Information Notice No. 95-49, Supplement 1: Seismic Adequacy of Thermo-Lag Panels

file:////acfnas/perm/netsite-docs/gpo5444/in95049s1.html[4/18/2018 3:00:09 PM]

Index | Site Map | FAQ | Facility Info | Reading Rm | New | Help | Glossary | Contact Us

Home > Electronic Reading Room > Document Collections > General Communications > Information Notices > 1995 > IN 95-49

UNITED STATES

NUCLEAR REGULATORY COMMISSION

OFFICE OF NUCLEAR REACTOR REGULATION

WASHINGTON, D.C. 20555-0001

December 10, 1997

NRC INFORMATION NOTICE 95-49, Supplement 1: SEISMIC ADEQUACY OF THERMO-LAG PANELS

Addressees

All holders of operating licenses for nuclear power reactors.

Purpose

The U.S. Nuclear Regulatory Commission (NRC) is issuing this information notice to inform addressees about the results of mechanical properties

testing of Thermo-Lag 330-1 fire barrier material performed by the National Institute of Standards and Technology (NIST). The results of the

testing indicated significantly lower mechanical properties than those used by the vendor to demonstrate the seismic adequacy of Thermo-Lag 330-

1 panels. It is expected that recipients will review the information for applicability to their facilities and consider actions, as appropriate. However,

suggestions contained in this information notice are not NRC requirements; therefore, no specific action or written response is required.

Description of Circumstances

In response to a "seismic issue" concern raised by the Nuclear Information and Resource Service regarding the Thermo-Lag fire barrier (Accession

Number 9208280125), the staff studied the issue and concluded that the "shattering of raceways or severing of cables required for safe shutdown

were not credible scenarios" under postulated seismic events at nuclear power plant sites (Accession Number 9302110146). The staff's response

was based on acceptance of the analyses performed by a consultant who used mechanical properties data for Thermo-Lag, which were provided by

Thermal Science, Incorporated (TSI), the manufacturer and supplier of the Thermo-Lag fire barrier material.

The Tennessee Valley Authority (TVA) subsequently submitted the results of its simulated seismic tests and mechanical properties tests related to

the use of Thermo-Lag fire barrier material at Watts Bar Nuclear Plant (Accession Number 9411250234). These tests indicated significantly lower

mechanical properties values compared to those used by the TSI consultant.

The NRC staff, therefore, contracted with the NIST to perform appropriate mechanical properties testing of Thermo-Lag material. The tests, test

methods, and test results are described in the NIST's letter report to NRC entitled "Mechanical Properties of Samples of a 'Subliming' Fire Barrier

Panel Material as a Function of Temperature (Accession Number 9608140068)." NIST also compared its test results with TSI's and TVA's. NIST's

test results for mean tensile strength, flexural strength, and elastic modulus of the 1-hour fire-rated Thermo-Lag material were at least 40 percent

lower than TSI's at 23 C (73 F) and 50 C (122 F). NIST's test results were similar to those of TVA.

Discussion

As stated in Information Notice (IN) 95-49, "Seismic Adequacy of Thermo-Lag Panels," dated October 27, 1995 (Accession Number 9510240388),

fire barriers may undergo damage during postulated seismic events, but the fire barriers should not be damaged to such an extent that they could

reduce the functioning of the protected cables or other safety-related structures, systems, or components. Therefore, NRC is concerned that the

correct or conservative values for pertinent mechanical properties may not have been used in evaluating the seismic adequacy of Thermo-Lag

panels and, as a result, the fire barriers may not maintain their integrity during postulated seismic events.

The following is a summary comparison of the mechanical properties of Thermo-Lag 330-1 reported by TSI and NIST for the 1-hour fire-rated

material at 50 C (122 F):

Tensile Strength: TSI-5.0 MPa (720 psi); NIST-2.46 MPa (360 psi)

Flexural Strength: TSI-12.4 MPa (1800 psi); NIST-4.56 MPa (660 psi)

Modulus of Elasticity: TSI-379 MPa (54.9 ksi); NIST-137 MPa (19.9 ksi)

NIST summarizes the results as follows: "The mean values of the mechanical properties measured in this study are lower than those reported by

the manufacturer in Technical Note 90181. Some of the differences can be attributed, in part, to the different testing methods that were used.

However, the differences are sufficiently large to indicate that there are real differences between the tensile strength, flexural strength, and static

modulus of elasticity of the samples used in the study by NIST and those used in the manufacturer's tests."

A reevaluation by the NRC staff of Thermo-Lag stresses under postulated seismic events, using NIST's test results, indicated that at 23 C, properly

installed [in accordance with TSI's installation procedure (see also IN 91-79, "Deficiencies in the Procedures for Installing Thermo-Lag Fire Barrier

Material," and TSI's seismic evaluation criteria)] 1-hour fire-rated Thermo-Lag panels can safely withstand the seismic loadings imposed by 3.3 g

vertical acceleration and 5.0 g horizontal acceleration ("g" being acceleration due to gravity). At 50 C, the corresponding acceleration levels are 1.2

g vertical and 1.8 g horizontal (the g values indicated here are the spectral acceleration values at the location of the fire barrier material).

The Thermo-Lag fire barrier material has been removed from plants in high seismic areas (i.e., Diablo Canyon and San Onofre), and it is the staff's

judgment that the acceptable acceleration levels at 23 C (5.0 g horizontal, 3.3 g vertical) will not be exceeded at the remaining operating plants

during the design-basis seismic events. However, at higher sustained temperatures, the acceleration levels generated by design-basis seismic

events at the locations of the Thermo-Lag protected cable trays or equipment could exceed the acceptable acceleration levels at a number of

About NRC Nuclear

Reactors

Nuclear

Materials

Radioactive

Waste

Nuclear

Security

Public Meetings

& Involvement

Protecting People and the Environment

UNITED STATES NUCLEAR REGULATORY COMMISSION
Information Notice No. 95-49, Supplement 1: Seismic Adequacy of Thermo-Lag Panels

file:////acfnas/perm/netsite-docs/gpo5444/in95049s1.html[4/18/2018 3:00:09 PM]

operating nuclear power plants. The dynamic forces generated by such accelerations could detach the large pieces of Thermo-Lag panels from the

cable trays, which, in turn, could act as missiles and jeopardize the safety functions of the safety-related equipment and components in the vicinity.

However, the potential for such a hazard depends on the plant specific installation, spatial separation, and sustained elevated temperature.

This information notice requires no specific action or written response. If you have any questions about the information in this notice, please

contact the technical contact listed below or the appropriate Office of Nuclear Reactor Regulation (NRR) project manager.

signed by S.H. Weiss for

Jack W. Roe, Acting Director

Division of Reactor Program Management

Office of Nuclear Reactor Regulation

Technical contact: Hans Ashar, NRR

301-415-2851

E-mail: hga@nrc.gov

(NUDOCS Accession Number 9712090017)