Name: Ms. Debi Schramm

Title:

Company: FirstEnergy Corporation

Sign Date: 9/3/2010

Name: Mr. James E. Locke

Title: Manager, Field Testing & Operation

Company: CONSOL Energy, Inc.

Sign Date: 9/3/2010

Permitted Facility Representative / Date Testing Company Representative / Date

FirstEnergy - Bay Shore Station ICR

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 17, 2011 Page 1 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Facility Information:

FirstEnergy Corp. Bay Shore

4701 Bay Shore Road

Oregon OH 43616

Contact: Mr. Ray Evans

Phone: 330-761-4482

Fax:

Email: rlevans@firstenergycorp.com

Testing Company:

CONSOL Energy Inc.

4000 Brownsville Road

South Park PA 15129

Contact:Mr. James E. Locke

Phone: 412-854-6607

Fax: 412-854-6613

Email: jimlocke@consolenergy.com

Air Permit Number:

48-4911-895-2

Permitted Source ID/Name:

0448020006 B006

Permitted Maximum Process Rate:

1736 mmBtu/hr

Max. Normal Operation Process Rate:

1736 mmBtu/hr

Target Process Test Rate

1736 mmBtu/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Bay Shore is located on the east bank of the Maumee River, on the Shore of Lake Erie, in Oregon, Ohio. Unit 1 is a 

vertically-fired boiler that fires petroleum coke to produce a maximum of 1,410 pounds of steam per hour (KPPH). 

Emissions are controlled with a baghouse.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000384325 FRS #: 110000384325

SCC / Description 10100818 External Combustion Boilers - Electric Generation - Petroleum Coke - Circulating 

Fluidized Bed Combustion 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Unit 1 Stack 178 0 0 0 0 0 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Unit 1 Stack Carbon Monoxide Method 10 3 120 0

Unit 1 Stack 2,3,7,8-TCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8-PeCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

NA 0

Thursday, February 17, 2011 Page 2 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Unit 1 Stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Unit 1 Stack OCDD Method 23 3 480 0

Unit 1 Stack 2,3,7,8-TCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8-PeCDF Method 23 3 480 0

Unit 1 Stack 2,3,4,7,8-PeCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Unit 1 Stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Unit 1 Stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Unit 1 Stack OCDF Method 23 3 480 0

Unit 1 Stack Other TCDD Method 23 3 480 0

Unit 1 Stack Other PeCDD Method 23 3 480 0

Unit 1 Stack Other HxCDD Method 23 3 480 0

Unit 1 Stack Other HpCDD Method 23 3 480 0

Unit 1 Stack Other TCDF Method 23 3 480 0

Unit 1 Stack Other PeCDF Method 23 3 480 0

Unit 1 Stack Other HxCDF Method 23 3 480 0

Unit 1 Stack Other HpCDF Method 23 3 480 0

Unit 1 Stack Total Dioxins Method 23 3 480 0

Unit 1 Stack Total Furans Method 23 3 480 0

Unit 1 Stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Unit 1 Stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Unit 1 Stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Unit 1 Stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Unit 1 Stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Unit 1 Stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Unit 1 Stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Unit 1 Stack Method 23 3 480 0

Unit 1 Stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Unit 1 Stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Unit 1 Stack Method 23 3 480 0

Unit 1 Stack Total PCBs Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Unit 1 Stack Method 25A 3 120 0

Unit 1 Stack Filterable Particulate OTM - 27/28 3 360 0

Organic Condensible 

Particulate

Unit 1 Stack OTM - 27/28 3 360 0

Unit 1 Stack Filterable PM2.5 OTM - 27/28 3 360 0

Unit 1 Stack Total Particulate OTM - 27/28 3 360 0

Unit 1 Stack Total PM2.5 OTM - 27/28 3 360 0

Inorganic (Aqueous) 

Condensible Part.

Unit 1 Stack OTM - 27/28 3 360 0

Unit 1 Stack Antimony Method 29 3 240 0

Unit 1 Stack Beryllium Method 29 3 240 0

Unit 1 Stack Cadmium Method 29 3 240 0

Unit 1 Stack Cobalt Method 29 3 240 0

Unit 1 Stack Chromium Method 29 3 240 0

Unit 1 Stack Manganese Method 29 3 240 0

Unit 1 Stack Selenium Method 29 3 240 0

Thursday, February 17, 2011 Page 3 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Unit 1 Stack Lead Method 29 3 240 0

Unit 1 Stack Arsenic Method 29 3 240 0

Unit 1 Stack Filterable Particulate Method 29 3 240 0

Unit 1 Stack Nickel Method 29 3 240 0

Unit 1 Stack O2 Method 3A O2 3 120 0

Unit 1 Stack Co2 Method 3A CO2 3 120 0

Unit 1 Stack Sulfur Dioxide Method 6C 3 120 0

Unit 1 Stack Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, February 17, 2011 Page 4 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Sampling / Stack Data Results Summary

Location Unit 1 Stack - Method 10

Average

Run Number U1-M10-1 U1-M10-2 U1-M10-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 

AM

1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9827 9892 9892 9,870.333

Moisture, % 7.2 7.2 7.2 7.200

Fuel Type Override Override Override

Fw 11122 11121 11121 11,121.333

Fc 1836 1836 1836 1,836.000

Location Unit 1 Stack - Method 23

Average

Run Number U1-M23-1 U1-M23-2 U1-M23-3

Test Date 6/9/2010 6/10/2010 6/11/2010

Run Start Time 12:47:00 PM 9:01:00 

AM

8:31:00 AM

Run Finish Time 8:37:00 PM 4:51:00 PM 4:21:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 1,166.212 304.191 298.110 589.504

Moisture Content of Stack Gas, % 95.96 6.74 7.19 36.630

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 17.4 17.6 17.6 17.533

Oxygen, % 2.6 2.4 2.4 2.467

Average Stack Gas Temperature, °F 342.46 342.08 403.10 362.547

Dry Volumetric Flow Rate, dry scfm 21,023.1 404,067.2 344,183.1 256,424.467

Actual Wet Volumetric Flue Gas Flow Rate, acfm 810,094.0 673,021.9 616,720.8 699,945.567

Percent Isokinetic of Sampling Rate, % 6,410.4 87.0 100.1 2,199.167

F-Factor, dscfm/MMBtu @ %O2 9956 9720 9892 9,856.000

Fw 11675 11175 11121 11,323.667

Fc 1846 1804 1836 1,828.667

Thursday, February 17, 2011 Page 5 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 25A

Average

Run Number U1-M25A-1 U1-M25A2U1-M25A-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 

AM

1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Location Unit 1 Stack - Method 29

Average

Run Number U1-M29-1 U1-M29-2 U1-M29-3

Test Date 6/7/2010 6/8/2010 6/9/2010

Run Start Time 9:45:00 AM 10:15:00 

AM

8:07:00 AM

Run Finish Time 1:35:00 PM 2:05:00 PM 11:57:00 AM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 131.498 129.994 127.515 129.669

Moisture Content of Stack Gas, % 6.57 7.12 7.85 7.180

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 17 16.9 17.5 17.133

Oxygen, % 3 3.1 2.5 2.867

Average Stack Gas Temperature, °F 331.17 337.79 333.21 334.057

Dry Volumetric Flow Rate, dry scfm 389,744.3 381,324.9 373,065.1 381,378.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 638,080.0 628,955.6 625,119.3 630,718.300

Percent Isokinetic of Sampling Rate, % 92.0 93.8 94.1 93.300

F-Factor, dscfm/MMBtu @ %O2 9825 9875 9956 9,885.333

Fw

Fc

Thursday, February 17, 2011 Page 6 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 3A CO2

Average

Run Number U1-

M3ACO2-1

U1-

M3ACO2-

2

U1-

M3ACO2-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 

AM

1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Dry Volumetric Flow Rate, dry scfm 385534 385535 385534 385,534.333

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Fuel Type Override Override Override

Fw 11123 11122 11122 11,122.333

Fc 1836 1836 1836 1,836.000

Location Unit 1 Stack - Method 3A O2

Average

Run Number U1-M3AO2-

1

U1-

M3AO2-2

U1-M3AO2-

3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 

AM

1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Thursday, February 17, 2011 Page 7 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 6C

Average

Run Number U1-M6C-1 U1-M6C-2 U1-M6C-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 

AM

1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Location Unit 1 Stack - Method 7E

Average

Run Number U1-M7E-1 U1-M7E-2 U1-M7E-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 

