C

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

POLLUTANT EMISSIONS SUMMARY



# The following table indicates the facility’s Potential to Emit (PTE) emissions summary:

Facility Total Potential to Emit

(tons per year)

Primary Secondary Source Categories

VOC

(total) NO

x 

# CO SO 2 

# TSP

(total) Other

(total) PM 10 

# (total) Pb HAPs

(total)

Emission Unit

Summary 24.3 471 99.1 224 29.3 NA 39.7 2.4 69

Batch Process

Summary NA NA NA NA NA NA NA NA NA

Non-Source Fugitive

Emissions 1 

# NA NA NA NA 2.1 NA 2.1 NA NA

Group

Summary NA NA NA NA NA NA NA NA NA

Total

Emissions 2 

# 24.3 471 99.1 224 31.4 NA 41.8 2.4 69

VOC Volatile Organic Compounds PM 10 

# Particulates under 10 microns

NO

x 

# Nitrogen Oxides Pb Lead

CO Carbon Monoxide HAPs Hazardous Air Pollutants

SO 2 

# Sulfur Dioxide

TSP Total Suspended Particulates

Other Any other air contaminant regulated under the Federal Clean Air Act

1 

# Not applicable to this facility.

2 

# Total emissions from this facility do not include emissions from Insignificant Sources.

# Revision 4.3

1/19/10 

# Section C

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

The following table indicates the facility’s ha zardous air pollutants (HAP) emissions summary: 3



# HAP TPY

Hydrogen Chloride 64.4

Hydrogen Fluoride 1.92

Mercury 0.03

Arsenic 0.028

Beryllium 0.0000964

Cadmium 0.096

Chromium 0.048

Lead 2.4

Nickel 0.048

TCDD (2,3,7,8-) 0.00000048

Polycyclic Organic Matter 0.123

3 

# Do not sum these values for the purpose of establishing a total HAP potential to emit. See previous page for the

allowable total HAP emissions.

# Revision 4.3

1/19/10 

# Section D

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

POLLUTION PREVENTION REPORTING

General Pollution Prevention conditions

The following evaluation requirements are included to track the facility’s progress in several critical areas identified

in the National Environmental Performance Partnership System (NEPPS). Nitrogen Oxides (NOx) and Volatile

Organic Compounds (VOC) are precursors to the air pollutant Ozone, for which New Jersey is non-attainment with

the air quality standard for the protection of public health . The control of hazardous air pollutants (HAPs) is also a

focus item for the next decade in order to minimize localized hot spots and general urban air toxics levels.

Therefore, the Department is requiring evaluation of emission trends at 5-year intervals for major sources of these

air contaminants. Also, as part of significant modification applications, proposed major increases of these air

contaminants requires evaluation of po llution prevention and cross media effects.

The evaluation of these trends requires no increased monito ring. Rather it utilizes existing monitoring data, as

reported annually in Emission Statements (for NOx and VOC) and annual Release and Pollution Prevention Reports

(for HAPs). The intent of this evaluation is to better utilize the existing data by having the company, the public and

the Department review major source trends periodically, as part of the 5-year renewal review and public comment

process. The Department requests that the facility-wide tr ends be presented on graphs for attachment to the public

information document for the 5-year renewal.

Pollution prevention includes changes that result in the reduction in use or generation of non-product output per unit

of product. Cross media effects are practices that result in transferring the ultimate release or disposal of a

contaminant from one environmental medium (e.g. air) to another environmental medium (e.g. water, solid or

hazardous wastes).

Information to include with the renewal application:

1. The facility will evaluate annual emission trends over the last five years for actual air contaminant

emissions of Volatile Organic Compounds (VOC), Nitr ogen Oxides (NOx), if the facility’s potential to

emit VOC or NOx is greater than 25 tons per year, or any Hazardous Air Pollutants (HAP), for which the

facility’s potential to emit is greater than 10 tons per year. The VOC and NOx emission data should reflect

annual emission statement reports submitted pursuant to N.J.A.C. 7:27-21, and the HAP emissions data

should reflect the annual Release and Pollution Prevention Report submitted pursuant to N.J.A.C. 7:1G-4

and 5 and N.J.A.C. 7:1K-6. Although not required, the Department encourages the facility to explain the

reason for any significant trend, including whether it is the result of cross media shifts (to air, water, or

solid waste) and/or pollution preven tion. Changes should be itemized for each emission unit (or process)

with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton per year

of any HAP. Also, show the net change for the facility.

2. The facility will summarize annual potential to emit limits (allowable emissions) for VOC, NOx, and

HAPs, which are subject to reporting under 1 above, for the last five years. Changes should be itemized for

each emission unit (or process) with a potential to emit over five tons per year of VOC or NOx or a

potential to emit over one ton per year of any HAP. Also, show the net change for the facility.

3. The facility will summarize five-year trends in annual VOC, NOx, and HAP emissions, which are subject

to reporting under 1 above, on a pound per unit of pr oduct basis, based on annual actual emissions and

annual production over the five year period. Changes should be itemized for each emission unit (or

# Revision 4.3

1/19/10 

# process) with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton

per year of any HAP. Also, show the net change for the facility.

4. The facility will discuss five-year trends in actual air contaminant emissions of non-source VOC and HAP

fugitives, which are subject to reporting under (1) above; explain measures taken to minimize such

fugitives; and provide an explanation for any significant changes.

Information to include with an application for a significant modification to this permit:

1. For any significant modifications, the facility is encouraged to explain any cross media shifts of VOC and

HAP air contaminants as part of the significant modifica tion application. If an explanation is provided, the

facility should identify the pollutant and the specific environmental media to which the pollutant is

anticipated to be transferred, whether it be from air to solid waste or water, or from water or solid waste to

the air.

# Revision 4.3

1/19/10 

# Section E

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

GENERAL PROVISIONS AND AUTHORITIES

Operating Permits

1. No permittee shall allow any air contaminant, including an air contaminant detectable by the sense of

smell, to be present in the outdoor atmosphere in a quantity and duration which is, or tends to be, injurious

to human health or welfare, animal or plant life or property, or which would unreasonably interfere with the

enjoyment of life or property. This shall not include an air contaminant that occurs only in areas over

which the permittee has exclusive use or occupancy. Conditions relative only to nuisance situations,

including odors, are not considered Federa lly enforceable. [N.J.A.C. 7:27-22.16(g)8]

2. Any deviation from operating permit requirements which results in a release of air contaminants shall be

reported to the Department as follows:

If the air contaminants are released in a quantity or concentration which poses a potential threat to public

health, welfare or the environment or which might reasonably result in citizen complaints, the permittee

shall report the release to the Department:

i. Immediately on the Department hotline at 1-877-927-6337, pursuant to N.J.S.A. 26:2C-19(e); and

ii. As part of the compliance certification required in N.J.A.C. 7:27-22.19(f). However, if the

deviation is identified through source emissions testing, it shall be reported through the source

emissions testing and monitoring procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, the permittee shall

report the release to the Department as part of th e compliance certification required in N.J.A.C. 7:27-

22.19(f), except for deviations identified by source emissions testing reports, which shall be reported

through the procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, and the permittee

intends to assert the affirmative defense afforded by N.J.A.C. 7:27-22.16(l), the violation shall be reported

by 5:00 P.M. of the second full calendar day following the occurrence, or of becoming aware of the

occurrence, consistent with N.J.A.C. 7:27-22.16(l). [N.J.A.C. 7:27-22.19(g)]

3. The permittee shall comply with all conditions of the operating permit including the approved compliance

plan. Any non-compliance with a permit condition constitutes a violation of the New Jersey Air Pollution

Control Act N.J.S.A. 26:2C-1 et seq., or the CAA, 42 U.S.C. §7401 et seq., or both, and is grounds for

enforcement action; for termination, revocation and reissuance, or for modification of the operating permit;

or for denial of an application for a renewal of the operating permit. [N.J.A.C. 7:27-22.16(g)1]

4. It shall not be a defense for the permittee in an enfo rcement action that it would have been necessary to halt

or reduce the permitted activity in order to maintain compliance with the conditions of its operating permit.

[N.J.A.C. 7:27-22.16(g)2]

# Revision 4.3

1/19/10 

# 5. This operating permit may be modified, terminated, or revoked for cause by the EPA pursuant to 40 CFR

70.7(g) and revoked or reopened and modified for cause by the Department pursuant to N.J.A.C. 7:27-

22.25. [N.J.A.C. 7:27-22.16(g)3]

6. The permittee shall furnish to the Department, within a reasonable time, any information that the

Department may request in writing to determine whether cause exists for modifying, revoking and

reissuing, or terminating this operating permit; or to determine compliance with the operating permit.

[N.J.A.C. 7:27-22.16(g)4]

7. The filing of an application for a modification of an operating permit, or of a notice of planned changes or

anticipated non-compliance, does not stay any operating permit condition. [N.J.A.C. 7:27-22.16(g)5]

8. The operating permit does not convey any property rights of any sort, or any exclusive privilege. [N.J.A.C.

7:27-22.16(g)6]

9. Upon request, the permittee shall furnish to the Department copies of records required by the operating

permit to be kept. [N.J.A.C. 7:27-22.16(g)7]

10. The Department and its authorized representatives shall have the right to enter and inspect any facility

subject to N.J.A.C. 7:27-22, or portion thereof, pursuant to N.J.A.C. 7:27-1.31. [N.J.A.C. 7:27-22.16(g)9]

11. The permittee shall pay fees to the Department pursuant to N.J.A.C. 7:27. [N.J.A.C. 7:27-22.16(g)10]

12. Each permittee shall maintain records of all source em issions testing or monitoring performed at the facility

and required by the operating permit in accordance with N.J.A.C. 7:27-22.19. Records shall be maintained,

for at least five years from the date of each sample, measurement, or report. Each permittee shall maintain

all other records required by this operating permit for a period of five years from the date each record is

made. At a minimum, source emission testing or mon itoring records shall contain the information specified

at N.J.A.C. 7:27-22.19(b). [N.J.A.C. 7:27-22.19(a) and N.J.A.C. 7:27-22.19(b)]

13. In accordance with N.J.A.C. 7:27-22.19(c) and 22.19(d) 3, each permittee shall submit to the Department,

on forms provided by the Department, a six month deviation report relating to testing and monitoring

required by the operating permit, not including information for testing and monitoring which have other

reporting schedules specified in the permit. Normally, stack testing reporting is submitted within 45 days

of test completion and continuous monitoring reporting is done quarterly. The six month report must

address other specified monitoring, including, but not limited to, continuous and periodic monitoring data

required by this permit. (See column two and three entitled “Monitoring Requirement” and

“Recordkeeping Requirement,” respectively, in the Facili ty Specific Requirements section of this permit.).

The six month reports for the testing and monitoring performed from January 1 through June 30, shall be

reported by July 30 of the same calendar year; or from July 1 through December 31, shall be reported by

January 30 of the following calendar year. Pursuant to N.J.A.C. 7:27-22.19(e), these six month reports

shall clearly identify all deviations from operating permit requirements, the probable cause of such

deviations, and any corrective actions taken. Any “None” listed in the Submittal/Action Requirement in

the operating permit is not intended to override the six- month deviation report. The report shall be certified

pursuant to N.J.A.C. 7:27-1.39 by a responsible official. Forms provided by the Department can be found

on the Department's website at: http://www.nj.gov/dep/enforcement/compliancecertsair.htm [N.J.A.C.

7:27-22.19(d) 3 and N.J.A.C. 7:27-22.19(e)]

An annual compliance certification required by paragraph 2 above and required by N.J.A.C. 7:27-19(f) may

also be considered as your six month deviation report for the period from July 1 through December 31

which is due by January 30 of each year if the annual compliance certification is submitted by January 30.

14. For emergencies (as defined at 40 CFR 70.6(g)(1)) that result in non-compliance with any promulgated

federal technology-based standard such as NSPS, NESHAPS, or MACT, a federal affirmative defense is

available, pursuant to 40 CFR 70. To assert a federal affirmative defense, the permittee must use the

procedures set forth in 40 CFR 70. The affirmative defense provisions described in 15 below may not be

applied to any situation that caused the Facility to exceed any federally delegated regulation, including but

not limited to NSPS, NESHAP, or MACT.

# Revision 4.3

1/19/10 

# 15. For situations other than those covered by 14 above, an affirmative defense is available for a violation of a

provision or condition of the operating permit only if:

i. The violation occurred as a result of an eq uipment malfunction, an equipment start-up or

shutdown, or during the performance of necessary equipment maintenance; and

ii. The affirmative defense is asserted and established as required by N.J.S.A. 26:2C-19.1 through

19.5 and any implementing rules. [N.J.A.C. 7:27-22.16(l)]

16. Each permittee shall meet all requirements of the approved source emissions testing and monitoring

protocol during the term of the operating permit. N.J.A.C. 7:27-22.18(j)]

The following paragraphs of this section are included for the permittee's convenience to remind them of their

obligations with certain key applicable requirements. These paragraphs are not enforceable since they paraphrase

areas of the operating permits rule. Also, these paragraphs do not reference all the applicable requirements with

which the permittee must comply.

17. Each owner and each operator of any facility, source operation, or activity to which this permit applies is

responsible for ensuring compliance with all requirements of N.J.A.C. 7:27-22. If the owner and operator

are separate persons, or if there is more than one owner or operator, each owner and each operator is jointly

and severally liable for any fees due under N.J.A.C. 7:27-22, and for any penalties for violation of N.J.A.C.

7:27-22.

18. In the event of a challenge to any part of this operating permit, all other parts of the permit shall continue to

be valid.

19. The permittee shall ensure that no air contaminant is emitted from any significant source operation at a rate,

calculated as the potential to emit, that exceeds the app licable threshold for reporting emissions set forth in

the Appendix to N.J.A.C. 7:27-22, unless emission of the air contaminant is authorized by this operating

permit.

20

. Consistent with the provisions of N.J.A.C. 7:27-22.3(e), the permittee shall ensure that all requirements of

this operating permit are met. In the event that there are multiple emission limitations, monitoring,

recordkeeping, and/or reporting requirements for a give n source operation, the facility must comply with all

requirements, including the most stringent.

21. Consistent with the provisions of N.J.A.C. 7:27-22.9(c), the permittee shall use monitoring of operating

parameters, where required by the compliance plan, as a surrogate for direct emissions testing or

monitoring, to demonstrate compliance with applicable requirements.

22. The permittee shall file a timely and complete application for:

Administrative Amendments;

Seven-Day-Notice changes;

Minor Modifications;

Significant Modifications; and

Renewals.

23. Process monitors must be operated at all times wh en the associated process equipment is operating except

during outage time allowed by Department guidelines/procedures or as outlined in Technical Manual 1005.

The permittee must keep a service log as required.

# Revision 4.3

1/19/10 

# Section F

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

STATE-ONLY APPLI CABLE REQUIREMENTS

N.J.A.C. 7:27-22.16(b)5 requires the Department to specifi cally designate as not being federally enforceable any

permit conditions based only on applicable state requirements. The applicable state requirements to which this

provision applies are listed in the table titled “State-Only Applicable Requirements.”

STATE-ONLY APPLICABLE REQUIREMENTS

The following applicable requirements are not federally enforceable:

SECTION SUBJECT ITEM ITEM # REF. #

E --- 15 ---

G FC --- 3

G FC --- 9

G FC --- 16

# Revision 4.3

1/19/10 

# Section G

Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

COMPLIANCE PLAN AND INVENTORIES

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

• FACILITY SPECIFIC REQUIREMENTS (COMPLIANCE PLAN)

• FACILITY PROFILE (ADMINISTRATIVE INFORMATION)

• REASON FOR APPLICATION

• NON-SOURCE FUGITIVE EMISSIONS

• INSIGNIFICANT SOURCE EMISSIONS

• EQUIPMENT INVENTORY

• EQUIPMENT DETAILS

• CONTROL DEVICE INVENTORY

• CONTROL DEVICE DETAILS

• EMISSION POINT INVENTORY

• EMISSION UNIT/BATCH PROCESS INVENTORY

• SUBJECT ITEM GROUP INVENTORY

# Revision 4.3

1/19/10 

# Facility Name: WHEELABRATOR GLOUCESTER COMPANY L P

Program Interest Number: 55793

Permit Activity Number: BOP090002

FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

Subject Item and Name Page Number

Facility (FC) :

FC 1

Non-Source Fugitive Emissions (FG):

FG1 –Facility Roadways 5

Insignificant Sources (IS):

IS2 –350-Gallon Fire Engine Diesel Storage Tank 6

IS3 –550-Gallon Vehicle Refueling Diesel Storage Tank 7

IS4 –1,960-Gallon Hydrochloric Acid Storage Tank 8

IS5 –1,700-Gallon Sodium Hydroxide Storage Tank 9

IS6 –Cold Cleaner Degreaser (Top Opening<6 Square Feet) 10

IS7 –Lubricating Oil Storage Vessel 14

IS8 –Small Combustion Sources (<1 MMBTU/hr) 16

IS9 –10,000-Gallon Phosphoric Acid Tank 17

Subject Item Group (GR):

GR1 – Equipment Subject to NSPS General Provisions 10

Emission Unit (U):

U1 – Two 287.5 Ton/day, 108 MMBTU/hr Municipal Solid Waste (MSW)

