Name: Gary Kowalczyk

Title: General Manager Martin Plant

Company: Florida Power & Light

Sign Date: 7/29/2010

Name: Thomas K. Graham

Title: Director of Operations

Company: Air Hygiene International, Inc.

Sign Date: 6/9/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Martin Energy Center, Unit #2, Information Collection Request

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 15, 2011 Page 1 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Facility Information:

Martin Energy Center

21900 SW Warfield Boulevard, SR 710

Indiantown FL 34956

Contact: Augie De La Vega

Phone: (305) 242-3896

Fax:

Email: augie.de.la.vega@fpl.com

Testing Company:

Air Hygiene International, Inc.

5634 S. 122nd East Ave, Suite F

Tulsa OK 74146

Contact:Thomas Graham

Phone: (918) 307-8865

Fax: (918) 307-9131

Email: tom@airhygiene.com

Air Permit Number:

0850001-018-AV

Permitted Source ID/Name:

PMR2 Foster Wheeler, Wall Fired Boiler

Permitted Maximum Process Rate:

863.3 MW

Max. Normal Operation Process Rate:

800 MW

Target Process Test Rate

800 MW

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster 

Wheeler design, designated as Units PMR1 and PMR2. The facility is located at 21900 Southwest Warfield 

Boulevard, State Route 710 in Indiantown, Florida. Unit PMR1 and PMR2 are of identical design and consists of 

two wall fired boilers and ancillary equipment designed to generate 863.3 megawatts (MW) of electricity each with 

rated heat inputs of 8,650 million British thermal units per hour (MMBtu/hr) based on high heating value (HHV). 

Fuel oil consumption is rated at 600,000 pounds per hour. Unit PMR1 and PMR2 utilize low nitrogen oxide (NOx) 

burner technology to control NOx emissions and cyclone separators to control particulate matter (PM) emissions. 

Emission testing will be conducted from platforms on the independent stacks of each unit.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 0850001 FRS #: 110008320566

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

PMR2 - D/F 357.4 0 0 0 4524 876 4 24

PMR2 - Gases 357.4 0 0 0 4524 876 4 1

PMR2 - Metals 357.4 0 0 0 4524 876 4 24

PMR2 - PM 357.4 0 0 0 4524 876 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Regulation Description Compound Limit Unit

Not applicable.

Tuesday, February 15, 2011 Page 2 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

PMR2 - D/F % H2O Method 1 - 4 3 480 24

PMR2 - D/F 2,3,7,8-TCDD Method 23 3 480 24

PMR2 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 24

PMR2 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 24

PMR2 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 24

PMR2 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 24

PMR2 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 24

PMR2 - D/F OCDD Method 23 3 480 24

PMR2 - D/F 2,3,7,8-TCDF Method 23 3 480 24

PMR2 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 24

PMR2 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 24

PMR2 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 24

PMR2 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 24

PMR2 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 24

PMR2 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 24

PMR2 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 24

PMR2 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 24

PMR2 - D/F OCDF Method 23 3 480 24

PMR2 - D/F Total Dioxins Method 23 3 480 24

PMR2 - D/F Total Furans Method 23 3 480 24

PMR2 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 24

PMR2 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 24

PMR2 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 24

PMR2 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 24

PMR2 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 24

PMR2 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 24

PMR2 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 24

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

PMR2 - D/F Method 23 3 480 24

PMR2 - D/F 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 24

PMR2 - D/F 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 24

2,3,3',4,4',5,5'-HpCB 

(PCB189)

PMR2 - D/F Method 23 3 480 24

PMR2 - D/F O2 Method 3A O2 3 480 24

PMR2 - D/F Co2 Method 3A CO2 3 480 24

% H2O Method 1 - 4 3 120 1 Determined after 

initial stratification test

PMR2 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after 

initial stratification test

PMR2 - Gases

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 1 Determined after 

initial stratification test

PMR2 - Gases

O2 Method 3A O2 3 120 1 Determined after 

initial stratification test

PMR2 - Gases

Co2 Method 3A CO2 3 120 1 Determined after 

initial stratification test

PMR2 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after 

initial stratification test

PMR2 - Gases

Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after 

initial stratification test

PMR2 - Gases

PMR2 - Metals% H2O Method 1 - 4 3 240 24

PMR2 - MetalsSelenium Method 29 3 240 24

PMR2 - MetalsManganese Method 29 3 240 24

Tuesday, February 15, 2011 Page 3 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

PM Run All - reduced to 2 hour runs to avoid high vacuum, did not pull required volumes.
PM Run 3 - oily 

substance in organic backhalf.

PMR2 - MetalsLead Method 29 3 240 24

PMR2 - MetalsFilterable Particulate Method 29 3 240 24

PMR2 - MetalsCobalt Method 29 3 240 24

PMR2 - MetalsCadmium Method 29 3 240 24

PMR2 - MetalsChromium Method 29 3 240 24

PMR2 - MetalsNickel Method 29 3 240 24

PMR2 - MetalsCo2 Method 3A CO2 3 240 24

PMR2 - MetalsO2 Method 3A O2 3 240 24

% H2O Method 1 - 4 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Filterable Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Filterable PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Organic Condensible 

Particulate

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Total PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Total Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

O2 Method 3A O2 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Co2 Method 3A CO2 3 120 12 Run times vary based 

on method calculations

PMR2 - PM

Tuesday, February 15, 2011 Page 4 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Sampling / Stack Data Results Summary

Location PMR2 - D/F - Method 23

Average

Run Number PMR2-23-1 PMR2-23-

2

PMR2-23-3

Test Date 4/13/2010 4/14/2010 4/15/2010

Run Start Time 8:30:00 AM 8:20:00 

AM

8:29:00 AM

Run Finish Time 4:30:00 PM 4:20:00 PM 4:29:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 366.702 307.304 312.237 328.748

Moisture Content of Stack Gas, % 9.58 10.01 9.57 9.720

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.82 13.81 13.89 13.840

Oxygen, % 4.04 4.13 4 4.057

Average Stack Gas Temperature, °F 323.63 325.50 327.00 325.377

Dry Volumetric Flow Rate, dry scfm 1,551,963.0 1,325,062.4 1,342,738.0 1,406,587.80

0

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,563,661.5 2,197,901.8 2,218,384.4 2,326,649.23

3

Percent Isokinetic of Sampling Rate, % 100.6 98.7 99.0 99.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR2 - Gases - Method 10

Average

Run Number 2-CO-1 2-CO-2 2-CO-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 5 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 25A

Average

Run Number 2-THC-1 2-THC-2 2-THC-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR2 - Gases - Method 3A CO2

Average

Run Number 2-CO2-1 2-CO2-2 2-CO2-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 6 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 3A O2

Average

Run Number 2-O2-1 2-O2-2 2-O2-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR2 - Gases - Method 6C

Average

Run Number 2-SO2-1 2-SO2-2 2-SO2-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 7 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 7E

Average

Run Number 2-NOx-1 2-NOx-2 2-NOx-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.00

0

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PMR2 - Metals - Method 29

Average

Run Number PMR2-29-1 PMR2-29-

2

PMR2-29-3

Test Date 4/13/2010 4/13/2010 4/14/2010

Run Start Time 9:20:00 AM 2:10:00 PM 11:06:00 AM

Run Finish Time 1:20:00 PM 6:10:00 PM 3:06:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 181.467 162.907 194.024 179.466

