NIST NCSTAR 1 Federal BuUding and Fire Safety Investigation

of the World Trade Center Disaster

Final Report on the Collapse of

the World Trade Center Towers

Technology Administration

U.S. Department of Commerce

NIST NCSTAR 1 Federal Building and Fire Safety Investigation

of the World Trade Center Disaster

Final Report on the Collapse of

the World Trade Center Towers

September 2005

U.S. Department of Commerce

Carlos M. Gutierrez. Secretary

Technology Administration

Michelle O'Neill. Acting Under Secretary for Technology

National Institute of Standards and Technology

William Jeffrey, Director
Disclaimer No. 1

Certain commercial entities, equipment, products, or materials are identified in this document in order to describe a procedure or concept adequately or to trace the history of the procedures and practices used. Such identification is not intended to imply recommendation, endorsement, or implication that the entities, products, materials, or equipment are necessarily the best available for the purpose. Nor does such identification imply a finding of fault or negligence by the National Institute of Standards and Technology.

Disclaimer No. 2

The policy of NIST is to use the International System of Units (metric units) in all publications. In this document,

however, units are presented in metric units or the inch-pound system, whichever is prevalent in the discipline.

Disclaimer No. 3

Pursuant to section 7 of the National Construction Safety Team Act, the NIST Director has determined that certain evidence received by NIST in the course of this Investigation is "voluntarily provided safety-related information" that is "not directly related to the building failure being investigated" and that "disclosure of that information would inhibit the voluntary provision of that type of information" (15 USC 7306c).

In addition, a substantial portion of the evidence collected by NIST in the course of the Investigation has been

provided to NIST under nondisclosure agreements.

Disclaimer No. 4

NIST takes no position as to whether the design or construction of a WTC building was compliant with any code

since, due to the destruction of the WTC buildings, NIST could not verify the actual (or as-built) construction, the

properties and condition of the materials used, or changes to the original construction made over the life of the

buildings. In addition, NIST could not verify the interpretations of codes used by applicable authorities in determining

compliance when implementing building codes. Where an Investigation report states whether a system was

designed or installed as required by a code provision, NIST has documentary or anecdotal evidence indicating

whether the requirement was met, or NIST has independently conducted tests or analyses indicating whether the requirement was met.

Use in Legal Proceedings

No part of any report resulting from a NIST investigation into a structural failure or from an investigation under the

National Construction Safety Team Act may be used in any suit or action for damages arising out of any matter mentioned in such report (15 USC 281a; as amended by P.L. 107-231).

National Institute of Standards and Technology National Construction Safety Team Act Report 1 Natl. Inst. Stand. Technol. Natl. Constr. Sfty. Tm. Act Rpt. 1, 298 pages (September 2005)

CODEN: NSPUE2

U.S. GOVERNMENT PRINTING OFFICE

WASHINGTON; 2005

For sale by the Superintendent of Documents, U.S. Government Printing Office

Internet: bookstore.gpo.gov — Phone: (202) 512-1800 — Fax: (202) 512-2250

Mail: Stop SSOP, Washington, DC 20402-0001
National Construction Safety Team for the Federal

Building and Fire Safety Investigation of the World Trade

Center Disaster

S. Shyam Sunder, Sc.D. (NIST) Lead Investigator

Richard G. Gann, Ph.D. (NIST) Final Report Editor; Project Leader, Project 5: Reconstruction of Thennal and Tenability Environment

William L. Grosshandler, Ph.D. (NIST) Associate Lead Investigator; Project Leader, Project 4: Investigation of Active Fire Protection Systems

H.S. Lew, Ph.D., P.E. (NIST) Co-Project Leader, Project 1: Analysis of Building and Fire

Codes and Practices

Richard W. Bukowski, P.E. (NIST) Co-Project Leader, Project I: Analysis of Building and Fire

Codes and Practices

Fahim Sadek, Ph.D. (NIST) Project Leader, Project 2: Baseline Stmctiiral Performance

and Aircraft Impact Damage Analysis

Frank W. Gayle, Ph.D. (NIST) Project Leader, Project 3: Mechanical and Metallurgical

Analysis of Structural Steel

John L. Gross, Ph.D., P.E. (NIST) Co-Project Leader, Project 6: Structural Fire Response and

Collapse Analysis

Therese P. McAllister, Ph.D., P.E. (NIST) Co-Project Leader, Project 6: Structural Fire Response and

Collapse Analysis

Jason D. Averill (NIST) Project Leader, Project 7: Occupant Behavior, Egress, and

Emergency Communications

J. Randall Lawson (NIST) Project Leader, Project 8: Fire Service Technologies and

Guidelines

Harold E. Nelson, P.E. Fire Protection Engineering Expert

Stephen A. Cauffman (NIST) Program Manager

NISTNCSTAR 1, WTC Investigation ni
National Construction Safety Team

This page intentionally left blank.