Fired Combustors (E1 and E2) 28

U2 1.7 MMBtu/hr Diesel Fire Pump (E6) 94

U3 –4,380 ton/year Lime Silo (E3) - OS Summary 98

U4 –Secondary Ash Conditioning Equipment 101

U5 – Ash and Metals Loadout Building 104New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:FCRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1General Provisions: Defines numerous termsused in N.J.A.C. 7:27. Specifies proceduresfor making confidentiality claims, certifyingapplications, reports, and other documentsto the Department, and requestingadjudicatory hearings and stays of theeffective date of departmental decisions.Also, provides provisions regardingapplicability, severability, and liberalconstruction of N.J.A.C. 7:27. [N.J.A.C.7:27- 1]None.None.None.2Control and Prohibition of Open Burning:Prohibits any person from open burning ofrubbish, garbage, trade waste, buildings,structures, leaves, other plant life andsalvage. Open burning of infested plant lifeor dangerous material may only beperformed with a permit from theDepartment. [N.J.A.C. 7:27- 2]None.None.Obtain an approved permit: Prior tooccurrence of event (prior to open burning).[N.J.A.C. 7:27- 2]3Prohibition of Air Pollution:Notwithstanding compliance with othersubchapters of N.J.A.C. 7:27, no personshall suffer, allow, or permit to be emittedinto the outdoor atmosphere substances inquantities that resultin air pollution asdefined at N.J.A.C. 7:27-5.1. Applicable toall facilities located in New Jersey.[N.J.A.C. 7:27- 5]None.None.None.4Prevention and Control of Air PollutionControl Emergencies: Requires that writtenStandby Plans, consistent with goodindustrial practice and safe operatingprocedures, be prepared for reducing theemission of air contaminants during periodsof an air pollution alert, warning, oremergency. Any person responsible for theoperation of a source of air contaminationnot set forth in Table 1 of N.J.A.C. 7:27-12is not required to prepare such a plan unlessrequested by the Department in writing.[N.J.A.C. 7:27-12]None.None.Comply with the requirement: Uponoccurrence of event. Upon proclamation bythe Governor of an air pollution alert,warning, or emergency, the permittee shallput the Standby Plan into effect. In addition,the permittee shall ensure that all of theapplicable emission reduction objectives ofN.J.A.C. 7:27-12.4, Table I, II, and III arecomplied with whenever there is an airpollution alert, warning, or emergency.[N.J.A.C. 7:27-12]Page 1 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Emission Offsets Rules. [N.J.A.C. 7:27-18]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Comply with the requirement: Uponoccurrence of event. Submit anadministratively complete application whenapplying for a minor modification pursuantto N.J.A.C. 7:27-22.23 or a significantmodification pursuant to N.J.A.C.7:27-22.24. [N.J.A.C. 7:27-22]6Emissions Statements: Submit an annualemission statement (if required)electronically to the NJDEP by May 15 ofeach year (or by mutually agreedupon date,but no later than June 15 of each year).[N.J.A.C. 7:27-21]Other: The emission statement will be basedon monitoring, recording and recordkeepingof actual emissions, capture and controlefficiencies, process rate and operating datafor source operations with the potential toemit certain air contaminants. [N.J.A.C.7:27-21].Other: The emission statement and allsupporting records shall be maintained onthe operating premises for a period of five(5) years from the due date of each emissionstatement. [N.J.A.C. 7:27-21].Submit an Annual Emission Statement:Annually (if required) electronically by May15 or by any mutually agreed upon date, butnot later than June 15 of each year.[N.J.A.C. 7:27-21]7Compliance Certification: Submit annualcompliance certification for each applicablerequirement, pursuant to N.J.A.C.7:27-22.19(f), within 60 days after the endof each calendar year during which thispermit was in effect. [N.J.A.C. 7:27-22]None.None.Submit an Annual Compliance Certification:Annually to the Department and EPA onforms provided by the Department within 60days after the end of each calendar yearduring which this permit was in effect. Theannual compliance certification reportingperiod will cover the calendar year endingDecember 31. Forms provided by theDepartment can be found on theDepartment's web site at the following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]8Prevention of Air Pollution fromArchitectural Coatings and ConsumerProducts. [N.J.A.C. 7:27-23]None.None.None.9Any operation of equipment which causesoff-property effects, including odors, orwhich might reasonably result in citizen'scomplaints shall be reported to theDepartment to the extent required by the AirPollution Control Act, N.J.S.A.26:2C-19(e). [N.J.S.A. 26:2C-19(e)]Other: Observation of plant operations.[N.J.S.A. 26:2C-19(e)].Other: Maintain a copy of all informationsubmitted to the Department. [N.J.S.A.26:2C-19(e)].Notify by phone: Upon occurrence of event.A person who causes a release of aircontaminants in a quantity or concentrationwhich poses a potential threat to publichealth, welfare or the environment or whichmight reasonably result in citizen complaintsshall immediately notify the Department.Such notification shall be made by callingthe Environmental Action Hotline at (877)927-6337. [N.J.S.A. 26:2C-19(e)]Page 2 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10Prevention of Significant Deterioration(PSD). [40 CFR 52.21]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Comply with the requirement: Uponoccurrence of event. If subject to PSD, thepermittee shall submit an administrativelycomplete application when applying for asignificant modification pursuant toN.J.A.C. 7:27-22.24. [N.J.A.C. 7:27-22]11National Emission Standards for HazardousAir Pollutants (NESHAPS) for Asbestos.[40 CFR 61]Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 61.145 and 61.150when conducting any renovation ordemolition activities at the facility. [40 CFR61]12Protection of Stratospheric Ozone:1) If thepermittee manufactures, transforms,destroys, imports, or exports a Class I orClass II substance, the permittee is subjectto all the requirements as specified at 40CFR 82, Subpart A; 2) If the permitteeperforms a service on motor "fleet" vehicleswhen this service involves an ozonedepleting substance refrigerant (or regulatedsubstance) in the motor vehicle airconditioner (MVAC), the permittee issubject to all the applicable requirements asspecified at 40 CFR 82, Subpart B. 3) Thepermittee shall comply with the standardsfor labeling of products containing ormanufactured with ozone depletingsubstances pursuant to 40 CFR 82, SubpartE. 4). The permittee shall comply with thestandards for recycling and emissionreductions of Class I and Class IIrefrigerants or a regulated substitutesubstance during the service, maintenance,repair, and disposal of appliances pursuantto 40 CFR 82, Subpart F, except as providedfor motor vehicle air conditioners (MVACs)in Subpart B. 5) The permittee shall beallowed to switch from any ozone depletingsubstance to any alternative that is listed inthe Significant New Alternative Program(SNAP) promulgated pursuant to 40 CFR82, Subpart G. [40 CFR 82]Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 82 Subparts A, B, E,F, and G. [40 CFR 82]Page 3 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement13Deviation Report: In accordance withN.J.A.C. 7:27-22.19(c) and 22.19(d)3, thepermittee shall submit to the Department, onforms provided by the Department, acertified six-month deviation report relatingto testing and monitoring required by theoperating permit, not including informationfor stack emissions testing or continuousemissions monitoring which have otherreporting schedules specified in the permit(normally, stack test report is submittedwithin 45 days of test completion andcontinuous monitor reporting is donequarterly). Pursuant to N.J.A.C.7:27-22.19(e), the six-month report mustaddress other specified monitoring,including continuous and periodicmonitoring requirements found in column 2and 3, entitled "Monitoring Requirement"and "Recordkeeping Requirement,"respectively, of the Facility SpecificRequirements section of this permit. Thesesix-month reports shall clearly identify alldeviations from operating permitrequirements, the probable cause of suchdeviations, and any corrective actions orpreventive measures taken. If no deviationsoccurred, the report should say so. Any"None" listed in the Submittal/ActionRequirement in the Operating Permit is notintended to override the six-month deviationreport. [N.J.A.C. 7.27-22.19(d)3, N.J.A.C.7.27-22.19(e), and [N.J.A.C. 7:27-22.19(c)]None.Other: The permittee shall maintaindeviation reports for a period of five yearsfrom the date each report is submitted to theDepartment. [N.J.A.C. 7:27-22.19(a)].Submit a report: As per the approvedschedule. The six-month reports for otherspecified testing or monitoring required bythe operating permit performed fromJanuary 1 through June 30 shall besubmitted by July 30 of the same calendaryear, and from July 1 through December 31,shall be submitted by January 30 of thefollowing calendar year. The report shall besubmitted to the Regional EnforcementOffice and shall be certified pursuant toN.J.A.C. 7:27-1.39 by the responsibleofficial. Forms provided by the Departmentcan be found on the Department's web site atthe following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]14No person shall combust used oil except asauthorized pursuant to N.J.A.C. 7:27-20.[N.J.A.C. 7:27-20.2]None.None.Comply with the requirement: Prior tooccurrence of event (prior to burning usedoil) either register with the Departmentpursuant to N.J.A.C. 7:27-20.3 or obtain apermit issued by the Department pursuantto N.J.A.C. 7:27-8 or 7:27-22, whichever isapplicable. [N.J.A.C. 7:27-20.2(d)]Page 4 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15Prevention of Accidental Releases: Facilitiesproducing, processing, handling or storing achemical, listed in the tables of 40 CFR Part68.130, and present in a process in aquantity greater than the listed ThresholdQuantity, shall comply with 40 CFR 68. [40CFR 68]Other: Comply with 40 CFR 68. [40 CFR68].Other: Comply with 40 CFR 68. [40 CFR68].Other (provide description): Other. Complywith 40 CFR 68 as described in theApplicable Requirement. [40 CFR 68]16For equipment subject to CO2 BudgetTrading Program, comply with N.J.A.C.7:27C. [N.J.A.C. 7:27C]Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Comply with the requirement: Uponoccurrence of event. [N.J.A.C. 7:27C]Page 5 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:FG1 Facility RoadwaysRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1There are no additional applicablerequirements for this subject item. [N.J.A.C.7:27-22.16(a)]None.None.None.Page 6 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS2 350 Gallon Fire Diesel Engine Diesel Storage TankRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Maximum allowable sulfur content indistillate fuel by viscosity and geographicallocation (Gloucester County, Zone 3) .Sulfur Content in Fuel <= 0.2 % by weight.[N.J.A.C. 7:27- 9.2(a)]Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery, basedon an instantaneous determination. Thepermittee shall review the certificate ofanalysis from the oil distributor for fuel oilsulfur content. [N.J.A.C. 7:27-22.16(o)]None.None.Page 7 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS3 550 Gallon Vehicle Refueling Diesel Storage TankRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Maximum allowable sulfur content indistillate fuel by viscosity and geographicallocation (Gloucester County, Zone 3).Sulfur Content in Fuel <= 0.2 % by weight.[N.J.A.C. 7:27- 9.2(a)]Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery, basedon an instantaneous determination. Thepermittee shall review the certificate ofanalysis from the oil distributor for fuel oilsulfur content. [N.J.A.C. 7:27-22.16(o)]None.None.Page 8 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS4 1,960 Gallon Hydrochloric Acid Storage TankRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Opacity <= 20 % exclusive of visible watervapor, except for 3 minutes in anyconsecutive 30 minute period. [N.J.A.C.7:27-6.2(d)]&. [N.J.A.C. 7:27- 6.2(e)]None.None.None.Page 9 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS5 1,700 Gallon Sodium Hydroxide Storage TankRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Opacity <= 20 % exclusive of visible watervapor, except for 3 minutes in anyconsecutive 30 minute period. [N.J.A.C.7:27-6.2(d)]&. [N.J.A.C. 7:27- 6.2(e)]None.None.None.Page 10 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS6 Cold Cleaner Degreaser (top opening < 6 square feet, Capacity<100 gallons)Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Applicable requirement when VOC is usedin degreaser: The machine shall have (1) afreeboard ratio of 0.75 or greater and (2) avisible fill line and high level liquid mark.(Updated requirement added as part ofmodification BOP060001.) [N.J.A.C.7:27-16.6(j)1i]None.None.None.2Applicable requirement when VOC is usedin degreaser: The machine shall have: apermanent, conspicuous label placed in aprominent location on the machine settingforth the applicable provisions of theoparating requirements in N.J.A.C.7:27-16.6(j)2. (Updated requirement addedas part of modification BOP060001.)[N.J.A.C. 7:27-16.6(j)1ii]None.None.None.3Applicable requirement when VOC is usedin degreaser: The machine shall beequipped with a tightly fittingworking-mode cover that completly coversthe machine's opening and that shal be keptclosed at all times except when parts arebeing placed into or being removed from themachine or when solvent is being added orremoved. For a remote reservoir coldcleaning machine which drains directly intothe solvent storage reservoir, a perforateddrain with a diameter or not more than sixinches shall constitue an acceptable cover.(Updated requirement added as part ofmodification BOP060001.) [N.J.A.C.7:27-16.6(j)1iii]None.None.None.4Applicable requirement when VOC is usedin degreaser: The solvent level in themachine shall not exceed the fill line whenthere are no parts in the machine forcleaning and shall not exceed the high levelliquid mark during cleaning operations.(Updated requirement added as part ofmodification BOP060001.) [N.J.A.C.7:27-16.6(j)2i]None.None.None.Page 11 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Applicable requirement when VOC is usedin degreaser: Flushing of parts with asolvent spray, using a spray head attached toa flexible hose or other flushing device,shall be performed only within the freeboardare of the machine. The solvent spray shallbe a continuous fluid stream not anatomized or shower spray, and shall beunder a pressure that does not exceed tenpounds per square inch gauge. (Updatedrequirement added as part of modificationBOP060001.) [N.J.A.C. 7:27-16.6(j)ii]None.None.None.6Applicable requirement when VOC is usedin degreaser: Parts being cleaned shall bedrained for at least 15 seconds or untildripping ceases, whichever is longer. Partshaving cavities or blind holes shall be tippedor rotated while the part is draining. Duringthe draining, tipping or rotating, the partsshall be positioned so that solvent drainsdirectly back into the machine. (Updatedrequirement added as part of modificationBOP060001.) [N.J.A.C. 7:27-16.6(j)2iii]None.None.None.7Applicable requirement when VOC is usedin degreaser: When the machine's cover isopen, the machine shall not be exposed todrafts greater than 40 meters per minute(132 feet per minute) as measured betweenone and two meters (between 2.2 and 6.6feet) upwind and a the same elevation as thetank lip. (Updated requirement added aspart of modification BOP060001.) [N.J.A.C.7:27-16.6(j)2iv]None.None.None.8Applicable requirement when VOC is usedin degreaser: Sponges, fabric, leather, paperproducts and other adsorbent materials shallnot be cleaned in the machine. (Updatedrequirement added as part of modificationBOP060001.) [N.J.A.C. 7:27-16.6(j)2v]None.None.None.Page 12 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9Applicable requirement when VOC is usedin degreaser: When a pump-agitated solventbath is used, the agitator shall be operated toproduce a rolling motion of the solvent withno observable splashing of solvent againstthe tank walls or the parts being cleaned.Air agitated solvent baths may not be used.(Updated requirement added as part ofmodification BOP060001.) [N.J.A.C.7:27-16.6(j)2vi]None.None.None.10Applicable requirement when VOC is usedin degreaser: Spills during solvent transferand use of the machine shall be cleaned upimmediately, and the wipe rags or othersorbent material used shall be immediatelystored in covered containers for disposal orrecycling. (Updated requirement added aspart of modification BOP060001.) [N.J.A.C.7:27-16.6(j)2vii]None.None.None.11Applicable requirement when VOC is usedin degreaser: Waste solvent shall becollected and stored in a closed container.The closed container may contain a devicethat allows pressure relief, provided that itdoes not allow liquid solvent to drain fromthe container. (Updated requirement addedas part of modification BOP060001.)[N.J.A.C. 7:27-16.6(j)2viii]None.None.None.12Applicable requirement when VOC is usedin degreaser: Work area fans shall belocated and positioned so that they do notblow across the opening of the degreaserunit. (Updated requirement added as part ofmodification BOP060001.) [N.J.A.C.7:27-16.6(j)2ix]None.None.None.13Applicable requirement when VOC is usedin degreaser: No person shall use anysolvent that has a vapor pressure of onemillimeter of mercury or greater, measuredat 20 degrees centigrade (68 degreesFahrenheit). (Updated requirement added aspart of modification BOP060001.) [N.J.A.C.7:27-16.6(j)3]None.None.None.Page 13 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement14Applicable requirement when VOC is usedin degreaser: The permittee shall maintainthe following information:i. The name and address of the personselling the solvent. Aninvoice, bill of sale,or a certificate that corresponds to a numberof sales, if it has the seller's name andaddress on it, may be used to satisfy thisrequirement.ii. A list of VOC(s) and their concentrationinformation in the solvent.iii. Information abouteach VOC pursuant toii above. A Material Safety Data Sheet(MSDS) may be used to satisfy thisrequirement.iv. The solvents product number assigned bythe manufacturer.v. The vapor pressure of the solventmeasured in millimeters of mercury at 20degrees centigrade (68 degrees Fahrenheit).(Updated requirement added as part ofmodification BOP060001.) [N.J.A.C.7:27-16.6(j)4]None.None.None.15The top opening shall be less than 6 squarefeet or the capacity less than 100 gallons, orthe degreaser shall use less than 5% VOC,HAPs, or VOC and HAPs combined.[N.J.A.C. 7:27-22.1]Other: Monitored by formulation data at theapproved frequency, based on no averagingperiod. At the time of filling, confirm byMSDS or bill of lading.[N.J.A.C.7:27-22.16(o)].Other: Recordkeeping by invoices/bills oflading, or Material Safety Data Sheets at theapproved frequency (per filling, showingmaterials being delivered).[N.J.A.C.7:27-22.16(o)].None.16No halogenated solvents are to be used inthis equipment. [N.J.A.C. 7:27-22.16(a)]Other: Monitored by formulation data at theapproved frequency, based on no averagingperiod. At the time of filling, confirm byMSDS or bill of lading.[N.J.A.C.7:27-22.16(o)].Other: Recordkeeping by invoices/bills oflading at the approved frequency (per filling,showing materials beingdelivered).[N.J.A.C. 7:27-22.16(o)].None.Page 14 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS7 Lubricating Oil Storage VesselRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1The operating temperature shall not begreater than 350 degrees F. [N.J.A.C.7:27-22.1]None.None.None.2The vapor pressure of the liquid, excludingthe vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]None.None.None.3The tank shall have no visible emissions,exclusive of water vapor, to the outdooratmosphere. [N.J.A.C. 7:27-22.1]None.None.None.4The tank shall not emit any air contaminantswhich may cause an odor detectable outsidethe property boundaries of the facility.[N.J.A.C. 7:27-22.1]None.None.None.5The tank shall not qualify for anyNESHAPS, MACT, or NSPS air pollutioncontrol standards, excluding the NSPSrequirements to maintain a record of thecontents of the tank, the period of storage ofthese contents, and the maximum true vaporpressure of the liquid stored. [N.J.A.C.7:27-22.1]None.None.None.6The tank's potential to emit each TXS andeach HAP shall not exceed the de minimisreporting thresholds as specified in N.J.A.C.7:27-22, Appendix. [N.J.A.C. 7:27-22.1]None.None.None.7The percentage by weight of all HAPscollectively in the raw material stored in thetank shall be less than 1.0 percent. [N.J.A.C.7:27-22.1]None.None.None.Page 15 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8The owner or operator shall have readilyavailable upon Department request astatement certified in accordance withN.J.A.C. 7:27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank meets theapplicable requirements of Ref. #1 to #7above and (3) attests that the tank is incompliance with all other applicable State orfederal air pollution requirements. [N.J.A.C.7:27-22.1]None.None.None.Page 16 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS8 Small Combustion Sources (<1 MMBtu/hr) Using Natural GasRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1No visible emissions. As specified inN.J.A.C. 7:27-3.2(c), this provision does notapply to smoke which is visible for a periodof time of not longer than three (3) minutesin any consecutive 30-minute period.[N.J.A.C. 7:27-3.2(a)]& [N.J.A.C. 7:27-3.2(c)]None.None.None.Page 17 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:IS9 Phosphoric Acid Tank (Non-VOC storage tank with capacity less than 10,000 gallons)Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Opacity <= 20 % exclusive of visible watervapor, except for 3 minutes in anyconsecutive 30 minute period. [N.J.A.C.7:27-6.2(d)]&. [N.J.A.C. 7:27- 6.2(e)]None.None.None.Page 18 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Subject Item:GR1 Equipment Subject to NSPS Subpart A General ProvisionsRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): All requests,reports, applications,submittals, and othercommunications to the Administratorpursuant to Part 60 shall be submitted induplicate to the Regional Office of USEnvironmental Protection Agency. Submitinformation to: Region II, Director, Air andWaste Management Division, USEnvironmental Protection Agency, 21stFloor, 290 Broadway, New York, NY10007. [40 CFR 60.4(a)]None.None.Submit a report: As per the approvedschedule to EPA Region II as required by 40CFR 60. [40 CFR 60.4(a)]2For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): Copies of allinformation submitted to EPA pursuant to40 CFR Part 60, must also be submitted tothe Southern Regional Enforcement Officeof NJDEP at One Port Center, 2 RiversideDrive Suite 201, Camden NJ 08102. [40CFR 60.4(b)]None.None.Submit a report: As per the approvedschedule to the Southern RegionalEnforcement Office of NJDEP as requiredby 40 CFR 60. [40 CFR 60.4(b)]Page 19 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): The owner oroperator subject to the provisions of 40 CFRPart 60 shall furnish the Administratorwritten notification or, if acceptable to boththe Administrator and the owner or operatorof a source, electronic notification, of anyphysical or operational change to an existingfacility which may increase the emission rateof any air pollutant to which a standardapplies, unless that change is specificallyexempted under an applicable subpart or insection 60.14(e). The notification shallinclude information describing the precisenature of the change, present and proposedemission control systems, productivecapacity of facility before and after thechange and the expected completion date ofthe change. Notification shall be postmarkedwithin 60 days or as soon as practicablebefore any change is commenced. TheAdministrator may request additionalrelevant information subsequent to thisnotice. [40 CFR 60.7(a)(4)]None.None.Submit notification: Upon occurrence ofevent to EPA Region II and the SouthernRegional Enforcement Office of NJDEP asrequired by 40 CFR 60.7. [40 CFR60.7(a)(4)]4For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): The owner oroperator shall maintain records of theoccurrence and duration of any startup,shutdown, or malfunction in the operation ofan affected facility, any malfunction of airpollution control equipment or any periodsduring which continuous monitoring systemor monitoring device is inoperative. [40CFR 60.7(b)]None.Recordkeeping by manual logging ofparameter upon occurrence of event in apermanently bound logbook or by electronicdata storage in readily accessible computermemories upon occurrence of event. Therecords should be kept in a permanent formsuitable for inspections. [40 CFR 60.7(b)]None.Page 20 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCMS requirements (E1 and E2): Each owneror operator required to install a continuousmonitoring device shall submit an excessemissions and monitoring systemsperformance report (excess emissions aredefined in applicable subparts) and/or asummary report form (see section 60.7(d))to the Administrator semiannually, exceptwhen: more frequent reporting isspecifically required by an applicablesubpart; or the Administrator, on acase-by-case basis, determines that morefrequent reporting is necessary to accuratelyassess the compliance status of the source.All reports shall be postmarked by the 30thday following the end of each six-monthperiod. [40 CFR 60.7(c)]None.None.Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Semi-annually beginning on the30th day of the 6th month following initialperformance tests. The report shall bepostmarked by the 30th day following theend of each six-month period. The reportshall be submitted to the EPA Region IIAdministrator and the Southern RegionalEnforcement Office of NJDEP and be in theformat specified at 40 CFR Part 60.7(c) and40 CFR Part 60.7(d). Written reports ofexcess emissions shall include the followinginformation: (1) The magnitude of excessemissions computed in accordance withsection 60.13(h), any conversion factor(s)used, and the date and time ofcommencement and completion of each timeperiod and excess emissions. The processoperating time during the reporting period.(2) Specific identification of each period ofexcess emissions that occurs during startups,shutdowns, and malfunctions of the affectedfacility. The nature and cause of anymalfunction (if known), the corrective actiontaken or preventative measures adopted. (3)The date and time identifying each periodduring which the continuous monitoringsystem was inoperative except for zero andspan checks and the nature of the systemrepairs or adjustments. (4) When no excessemissions have occurred or the continuousmonitoring system(s) have not beeninoperative, repaired, or adjusted, suchinformation shall be stated in the report. [40CFR 60.7(c)]Page 21 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): The owner oroperator shall maintain a file, suitable forinspection, of all monitoring measurementsas indicated in Recordkeeping Requirementcolumn. [40 CFR 60.7(f)]None.Other: The file shall include allmeasurements (including continuousmonitoring system, monitoring device, andperformance testing measurements), allcontinuous monitoring system performanceevaluations, all continuous monitoringsystem or monitoring device calibrationchecks, all adjustments/maintenanceperformed on these systems or devices, andall other information required by 40 CFRPart 60 recorded in a permanent formsuitable for inspection. [40 CFR 60.7(f)].None.7For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): The owner oroperator shall conduct performance tests anddata reduced in accordance with the testmethods and procedures contained ineachapplicable subpart, unless otherwisespecified and approved by theAdministrator. [40 CFR 60.8(b)]None.None.None.8For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): Performancetests shall be conducted under conditions theAdministrator specifies to the plant operatorbased on representative performance of theaffected facility. Operations during periodsof startup, shutdown and malfunction shallnot constitute representative conditions forthe purpose of the performance test nor shallemissions in excess of the level of theapplicable emission limit be considered aviolation of the applicable emission limitunless otherwise specified in the applicablestandard. [40 CFR 60.8(c)]None.None.None.9For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): The owner oroperator shall provide the Administrator atleast 30 days prior notice of anyperformance test and shall provide adequateperformance testing facilities as specified in40 CFR Part 60.8(e). [40 CFR 60.8(d)]None.None.None.Page 22 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7and E8): Unlessotherwise specified in the applicablesubpart,each performance test shall consistof three separate runs using the applicabletest method. [40 CFR 60.8(f)]None.None.None.11For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFperformance tests for standards other thanopacity (E1 and E2): Compliance withNSPS standards specified in this permit,other than opacity, shall be determined onlyby performance tests established by 40 CFR60.8, unless otherwise specified in NSPS.[40 CFR 60.11(a)]None.None.None.12For equipment required to conduct visualopacity tests pursuant to 40 CFR 60,Subpart Cb and 40 CFR 62, Subpart FFF(E1, E2, E3, E5, E7 and E8): The owner oroperator shall demonstrate compliance withNSPS opacity standards specified in 40 CFRPart 60. [40 CFR 60.11(b)]Monitored by visual determination annually,based on 6 minute blocks. Testing shall beconducted using Reference Method 9 inAppendix A of NSPS. [40 CFR 60.11(b)]Recordkeeping by manual logging ofparameter annually. The owner or operatorshall maintain records of opacity ofemissions based on Method 9 observations.