Moisture Content of Stack Gas, % 10.35 10.19 9.83 10.123

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.82 13.82 13.81 13.817

Oxygen, % 4.04 4.04 4.13 4.070

Average Stack Gas Temperature, °F 317.88 324.17 326.92 322.990

Dry Volumetric Flow Rate, dry scfm 1,566,802.6 1,372,399.4 1,636,364.7 1,525,188.90

0

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,591,250.2 2,279,414.0 2,708,293.3 2,526,319.16

7

Percent Isokinetic of Sampling Rate, % 98.6 101.1 101.0 100.233

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 8 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - PM - OTM - 27/28

Average

Run Number PMR2-

27/28-1

PMR2-

27/28-2

PMR2-

27/28-3

Test Date 4/12/2010 4/12/2010 4/14/2010

Run Start Time 2:38:00 PM 6:49:00 PM 8:23:00 AM

Run Finish Time 5:34:00 PM 9:30:00 PM 10:56:00 AM

Net Run Time, minutes 129 126 127

Dry Gas Meter Volume Sampled, dscf 44.745 42.447 43.709 43.634

Moisture Content of Stack Gas, % 9.54 9.43 9.45 9.473

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.82 13.82 13.89 13.843

Oxygen, % 4.04 4.04 4 4.027

Average Stack Gas Temperature, °F 314.58 313.58 324.00 317.387

Dry Volumetric Flow Rate, dry scfm 1,390,346.0 1,407,916.1 1,455,776.5 1,418,012.86

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,266,873.7 2,293,626.4 2,395,203.0 2,318,567.70

0

Percent Isokinetic of Sampling Rate, % 107.7 103.3 102.1 104.367

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 9 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Emissions Summary

Location: PMR2 - D/F - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000081 0.00000000559 0.0000000039 0.000

lb/mmBtuO2 5.55E-13 4.59E-13 3.13E-13 0.000

ng/dscm 7.80E-04 6.42E-04 4.41E-04 0.001

ng/dscm@7%O2 6.43E-04 5.32E-04 3.63E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000096 0.0000000062 0.0000000011 0.000

lb/mmBtuO2 6.58E-13 5.09E-13 8.83E-14 0.000

ng/dscm 9.25E-04 7.13E-04 1.24E-04 0.001

ng/dscm@7%O2 7.63E-04 5.91E-04 1.02E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000023 0.0000000029 0.0000000014 0.000

lb/mmBtuO2 1.58E-13 2.38E-13 1.12E-13 0.000

ng/dscm 2.22E-04 3.33E-04 1.58E-04 0.000

ng/dscm@7%O2 1.83E-04 2.76E-04 1.30E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000024 0.0000000023 0.0000000012 0.000

lb/mmBtuO2 1.64E-13 1.89E-13 9.63E-14 0.000

ng/dscm 2.31E-04 2.64E-04 1.36E-04 0.000

ng/dscm@7%O2 1.90E-04 2.19E-04 1.12E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000017 0.0000000014 0.0000000026 0.000

lb/mmBtuO2 1.16E-13 1.15E-13 2.09E-13 0.000

ng/dscm 1.64E-04 1.61E-04 2.94E-04 0.000

ng/dscm@7%O2 1.35E-04 1.33E-04 2.42E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000033 0.0000000016 0.0000000012 0.000

lb/mmBtuO2 2.26E-13 1.31E-13 9.63E-14 0.000

ng/dscm 3.18E-04 1.84E-04 1.36E-04 0.000

ng/dscm@7%O2 2.62E-04 1.53E-04 1.12E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Tuesday, February 15, 2011 Page 10 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000016 0.0000000015 0.00000000095 0.000

lb/mmBtuO2 1.10E-13 1.23E-13 7.62E-14 0.000

ng/dscm 1.54E-04 1.72E-04 1.07E-04 0.000

ng/dscm@7%O2 1.27E-04 1.43E-04 8.80E-05 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000000236 0.0000000016 0.0000000012 0.000

lb/mmBtuO2 1.62E-13 1.31E-13 9.63E-14 0.000

ng/dscm 2.27E-04 1.84E-04 1.36E-04 0.000

ng/dscm@7%O2 1.87E-04 1.53E-04 1.12E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000018 0.0000000014 0.0000000011 0.000

lb/mmBtuO2 1.23E-13 1.15E-13 8.83E-14 0.000

ng/dscm 1.73E-04 1.61E-04 1.24E-04 0.000

ng/dscm@7%O2 1.43E-04 1.33E-04 1.02E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000025 0.000000002 0.0000000014 0.000

lb/mmBtuO2 1.71E-13 1.64E-13 1.12E-13 0.000

ng/dscm 2.41E-04 2.30E-04 1.58E-04 0.000

ng/dscm@7%O2 1.99E-04 1.91E-04 1.30E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000000327 0.0000000017 0.000000001 0.000

lb/mmBtuO2 2.24E-13 1.40E-13 8.02E-14 0.000

ng/dscm 3.15E-04 1.95E-04 1.13E-04 0.000

ng/dscm@7%O2 2.60E-04 1.62E-04 9.29E-05 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000027 0.000000003 0.0000000018 0.000

lb/mmBtuO2 1.85E-13 2.46E-13 1.44E-13 0.000

ng/dscm 2.60E-04 3.45E-04 2.04E-04 0.000

ng/dscm@7%O2 2.14E-04 2.86E-04 1.68E-04 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000146 0.0000000071 0.0000000051 0.000

lb/mmBtuO2 1.00E-12 5.83E-13 4.09E-13 0.000

ng/dscm 1.41E-03 8.16E-04 5.77E-04 0.001

ng/dscm@7%O2 1.16E-03 6.76E-04 4.75E-04 0.001

Tuesday, February 15, 2011 Page 11 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.000000376 0.000000257 0.000000197 0.000

lb/mmBtuO2 2.58E-11 2.11E-11 1.58E-11 0.000

ng/dscm 3.62E-02 2.95E-02 2.23E-02 0.029

ng/dscm@7%O2 2.98E-02 2.45E-02 1.83E-02 0.024

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000259 0.00000002 0.0000000165 0.000

lb/mmBtuO2 1.77E-12 1.64E-12 1.32E-12 0.000

ng/dscm 2.49E-03 2.30E-03 1.87E-03 0.002

ng/dscm@7%O2 2.05E-03 1.91E-03 1.54E-03 0.002

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000392 0.0000000201 0.0000000187 0.000

lb/mmBtuO2 2.68E-12 1.65E-12 1.50E-12 0.000

ng/dscm 3.78E-03 2.31E-03 2.12E-03 0.003

ng/dscm@7%O2 3.12E-03 1.91E-03 1.74E-03 0.002

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000104 0.000000773 0.00000058 0.000

lb/mmBtuO2 7.12E-11 6.35E-11 4.65E-11 0.000

ng/dscm 1.00E-01 8.88E-02 6.56E-02 0.085

ng/dscm@7%O2 8.24E-02 7.36E-02 5.40E-02 0.070

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000002 0.0000000185 0.0000000119 0.000