AM

1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Thursday, February 17, 2011 Page 8 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - OTM - 27/28

Average

Run Number U1-

OTM27/28-1

U1-

OTM27/28

-2

U1-

OTM27/28-3

Test Date 6/10/2010 6/11/2010 6/12/2010

Run Start Time

Run Finish Time

Net Run Time, minutes 360.5 331.75 338.75

Dry Gas Meter Volume Sampled, dscf 130.133 118.772 121.542 123.482

Moisture Content of Stack Gas, % 7.24 7.43 7.69 7.453

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 17 17 17 17.000

Oxygen, % 3 3 3 3.000

Average Stack Gas Temperature, °F 336.58 334.00 337.58 336.053

Dry Volumetric Flow Rate, dry scfm 372,121.5 374,186.6 382,977.1 376,428.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 619,727.6 622,423.5 639,531.5 627,227.533

Percent Isokinetic of Sampling Rate, % 103.9 102.5 100.3 102.233

F-Factor, dscfm/MMBtu @ %O2 9720 9892 9821 9,811.000

Fw 11175 11121 11363 11,219.667

Fc 1804 1836 1827 1,822.333

Thursday, February 17, 2011 Page 9 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Emissions Summary

Location: Unit 1 Stack - Method 10

Compound: Carbon Monoxide

Average

Run U1-M10-1 U1-M10-2 U1-M10-3

Elb/hr 2.73E+01 2.83E+01 3.12E+01 28.933

gr/dscf 8.26E-03 8.55E-03 9.44E-03 0.009

lb/mmBtuO2 1.32E-02 1.37E-02 1.52E-02 0.014

mg/dscm 1.89E+01 1.96E+01 2.16E+01 20.033

ppm 1.62E+01 1.68E+01 1.86E+01 17.200

Location: Unit 1 Stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000101 0.0000000074 0.0000000065 0.000

Elb/hr 2.41E-11 1.30E-09 9.93E-10 0.000

gr/dscf 1.34E-13 3.75E-13 3.36E-13 0.000

lb/mmBtuO2 2.17E-13 5.89E-13 5.37E-13 0.000

mg/dscm 3.06E-10 8.59E-10 7.70E-10 0.000

ng/dscm 3.06E-04 8.59E-04 7.70E-04 0.001

ng/dscm@7%O2 2.32E-04 6.45E-04 5.79E-04 0.000

ppm 1.73E-11 4.86E-11 4.35E-11 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000076 0.000000016 0.0000000052 0.000

Elb/hr 1.81E-11 2.81E-09 7.94E-10 0.000

gr/dscf 1.01E-13 8.12E-13 2.69E-13 0.000

lb/mmBtuO2 1.63E-13 1.27E-12 4.30E-13 0.000

mg/dscm 2.30E-10 1.86E-09 6.16E-10 0.000

ng/dscm 2.30E-04 1.86E-03 6.16E-04 0.001

ng/dscm@7%O2 1.75E-04 1.40E-03 4.63E-04 0.001

ppm 1.35E-11 1.09E-10 3.62E-11 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000019 0.0000000058 0.0000000021 0.000

Elb/hr 4.53E-12 1.02E-09 3.21E-10 0.000

gr/dscf 2.51E-14 2.94E-13 1.09E-13 0.000

lb/mmBtuO2 4.08E-14 4.62E-13 1.74E-13 0.000

mg/dscm 5.75E-11 6.73E-10 2.49E-10 0.000

ng/dscm 5.75E-05 6.73E-04 2.49E-04 0.000

ng/dscm@7%O2 4.37E-05 5.06E-04 1.87E-04 0.000

ppm 3.38E-12 3.96E-11 1.46E-11 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000019 0.000000002 0.0000000019 0.000

Thursday, February 17, 2011 Page 10 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Elb/hr 4.53E-12 3.51E-10 2.90E-10 0.000

gr/dscf 2.51E-14 1.01E-13 9.84E-14 0.000

lb/mmBtuO2 4.08E-14 1.59E-13 1.57E-13 0.000

mg/dscm 5.75E-11 2.32E-10 2.25E-10 0.000

ng/dscm 5.75E-05 2.32E-04 2.25E-04 0.000

ng/dscm@7%O2 4.37E-05 1.74E-04 1.69E-04 0.000

ppm 3.54E-12 1.43E-11 1.39E-11 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000052 0.0000000055 0.0000000029 0.000

Elb/hr 1.24E-11 9.66E-10 4.43E-10 0.000

gr/dscf 6.88E-14 2.79E-13 1.50E-13 0.000

lb/mmBtuO2 1.12E-13 4.38E-13 2.40E-13 0.000

mg/dscm 1.57E-10 6.39E-10 3.44E-10 0.000

ng/dscm 1.57E-04 6.39E-04 3.44E-04 0.000

ng/dscm@7%O2 1.19E-04 4.80E-04 2.58E-04 0.000

ppm 1.01E-11 4.10E-11 2.20E-11 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000028 0.000000002 0.0000000022 0.000

Elb/hr 6.68E-12 3.51E-10 3.36E-10 0.000

gr/dscf 3.71E-14 1.01E-13 1.14E-13 0.000

lb/mmBtuO2 6.02E-14 1.59E-13 1.82E-13 0.000

mg/dscm 8.48E-11 2.32E-10 2.61E-10 0.000

ng/dscm 8.48E-05 2.32E-04 2.61E-04 0.000

ng/dscm@7%O2 6.44E-05 1.74E-04 1.96E-04 0.000

ppm 5.22E-12 1.43E-11 1.60E-11 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000004 0.0000000031 0.0000000032 0.000

Elb/hr 9.54E-12 5.45E-10 4.89E-10 0.000

gr/dscf 5.29E-14 1.57E-13 1.66E-13 0.000

lb/mmBtuO2 8.60E-14 2.47E-13 2.64E-13 0.000

mg/dscm 1.21E-10 3.60E-10 3.79E-10 0.000

ng/dscm 1.21E-04 3.60E-04 3.79E-04 0.000

ng/dscm@7%O2 9.19E-05 2.70E-04 2.85E-04 0.000

ppm 7.77E-12 2.31E-11 2.43E-11 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000027 0.0000000018 0.0000000017 0.000

Elb/hr 6.44E-12 3.16E-10 2.60E-10 0.000

gr/dscf 3.57E-14 9.13E-14 8.80E-14 0.000

lb/mmBtuO2 5.80E-14 1.43E-13 1.40E-13 0.000

mg/dscm 8.18E-11 2.09E-10 2.01E-10 0.000

ng/dscm 8.18E-05 2.09E-04 2.01E-04 0.000

ng/dscm@7%O2 6.21E-05 1.57E-04 1.51E-04 0.000

Thursday, February 17, 2011 Page 11 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

ppm 5.03E-12 1.29E-11 1.24E-11 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000002 0.0000000017 0.0000000017 0.000

Elb/hr 4.77E-12 2.99E-10 2.60E-10 0.000

gr/dscf 2.65E-14 8.62E-14 8.80E-14 0.000

lb/mmBtuO2 4.30E-14 1.35E-13 1.40E-13 0.000

mg/dscm 6.06E-11 1.97E-10 2.01E-10 0.000

ng/dscm 6.06E-05 1.97E-04 2.01E-04 0.000

ng/dscm@7%O2 4.60E-05 1.48E-04 1.51E-04 0.000

ppm 3.89E-12 1.27E-11 1.29E-11 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000031 0.0000000016 0.0000000019 0.000

Elb/hr 7.39E-12 2.81E-10 2.90E-10 0.000

gr/dscf 4.10E-14 8.12E-14 9.84E-14 0.000

lb/mmBtuO2 6.66E-14 1.27E-13 1.57E-13 0.000

mg/dscm 9.39E-11 1.86E-10 2.25E-10 0.000

ng/dscm 9.39E-05 1.86E-04 2.25E-04 0.000

ng/dscm@7%O2 7.13E-05 1.40E-04 1.69E-04 0.000

ppm 6.33E-12 1.25E-11 1.52E-11 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000039 0.0000000029 0.000000002 0.000

Elb/hr 9.30E-12 5.10E-10 3.05E-10 0.000

gr/dscf 5.16E-14 1.47E-13 1.04E-13 0.000

lb/mmBtuO2 8.38E-14 2.31E-13 1.65E-13 0.000

mg/dscm 1.18E-10 3.37E-10 2.37E-10 0.000

ng/dscm 1.18E-04 3.37E-04 2.37E-04 0.000

ng/dscm@7%O2 8.96E-05 2.53E-04 1.78E-04 0.000

ppm 8.34E-12 2.38E-11 1.67E-11 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000055 0.0000000028 0.0000000046 0.000