IV NISTNCSTAR 1, WTC Investigation
Contributors to the Investigation

NIST Technical Staff

Mohsen Altafi Jeffrey Fong Max Peltz Robert Anleitner Glenn Forney Lisa Petersen

Elisa Baker William Fritz Rochelle Plummer

Stephen Banovic Anthony Hamins Kuldeep Prasad

Howard Baum Edward Hnetkovsky Natalia Ramirez

Carlos Beauchamp Erik Johnsson Ronald Rehm

Dale Bentz Dave Kelley Paul Reneke

Charles Bouldin Mark Kile Michael Riley

Paul Brand Erica Kuligowski Lonn Rodine

Lori Brassell Jack Lee Schuyler Ruitberg

Kathy Butler William Luecke Jose Sanchez

Nicholas Carino Alexander Maranghides Raymond Santoyo

Sandy Clagett David McColskey Steven Sekellick

Ishmael Conteh Chris McCowan Michael Selepak

Matthew Covin Jay McElroy Thomas Siewert

Frank Davis Kevin McGrattan Emil Simiu

David Dayan Roy McLane Monica Stames

Laurean DeLauter George Mulholland David Stroup

Jonathan Demarest Lakeshia Murray Laura Sugden

Stuart Dols Kathy Notarianni Robert Vettori

Michelle Donnelly Joshua Novosel John Widmann

Dat Duthinh Long Phan Brendan Williams

David Evans William Pitts Maureen Williams

Richard Fields Thomas Ohlemiller Jiann Yang

James Filliben Victor Ontiveros Robert Zarr Tim Foecke Richard Peacock

NIST EXPERTS AND CONSULTANTS

Vincent Dunn

Steven Hill John Hodgens

Kevin Malley

Valentine Junker

NISTNCSTAR 1, WTC Investigation V
Contributors to the Investigation

Department of Commerce and NIST Institutional Support

Michele Abadia-Dalmau James Hill Karen Perry

Kellie Beall Vema Hines Sharon Rinehart

Arden Bement, Jr. Kathleen Kilmer Michael Rubin

Audra Bingaman Kevin Kimball Rosamond Rutledge-Bums

Sharon Bisco Thomas Klausing John Sanderson

Phyllis Boyd Dorma Kline Hratch Semerjian

Marie Bravo Fred Kopatich Sharon Shaffer

Craig Burkhardt Kenneth Lechter Elizabeth Simon

Paul Cataldo Melissa Liebemian Jack Snell

Virginia Covahey Darren Lowe Michael Szwed

Deborah Cramer Mark Madsen Kelly Talbott

Gail Crum Ronald Meininger Anita Tolliver

Jane Dana Romena Moy Joyce Waters

Sherri Diaz Michael Newman Teresa Vicente

Sandra Febach Gail Porter Dawn Williams

Susan Ford Thomas 0'Brian

James Fowler Nualla O'Connor-Kelly

Matthew Heyman Norman Osinski

NIST Contractors

Applied Research Associates, Inc.

olCVCIl rvirKpdiriLK. ividrsii fidiuy VwlaUClla iNdVdrrU

Robert T. Bocchieri Samuel Holmes Brian D. Peterson Robert W. Cilke Robert A. MacNeill Justin Y-T. Wu

Baseline, Inc. Martin Klain

Computer Aided Engineerine Associates, Inc.

Peter Barrett* Daniel Fridline

Michael Bak James J. Kosloski

DataSource, Inc. John Wivaag

GeoStats, Inc.

Marcello Oliveira

vi NIST NCSTAR 1, WTC Investigation
Contributors to the Investigation

Gilsanz Murray Steficek LLP

Ramon Gilsanz

Hughes Associates, Inc. Ed Budnick* Matt Hulcher John Schoenrock

Steven Strege

Mark Hopkins Karen Dawn Tooren

Mike Ferreira* Alwin Kelly

Chris Mealy

Independent Contractors

Ajmal Abbasi

Eduardo Kausel

David Parks

David Sharp

Daniele Veneziano

Josef Van Dyck

Kaspar Willam

Isolatek International, Inc.

Paulette Kaminski

John Jay College

Norman Groner

Leslie E. Robertson Associates, R.L.L.P.

William J. Faschan* William C. Howell

Richard B. Garlock* Raymond C. Lai

National Fire Protection Association

Rita Fahey*

Norma Candeloro

Joseph Molis

National Research Council, Canada

Guylene Proulx*

Amber Walker

NuStats, Inc.

Johanna Zmud* Christopher Frye Delia Santos

Carlos Arce Nancy McGuckin Robert Santos

Heather Contrino Sandra Rodriguez

NISTNCSTAR 1, WTC Investigation vii
Contributors to the Investigation

Rolf Jensen & Associates, Inc. Ray Grill*

Ed Araun

Tom Brown

Duane Johnson

Bob Keough

Joseph Razz

Rosenwasser/Grossman Consulting Engineers, P.C.