lb/mmBtuO2 1.37E-12 1.52E-12 9.55E-13 0.000

ng/dscm 1.93E-03 2.13E-03 1.35E-03 0.002

ng/dscm@7%O2 1.59E-03 1.77E-03 1.11E-03 0.001

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000029 0.0000000015 0.00000000097 0.000

lb/mmBtuO2 1.99E-13 1.23E-13 7.78E-14 0.000

ng/dscm 2.79E-04 1.72E-04 1.10E-04 0.000

ng/dscm@7%O2 2.30E-04 1.43E-04 9.05E-05 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000039 0.0000000016 0.00000000093 0.000

lb/mmBtuO2 2.67E-13 1.31E-13 7.46E-14 0.000

Tuesday, February 15, 2011 Page 12 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

ng/dscm 3.76E-04 1.84E-04 1.05E-04 0.000

ng/dscm@7%O2 3.10E-04 1.53E-04 8.64E-05 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000024 0.000000002 0.0000000019 0.000

lb/mmBtuO2 1.64E-13 1.64E-13 1.52E-13 0.000

ng/dscm 2.31E-04 2.30E-04 2.15E-04 0.000

ng/dscm@7%O2 1.90E-04 1.91E-04 1.77E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.000000005 0.000000002 0.0000000013 0.000

lb/mmBtuO2 3.42E-13 1.64E-13 1.04E-13 0.000

ng/dscm 4.82E-04 2.30E-04 1.47E-04 0.000

ng/dscm@7%O2 3.97E-04 1.91E-04 1.21E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000000235 0.00000000079 0.0000000013 0.000

lb/mmBtuO2 1.61E-13 6.49E-14 1.04E-13 0.000

ng/dscm 2.26E-04 9.08E-05 1.47E-04 0.000

ng/dscm@7%O2 1.86E-04 7.53E-05 1.21E-04 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000031 0.0000000031 0.0000000028 0.000

lb/mmBtuO2 2.12E-13 2.55E-13 2.25E-13 0.000

ng/dscm 2.99E-04 3.56E-04 3.17E-04 0.000

ng/dscm@7%O2 2.47E-04 2.95E-04 2.61E-04 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.000000131 0.0000000958 0.0000000675 0.000

lb/mmBtuO2 8.97E-12 7.87E-12 5.42E-12 0.000

ng/dscm 1.26E-02 1.10E-02 7.64E-03 0.010

ng/dscm@7%O2 1.04E-02 9.12E-03 6.28E-03 0.009

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000000804 0.00000000538 0.00000000424 0.000

lb/mmBtuO2 5.51E-13 4.42E-13 3.40E-13 0.000

ng/dscm 7.74E-04 6.18E-04 4.80E-04 0.001

ng/dscm@7%O2 6.38E-04 5.12E-04 3.95E-04 0.001

Compound: OCDD

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Tuesday, February 15, 2011 Page 13 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Mass_mg 0.000000022 0.0000000048 0.0000000224 0.000

lb/mmBtuO2 1.51E-12 3.94E-13 1.80E-12 0.000

ng/dscm 2.12E-03 5.52E-04 2.53E-03 0.002

ng/dscm@7%O2 1.75E-03 4.58E-04 2.08E-03 0.001

Compound: OCDF

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.0000000062 0.0000000047 0.0000000116 0.000

lb/mmBtuO2 4.25E-13 3.86E-13 9.31E-13 0.000

ng/dscm 5.97E-04 5.40E-04 1.31E-03 0.001

ng/dscm@7%O2 4.92E-04 4.48E-04 1.08E-03 0.001

Compound: Total Dioxins

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000004306 0.00000001989 0.0000000332 0.000

lb/mmBtuO2 2.95E-12 1.63E-12 2.66E-12 0.000

ng/dscm 4.15E-03 2.29E-03 3.76E-03 0.003

ng/dscm@7%O2 3.42E-03 1.90E-03 3.09E-03 0.003

Compound: Total Furans

Average

RunNumber PMR2-23-1 PMR2-23-2 PMR2-23-3

Mass_mg 0.00000003827 0.0000000249 0.00000002295 0.000

lb/mmBtuO2 2.62E-12 2.05E-12 1.84E-12 0.000

ng/dscm 3.69E-03 2.86E-03 2.60E-03 0.003

ng/dscm@7%O2 3.04E-03 2.37E-03 2.14E-03 0.003

Location: PMR2 - Gases - Method 10

Compound: Carbon Monoxide

Average

Run 2-CO-1 2-CO-2 2-CO-3

lb/mmBtuO2 4.60E-01 4.55E-01 5.49E-01 0.488

ppm 5.52E+02 5.51E+02 6.66E+02 589.667

ppm@7%O2 4.58E+02 4.53E+02 5.47E+02 486.000

Location: PMR2 - Gases - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 2-THC-1 2-THC-2 2-THC-3

lb/mmBtuO2 1.22E-03 2.22E-04 3.75E-04 0.001

ppm 9.26E-01 1.70E-01 2.89E-01 0.462

ppm@7%O2 7.68E-01 1.40E-01 2.37E-01 0.382

Location: PMR2 - Gases - Method 6C

Compound: Sulfur Dioxide

Average

Run 2-SO2-1 2-SO2-2 2-SO2-3

lb/mmBtuO2 4.69E-01 5.96E-01 6.29E-01 0.565

ppm 2.46E+02 3.15E+02 3.33E+02 298.000

ppm@7%O2 2.04E+02 2.59E+02 2.73E+02 245.333

Tuesday, February 15, 2011 Page 14 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location: PMR2 - Gases - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 2-NOx-1 2-NOx-2 2-NOx-3

lb/mmBtuO2 2.96E-01 2.97E-01 2.98E-01 0.297

ppm 2.16E+02 2.19E+02 2.20E+02 218.333

ppm@7%O2 1.79E+02 1.80E+02 1.81E+02 180.000

Location: PMR2 - Metals - Method 29

Compound: Antimony

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.326 0.144 0.36 0.277

Elb/hr 3.72E-01 1.60E-01 4.02E-01 0.311

lb/mmBtuO2 4.51E-05 2.22E-05 4.69E-05 0.000

mg/dscm 6.35E-02 3.12E-02 6.55E-02 0.053

mg/dscm@7%O2 5.24E-02 2.57E-02 5.43E-02 0.044

Compound: Arsenic

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.0178 0.012 0.0249 0.018

Elb/hr 2.03E-02 1.34E-02 2.78E-02 0.021

lb/mmBtuO2 2.46E-06 1.85E-06 3.24E-06 0.000

mg/dscm 3.46E-03 2.60E-03 4.53E-03 0.004

mg/dscm@7%O2 2.85E-03 2.14E-03 3.75E-03 0.003

Compound: Beryllium

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.00162 0.00117 0.00188 0.002

Elb/hr 1.85E-03 1.30E-03 2.10E-03 0.002

lb/mmBtuO2 2.24E-07 1.80E-07 2.45E-07 0.000

mg/dscm 3.15E-04 2.54E-04 3.42E-04 0.000

mg/dscm@7%O2 2.60E-04 2.09E-04 2.83E-04 0.000

Compound: Cadmium

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.000659 0.00044 0.000586 0.001