[40 CFR 60.11(e)(2)]Submit a report: Annually. The owner oroperator shall submit results of Method 9observation data to the Administrator. [40CFR 60.11(e)(2)]13For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCOM requirements (E1 and E2): The owneror operator shall demonstrate compliancewith NSPS opacity standards specified in 40CFR Part 60. [40 CFR 60.11(b)]Monitored by continuous opacity monitorcontinuously, based on 6 minute blocks. [40CFR 60.11(b)]Recordkeeping by strip chart, round chart ordata acquisition (DAS) system / electronicdata storage continuously. [40 CFR60.13(h)]Submit a report: At a common scheduleagreed upon by the operator and theAdministrator. The owner or operator shallsubmit Continuous Opacity MonitoringSystem (COMS) data produced during anyperformance test in lieu of Method 9 data.The owner or operator shall notify theAdministrator in writing of intent todemonstrate compliance using COMS dataat least 30 days before any performancerequired under 40 CFR Part 60.8 isconducted and shall follow proceduresoutlined in 40CFR Part 60.11(e). [40 CFR60.11(e)(5)]14For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): The NSPSopacity standard shall apply at all timesexcept during periods of startup, shutdown,malfunctions and as otherwise specified inthis permit. [40 CFR 60.11(c)]None.None.None.Page 23 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): At all times,including periods of start-up, shutdown, andmalfunction, owners and operators shall, tothe extent practicable, maintain and operateany affected facility including associated airpollution control equipment in a mannerconsistent with good air pollution controlpractice for minimizing emissions.Determination of whether acceptableoperating and maintenance procedures arebeing used will be based on informationavailable to the Administrator which mayinclude, but is not limited to, monitoringresults, opacity observations, review ofoperation and maintenance procedures, andinspection of the source. [40 CFR 60.11(d)]None.None.None.16For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): No owner oroperator subject to NSPS standards in Part60, shall build, erect, install, or use anyarticle, machine, equipment or process, theuse of which conceals an emission whichwould otherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to the atmosphere.[40 CFR 60.12]None.None.None.17For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCEM requirements (E1 and E2): The owneror operator shall perform zero and spanadjustments daily for continuous emissionmonitors and continuous opacity monitorsfollowing procedures outlined in 40 CFRPart 60.13(d)1 & 2. [40 CFR 60.13(d)]None.None.None.Page 24 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement18For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCOM requirements (E1 and E2): Except forsystem breakdowns, repairs, calibrationchecks, and zero and span adjustments, allcontinuous opacity monitoring systems shallbe in continuous operation. They shallcomplete a minimum of one cycle ofsampling and analyzing for each successive10-second period and one cycle of datarecording for each successive 6-minuteperiod. [40 CFR 60.13(e)(1)]None.None.None.19For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCEM requirements (E1 and E2): Except forsystem breakdowns, repairs, calibrationchecks, and zero and span adjustments, allcontinuous monitoring systems measuringemissions except opacity shall be incontinuous operation. They shall completea minimum of one cycle of operation(sampling, analyzing and data recording) foreach successive 15-minute period. [40 CFR60.13(e)(2)]None.None.None.20For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCMS requirements (E1 and E2): Allcontinuous monitoring systems ormonitoring devices shall be installed suchthat representative measurements ofemissions or process parameters from theaffected facility are obtained. Proceduresfor location of continuous monitoringsystems contained in the applicablePerformance Specifications of Appendix Bof 40 CFR Part 60 shall be used. [40 CFR60.13(f)]None.None.None.Page 25 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement21For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCOM requirements (E1 and E2): The owneror operator shall reduce all continuousmonitoring systems for measuring opacitydata to 6-minute averages which shall becalculated from 36 or more data pointsequally spaced over each 6-minute period.Data recorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmetic orintegrated average of all data may be used.The data may be recorded in reduced ornonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]None.None.None.Page 26 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement22For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFFCEM requirements (E1 and E2): The owneror operator shall reduce all continuousmonitoring systems (other than opacity) datato 1-hour averages which shall be computedfrom four or more data points equallyspaced over each 1-hour period. Datarecorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmetic orintegrated average of all data may be used.The data may be recorded in reduced ornonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]None.None.None.23For equipment subject to 40 CFR 60Subpart Cb and 40 CFR 62 Subpart FFF(E1, E2, E3, E5, E7 and E8): Changes intime periods for submittal of informationand postmark deadlines set forth in thissubpart, may be made only upon approvalby the Administrator and shall followprocedures outlined in 40 CFR Part 60.19.[40 CFR 60.19]None.None.None.Page 27 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U1 Two 287.5 Ton Per Day, 108 MMBTU/hr Municipal Solid Waste (MSW) Fired Combustors (E1 and E2)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1STACK TESTING REQUIREMENTS:Conduct annual stack tests oneachmunicipal solid waste combustor todemonstrate compliance with the lead andcadmium emission limits. Stack testing is asrequired at 40 CFR 60.58b(d) and 40 CFR60.58b(f). [N.J.A.C. 7:27-22.16 (o)], [40CFR 60.39b(d)], [40 CFR 60.39(f)] & [40CFR 62.14109(b)]Monitored by stack emission testingannually, based on the average of three tests.Stack testing for lead and cadmium (usingEPA Method 29) shall be as required at 40CFR 60.58b(d)(1). [N.J.A.C. 22.16(o)],[40 CFR 60.39(d)], [40 CFR 60.39(f)] &.[40 CFR 62.14109(b)]Recordkeeping by stack test results annuallyAll records shall be maintained onsite ineither paper copy or computer-readableformat. This is as indicated in 40 CFR60.59b(d)(9)(i) and 40 CFR 60.59b(d)(k).[N.J.A.C. 7:27-22.16(o)], [40 CFR60.39b(d)], [40 CFR 60.39b(f)] &. [40 CFR62.14109(a)]Stack Test - Submit protocol, conduct testand submit results: Annually. The permitteemust contact BTS at 609-530-4041 toschedule a mutually acceptable test datewhich shall be no later than one year afterthe previous test. Stack test reports must besubmitted to BTS within 45 days afterperforming the stack test pursuant toN.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a New Jersey licensedprofessional engineer or certified industrialhygienist.A copy of all test results during the permitterm must be submitted with the operatingpermit renewal application due at least 12months prior to expiration of the OperatingPermit.Test results shall report lbs/hour.As indicated in 40 CFR 60.59b(g)(1), a listof the emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(d), 40 CFR 60.39b(f), and 40CFR 14109(a). [N.J.A.C. 7:27-22.18(e)],[N.J.A.C. 7:27-22.18(h)], [40 CFR60.39b(d)], [40 CFR 60.39b(f)], &. [40 CFR62.14109(a)]OS SummaryPage 28 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement2STACK TESTING REQUIREMENTS:Conduct annual stack testseach municipalsolid waste combustor to determinecompliance with HCl emission limits.[N.J.A.C. 7:27-22.16(e)], [40 CFR60.39b(f)] & [40 CFR 62.14109(b)]Monitored by stack emission testingannually, based on any 60 minute period todetermine compliance with emission limitspursuant to N.J.A.C. 7:27-22.16(e), and theaverage of three tests to determinecompliance with emission limits pursuant to40 CFR 60.39b(f) and 40 CFR62.14103(b)(2). Stack testing for HCl(using EPA Method 26 or 26A) shall satisfythe requirements at 40 CFR 60.58b(f).[N.J.A.C. 7:27-22.16(e)], 40 CFR 60.39b(f),&. [40 CFR 62.14109(b)]Recordkeeping by stack test results annuallyAll records shall be maintained onsite ineither paper copy or computer-readableformat. This is as indicated in 40 CFR60.59b(d)(9)(i) and 40 CFR 60.59b(d)(k).[N.J.A.C. 7:27-22.16(o)], [40 CFR60.39b(f)] &. [40 CFR 62.14109(a)]Stack Test - Submit protocol, conduct testand submit results: Annually. The permitteemust contact BTS at 609-530-4041 toschedule a mutually acceptable test datewhich shall be no later than one year afterthe previous test. Stack test reports must besubmitted to BTS within 45 days afterperforming the stack test pursuant toN.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a New Jersey licensedprofessional engineer or certified industrialhygienist.A copy of all test results during the permitterm must be submitted with the operatingpermit renewal application due at least 12months prior to expiration of the OperatingPermit.Test results shall report lbs/hour, lbs/MMBtu, ppm (as needed).As indicated in 40 CFR 60.59b(g)(1), a listof the emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(f) and 40 CFR 14109(a).[N.J.A.C. 7:27-22.18(e)], [N.J.A.C.7:27-22.18(h)], [40 CFR 60.39b(f)], &. [40CFR 62.14109(a)]Page 29 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3STACK TESTING REQUIREMENTS:Conduct annual stack tests fordioxins/furans. Total polychlorinateddibenzodioxins emissions and totalpolychlorinated dibenzofurans(dioxins/furans) must be measured usingEPA Reference Method 23. This is asindicated at 40 CFR 60.59b(g)(3). [N.J.A.C.7:27-22.16(o)], [40 CFR 60.39b(d)]& [40CFR 62.14109(b)]Monitored by stack emission testingannually, based on the average of three tests.The minumum sample time shall be 4 hoursper run, using EPA test Method 23 asspecified at 40 CFR 60.58b(g)(3). This is asspecified at 40 CFR 60.58b(g)(5), exceptthat: Where all performance tests over a2-year period indicate that dioxin/furanemissions are less than or equal to 15ng/dscm corrected to 7% O2 (total mass) forall units, the GCRRF may elect to conductannual performance tests in one unit peryear. At a minimum, a performance test fordioxin/furan emissions shall be conductedannually (no more than 12 months followingthe previous performance test) on one unit.Each year a different unit shall be tested,and the units shall be tested in sequence(e.g., unit 1, unit 2, unit 3). If each annualperformance test continues to indicate adioxin/furan emission level less than orequal to 15 ng/dscm (total mass), the facilitymay continue conducting a performance teston only one unit per year. If annualperformance test indicates a dioxin/furanemission level greater than 15 ng/dscmcorrected to 7% O2 (total mass),performance tests thereafter shall beconducted annually on all units until andunless all annual performance tests for allunits over a 2-year period indicate adioxin/furan emission level less than orequal to 15 ng/dscm corrected to 7% O2(total mass). [N.J.A.C. 7:27-22.16(o)], [40CFR 60.39b(d)], [40 CFR 62.14109(b)] &.[40 CFR 62.14109(d)(1)]Recordkeeping by stack test results annuallyAll records shall be maintained onsite ineither paper copy or computer-readableformat. This is as specified at 40 CFR60.59b(d)(9)(i) and 40 CFR 60.59b(k).[N.J.A.C. 22.16(o)], [40 CFR 60.39b(d)] &.[40 CFR 62.14109(a)]Stack Test - Submit protocol, conduct testand submit results: Annually. The permitteemust contact BTS at 609-530-4041 toschedule a mutually acceptable test datewhich shall be no later than one year afterthe previous test. Stack test reports must besubmitted to BTS within 45 days afterperforming the stack test pursuant toN.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a New Jersey licensedprofessional engineer or certified industrialhygienist.A copy of all test results during the permitterm must be submitted with the operatingpermit renewal application due at least 12months prior to expiration of the OperatingPermit.Test results shall report lbs/hour, lbs/MMBtu, ppm, ng/dscm (as needed). Emissionrates of each congener which contains 4 ormore chlorine atoms shall be reported.As indicated in 40 CFR 60.59b(g)(1), a listof the emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(d), 40 CFR 60.39b(f), and 40CFR 14109(a). [N.J.A.C. 7:27-22.16(o)],[N.J.A.C. 7:27-22.18(e)], [N.J.A.C.7:27-22.18(h)], [40 CFR 60.39b(d)], [40CFR 60.39b(f)], &. [40 CFR 62.14109(a)]Page 30 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4STACK TESTING REQUIREMENTS: Todetermine compliance with particulateemission limits, the Permittee shall annuallyperform on each municipal solid wastecombustor: i. Three test runs using EPAReference Method 5; ii. Three test runsusing the New Jersey Test Method forincinerators (as required by the test method,paticulate matter shall include solid andliquid particles, excluding water, collectedin the "front half" and the "back half" of thesampling train);iii. One separate test runconducted using EPA Reference Method 5during which boiler tube rapping isperformed. [N.J.A.C. 7:27-22.16(a)],[N.J.A.C. 7:27-22.6(e)], [40 CFR60.39b(d)]& [40 CFR 62.14109(b)]Monitored by stack emission testingannually, based on the average of three tests.Compliance with all TSP emission limits(except for the limit which stipuates boilertube rapping) pursuant to N.J.A.C.7:27-22.16(e) and 40 CFR 62.14103(a)(1)shall be determined by the average of thethree EPA Method 5 test runs indicated in(i) of the applicable requirement, as requiredin the preconstruction permit and 40 CFR60.58b(c). Compliance with the emissionlimit pusuant to N.J.A.C. 7:27-11 shall bedetermined from the average of the threeeruns indicated in (ii) of the applicablerequirement. Compliance with the limitstipulated under N.J.A.C. 7:27-22.16(e)when boiler tube rapping is performed shallbe determined by the test run indicated in(iii) of the applicable requirement. [N.J.A.C.7:27-22.16(e)], [40 CFR 60.39b(d)],&. [40CFR 62.14109(b)]Recordkeeping by stack test resultsannually. All records shall be maintainedonsite in either paper copy orcomputer-readable format. This is asspecified at 40 CFR 60.59b(d)(9)(i) and 40CFR 60.59b(k). [N.J.A.C. 22.16(e)], [40CFR 60.39b(d)] &. [40 CFR 62.14109(a)]Submit a stack test report: Annually. Thepermittee must contact BTS at609-530-4041 to schedule a mutuallyacceptable test date which shall be no laterthan one year after the previous test. Stacktest reports must be submitted to BTS within45 days after performing the stack testpursuant to N.J.A.C. 7:27-22.19(d). The testresults must be certified by a New Jerseylicensed professional engineer or certifiedindustrial hygienist.A copy of all test results during the permitterm must be submitted with the operatingpermit renewal application due at least 12months prior to expiration of the OperatingPermit.Test results shall report lbs/hour, lbs/MMBtu, ppm (as needed).As indicated in 40 CFR 60.59b(g)(1), a listof the emission levels achieved duringperformance tests shall be included in thesemi annual report submitted pursuant to 40CFR 60.39b(d), 40 CFR 60.39b(f), and 40CFR 14109(a). [N.J.A.C. 7:27-22.16(o)],[N.J.A.C. 7:27-22.18(e)], [N.J.A.C.7:27-22.18(h)], [40 CFR 60.39b(d)], [40CFR 60.39b(f)], &. [40 CFR 62.14109(a)]Page 31 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5STACK TESTING REQUIREMENTS: ForPt1 and Pt2, the owner or operator shallconduct stack tests oneach municipal solidwaste combustor to determine compliancewith the total PM-10 emission limit of 4.52lb/hr. Total PM-10 shall include bothfilterable and condensible catches from thetest. Testing must be conducted atworst-case permitted operating conditionswith regard to meeting the applicableemission standards, but without creating anunsafe condition. [N.J.A.C. 7:27-22.16(a)]Monitored by stack emission testingannually, based on the average of threeDepartment validated stack test runs. Whenconducting stack emission testing, aminimum of three test runs shall beconducted. [N.J.A.C. 7:27-22.16(o)]Recordkeeping by stack test resultsannually. Recordkeeping shall be donethrough test reports pursuant to N.J.A.C.7:27-22.19. [N.J.A.C. 7:27-22.16(o)]Submit a stack test report: As per theapproved schedule. The PM-10 testing shallbe performed using approved protocols. Forsubsequent annual tests the permittee mustcontact BTS to schedule a mutuallyacceptable test date which shall be no laterthan one year after the previous test. Thestack test report must be submitted to BTSand BOP within 45 days after performingthe stack test pursuant to N.J.A.C.7:27-22.19(d) unless an extension approvalis granted in advance in writing by theBureau of Technical Services. The testresults must be certified by a New Jerseylicensed professional engineer or certifiedindustrial hygienist. Test results shall reportgrains/dscf and lb/hr. As indicated in 40CFR 60. 59b(g)(1), a list of the emissionlevels achieved during performance testsshall be included in the semi annual report.[N.J.A.C. 7:27-22.18(h)]Page 32 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6STACK TESTING REQUIREMENTS: Thepermittee shall conduct stack emissiontesting for mercury on each municipal solidwaste combustor to satisfy the requirementsunder N.J.A.C. 7:27-22.16(e), N.J.A.C.7:27-27.4 and 40 CFR 60.58b(d)(2).[N.J.A.C. 7:27-22.16(e)], [N.J.A.C.7:27-27.4], [40 CFR 60.39b(d)], & [40 CFR62.14109(b)]Monitored by stack emission testingannually, based on the average of three testsusing EPA Reference Method 29. The testsfor mercury shall consist of three sourceemission tests to measure mercury in the gasstream at the inletof the air pollutioncontrol apparatus serving each combustionunit, and simultaneously perform threesource emission tests to measure mercury inthe gas stream at the exit of the controlapparatus. If source emission testing failsto demonstrate compliance with theapplicable requirement, then the frequencyof source testing shall increase to threesource emission tests quarterly. In this case,there shall be at least a 45 calendar dayinterval between the testing performed for agiven quarter and the testing performed forthe preceding quarter, unless a shorterperiod is approved by the Department. Ifcompliance with the applicable requirementis then achieved and maintained during twoconsecutive years, the permittee may againreduce the frequency of source emissiontesting from three source emission testsperformed quarterly to three source emissiontests performed in the first quarter of eachcalendar year. Testing shall also satisfy therequirements at 40 CFR 60. 58b(d)(2),which requires annual testing. [N.J.A.C.7:27-27.4(c)], [40 CFR 60.39b(d)]&. [40CFR 62.14109(b)]Recordkeeping by stack test results at theapproved frequency. All records shall bemaintained onsite in either paper copy orcomputer-readable format. This is asindicated in 40 CFR 60.59b(d)(9)(i) and 40CFR 60.59b(d)(k). [N.J.A.C.7:27-22.16(o)], [40 CFR 60.39b(d)], [40CFR 60.39b(f)] &. [40 CFR 62.14109(a)]Submit a stack test report: As per theapproved schedule. GCRRF shall submit acopy of the report of the results of each testconducted ateach unit within 60 days aftercompletion of the compliance testing forthat quarter to the Chief, BTS. [N.J.A.C.7:27-27.4(f)]Page 33 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7STACK TESTING REQUIREMENTS:Conduct comprehensive stack tests oneachmunicipal solid waste combustor at least 18months prior to the expiration of the renewaloperating permit to demonstrate compliancewith the SO2, nitrogen oxides, SO3 +H2SO4 (as converted and expressed asH2SO4), Volatile Organic Compounds(VOC), Arsenic, Beryllium, Chromium,Nickel, Ammonia, and TCDD (2,3,7,8-)emission limits. In addition, tests for Benzo(A) Pyrene emissions must be conducted.This is based on the preconstruction permit.[N.J.A.C. 7:27-22.16(a)]Monitored by stack emission testing prior topermit renewal, based on the average ofthree Department validated stack test runs.Unless otherwise approved in the stack testprotocol or by the Department, each test runshall be 60 minutes in sampling duration.Stack test shall be conducted for SO2, HCl,HF, nitrogen oxides, SO3+H2SO4 (asconverted and expressed as H2SO4), VOC,Ammonia, Arsenic, Beryllium, Chromium,Nickel, and TCDD (2,3,7,8-) emissionlimits. In addition, tests for Benzo (A)Pyrene emissions must be conducted. Thisis based on the preconstruction permit.[N.J.A.C. 7:27-22.16(o)]Recordkeeping by stack test results prior topermit renewal. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Submit a stack test protocol to theBureau of Technical Services (BTS) at POBox 437, Trenton, NJ 08625 at least 30months prior to the expiration of theapproved renewal permit. Within 30 days ofprotocol approval, the permittee mustcontact BTS at 609-530-4041 to schedule amutually acceptable test date. The stack testreport must be submitted to BTS within 45days after performing the stack test pursuantto N.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a New Jersey licensedprofessional engineer or certified industrialhygienist.A copy of the test results must be submittedwith the operating permit renewalapplication due at least 12 months prior tothe expiration of the Operating Permit.Test results shall reportlbs/hour,lbs/MMMtu, ppm (as needed).[N.J.A.C. 7:27-22.18(e)] &. [N.J.A.C.7:27-22.18(h)]Page 34 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8STACK TESTING REQUIREMENTS:Perform stack tests on each municipal solidwaste combustor at least 18 months prior tothe expiration of the approved operatingpermit renewal to demonstrate compliancewith the 4-hour CO and 1-hour HF emissionlimits. [N.J.A.C. 7:27-22.16(e)]Monitored by stack emission testing prior topermit renewal, based on each of threeDepartment validated stack test runs Unlessotherwise approved in the stack test protocolor by the Department, each test run shall be60 minutes in sampling duration. Tests shallbe conducted for HF and a 4-hour blockaverage for CO, using EPA Method 10 forCO and EPA Method 13A for HF, ormethods approved by the Department andEPA, based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Recordkeeping by stack test results prior topermit renewal. [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. Submit a stack test protocol to theBureau of Technical Services (BTS) at POBox 437, Trenton, NJ 08625 at least 30months prior to the expiration of theapproved renewal permit. Within 30 days ofprotocol approval, the permittee mustcontact BTS at 609-530-4041 to schedule amutually acceptable test date. The stack testreport must be submitted to BTS within 45days after performing the stack test pursuantto N.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a New Jersey licensedprofessional engineer or certified industrialhygienist.A copy of the test results must be submittedwith the operating permit renewalapplication due at least 12 months prior tothe expiration of the Operating Permit.Test results shall report lbs/hour, lbs/MMBtu, ppm (as needed) [N.J.A.C.7:27-22.18(e)] &. [N.J.A.C. 7:27-22.18(h)]9Particulate Emissions <= 15.6 lb/hr.Maximum emission rate for each MSWincinerator from the table at N.J.A.C.7:27-4.2(a), based on the Maximum GrossHeat input. Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 4.2(a)]None.None.None.10SO2 <= 2,000 ppmv fromeach emissionpoint, at standard conditions. Emissionlimit applies at all times, including startupand shutdown. [N.J.A.C. 7:27- 7.2(b)1]None.None.None.11SO2 <= 1,000 lb/hr (in any 60-minuteperiod) from each emission point, based onthe calculation procedure at N.J.A.C.7:27-7.2(r). Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 7.2(b)2]None.None.None.Page 35 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement12SO2 <= 2,000 lb/hr fromeach emissionpoint, at any instant, based on thecalculation procedure at N.J.A.C.7:27-7.2(r). Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 7.2(b)2]None.None.None.13SO3 and H2SO4, as converted andexpressed as H2SO4 <= 10 mg/ft^3 atstandard conditions from each emissionpoint. Emission limit applies at all times,including startup and shutdown. [N.J.A.C.7:27- 7.2(g)1]None.None.None.14SO3 and H2SO4, as converted andexpressed as H2SO4 <= 325 lb/hr in any60-minute period from each emission point,based on the calculation procedure atN.J.A.C. 7:27-7.2(r). Emission limit appliesat all times, including startup and shutdown.[N.J.A.C. 7:27- 7.2(g)2]None.None.None.15SO3 and H2SO4, as converted andexpressed as H2SO4 <= 650 lb/hr at anyinstant from each emission point, based onthe calculation procedure at N.J.A.C.7:27-7.2(r). Emission limit applies at alltimes, including startup and shutdown.[N.J.A.C. 7:27- 7.2(g)2]None.None.None.16SO2 <= 0.3 lb/MMBTU. Maximumemission rate from each MSW incinerator,based on Table 2 at N.J.A.C. 7:27-10.2(c)and the location of the facility (GloucesterCounty, Zone Three). Emission limitapplies at all times, including startup andshutdown. [N.J.A.C. 7:27-10.2(c)]SO2: Monitored by continuous emissionmonitor continuously, based on theaveraging period as per approved samplingprotocol. [N.J.A.C. 7:27-22.16(o)]SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]Submit an equipment protocol: Within 90days from the date of the approved permit.The permittee will submit a CEMSprotocol, including an appropriate averagingtime, for monitoring SO2 to determinecompliance with the N.J.A.C. 7:27-10requirement to the Bureau of TechnicalServices for approval . [N.J.A.C.7:27-22.16(o)]&. [N.J.A.C. 7:27-22.18(b)]17SO2 <= 1.2 lb/MMBTU gross heat inputdetermined as a 30-day rolling average foreach MSW incinerator. Emission limitapplies at all times, including startup andshutdown. [N.J.A.C. 7:27-10.3(a)3]None.None.None.Page 36 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement18Particulate Emissions <= 0.1 gr/dscf @ 12%CO2 (including ash, excluding thecontribution of auxiliary fuel) for eachMSW incinerator. Emission limit applies atall times, including startup and shutdown.[N.J.A.C. 7:27-11.3(a)4]Other: See stack testing requirement, U1,OS Summary.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirement, U1,OS Summary.[N.J.A.C. 7:27-22.16(o)].None.19Opacity <= 1 Ringlemann Smoke Chart foreach incinerator. Emission limit applies atall times, including startup and shutdown.[N.J.A.C. 7:27-11.3(b)2ii]None.None.None.20The provisions of 7:27-11.3(b)(2) shall notapply to: 1. Smoke emitted during thebuilding of a new fire, the shade orappearance of which is not greater thanNumber 2 of the Ringelmann smoke chartfor a period of three consecutive minutes;or ii. Emissions of such opacity within astack or chimney to a degree greater than theemission designated as Number 2 of theRingelmann smoke chart for a period notgreater than three consecutive minutes.[N.J.A.C. 7:27-11.3(b)3]None.None.None.21No person shall cause, suffer, allow orpermit the emission of particles of unburnedwaste or ash from any common incineratoror from any special incinerator which areindividually large enough to be visible whilesuspended in the atmosphere. This appliesat all times, including startup and shutdown.[N.J.A.C. 7:27-11.3(c)]None.None.None.22Odor: No person shall construct, install, useor cause to be used any common incineratoror any special incinerator which will resultin odors being detectable by sense of smellin any area of human use or occupancy.This applies at all times, including startupand shutdown. [N.J.A.C. 7:27-11.3(d)]None.None.None.Page 37 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement23Any person responsible for the use of anincinerator shall when ordered by theDepartment, provide the facilities andnecessary equipment for determining thedensity of smoke being discharged from astack or chimney and shall conduct suchsmoke tests using methods approved by theDepartment. [N.J.A.C. 7:27-11.3(e)1]None.Other: All smoke test data shall be recordedin a permanent log at such time intervals asspecified by the Department. Data shall bemaintained for a period of not less than oneyear and shall be available for review by theDepartment.[N.J.A.C. 7:27-11.3(e)1].None.24Any person responsible for the use of anexisting incinerator shall upon request of theDepartment provide such sampling facilitiesand testing facilities exclusive ofinstruments and sensing devices as may benecessary for the Department to determinethe nature and quantity of emissions fromsuch incinerators and shall during suchtesting operate the incinerator at a chargingrate of waste no less than the designedcapacity of the incinerator using materialsrepresentative of the types of wastesnormally burned. [N.J.A.C. 7:27-11.3(e)]None.None.None.25No person shall use or cause to be used anyincinerator unless all componentsconnected, or attached to, or serving theincinerator, including control apparatus arefunctioning properly and are in use, inaccordance with this permit. [N.J.A.C.7:27-11.5(c)]None.None.None.26VOC (Total) <= 3.5 lb/hr. Maximumuncontrolled emission rate from eachmunicipal solid waste combuster, based onthe Table 16A at N.J.A.C. 16.16. This limitapplies at all times, including startup andshutdown. [N.J.A.C. 7:27-16.16(d)]Other: Refer to VOC stack testingrequirement in U1 OS0, except thatcompliance with this requirement is basedon any 60-minute period (worst caserun).[N.J.A.C. 7:27-16.16(g)1ii].Other: Refer to VOC stack testingrequirement in U1 OS0.[N.J.A.C.7:27-16.16(g)1ii].None.27Nitrogen oxides (NOx) <= 150 ppmvd @7% O2 by May 1, 2011, from BOP090001.[N.J.A.C. 7:27-19.12(a)2]Nitrogen oxides (NOx): Monitored bycontinuous emission monitoring systemcontinuously, based on one calendar day[N.J.A.C. 7:27-19.12 &. [N.J.A.C.7:27-19.15(a)]Nitrogen oxides: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-19.19(a)]None.Page 38 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement28Opacity <= 10 % average during any6-minute block period for each MSW firedboiler. This opacity limit from thepreconstruction permit applies at all times,including startup and shutdown. [N.J.A.C.7:27-22.16(e)]Opacity: Monitored by continuous opacitymonitor continuously, based on 6 minuteblocks. [N.J.A.C. 7:27-22.16(e)]Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.29Fuel type for each MSW incinerator islimited to municipal solid waste and naturalgas, based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.30Maximum Gross Heat Input <= 108.33MMBTU/hr for each of the two municipalwaste fired combusters, based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Other: Maximum rated heatcapacity.[N.J.A.C. 7:27-22.16(o)].None.None.31Natural Gas Usage <= 21.9 MMft^3/yr foreach MSW fired combuster based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Natural Gas Usage: Monitored bycalculations each month during operation,based on a consecutive 12 month period(rolling 1 month basis). [N.J.A.C.7:27-22.16(o)]Other: Recordkeeping by manual logging,DAS or readily accessible electronic datastorage monthly. The owner or operatorshall maintain the records of the amounts ofeach fuel combusted during eachmonth.