Elb/hr 1.31E-11 4.92E-10 7.03E-10 0.000

gr/dscf 7.28E-14 1.42E-13 2.38E-13 0.000

lb/mmBtuO2 1.18E-13 2.23E-13 3.80E-13 0.000

mg/dscm 1.67E-10 3.25E-10 5.45E-10 0.000

ng/dscm 1.67E-04 3.25E-04 5.45E-04 0.000

ng/dscm@7%O2 1.27E-04 2.44E-04 4.09E-04 0.000

ppm 1.01E-11 1.97E-11 3.31E-11 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000057 0.000000027 0.000000024 0.000

Thursday, February 17, 2011 Page 12 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Elb/hr 1.36E-10 4.74E-09 3.67E-09 0.000

gr/dscf 7.54E-13 1.37E-12 1.24E-12 0.000

lb/mmBtuO2 1.23E-12 2.15E-12 1.98E-12 0.000

mg/dscm 1.73E-09 3.14E-09 2.84E-09 0.000

ng/dscm 1.73E-03 3.14E-03 2.84E-03 0.003

ng/dscm@7%O2 1.31E-03 2.36E-03 2.13E-03 0.002

ppm 0.000

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.00000017 0.00000016 0.00000011 0.000

Elb/hr 4.05E-10 2.81E-08 1.68E-08 0.000

gr/dscf 2.25E-12 8.12E-12 5.69E-12 0.000

lb/mmBtuO2 3.65E-12 1.27E-11 9.09E-12 0.000

mg/dscm 5.15E-09 1.86E-08 1.30E-08 0.000

ng/dscm 5.15E-03 1.86E-02 1.30E-02 0.012

ng/dscm@7%O2 3.91E-03 1.40E-02 9.77E-03 0.009

ppm 0.000

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000019 0.0000000099 0.000000011 0.000

Elb/hr 4.53E-11 1.74E-09 1.68E-09 0.000

gr/dscf 2.51E-13 5.02E-13 5.69E-13 0.000

lb/mmBtuO2 4.08E-13 7.88E-13 9.09E-13 0.000

mg/dscm 5.75E-10 1.15E-09 1.30E-09 0.000

ng/dscm 5.75E-04 1.15E-03 1.30E-03 0.001

ng/dscm@7%O2 4.37E-04 8.64E-04 9.77E-04 0.001

ppm 3.83E-11 7.66E-11 8.69E-11 0.000

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000014 0.0000000094 0.0000000072 0.000

Elb/hr 3.34E-11 1.65E-09 1.10E-09 0.000

gr/dscf 1.85E-13 4.77E-13 3.73E-13 0.000

lb/mmBtuO2 3.01E-13 7.48E-13 5.95E-13 0.000

mg/dscm 4.24E-10 1.09E-09 8.53E-10 0.000

ng/dscm 4.24E-04 1.09E-03 8.53E-04 0.001

ng/dscm@7%O2 3.22E-04 8.19E-04 6.41E-04 0.001

ppm 0.000

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.00000047 0.0000004 0.00000029 0.000

Elb/hr 1.12E-09 7.03E-08 4.43E-08 0.000

gr/dscf 6.22E-12 2.03E-11 1.50E-11 0.000

lb/mmBtuO2 1.01E-11 3.18E-11 2.40E-11 0.000

mg/dscm 1.42E-08 4.64E-08 3.44E-08 0.000

ng/dscm 1.42E-02 4.64E-02 3.44E-02 0.032

ng/dscm@7%O2 1.08E-02 3.49E-02 2.58E-02 0.024

Thursday, February 17, 2011 Page 13 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

ppm 0.000

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000025 0.0000000044 0.0000000032 0.000

Elb/hr 5.96E-12 7.73E-10 4.89E-10 0.000

gr/dscf 3.31E-14 2.23E-13 1.66E-13 0.000

lb/mmBtuO2 5.37E-14 3.50E-13 2.64E-13 0.000

mg/dscm 7.57E-11 5.11E-10 3.79E-10 0.000

ng/dscm 7.57E-05 5.11E-04 3.79E-04 0.000

ng/dscm@7%O2 5.75E-05 3.84E-04 2.85E-04 0.000

ppm 0.000

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000031 0.0000000047 0.0000000032 0.000

Elb/hr 7.39E-12 8.26E-10 4.89E-10 0.000

gr/dscf 4.10E-14 2.38E-13 1.66E-13 0.000

lb/mmBtuO2 6.66E-14 3.74E-13 2.64E-13 0.000

mg/dscm 9.39E-11 5.46E-10 3.79E-10 0.000

ng/dscm 9.39E-05 5.46E-04 3.79E-04 0.000

ng/dscm@7%O2 7.13E-05 4.10E-04 2.85E-04 0.000

ppm 6.02E-12 3.50E-11 2.43E-11 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000005 0.0000000044 0.0000000033 0.000

Elb/hr 1.19E-11 7.73E-10 5.04E-10 0.000

gr/dscf 6.62E-14 2.23E-13 1.71E-13 0.000

lb/mmBtuO2 1.07E-13 3.50E-13 2.73E-13 0.000

mg/dscm 1.51E-10 5.11E-10 3.91E-10 0.000

ng/dscm 1.51E-04 5.11E-04 3.91E-04 0.000

ng/dscm@7%O2 1.15E-04 3.84E-04 2.94E-04 0.000

ppm 1.07E-11 3.61E-11 2.76E-11 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000025 0.0000000016 0.0000000018 0.000

Elb/hr 5.96E-12 2.81E-10 2.75E-10 0.000

gr/dscf 3.31E-14 8.12E-14 9.32E-14 0.000

lb/mmBtuO2 5.37E-14 1.27E-13 1.49E-13 0.000

mg/dscm 7.57E-11 1.86E-10 2.13E-10 0.000

ng/dscm 7.57E-05 1.86E-04 2.13E-04 0.000

ng/dscm@7%O2 5.75E-05 1.40E-04 1.60E-04 0.000

ppm 5.66E-12 1.39E-11 1.59E-11 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000097 0.000000006 0.0000000051 0.000

Thursday, February 17, 2011 Page 14 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Elb/hr 2.31E-11 1.05E-09 7.79E-10 0.000

gr/dscf 1.28E-13 3.04E-13 2.64E-13 0.000

lb/mmBtuO2 2.09E-13 4.78E-13 4.21E-13 0.000

mg/dscm 2.94E-10 6.97E-10 6.04E-10 0.000

ng/dscm 2.94E-04 6.97E-04 6.04E-04 0.001

ng/dscm@7%O2 2.23E-04 5.24E-04 4.54E-04 0.000

ppm 2.31E-11 5.48E-11 4.75E-11 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000039 0.0000000021 0.0000000026 0.000

Elb/hr 9.30E-12 3.69E-10 3.97E-10 0.000

gr/dscf 5.16E-14 1.07E-13 1.35E-13 0.000

lb/mmBtuO2 8.38E-14 1.67E-13 2.15E-13 0.000

mg/dscm 1.18E-10 2.44E-10 3.08E-10 0.000

ng/dscm 1.18E-04 2.44E-04 3.08E-04 0.000

ng/dscm@7%O2 8.96E-05 1.83E-04 2.31E-04 0.000

ppm 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000025 0.0000000035 0.0000000032 0.000

Elb/hr 5.96E-12 6.15E-10 4.89E-10 0.000

gr/dscf 3.31E-14 1.78E-13 1.66E-13 0.000

lb/mmBtuO2 5.37E-14 2.79E-13 2.64E-13 0.000

mg/dscm 7.57E-11 4.06E-10 3.79E-10 0.000

ng/dscm 7.57E-05 4.06E-04 3.79E-04 0.000

ng/dscm@7%O2 5.75E-05 3.05E-04 2.85E-04 0.000

ppm 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000086 0.00000009 0.000000087 0.000

Elb/hr 2.05E-10 1.58E-08 1.33E-08 0.000

gr/dscf 1.14E-12 4.57E-12 4.50E-12 0.000

lb/mmBtuO2 1.85E-12 7.16E-12 7.19E-12 0.000

mg/dscm 2.60E-09 1.05E-08 1.03E-08 0.000

ng/dscm 2.60E-03 1.05E-02 1.03E-02 0.008

ng/dscm@7%O2 1.97E-03 7.89E-03 7.74E-03 0.006

ppm 0.000

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000041 0.0000000071 0.0000000057 0.000