Elb/hr 7.53E-04 4.90E-04 6.54E-04 0.001

lb/mmBtuO2 9.12E-08 6.78E-08 7.63E-08 0.000

mg/dscm 1.28E-04 9.54E-05 1.07E-04 0.000

mg/dscm@7%O2 1.06E-04 7.87E-05 8.87E-05 0.000

Compound: Chromium

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.0439 0.0275 0.0404 0.037

Elb/hr 5.01E-02 3.06E-02 4.51E-02 0.042

lb/mmBtuO2 6.08E-06 4.24E-06 5.26E-06 0.000

mg/dscm 8.54E-03 5.96E-03 7.35E-03 0.007

Tuesday, February 15, 2011 Page 15 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

mg/dscm@7%O2 7.04E-03 4.91E-03 6.09E-03 0.006

Compound: Cobalt

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.229 0.114 0.261 0.201

Elb/hr 2.62E-01 1.27E-01 2.91E-01 0.227

lb/mmBtuO2 3.17E-05 1.76E-05 3.40E-05 0.000

mg/dscm 4.46E-02 2.47E-02 4.75E-02 0.039

mg/dscm@7%O2 3.68E-02 2.04E-02 3.94E-02 0.032

Compound: Filterable Particulate

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 167.8 52.2 194.9 138.300

Elb/hr 1.92E+02 5.82E+01 2.17E+02 155.733

lb/mmBtuO2 2.32E-02 8.05E-03 2.54E-02 0.019

mg/dscm 3.27E+01 1.13E+01 3.55E+01 26.500

mg/dscm@7%O2 2.70E+01 9.32E+00 2.94E+01 21.907

Compound: Lead

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.0727 0.0368 0.0687 0.059

Elb/hr 8.30E-02 4.10E-02 7.66E-02 0.067

lb/mmBtuO2 1.01E-05 5.67E-06 8.94E-06 0.000

mg/dscm 1.42E-02 7.98E-03 1.25E-02 0.012

mg/dscm@7%O2 1.17E-02 6.58E-03 1.04E-02 0.010

Compound: Manganese

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.296 0.168 0.338 0.267

Elb/hr 3.38E-01 1.87E-01 3.77E-01 0.301

lb/mmBtuO2 4.10E-05 2.59E-05 4.40E-05 0.000

mg/dscm 5.76E-02 3.64E-02 6.15E-02 0.052

mg/dscm@7%O2 4.75E-02 3.00E-02 5.10E-02 0.043

Compound: Nickel

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 2.77 1.36 3.12 2.417

Elb/hr 3.16E+00 1.52E+00 3.48E+00 2.720

lb/mmBtuO2 3.83E-04 2.10E-04 4.06E-04 0.000

mg/dscm 5.39E-01 2.95E-01 5.68E-01 0.467

mg/dscm@7%O2 4.44E-01 2.43E-01 4.71E-01 0.386

Compound: Selenium

Average

RunNumber PMR2-29-1 PMR2-29-2 PMR2-29-3

Mass_mg 0.00954 0.00766 0.0258 0.014

Elb/hr 1.09E-02 8.54E-03 2.88E-02 0.016

lb/mmBtuO2 1.32E-06 1.18E-06 3.36E-06 0.000

mg/dscm 1.86E-03 1.66E-03 4.70E-03 0.003

Tuesday, February 15, 2011 Page 16 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Process Run Data

mg/dscm@7%O2 1.53E-03 1.37E-03 3.90E-03 0.002

Location: PMR2 - PM - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber PMR2-27/28-2 PMR2-27/28-3 PMR2-27/28-1

Mass_mg 41.75 43.427 37.825 41.001

lb/mmBtuO2 2.47E-02 2.49E-02 2.12E-02 0.024

Compound: Filterable PM2.5

Average

RunNumber PMR2-27/28-1 PMR2-27/28-2 PMR2-27/28-3

Mass_mg 24.95 38.475 38.125 33.850

lb/mmBtuO2 1.40E-02 2.28E-02 2.19E-02 0.020

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber PMR2-27/28-1 PMR2-27/28-2 PMR2-27/28-3

Mass_mg 2.995 5.859 1.79 3.548

lb/mmBtuO2 1.68E-03 3.47E-03 1.03E-03 0.002

Compound: Organic Condensible Particulate

Average

RunNumber PMR2-27/28-1 PMR2-27/28-2 PMR2-27/28-3

Mass_mg 3.988 3.406 31.306 12.900

lb/mmBtuO2 2.24E-03 2.02E-03 1.79E-02 0.007

Compound: Total Particulate

Average

RunNumber PMR2-27/28-1 PMR2-27/28-2 PMR2-27/28-3

Mass_mg 44.807 51.015 76.524 57.449

lb/mmBtuO2 2.52E-02 3.02E-02 4.39E-02 0.033

Compound: Total PM2.5

Average

RunNumber PMR2-27/28-1 PMR2-27/28-2 PMR2-27/28-3

Mass_mg 31.932 47.74 71.221 50.298

lb/mmBtuO2 1.79E-02 2.82E-02 4.08E-02 0.029

Tuesday, February 15, 2011 Page 17 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Residual Oil (No. 6) Burned 56990 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/13/2010; 

Start - 15:25; 

End - 17:24

0

10 Residual Oil (No. 6) Burned 56486 gal/hr Method 027/028; 

Run PM-1; Date - 

4/12/2010; Start - 

14:38; End - 17:34

0

11 Residual Oil (No. 6) Burned 56457 gal/hr Method 027/028; 

Run PM-2; Date - 

4/12/2010; Start - 

18:49; End - 21:30

0

12 Residual Oil (No. 6) Burned 57570 gal/hr Method 027/028; 

Run PM-3; Date - 

4/14/2010; Start - 

08:23; End - 10:56

0

2 Residual Oil (No. 6) Burned 57005 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/13/2010; 

Start - 17:43; 

End - 19:42

0

3 Residual Oil (No. 6) Burned 57474 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/13/2010; 

Start - 19:52; 

End - 21:51

0

4 Residual Oil (No. 6) Burned 57101 gal/hr Method 23; Run 

D/F-1; Date - 

4/13/2010; Start - 

08:30; End - 17:13

0

5 Residual Oil (No. 6) Burned 57570 gal/hr Method 23; Run 

D/F-2; Date - 

4/14/2010; Start - 

08:20; End - 17:00

0

6 Residual Oil (No. 6) Burned 57218 gal/hr Method 23; Run 

D/F-3; Date - 

4/15/2010; Start - 

08:29; End - 16:56

0

7 Residual Oil (No. 6) Burned 57101 gal/hr Method 29; Run 

M-1; Date - 

4/13/2010; Start - 

09:20; End - 13:48

0

Tuesday, February 15, 2011 Page 18 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

8 Residual Oil (No. 6) Burned 57042 gal/hr Method 29; Run 

M-2; Date - 

4/13/2010; Start - 

14:10; End - 18:48

0

9 Residual Oil (No. 6) Burned 57599 gal/hr Method 29; Run 

M-3; Date - 

4/14/2010; Start - 

11:06; End - 15:36

0

1 Average Heat Input 7184 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/13/2010; 

Start - 15:25; 

End - 17:24

0

10 Average Heat Input 7121 MMBtu/hr Method 027/028; 

Run PM-1; Date - 

4/12/2010; Start - 

14:38; End - 17:34

0

11 Average Heat Input 7133 MMBtu/hr Method 027/028; 

Run PM-2; Date - 

4/12/2010; Start - 

18:49; End - 21:30

0

12 Average Heat Input 72585 MMBtu/hr Method 027/028; 

Run PM-3; Date - 

4/14/2010; Start - 

08:23; End - 10:56

0

2 Average Heat Input 7187 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/13/2010; 

Start - 17:43; 