[N.J.A.C. 7:27-22.16(o)].None.32Nominal Waste Feed Rate <= 287.5tons/day for each of the two municipal wastefired combusters, based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Other: (See applicable requirement formaximum steam production limit of thisboiler)[N.J.A.C. 7:27-22.16(o)].None.None.33Maximum Steam Production Limit<=286,664 pounds of steam per boiler inany discrete four - hour block period[N.J.A.C. 7:27-22.16(a)]Monitored by integrated steam flow monitorcontinuously over a distinct four hour blockperiod. [N.J.A.C. 7:27-22.16(a)]Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]None.34TSP <= 29.2 tons/yr. Maximum emissionrate, based on the preconstruction permit(total for 2 pieces of equipment). [N.J.A.C.7:27-22.16(e)]None.None.None.35PM-10 (Total) <= 39.6 tons/yr filterableplus condensible, form BOP080001.[N.J.A.C. 7:27-22.16(a)]None.None.None.36VOC (Total) <= 24.2 tons/yr. Maximumemission rate, based on the preconstructionpermit (total for 2 pieces of equipment).[N.J.A.C. 7:27-22.16(e)]None.None.None.Page 39 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement37CO <= 98.8 tons/yr. Maximum emissionrate, based on the preconstruction permit(total for 2 pieces of equipment). [N.J.A.C.7:27-22.16(e)]None.None.None.38SO2 <= 224 tons/yr. Maximum emissionrate, based on the preconstruction permit(total for 2 pieces of equipment). [N.J.A.C.7:27-22.16(e)]None.None.None.39NOx (Total) <= 470 tons/yr. Maximumemission rate, based on the preconstructionpermit (total for 2 pieces of equipment).[N.J.A.C. 7:27-22.16(e)]None.None.None.40Ammonia <= 12 tons/yr based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.41HAPs (Total) <= 69 tons/yr based on theoperating permit application (total for twopieces of equipment). [N.J.A.C.7:27-22.16(a)]None.None.None.42HCl Emissions <= 64.4 tons/yr. Maximumemission rate, based on the operating permitapplication (total for 2 pieces of equipment).[N.J.A.C. 7:27-22.16(a)]None.None.None.43Hydrogen fluoride <= 1.92 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.44SO3 and H2SO4, as converted andexpressed as H2SO4 <= 22.8 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.45Mercury Emissions <= 0.03 tons/yr.Maximum emission rate calculated based onthe allowable stack concentration pursuantto N.J.A.C. 7:27-27 (total for two pieces ofequipment). [N.J.A.C. 7:27-22.16(a)]None.None.None.46Arsenic Emissions <= 0.028 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 40 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement47Beryllium Emissions<= 0.0000964 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.48Cadmium Emissions <= 0.096 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.49Chromium Emissions <= 0.048 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.50Lead Emissions <= 2.4 tons/yr. Maximumemission rate, based on the preconstructionpermit (total for 2 pieces of equipment).[N.J.A.C. 7:27-22.16(e)]None.None.None.51Nickel Emissions <= 0.048 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.52TCDD Emissions (2,3,7,8-) <= 4.8E-7tons/yr. Maximum emission rate, based onthe preconstruction permit (total for 2 piecesof equipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.53Polycyclic organic matter <= 0.123 tons/yr.Maximum emission rate, based on thepreconstruction permit (total for 2 pieces ofequipment). [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 41 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement54Monitoring, Recording and Recordkeeping -Continuous Emission Monitors andRecorders - The facility shall operate thecontinuous emission monitoring andcontinuous opacity monitoring systems inaccordance with the procedures submitted toand approved by the Department.A minimum of ninety (90) percent dataavailability per calendar quarter based onsource operating hours, is required for thecontinuous emission monitors.A minimum of ninety-five (95) percent dataavailability per calendar quarter, based onsource operating hours, is required for thecontinuous opacity monitoring systems.For each blockhour, a minimum ofseventy-five (75) percent data availability isrequired. For each blockhour in which atleast seventy-five percent data availability isnot maintained, the entire 60-minute periodshall be included as downtime accumulatedfor the calendar quarter. [N.J.A.C.7:27-22.16(e)]None.None.None.55Monitoring, Recording and Recordkeeping -Continuous Emission Monitors andRecorders - Continuous emissionmonitoring and continuous opacitymonitoring systems shall be in operation andproviding representative data, in accordancewith the procedures submitted to andapproved by the Department. [N.J.A.C.7:27-22.16(e)]None.None.None.Page 42 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement56Each unit shall be equipped with continuousmonitors and recorders which shall beoperated to accurately record:a. temperature at the inlet of the boilerconvection section;b. pressure drop in each compartment of thebaghouse;c. temperatures and pressures of waterentering the boiler and of steam from theboiler;d. mass flow rate of steam from the boiler;e. flow rate of slurry to scrubber; andf. activated carbon volumetric feeder setting.[N.J.A.C. 7:27-22.16(e)]None.None.None.57The following shall be recorded in apermanently bound log book or readilyaccessible computer memories:a. specific times of operation of each furnace;b. specific times of operation of the auxiliaryburners;c. incidents of low oxygen concentrations asspecified in this permit;d. equipment malfunctions included in thispermit;e. exceedances of emission standardsdetermined by continuous monitoring;f. quantity of refuse charged hourly toeachfurnace; andg. date and time activated carbon feedcontainers are changed. [N.J.A.C.7:27-22.16(e)]None.None.None.58Start-up/ Shutdown Allowances - ObtainingAllowances - To obtain start-up/shutdownallowances, the facility must:a. Maintain the equipment;b. Operate the equipment properly;c. Take steps to minimize emissions duringstart-up/shutdown;[N.J.A.C. 7:27-22.16(e)]None.None.None.Page 43 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement59Start-up and Shutdown Allowances - Theemission limits specified U1 OS1 and U1OS2 of this permit shall not apply duringstart-up and shutdown periods, as definedbelow.i. The start-up period commences when theaffected incinerator begins the combustionof MSW, including continuous,semicontinuous, or batch feeding of MSWto the furnace. The start-up period does notinclude any warm-up period when theaffected unit is combusting only auxiliaryfuel (natural gas) and no MSW is beingcombusted. The duration of exemption fromemission limits during the start-up periodshall not exceed 3hours.ii. The shutdown period commences whenthe feeding of MSW to the hopper isterminated as a result of a scheduledshutdown or malfunction. The shutdownperiod ends when MSW is no longercombusting on the grate. The duration ofexemption from emission limits during theshutdown period shall not exceed 3hours.Malfunction resulting in shutdown of a unitshall be considered a shutdown, unlessoperation of the affected unit is resumedbefore the shutdown is completed.Resuming the operation of a unit before ashutdown is completed, if the shutdown isthe result of a malfunction, shall beconsidered a malfunction.[N.J.A.C. 7:27-22.16(e)]None.None.None.Page 44 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement60Carbon monoxide: Start-up and ShutdownAllowances - The hourly CO emission limitsspecified in this permit (see U1 OS1 andU1 OS2) shall not apply during periods,including warm-up periods, when no wasteis burned and fossil fuel is being combusted.Only auxiliary fuel (natural gas) shall becombusted during warm-up periods and noMSW shall be combusted. The warm-upperiod begins upon initiation of auxiliaryfuel (natural gas) combusted in the furnace.The duration of exemption from emissionlimits during these periods shall not exceed10 consecutive hours per warm-up period.[N.J.A.C. 7:27-22.16(e)]None.None.None.61Upon startup of a unit, no solid waste maybe introduced into the furnace unless thetemperature 0.3 seconds downstream, ofsecondary air injection is 1500 degrees F orhigher. A temperature of less than 870degrees F as recorded at the retractablethermoprobe (located at elevation 173' 6")will be considered a violation of this permitcondition. This is based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.62Ammonia Slip <= 20 ppmvd @ 7% O2 foreach selective catalytic reduction system(SNCR), based on the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1,OS0[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1,OS0[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1, OS0. [N.J.A.C. 7:27-22.16(e)]63Temperature at Reagent Injection Point >=1,650 and Temperature at Reagent InjectionPoint <= 2,000 degrees F foreach SNCR.This is the recommended design operatingtemperature injection range, based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.64For each SNCR, The permittee shall conductoptimization tests (once initially) todetermine both the performance of theSNCR system and the optimized ureainjection rate versus NOx removalefficiency. [N.J.A.C. 7:27-22.16(e)]None.None.Submit a stack test report: As per theapproved schedule. Submit a report byDecember 23,2003, based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Page 45 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement65Flowrate >= 0.033 and Flowrate <= 0.2gal/min charge rate for industrial grade ureareagent from BOP090001. [N.J.A.C.7:27-22.16(a)]Flowrate: Monitored by material feed/flowmonitoring continuously. [N.J.A.C.7:27-22.16(o)]Flowrate: Recordkeeping by data acquisitionsystem (DAS) / electronic data storage onceinitially. [N.J.A.C. 7:27-22.16(o)]None.66industrial grade urea in the reagent fromBOP090001 Concentration of Reagent inSolution >= 50 % by volume. [N.J.A.C.7:27-22.16(a)]None.None.None.67The permittee shall submit an ExcessEmissions and Monitoring SystemsPerformance Report to the Department forreview and approval. [N.J.A.C.7:27-22.16(e)]None.None.Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) to theDepartment for review and approval. Thepermittee is required to submit the EEMPRvia the Department's electronic reportingsystem. [N.J.A.C. 7:27-22.16(a)] &.[N.J.A.C. 7:27-22.16(e)]68Inlet Temperature to Baghouse >= 200 andInlet Temperature to Baghouse <= 500degrees F for each baghouse (CD2 andCD5) except that the lower temperature limitshall not apply during startup and shutdown.This is based on the operating permitapplication and the preconstruction permits[N.J.A.C. 7:27-22.16(a)]&. [N.J.A.C.7:27-22.16(e)]Inlet Temperature to Baghouse: Monitoredby temperature instrument continuously,based on a 1 hour block average which shallbe used to calculate a 4 hour block average.[N.J.A.C. 7:27-22.16(o)]Inlet Temperature to Baghouse:Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.69Particulates Control Efficiency >= 99 %.Minimum control efficiency for eachbaghouse (CD2 and CD5) from thepreconstruction permits. [N.J.A.C.7:27-22.16(e)]None.None.None.70The baghouses (CD2 and CD5) shalleachcontain 1020 bags, based on the operatingpermit application. [N.J.A.C. 7:27-22.16(a)]None.None.None.71Air-to-Cloth Ratio <= 3.45 ACFM/sq.ft..Maximum air-to cloth ratio for eachbaghouse (CD2 and CD5) from thepreconstruction permits. [N.J.A.C.7:27-22.16(e)]None.None.None.Page 46 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement72The bags in CD2 and CD5 shall be Ryton(3x1 double woven filling face) with an acidresistant finish, or a fabric which has beendemonstrated to provide the same or greaterparticulate removal efficiency under thesame operating conditions, based on theoperating permit application. [N.J.A.C.7:27-22.16(a)]None.None.None.73The pulse-jet method shall be used to cleanthe bags in CD2 and CD5, based on thepreconstruction permits. [N.J.A.C.7:27-22.16(e)]None.None.None.74The permittee shall conduct bag cleaning,maintenance and replacement in CD2 andCD5 on a schedule necessary to achieve therequired particulate removal efficiency asspecified by the manufacturer. [N.J.A.C.7:27-22.16(a)]Other: Visually inspect the bags accordingto the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].None.None.75Scrubbing Medium Flow Rate >= 3 gal/minfor each spray dryer absorber (CD1 andCD4) during normal operation. This isbased on the operating permit application.[N.J.A.C. 7:27-22.16(a)]Scrubbing Medium Flow Rate: Monitoredby scrubber flow rate instrumentcontinuously, based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]Scrubbing Medium Flow Rate:Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.76Concentration of Chemical Additive inScrubbing Solution >= 1.01 andConcentration of Chemical Additive inScrubbing Solution <= 1.2 % foreach spraydryer absorber (CD1 and CD4; additive iscalcium hydroxide). This is based on thepreconstruction permit and the operatingpermit application. [N.J.A.C.7:27-22.16(a)]&. [N.J.A.C. 7:27-22.16(e)]Concentration of Chemical Additive inScrubbing Solution: Monitored bygravimetric monitoring twice per day.[N.J.A.C. 7:27-22.16(o)]Concentration of Chemical Additive inScrubbing Solution: Recordkeeping bymanual logging of parameter twice per dayin a permanently bound log book or byelectronic data storage in readily accessiblecomputer memories twice per day. [N.J.A.C.7:27-22.16(o)]None.77SO2 Removal Efficiency >= 80 % for eachspray dryer absorber (CD1 and CD4), unlessthe SO2 outlet average concentration is lessthan 50 ppm@7%O2 (for any three hourperiod), based on the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]SO2 Removal Efficiency: Monitored bycontinuous emission monitor continuously,based on a 3 hour rolling average based on a1 hour block average. The permittee shallmonitor SO2 emissions (in ppmvd @ 7%O2) at both the inlet and outlet of thescrubber. [N.J.A.C. 7:27-22.16(e)]SO2 Removal Efficiency: Recordkeeping bydata acquisition system (DAS) / electronicdata storage continuously. [N.J.A.C.7:27-22.16(e)]None.Page 47 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement78Carbon feed rate >= 2.0 lb/hr foreachcarbon injector (CD3 and CD6)Pursuant to N.J.A.C. 7:27-27.4(k), theowner or operator of any MSW Incineratorthat has a reagent based mercury emissioncontrol system must operate each MSWincinerator at, or above, the optimizedreagent feed rate approved by theDepartment. Compliance with thisrequirement will be determined bycontinuous monitoring. Operation of thecarbon injection system below the minimumrequired carbon feed rate, as indicated byauger speed, is a permit violation unless oneof the following occurs:i. within 3 hours, the condition thatcaused the excursions is corrected andproper feed rate is restored or wastecharging to the hopper of the affectedfurnace must cease until the carbon feed rateis again at or above the required minimumcarbon feed rate; orii. the feed rate of the operating unit isdoubled, with the flow being diverted toboth units.The total time of all such exceedances foreach unit in a calendar quarter must notexceed 2% of the total operating time for thequarter. Temporary diversions of carbonduring calibrations of feed auger speed, forup to one hour foreach calibration event,are not considered an exceedance. [N.J.A.C.7:27-22.16(e)]Other: The carbon feed rate foreach unitmust be continuously monitored by augerspeed. The average carbon feed auger speedfor each unit, for each consecutive 3-hourperiod (12 to 3, 3 to 6, etc.), must bemaintained at or above the speed that hasbeen determined, by actual measurementduring calibration, to deliver the minimumrequired carbon feed rate. The carbon feedauger speed, versus actual carbon deliveryrate, shall be calibrated by actualmeasurement (by collecting and weighingthe quantity of carbon delivered by thefeeder) at least once a quarter for eachunit.[N.J.A.C. 7:27-22.16(e)].Other: The date and time of each calibrationof the auger speed, and the results of theactual carbon delivery rate must be manuallyrecorded in a permanently bound log bookor stored electronically in readily accessiblecomputer memories and must be madeavailable upon request by the Departmentpersonnel.[N.J.A.C. 7:27-22.16(e)].None.Page 48 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement79Actual Carbon Usage:1. The carbon feed auger foreachcombustor shall be operational when wasteis being fed. The period when a combustoris being fed begins at the time when thecombustor's archbreaker is opened duringstartup, and ends when the archbreaker isclosed to stop feeding of the combustor.2. Each combustion unit is equipped withits own carbon supply container (bulk bag)and feed system. The quantity of carbonactually fed to each combustion unit mustequal or exceed the approved minimumhourly carbon feed rate multiplied by thetotal hours that waste is burned in thecombustor based on a 4 quarter rollingaverage.Minimum required quantity of carbon willbe calculated by:Total hours that waste is burned in thecombustor for the last 4 quarters x 2.0 lbs/hrActual Carbon Usage will be estimated by:Number of complete carbon bags used in thelast 4 quarters x average weight of carbonbag.[N.J.A.C. 7:27-22.16(e)]Other: For calculation of Actual CarbonUsage: the quarter will end and a newquarter begun on the date and time the lastcarbon bag was replaced in a calendarquarter. For instance if a carbon bag wasemptied and replaced at 10:00 am on March29th, the next carbon bag was not installeduntil April 15th, the quarter will have endedand the next quarter started at 10:00 am onMarch 29th, instead of April 1st.Average weight per bag will be determinedby the following method:- For each delivery of carbon, the totalweight of carbon specified on carbonsupplier's delivery invoice divided by thenumber of bags delivered will determine theaverage weight.- The average weight for a 4 quarteraverage will be determined by calculatingthe average based on all deliveries made inthe 4 quarters by the following equation:(BB1 x W1) + (BB2 x W2)/(BB1 + BB2) =Average weight of bulk bagwhere,BB1 = # of bulk bags used from delivery#1 in 4 quarter periodW1 = Average weight of bulk bag indelivery #1BB2 = # of bulk bags used from delivery#2 in 4 quarter periodW2 = Average weight of bulk bag indelivery #2[N.J.A.C. 7:27-22.16(e)].Other:The following quarterly records will bemaintained in a permanently bound log bookor stored electronically in readily accessiblecomputer memories:a. Number of bulk bags and total weightdelivered for each delivery.b. Number of complete bulk bags used oneach combustor and average bulk bagweight.c. Date and time that an empty bulk bagwas replaced and the unit on which it wasreplaced.d. Total hours that waste was fed toeachcombustor.e. Total pounds of carbon actually usedon each combustor as calculated by theformula given in the applicable requirement.In addition, the facility will retain vendordelivery invoices.[N.J.A.C. 7:27-22.16(e)].Submit a report: As per the approvedschedule. The following information shallbe submitted with quarterly excessemissions reports within 30 days of the endof each calendar quarter:a. The minimum required quantity ofcarbon required foreach combustorb. Actual carbon usage, in pounds usedfor the last 4 quartersc. Total hours that waste is fed toeachunit, for the last 4 quarters. [N.J.A.C.7:27-22.16(e)]80Mercury Emissions: The carbon injectionmercury control system on each MSWcombustor shall be operated any time MSWis combusted. [N.J.A.C. 7:27-22.16(e)]None.None.None.81The two municipal waste incinerators mustbe operated in a manner that satisfies all ofthe applicable requirements of thePrevention of Significant Deterioration(PSD) regulations codified at 40CFR 52.21and of the New Jersey Air Pollution ControlRegulations codified at N.J.A.C. 7:27-1 etseq. [N.J.A.C. 7:27-22.16(a)]None.None.None.Page 49 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement82Each owner or operator of an MSWincinerator of any size shall operate theMSW incinerator in accordance withprovisions specified in either 1 or 2 below.Compliance with thisstandard shall bemeasured pursuant to Ref. #80 below.1.The emissions of mercury from anyMSW incinerator shall not exceed 28ug/dscm, corrected to seven percent oxygen,based on the annual average of all validstack emission tests performed for fourconsecutive quarters; or2. The reduction efficiency for control ofmercury emissions of the air pollutioncontrol apparatus of any MSW incineratorshall be at least:i. 80 percent until January 3, 2006determined quarterly based on all valid stackemission testing performed during eachquarter;ii. 85 percent on and after January 3,2006 based on the annual average of allvalid tests performed for each fourconsecutive quarters; andiii. 95 percent on and after January 3,2012 based on the annual average of allvalid tests performed for each fourconsecutive quarters.[N.J.A.C. 7:27-27.4(a)]None.None.None.Page 50 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement83The owner or operator of a MSW incineratorthat is demonstrating compliance with themercury emission standard of N.J.A.C.7:27-27.4(a)1 shall conduct stack emissiontesting every quarter to measure mercury inthe gas stream at the exit of the controlapparatus. The owner or operator of a MSWincinerator that is demonstrating compliancewith the control efficiency standards ofN.J.A.C. 7:27-27.4(a)2i, ii, or iii shallconduct stack emission testing every quarterto measure mercury in the gas stream at theinlet of the air pollution control apparatusserving each incinerator and simultaneouslyconduct stack emission testing every quarterto measure mercury in the gas stream at theexit of the control apparatus. There shall beat least three valid tests per quarter and atleast 45 days between the stack emissiontesting performed for a given quarter and thestack emission testing performed for thepreceding quarter, unless a shorter period isapproved by the Department. The stackemission testing shall be conducted inaccordance with a stack emission testprotocol approved pursuant to N.J.A.C.7:27-27.8 (a) and (b). [N.J.A.C.7:27-27.4(b)]Other: See stack testing requirements formercury at beginning of OSO.[N.J.A.C.7:27-27.4(c)].Other: See stack testing requirements atbeginning of OSO.[N.J.A.C. 7:27-22.16(o)].Other (provide description): Submit a stacktest report See stack test requirements atbeginning of OSO. [N.J.A.C. 7:27-22.16(o)]MOST STRINGENT.84Notwithstanding the provisions of Ref #82above, any owner or operator who achievesand maintains compliance with Ref #80above, for all applicable incinerators locatedat a facility, during eight consecutivequarters, may reduce the frequency of stackemission testing from each quarter to stackemission testing performed every fourthquarter after the eighth quarter test in whichannual average compliance was determined.However, if subsequent stack emissiontesting fails to demonstrate compliance withRef #79 above, then the frequency of stackemission testing shall revert to that indicatedin Ref #80 above for the unit that failed.[N.J.A.C. 7:27-27.4(c)]Other: See stack testing requirements formercury at beginning of OSO.[N.J.A.C.7:27-27.4(d)].Other: See stack testing requirements formercury at beginning of OSO.[N.J.A.C.7:27-27.4(d)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. [N.J.A.C. 7:27-27.4(a)]Page 51 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement85An MSW incinerator that complies with therequirements of N.J.A.C. 7:27-27.4 is notsubject to the requirements of N.J.A.C.7:27-27.4(a)2iii, or Ref #79 requirement 2iii.1. Beginning on April 1, 2006, the averageemissions of mercury from the entire MSWincinerator facility calculated under 3 belowshall not exceed 14.0 micrograms/dscm,corrected to 7 percent oxygen.2. In each quarter, three valid stackemission tests shall be conducted foreachunit at the MSW incinerator facility.3. The average emissions of mercury fromthe entire MSW incinerator facility shall becalculated for each period of 12 consecutivequarters. The average emissions shall beequal to the sum of the mercury emissions inall valid stack emission tests for all units,divided by the number of stack emissiontests conducted during the 12 quarter period.4. If the facility fails to demonstratemercury emissions less than the 14.0micrograms/dscm (corrected to 7 percentoxygen) average for any 12 consecutivequarter period up until January 3, 2012, therequirements of N.J.A.C. 7:27-27.4(a)2 iii ,or Ref #79 requirement 2iii. shall applystarting January 3, 2012.[N.J.A.C. 7:27-27.4(d)]Other: See stack testingrequirement.[N.J.A.C. 7:27-22.16(o)].Other: See stack testingrequirement.[N.J.A.C. 7:27-22.16(o)].Submit a stack test report: Within 60 days ofstack testing or by February 28 of thefollowing calendar year. [N.J.A.C.7:27-27.9(c)]Page 52 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement86Continued from previous applicablerequirement:5. If the facility demonstrates mercuryemissions less than the 14.0microgram/dscm (corrected to 7 percentoxygen) average for all rolling 12consecutive quarter periods up until January3, 2012 and the facility chooses to continueto comply with this standard after this trialperiod, the 14.0 microg/dscm limit(corrected to 7 percent oxygen) shall applyfor every 12 consecutive quarter periodthereafter. Compliance shall be determinedusing valid stack test data from the firstquarter after the end of the trial period andusing the valid stack emission test data fromthe eleven quarters immediately precedingthe first quarter. Thereafter, the facility shallnot revert back to compliance with N.J.A.C.7:27-27.4(a)2iii. [N.J.A.C. 7:27-27.4(d)]Other: See stack testingrequirement.[N.J.A.C. 7:27-22.16(o)].Other: See stack testingrequirement.[N.J.A.C. 7:27-22.16(o)].Submit a stack test report: Within 60 days ofstack testing or by Febrary 28 of thefollowing calendar year. [N.J.A.C.7:27-27.9(c)]87Mercury Emissions: The owner or operatorof any MSW incinerator that has a reagentbased mercury emision control system shalloperate each MSW incinerator at, or above,the optimized reagent feed rate establishedin the optimization tests and approved bythe Department. [N.J.A.C. 7:27-22.16(a)]None.None.None.88Any owner or operator of a MSWincinerator that submits to the Department areport of compliance testing, including alltest runs for a MSW incinerator shall havesuch report reviewed prior to submissionand certified by a registered professionalengineer or an industrial hygenist certifiedby the American Board of IndustrialHygiene. [N.J.A.C. 7:27-27.9(d)]None.None.None.89Any owner or operator of a MSWincinerator shall maintain at the facility acomplete record, including all compliancetest reports, of all compliance testing,including all test runs, conducted at thefacility on equipment subject to thissubchapter. [N.J.A.C. 7:27-27.9(e)]None.None.None.Page 53 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement90Any owner or operator of a MSWincinerator who submits to the Department areport of compliance testing, including alltest runs, shall certify that report. [N.J.A.C.7:27-27.9(f)]None.None.None.91The two municipal waste incinerators areeach subject to the New Source PerformanceStandards ( NSPS ) for incinerators 40CFRPart 60, Subpart E. Compliance with allapplicable portions of this regulation isrequired. [40 CFR 60.50]None.None.None.92The two municipal waste incinerators arealso subject to certain provisions of the NewSource Performance Standards (NSPS) forboilers 40 CFR Part 60, Subpart Db.Compliance with all applicable portions ofthis regulation is required. [40 CFR60.40(b)(d)]None.None.None.93See Ref.#s 1 through 23 in Subject ItemGR1 for applicable requirements from NSPSSubpart A, General Provisions.(Requirement updated as part ofmodification BOP060001.) [40 CFR 60]None.None.None.Page 54 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement94Each chief facility operator and shiftsupervisor must obtain and maintain acurrent full or provisional operatorcertification from either the AmericanSociety of Mechanical Engineers(QRO-1-1994) or a State certificationprogram. [40 CFR 60.39b(d)] & [40 CFR62.14105(a)]None.Other: The facility shall maintain thefollowing records for a period of five years:Records showing the names of the municipalwaste combustor chief facility operator, shiftsupervisors and control room operators whohave been fully certified or who areprovisionally certified by the AmericanSociety of Mechanical Engineers (ASME)or an equivalent State approved certificationprogram, including the dates of initial andrenewal and renewal certifications anddocumentation of current certification.Records showing the names of the municipalwaste combustor chief facility operator, shiftsupervisors and control room operators whohave completed the EPA municipal wastecombustor operator training course or aState approved equivalent course includingdocumentation of training completion.This is based on the recordkeepingrequirements at 40 CFR 60.59b(d)(12). 40CFR 60.39b(d)&[40 CFR 62.14105(a)].None.95Each chief facility operator and shiftsupervisor must complete full certificationor must have scheduled a full certificationexam with either the American Society ofMechanical Engineers (QRO-1-1994) or aState certification program. 40 CFR60.39b(d) & [40 CFR 62.14105(b)]None.None.None.Page 55 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement96The facility must not be operated unless oneof the following persons is on duty:- a fully certified chief facility operator;- a fully certified shift supervisor;If one of the persons listed above mustleave the facility during their operating shift,a provisionally certified control roomoperator who is onsite may fulfill thisrequirement. [40 CFR 60.39b(d)] & [40CFR 62.14105(c)]None.None.None.97Each chief facility operator, shift supervisorand control room operator at an affectedfacility must complete the EPA municipalwaste combustor operator training course orthe State municipal waste operator trainingcourse, except for chief facility operators,shift supervisors, and control room operatorswho have obtained full certification from theASME on or before the effective date of 40CFR 62 Subpart FFF. [40 CFR 60.39b(d)]&. [40 CFR 62.14105(d)]None.None.None.Page 56 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement98OPERATING MANUAL:The facility must develop and update on ayearly basis a manual that must, at aminimum, address the following elements ofmunicipal waste combustor unit operation:- A summary of the applicable standardsof 40 CFR 62 Subpart FFF;- A description of basic combustiontheory applicable to a MWC unit;- Procedures for receiving, handling andfeeding MSW;- Procedures for MWC unit startup,shutdown and malfunction;- Procedures for maintaining propercombustion air supply levels;- Procedures for operating the MWC unitwithin the standards established under 40CFR 62 Subpart FFF;- Procedures for responding to periodicupset or off-specification conditions;- Procedures for minimizing particulatematter carryover;- Procedures for handling ash;- Procedures for monitoring MWC unitemissions;- Reporting and Recordkeepingprocedures. [40 CFR 60.39b(d)] & [40CFR 62.14105(e)]None.Other: The operating manual and records oftraining must be available for inspection byUSEPA or the Department upon request.