PSNH - Newington Station

Process Data during ICR testing 

Reporting Period

From: 2/16/2010 0:00:01

To: 2/17/2010 12:00:00 AM

Gross Electric Output Net Electric Output No. 6 Fuel Oil Flow Natural Gas Flow Steam Flow Total Heat Input

Date and Time MWH MWH KLB/HR KSCFH KPPH MMBTU/HR

2/16/10 1:00:00 -0.7 0 0 0 0 0

2/16/10 2:00:00 -0.8 0 0 0 0 0

2/16/10 3:00:00 -0.7 0 0 0 0 0

2/16/10 4:00:00 -0.8 0 0 0 0 0

2/16/10 5:00:00 -0.7 0 0 209 0 283

2/16/10 6:00:00 0.1 0 4 280 17 297

2/16/10 7:00:00 51.1 31 16 534 431 977

2/16/10 8:00:00 140.6 128 39 850 977 1,888

2/16/10 9:00:00 162.3 141 54 811 1,083 2,144

2/16/10 10:00:00 162.3 152 53 791 1,062 2,041

2/16/10 11:00:00 162.3 151 53 796 1,057 2,123

2/16/10 12:00:00 162.3 144 52 799 1,057 2,059

2/16/10 13:00:00 162.3 151 51 800 1,057 2,056

2/16/10 14:00:00 162.3 152 51 798 1,058 2,059

2/16/10 15:00:00 162.3 151 52 798 1,057 2,024

2/16/10 16:00:00 162.3 152 53 800 1,056 2,067

2/16/10 17:00:00 162.3 151 52 801 1,057 2,052

2/16/10 18:00:00 162.3 152 52 804 1,057 2,055

2/16/10 19:00:00 162.3 151 52 802 1,056 2,093

2/16/10 20:00:00 161.2 152 52 806 1,049 2,007

2/16/10 21:00:00 110.5 143 27 765 760 1,043

2/16/10 22:00:00 10.7 94 0 170 83 702

2/16/10 23:00:00 -0.8 4 0 0 0 0

2/17/10 0:00:00 -0.8 4 0 0 0 0

average 162.2 150 52.2 800.5 1059 2065

The unit operated for the ICR testing only and not for a full 24 hours per day. The averages provided include the average of hours the unit operated for testing only. 

Notes:

A mixture of natural gas and No.6 fuel oil was used during the ICR testing.

PSNH - Newington Station

Process Data during ICR testing 

Reporting Period

From: 2/17/2010 0:00:01

To: 2/18/2010 12:00:00 AM

Gross Electric Output Net Electric Output No. 6 Fuel Oil Flow Natural Gas Flow Steam Flow Total Heat Input

Date and Time MWH MWH KLB/HR KSCFH KPPH MMBTU/HR

2/17/10 1:00:00 -0.8 0 0 0 0 0

2/17/10 2:00:00 -0.8 0 0 0 0 0

2/17/10 3:00:00 -0.8 0 0 0 0 0

2/17/10 4:00:00 -0.8 0 0 0 0 0

2/17/10 5:00:00 -0.8 0 0 257 0 274

2/17/10 6:00:00 2.3 0 6 246 38 369

2/17/10 7:00:00 67.3 52 19 674 552 1194

2/17/10 8:00:00 151.4 136 47 860 1,071 2,244

2/17/10 9:00:00 162.3 141 55 832 1,118 2,217

2/17/10 10:00:00 162.3 151 54 819 1,086 2,195

2/17/10 11:00:00 162.4 146 52 807 1,060 2,083

2/17/10 12:00:00 162.3 152 53 804 1,050 1,802

2/17/10 13:00:00 162.3 152 54 797 1,051 1,953

2/17/10 14:00:00 162.3 151 54 798 1,052 1,944

2/17/10 15:00:00 162.3 152 54 793 1,052 1,959

2/17/10 16:00:00 162.3 151 53 800 1,053 2,024

2/17/10 17:00:00 162.3 152 51 795 1,052 1,942

2/17/10 18:00:00 162.4 152 52 796 1,051 2,016

2/17/10 19:00:00 162.3 152 54 796 1,051 1,477

2/17/10 20:00:00 99.1 151 24 662 666 700

2/17/10 21:00:00 -0.7 84 0 0 1 0

2/17/10 22:00:00 -0.8 0 0 0 0 0

2/17/10 23:00:00 -0.8 0 0 0 0 0

2/18/10 0:00:00 -0.8 0 0 0 0 0

average 162.3 150.2 53.3 803.4 1061 1965

The unit operated for the ICR testing only and not for a full 24 hours per day. The averages provided include the average of hours the unit operated for testing only. 

Notes:

A mixture of natural gas and No.6 fuel oil was used during the ICR testing.