Elb/hr 9.78E-12 1.25E-09 8.71E-10 0.000

gr/dscf 5.43E-14 3.60E-13 2.95E-13 0.000

lb/mmBtuO2 8.81E-14 5.65E-13 4.71E-13 0.000

mg/dscm 1.24E-10 8.24E-10 6.75E-10 0.000

ng/dscm 1.24E-04 8.24E-04 6.75E-04 0.001

ng/dscm@7%O2 9.42E-05 6.19E-04 5.07E-04 0.000

Thursday, February 17, 2011 Page 15 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

ppm 0.000

Compound: OCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000614 0.0000000585 0.0000000446 0.000

Elb/hr 1.46E-10 1.03E-08 6.81E-09 0.000

gr/dscf 8.13E-13 2.97E-12 2.31E-12 0.000

lb/mmBtuO2 1.32E-12 4.66E-12 3.69E-12 0.000

mg/dscm 1.86E-09 6.79E-09 5.28E-09 0.000

ng/dscm 1.86E-03 6.79E-03 5.28E-03 0.005

ng/dscm@7%O2 1.41E-03 5.10E-03 3.97E-03 0.003

ppm 9.73E-11 3.55E-10 2.76E-10 0.000

Compound: OCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000082 0.0000000779 0.0000000061 0.000

Elb/hr 1.96E-11 1.37E-08 9.32E-10 0.000

gr/dscf 1.09E-13 3.95E-12 3.16E-13 0.000

lb/mmBtuO2 1.76E-13 6.20E-12 5.04E-13 0.000

mg/dscm 2.48E-10 9.05E-09 7.23E-10 0.000

ng/dscm 2.48E-04 9.05E-03 7.23E-04 0.003

ng/dscm@7%O2 1.88E-04 6.80E-03 5.43E-04 0.003

ppm 1.35E-11 4.90E-10 3.92E-11 0.000

Compound: Other HpCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000078 -0.0000000058 0.0000000043 0.000

Elb/hr 1.86E-11 -1.02E-09 6.57E-10 0.000

gr/dscf 1.03E-13 -2.94E-13 2.23E-13 0.000

lb/mmBtuO2 1.68E-13 -4.62E-13 3.55E-13 0.000

mg/dscm 2.36E-10 -6.73E-10 5.09E-10 0.000

ng/dscm 2.36E-04 -6.73E-04 5.09E-04 0.000

ng/dscm@7%O2 1.79E-04 -5.06E-04 3.82E-04 0.000

ppm 1.34E-11 -3.81E-11 2.88E-11 0.000

Compound: Other HpCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000065 0.000000004 -0.0000000016 0.000

Elb/hr 1.55E-11 7.03E-10 -2.44E-10 0.000

gr/dscf 8.60E-14 2.03E-13 -8.28E-14 0.000

lb/mmBtuO2 1.40E-13 3.18E-13 -1.32E-13 0.000

mg/dscm 1.97E-10 4.64E-10 -1.90E-10 0.000

ng/dscm 1.97E-04 4.64E-04 -1.90E-04 0.000

ng/dscm@7%O2 1.50E-04 3.49E-04 -1.43E-04 0.000

ppm 1.16E-11 2.73E-11 -1.11E-11 0.000

Compound: Other HxCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg -0.0000000027 -0.0000000019 -0.0000000017 0.000

Thursday, February 17, 2011 Page 16 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Elb/hr -6.44E-12 -3.34E-10 -2.60E-10 0.000

gr/dscf -3.57E-14 -9.64E-14 -8.80E-14 0.000

lb/mmBtuO2 -5.80E-14 -1.51E-13 -1.40E-13 0.000

mg/dscm -8.18E-11 -2.21E-10 -2.01E-10 0.000

ng/dscm -8.18E-05 -2.21E-04 -2.01E-04 0.000

ng/dscm@7%O2 -6.21E-05 -1.66E-04 -1.51E-04 0.000

ppm -5.03E-12 -1.36E-11 -1.24E-11 0.000

Compound: Other HxCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000249 0.0000000136 -0.0000000009 0.000

Elb/hr 5.94E-11 2.39E-09 -1.37E-10 0.000

gr/dscf 3.29E-13 6.90E-13 -4.66E-14 0.000

lb/mmBtuO2 5.35E-13 1.08E-12 -7.44E-14 0.000

mg/dscm 7.54E-10 1.58E-09 -1.07E-10 0.000

ng/dscm 7.54E-04 1.58E-03 -1.07E-04 0.001

ng/dscm@7%O2 5.73E-04 1.19E-03 -8.04E-05 0.001

ppm 4.84E-11 1.01E-10 -6.84E-12 0.000

Compound: Other PeCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0 0.0000000004 0.0000000007 0.000

Elb/hr 0.00E+00 7.03E-11 1.07E-10 0.000

gr/dscf 0.00E+00 2.03E-14 3.62E-14 0.000

lb/mmBtuO2 0.00E+00 3.18E-14 5.79E-14 0.000

mg/dscm 0.00E+00 4.64E-11 8.29E-11 0.000

ng/dscm 0.00E+00 4.64E-05 8.29E-05 0.000

ng/dscm@7%O2 0.00E+00 3.49E-05 6.23E-05 0.000

ppm 0.00E+00 3.13E-12 5.60E-12 0.000

Compound: Other PeCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000571 0.0000000457 0.0000000041 0.000

Elb/hr 1.36E-10 8.03E-09 6.26E-10 0.000

gr/dscf 7.56E-13 2.32E-12 2.12E-13 0.000

lb/mmBtuO2 1.23E-12 3.64E-12 3.39E-13 0.000

mg/dscm 1.73E-09 5.31E-09 4.86E-10 0.000

ng/dscm 1.73E-03 5.31E-03 4.86E-04 0.003

ng/dscm@7%O2 1.31E-03 3.99E-03 3.65E-04 0.002

ppm 1.22E-10 3.75E-10 3.43E-11 0.000

Compound: Other TCDD

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000044 0.0000000006 0.0000000003 0.000

Elb/hr 1.05E-11 1.05E-10 4.58E-11 0.000

gr/dscf 5.82E-14 3.04E-14 1.55E-14 0.000

lb/mmBtuO2 9.46E-14 4.78E-14 2.48E-14 0.000

mg/dscm 1.33E-10 6.97E-11 3.55E-11 0.000

ng/dscm 1.33E-04 6.97E-05 3.55E-05 0.000

ng/dscm@7%O2 1.01E-04 5.24E-05 2.67E-05 0.000

Thursday, February 17, 2011 Page 17 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

ppm 9.95E-12 5.20E-12 2.65E-12 0.000

Compound: Other TCDF

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000000064 0.0000000224 0.0000000021 0.000

Elb/hr 1.53E-11 3.94E-09 3.21E-10 0.000

gr/dscf 8.47E-14 1.14E-12 1.09E-13 0.000

lb/mmBtuO2 1.38E-13 1.78E-12 1.74E-13 0.000

mg/dscm 1.94E-10 2.60E-09 2.49E-10 0.000

ng/dscm 1.94E-04 2.60E-03 2.49E-04 0.001

ng/dscm@7%O2 1.47E-04 1.95E-03 1.87E-04 0.001

ppm 1.52E-11 2.04E-10 1.96E-11 0.000

Compound: Total Dioxins

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000094 0.0000000682 0.0000000642 0.000

Elb/hr 2.24E-10 1.20E-08 9.80E-09 0.000

gr/dscf 1.24E-12 3.46E-12 3.32E-12 0.000

lb/mmBtuO2 2.02E-12 5.43E-12 5.31E-12 0.000

mg/dscm 2.85E-09 7.92E-09 7.61E-09 0.000

ng/dscm 2.85E-03 7.92E-03 7.61E-03 0.006

ng/dscm@7%O2 2.16E-03 5.95E-03 5.72E-03 0.005

ppm 0.000

Compound: Total Furans

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.000000132 0.0000002137 0.0000000391 0.000