[40 CFR 60.39b(d)] &[40 CFR62.14105(g)].None.Page 57 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement99TRAINING FOR OPERATING MANUALREVIEW:- The facility must establish a trainingprogram to review the operating manualaccording to the schedule specified belowwith each person who has responsibilitiesaffecting the operation of the facility,including but not limited to, chief facilityoperators, shift supervisors, control roomoperators, ash handlers, maintenancepersonnel and crane/load handlers.Each person undergoing the manual reviewtraining shall do so no later than the datesspecified below, whichever is later:- The date prior to the day the personassumes responsibilities affecting MWC unitoperation; or- The date 12 months after the effectivedate of 40 CFR 62 Subpart FFF; or- Annually following the initial review.ACCESS TO OPERATING MANUAL:The operating manual must be kept in alocation readily accessible to each personrequired to undergo training. [40 CFR60.39b(d)] & [40 CFR 62.14105(f)]None.Other: The facility shall maintain recordsshowing the names of persons who havecompleted a review of the operating manualincluding the date of initial review andsubsequent annual reviews. This is based onthe recordkeeping requirement at 40 CFR60.59b(d)(13). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].None.Page 58 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement100SEMI-ANNUAL REPORT:The facility shall submit a semi-annualreport which shall include the following:- Information recorded which indicates theaverage sulfur dioxide, nitrogen oxides,carbon monoxide, municipal wastecombustor unit load level, particulate mattercontrol device inlet temperature or opacitydata were above the applicable limits withreasons for such exceedances and adescription of the corrective action taken.- A copy of the annual test reportdocumenting the emissions level and thecorrective action taken if the test reportindicates any particulate matter, opacity,cadmium, lead, mercury, dioxins/furans,hydrogen chloride or fugitive ash emissionlevels that were above applicable pollutantlimits.- Identification of the calendar dates whenthe average hourly carbon feed rate wasbelow the required feed rate with reasons forsuch occurrences and a description ofcorrective action taken.- Identification of the calendar dates whenthe average hourly carbon feed rate is notoperational, with reasons for suchoccurrences and a description of correctiveaction taken. This is as stated at 40 CFR60.59b(h). [40 CFR 60.39b(d)] & [40 CFR62.14109(a)]None.Other: All semi-annual reports must bemaintained on site as a paper copy for aminimum of 5 years. This is as stated at 40CFR 60.59b(j). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].Submit a report: As per the approvedschedule that follows. The report for thefirst half of the calendar year must besubmitted by August 1 of the same year.The report for the second half of thecalendar year must be submitted byFebruary 1 of the following year. This is asstated at 40 CFR 50.59(h). [40 CFR60.39b(d)] &. [40 CFR 62.14109(a)]Page 59 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement101SEMI-ANNUAL REPORT (continued):Upon issuance of the operating permit, thesemi-annual report shall include thefollowing:- A list of the particulate matter, opacity,cadmium, lead, mercury, dioxins/furans,hydrogen chloride and fugitive ash emissionlevels achieved during performance tests- A list of the highest emission levelrecorded for sulfur dioxide, nitrogendioxides, carbon monoxide, municipal wastecombustor load level and particulate mattercontrol device inlet temperature.- A list of the highest opacity level measured- The total number of days that the minimumnumber of hours of data for sulfur dioxide,nitrogen oxides, carbon monoxide,municipal waste combustor unit load leveland particulate matter control device inlettemperature were not obtained for thecalculation of the average emissionsconcentrations or parameters.- The total number of hours that data forsulfur dioxide, nitrogen oxides, carbonmonoxide, municipal waste combustor unitload and particulate matter control deviceinlet temperature were excluded from thecalculation of average emissionsconcentrations or parameters. This is basedon the requirements of 40 CFR 59b(g)(1).[40 CFR 60.39b(d)] & [40 CFR62.14109(a)]None.Other: All semi-annual reports must bemaintained on site as a paper copy for aminimum of 5 years. This is as stated at 40CFR 60.59b(j). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].Submit a report: As per the approvedschedule that follows. The report for thefirst half of the calendar year must besubmitted by August 1 of the same year.The report for the second half of thecalendar year must be submitted byFebruary 1 of the following year. This isbased on the requirments at 40 CFR60.59b(g). [40 CFR 60.39b(d)] &. [40 CFR62.14109(a)]Page 60 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement102SEMI-ANNUAL REPORT (continued):-The facility shall also provide a summaryreport with the same data specified in thesemi-annual reports for the preceding year inorder to provide the Administrator with asummary of the performance of the facilityover a 2 year period. This summary reportshall highlight any emission or parameterlevel that did not achieve the requiredemission or parameter limits.- The facility will also include a notificationof intent to begin reduced dioxin/furanperformance testing schedule as allowed in40 CFR 60.58(g)(5)(iii), i.e. NSPS SubpartEb. These are based on the requirements of40 CFR 60.59b(g). [40 CFR 60.39b(d)] &[40 CFR 62.14109(a)]None.Other: All semi-annual reports must bemaintained on site as a paper copy for aminimum of 5 years. This is as stated at 40CFR 60.59b(j). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].Submit a report: As per the approvedschedule that follows. The report for thefirst half of the calendar year must besubmitted by August 1 of the same year.The report for the second half of thecalendar year must be submitted byFebruary 1 of the following year. This isbased on the requrements at 40 CFR60.59b(g). [40 CFR 60.39b(d)] &. [40CFR 62.14109(a)]103REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:Identification of the calendar dates when anyof the average emission concentrations,percent reductions, operating parameters oropacity levels are above applicable limits,with reasons for such exceedances and adescription of corrective action taken. Thisis as stated at 40 CFR 60.59b(d)(3). [40CFR 60.39b(d)]& [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109].None.104REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:Identification of the calendar dates forwhich the minimum number of hours of thedata specified below have not been obtainedand the reasons for not obtaining sufficientdata and a description of the correctiveaction taken:- Sulfur Dioxide emissions data- Nitrogen Oxides emissions data- Carbon Monoxide emissions data- Municipal waste combustor unit load data- Particulate matter control devicetemperature dataThis is as stated at 40 CFR 60.59b(d)(6). [40CFR 60.39b(d)] & [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109(a)].None.Page 61 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement105REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:Identification of each occurrence that sulfurdioxide emissions data, nitrogen oxidesemissions data or operational data (i.e.carbon monoxide emissions, unit load andparticulate matter control devicetemperature) have been excluded from thecalculation of average emissionconcentration or parameters, and the reasonsfor excluding the data. This is as stated at40 CFR 60.59b(d)(7). [40 CFR 60.39b(d)]& [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109(a)].None.106REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:The results of daily drift test and quarterlyaccuracy determinations for sulfur dioxide,nitrogen oxides and carbon monoxidecontinuous emission monitoring systems asrequired under 40 CFR Part 60 Appendix F,Procedure 1. This is based on therequirements at 40 CFR 60.59b(d)(8). [40CFR 60.39b(d)] & [40 CFR 62.14109(a)]None.Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109(a)].None.Page 62 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement107REPORTING/RECORDKEEPING OFANNUAL PERFORMANCE TESTS:The facility shall maintain the followingrecords for a period of at least five years:The test reports documenting the results ofall annual performance tests shall berecorded along with supporting calculationsspecifically as follows:- The results of all annual performance testsconducted to determine compliance withparticulate matter, opacity, cadmium, lead,dioxin/furans, hydrogen chloride andfugitive ash emission limits.- The maximum demonstrated municipalwaste combustor unit load and maximumdemonstrated particulate matter controldevice temperature during dioxin/furanperformance tests.This condition is based on the requirementsat 40 CFR 60.59b(d)(9). [40 CFR60.39b(d)] & [40 CFR 62.14109(a)]None.Other: Maintain records for a period of atleast 5 years from the date of record. [40CFR 60.39b(d)] &[40 CFR 62.14109(a)].None.108REPORTING/RECORDKEEPING:The facility shall maintain the followingrecords for a period of at least five years:Identification of the calendar dates when theaverage carbon mass feed rates as measuredby auger speed were less that the hourlycarbon feed rates estimated duringperformance tests for mercury emissionswith reasons for such feed rates and adescription of corrective action taken.Identification of the calendar dates when thecarbon injection system carbon feed auger isnot operational, with reasons for suchoccurrences and a description of correctiveactions taken. This is based on therequirements at 40 CFR 60.59b(d)(14). [40CFR 60.39b(d)] & [40 CFR 62.14109(a)]Other: Carbon usage is continuouslymeasured by auger speed. [40 CFR60.39b(d)] &[40 CFR 62.14109(a)].Other: Maintain records on paper copy or acomputer readable format for a period of atleast 5 years from the date of record. This isas stated at 40 CFR 60.59b(d) and 40 CFR60.59b(k). [40 CFR 60.39b(d)] &[40 CFR62.14109(a)].None.Page 63 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement109The standards under 40 CFR 62, SubpartFFF apply at all times except during periodsof startup, shutdown, or malfunction.Duration of startup, shutdown, ormalfunction periods are limited to 3 hoursper occurrence. The startup periodcommences when the affected facility beginsthe continuous burning of municipal solidwaste and does not include any warmupperiod when the affected facility iscombusting fossil fuel or othernonmunicipal solid waste fuel, and nomunicipal solid waste is being fed to thecombustor. Continuous burning is thecontinuous, semicontinuous, or batchfeeding of municipal solid waste forpurposes of waste disposal, energyproduction, or providing heat to thecombustion system in preparation for wastedisposal or energy production. The use ofmunicipal solid waste solely to providethermal protection of the grate or hearthduring the startup period when municipalsolid waste is not being fed to the grate isnot considered to be continuous burning.This is based on the requirement at 40 CFR60.58b(a)(1). 40 CFR 60.39b(d) & [40 CFR62.14109(b)]None.None.None.110The annual fuel capacity for natural gasshall be less than 10%. [40 CFR 60.44b(d)]Monitored by calculations each monthduring operation, based on a consecutive 12month period (rolling 1 month basis). Theowner or operator shall calculate the annualcapacity factor for each fuel individually.[40 CFR 60.49b(d)]Other: The owner or operator shall maintainrecords of the amounts ofeach fuelcombusted during each day.[40 CFR60.49b(d)].None.111The owner or operator of any incineratorsubject to the provisions of 40 CFR Part 60shall record the daily charging rates andhours of operation. [40 CFR 60.53(a)]Other: Monitor charging rates and hours ofoperation daily.[N.J.A.C. 7:27-22.16(o)].Other: Record the daily charging rates andhours of operation.[40 CFR 60.53(a)].None.112The facility shall not accept any berylliumcontaining waste as defined at 40 CFR61.31(g). [N.J.A.C. 7:27-22.16(e)]Other: Waste contents. Perdelivery[N.J.A.C. 7:27-22.16(a)].Other: Waste manifests. PerDelivery.[N.J.A.C. 7:27-22.16(o)].None.Page 64 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement113The owner or operator shall develop aQA/QC plan for all CEMS/COMS requiredby this permit. This QA/QC plan shallincorporate at a minimum those proceduresoutlined in 40 CFR, Part 60, Appendix Fand/or 40 CFR, Part 75, Appendix B forCEMS and those procedures outlined in 40CFR, Part 60, Appendix B, SpecificationOne and 40 CFR, Part 51, Proposed RM203 for COMS, published DepartmentTechnical Manuals or other proceduresapproved in writing by the Department. TheQA/QC plan shall designate a coordinatorfor the facility who is responsible to ensurethat the QA/QC plan is implemented. TheDepartment reserves the right to require theQA/QC plan to be revised at any time basedon the results of quarterly EEMPR reviews,inspections, audits or any other informationavailable to the Department. All proceduresoutlined in the QA/QC plan shall commenceupon the completion date of the PST. Allredundant CEMS/COMS must undergo theQA/QC procedure. [N.J.A.C. 7:27-22.16(a)][N.J.A.C. 7:27-22.16(a)]Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis. [N.J.A.C.7:27-22.16(o)][N.J.A.C. 7:27-22.16(o)].Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports.[N.J.A.C. 7:27-22.16(o)].Submit a report: As per the approvedschedule Every April 30, July 30, October30 and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1 and October 1). All quarterlyand annual QA data shall be included inquarterly EEMPR reports and kept on file atthe facility. The QA data must be madeavailable to the Department upon request.[N.J.A.C. 7:27-22.16(o)]Page 65 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U1 Two 287.5 Ton Per Day, 108 MMBTU/hr Municipal Solid Waste (MSW) Fired Combustors (E1 and E2)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1TSP <= 3.34 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]2PM-10 (Total) <= 4.52 lb/hr fromBOP080001. [N.J.A.C. 7:27-22.16(a)]PM-10 (Total): Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runsSee stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]PM-10 (Total): Recordkeeping by stack testresults annually See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]3VOC (Total) <= 2.8 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]4CO <= 11.3 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]5CO <= 100 ppmvd @ 7% O2 based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]CO: Monitored by continuous emissionmonitor continuously based on a 4-hourblock average. [N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.6SO2 <= 25.6 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]OS1 Boiler No. 1 - Burning Municipal Solid Waste (E1), Controlled by Scrubber CD1, Baghouse CD2, and Carbon Injection SystemCD3Page 66 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7NOx (Total) <= 65.8 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]8Particulate Emissions <= 0.015 gr/dscf @7% O2 based on the preconstruction permit.The emission limitations shall apply at alltimes when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]9Particulate Emissions <= 0.03 gr/dscf @ 7%O2 as tested when boiler tube rapping isperformed, based on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1,OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1,OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1, OS0. [N.J.A.C. 7:27-22.16(e)]10SO2 <= 50 ppmvd corrected to 7% O2concentration in the flue gas (3-houraverage, rolling on a 1-hour block basis,beginning on the hour and ending on thehour)The 50 ppmdv @ 7% O2 emissionlimitation shall not apply to a unit if theaverage 3-hour concentration of SO2 in theflue gas from that unit is less than 20% ofthe average concentration at the inlet to theacid gas control equipment for that unit asdetermined by continuous monitoring. Theaverage 3-hour concentration of SO2 in theflue gas can never exceed100 ppmv on adry basis corrected to 7% O2.The emission limitations shall apply at alltimes MSW is being combusted, exceptduring start-up and shutdown periods asdefined in this operating permit. This isbased on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]SO2: Monitored by continuous emissionmonitor continuously, based on a 3 hourrolling average based on a 1 hour blockaverage beginning on the hour and endingon the hour. The permittee shall monitorSO2 emissions at both the inlet and theoutlet to the scrubber. [N.J.A.C.7:27-22.16(e)]SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.Page 67 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement11HCl Emissions <= 50 ppmvd @ 7% O2 orthe average concentration of HCl in thestack gas shall be less than 10% of theconcentration at the inlet of the acid gascontrol device, based on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]12Hydrogen fluoride <= 0.22 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]13Nitrogen oxides (NOx) <= 350 ppmvd @7% O2 for any 3-hour average, rolling1-hour block basis, based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. This emission limitapplies until approval of a subsequentmodification to set the lower NOx emissionrate based on SNCR enhancement andoptimization testing and no later than May1, 2011, from BOP090001. [N.J.A.C.7:27-22.16(e)]Nitrogen oxides: Monitored by continuousemission monitor continuously, based on a 3hour rolling average based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]Nitrogen oxides: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.14Nitrogen oxides (NOx) <= 290 ppmvd @7% O2 for any 24-hour day, beginning atmidnight and ending at midnight thefollowing day based on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. Thisemission limit applies until approval of asubsequent modification to set the lowerNOx emission rate based on SNCRenhancement and optimization testing andno later than May 1, 2011, fromBOP090001. [N.J.A.C. 7:27-22.16(e)]Nitrogen oxides: Monitored by continuousemission monitor continuously, based onone calendar day beginning at midnight andending at midnight the following day.[N.J.A.C. 7:27-22.16(e)]Nitrogen oxides: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.Page 68 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15SO3 and H2SO4, as converted andexpressed as H2SO4 <= 2.6 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]16Mercury Emissions <= 0.12 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]17Arsenic Emissions <= 0.00325 lb/hr basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]18Beryllium Emissions <= 0.000011 lb/hrbased on the preconstruction permit. Theemission limitations shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]19Cadmium Emissions <= 0.011 lb/hr basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]20Chromium Emissions <= 0.0055 lb/hr basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]21Lead Emissions <= 0.28 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]Page 69 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement22Nickel Emissions <= 0.0055 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]23VOC (Total) <= 43 ppmvd @ 7% O2 basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]24TCDD Emissions (2,3,7,8-) <= 5.5E-8 lb/hrbased on the preconstruction permit. Theemission limitations shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]25Polycyclic Aromatic Hydrocarbons (PAH)<= 0.0014 lb/hrbased on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]26Benzo (A) Pyrene emissions must bemeasured using test methods approved bythe Department, based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]27Temperature: Within one hour after wastehas been introduced into a furnace, thetemperature one second downstream ofsecondary air injection must be no less than1500 degrees F. A temperature of less than790 degrees F as recorded at either of thesuperheater exit thermocouples will beconsidered a violation of this permitcondition. This is based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Temperature: Monitored by temperatureinstrument continuously. [N.J.A.C.7:27-22.16(e)]Temperature: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.Page 70 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement28Temperature: The temperature one seconddownstream of secondary air injection atwhich the furnace must operate at least 90%of the time when waste is being burned,must be no less than 1600 degrees F. Inorder to comply with this permit condition, atemperature equal to or higher than 810degrees F as recorded at either of thesuperheater exit thermocouples, must bemaintained at least 90% of the daily wasteburning time of the furnace. This is fromthe preconstruction permit. [N.J.A.C.7:27-22.16(e)]Temperature: Monitored by temperatureinstrument continuously. [N.J.A.C.7:27-22.16(e)]Temperature: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.29The auxiliary burners shall operateautomatically if the temperature one seconddownstream of secondary air injection dropsbelow 1550 degrees F during thecombustion of waste. This is based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.30Failure to maintain at least 1500 degrees F,one second after secondary air injectionshall require cessation of waste charging tothe affected furnace. This is from thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.31O2 >= 3 % by volume measured on a drybasis at the boiler exit for any five minuteblock, based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Other: Monitored by O2 monitorcontinuously, based on 5-minute blocks. O2monitors must comply with EPAperformance and siting specificationspursuant to 40 CFR Part 60, Appendix Band F.[N.J.A.C. 7:27-22.16(e)].O2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.32If the oxygen level in the flue gas at theboiler exit drops below 3.0% by volume formore than five consecutive minutes, wastecharging to the affected incinerator shallcease within five minutes of the low oxygenincident. [N.J.A.C. 7:27-22.16(e)]Other: Boiler controls shall automaticallystop the ram feeder when a low oxygen levelexists.[N.J.A.C. 7:27-22.16(o)].Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. The low oxgenindication shall be logged as an alarm andpermanently recorded. [N.J.A.C.7:27-22.16(o)]None.Page 71 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement33A low oxygen incident alone shall not be abasis for violating the two immediatelypreceeding Ref #s. However, the followingshall be considered violations and subject toenforcement action:i. Failure to cease waste feed within 5minutes of identification of a low oxygenincident.ii. Failure to report a low oxygen incident.iii. Failure to maintain the allowable COconcentration levels during a low oxygenincident.This is based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.34Opacity <= 10 % except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(a)(1)]Opacity: Monitored by continuous opacitymonitor continuously, based on 6 minuteblocks. The continuous opacity monitoringsystem shall conform to PerformanceSpecification 1 in 40 CFR 60, appendix B.This is as required at 40 CFR 60.58b(8).Also, perform annual opacity observationsusing EPA Method 9, which is as required at40 CFR 60.58b(11). [40 CFR 60.39b(d)] &.[40 CFR 62.14109(b)]Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. All 6-minute opacity levelsshall be available for submittal or reviewonsite by an inspector, as required at 40CFR 60.59b(d)(i)(A). Also, maintainrecords of annual Method 9 opacityobservations on paper copy or computerreadable format, based on the requirementsat 40 CFR 60.59b(d)(9) and 40 CFR60.59b(k). [40 CFR 60.39b(d)]&. [40 CFR62.14109(a)]None.35Nitrogen oxides <= 205 ppmvd @ 7% O2 ,24-hour daily arithmetic average (midnightto midnight) except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(d)]Nitrogen oxides: Monitored by continuousemission monitor continuously, based on a 1hour block average. Monitor as specified at40 CFR 60.58b(h). EPA Reference Method19, section 4.1, shall be used fordetermining the 24-hour daily arithmeticaverage nitrogen oxides emissionconcentration. [40 CFR 60.39b(d)]&. [40CFR 62.14109(b)]Nitrogen oxides: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. All 1-hour averagenitrogen oxide concentrations shall berecorded and be available for submittal orreview onsite by an inspector. This is asspecified at 40 CFR 60.59b(d)(2)(i)(C). [40CFR 60.39b(d)] &. [40 CFR 62.14109(a)]None.Page 72 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement36Particulate Emissions <= 25 mg/dscm @ 7%O2 from each MWC on and after April 28,2009, except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b). [40 CFR60.33b(a)(1)(i)] &. [40 CFR62.14103(a)(1)]Particulate Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the requirements at40 CFR 60.58b(c)(9). [40 CFR62.14109(b)]Particulate Emissions: Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.37Lead Emissions <= 0.4 mg/dscm @ 7% O2from each MWC on and after April 28,2009, except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b). 40 CFR60.33b(a)(4) &. [40 CFR 62.14103(a)(2)]Lead Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the Method 29requirements at 40 CFR 60.58b(d)(1). [40CFR 62.14109(b)]Lead Emissions: Recordkeeping by stacktest results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.38Cadmium Emissions <= 0.035 mg/dscm @7% O2 from each MWC on and after April28, 2009 except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b). [40 CFR60.33b(a)(2)(i) &. [40 CFR 62.14103(a)(2)]Cadmium Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring requirements are based on therequirements at 40 CFR 60.58b(d)(1). [40CFR 62.14109(b)]Cadmium Emissions: Recordkeeping bystack test results annually. See stack testingrequirements in U1 OS0. Recordkeeping isbased on the requirements at 40 CFR60.59b(d)(9). [40 CFR 62.14109(a)]None.39Mercury Emissions <= 0.05 mg/dscm @ 7%O2 or 15 percent of the potential mercuryemission concentration (85-percentreduction by weight), corrected to 7%oxygen, whichever is less stringent, fromeach MWC on and after April 28,2009except during periods of startup, shutdown,and malfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b). [40 CFR 60.33b(a)(3)]&. [40 CFR 62.14103(a)(3)]Mercury Emissions: Monitored by stackemission testing annually, based on theaverage of three 1-hour tests. See stacktesting requirements in U1 OS0.Monitoring is based on the requirements of40 CFR 60.58b(d)(2). [40 CFR62.14109(b)]Mercury Emissions: Recordkeeping by stacktest results annually. See stack testingrequirements in U1 OS0.. Recordkeeping isbased on the requirements at 40 CFR50.59b(d)(9)(i). [40 CFR 62.14109(a)]None.40SO2 <= 29 ppmvd @ 7% O2 or 25% of thepotential sulfur dioxide emissionconcentration (75 percent reduction byweight or volume) whichever is lessstringent,except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(b)(1)]SO2: Monitored by continuous emissionmonitor continuously, based on a dailyaverage (a 24-hour daily geometricaverage), or a daily geometric averagepercent reduction using EPA ReferenceMethod 19. This is based on the requirementat 40 CFR 60.58b(e)(4). [40 CFR60.39b(d)]&. [40 CFR 62.14109(b)]SO2: Recordkeeping by strip chart, roundchart or data acquisition (DAS) system /electronic data storage continuously. Theowner or operator shall maintain records ofall 1-hour average sulfur dioxide emissionconcentrations. This is as specified at 40CFR 60.59b(d)(2)(i)(B). [40 CFR60.39b(d)]&. [40 CFR 61.14109(a)]None.Page 73 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement41HCl Emissions <= 29 ppmvd @ 7% O2 or5% of the potential hydrogen chlorideemission concentration (95 percentreduction by weight or volume) whichever isless stringent, except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(f)] &.[40 CFR 62.14103(b)(2)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring, including detemining %reduction, is based on the requirements at 40CFR 60.58b(f). [40 CFR 60.39b(f)] &[40CFR 62.14109(b)].Other: See stack testing requirementscontained in Subject Item U1 OS0.Recordkeeping is based on the requirementsat 40 CFR 60.59b(d)(9). [40 CFR60.39b(f)]&[40 CFR 62.14109(a)].None.42Dioxins/furans <= 30 ng/dscm, corrected to7% O2, except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &[40 CFR 62.14103(c)(2)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring is as required at 40 CFR60.58b(h)(5), except as specified at 40 CFR62.14109(d)(1). [40 CFR 60.39b(d)], [40CFR 62.14109(b)] &[40 CFR62.14109(d)(1)].Other: See stack testing requirementscontained in Subject Item U1, OS0.Recordkeeping is as specified at 40 CFR60.59b(d)(9)(i). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].None.43CO <= 100 ppmvd @ 7% O2 except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b) and 40 CFR 60.58b(a)(1).[40 CFR 60.39b(d)] &. [40 CFR62.14104(a)]CO: Monitored by continuous emissionmonitor continuously, based on a 1 hourblock average which shall be used tocalcuate a 4-hour block average. Thecontinuous emission monitoring systemshall be operated according to PerformanceSpecification 4A in 40 CFR 60, appendix B.Monitoring is as specified at 40 CFR60.58b(i)(1), 40 CFR 60.58b(i)(3), and 40CFR 60.58b(i)(4). [40 CFR 60.39b(d)]&.[40 CFR 62.14109(b)]CO: Recordkeeping by strip chart, roundchart or data acquisition (DAS) system /electronic data storage continuously. All1-hour average CO concentrations shall berecorded and available for submittal to theadministrator or review onsite by aninspector. This is as stated at 40 CFR60.59b(d)(2)(i)(D). [40 CFR 60.39b(d)]&.