End - 19:42

0

3 Average Heat Input 7245 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/13/2010; 

Start - 19:52; 

End - 21:51

0

4 Average Heat Input 7199 MMBtu/hr Method 23; Run 

D/F-1; Date - 

4/13/2010; Start - 

08:30; End - 17:13

0

5 Average Heat Input 7258 MMBtu/hr Method 23; Run 

D/F-2; Date - 

4/14/2010; Start - 

08:20; End - 17:00

0

6 Average Heat Input 7213 MMBtu/hr Method 23; Run 

D/F-3; Date - 

4/15/2010; Start - 

08:29; End - 16:56

0

Tuesday, February 15, 2011 Page 19 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

7 Average Heat Input 7199 MMBtu/hr Method 29; Run 

M-1; Date - 

4/13/2010; Start - 

09:20; End - 13:48

0

8 Average Heat Input 7191 MMBtu/hr Method 29; Run 

M-2; Date - 

4/13/2010; Start - 

14:10; End - 18:48

0

9 Average Heat Input 7262 MMBtu/hr Method 29; Run 

M-3; Date - 

4/14/2010; Start - 

11:06; End - 15:36

0

1 Steam Output 5191 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/13/2010; 

Start - 15:25; 

End - 17:24

0

10 Steam Output 5147 1000 lb Method 027/028; 

Run PM-1; Date - 

4/12/2010; Start - 

14:38; End - 17:34

0

11 Steam Output 5141 1000 lb Method 027/028; 

Run PM-2; Date - 

4/12/2010; Start - 

18:49; End - 21:30

0

12 Steam Output 5214 1000 lb Method 027/028; 

Run PM-3; Date - 

4/14/2010; Start - 

08:23; End - 10:56

0

2 Steam Output 5173 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/13/2010; 

Start - 17:43; 

End - 19:42

0

3 Steam Output 5184 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/13/2010; 

Start - 19:52; 

End - 21:51

0

4 Steam Output 5176 1000 lb Method 23; Run 

D/F-1; Date - 

4/13/2010; Start - 

08:30; End - 17:13

0

5 Steam Output 5194 1000 lb Method 23; Run 

D/F-2; Date - 

4/14/2010; Start - 

08:20; End - 17:00

0

Tuesday, February 15, 2011 Page 20 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

6 Steam Output 5150 1000 lb Method 23; Run 

D/F-3; Date - 

4/15/2010; Start - 

08:29; End - 16:56

0

7 Steam Output 5170 1000 lb Method 29; Run 

M-1; Date - 

4/13/2010; Start - 

09:20; End - 13:48

0

8 Steam Output 5189 1000 lb Method 29; Run 

M-2; Date - 

4/13/2010; Start - 

14:10; End - 18:48

0

9 Steam Output 5187 1000 lb Method 29; Run 

M-3; Date - 

4/14/2010; Start - 

11:06; End - 15:36

0

1 Unit Gross Electrical Output 802 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/13/2010; 

Start - 15:25; 

End - 17:24

0

10 Unit Gross Electrical Output 800 MWg Method 027/028; 

Run PM-1; Date - 

4/12/2010; Start - 

14:38; End - 17:34

0

11 Unit Gross Electrical Output 800 MWg Method 027/028; 

Run PM-2; Date - 

4/12/2010; Start - 

18:49; End - 21:30

0

12 Unit Gross Electrical Output 803 MWg Method 027/028; 

Run PM-3; Date - 

4/14/2010; Start - 

08:23; End - 10:56

0

2 Unit Gross Electrical Output 802 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/13/2010; 

Start - 17:43; 

End - 19:42

0

3 Unit Gross Electrical Output 803 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/13/2010; 

Start - 19:52; 

End - 21:51

0

4 Unit Gross Electrical Output 802 MWg Method 23; Run 

D/F-1; Date - 

4/13/2010; Start - 

08:30; End - 17:13

0

Tuesday, February 15, 2011 Page 21 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

5 Unit Gross Electrical Output 803 MWg Method 23; Run 

D/F-2; Date - 

4/14/2010; Start - 

08:20; End - 17:00

0

6 Unit Gross Electrical Output 799 MWg Method 23; Run 

D/F-3; Date - 

4/15/2010; Start - 

08:29; End - 16:56

0

7 Unit Gross Electrical Output 802 MWg Method 29; Run 

M-1; Date - 

4/13/2010; Start - 

09:20; End - 13:48

0

8 Unit Gross Electrical Output 802 MWg Method 29; Run 

M-2; Date - 

4/13/2010; Start - 

14:10; End - 18:48

0

9 Unit Gross Electrical Output 802 MWg Method 29; Run 

M-3; Date - 

4/14/2010; Start - 

11:06; End - 15:36

0

1 Unit Net Electric Generation 774 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 4/13/2010; 

Start - 15:25; 

End - 17:24

0

10 Unit Net Electric Generation 771 MWn Method 027/028; 

Run PM-1; Date - 

4/12/2010; Start - 

14:38; End - 17:34

0

11 Unit Net Electric Generation 771 MWn Method 027/028; 

Run PM-2; Date - 

4/12/2010; Start - 

18:49; End - 21:30

0

12 Unit Net Electric Generation 773 MWn Method 027/028; 

Run PM-3; Date - 

4/14/2010; Start - 

08:23; End - 10:56

0

2 Unit Net Electric Generation 773 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 4/13/2010; 

Start - 17:43; 

End - 19:42

0

3 Unit Net Electric Generation 773 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 4/13/2010; 

Start - 19:52; 

End - 21:51

0

Tuesday, February 15, 2011 Page 22 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

APCD Run Data

Process Lab Run Data

4 Unit Net Electric Generation 774 MWn Method 23; Run 

D/F-1; Date - 

4/13/2010; Start - 

08:30; End - 17:13

0

5 Unit Net Electric Generation 774 MWn Method 23; Run 

D/F-2; Date - 

4/14/2010; Start - 

08:20; End - 17:00

0

6 Unit Net Electric Generation 771 MWn Method 23; Run 

D/F-3; Date - 

4/15/2010; Start - 

08:29; End - 16:56

0

7 Unit Net Electric Generation 774 MWn Method 29; Run 

M-1; Date - 

4/13/2010; Start - 

09:20; End - 13:48

0

8 Unit Net Electric Generation 774 MWn Method 29; Run 

M-2; Date - 

4/13/2010; Start - 

14:10; End - 18:48

0

9 Unit Net Electric Generation 774 MWn Method 29; Run 

M-3; Date - 

4/14/2010; Start - 

11:06; End - 15:36

0

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 194 NOx Emissions 0

2 LOW NOX BURNERS 194 NOx Emissions 0

3 LOW NOX BURNERS 195 NOx Emissions 0

1 CYCLONE SEPARATORS 10.6 Opacity 0

2 CYCLONE SEPARATORS 10.7 Opacity 0

3 CYCLONE SEPARATORS 12.2 Opacity 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 18500 Btu/lb

1 Fuel Moisture 0.794 %

1 Fuel Mercury Content 0.001 mg/kg

1 Fuel Chlorine Content 835 mg/kg

1 Fuel Fluorine Content 40 mg/kg

1 Fuel Antimony Content 1.5 mg/kg

1 Fuel Arsenic Content 0.1 mg/kg

1 Fuel Beryllium Content 0.01 mg/kg

Tuesday, February 15, 2011 Page 23 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