Elb/hr 3.15E-10 3.75E-08 5.97E-09 0.000

gr/dscf 1.75E-12 1.08E-11 2.02E-12 0.000

lb/mmBtuO2 2.84E-12 1.70E-11 3.23E-12 0.000

mg/dscm 4.00E-09 2.48E-08 4.63E-09 0.000

ng/dscm 4.00E-03 2.48E-02 4.63E-03 0.011

ng/dscm@7%O2 3.04E-03 1.86E-02 3.48E-03 0.008

ppm 0.000

Compound: Total PCBs

Average

RunNumber U1-M23-1 U1-M23-2 U1-M23-3

Mass_mg 0.0000008345 0.0000007162 0.0000005485 0.000

Elb/hr 1.99E-09 1.26E-07 8.38E-08 0.000

gr/dscf 1.10E-11 3.63E-11 2.84E-11 0.000

lb/mmBtuO2 1.79E-11 5.70E-11 4.53E-11 0.000

mg/dscm 2.53E-08 8.32E-08 6.50E-08 0.000

ng/dscm 2.53E-02 8.32E-02 6.50E-02 0.058

ng/dscm@7%O2 1.92E-02 6.25E-02 4.88E-02 0.044

ppm 0.000

Location: Unit 1 Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Thursday, February 17, 2011 Page 18 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Run U1-M25A-1 U1-M25A-2 U1-M25A-3

Elb/hr 2.88E-01 2.93E-01 1.51E-01 0.244

gr/dscf 8.70E-05 8.87E-05 4.57E-05 0.000

lb/mmBtuO2 1.40E-04 1.42E-04 7.33E-05 0.000

mg/dscm 1.99E-01 2.03E-01 1.05E-01 0.169

ppm 1.09E-01 1.11E-01 5.70E-02 0.092

Location: Unit 1 Stack - Method 29

Compound: Antimony

Average

RunNumber U1-M29-1 U1-M29-2 U1-M29-3

Mass_mg 0.0004704 0.0003852 0.0003306 0.000

Elb/hr 1.84E-04 1.49E-04 1.28E-04 0.000

gr/dscf 5.52E-08 4.57E-08 4.00E-08 0.000

lb/mmBtuO2 9.05E-08 7.57E-08 6.46E-08 0.000

mg/dscm 1.26E-04 1.05E-04 9.16E-05 0.000

ppm 2.50E-05 2.07E-05 1.81E-05 0.000

Compound: Arsenic

Average

RunNumber U1-M29-1 U1-M29-2 U1-M29-3

Mass_mg 0.0007395 0.0007465 0.0007517 0.001

Elb/hr 2.90E-04 2.90E-04 2.91E-04 0.000

gr/dscf 8.68E-08 8.86E-08 9.10E-08 0.000

lb/mmBtuO2 1.42E-07 1.47E-07 1.47E-07 0.000

mg/dscm 1.99E-04 2.03E-04 2.08E-04 0.000

ppm 6.38E-05 6.51E-05 6.68E-05 0.000

Compound: Beryllium

Average

RunNumber U1-M29-1 U1-M29-2 U1-M29-3

Mass_mg 0.0000632 0.00008 0.0000636 0.000

Elb/hr 2.48E-05 3.10E-05 2.46E-05 0.000

gr/dscf 7.42E-09 9.50E-09 7.70E-09 0.000

lb/mmBtuO2 1.22E-08 1.57E-08 1.24E-08 0.000

mg/dscm 1.70E-05 2.17E-05 1.76E-05 0.000

ppm 4.53E-05 5.80E-05 4.70E-05 0.000

Compound: Cadmium

Average

RunNumber U1-M29-1 U1-M29-2 U1-M29-3

Mass_mg 0.007621 0.0017087 0.001035 0.003

Elb/hr 2.99E-03 6.63E-04 4.01E-04 0.001

gr/dscf 8.94E-07 2.03E-07 1.25E-07 0.000

lb/mmBtuO2 1.47E-06 3.36E-07 2.02E-07 0.000

mg/dscm 2.05E-03 4.64E-04 2.87E-04 0.001

ppm 4.38E-04 9.93E-05 6.13E-05 0.000

Compound: Chromium

Average

RunNumber U1-M29-1 U1-M29-2 U1-M29-3

Mass_mg 0.05429 0.021168 0.013615 0.030

Elb/hr 2.13E-02 8.21E-03 5.27E-03 0.012

Thursday, February 17, 2011 Page 19 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Process Run Data

gr/dscf 6.37E-06 2.51E-06 1.65E-06 0.000

lb/mmBtuO2 1.04E-05 4.16E-06 2.66E-06 0.000

mg/dscm 1.46E-02 5.75E-03 3.77E-03 0.008

ppm 6.74E-03 2.66E-03 1.74E-03 0.004

Compound: Cobalt

Average

RunNumber U1-M29-1 U1-M29-2 U1-M29-3

Mass_mg 0.004828 0.0074462 0.0049431 0.006

Elb/hr 1.89E-03 2.89E-03 1.91E-03 0.002

gr/dscf 5.67E-07 8.84E-07 5.98E-07 0.000

lb/mmBtuO2 9.29E-07 1.46E-06 9.66E-07 0.000

mg/dscm 1.30E-03 2.02E-03 1.37E-03 0.002

ppm 5.29E-04 8.26E-04 5.59E-04 0.001

Compound: Filterable Particulate

Average

RunNumber U1-M29-1 U1-M29-2 U1-M29-3

Mass_mg 79.6 257.5 155 164.033

Elb/hr 3.12E+01 9.99E+01 6.00E+01 63.700

gr/dscf 9.34E-03 3.06E-02 1.88E-02 0.020

lb/mmBtuO2 1.53E-02 5.06E-02 3.03E-02 0.032

mg/dscm 2.14E+01 7.00E+01 4.29E+01 44.767

ppm #Num!

Thursday, February 17, 2011 Page 20 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Average Heat Input 1846.1/million BTU using O2 6/7/10 - M29 Run 

1

0

2 Average Heat Input 1835.5/million BTU using O2 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Average Heat Input 1852.5/million BTU using O2 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Average Heat Input 1847.2/million BTU using O2 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Average Heat Input 1743.5/million BTU using O2 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Average Heat Input 1817.6/million BTU using O2 6/12/10 - OTM 

27/28 Run 3

0

7 Average Heat Input 1789.5/million BTU using O2 6/16/10 - FTIR 

Runs 1-3

0

8 Average Heat Input 1771.3/million BTU using O2 7/26/10 - 30B Run 

1

0

9 Average Heat Input 1790.1/million BTU using O2 7/27/10 - 30B 

Runs 2-3

0

1 Pet Coke Firing Rate 63.64 Tons per Hour 6/7/10 - M29 Run 

1

0

2 Pet Coke Firing Rate 63.93 Tons per Hour 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Pet Coke Firing Rate 65.16 Tons per Hour 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Pet Coke Firing Rate 63.45 Tons per Hour 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Pet Coke Firing Rate 61.36 Tons per Hour 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Pet Coke Firing Rate 62.13 Tons per Hour 6/12/10 - OTM 

27/28 Run 3

0

Thursday, February 17, 2011 Page 21 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

7 Pet Coke Firing Rate 57.59 Tons per Hour 6/16/10 - FTIR 

Runs 1-3

0

8 Pet Coke Firing Rate 61.71 Tons per Hour 7/26/10 - 30B Run 

1

0

9 Pet Coke Firing Rate 62.34 Tons per Hour 7/27/10 - 30B 

Runs 2-3

0

1 Steam Output 1285.6 KPPH 6/7/10 - M29 Run 

1

0

2 Steam Output 1268.6 KPPH 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Steam Output 1287.3 KPPH 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Steam Output 1283.8 KPPH 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Steam Output 1246.8 KPPH 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Steam Output 1262.2 KPPH 6/12/10 - OTM 

27/28 Run 3

0

7 Steam Output 1200.3 KPPH 6/16/10 - FTIR 

Runs 1-3

0

8 Steam Output 1236.8 KPPH 7/26/10 - 30B Run 

1

0

9 Steam Output 1262.4 KPPH 7/27/10 - 30B 

Runs 2-3

0

1 Unit Net Electric Generation 3467 MWh 6/7/10 - M29 Run 

1

0

2 Unit Net Electric Generation 3483 MWh 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Unit Net Electric Generation 3492 MWh 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Unit Net Electric Generation 3493 MWh 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Unit Net Electric Generation 3493 MWh 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

Thursday, February 17, 2011 Page 22 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