[40 CFR 62.14109(a)(1)]None.Page 74 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement44The temperature at the particulate controldevice inlet shall not exceed the maximumdemonstrated particulate matter controldevice temperature as defined in 40 CFR60.51b by more than 17 degrees Celsius,except: (1) During the annual dioxin/furanperformance test the 2 weeks preceding theannual dioxin/furan performance test, noparticulate matter control device temperaturelimitations pursuant to NSPS Subpart Eb areapplicable; (2) The particulate matter controldevice temperature limits pursuant to NSPSSubpart Eb may be waived inaccordancewith permission granted by theAdministrator or delegated State regulatoryauthority for the purpose of evaluationsystem performance, testing new technologyor control technologies, diagnostic testing,or related activities for the purpose ofimproving facility performance or advancingthe state-of the-art for controlling facilityemissions. This is based on the requirementat 40 CFR 60.53b(c). [40 CFR 39b(d)] &[40 CFR 62.14104(b)]Monitored by temperature instrumentcontinuously, based on a 1 hour blockaverage which shall be used to calculate4-hour block arthithmetic avarages, basedon the requirement at 40 CFR 60.58b(i)(7).[40 CFR 60.39b(d)] &. [40 CFR62.14109(b)]Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. All 4-hour block arithmetictemperature averages shall be computed andrecorded and be available for submittal tothe Administrator or review onsite by aninspector. This is as stated at 40 CFR60.59b(d)(2)(ii). [40 CFR 60.39b(d)] &.[40 CFR 62.14109(a)]None.Page 75 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement45No owner or operator of an affected facilityshall cause it to operate at a load levelgreater than 110 percent of the maximumdemonstrated municipal waste combustorunit load as defined in 40 CFR 60.51b,except: (1) During the annual dioxin/furanperformance test and the 2 weeks precedingthat test, no municipal waste combustor unitload limit pursuant to NSPS Subpart Eb isapplicable; (2)The municipal wastecombustor unit load limit pursuant to NSPSSubpart Eb may be waived inaccordancewith permission granted by theAdministrator or delegated State regulatoryauthority for the purpose of evaluatingsystem performance, testing new technologyor control technologies, diagnostic testing,or related activities for the purpose ofimproving facility performance or advancingthe state-of-the art for controlling facilityemissions. This is as stated at 40 CFR60.53b(b). [40 CFR 60.39b(d)]& [40 CFR62.14104(b)]Other: The owner or operator shall operate asteam or feedwater flow meter on acontinuous basis, as required at 40 CFR60.58(i)(6)(i). Steam (or feed water flow)flow calculations as required under 40 CFR60.58(i)(6)(i) shall be in accordance withASME PTC 4.1-1964 (Reaffirmed 1991),Power test codes : Test Code for SteamGenerating Units (with 1968 and 1969Addenda). For design, construction,installation, calibration, and use of nozzlesand orifices required in 40 CFR60.58(i)(6)(ii), proceed in accordance withthe recommendations in ASME InterimSupplement 19.5 on Instruments andApparatus: Application, Part II of FluidMeters, 6th Edition (1971). [40 CFR60.39b(d)] &[40 CFR 62.14104(b)].Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslybased on the requirement at 40 CFR60.58(i)(6)(i). [40 CFR 60.39b(d)] &. [40CFR 62.14104(b)]None.Page 76 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement46FUGITIVE ASH EMISSIONS -The facilitymust not cause to be discharged to theatmosphere visible emissions of combustionash from an ash conveying system(including conveyor transfer points) inexcess of 5 percent of the observation period(i.e., 9-min. per 3-hour period), exceptduring periods of startup, shutdown, andmalfunction and as provided below.Startup, shutdown, and malfunctionexception is specified by 40 CFR62.15109(b) and 40 CFR 60.58b(a)(1).- The emission limit specified above doesnot cover visible emissions dischargedinside buildings or enclosures of ashconveying systems; however, the emissionlimit specified above does cover visibleemissions discharged to the atmospherefrom buildings or enclosures of ashconveying systems.- The provisions specified above do notapply during maintenance and repair of ashconveying systems. 40 CFR 60.39b(d)& [40CFR 62.14106(a)]Monitored by visual determination annually,based on the average of three tests.Compliance with fugitive ash emissionlimits shall be based on a series of three onehour observations, performed annually,using EPA Reference Method 22. This isbased on the requirement at 40 CFR60.58b(k). [40 CFR 60.39b(d)]&. [40 CFR62.14106(a)]Other: Maintain records of annual method22 results along with all supportingcalculations. This is as specified at 40 CFR60.59b(d)(9). [40 CFR 60.39b(d)]&[40CFR 62.14109(a)].None.47During operation, the carbon injectionsystem operating parameter(s) that are theprimary indicator(s) of the carbon mass feedrate (e.g., screw feeder setting) must equalor exceed the level established duringperformance tests for mercury anddioxin/furan emissions. This is as requiredby 40 CFR 60.58b(m)(2). [40 CFR60.39b(d)] & [40 CFR 62.14109(b)]Other: Monitored by carbon feed rate, asrequired at 40 CFR 60.58b(m)(2). [40 CFR60.39b(d)]&[40 CFR 62.14109(b)].Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslyThe facility shall record the average carbonmass feed rate (in kg/hr or lb/hr) estimatedfor eachhour of operation. This is asrequired at 40 CFR 60.59b(d)(4)(iii). Also,as required at 40 CFR 60.59b(d)(15), thefacility shall record the dates where thecarbon feed rate is less than the levelsestablished by the performance tests formercury and dioxins/furans. [40 CFR60.39b(d)]&. [40 CFR 62.14109(a)]None.48Particulate Emissions <= 0.1 lb/MMBTU.This emission standard does not applyduring periods of start-up, shutdown, ormalfunction [40 CFR 60.43b(d)(1)].None.Other: Maintain record of initialperformance test from April 24-April 27,1990.[40 CFR 60.49b(b)].None.49Particulate Emissions <= 0.08 gr/dscf @12% CO2 (0.18 g/dscm @ 12% CO2) [40CFR 60.52(a)].None.Other: Maintain record of initialperformance test from April 24-April 27,1990.[N.J.A.C. 7:27-22.16(o)].None.Page 77 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U1 Two 287.5 Ton Per Day, 108 MMBTU/hr Municipal Solid Waste (MSW) Fired Combustors (E1 and E2)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1TSP <= 3.34 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]2PM-10 (Total) <= 4.52 lb/hr fromBOP080001. [N.J.A.C. 7:27-22.16(a)]PM-10 (Total): Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runsSee stack testing requirements in U1 OS0.[N.J.A.C. 7:27-22.16(o)]PM-10 (Total): Recordkeeping by stack testresults annually See stack testingrequirements in U1 OS0. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(o)]3VOC (Total) <= 2.8 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]4CO <= 11.3 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]5CO <= 100 ppmvd @ 7% O2 based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]CO: Monitored by continuous emissionmonitor continuously based on a 4-hourblock average. [N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.6SO2 <= 25.6 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]OS2 Boiler No. 2 - Burning Municipal Solid Waste (E2), Controlled by Scrubber CD4, Baghouse CD5, and Carbon Injection SystemCD6Page 78 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7NOx (Total) <= 65.8 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]8Particulate Emissions <= 0.015 gr/dscf @7% O2 based on the preconstruction permit.The emission limitations shall apply at alltimes when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]9Particulate Emissions <= 0.03 gr/dscf @ 7%O2 as tested when boiler tube rapping isperformed, based on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1,OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1,OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1, OS0. [N.J.A.C. 7:27-22.16(e)]10SO2 <= 50 ppmvd corrected to 7% O2concentration in the flue gas (3-houraverage, rolling on a 1-hour block basis,beginning on the hour and ending on thehour)The 50 ppmdv @ 7% O2 emissionlimitation shall not apply to a unit if theaverage 3-hour concentration of SO2 in theflue gas from that unit is less than 20% ofthe average concentration at the inlet to theacid gas control equipment for that unit asdetermined by continuous monitoring. Theaverage 3-hour concentration of SO2 in theflue gas can never exceed100 ppmv on adry basis corrected to 7% O2.The emission limitations shall apply at alltimes MSW is being combusted, exceptduring start-up and shutdown periods asdefined in this operating permit. This isbased on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]SO2: Monitored by continuous emissionmonitor continuously, based on a 3 hourrolling average based on a 1 hour blockaverage beginning on the hour and endingon the hour. The permittee shall monitorSO2 emissions at both the inlet and theoutlet to the scrubber. [N.J.A.C.7:27-22.16(e)]SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.Page 79 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement11HCl Emissions <= 50 ppmvd @ 7% O2 orthe average concentration of HCl in thestack gas shall be less than 10% of theconcentration at the inlet of the acid gascontrol device, based on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]12Hydrogen fluoride <= 0.22 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]13Nitrogen oxides (NOx) <= 350 ppmvd @7% O2 for any 3-hour average, rolling1-hour block basis, based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. This emission limitapplies until approval of a subsequentmodification to set the lower NOx emissionrate based on SNCR enhancement andoptimization testing and no later than May1, 2011, from BOP090001. [N.J.A.C.7:27-22.16(e)]Nitrogen oxides: Monitored by continuousemission monitor continuously, based on a 3hour rolling average based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]Nitrogen oxides: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.14Nitrogen oxides (NOx) <= 290 ppmvd @7% O2 for any 24-hour day, beginning atmidnight and ending at midnight thefollowing day based on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. Thisemission limit applies until approval of asubsequent modification to set the lowerNOx emission rate based on SNCRenhancement and optimization testing andno later than May 1, 2011, fromBOP090001. [N.J.A.C. 7:27-22.16(e)]Nitrogen oxides: Monitored by continuousemission monitor continuously, based onone calendar day beginning at midnight andending at midnight the following day.[N.J.A.C. 7:27-22.16(e)]Nitrogen oxides: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.Page 80 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15SO3 and H2SO4, as converted andexpressed as H2SO4 <= 2.6 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]16Mercury Emissions <= 0.12 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]17Arsenic Emissions <= 0.00325 lb/hr basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]18Beryllium Emissions <= 0.000011 lb/hrbased on the preconstruction permit. Theemission limitations shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]19Cadmium Emissions <= 0.011 lb/hr basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]20Chromium Emissions <= 0.0055 lb/hr basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]21Lead Emissions <= 0.28 lb/hr based on thepreconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]Page 81 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement22Nickel Emissions <= 0.0055 lb/hr based onthe preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]23VOC (Total) <= 43 ppmvd @ 7% O2 basedon the preconstruction permit. The emissionlimitations shall apply at all times whenMSW is being combusted, except duringstart-up and shutdown as defined in thisoperating permit. [N.J.A.C. 7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]24TCDD Emissions (2,3,7,8-) <= 5.5E-8 lb/hrbased on the preconstruction permit. Theemission limitations shall apply at all timeswhen MSW is being combusted, exceptduring start-up and shutdown as defined inthis operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]25Polycyclic Aromatic Hydrocarbons (PAH)<= 0.0014 lb/hrbased on the preconstructionpermit. The emission limitations shall applyat all times when MSW is being combusted,except during start-up and shutdown asdefined in this operating permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]26Benzo (A) Pyrene emissions must bemeasured using test methods approved bythe Department, based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Other: See stack testing requirements in U1OS0.[N.J.A.C. 7:27-22.16(e)].Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. See stack testing requirements inU1 OS0. [N.J.A.C. 7:27-22.16(e)]27Temperature: Within one hour after wastehas been introduced into a furnace, thetemperature one second downstream ofsecondary air injection must be no less than1500 degrees F. A temperature of less than790 degrees F as recorded at either of thesuperheater exit thermocouples will beconsidered a violation of this permitcondition. This is based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]Temperature: Monitored by temperatureinstrument continuously. [N.J.A.C.7:27-22.16(e)]Temperature: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.Page 82 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement28Temperature: The temperature one seconddownstream of secondary air injection atwhich the furnace must operate at least 90%of the time when waste is being burned,must be no less than 1600 degrees F. Inorder to comply with this permit condition, atemperature equal to or higher than 810degrees F as recorded at either of thesuperheater exit thermocouples, must bemaintained at least 90% of the daily wasteburning time of the furnace. This is fromthe preconstruction permit. [N.J.A.C.7:27-22.16(e)]Temperature: Monitored by temperatureinstrument continuously. [N.J.A.C.7:27-22.16(e)]Temperature: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(e)]None.29The auxiliary burners shall operateautomatically if the temperature one seconddownstream of secondary air injection dropsbelow 1550 degrees F during thecombustion of waste. This is based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.30Failure to maintain at least 1500 degrees F,one second after secondary air injectionshall require cessation of waste charging tothe affected furnace. This is from thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.31O2 >= 3 % by volume measured on a drybasis at the boiler exit for any five minuteblock, based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Other: Monitored by O2 monitorcontinuously, based on 5-minute blocks. O2monitors must comply with EPAperformance and siting specificationspursuant to 40 CFR Part 60, Appendix Band F.[N.J.A.C. 7:27-22.16(e)].O2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]None.32If the oxygen level in the flue gas at theboiler exit drops below 3.0% by volume formore than five consecutive minutes, wastecharging to the affected incinerator shallcease within five minutes of the low oxygenincident. [N.J.A.C. 7:27-22.16(e)]Other: Boiler controls shall automaticallystop the ram feeder when a low oxygen levelexists.[N.J.A.C. 7:27-22.16(o)].Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. The low oxgenindication shall be logged as an alarm andpermanently recorded. [N.J.A.C.7:27-22.16(o)]None.Page 83 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement33A low oxygen incident alone shall not be abasis for violating the two immediatelypreceeding Ref #s. However, the followingshall be considered violations and subject toenforcement action:i. Failure to cease waste feed within 5minutes of identification of a low oxygenincident.ii. Failure to report a low oxygen incident.iii. Failure to maintain the allowable COconcentration levels during a low oxygenincident.This is based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.34Opacity <= 10 % except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(a)(1)]Opacity: Monitored by continuous opacitymonitor continuously, based on 6 minuteblocks. The continuous opacity monitoringsystem shall conform to PerformanceSpecification 1 in 40 CFR 60, appendix B.This is as required at 40 CFR 60.58b(8).Also, perform annual opacity observationsusing EPA Method 9, which is as required at40 CFR 60.58b(11). [40 CFR 60.39b(d)] &.[40 CFR 62.14109(b)]Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. All 6-minute opacity levelsshall be available for submittal or reviewonsite by an inspector, as required at 40CFR 60.59b(d)(i)(A). Also, maintainrecords of annual Method 9 opacityobservations on paper copy or computerreadable format, based on the requirementsat 40 CFR 60.59b(d)(9) and 40 CFR60.59b(k). [40 CFR 60.39b(d)]&. [40 CFR62.14109(a)]None.35Particulate Emissions <= 27 mg/DSCMcorrected to 7% oxygen, except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b) and 40 CFR 60.58b(a)(1).[40 CFR 60.39b(d)] &. [40 CFR62.14103(a)(1)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring is based on the requirements at40 CFR 60.58b(c)(9). [40 CFR60.39b(d)]&[40 CFR 62.14109(b)].Other: See stack testing requirementscontained in Subject Item U1, OS0.Recordkeeping is based on the requirementsat 40 CFR 60.59b(d)(9). [40 CFR60.39b(d)]&[40 CFR 62.14109(a)].None.Page 84 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement36Nitrogen oxides <= 205 ppmvd @ 7% O2 ,24-hour daily arithmetic average (midnightto midnight) except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(d)]Nitrogen oxides: Monitored by continuousemission monitor continuously, based on a 1hour block average. Monitor as specified at40 CFR 60.58b(h). EPA Reference Method19, section 4.1, shall be used fordetermining the 24-hour daily arithmeticaverage nitrogen oxides emissionconcentration. [40 CFR 60.39b(d)]&. [40CFR 62.14109(b)]Nitrogen oxides: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. All 1-hour averagenitrogen oxide concentrations shall berecorded and be available for submittal orreview onsite by an inspector. This is asspecified at 40 CFR 60.59b(d)(2)(i)(C). [40CFR 60.39b(d)] &. [40 CFR 62.14109(a)]None.37Lead Emissions <= 0.44 mg/DSCMcorrected to 7% O2 except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(a)(2)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring is based on the requirements at40 CFR 60.58b(d)(1). [40 CFR60.39b(d)]&[40 CFR 62.14109(b)].Other: See stack testing requirementscontained in Subject Item U1, OS0.Recordkeeping is based on the requirementsat 40 CFR 60.59b(d)(9). [40 CFR60.39b(d)]&[40 CFR 62.14109(a)].None.38Cadmium Emissions <= 0.04 mg/DSCMcorrected to 7% oxygen except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b) and 40 CFR 60.58b(a)(1).[40 CFR 60.39b(d)] &. [40 CFR62.14103(a)(2)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring requirements are based on therequirements at 40 CFR 60.58b(d)(1). [40CFR 60.39b(d)]&[40 CFR 62.14109(b)].Other: See stack testing requirementscontained in Subject Item U1, OS0.Recordkeeping is based on the requirementsat 40 CFR 60.59b(d)(9). [40 CFR60.39b(d)]&[40 CFR 62.14109(a)].None.39Mercury Emissions <= 0.08 mg/DSCM or15 percent of the potential mercury emissionconcentration (85-percent reduction byweight), corrected to 7% oxygen, whicheveris less stringent, except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(a)(3)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring is based on the requirements of40 CFR 60.58b(d)(2). [40 CFR60.39b(d)]&[40 CFR 62.14109(b)].Other: See stack testing requirementscontained in Subject Item U1, OS0.Recordkeeping is based on the requirementsat 40 CFR 50.59b(d)(9)(i). [40 CFR60.39b(d)][40 CFR 62.14109(a)].None.40SO2 <= 29 ppmvd @ 7% O2 or 25% of thepotential sulfur dioxide emissionconcentration (75 percent reduction byweight or volume) whichever is lessstringent,except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &.[40 CFR 62.14103(b)(1)]SO2: Monitored by continuous emissionmonitor continuously, based on a dailyaverage (a 24-hour daily geometricaverage), or a daily geometric averagepercent reduction using EPA ReferenceMethod 19. This is based on the requirementat 40 CFR 60.58b(e)(4). [40 CFR60.39b(d)]&. [40 CFR 62.14109(b)]SO2: Recordkeeping by strip chart, roundchart or data acquisition (DAS) system /electronic data storage continuously. Theowner or operator shall maintain records ofall 1-hour average sulfur dioxide emissionconcentrations. This is as specified at 40CFR 60.59b(d)(2)(i)(B). [40 CFR60.39b(d)]&. [40 CFR 61.14109(a)]None.Page 85 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement41HCl Emissions <= 29 ppmvd @ 7% O2 or5% of the potential hydrogen chlorideemission concentration (95 percentreduction by weight or volume) whichever isless stringent, except during periods ofstartup, shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(f)] &.[40 CFR 62.14103(b)(2)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring, including detemining %reduction, is based on the requirements at 40CFR 60.58b(f). [40 CFR 60.39b(f)] &[40CFR 62.14109(b)].Other: See stack testing requirementscontained in Subject Item U1 OS0.Recordkeeping is based on the requirementsat 40 CFR 60.59b(d)(9). [40 CFR60.39b(f)]&[40 CFR 62.14109(a)].None.42Dioxins/furans <= 30 ng/dscm, corrected to7% O2, except during periods of startup,shutdown, and malfunction. Startup,shutdown, and malfunction exception isspecified by 40 CFR 62.14109(b) and 40CFR 60.58b(a)(1). [40 CFR 60.39b(d)] &[40 CFR 62.14103(c)(2)]Other: See stack testing requirementscontained in Subject Item U1, OS0.Monitoring is as required at 40 CFR60.58b(h)(5), except as specified at 40 CFR62.14109(d)(1). [40 CFR 60.39b(d)], [40CFR 62.14109(b)] &[40 CFR62.14109(d)(1)].Other: See stack testing requirementscontained in Subject Item U1, OS0.Recordkeeping is as specified at 40 CFR60.59b(d)(9)(i). [40 CFR 60.39b(d)] &[40CFR 62.14109(a)].None.43CO <= 100 ppmvd @ 7% O2 except duringperiods of startup, shutdown, andmalfunction. Startup, shutdown, andmalfunction exception is specified by 40CFR 62.14109(b) and 40 CFR 60.58b(a)(1).[40 CFR 60.39b(d)] &. [40 CFR62.14104(a)]CO: Monitored by continuous emissionmonitor continuously, based on a 1 hourblock average which shall be used tocalcuate a 4-hour block average. Thecontinuous emission monitoring systemshall be operated according to PerformanceSpecification 4A in 40 CFR 60, appendix B.Monitoring is as specified at 40 CFR60.58b(i)(1), 40 CFR 60.58b(i)(3), and 40CFR 60.58b(i)(4). [40 CFR 60.39b(d)]&.[40 CFR 62.14109(b)]CO: Recordkeeping by strip chart, roundchart or data acquisition (DAS) system /electronic data storage continuously. All1-hour average CO concentrations shall berecorded and available for submittal to theadministrator or review onsite by aninspector. This is as stated at 40 CFR60.59b(d)(2)(i)(D). [40 CFR 60.39b(d)]&.[40 CFR 62.14109(a)(1)]None.Page 86 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement44The temperature at the particulate controldevice inlet shall not exceed the maximumdemonstrated particulate matter controldevice temperature as defined in 40 CFR60.51b by more than 17 degrees Celsius,except: (1) During the annual dioxin/furanperformance test the 2 weeks preceding theannual dioxin/furan performance test, noparticulate matter control device temperaturelimitations pursuant to NSPS Subpart Eb areapplicable; (2) The particulate matter controldevice temperature limits pursuant to NSPSSubpart Eb may be waived inaccordancewith permission granted by theAdministrator or delegated State regulatoryauthority for the purpose of evaluationsystem performance, testing new technologyor control technologies, diagnostic testing,or related activities for the purpose ofimproving facility performance or advancingthe state-of the-art for controlling facilityemissions. This is based on the requirementat 40 CFR 60.53b(c). [40 CFR 39b(d)] &[40 CFR 62.14104(b)]Monitored by temperature instrumentcontinuously, based on a 1 hour blockaverage which shall be used to calculate4-hour block arthithmetic avarages, basedon the requirement at 40 CFR 60.58b(i)(7).[40 CFR 60.39b(d)] &. [40 CFR62.14109(b)]Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. All 4-hour block arithmetictemperature averages shall be computed andrecorded and be available for submittal tothe Administrator or review onsite by aninspector. This is as stated at 40 CFR60.59b(d)(2)(ii). [40 CFR 60.39b(d)] &.[40 CFR 62.14109(a)]None.Page 87 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement45No owner or operator of an affected facilityshall cause it to operate at a load levelgreater than 110 percent of the maximumdemonstrated municipal waste combustorunit load as defined in 40 CFR 60.51b,except: (1) During the annual dioxin/furanperformance test and the 2 weeks precedingthat test, no municipal waste combustor unitload limit pursuant to NSPS Subpart Eb isapplicable; (2)The municipal wastecombustor unit load limit pursuant to NSPSSubpart Eb may be waived inaccordancewith permission granted by theAdministrator or delegated State regulatoryauthority for the purpose of evaluatingsystem performance, testing new technologyor control technologies, diagnostic testing,or related activities for the purpose ofimproving facility performance or advancingthe state-of-the art for controlling facilityemissions. This is as stated at 40 CFR60.53b(b). [40 CFR 60.39b(d)]& [40 CFR62.14104(b)]Other: The owner or operator shall operate asteam or feedwater flow meter on acontinuous basis, as required at 40 CFR60.58(i)(6)(i). Steam (or feed water flow)flow calculations as required under 40 CFR60.58(i)(6)(i) shall be in accordance withASME PTC 4.1-1964 (Reaffirmed 1991),Power test codes : Test Code for SteamGenerating Units (with 1968 and 1969Addenda). For design, construction,installation, calibration, and use of nozzlesand orifices required in 40 CFR60.58(i)(6)(ii), proceed in accordance withthe recommendations in ASME InterimSupplement 19.5 on Instruments andApparatus: Application, Part II of FluidMeters, 6th Edition (1971). [40 CFR60.39b(d)] &[40 CFR 62.14104(b)].Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslybased on the requirement at 40 CFR60.58(i)(6)(i). [40 CFR 60.39b(d)] &. [40CFR 62.14104(b)]None.Page 88 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement46FUGITIVE ASH EMISSIONS -The facilitymust not cause to be discharged to theatmosphere visible emissions of combustionash from an ash conveying system(including conveyor transfer points) inexcess of 5 percent of the observation period(i.e., 9-min. per 3-hour period), exceptduring periods of startup, shutdown, andmalfunction and as provided below.Startup, shutdown, and malfunctionexception is specified by 40 CFR62.15109(b) and 40 CFR 60.58b(a)(1).- The emission limit specified above doesnot cover visible emissions dischargedinside buildings or enclosures of ashconveying systems; however, the emissionlimit specified above does cover visibleemissions discharged to the atmospherefrom buildings or enclosures of ashconveying systems.- The provisions specified above do notapply during maintenance and repair of ashconveying systems. 40 CFR 60.39b(d)& [40CFR 62.14106(a)]Monitored by visual determination annually,based on the average of three tests.Compliance with fugitive ash emissionlimits shall be based on a series of three onehour observations, performed annually,using EPA Reference Method 22. This isbased on the requirement at 40 CFR60.58b(k). [40 CFR 60.39b(d)]&. [40 CFR62.14106(a)]Other: Maintain records of annual method22 results along with all supportingcalculations. This is as specified at 40 CFR60.59b(d)(9). [40 CFR 60.39b(d)]&[40CFR 62.14109(a)].None.47During operation, the carbon injectionsystem operating parameter(s) that are theprimary indicator(s) of the carbon mass feedrate (e.g., screw feeder setting) must equalor exceed the level established duringperformance tests for mercury anddioxin/furan emissions. This is as requiredby 40 CFR 60.58b(m)(2). [40 CFR60.39b(d)] & [40 CFR 62.14109(b)]Other: Monitored by carbon feed rate, asrequired at 40 CFR 60.58b(m)(2). [40 CFR60.39b(d)]&[40 CFR 62.14109(b)].Recordkeeping by data acquisition system(DAS) / electronic data storage continuouslyThe facility shall record the average carbonmass feed rate (in kg/hr or lb/hr) estimatedfor eachhour of operation. This is asrequired at 40 CFR 60.59b(d)(4)(iii). Also,as required at 40 CFR 60.59b(d)(15), thefacility shall record the dates where thecarbon feed rate is less than the levelsestablished by the performance tests formercury and dioxins/furans. [40 CFR60.39b(d)]&. [40 CFR 62.14109(a)]None.48Particulate Emissions <= 0.1 lb/MMBTU.This emission standard does not applyduring periods of start-up, shutdown, ormalfunction [40 CFR 60.43b(d)(1)].None.Other: Maintain record of initialperformance test from April 24-April 27,1990.[40 CFR 60.49b(b)].None.49Particulate Emissions <= 0.08 gr/dscf @12% CO2 (0.18 g/dscm @ 12% CO2) [40CFR 60.52(a)].None.Other: Maintain record of initialperformance test from April 24-April 27,1990.