PSNH - Newington Station

Process Data during ICR testing 

Reporting Period

From: 2/18/2010 0:00:01

To: 2/19/2010 12:00:00 AM

Gross Electric Output Net Electric Output No. 6 Fuel Oil Flow Natural Gas Flow Steam Flow Total Heat Input

Date and Time MWH MWH KLB/HR KSCFH KPPH MMBTU/HR

2/18/10 1:00:00 -0.8 0 0 0 0 0

2/18/10 2:00:00 -0.8 0 0 0 0 0

2/18/10 3:00:00 -0.8 0 0 0 0 0

2/18/10 4:00:00 -0.8 0 0 0 0 38

2/18/10 5:00:00 -0.7 0 0 60 0 298

2/18/10 6:00:00 -0.7 0 0 327 2 740

2/18/10 7:00:00 35.6 21 11 436 320 1707

2/18/10 8:00:00 128 107 39 798 905 2,168

2/18/10 9:00:00 162.3 141 55 820 1,079 2,121

2/18/10 10:00:00 162.3 151 54 816 1,061 2,144

2/18/10 11:00:00 162.3 151 54 813 1,061 2,119

2/18/10 12:00:00 162.3 151 53 815 1,060 1,755

2/18/10 13:00:00 162.5 151 53 817 1,059 1,993

2/18/10 14:00:00 162.4 151 55 815 1,056 2,009

2/18/10 15:00:00 162.4 151 55 814 1,057 1,956

2/18/10 16:00:00 162.5 151 54 814 1,058 2,027

2/18/10 17:00:00 162.4 151 53 814 1,058 1,484

2/18/10 18:00:00 92.5 152 24 624 641 659

2/18/10 19:00:00 -0.7 75 0 0 1 0

2/18/10 20:00:00 -0.8 0 0 0 0 0

2/18/10 21:00:00 -0.8 0 0 0 0 0

2/18/10 22:00:00 -0.7 0 0 0 0 0

2/18/10 23:00:00 -0.8 0 0 0 0 0

2/19/10 0:00:00 -0.8 0 0 0 0 0

average 162.4 149.9 54 815.3 1061 1956

The unit operated for the ICR testing only and not for a full 24 hours per day. The averages provided include the average of hours the unit operated for testing only. 

Notes:

A mixture of natural gas and No.6 fuel oil was used during the ICR testing.

PSNH - Newington Station

Process Data during ICR testing 

Reporting Period

From: 2/19/2010 0:00:01

To: 2/20/2010 12:00:00 AM

Gross Electric Output Net Electric Output No. 6 Fuel Oil Flow Natural Gas Flow Steam Flow Total Heat Input

Date and Time MWH MWH KLB/HR KSCFH KPPH MMBTU/HR

2/19/10 1:00:00 -0.8 0 0 0 0 0

2/19/10 2:00:00 -0.8 0 0 0 0 0

2/19/10 3:00:00 -0.8 0 0 0 0 0

2/19/10 4:00:00 -0.7 0 0 0 0 0

2/19/10 5:00:00 -0.8 0 0 168 0 202

2/19/10 6:00:00 1.4 0 5 250 29 436

2/19/10 7:00:00 70.1 54 19 643 567 1281

2/19/10 8:00:00 153.7 135 51 813 1,047 2,188

2/19/10 9:00:00 162.3 141 55 823 1,079 2,267

2/19/10 10:00:00 162.3 151 54 812 1,060 2,229

2/19/10 11:00:00 162.3 151 53 800 1,062 2,128

2/19/10 12:00:00 162.3 144 52 786 1,064 1,800

2/19/10 13:00:00 162.3 144 53 787 1,064 1,846

2/19/10 14:00:00 162.3 151 51 789 1,064 1,885

2/19/10 15:00:00 162.2 151 52 790 1,064 1,943

2/19/10 16:00:00 162.3 151 52 783 1,063 1,895

2/19/10 17:00:00 162.3 151 52 793 1,061 1,977

2/19/10 18:00:00 162.3 151 52 786 1,061 1,961

2/19/10 19:00:00 162.3 151 52 789 1,062 1,976

2/19/10 20:00:00 162.3 144 50 799 1,064 1,985

2/19/10 21:00:00 162.3 151 53 806 1,064 2,016

2/19/10 22:00:00 162.3 151 53 808 1,063 2,096

2/19/10 23:00:00 162.3 151 54 811 1,063 2,097

2/20/10 0:00:00 156.7 151 48 841 1,029 2,106

average 162.3 148.9 52.5 797.5 1064 2007

The unit operated for the ICR testing only and not for a full 24 hours per day. The averages provided include the average of hours the unit operated for testing only. 

Notes:

A mixture of natural gas and No.6 fuel oil was used during the ICR testing.