6 Unit Net Electric Generation 3493 MWh 6/12/10 - OTM 

27/28 Run 3

0

7 Unit Net Electric Generation 3490 MWh 6/16/10 - FTIR 

Runs 1-3

0

8 Unit Net Electric Generation 3493 MWh 7/26/10 - 30B Run 

1

0

9 Unit Net Electric Generation 3492 MWh 7/27/10 - 30B 

Runs 2-3

0

1 Unit Gross Electric Generation 152.45 Mwe 6/7/10 - M29 Run 

1

0

2 Unit Gross Electric Generation 153.2 Mwe 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Unit Gross Electric Generation 153.65 Mwe 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Unit Gross Electric Generation 153.58 Mwe 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Unit Gross Electric Generation 153.68 Mwe 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Unit Gross Electric Generation 153.6 Mwe 6/12/10 - OTM 

27/28 Run 3

0

7 Unit Gross Electric Generation 153.44 Mwe 6/16/10 - FTIR 

Runs 1-3

0

8 Unit Gross Electric Generation 153.5 Mwe 7/26/10 - 30B Run 

1

0

9 Unit Gross Electric Generation 153.5 Mwe 7/27/10 - 30B 

Runs 2-3

0

1 Flue Gas Flow Rate 375990 dscfm 6/7/10 - M29 Run 

1

0

2 Flue Gas Flow Rate 371242 dscfm 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Flue Gas Flow Rate 369053 dscfm 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Flue Gas Flow Rate 363305 dscfm 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

Thursday, February 17, 2011 Page 23 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

5 Flue Gas Flow Rate 360280 dscfm 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Flue Gas Flow Rate 362758 dscfm 6/12/10 - OTM 

27/28 Run 3

0

7 Flue Gas Flow Rate 355624 dscfm 6/16/10 - FTIR 

Runs 1-3

0

8 Flue Gas Flow Rate 364702 dscfm 7/26/10 - 30B Run 

1

0

9 Flue Gas Flow Rate 364905 dscfm 7/27/10 - 30B 

Runs 2-3

0

1 Flue Gas Pressure 14.46 atm 6/7/10 - M29 Run 

1

0

2 Flue Gas Pressure 14.5 atm 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Flue Gas Pressure 14.36 atm 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Flue Gas Pressure 14.42 atm 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Flue Gas Pressure 14.46 atm 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Flue Gas Pressure 14.42 atm 6/12/10 - OTM 

27/28 Run 3

0

7 Flue Gas Pressure 14.4 atm 6/16/10 - FTIR 

Runs 1-3

0

8 Flue Gas Pressure 14.51 atm 7/26/10 - 30B Run 

1

0

9 Flue Gas Pressure 14.49 atm 7/27/10 - 30B 

Runs 2-3

0

1 Flue Gas Sampling Point Temperature 331.12 Deg F 6/7/10 - M29 Run 

1

0

2 Flue Gas Sampling Point Temperature 33.8 Deg F 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Flue Gas Sampling Point Temperature 332.41 Deg F 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

Thursday, February 17, 2011 Page 24 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

4 Flue Gas Sampling Point Temperature 333.97 Deg F 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Flue Gas Sampling Point Temperature 336.08 Deg F 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Flue Gas Sampling Point Temperature 337.32 Deg F 6/12/10 - OTM 

27/28 Run 3

0

7 Flue Gas Sampling Point Temperature 337.63 Deg F 6/16/10 - FTIR 

Runs 1-3

0

8 Flue Gas Sampling Point Temperature 339.74 Deg F 7/26/10 - 30B Run 

1

0

9 Flue Gas Sampling Point Temperature 340.83 Deg F 7/27/10 - 30B 

Runs 2-3

0

1 Flue Gas Oxygen Content 3.98 % 6/7/10 - M29 Run 

1

0

2 Flue Gas Oxygen Content 3.85 % 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

3 Flue Gas Oxygen Content 3.62 % 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Flue Gas Oxygen Content 3.38 % 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Flue Gas Oxygen Content 4.24 % 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Flue Gas Oxygen Content 3.63 % 6/12/10 - OTM 

27/28 Run 3

0

7 Flue Gas Oxygen Content 3.57 % 6/16/10 - FTIR 

Runs 1-3

0

8 Flue Gas Oxygen Content 4.18 % 7/26/10 - 30B Run 

1

0

9 Flue Gas Oxygen Content 4.02 % 7/27/10 - 30B 

Runs 2-3

0

1 Flue Gas Carbon Dioxide Content 15.12 % 6/7/10 - M29 Run 

1

0

2 Flue Gas Carbon Dioxide Content 15.25 % 6/8/10 - M0010 

Runs 1&2, M29 

Run 2

0

Thursday, February 17, 2011 Page 25 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

APCD Run Data

Process Lab Run Data

3 Flue Gas Carbon Dioxide Content 15.44 % 6/9/10 - M0031 

Runs 1-3, M0010 

Run 4, M29 Run 

3, M23 Run 1

0

4 Flue Gas Carbon Dioxide Content 15.66 % 6/10/10 - OTM 

27/28 Run 1, M23 

Run 2

0

5 Flue Gas Carbon Dioxide Content 14.89 % 6/11/10 - OTM 

27/28 Run 2, M23 

Run 3, M3A, 6C, 

7E, 10, 25A Runs 

1-3

0

6 Flue Gas Carbon Dioxide Content 15.43 % 6/12/10 - OTM 

27/28 Run 3

0

7 Flue Gas Carbon Dioxide Content 15.48 % 6/16/10 - FTIR 

Runs 1-3

0

8 Flue Gas Carbon Dioxide Content 15 % 7/26/10 - 30B Run 

1

0

9 Flue Gas Carbon Dioxide Content 15.1 % 7/27/10 - 30B 

Runs 2-3

0

Thursday, February 17, 2011 Page 26 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Sampling / Stack Data Results Detail

Location Unit 1 Stack - Method 10

Average

Run Number U1-M10-1 U1-M10-2 U1-M10-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 AM 1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Fuel Factor 1.09 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9827 9892 9892 9,870.333

Moisture, % 7.2 7.2 7.2 7.200

Analyzer Make California 

Analytical 

Instruments

California 

Analytical 

Instruments

California 

Analytical 

Instruments

Analyzer Model Model 602P Model 602P Model 602P

Analyzer Serial Number

Operating Range 100 100 100 100.000

Operating Units PPM PPM PPM

No. Readings/Avg. 60 60 60 60.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Pre Zero Cylinder Instrument Response 1.1 0.3 -0.3 0.367

Calibration Pre Zero Cylinder Bias 1.1 0.3 -0.3 0.367

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID XL001279BCOXL001279BCOXL001279BCO

Calibration Pre High Cylinder Instrument Response 32 30.2 30 30.733

Calibration Pre High Cylinder Bias 2.3 0.5 0.3 1.033

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Post Zero Cylinder Instrument Response 0.3 -0.3 1.2 0.400

Calibration Post Zero Cylinder Bias 0.3 -0.3 1.2 0.400

Calibration Post Zero Cylinder Drift 0.8 0.6 1.5 0.967

Calibration Post High Cylinder ID XL001279BCOXL001279BCOXL001279BCO

Calibration Post High Cylinder Instrument Response 30.2 30 31.2 30.467

Calibration Post High Cylinder Bias 0.5 0.3 1.5 0.767

Calibration Post High Cylinder Drift 1.8 0.2 1.2 1.067

Cavg 16.8 16.5 18.7 17.333

Cavg Units ppmvd ppmvd ppmvd

Cgas 16.2377 16.807 18.5587 17.201

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 11122 11121 11121 11,121.333

Fc 1836 1836 1836 1,836.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 27 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 23

