Skip to Main Page ContentSkip to SearchSkip to Site Map NavigationSkip to Footer Links

        - Home

        - FAQ
        - Glossary
        - Facility Locator
        - What's New
        - Site Help
        - Index A-Z
        - Contact Us
        - Browse Aloud
        - Email Updates

Report a Safety Concern

      - Nuclear Reactors  - Power Reactors
- Research & Test Reactors
- Operating Reactors
- Operator Licensing
- New Reactors
- Advanced Reactors
- Operator Licensing for New Reactors
- Research Activities
- Nuclear Reactor Quick Links
 
      - Nuclear Materials  - Special Nuclear Material
- Source Material
- Byproduct Material
- Med, Ind, & Academic Uses
- Source Materials Facilities
- Uranium Recovery
- Fuel Cycle Facilities
- Materials Transportation
- Research Activities
- Nuclear Materials Quick Links
 
      - Radioactive Waste  - Decommissioning of Nuclear Facilities
- Low-Level Waste
- Waste Incidental to Reprocessing
- High-Level Waste
- Uranium Mill Tailings
- Low-Level Waste Disposal
- High-Level Waste Disposal
- Storage of Spent Nuclear Fuel
- Transporation of Spent Nuclear Fuel
- Research Activities
- Radioactive Waste Quick Links
 
      - Nuclear Security  - Domestic Safeguards
- Information Security
- Radioactive Material Security
- Contact Us
 
      - Public Meetings & Involvement  - The NRC Approach to Open Government
- About Meetings Open to the Public
- Conferences & Symposia
- Documents for Comment
- Facilitating Stakeholder Involvement
- NRC Information Quality Guidelines
- Subscribe to E-mail Updates
- Commission Schedule
- Public Meeting Schedule
- Adjudications (Hearings)
 
      - NRC Library  - Basic References
- Document Collections
- ADAMS Public Documents
- Public Document Room
- Get Copies of Documents
- FOIA & Privacy Act Requests
- Photos & Video
- Records Management 
- Withholding of Sensitive Information
- FAQ Index
- Electronic Hearing Docket
 
      - About NRC  - The Commission
- Organization & Functions
- Governing Legislation
- Plans, Budget, & Performance
- Locations
- History
- Values
- Direction-Setting & Policymaking
- Research Activities
- Radiation Protection
- Fire Protection
- Safety Culture
- How We Regulate
- Emergency Preparedness & Response
- Public Affairs
- Congressional Affairs
- International Programs
- State & Tribal Programs
- Alternative Dispute Resolution Programs
- Civil Rights
- Contact Us
- Career Opportunities
- Contracting Opportunities
- Grant Opportunities
 