[N.J.A.C. 7:27-22.16(o)].None.Page 89 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U1 Two 287.5 Ton Per Day, 108 MMBTU/hr Municipal Solid Waste (MSW) Fired Combustors (E1 and E2)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Emergency Malfunction:The emission limits specified in U1 OS1 andU1 OS2 shall apply at all times except asspecified for startup and shutdown, unlessthe permittee demonstrates, pursuant to theconditions in U1 OS3 for boiler No. 1 or U1OS4 for boiler No. 2, that an emergencymalfunction occurred. [N.J.A.C.7:27-22.16(e)]None.None.Submit notification: Upon occurrence ofevent. The following informatioin shall besubmitted to the Department within 30calendar days of the occurrence of theincident, which identifies the contravention,includes the information listed below, andcertifies the information pursuant to NJAC7:27-1:39, and shall include the following:i. Copies of relevant operating dataincluding, but not limited to, continuousmonitoring data or portions of log booksthat show the malfunction to be sudden andunavoidable. "Relevant operating data"shall, at a minimum, include data recordedimmediately preceding (usually onehour),during, and immediately after (usually onehour) the malfunction;ii. List of the actions the facility willundertake to prevent, or minimize, thepotential for the malfunction to occur in thefuture;iii. Certification, in accordance with NJAC7:27-1:39, that the malfunction did notoccur as a result of the following: (a)Improperly designed equipment, to the bestof the facility's knowledge; (b) Lack ofpreventative maintenance; (c) Careless orimproper operation; or (d) Operator error;andiv. Certification, in accordance with NJAC7:27-1:39, that the information submitted inthe preliminary notice is accurate. If theinformation submitted in the preliminarynotice is inaccurate, a certified revision ofthe notice shall be submitted. [N.J.A.C.7:27-22.16(e)]OS3 Boiler No. 1 - Emergencymalfunction, OS4 Boiler No. 2 - Emergency malfunctionPage 90 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement2EMERGENCY MALFUNCTION:The Department will review the EmergencyMalfunction information submitted by thefacility. If the Department determines thatan Emergency Malfunction event did notmeet the requirements to obtain anemergency malfunction allowance, theDepartment will reject the claim and takeappropriate enforcement action [N.J.A.C.7:27-22.16(e)]None.None.None.3EMERGENCY MALFUNCTION::Emergency malfunction means any suddenand unavoidable failure to the equipment orcontrol apparatus to operate in a normalmanner. Malfunctions that are causedentirely or in part by improperly designedequipment, lack of preventativemaintenance, poor maintenance, careless orimproper operation, operator error, or anyother preventable upset condition orpreventable equipment or control apparatusbreakdown shall not be consideredemergency malfunctions. In anyenforcement proceeding, the Permitteeseeking to establish the occurrence of anemergency malfunction has the burden ofproof. [N.J.A.C. 7:27-22.16(e)]None.None.Submit notification: Upon occurrence ofevent. I. PRELIMINARY NOTICE -Preliminary notice of the malfunction shallbe submitted to the Department by 5:00 pmon the 2nd full working day (Mon-Fri)following the incident, which identifies theincident that caused the contravention, andincludes, but is not limited to:i. A description of the malfunction and howit resulted in the contravention;ii. A description of the measures taken tocorrect, as expiditiously as practicable, theconditions causing the emissions oroperating parameters to contravene thelimits; andiii. A description of the measures taken tominimize any excess emissons, which mayinclude, but not be limited to, curtailment ofoperation or shutdown of the combustor.This provision does not relieve the Permitteefrom immediately notifying the Departmentof any release of air contaminants in aquantity or concentration which poses apotential threat to public health, welfare, orthe environment, or which reasonablyresults in citizen complaints, pursuant toN.J.S.A. 26:2C-19(e). [N.J.A.C.7:27-22.16(e)]Page 91 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4EMERGENCY MALFUNCTION::To obtain emergency malfunctionallowances, the facility must:a. Maintain the equipment;b. Operate the equipment properly;c. Take steps to minimize emissions duringstart-up/shutdown and malfunction periods;d. Identify and take steps to preventmalfunctions from occurring in the future;ande. Report malfunctions in accordance withthis permit. [N.J.A.C. 7:27-22.16(e)]None.None.None.5Emergency Malfunction:The duration of excursion of sulfur dioxideemission limits caused by malfunctions shallnot exceed maximum180 minutes peroccurrence, per unit.The duration of excursion of sulfur dioxideemission limits caused by malfunctions shallnot exceed maximum 2% percent of annualoperating time, per calendar year, per unit.[N.J.A.C. 7:27-22.16(e)]Monitored by continuous emission monitorupon occurrence of event ( and hour timemonitor). [N.J.A.C. 7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. [N.J.A.C.7:27-22.16(e)]None.6Emergency Malfunction:The duration of excursion of carbonmonoxide emission limits caused bymalfunctions shall not exceed maximum 60minutes per occurrence, per unit.The duration of excursion of carbonmonoxide emission limits caused bymalfunctions shall not exceed maximum0.2% percent of annual operating time, percalendar year, per unit. [N.J.A.C.7:27-22.16(e)]Monitored by continuous emission monitorupon occurrence of event ( and hour timemonitor). [N.J.A.C. 7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. [N.J.A.C.7:27-22.16(e)]None.7Emergency Malfunction:The duration of excursion of nitrogen oxidesemission limits caused by malfunctions shallnot exceed maximum180 minutes peroccurrence, per unit.The duration of excursion of nitrogen oxidesemission limits caused by malfunctions shallnot exceed maximum 2% percent of annualoperating time, per calendar year, per unit.[N.J.A.C. 7:27-22.16(e)]Monitored by continuous emission monitorupon occurrence of event ( and hour timemonitor). [None]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. [N.J.A.C.7:27-22.16(e)]None.Page 92 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8Emergency Malfunction:The duration of excursion of operatingrequirements for temperature, caused bymalfunctions shall not exceed maximum 60minutes per occurrence, per unit.The duration of excursion of operatingrequirements for temperature, caused bymalfunctions shall not exceed maximum0.1% percent of operating time, per calendaryear, per unit. [N.J.A.C. 7:27-22.16(e)]Monitored by parametric monitoring systemupon occurrence of event (temperaturemonitor and hour time monitor). [N.J.A.C.7:27-22.16(e)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponoccurrence of event. [N.J.A.C.7:27-22.16(e)]None.9Emergency Malfunction:Neither the time, nor the emissions, duringthe periods of emergency malfunctionsmeeting the criteria shall be used in thecalculation of emission levels forcomparison to allowable emission limits.Malfunctions resulting in an excursion of anemission limit with an averaging time of lessthan or equal to one hour shall be deemed tohave occurred during the entire applicableaveraging time of that emission limit.Malfunctions resulting in an excursion of anemission limit with an averaging time ofgreater than one hour shall be deemed tohave occurred only during the hours of themalfunction. For example, a 15 minutemalfunction resulting in an excursion of anemission limit with a one hour averagingtime shall be deemed to have occurred forone hour. A malfunction of 70 minutes,which results in an excursion of an emissionlimit with a three hour averaging time, shallbe deemed to have occurred for 2 hours.[BACT - 40 CFR Part 52] [N.J.A.C.7:27-22.16(e)]None.None.None.10Opacity: Any visible emission caused by amalfunction shall not exceed an average of10% opacity in any 6-minute block period,as determined by the continuous emissionmonitoring equipment, USEPA ReferenceMethod 9, or an equivalent methodapproved by the Department. [N.J.A.C.7:27-22.16(e)]Opacity: Monitored by continuous opacitymonitor continuously, based on 6 minuteblocks. [N.J.A.C. 7:27-22.16(e)]Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]CEMS/COMS - Submit equipment protocol,submit a PST protocol, conduct PST andsubmit results: As per the approvedschedule. [N.J.A.C. 7:27-22.16(e)]Page 93 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U2 1.7 MMBTU/hr Diesel Fire Pump (E6)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Smoke emissions from stationary internalcombustion engines no greater than 20%opacity, exclusive of visible condensedwater vapor, for more than 10 consecutiveseconds. [N.J.A.C. 7:27- 3.5]None.None.None.2Particulate emission limit from thecombustion of fuel based on rated heat inputof source is 0.84 pounds per hour. [N.J.A.C.7:27- 4.2(a)]None.None.None.3Sulfur Content in Fuel <= 0.2 % by weight.Maximum allowable sulfur content in fueloil by fuel oil type/viscosity andgeographical zone. [N.J.A.C. 7:27- 9.2(b)]Sulfur Content in Fuel: Monitored bycontent in fuel oil. Per delivery.[N.J.A.C.7:27- 9.2(b)].Sulfur Content in Fuel: Recordkeeping by dsof invoices / bills of lading showing fuelsulfur content. Per delivery.[N.J.A.C. 7:27-9.2(b)].None.4"Emergency generator" means a combustionsource that:1. Is located at a facility and producesmechanical or thermal energy, or electricalpower exclusively for use at the facility;2. Is the source of mechanical or thermalenergy, or electrical power during anemergency when the primary source ofenergy is unavailable; and3. Is operated only:i.During the performance of normal testingand maintenance procedures, asrecommended in writing by themanufacturer and/or as required in writingby a Federal or State law or regulation;ii.When there is power outage or the primarysource of mechanical or thermal energy failsbecause of an emergency; oriii.When there is a voltage reduction issuedby PJM and posted on the PJM internetwebsite (www.pjm.com)under the"emergency procedures" menu. (Updatedrequirement added as part of modificationBOP060001.) [N.J.A.C. 7:27-19.1]None.None.None.OS SummaryPage 94 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5This emergency generator shall not be used:1. For normal testing and maintenance ondays when the Department forecasts airquality anywhere in New Jersey to be"unhealthy for sensitive groups,""unhealthy," or "very unhealthy" as definedin the EPA's Air Quality Index athttp://airnow.gov/, as supplemented oramended and incorporated herein byreference, unless required in writing by aFederal or State law or regulation.Procedures for determining the air qualityforecasts for New Jersey are available at theDepartment's air quality permitting web siteathttp://www.state.nj.us/dep/aqpp/aqforecast;and2. As a source of energy or power after theprimary energy or power source has becomeoperable again. If the primary energy orpower source is under the control of theowner or operator of the emergencygenerator, the owner or operator shall makea reasonable, timely effort to repair theprimary energy or power source. (Updatedrequirement added as part of modificationBOP060001.) [N.J.A.C. 7:27-19.2(d)]None.None.None.6Maximum Gross Heat Input <= 1.7MMBTU/hr based on the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]Other: Maximum rated heatcapacity.[N.J.A.C. 7:27-22.16(e)].None.None.7Emergency fire pump fuel limited to dieselfuel oil. [N.J.A.C. 7:27-22.16(e)]None.None.None.8The Permittee shall, once per month, recordthe total operating time from the generator'shour meter.[N.J.A.C. 7:27-19.11]Monitored by hour/time monitorcontinuously . [N.J.A.C. 7:27-22.16(o)]Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem the total operating time from thegenerator's hour meter. Once per month.[N.J.A.C. 7:27-19.11].None.Page 95 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement9Hours of Operation <= 500 hr/yr. ThePermittee shall comply with the above hourper year limit. This emergency generatorshall be operated only:1. During the performance of normal testingand maintenance procedures, asrecommended in writing by themanufacturer and/or as required in writingby a Federal or State law or regulation,2. When there is power outage or theprimary source of mechanical or thermalenergy fails because of an emergency, or3. When there is a voltage reduction issuedby PJM and posted on the PJM internetwebsite (www.pjm.com)under the"emergency procedures" menu. [N.J.A.C.7:27-22.16(a)]Hours of Operation: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]Other: The Permittee shall maintain on siteand record in a logbook or computer datasystem the total operating time from thegenerator's hour meter. Once per month.[N.J.A.C. 7:27-19.11].None.10VOC (Total) <= 0.113 tons/yr. Annualemission limit based on 500 hours/year ofoperation from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.11NOx (Total) <= 1.41 tons/yr. Annualemission limit based on 500 hours/year ofoperation from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.12CO <= 0.306 tons/yr. Annual emission limitbased on 500 hours/year of operation fromthe preconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.13SO2 <= 0.0936 tons/yr. Annual emissionlimit based on 500 hours/year of operationfrom the preconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.14TSP <= 0.101 tons/yr. Annual emissionlimit based on 500 hours/year of operationfrom the preconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.15PM-10 (Total) <= 0.101 tons/yr. Annualemission limit based on 500 hours/year ofoperation from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.Page 96 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U2 1.7 MMBTU/hr Diesel Fire Pump (E6)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1VOC (Total) <= 0.45 lb/hr. Maximumemission rate from the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]None.None.None.2NOx (Total) <= 5.63 lb/hr. Maximumemission rate from the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]None.None.None.3CO <= 1.22 lb/hr. Maximum emission ratefrom the preconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.4SO2 <= 0.374 lb/hr. Maximum emissionrate from the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.5TSP <= 0.402 lb/hr. Maximum emission ratefrom the preconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.6PM-10 (Total) <= 0.402 lb/hr. Maximumemission rate from operating permitapplication. [N.J.A.C. 7:27-22.16(a)]None.None.None.OS1 Diesel OperationPage 97 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U3 4,380 ton/yr Lime Silo (E3), Controlled by Baghouse CD7Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Particulate Emissions <= 0.5 lb/hr.Maximum allowable Emission Rate ofParticulate as Determined in the Table atN.J.A.C. 7:27-6.2(a), based on 0.02 grainsper standard cubic foot. [N.J.A.C. 7:27-6.2(a)]None.None.None.2Opacity <= 20 % exclusive of visible watervapor, except for 3 minutes in anyconsecutive 30 minute period. [N.J.A.C.7:27-6.2(d)]&. [N.J.A.C. 7:27- 6.2(e)]Opacity: Monitored by visual determinationeach month during operation, based on aninstantaneous determination. Forcompliance with the monitoring and recordkeeping requirements for the opacitystandard, the permittee shall conduct visualopacity inspections during daylight hours.Visual inspections shall consist of a visualsurvey to identify if the stack has visibleemissions, other than condensed watervapor, greater than the prescribed standard.If visible emissions are observed, thepermittee shall do the following: (1) Verifythat the equipment and/or control devicecausing the emission is operating accordingto manufacturer's specifications and theoperating permit compliance plan. If theequipment or control device is not operatingproperly, the permittee shall take correctiveaction immediately to eliminate the excessemissions. The permittee must report anypermit violation to NJDEP pursuant toN.J.A.C. 7:27-22.19; (2) If the correctiveaction taken in step one does not correct theopacity problem within 24 hours, theapplicant shall perform a check via acertified opacity reader, in accordance withN.J.A.C. 7:27B-2. Such a test shall beconductedeach day until corrective action istaken to successfully correct the opacityproblem. The permittee must report anycontinuing permit violation to NJDEPpursuant to N.J.A.C. 7:27-22.19. [N.J.A.C.7:27-22.16(o)]Opacity: Recordkeeping by manual loggingof parameter each month during operation ina permanently bound log book or byelectronic data storage in readily accessiblecomputer memories each month duringoperation. The permittee must retain thefollowing records: (1) Date and time ofinspection; (2) Emission Point number; (3)Operational status of equipment; (4)Observed results and conclusions; (5)Description of corrective action taken ifneeded; (6) Date and time opacity problemwas solved, if applicable; (7) N.J.A.C.7:27B-2 results if conducted; and (8)Name(s) of person(s) conducting inspection.[N.J.A.C. 7:27-22.16(o)]None.OS SummaryPage 98 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3TSP <= 0.0052 tons/yr based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.4PM-10 (Total) <= 0.0052 tons/yr based onthe operating permit application. [N.J.A.C.7:27-22.16(a)]None.None.None.5TSP <= 0.1 lb/hr based on thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.6PM-10 (Total) <= 0.1 lb/hr based on theoperating permit application. [N.J.A.C.7:27-22.16(a)]None.None.None.7Total Throughput <= 4,380 tons/yr of lime,based on the preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Other: Total Throughput: Monitored by theuse of scale tickets to determine net weightfor each load and annual tonnage.[N.J.A.C.7:27-22.16(o)].Total Throughput: Recordkeeping bymanual logging of parameter per delivery ina permanently bound log book or byelectronic data storage in readily accessiblecomputer memories per delivery. Thepermittee shall record the net scale weightfor each delivery. [N.J.A.C. 7:27-22.16(o)]None.8Pressure Drop Across the Baghouse >= 0and Pressure Drop Across the Baghouse <=24 inches w.c.. Pressure drop range fromthe operating permit application. [N.J.A.C.7:27-22.16(a)]None.None.None.9Particulates Control Efficiency >= 99 %.Minimum control efficiency from thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.10The baghouse shall contain 20 bags, basedon the preconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.11Air-to-Cloth Ratio <= 6 ACFM/sq.ft..Maximum air-to cloth ratio from thepreconstruction permit. [N.J.A.C.7:27-22.16(e)]None.None.None.12The bags shall be polypropyled felt with astandard twill weave and a fabric weight of16 oz/sq. yd. [N.J.A.C. 7:27-22.16(e)]None.None.None.13The pulse-jet method shall be used to cleanthe bags, based on the preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]None.None.None.Page 99 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement14The permittee shall conduct bag cleaning,maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]Other: Visually inspect the bags accordingto the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].Recordkeeping by manual logging ofparameter upon occurrence of event in apermanently bound log book or byelectronic data storage in readily accessiblecomputer memories upon occurrence ofevent. The permittee shall record eachinstance of bag maintenance and bagreplacement. [N.J.A.C. 7:27-22.16(o)]None.Page 100 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U4 Secondary Ash Conditioning EquipmentOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Particulate Emissions <= 0.95 lb/hr.Maximum allowable Emission Rate ofParticulate as Determined in the Table atN.J.A.C. 7:27-6.2(a), based on 0.02 grainsper standard cubic foot. [N.J.A.C. 7:27-6.2(a)]None.None.None.2Opacity: No visible emissions, exclusive ofvisible water vapor. [N.J.A.C.7:27-22.16(a)]Opacity: Monitored by visual determinationeach month during operation, based on aninstantaneous determination. Forcompliance with the monitoring and recordkeeping requirements for the opacitystandard, the permittee shall conduct visualopacity inspections during daylight hours.Visual inspections shall consist of a visualsurvey to identify if the stack has visibleemissions, other than condensed watervapor, greater than the prescribed standard.If visible emissions are observed, thepermittee shall do the following: (1) Verifythat the equipment and/or control devicecausing the emission is operating accordingto manufacturer's specifications and theoperating permit compliance plan. If theequipment or control device is not operatingproperly, the permittee shall take correctiveaction immediately to eliminate the excessemissions. The permittee must report anypermit violation to NJDEP pursuant toN.J.A.C. 7:27-22.19; (2) If the correctiveaction taken in step one does not correct theopacity problem within 24 hours, theapplicant shall perform a check via acertified opacity reader, in accordance withN.J.A.C. 7:27B-2. Such a test shall beconductedeach day until corrective action istaken to successfully correct the opacityproblem. The permittee must report anycontinuing permit violation to NJDEPpursuant to N.J.A.C. 7:27-22.19. [N.J.A.C.7:27-22.16(o)]Opacity: Recordkeeping by manual loggingof parameter or storing data in a computerdata system each month during operationThe permittee must retain the followingrecords: (1) Date and time of inspection; (2)Emission Point number; (3) Operationalstatus of equipment; (4) Observed resultsand conclusions; (5) Description ofcorrective action taken if needed; (6) Dateand time opacity problem was solved, ifapplicable; (7) N.J.A.C. 7:27B-2 results ifconducted; and (8) Name(s) of person(s)conducting inspection. [N.J.A.C.7:27-22.16(o)]None.OS SummaryPage 101 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3The permittee shall conduct scrubbercleaning, and maintenance in accordancewith the manufacturer's recommendation.[N.J.A.C. 7:27-22.16(a)]Other: Visually, according to themanufacturer's specifications andschedule.[N.J.A.C. 7:27-22.16(o)].Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event Thepermittee shall record each instance ofscrubber maintenance and parts replacement.The permittee shall have available themanufacturer's manual for maintenance ofscrubber easily available for inspection onDepartment's request. [N.J.A.C.7:27-22.16(o)]None.4See Subject Item Goup, GR1, for applicablerequirements from NSPS Subpart A,General Provisions. [N.J.A.C.7:27-22.16(a)]None.None.None.5FUGITIVE ASH EMISSIONS -The facilitymust not cause to be discharged to theatmosphere visible emissions of combustionash from an ash conveying system(including conveyor transfer points) inexcess of 5 percent of the observation period(i.e., 9-min. per 3-hour period), exceptduring periods of startup, shutdown, andmalfunction and as provided below.Startup, shutdown, and malfunctionexception is specified by 40 CFR62.15109(b) and 40 CFR 60.58b(a)(1).- The emission limit specified above doesnot cover visible emissions dischargedinside buildings or enclosures of ashconveying systems; however, the emissionlimit specified above does cover visibleemissions discharged to the atmospherefrom buildings or enclosures of ashconveying systems.- The provisions specified above do notapply during maintenance and repair of ashconveying systems. 40 CFR 60.39b(d)& [40CFR 62.14106(a)]Monitored by visual determination annually,based on the average of three tests.Compliance with fugitive ash emissionlimits shall be based on a series of three onehour observations, performed annually,using EPA Reference Method 22. This isbased on the requirement at 40 CFR60.58b(k). [40 CFR 60.39b(d)]&. [40 CFR62.14106(a)]Other: Maintain records of annual method22 results along with all supportingcalculations. This is as specified at 40 CFR60.59b(d)(9). [40 CFR 60.39b(d)]&[40CFR 62.14109(a)].Submit a report: Semi-annually on January31 and July 31 of each year. Includeobservation results, and any correctiveaction taken for exceedences in semi-annualreport. This is based on the requirements at40 CFR 60.59b(g)(1) and 40 CFR 59b(h).[40 CFR 60.39b(d)}&. [40 CFR62.14109(a)]6The water level in the scrubber should bemaintained according to the manufaturer'srecommendation [N.J.A.C. 7:27-22.16(a)]Monitored by liquid level indicator eachweek during operation, based on aninstantaneous determination. [N.J.A.C.7:27-22.16(a)]Recordkeeping by manual logging ofparameter or storing data in a computer datasystem each week during operation.[N.J.A.C. 7:27-22.16(a)]Page 102 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7Total Throughput <= 2,638 lb/hr maximummaterial processed for E8, in the AshConditioning Area. [N.J.A.C. 7:27-22.16(a)]Total Throughput: Monitored by materialfeed/flow monitoring daily, based on a dailyaverage.The following formula shall be used todetermine the material (fly ash) processed:Fly Ash (lb/hr) = 0.041 x Total DailyRefused Processed (tons/day) x (2000lbs./ton) / 24 hrs/daywhere:Total Daily Refuse Processed (tons/day) =sum of the nominal waste feed rate of thetwo municipal waste fired combustors, intons per day, based on the nominal wastefeed rate of 287.5 tons/day foreach boiler,and maximum steam production of 286,664lbs of steam per boiler in any discrete 4-hourblock period.. [N.J.A.C. 7:27-22.16(o)]Total Throughput: Recordkeeping bymanual logging of parameter or storing datain a computer data system daily. [N.J.A.C.7:27-22.16(o)]None.8Wet Scrubber Hours of Operation >= 2,000hr/yr. [N.J.A.C. 7:27-22.16(a)]Hours of Operation: Monitored by hour/timemonitor continuously, based on onecalendar month. [N.J.A.C. 7:27-22.16(o)]Hours of Operation: Recordkeeping bymanual logging of parameter or storing datain a computer data system each monthduring operation. [N.J.A.C. 7:27-22.16(o)]None.Page 103 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Emission Unit:U5 Ash and Metals Loadout BuildingOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Particulate Emissions <= 3.23 lb/hr.Maximum allowable Emission Rate ofParticulate as Determined in the Table atN.J.A.C. 7:27-6.2(a), based on 0.02 grainsper standard cubic foot. [N.J.A.C. 7:27-6.2(a)]None.None.None.2Opacity: No visible emissions, exclusive ofvisible water vapor. [N.J.A.C.7:27-22.16(a)]Opacity: Monitored by visual determinationeach month during operation, based on aninstantaneous determination. Forcompliance with the monitoring and recordkeeping requirements for the opacitystandard, the permittee shall conduct visualopacity inspections during daylight hours.Visual inspections shall consist of a visualsurvey to identify if the stack has visibleemissions, other than condensed watervapor, greater than the prescribed standard.If visible emissions are observed, thepermittee shall do the following: (1) Verifythat the equipment and/or control devicecausing the emission is operating accordingto manufacturer's specifications and theoperating permit compliance plan. If theequipment or control device is not operatingproperly, the permittee shall take correctiveaction immediately to eliminate the excessemissions. The permittee must report anypermit violation to NJDEP pursuant toN.J.A.C. 7:27-22.19; (2) If the correctiveaction taken in step one does not correct theopacity problem within 24 hours, theapplicant shall perform a check via acertified opacity reader, in accordance withN.J.A.C. 7:27B-2. Such a test shall beconductedeach day until corrective action istaken to successfully correct the opacityproblem. The permittee must report anycontinuing permit violation to NJDEPpursuant to N.J.A.C. 7:27-22.19. [N.J.A.C.7:27-22.16(o)]Opacity: Recordkeeping by manual loggingof parameter or storing data in a computerdata system each month during operationThe permittee must retain the followingrecords: (1) Date and time of inspection; (2)Emission Point number; (3) Operationalstatus of equipment; (4) Observed resultsand conclusions; (5) Description ofcorrective action taken if needed; (6) Dateand time opacity problem was solved, ifapplicable; (7) N.J.A.C. 7:27B-2 results ifconducted; and (8) Name(s) of person(s)conducting inspection. [N.J.A.C.7:27-22.16(o)]None.OS SummaryPage 104 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3Total Throughput <= 16,700 lb/hr maximummaterial processed for the ash/metals loadout operation. [N.J.A.C. 7:27-22.16(a)]Total Throughput: Monitored by materialfeed/flow monitoring daily, based on a dailyaverage.The following formula shall be used todetermine the maximum material processed(Total Ash):Total Ash Processing Rate Average (lb/hr) =0.32 x Total Daily Refused Processed(tons/day) x (2000 lbs./ton) / 24 hrs/daywhere:Total Daily Refuse Processed (tons/day) =sum of the nominal waste feed rate of thetwo municipal waste fired combustors, intons per day, based on the nominal wastefeed rate of 287.5 tons/day foreach boiler,and maximum steam production of 286,664lbs of steam per boiler in any discrete 4-hourblock period. [N.J.A.C. 7:27-22.16(o)]Total Throughput: Recordkeeping bymanual logging of parameter or storing datain a computer data system daily. [N.J.A.C.7:27-22.16(o)]None.4Hours of Operation >= 2,000 hr/yr for thewet scrubber. [N.J.A.C. 7:27-22.16(a)]Hours of Operation: Monitored by hour/timemonitor continuously, based on onecalendar month. [N.J.A.C. 7:27-22.16(o)]Hours of Operation: Recordkeeping bymanual logging of parameter or storing datain a computer data system each monthduring operation. [N.J.A.C. 7:27-22.16(o)]None.5The permittee shall conduct scrubbercleaning, and maintenance as specified bythe manufacturer's schedule. [N.J.A.C.7:27-22.16(a)]Other: Visually, according to themanufacturer's specifications andschedule.[N.J.A.C. 7:27-22.16(o)].Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event Thepermittee shall record each instance ofscrubber maintenance and parts replacement.The permittee shall have available themanufacturer's manual for maintenance ofscrubber easily available for inspection onDepartment's request. [N.J.A.C.7:27-22.16(o)]None.6See Subject Item, GR1, for applicablerequirements from NSPS Subpart A,General Provisions. [N.J.A.C.7:27-22.16(a)]None.None.None.Page 105 of 106New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/25/2010WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7FUGITIVE ASH EMISSIONS -The facilitymust not cause to be discharged to theatmosphere visible emissions of combustionash from an ash conveying system(including conveyor transfer points) inexcess of 5 percent of the observation period(i.e., 9-min. per 3-hour period), exceptduring periods of startup, shutdown, andmalfunction and as provided below.Startup, shutdown, and malfunctionexception is specified by 40 CFR62.15109(b) and 40 CFR 60.58b(a)(1).- The emission limit specified above doesnot cover visible emissions dischargedinside buildings or enclosures of ashconveying systems; however, the emissionlimit specified above does cover visibleemissions discharged to the atmospherefrom buildings or enclosures of ashconveying systems.- The provisions specified above do notapply during maintenance and repair of ashconveying systems. 40 CFR 60.39b(d)& [40CFR 62.14106(a)]Monitored by visual determination annually,based on the average of three tests.Compliance with fugitive ash emissionlimits shall be based on a series of three onehour observations, performed annually,using EPA Reference Method 22. This isbased on the requirement at 40 CFR60.58b(k). [40 CFR 60.39b(d)]&. [40 CFR62.14106(a)]Other: Maintain records of annual method22 results along with all supportingcalculations. This is as specified at 40 CFR60.59b(d)(9). [40 CFR 60.39b(d)]&[40CFR 62.14109(a)].Submit a report: Semi-annually on January31 and July 31 of each year. Includeobservation results, and any correctiveaction taken for exceedences in semi-annualreport. This is based on the requirements at40 CFR 60.59b(g)(1) and 40 CFR 59b(h).[40 CFR 60.39b(d)}&. [40 CFR62.14109(a)]8The permittee shall maintain the water levelin the scrubberaccording to themanufacturer's recommendation. [N.J.A.C.7:27-22.16(a)]Monitored by liquid level indicator eachweek during operation, based on aninstantaneous determination. [N.J.A.C.7:27-22.16(o)]Recordkeeping by strip chart or dataacquisition (DAS) system each week duringoperation. [N.J.A.C. 7:27-22.16(o)]Page 106 of 106