1 Fuel Cadmium Content 0.006 mg/kg

1 Fuel Chromium Content 0.081 mg/kg

1 Fuel Cobalt Content 1.2 mg/kg

1 Fuel Lead Content 0.35 mg/kg

1 Fuel Manganese Content 1.5 mg/kg

1 Fuel Nickel Content 12.8 mg/kg

1 Fuel Selenium Content 0.03 mg/kg

1 Fuel Sulfur Content 6550 mg/kg

1 Fuel Proximate Analysis (Carbon) 88.38 %

1 Fuel Proximate Analysis (Hydrogen) 10.32 %

1 Fuel Proximate Analysis (Nitrogen) 0.5 %

1 Fuel Proximate Analysis (Oxygen) 0.5 %

1 Fuel Proximate Analysis (Sulfur) 0.592 %

2 Fuel Higher Heating Value 18500 Btu/lb

2 Fuel Moisture 1.13 %

2 Fuel Mercury Content 0.002 mg/kg

2 Fuel Chlorine Content 107 mg/kg

2 Fuel Fluorine Content 40 mg/kg

2 Fuel Antimony Content 1.5 mg/kg

2 Fuel Arsenic Content 0.092 mg/kg

2 Fuel Beryllium Content 0.01 mg/kg

2 Fuel Cadmium Content 0.007 mg/kg

2 Fuel Chromium Content 0.08 mg/kg

2 Fuel Cobalt Content 1.1 mg/kg

2 Fuel Lead Content 0.35 mg/kg

2 Fuel Manganese Content 1.5 mg/kg

2 Fuel Nickel Content 12.6 mg/kg

2 Fuel Selenium Content 0.03 mg/kg

2 Fuel Sulfur Content 6480 mg/kg

2 Fuel Proximate Analysis (Carbon) 88.03 %

2 Fuel Proximate Analysis (Hydrogen) 10.25 %

2 Fuel Proximate Analysis (Nitrogen) 0.5 %

2 Fuel Proximate Analysis (Oxygen) 0.5 %

2 Fuel Proximate Analysis (Sulfur) 0.647 %

3 Fuel Higher Heating Value 18500 Btu/lb

3 Fuel Moisture 1.33 %

3 Fuel Mercury Content 0.002 mg/kg

3 Fuel Chlorine Content 91.7 mg/kg

3 Fuel Fluorine Content 400 mg/kg

3 Fuel Antimony Content 1.5 mg/kg

3 Fuel Arsenic Content 0.075 mg/kg

3 Fuel Beryllium Content 0.012 mg/kg

3 Fuel Cadmium Content 0.007 mg/kg

Tuesday, February 15, 2011 Page 24 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

3 Fuel Chromium Content 0.078 mg/kg

3 Fuel Cobalt Content 1.2 mg/kg

3 Fuel Lead Content 0.35 mg/kg

3 Fuel Manganese Content 1.5 mg/kg

3 Fuel Nickel Content 12.6 mg/kg

3 Fuel Selenium Content 0.03 mg/kg

3 Fuel Sulfur Content 6430 mg/kg

3 Fuel Proximate Analysis (Carbon) 87.84 %

3 Fuel Proximate Analysis (Hydrogen) 10.33 %

3 Fuel Proximate Analysis (Nitrogen) 0.54 %

3 Fuel Proximate Analysis (Oxygen) 0.5 %

3 Fuel Proximate Analysis (Sulfur) 0.652 %

Tuesday, February 15, 2011 Page 25 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Sampling / Stack Data Results Detail

Location PMR2 - D/F - Method 23

Average

Run Number PMR2-23-1 PMR2-23-2 PMR2-23-3

Test Date 4/13/2010 4/14/2010 4/15/2010

Run Start Time 8:30:00 AM 8:20:00 AM 8:29:00 AM

Run Finish Time 4:30:00 PM 4:20:00 PM 4:29:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.002 0.979 1.002 0.994

Barometric Pressure, inches of Mercury 29.85 29.94 29.97 29.920

Average Orifice Meter Differential, inches H2O 2.04 1.41 1.53 1.660

Dry Gas Meter Volume Sampled, cubic feet 375.190 318.400 317.890 337.160

Average Dry Gas Meter Temperature, °F 82.75 77.79 81.56 80.700

Dry Gas Meter Volume Sampled, dscf 366.702 307.304 312.237 328.748

Total Moisture Liquid collected, g 825 726.5 701.8 751.100

Volume of Water Vapor, standard cubic feet 38.83 34.20 33.03 35.353

Moisture Content of Stack Gas, % 9.58 10.01 9.57 9.720

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9042 0.8999 0.9043 0.903

Carbon Dioxide, % 13.82 13.81 13.89 13.840

Oxygen, % 4.04 4.13 4 4.057

Carbon Monoxide & Nitrogen, % 82.14 82.06 82.11 82.103

Fuel Factor 1.22 1.21 1.22

Dry Molecular Weight, lb/lb-Mole 30.37 30.37 30.38 30.373

Wet Molecular weight, lb/lb-Mole 29.18 29.13 29.20 29.170

Flue Gas Static Pressure, inches of H2O -1.7 -1.7 -1.7 -1.700

Absolute Flue Gas Pressure, inches of Mercury 29.73 29.82 29.85 29.800

Average Stack Gas Temperature, °F 323.63 325.50 327.00 325.377

Average Velocity Head, inches of H2O 0.8075770879

27363

0.592948567

094617

0.604940115

158624

0.668

Average Stack Gas Velocity, feet/second 61.33 52.58 53.07 55.660

Stack Cross-Sectional Area, square feet 696.685 696.685 696.685 696.685

Dry Volumetric Flow Rate, dry scfm 1,551,963.0 1,325,062.4 1,342,738.0 1,406,587.8

00

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,563,661.5 2,197,901.8 2,218,384.4 2,326,649.2

33

Percent Isokinetic of Sampling Rate, % 100.6 98.7 99.0 99.433

Percent Excess Air, % 22.9 23.6 22.6 23.033

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 357.4 357.4 357.4

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 26 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 10

Average

Run Number 2-CO-1 2-CO-2 2-CO-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Analyzer Make THERMO THERMO THERMO

Analyzer Model 48i 48i 48i

Analyzer Serial Number INST-CO0017INST-CO0017INST-CO0017

Operating Range 1109 1109 1109 1,109.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 5 5 5 5.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 5.86 6.51 7.94 6.770