Print

HomeNRC LibraryDocument CollectionsGeneric CommunicationsInformation Notices1993

# Information Notice No. 93-85: Problems with X-Relays in DB- and DHB-Type Circuit Breakers Manufactured by Westinghouse

```
                                 UNITED STATES
                         NUCLEAR REGULATORY COMMISSION
                     OFFICE OF NUCLEAR REACTOR REGULATION
                            WASHINGTON, D.C.  20555

                               October 20, 1993

NRC INFORMATION NOTICE 93-85:  PROBLEMS WITH X-RELAYS IN DB- AND DHB-TYPE      
                               CIRCUIT BREAKERS MANUFACTURED BY WESTINGHOUSE   
                               

Addressees

All holders of operating licenses or construction permits for nuclear power
reactors.

Purpose

The U.S. Nuclear Regulatory Commission (NRC) is issuing this information
notice to alert addressees to the possible failure of the 52X-relay (X-relay)
to reset in DB- and DHB-type Westinghouse Electric Company (Westinghouse)
circuit breakers, thus preventing them from reclosing on demand.  It is
expected that recipients will review the information for applicability to
their facilities and consider actions, as appropriate, to avoid similar
problems.  However, suggestions contained in this information notice are not
NRC requirements; therefore, no specific action or written response is
required.

Description of Circumstances 

On June 27, 1993, power to a motor control center was lost at the Haddam Neck
nuclear power plant.  Connecticut Yankee Atomic Power Company, the licensee,
determined that the possible root cause for this event was a failure of the
X-relay (anti-pump relay) to reset to the de-energized position in a
Westinghouse DB-25 circuit breaker.  

Previously, between July 1 and August 24, 1984, the licensee reported five
incidents in which one DB-25 and four DHB-250 breakers failed to close when
required.  All five of those failures were attributed to malfunctions of the
X-relay.  The licensee believed that dirt had caused the problem and
instituted a program for cleaning the stationary and moving cores of the
relay.  

On June 11, 1991, and on January 28, 1992, Duke Power Company reported that,
at the Oconee Nuclear Station, X-relays failed to reset and prevented the
DB-25 breakers from closing in the Keowee hydroelectric generator field and
field flashing circuitry.  (The Keowee hydrostation supplies emergency power
to the Oconee station.)  The licensee modified the anti-pump function with an
electrical scheme that does not require the X-relay.

9310140277.

                                                             IN 93-85
                                                             October 20, 1993  
                                                             Page 2 of 3

                                                                    
Discussion

The X-relay is usually denoted by the symbol 52X in the electrical control
circuit schematic diagram for the breaker.  On receipt of a signal to close
the breaker, the X-relay energizes and one set of its normally open contacts
closes to enable momentary energizing of the breaker closing coil.  After the
breaker closes, the same set of X-relay contacts opens to deenergize the
closing coil even though the X-relay remains energized by the close signal. 
If the close signal is still present after the breaker trips, the X-relay
serves to inhibit repeated closure attempts until the close signal is removed. 
Thus, it provides anti-pump protection to the breaker by preventing repeated
breaker closure attempts when a standing closure signal exists after a breaker
trips.

The armature assembly of an X-relay (see Figure 1) fits inside a brass sleeve
and is surrounded by the electromagnetic coil (different from the breaker
closing coil) of the relay.  When this coil is energized, the plunger (moving
core) is drawn up towards the top cap piece (stationary core) of the assembly
and the latch arm operates the relay contacts.  In its uppermost position, an
air gap is maintained between the bullet-shaped top of the plunger and the
cavity in the cap piece, with the shoulder of the plunger mating with the lip
on the cap piece.  When the coil is de-energized, the moving core is designed
to fall, by gravity, into its lowest position.  The failure of the moving core
to fall to its lowest position is the possible failure mode of interest at
Haddam Neck.

Westinghouse and the licensee believe that residual magnetism associated with
continuous energization of the relay or mechanical adherence between the two
parts are probable causes for the plunger failing to fall.  Westinghouse is
testing a design enhancement that uses a brass spacer between the moving and
stationary cores to create a controlled air gap.  Westinghouse plans to issue
a Nuclear Safety Advisory Letter to notify users of this problem.  The
licensee is evaluating a design modification for the X-relay function in the
motor control center.  

.

                                                             IN 93-85
                                                             October 20, 1993  
                                                             Page 3 of 3

                                                                    
This information notice requires no specific action or written response.  If
you have any questions about the information in this notice, please contact
one of the technical contacts listed below or the appropriate office of
Nuclear Reactor Regulation (NRR) project manager.

                              /s/'d by BKGrimes

                              Brian K. Grimes, Director
                              Division of Operating Reactor Support
                              Office of Nuclear Reactor Regulation

Technical contacts:  Kamalakar Naidu, NRR
                     (301) 504-2980

                     Frederick H. Burrows, NRR
                     (301) 504-2901
Attachments: 
1.  Figure 1, X-Relay Magnetic Core
2.  List of Recently Issued NRC Information Notices
.
```

*Page Last Reviewed/Updated Tuesday, November 12, 2013*

#### Home

            - News Releases
            - Event Reports
            - ADAMS
            - Open Gov
            - Digital Government
            - Students & Teachers
            - Photos & Video
            - For Developers

#### About Us

            - Strategic Plan
            - Budget & Performance
            - Perf & Accountability Rept
            - History of the NRC
            - Career Opportunities
            - NRC Ethics
            - Agency Status
            - Contact Us

#### Popular Documents

            - Info Digest
            - Factsheets & Brochures
            - Forms
            - Electronic Submittals Application
            - NRC Reports – NUREG
            - NRC Regulations – 10-CFR
            - Inspection Reports
            - Plain Writing
            - Enforcement Actions
            - RULEMAKING

#### Stay Connected

            - Blog
            - Facebook
            - Twitter
            - YouTube
            - Flickr
            - GovDelivery
            - RSS

Regulations.govUSA.govRecoveryFOIANo Fear EEOInspector General ProgramSite MapAccessibilityPrivacy PolicySite DisclaimerFor Employees