Report

on measurements of flue gas emissions and efficiency in combination with a type test of a boiler for solid fuel

Test laboratory TUV SUD Industrie Service GmbH Priafbereich Warmetechnik DAkkS Akkreditation no. D-PL-14153-04 accredited according to DIN EN ISO/IEC 17025
Subject of test Heating boiler for solid fuel Type: BioWIN 100 Fuel: Compressed wood Fuel fed: automatic stoking Combustion air supply: with an induced draught fan
Customer Windhager Zentralheizung Technik GmbH Anton-Windhager-Strasse 20 5201 SEEKIRCHEN, AUSTRIA Date: 2012-03-28 Our reference: IS-TAF-MUCIsi Reportno.H-DK1 1190-01112 Order no. 1806552

Document: H-DK7 1190 0112.doc

Page 1 This document includes 4 pages

Manufacturer

Scope Windhager Zentralheizung Technik GmbH Anton-Windhager-Strasse 20 5201 SEEKIRCHEN, AUSTRIA

Evaluation of CO emissions Evaluation of emissions of unburnt hydrocarbons Evaluation of dust emissions Evaluation of efficiency Excerpts from this document may only be reproduced and used foradvertising purposes with the express written approval of TUV SUD Industrie Service GmbH.

The test results refer exclusively to the units under test.

Expert Dipl.-Ing. Uwe Schlosser

Period of test March 2012

Basis of test DIN EN 303-5:1999-06, clause 4.2 

### DAkkS
Deutlsche Akkredltlerungsstelle D-PL-14153-04-00

Headquarlers: Munich Telefon: i49 89 5190 -1027 Trade Register Munich HRB 96 869 SupervisoryBoard: Telefax:+49 89 51 90-3307 VAT ID No. DE129484218 Karslen Xander (Chairman) E-mall feuerung@tuev-sued.de Informa6onpursuanttoSec8on2(1) Board of Management: www.tuevsued.delis DL-InfoV (Germany) at Ferdinand Neuwieser (CEO), ® wrvw.tuev-sued.comfmprint Dr. Ulrich Klotz, Thomas Kainz TW TUV SUD Industrie Service GmbH Feuemngs- und Warmetechnik Ridlerstrasse 65 80339 Munich GermanyPage 2 of 4

Our reference / date: IS-TAF-MUC/sl, 2012-03-28 Document: H-DK11190_0112.doc Report no. H-DK1 1190-01/12 

### 'RN i % sua''

industrie Service

Scope The manufacturer orders the evaluation of ineasurements on flue gas emissions and efficiency. Basis for the evaluation are the results documented in the test report no. H-C1 1190-02/08 dated 2008-03-15.

Basis of test DIN EN 303-5:1999-06 Heating boilers for solid fuels, hand and automatically stocked, nominal heat output of up to 300 kW, clause 4.2

Test documentation Test report no. H-C1 1190-02/08 dated 2008-03-15 on the test of performance requirements of the heating boiler type BioWIN 100

4 Description The boiler was type-tested according to the requirements of DIN EN 303-5:1999-06 by the test laboratory for firing and heating technology of TOV SOD Industrie Service GmbH. A detailed description of the boiler and the test for boiler perFormance are documented in test report no. H-C1 1190-02/08. In the type test a measurement was included for CO, unburnt hydrocarbons, dust emission and efficiency.Page 3 of 4

Our reference / date: IS-TAF-MUC/sl, 2012-03-28 Document: H-DK71190_0112.doc Report no. H-0K1 1190-01/12 Tw` j

Intluslrie Service

5 Measurement and analysis methods 5.1 CO 2 / CO measurement For the CO 2 / CO measurement a calibrated device on the principle infrared absorption was used. The values are measured continuously during the complete test period. The mean values for CO 2 / CO are 13.4 % / 60 ppm (maximum load) 10.6 % / 153 ppm (minimum load) 5.2 Unburnt Hydrocarbons For the measurement of unburnt hydrocarbons a calibrated device on the principle of flame ionisation detection (FID) was used. The calibration was performed on the basis of propane (C 3 1-1 8 ). The values for unburnt hydrocarbons are measured continuously during the complete test period. The mean values for unburnt hydrocarbons are 1 ppm (maximum load) 2 ppm (minimum load) 5.3 Particulate emission (dust) For the measurement of the particulate emission (dust) a calibrated filter instrument and a calibrated balance were used in a gravimetric procedure according to CEN/TS 15883, annex A. The dust emission was measured 4 times in the test period. Each period of measurement takes 30 minutes with a constant volume of the sample. The mean values for dust emission are

- 17 mg/m' (maximum load, related to standard reference conditions)

- 27 mg/m 3 (minimum load, related to standard reference conditions) 5.4 Efficiency The test was perFormed by TOV SOD Industrie Service GmbH using a test rig according to picture A.2 of EN 304:2004-01. The values are measured continuously during the complete test period. The mean values for direct efficiency are 93.2 % (maximum load) 90.9 % (minimum load)Page 4 of 4

Ourreference/date:IS-TAF-MUC/sI,2012-03-28 ~ . Document: H-DK11190_0112.doc T'('J ~~ ~ Reportno.H-DK71190-01/12

~ sup7 ~'~ F .;' Industrie Service

Summary The emissions and efficiency as documented in report no. H-C1 1190-02/08 are measured

in line with EN 303-5 regarding the determination of inorganic and organic gaseous or particulate air constituents, using existing procedures in the quality system of the laboratory for firing and heating technology and

- using calibrated measurement devices.

The calculation of the measured emissions data with reference to 10 % 0 2 and on the measured data on efficiency as required by EN 303-5 is documented in the test report no. H-C1 1190-02/08.

Feuerungs- und Wtirmetechnik Prufbe eich Warmetechnik

Johannes Ste 

## ~ glechner The Expert

t Ae 

## ~ Uwe Schlosser