Average

Run Number U1-M23-1 U1-M23-2 U1-M23-3

Test Date 6/9/2010 6/10/2010 6/11/2010

Run Start Time 12:47:00 PM 9:01:00 AM 8:31:00 AM

Run Finish Time 8:37:00 PM 4:51:00 PM 4:21:00 PM

Net Traversing Points 49 49 49

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.239 0.239 0.239 0.239

Pitot Tube Coefficient 0.858 0.858 0.858 0.858

Dry Gas Meter Calibration Factor 1.047 1.047 1.047 1.047

Barometric Pressure, inches of Mercury 29.2 29.25 29.4 29.283

Average Orifice Meter Differential, inches H2O 1.64 1.51 1.45 1.533

Dry Gas Meter Volume Sampled, cubic feet 1,180.547 307.170 300.320 596.012

Average Dry Gas Meter Temperature, °F 88.40 87.80 89.22 88.473

Dry Gas Meter Volume Sampled, dscf 1,166.212 304.191 298.110 589.504

Total Moisture Liquid collected, g 504.6 467.2 490.8 487.533

Volume of Water Vapor, standard cubic feet 23.75 21.99 23.10 22.947

Moisture Content of Stack Gas, % 95.96 6.74 7.19 36.630

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 4.0400000000

0001E-02

0.9326 0.9281 0.634

Carbon Dioxide, % 17.4 17.6 17.6 17.533

Oxygen, % 2.6 2.4 2.4 2.467

Carbon Monoxide & Nitrogen, % 80 80 80 80.000

Fuel Factor 1.05 1.05 1.05

Dry Molecular Weight, lb/lb-Mole 30.89 30.91 30.91 30.903

Wet Molecular weight, lb/lb-Mole 18.52 30.04 29.98 26.180

Flue Gas Static Pressure, inches of H2O 0.2 0.2 0.2 0.200

Absolute Flue Gas Pressure, inches of Mercury 29.21 29.26 29.41 29.293

Average Stack Gas Temperature, °F 342.46 342.08 403.10 362.547

Average Velocity Head, inches of H2O 0.7648531970

35529

0.858179468

295008

0.671659768

715399

0.765

Average Stack Gas Velocity, feet/second 78.13 64.91 59.48 67.507

Stack Cross-Sectional Area, square feet 172.809 172.809 172.809 172.809

Dry Volumetric Flow Rate, dry scfm 21,023.1 404,067.2 344,183.1 256,424.467

Actual Wet Volumetric Flue Gas Flow Rate, acfm 810,094.0 673,021.9 616,720.8 699,945.567

Percent Isokinetic of Sampling Rate, % 6,410.4 87.0 100.1 2,199.167

Percent Excess Air, % 14.0 12.8 12.8 13.200

F-Factor, dscfm/MMBtu @ %O2 9956 9720 9892 9,856.000

Round Duct Diameter, inches 178 178 178

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 11675 11175 11121 11,323.667

Fc 1846 1804 1836 1,828.667

Thursday, February 17, 2011 Page 28 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 25A

Average

Run Number U1-M25A-1 U1-M25A-2 U1-M25A-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 AM 1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Fuel Factor 1.09 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Analyzer Make JUM 

Engineering

JUM 

Engineering

JUM 

Engineering

Analyzer Model Model VE-7 Model VE-7 Model VE-7

Analyzer Serial Number

Operating Range 10 10 10 10.000

Operating Units PPM PPM PPM

No. Readings/Avg. 60 60 60 60.000

Calibration Set 5 5 5 5.000

Calibration Pre Zero Cylinder ID VOC Free Air VOC Free 

Air

VOC Free Air

Calibration Pre Zero Cylinder Instrument Response 0 0 0.2 0.067

Calibration Pre Zero Cylinder Bias 0 0 2 0.667

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM027314-

PROP

ALM027314

-PROP

ALM027314-

PROP

Calibration Pre High Cylinder Instrument Response 5.3 5.1 5.3 5.233

Calibration Pre High Cylinder Bias 0 -2 0 -0.667

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID VOC Free Air VOC Free 

Air

VOC Free Air

Calibration Post Zero Cylinder Instrument Response 0 0.2 0.3 0.167

Calibration Post Zero Cylinder Bias 0 2 3 1.667

Calibration Post Zero Cylinder Drift 0 2 1 1.000

Calibration Post High Cylinder ID ALM027314-

PROP

ALM027314

-PROP

ALM027314-

PROP

Calibration Post High Cylinder Instrument Response 5.1 5.3 5.1 5.167

Calibration Post High Cylinder Bias -2 0 -2 -1.333

Calibration Post High Cylinder Drift 2 2 2 2.000

Cavg 0.1 0.2 0.3 0.200

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.1086 0.1107 0.057 0.092

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Cgasw 0.1007692307

69231

0.102745098

039216

5.292929292

92929E-02

0.085

Cgasw Units ppmvw ppmvw ppmvw

Thursday, February 17, 2011 Page 29 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 29

Average

Run Number U1-M29-1 U1-M29-2 U1-M29-3

Test Date 6/7/2010 6/8/2010 6/9/2010

Run Start Time 9:45:00 AM 10:15:00 AM 8:07:00 AM

Run Finish Time 1:35:00 PM 2:05:00 PM 11:57:00 AM

Net Traversing Points 25 25 25

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.22 0.219 0.219 0.219

Pitot Tube Coefficient 0.857 0.857 0.857 0.857

Dry Gas Meter Calibration Factor 0.958 0.958 0.958 0.958

Barometric Pressure, inches of Mercury 29.3 29.5 29.1 29.300

Average Orifice Meter Differential, inches H2O 1.12 1.08 1.06 1.087

Dry Gas Meter Volume Sampled, cubic feet 141.120 139.720 138.210 139.683

Average Dry Gas Meter Temperature, °F 73.08 77.48 74.65 75.070

Dry Gas Meter Volume Sampled, dscf 131.498 129.994 127.515 129.669

Total Moisture Liquid collected, g 196.6 211.9 230.8 213.100

Volume of Water Vapor, standard cubic feet 9.25 9.97 10.86 10.027

Moisture Content of Stack Gas, % 6.57 7.12 7.85 7.180

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9343 0.9288 0.9215 0.928

Carbon Dioxide, % 17 16.9 17.5 17.133

Oxygen, % 3 3.1 2.5 2.867

Carbon Monoxide & Nitrogen, % 80 80 80 80.000

Fuel Factor 1.05 1.05 1.05

Dry Molecular Weight, lb/lb-Mole 30.84 30.83 30.90 30.857

Wet Molecular weight, lb/lb-Mole 30.00 29.92 29.89 29.937

Flue Gas Static Pressure, inches of H2O 0.068 0.068 0.068 0.068

Absolute Flue Gas Pressure, inches of Mercury 29.31 29.51 29.11 29.310

Average Stack Gas Temperature, °F 331.17 337.79 333.21 334.057

Average Velocity Head, inches of H2O 0.7842559727

1793

0.758738946

823342

0.742890111

890253

0.762

Average Stack Gas Velocity, feet/second 61.54 60.66 60.29 60.830

Stack Cross-Sectional Area, square feet 172.809 172.809 172.809 172.809

Dry Volumetric Flow Rate, dry scfm 389,744.3 381,324.9 373,065.1 381,378.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 638,080.0 628,955.6 625,119.3 630,718.300

Percent Isokinetic of Sampling Rate, % 92.0 93.8 94.1 93.300

Percent Excess Air, % 16.6 17.2 13.4 15.733

F-Factor, dscfm/MMBtu @ %O2 9825 9875 9956 9,885.333

Round Duct Diameter, inches 178 178 178

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Thursday, February 17, 2011 Page 30 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 3A CO2

Average

Run Number U1-M3ACO2-

1

U1-

M3ACO2-2

U1-

M3ACO2-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 AM 1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Fuel Factor 1.09 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 385534 385535 385534 385,534.333

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Analyzer Make California 

Analytical 

Instruments

California 

Analytical 

Instruments

California 

Analytical 

Instruments

Analyzer Model Model 602P Model 602P Model 602P

Analyzer Serial Number

Operating Range 20 20 20 20.000

Operating Units % % %

No. Readings/Avg. 60 60 60 60.000

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Pre Zero Cylinder Instrument Response 0 0.2 0 0.067

Calibration Pre Zero Cylinder Bias 0 1 0 0.333

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID 32-

112579961-1-

CO2

32-

112579961-

1-CO2

32-

112579961-1-

CO2

Calibration Pre High Cylinder Instrument Response 17.1 17.1 17 17.067

Calibration Pre High Cylinder Bias -1 -1 -1.5 -1.167

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Post Zero Cylinder Instrument Response 0.2 0 0.1 0.100

Calibration Post Zero Cylinder Bias 1 0 0.5 0.500

Calibration Post Zero Cylinder Drift 1 1 0.5 0.833

Calibration Post High Cylinder ID 32-

112579961-1-

CO2

32-

112579961-

1-CO2

32-

112579961-1-

CO2

Calibration Post High Cylinder Instrument Response 17.1 17 16.9 17.000

Calibration Post High Cylinder Bias -1 -1.5 -2 -1.500

Calibration Post High Cylinder Drift 0 0.5 0.5 0.333

Cavg 16.8 16.8 16.8 16.800

Cavg Units %vd %vd %vd

Cgas 17.0242 17.0744 17.1762 17.092

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 11123 11122 11122 11,122.333

Fc 1836 1836 1836 1,836.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 31 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Thursday, February 17, 2011 Page 32 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 3A O2