Calibration Pre Zero Cylinder Bias 0.41 0.47 0.6 0.493

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID ALM042523-

CO

ALM042523

-CO

ALM042523-

CO

Calibration Pre High Cylinder Instrument Response 559 551.7 542.06 550.920

Calibration Pre High Cylinder Bias 0.27 -0.39 -1.26 -0.460

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 6.51 7.94 6.24 6.897

Calibration Post Zero Cylinder Bias 0.47 0.6 0.44 0.503

Calibration Post Zero Cylinder Drift 0.06 0.13 0.16 0.117

Calibration Post High Cylinder ID ALM042523-

CO

ALM042523

-CO

ALM042523-

CO

Calibration Post High Cylinder Instrument Response 551.7 542.06 543.01 545.590

Calibration Post High Cylinder Bias -0.39 -1.26 -1.17 -0.940

Calibration Post High Cylinder Drift 0.66 0.87 9.000000000

00001E-02

0.540

Cavg 557.94 549.08 656.16 587.727

Cavg Units ppmvd ppmvd ppmvd

Cgas 551.5892 551.2381 665.5015 589.443

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 27 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 25A

Average

Run Number 2-THC-1 2-THC-2 2-THC-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Analyzer Make VIG VIG VIG

Analyzer Model 20 20 20 20.000

Analyzer Serial Number INST-TH0007INST-TH0007INST-TH0007

Operating Range 50 50 50 50.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 6 6 6 6.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response -0.09 0.09 0.53 0.177

Calibration Pre Zero Cylinder Bias 0 0.36 1.24 0.533

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID CC115743 CC115743 CC115743

Calibration Pre High Cylinder Instrument Response 14.45 14.45 14.21 14.370

Calibration Pre High Cylinder Bias -0.06 -0.06 -0.54 -0.220

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.09 0.53 0.41 0.343

Calibration Post Zero Cylinder Bias 0.36 1.24 1 0.867

Calibration Post Zero Cylinder Drift 0.36 0.88 0.24 0.493

Calibration Post High Cylinder ID CC115743 CC115743 CC115743

Calibration Post High Cylinder Instrument Response 14.45 14.21 14.32 14.327

Calibration Post High Cylinder Bias -0.06 -0.54 -0.32 -0.307

Calibration Post High Cylinder Drift 0 0.48 0.22 0.233

Cavg 0.84 0.46 0.72 0.673

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.9259 0.1704 0.2886 0.462

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0.8370934256

05536

0.154065620

542083

0.260964117

433853

0.417

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 28 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 3A CO2

Average

Run Number 2-CO2-1 2-CO2-2 2-CO2-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Analyzer Make THERMO THERMO THERMO

Analyzer Model 410i 410i 410i

Analyzer Serial Number INST-C2-0010 INST-C2-

0010

INST-C2-

0010

Operating Range 19.3 19.3 19.3 19.300

Operating Units % % %

No. Readings/Avg. 240 240 240 240.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.06 0.29 0.16 0.170

Calibration Pre Zero Cylinder Bias 0.26 1.45 0.78 0.830

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID AAL12025-

CO2

AAL12025-

CO2

AAL12025-

CO2

Calibration Pre High Cylinder Instrument Response 8.8 8.92 8.85 8.857

Calibration Pre High Cylinder Bias -0.52 0.1 -0.26 -0.227

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.29 0.16 0.07 0.173

Calibration Post Zero Cylinder Bias 1.45 0.78 0.31 0.847

Calibration Post Zero Cylinder Drift 1.19 0.67 0.47 0.777

Calibration Post High Cylinder ID AAL12025-

CO2

AAL12025-

CO2

AAL12025-

CO2

Calibration Post High Cylinder Instrument Response 8.92 8.85 8.86 8.877

Calibration Post High Cylinder Bias 0.1 -0.26 -0.21 -0.123

Calibration Post High Cylinder Drift 0.62 0.36 0.05 0.343

Cavg 13.77 13.7 13.59 13.687

Cavg Units %vd %vd %vd

Cgas 13.9159 13.8329 13.7063 13.818

Cgas Units %vd %vd %vd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units %vw %vw %vw

Tuesday, February 15, 2011 Page 29 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 3A O2

Average

Run Number 2-O2-1 2-O2-2 2-O2-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Analyzer Make THERMO THERMO THERMO

Analyzer Model 42i-HL 42i-HL 42i-HL

Analyzer Serial Number INST-N2-0002 INST-N2-

0002

INST-N2-

0002

Operating Range 21.1 21.1 21.1 21.100

Operating Units % % %

No. Readings/Avg. 240 240 240 240.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 0.16 0.24 0.45 0.283

Calibration Pre Zero Cylinder Bias 0.9 1.28 2.27 1.483

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID AAL12025-O2 AAL12025-

O2

AAL12025-

O2

Calibration Pre High Cylinder Instrument Response 12 12.04 12.18 12.073

Calibration Pre High Cylinder Bias -0.28 -0.09 0.57 0.067

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 0.24 0.45 0.36 0.350

Calibration Post Zero Cylinder Bias 1.28 2.27 1.85 1.800

Calibration Post Zero Cylinder Drift 0.38 0.99 0.42 0.597

Calibration Post High Cylinder ID AAL12025-O2 AAL12025-

O2

AAL12025-

O2

Calibration Post High Cylinder Instrument Response 12.04 12.18 12.12 12.113

Calibration Post High Cylinder Bias -0.09 0.57 0.28 0.253

Calibration Post High Cylinder Drift 0.19 0.66 0.29 0.380

Cavg 4.25 4.23 4.25 4.243

Cavg Units %vd %vd %vd

Cgas 4.1459 3.9956 3.9612 4.034

Cgas Units %vd %vd %vd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units %vw %vw %vw

Tuesday, February 15, 2011 Page 30 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 6C

Average

Run Number 2-SO2-1 2-SO2-2 2-SO2-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Analyzer Make THERMO THERMO THERMO

Analyzer Model 43i-HL 43i-HL 43i-HL

Analyzer Serial Number INST-S2-0005 INST-S2-

0005

INST-S2-

0005

Operating Range 959 959 959 959.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 1.78 3.32 3.56 2.887

Calibration Pre Zero Cylinder Bias 0.16 0.33 0.35 0.280

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID CC66246 CC66246 CC66246

Calibration Pre High Cylinder Instrument Response 422.1 417 410.32 416.473

Calibration Pre High Cylinder Bias -0.82 -1.36 -2.05 -1.410

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 3.32 3.56 2.55 3.143

Calibration Post Zero Cylinder Bias 0.33 0.35 0.25 0.310

Calibration Post Zero Cylinder Drift 0.17 0.02 0.1 0.097

Calibration Post High Cylinder ID CC66246 CC66246 CC66246

Calibration Post High Cylinder Instrument Response 417 410.32 411.11 412.810

Calibration Post High Cylinder Bias -1.36 -2.05 -1.97 -1.793

Calibration Post High Cylinder Drift 0.54 0.69 7.999999999

99998E-02

0.437

Cavg 242.26 305.64 320.48 289.460

Cavg Units ppmvd ppmvd ppmvd

Cgas 246.0333 315.2981 333.2628 298.198

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 31 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Gases - Method 7E

Average

Run Number 2-NOx-1 2-NOx-2 2-NOx-3

Test Date 4/13/2010 4/13/2010 4/13/2010

Run Start Time 3:25:22 PM 5:43:22 PM 7:52:18 PM

Run Finish Time 5:24:52 PM 7:42:52 PM 9:51:48 PM

Carbon Dioxide, % 13.91 13.84 13.71 13.820

Oxygen, % 4.15 4 3.97 4.040

Fuel Factor 1.32 1.32 1.32

Dry Volumetric Flow Rate, dry scfm 1551695 1551695 1551695 1,551,695.0

00

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.59 9.59 9.59 9.590

Analyzer Make THERMO THERMO THERMO

Analyzer Model 42i-HL 42i-HL 42i-HL

Analyzer Serial Number INST-N2-0002 INST-N2-

0002

INST-N2-

0002

Operating Range 1110 1110 1110 1,110.000

Operating Units ppm ppm ppm

No. Readings/Avg. 240 240 240 240.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Pre Zero Cylinder Instrument Response 1.12 1.68 4.97 2.590