# WHEELABRATOR GLOUCESTER COMPANY L P (55793) Date: 2/25/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

312,958

379,231

New Jersey State Plane 8

NAD83

DEP-GIS

DEP Program Database

The facility is located at 600 US Route 130 in

West Deptford, NJ (the mailing address is

Westville). The facility incinerates municipal

solid waste and produces electricity 4953 State Plane Coordinates:

X-Coordinate:

Y-Coordinate:

Units:

Datum:

Source Org.:

Source Type:

County: Industry:

Location

Description: Primary SIC:

Secondary SIC: Gloucester Mailing

Address: Street

Address: 600 US RT 130

600 US RT 130

WESTVILLE, NJ 08093

600 US RT 130

600 US RT 130

WESTVILLE, NJ 08093 Facility Name (AIMS): WHEELABRATOR GLOUCESTER COMPA Facility ID (AIMS): 55793

562213 NAICS:

Page 1 of 4

# WHEELABRATOR GLOUCESTER COMPANY L P (55793) Date: 2/25/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(856) 456-5910 x

( ) - x

jmorris2@wm.com Wheelabrator Gloucester Company, L.P.

Jeff Morris

EH&S Manager

(856) 742-1484 x 600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: 02039672400 Contact Type: Air Permit Information Contact

Mobile (570) 619-7738 x

(570) 269-5265 x

bcorbin@envcompliance.com Environmental Compliance Assistance, LLC

William E. Corbin

Associate

(570) 619-7758 x RR#6 Box 6545

Saylorsburg, PA 18353 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: LLC

NJ EIN: Contact Type: Consultant

(856) 456-5910 x

( ) - x

jmorris2@wm.com Wheelabrator Gloucester Company, L.P.

Jeff Morris

EH&S Manager

(856) 742-1484 x 600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: 02039672400 Contact Type: Emission Statements

Page 2 of 4

# WHEELABRATOR GLOUCESTER COMPANY L P (55793) Date: 2/25/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(856) 456-5910 x

( ) - x

jmorris2@wm.com Wheelabrator Gloucester Company, L.P.

Jeff Morris

EH&S Manager

(856) 742-1484 x 600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: 02039672400 Contact Type: Environmental Officer

(856) 456-5910 x

( ) - x

jmorris2@wm.com Wheelabrator Gloucester Company, L.P.

Jeff Morris

EH&S Manager

(856) 742-1484 x 600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: 02039672400 Contact Type: Fees/Billing Contact

(856) 456-5910 x

( ) - x

mkissel@wm.com Wheelabrator Gloucester Company, L.P.

Michael Kissel

Plant Manager

(856) 742-1484 x 600 US Route 130

600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: 02039672400 Contact Type: General Contact

Page 3 of 4

# WHEELABRATOR GLOUCESTER COMPANY L P (55793) Date: 2/25/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(856) 456-5910 x

( ) - x

mkissel@wm.com Wheelabrator Gloucester Company, L.P.

Michael Kissel

Plant Manager

(856) 742-1484 x 600 US Route 130

600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: 02039672400 Contact Type: On-Site Manager

(856) 456-5910 x

( ) - x Wheelabrator Gloucester Company, L.P.

Wheelabrator Gloucester Company, L.P.

Owner

(856) 742-1484 x Wheelabrator Gloucester Company, L.P.

600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: Contact Type: Owner (Current Primary)

(856) 456-5910 x

( ) - x

mkissel@wm.com Wheelabrator Gloucester Company, L.P.

Michael Kissel

Plant Manager

(856) 742-1484 x 600 US Route 130

600 US Route 130

Westville, NJ 08093 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Partnership

NJ EIN: 02039672400 Contact Type: Responsible Official

Page 4 of 4

# WHEELABRATOR GLOUCESTER COMPANY L P (55793)

BOP090002



# New Jersey Department of Environmental Protection

Reason for Application Date: 2/25/2010



# Permit Being Modified

Permit Class: BOP Number: 90001

Description

of Modifications: This approval is for the proposed addition of non-ferrous metal separation and ash

conditioning equipment (E9, E10, E11, E12) to Emission Unit U5 (ash handling in ash and

metals loadout building) and the correction of an equipment designation error in U4 and U5.

The existing ash conditioning equipment in the ash conditioning area permitted as Emission

Unit U4 will then be used as backup or secondary equipment. A correction was made to the

equipment designation under OS1, U4. The equipm ent is E8 instead of E5, which is OS3 of

U5. No other changes to U4 are required. A ll emissions are less than de minimis emission

levels and no changes to the compliance plan are required

Page 1 of 1WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002New Jersey Department of Environmental ProtectionNon-Source Fugitive EmissionsDate:02/25/2010FGNJIDDescription ofActivity CausingEmissionLocationDescriptionReasonable Estimate of Emissions (tpy)VOC(Total)NOxCOSOTSP(Total)PM-10PbHAPS(Total)Other(Total)FG1Facility RoadwaysFacility-wide0.0000.0000.0000.0002.1002.1000.0000.000000000.000Total0.0000.0000.0000.0002.1002.1000.0000.000000000.000Page 1 of 1WHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002New Jersey Department of Environmental ProtectionInsignificant Source Emissions2/25/2010Date:ISNJIDSource/GroupDescriptionEquipment TypeLocationDescriptionEstimate of Emissions (tpy)VOC(Total)NOxCOSOTSPPM-10PbHAPS(Total)Other(Total)IS2350 Gallon Fire DieselEngine Diesel StorageTankStorage VesselBetween AshStorage andMaintenance andStorage Buildings0.0000.0000.0000.0000.0000.0000.0000.000000000.000IS3550 Gallon VehicleRefueling DieselStorage TankStorage VesselPlant Pumphouseon the Bank of theDelaware River0.0000.0000.0000.0000.0000.0000.0000.000000000.000IS41,960 GallonHydrochloric AcidStorage TankStorage VesselBoiler HouseChemical Room0.0000.0000.0000.0000.0000.0000.0000.006730000.000IS51,700 Gallon SodiumHydroxide StorageTankStorage VesselBoiler HouseChemical Room0.0000.0000.0000.0000.0000.0000.0000.000000000.001IS6Cold Cleaner Degreaser(top opening < 6 squarefeet, Capacity<100gallons)Cleaning Machine (OpenTop: Cold)Maintenance andStorage Building0.0830.0000.0000.0000.0000.0000.0000.000000000.000IS7Lubricating Oil StorageVesselStorage VesselLower Level of theTurbine/GeneratorRoom1.0000.0000.0000.0000.0000.0000.0000.000000000.000IS8Small CombustionSources (< 1MMBtu/hr) UsingNatural GasBoilerBoiler House0.0030.0510.0110.0000.0060.0060.0000.000000000.000IS9Phosphoric Acid Tank(Non-VOC storage tankwith capacity less than10,000 gallons)Storage VesselBetween AshBuilding and BoilerHouse0.0000.0000.0000.0000.0000.0000.0000.001940000.000Total1.0990.2090.0450.0110.0170.0000.0170.008803600.001Page 1 of 1Equip.NJIDFacility'sDesignationEquipmentDescriptionEquipment TypeCertificateNumberInstallDateGrandFatheredLast Mod.(Since 1968)Equip.Set IDNew Jersey Department of Environmental ProtectionEquipment InventoryBOP090002WHEELABRATOR GLOUCESTER COMPANY L P (55793)2/25/2010Date:E1Boiler No. 1BPCP0000011/1/1990No1/1/1996287.5 Tons Per Day MunicipalSolid Waste CombustorBoilerE2Boiler No. 2BPCP0000011/1/1990No1/1/1996287.5 Tons Per Day MunicipalSolid Waste CombustorBoilerE3Ash HandlingMBOP0400031/1/1990No1/29/2007Metals Truck LoadoutManufacturing andMaterials HandlingEquipmentE4Lime SiloM0919431/1/1990No1/1/1990Lime Silo for Pebble LimeStorageManufacturing andMaterials HandlingEquipmentE5Ash HandlingMBOP0400035/5/1998No1/29/2007Head Sprocket AreaManufacturing andMaterials HandlingEquipmentE6Fire pumpF0938841/10/1990No1.7 MMBTU/hr fire pumpFuel CombustionEquipment (Other)E7Ash HandlingMBOP0400031/1/1990No1/29/2007Ash Truck LoadoutManufacturing andMaterials HandlingEquipmentE8Ash HandlingMBOP0400031/1/1990No1/29/2007Secondary Ash ConditioningEquipmentManufacturing andMaterials HandlingEquipmentE9Ash HandlingMNoNonferrous Vibrating FeederScreenManufacturing andMaterials HandlingEquipmentE10Ash HandlingMNoNonferrous Eddy CurrentSeparatorManufacturing andMaterials HandlingEquipmentPage 1 of 2Equip.NJIDFacility'sDesignationEquipmentDescriptionEquipment TypeCertificateNumberInstallDateGrandFatheredLast Mod.(Since 1968)Equip.Set IDNew Jersey Department of Environmental ProtectionEquipment InventoryBOP090002WHEELABRATOR GLOUCESTER COMPANY L P (55793)2/25/2010Date:E11Ash HandlingMNoNonferrous Loadout HopperManufacturing andMaterials HandlingEquipmentE12Ash HandlingMNoPrimary Ash ConditioningEquipmentManufacturing andMaterials HandlingEquipmentPage 2 of 2WHEELABRATOR GLOUCESTER COMPANY L P (55793)Date:2/25/2010New Jersey Department of Environmental ProtectionControl Device InventoryCDNJIDFacility'sDesignationDescriptionCD TypeInstallDateGrandFatheredLast Mod.(Since 1968)CDSet IDBOP090002CD1Boiler No. 1 Spray DryerAbsorber1/1/1990No1/1/1990B1 SDAScrubber (Other)CD2Boiler No. 1 Fabric Filter1/1/1990No1/1/1990B1 FFParticulate Filter(Baghouse)CD3Boiler No. 1 Carbon InjectionSystem1/1/1996No1/1/1996B1 CIOtherCD4Boiler No. 2 Spray DryerAbsorber1/1/1990No1/1/1990B2 SDAScrubber (Other)CD5Boiler No. 2 Fabric Filter1/1/1990No1/1/1990B2 FFParticulate Filter(Baghouse)CD6Boiler No. 2 Carbon InjectionSystem1/1/1996No1/1/1996B2 CIOtherCD7Lime Silo Baghouse1/1/1990No1/1/1990Lime SiloParticulate Filter(Baghouse)CD9Boiler No. 1 SNCRNoB1 SNCRSelective Non-CatalyticReductionCD10Boiler No. 2 SNCRNoB2 SNCRSelective Non-CatalyticReductionCD11Secondary Ash ConditioningEquipment Wet Scrubber2/5/2007No1/29/2007Scrubber #1Scrubber (Other)CD12Loadout Building Wet Scrubber2/5/2007No1/29/2007Scrubber #2Scrubber (Other)Page 1 of 1WHEELABRATOR GLOUCESTER COMPANY L P (55793)Date:2/25/2010New Jersey Department of Environmental ProtectionEmission Points InventoryPTNJIDFacility'sDesignationDescriptionConfig.Equiv.Diam.(in.)Height(ft.)Dist. toProp.Line (ft)Exhaust Temp. (deg. F)Exhaust Vol. (acfm)Avg.Min.Max.Avg.Min.Max.DischargeDirectionPTSet IDBOP090002PT1002Flue for exhaust of Boiler No.1 (flue is housed in same stackas Boiler No. 2's flue)Round48260325250.0200.0500.0UpR80,000.070,000.018,000.0PT2004Flue for exhaust of Boiler No.2 (flue is housed in same stackas Boiler No. 1's flue)Round48260325250.0200.0500.0UpR80,000.070,000.018,000.0PT3003Exhaust from lime silobaghouseRectangle226536570.00.0260.0HorizontalR1,000.01,000.01,000.0PT4Ash HandlingExhaust from Secondary AshConditioning Equipment andScrubber #1Round165040070.020.0100.0HorizontalR6,300.06,000.00.0PT5Loadout BldgExhaust from LoadoutBuilding and Scrubber #2Round305160070.020.0100.0HorizontalR20,800.020,000.00.0PT6006Exhaust from Diesel FirePumpRound614150400.0400.0400.0HorizontalR1,200.01,200.01,200.0Page 1 of 1New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryWHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Date:2/25/2010U 1 MSW combust. Two 287.5 Ton Per Day, 108 MMBTU/hr Municipal Solid Waste (MSW) Fired Combustors (E1 and E2)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Boiler No. 1Boiler No. 1 - BurningMunicipal Solid Waste(E1), Controlled byScrubber CD1, BaghouseCD2, and CarbonInjection System CD3Normal - SteadyStateE1CD1 (P)CD2 (P)CD3 (P)PT11-01-012-010.08,760.018,000.080,000.0200.0500.0OS2Boiler No. 2Boiler No. 2 - BurningMunicipal Solid Waste(E2), Controlled byScrubber CD4, BaghouseCD5, and CarbonInjection System CD6Normal - SteadyStateE2CD4 (P)CD5 (P)CD6 (P)PT11-01-006-010.08,760.018,000.080,000.0200.0500.0OS3Blr 1-Emer MBoiler No. 1 - EmergencymalfunctionMalfunctionE1CD1 (P)CD2 (P)CD3 (P)OS4Blr 2-Emer MBoiler No. 2 - EmergencymalfunctionMalfunctionE2CD4 (P)CD5 (P)CD6 (P)Page 1 of 4New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryWHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Date:2/25/2010U 2 Fire Pump 1.7MMBTU/hr Diesel Fire Pump (E6)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Fire PumpDiesel OperationNormal - SteadyStateE6PT61-01-012-010.0500.01,200.01,200.0400.0400.0U 3 Lime Silo 4,380 ton/yr Lime Silo (E3), Controlled by Baghouse CD7UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Lime SiloLime SiloNormal - SteadyStateE4CD7 (P)PT33-05-102-980.08,760.01,000.01,000.00.0260.0Page 2 of 4New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryWHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Date:2/25/2010U 4 Ash Handling Secondary Ash Conditioning EquipmentUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Ash HandlingSecondary AshConditioning EquipmentNormal - SteadyStateE8CD11 (P)PT4PT53-05-101-990.08,760.00.06,300.020.0100.0U 5 Ash Handling Ash and Metals Loadout BuildingUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Ash HandlingMetals Truck LoadoutNormal - SteadyStateE3CD12 (P)PT4PT53-05-101-990.08,760.00.020,800.020.0100.0OS2Ash HandlingAsh Truck LoadoutNormal - SteadyStateE7CD12 (P)PT4PT53-05-101-990.08,760.00.020,800.020.0100.0OS3Ash HandlingHeadsprocket AreaNormal - SteadyStateE5CD12 (P)PT4PT53-05-101-990.08,760.00.020,800.020.0100.0OS4Ash HandlingNonferrous VibratingFeeder ScreenNormal - SteadyStateE9CD12 (P)PT53-05-101-990.08,760.00.020,800.020.0100.0OS5Ash HandlingNonferrous Eddy CurrentSeparatorNormal - SteadyStateE10CD12 (P)PT53-05-101-990.08,760.00.020,800.020.0100.0OS6Ash HandlingNonferrous LoadoutHopperNormal - SteadyStateE11CD12 (P)PT53-05-101-990.08,760.00.020,800.020.0100.0Page 3 of 4New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryWHEELABRATOR GLOUCESTER COMPANY L P (55793)BOP090002Date:2/25/2010U 5 Ash Handling Ash and Metals Loadout BuildingUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS7Ash HandlingPrimary Ash ConditioningEquipmentNormal - SteadyStateE12CD12 (P)PT53-05-101-990.08,760.00.020,800.020.0100.0Page 4 of 4Date:2/25/2010New Jersey Department of Environmental ProtectionSubject Item Group InventoryGR1 NSPsGroup NJID:Members:TypeIDOSStepUU 1OS0 SummaryUU 4OS0 SummaryUU 5OS0 SummaryFormal Reason(s) for Group/Cap:9OtherOther (explain):Equipment subject to common requirements from 40 CFR Subpart FFFCondition/Requirements that will be complied with or are no longerapplicable as a result of this Group:Operating Circumstances:Page 1 of 1