Average

Run Number U1-M3AO2-1 U1-M3AO2-

2

U1-M3AO2-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 AM 1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Fuel Factor 1.09 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Analyzer Make California 

Analytical 

Instruments

California 

Analytical 

Instruments

California 

Analytical 

Instruments

Analyzer Model Model 602P Model 602P Model 602P

Analyzer Serial Number

Operating Range 13 13 13 13.000

Operating Units % % %

No. Readings/Avg. 60 60 60 60.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Pre Zero Cylinder Instrument Response 0.1 0.1 0.1 0.100

Calibration Pre Zero Cylinder Bias 0.77 0.77 0.77 0.770

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID 32-

112579961-1-

O2

32-

112579961-

1-O2

32-

112579961-1-

O2

Calibration Pre High Cylinder Instrument Response 6.1 6 6.1 6.067

Calibration Pre High Cylinder Bias 0.77 0 0.77 0.513

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Post Zero Cylinder Instrument Response 0.1 0.1 0.1 0.100

Calibration Post Zero Cylinder Bias 0.77 0.77 0.77 0.770

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID 32-

112579961-1-

O2

32-

112579961-

1-O2

32-

112579961-1-

O2

Calibration Post High Cylinder Instrument Response 6 6.1 6.1 6.067

Calibration Post High Cylinder Bias 0 0.77 0.77 0.513

Calibration Post High Cylinder Drift 0.77 0.77 0 0.513

Cavg 2.6 2.4 2.5 2.500

Cavg Units %vd %vd %vd

Cgas 2.4819 2.2834 2.3628 2.376

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 33 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 6C

Average

Run Number U1-M6C-1 U1-M6C-2 U1-M6C-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 AM 1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Fuel Factor 1.09 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Analyzer Make Thermo Thermo Thermo

Analyzer Model Model 43i Model 43i Model 43i

Analyzer Serial Number

Operating Range 500 500 500 500.000

Operating Units PPM PPM PPM

No. Readings/Avg. 60 60 60 60.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Pre Zero Cylinder Instrument Response 3.3 2.2 3 2.833

Calibration Pre Zero Cylinder Bias 0.6 0.38 0.54 0.507

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM012269-

SO2

ALM012269

-SO2

ALM012269-

SO2

Calibration Pre High Cylinder Instrument Response 242.7 241.7 241.9 242.100

Calibration Pre High Cylinder Bias -1.46 -1.66 -1.62 -1.580

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Post Zero Cylinder Instrument Response 2.2 3 2.5 2.567

Calibration Post Zero Cylinder Bias 0.38 0.54 0.44 0.453

Calibration Post Zero Cylinder Drift 0.22 0.16 0.1 0.160

Calibration Post High Cylinder ID ALM012269-

SO2

ALM012269

-SO2

ALM012269-

SO2

Calibration Post High Cylinder Instrument Response 241.7 241.9 240 241.200

Calibration Post High Cylinder Bias -1.66 -1.62 -2 -1.760

Calibration Post High Cylinder Drift 0.2 3.999999999

99998E-02

0.38 0.207

Cavg 192.8 221.1 168.8 194.233

Cavg Units ppmvd ppmvd ppmvd

Cgas 200.0109 230.1923 175.67 201.958

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 34 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - Method 7E

Average

Run Number U1-M7E-1 U1-M7E-2 U1-M7E-3

Test Date 6/11/2010 6/11/2010 6/11/2010

Run Start Time 8:51:00 AM 11:15:00 AM 1:40:00 PM

Run Finish Time 10:59:00 AM 1:21:00 PM 3:43:00 PM

Carbon Dioxide, % 16.8 16.8 16.8 16.800

Oxygen, % 2.6 2.4 2.5 2.500

Fuel Factor 1.09 1.1 1.1

Dry Volumetric Flow Rate, dry scfm 385534 385534 385534 385,534.000

F-Factor, dscfm/MMBtu @ %O2 9893 9893 9893 9,893.000

Moisture, % 7.2 7.2 7.2 7.200

Analyzer Make Teledyne-API TeledyneAPITeledyne-API

Analyzer Model Model 200EH Model 

200EH

Model 200EH

Analyzer Serial Number

Operating Range 200 200 200 200.000

Operating Units PPM PPM PPM

No. Readings/Avg. 60 60 60 60.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Pre Zero Cylinder Instrument Response 0.9 0.8 0.7 0.800

Calibration Pre Zero Cylinder Bias 0.2 0.15 0.1 0.150

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALMX068001

-NOX

ALMX06800

1-NOX

ALMX06800

1-NOX

Calibration Pre High Cylinder Instrument Response 92.4 90.9 89.3 90.867

Calibration Pre High Cylinder Bias -1.25 -2 -2.8 -2.017

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0012998-

N2

EB0012998-

N2

EB0012998-

N2

Calibration Post Zero Cylinder Instrument Response 0.8 0.7 0.7 0.733

Calibration Post Zero Cylinder Bias 0.15 0.1 0.1 0.117

Calibration Post Zero Cylinder Drift 0.05 0.05 0 0.033

Calibration Post High Cylinder ID ALMX068001

-NOX

ALMX06800

1-NOX

ALMX06800

1-NOX

Calibration Post High Cylinder Instrument Response 90.9 89.3 89.3 89.833

Calibration Post High Cylinder Bias -2 -2.8 -2.8 -2.533

Calibration Post High Cylinder Drift 0.75 0.8 0 0.517

Cavg 55.2 51 56.2 54.133

Cavg Units ppmvd ppmvd ppmvd

Cgas 57.1034 53.6525 59.7596 56.839

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 11122 11122 11122 11,122.000

Fc 1836 1836 1836 1,836.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 35 of 36
FirstEnergy - Bay Shore Station ICR

9/3/2010

Location Unit 1 Stack - OTM - 27/28

Average

Run Number U1-

OTM27/28-1

U1-

OTM27/28-2

U1-

OTM27/28-3

Test Date 6/10/2010 6/11/2010 6/12/2010

Run Start Time

Run Finish Time

Net Traversing Points 12 12 12

Net Run Time, minutes 360.5 331.75 338.75

Nozzle Diameter, inches 0.172 0.172 0.172 0.172

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.958 0.958 0.958 0.958

Barometric Pressure, inches of Mercury 29.2 29.2 29.3 29.233

Average Orifice Meter Differential, inches H2O 0.46 0.46 0.46 0.460

Dry Gas Meter Volume Sampled, cubic feet 142.658 129.444 132.673 134.925

Average Dry Gas Meter Temperature, °F 81.79 78.63 81.33 80.583

Dry Gas Meter Volume Sampled, dscf 130.133 118.772 121.542 123.482

Total Moisture Liquid collected, g 215.8 202.4 215.3 211.167

Volume of Water Vapor, standard cubic feet 10.16 9.53 10.13 9.940

Moisture Content of Stack Gas, % 7.24 7.43 7.69 7.453

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9276 0.9257 0.9231 0.925

Carbon Dioxide, % 17 17 17 17.000

Oxygen, % 3 3 3 3.000

Carbon Monoxide & Nitrogen, % 80 80 80 80.000

Fuel Factor 1.05 1.05 1.05

Dry Molecular Weight, lb/lb-Mole 30.84 30.84 30.84 30.840

Wet Molecular weight, lb/lb-Mole 29.91 29.89 29.85 29.883

Flue Gas Static Pressure, inches of H2O 0.25 0.25 0.25 0.250

Absolute Flue Gas Pressure, inches of Mercury 29.22 29.22 29.32 29.253

Average Stack Gas Temperature, °F 336.58 334.00 337.58 336.053

Average Velocity Head, inches of H2O 0.7600081628

35822

0.768623436

136349

0.809407865

300302

0.779

Average Stack Gas Velocity, feet/second 59.77 60.03 61.68 60.493

Stack Cross-Sectional Area, square feet 172.809 172.809 172.809 172.809

Dry Volumetric Flow Rate, dry scfm 372,121.5 374,186.6 382,977.1 376,428.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 619,727.6 622,423.5 639,531.5 627,227.533

Percent Isokinetic of Sampling Rate, % 103.9 102.5 100.3 102.233

Percent Excess Air, % 16.6 16.6 16.6 16.600

F-Factor, dscfm/MMBtu @ %O2 9720 9892 9821 9,811.000

Round Duct Diameter, inches 178 178 178

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 11175 11121 11363 11,219.667

Fc 1804 1836 1827 1,822.333

Thursday, February 17, 2011 Page 36 of 36