Calibration Pre Zero Cylinder Bias 0.02 0.07 0.37 0.153

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID ALM042523-

NOx

ALM042523

-NOx

ALM042523-

NOx

Calibration Pre High Cylinder Instrument Response 538.2 528.2 521.78 529.393

Calibration Pre High Cylinder Bias -1.33 -2.23 -2.81 -2.123

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID ALM031337 ALM031337 ALM031337

Calibration Post Zero Cylinder Instrument Response 1.68 4.97 3.98 3.543

Calibration Post Zero Cylinder Bias 0.07 0.37 0.28 0.240

Calibration Post Zero Cylinder Drift 0.05 0.3 0.09 0.147

Calibration Post High Cylinder ID ALM042523-

NOx

ALM042523

-NOx

ALM042523-

NOx

Calibration Post High Cylinder Instrument Response 528.2 521.78 526.22 525.400

Calibration Post High Cylinder Bias -2.23 -2.81 -2.41 -2.483

Calibration Post High Cylinder Drift 0.9 0.58 0.4 0.627

Cavg 211.37 212.23 213.1 212.233

Cavg Units ppmvd ppmvd ppmvd

Cgas 215.9714 219.0506 219.6581 218.227

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw ppmvw ppmvw

Tuesday, February 15, 2011 Page 32 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - Metals - Method 29

Average

Run Number PMR2-29-1 PMR2-29-2 PMR2-29-3

Test Date 4/13/2010 4/13/2010 4/14/2010

Run Start Time 9:20:00 AM 2:10:00 PM 11:06:00 AM

Run Finish Time 1:20:00 PM 6:10:00 PM 3:06:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.979 0.979 1.002 0.987

Barometric Pressure, inches of Mercury 29.85 29.91 30 29.920

Average Orifice Meter Differential, inches H2O 1.99 1.53 2.27 1.930

Dry Gas Meter Volume Sampled, cubic feet 188.950 170.460 197.410 185.607

Average Dry Gas Meter Temperature, °F 79.60 82.73 82.73 81.687

Dry Gas Meter Volume Sampled, dscf 181.467 162.907 194.024 179.466

Total Moisture Liquid collected, g 445.2 392.6 449.6 429.133

Volume of Water Vapor, standard cubic feet 20.96 18.48 21.16 20.200

Moisture Content of Stack Gas, % 10.35 10.19 9.83 10.123

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8965 0.8981 0.9017 0.899

Carbon Dioxide, % 13.82 13.82 13.81 13.817

Oxygen, % 4.04 4.04 4.13 4.070

Carbon Monoxide & Nitrogen, % 82.14 82.14 82.06 82.113

Fuel Factor 1.22 1.22 1.21

Dry Molecular Weight, lb/lb-Mole 30.37 30.37 30.37 30.370

Wet Molecular weight, lb/lb-Mole 29.09 29.11 29.15 29.117

Flue Gas Static Pressure, inches of H2O -1.7 -1.7 -1.7 -1.700

Absolute Flue Gas Pressure, inches of Mercury 29.73 29.79 29.88 29.800

Average Stack Gas Temperature, °F 317.88 324.17 326.92 322.990

Average Velocity Head, inches of H2O 0.8284654510

41428

0.637761063

478517

0.901006123

011436

0.789

Average Stack Gas Velocity, feet/second 61.99 54.53 64.79 60.437

Stack Cross-Sectional Area, square feet 696.685 696.685 696.685 696.685

Dry Volumetric Flow Rate, dry scfm 1,566,802.6 1,372,399.4 1,636,364.7 1,525,188.9

00

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,591,250.2 2,279,414.0 2,708,293.3 2,526,319.1

67

Percent Isokinetic of Sampling Rate, % 98.6 101.1 101.0 100.233

Percent Excess Air, % 22.9 22.9 23.6 23.133

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 357.4 357.4 357.4

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 33 of 34
Martin Energy Center, Unit #2, Information Collection Request

7/29/2010

Location PMR2 - PM - OTM - 27/28

Average

Run Number PMR2-27/28-1 PMR2-

27/28-2

PMR2-27/28-

3

Test Date 4/12/2010 4/12/2010 4/14/2010

Run Start Time 2:38:00 PM 6:49:00 PM 8:23:00 AM

Run Finish Time 5:34:00 PM 9:30:00 PM 10:56:00 AM

Net Traversing Points 12 12 12

Net Run Time, minutes 129 126 127

Nozzle Diameter, inches 0.172 0.172 0.172 0.172

Pitot Tube Coefficient 0.8 0.8 0.8 0.800

Dry Gas Meter Calibration Factor 1.002 1.002 1.002 1.002

Barometric Pressure, inches of Mercury 29.88 29.83 29.94 29.883

Average Orifice Meter Differential, inches H2O 0.39 0.39 0.39 0.390

Dry Gas Meter Volume Sampled, cubic feet 45.670 43.400 44.190 44.420

Average Dry Gas Meter Temperature, °F 79.79 79.83 75.75 78.457

Dry Gas Meter Volume Sampled, dscf 44.745 42.447 43.709 43.634

Total Moisture Liquid collected, g 100.2 93.8 96.9 96.967

Volume of Water Vapor, standard cubic feet 4.72 4.42 4.56 4.567

Moisture Content of Stack Gas, % 9.54 9.43 9.45 9.473

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9046 0.9057 0.9055 0.905

Carbon Dioxide, % 13.82 13.82 13.89 13.843

Oxygen, % 4.04 4.04 4 4.027

Carbon Monoxide & Nitrogen, % 82.14 82.14 82.11 82.130

Fuel Factor 1.22 1.22 1.22

Dry Molecular Weight, lb/lb-Mole 30.37 30.37 30.38 30.373

Wet Molecular weight, lb/lb-Mole 29.19 29.20 29.21 29.200

Flue Gas Static Pressure, inches of H2O -1.7 -1.7 -1.7 -1.700

Absolute Flue Gas Pressure, inches of Mercury 29.76 29.71 29.82 29.763

Average Stack Gas Temperature, °F 314.58 313.58 324.00 317.387

Average Velocity Head, inches of H2O 0.7050553763

14312

0.721868404

195371

0.779776047

186202

0.736

Average Stack Gas Velocity, feet/second 54.23 54.87 57.30 55.467

Stack Cross-Sectional Area, square feet 696.685 696.685 696.685 696.685

Dry Volumetric Flow Rate, dry scfm 1,390,346.0 1,407,916.1 1,455,776.5 1,418,012.8

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,266,873.7 2,293,626.4 2,395,203.0 2,318,567.7

00

Percent Isokinetic of Sampling Rate, % 107.7 103.3 102.1 104.367

Percent Excess Air, % 22.9 22.9 22.6 22.800

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 357.4 357.4 357.4

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 15, 2011 Page 34 of 34