Jacob Grossman*

Craig Leech

Arthur Seigel

Science Applications International Corporation

John Eichner* Pamela Curry

Cheri Sawyer* John DiMarzio

Lori Ackman Heather Duvall

Marina Bogatine Mark Huffman

Sydel Cavanaugh Charlotte Johnson

Kathleen Clark Michael Kalmar

Mark Madara

Walter Soverow

Paul Updike

Yvonne Zagadou

Simpson Gumpertz & Heger Inc. Mehdi Zarghamee*

Glenn Bell

Said Bolourchi

Daniel W. Eggers

Omer O. Erbay

Ron Hamburger

Frank Kan

Yasuo Kitane

Atis Liepins

Michael Mudlock

Wassim I. Naguib

Rasko P. Ojdrovic

Andrew T. Sarawit

Pedro Sifre

S. K. Ghosh Associates, Inc.

S. K. Ghosh* Dave Fanella

Analdo Derecho Xumei Liang

Skidmore, Owings & Merrill, LLP

Bill Baker

Bob Sinn

John Zils

Teng & Associates, Inc.

Shankar Nair

Underwriters Laboratories, Inc.

Fred Hervey* Mark Izydorek William Joy

Joseph Treadway* Aldo Jimenez John Mammoser

viii NIST NCSTAR 1. WTC Investigation
Contributors to the Investigation

University at Buffalo. The State University of New York

Andrew Whitaker*

Andrei Reinhom

Joshua Repp

University of Chicago Survev University of Colorado University of Michigan

Lab Denms Mileti Jamie Abelson

Virginia Bartot Martha van Haitsma

W iss, Jannev. Elstner Associates, Inc. Ray Tide*

Jim Hauck

Conrad Paulson

Cooperating Organizations

American Airlines

Desmond Barr> Morgan Heyer

The Boeing Companv

Marlene Nelson

Blanford Land Development

Corporation

Lisa Lickman

Ron Lickman

John Sandy

Carr Futures, Inc. David MangoldCity of New York Fire

Department

Alexandra Fisher

Allen S. Hay

Federal Bureau of

Investigation

Kenneth Marr

Hugo Neu Schnitzer East

Robert Kelman

Steve Shinn

Frank Manzo

Laclede Steel

David McGee

Marsh & McLennan

Companies

Thomas Gress

Michael Lyons

Metal Management Northeast, Inc.

Michael Henderson

Alan Ratner

John Silva

National Commission on Terrorist Attacks Upon the United States

Madeline Blot George L. Delgrosso James Miller

Sam M. W. Casperson Daniel Marcus Catherine S. Taylor

NISTNCSTAR 1, WTC Investigation ix
Contributors to the Investigation

New York City Law Department

Lawrence S. Kahn

Jay L. Cohen

Gary Shaffer

Rachel Relkin

Joanna Weiss

George CD. Duke

Katherine Winningham

Jessie Levine

New York City Police Department

Michael F. Healey

The Port Authority of New York and New Jersey

James Begley

Saroj Bhol

Gerry Gaeta

Jeffrey Gertier

Frank Lombardi

Alan Reiss

Nancy Seliga

Siemens

Steven Shamash

John Farrington

Robert Salamone

Silverstein Properties Simpson, Thacher & Bartlett

LLP

Jamie Gamble

Structural Engineers

Association of New York

Ed DiPaolo

WachtelK Lipton, Rosen &

Katz

Marc Wolinsky

Andrew Cheung

United Air Lines

John Midgett

Norvis Huezo

Williams & Connolly LLP

Philip Sechler

Principal Investigator/Key Contact

X NISTNCSTAR 1. WTC Investigation
Dedication

On the morning of September 11, 2001, Americans and people around the world were shocked by the destruction of the World Trade Center (WTC) in New York City and the devastation of the Pentagon near Washington, D.C., after large aircraft were flown into the buildings, and the crash of an aircraft in a Pennsylvania field that averted further tragedy. Four years later, the world has been changed irrevocably

by those terrorist attacks. For some, the absence of people close to them is a constant reminder of the unpredictability of life and death. For millions of others, the continuing threats of further terrorist attacks

affect how we go about our daily lives and the attention we must give to homeland security and

emergency preparedness.

Within the construction, building, and public safety communities, there arose a question pressing to be

answered: How can we reduce our vulnerability to such attacks, and how can we increase our preparedness and safety while still ensuring the functionality of the places in which we work and live?

This Investigation has, to the best extent possible, reconstructed the response of the WTC towers and the people on site to the consequence of the aircraft impacts. It provides improved understanding to the professional communities and building occupants whose action is needed and to those most deeply

affected by the events of that morning. In this spirit, this report is dedicated to those lost in the disaster, to those who have borne the burden to date, and to those who will carry it forward to improve the safety

of buildings.

NISTNCSTAR 1, WTC Investigation xi
Dedication

This page intentionally left blank.

xii NISTNCSTAR 1, WTC Investigation
Abstract

This is the final report on the National Institute of Standards and Technology (NIST) investigation of the collapse of the World Trade Center (WTC) towers, conducted under the National Construction Safety

Team Act. This report describes how the aircraft impacts and subsequent fires led to the collapse of the towers after terrorists flew jet fuel laden commercial airliners into the buildings; whether the fatalities were low or high, including an evaluation of the building evacuation and emergency response procedures;

what procedures and practices were used in the design, construction, operation, and maintenance of the towers; and areas in current building and fire codes, standards, and practices that warrant revision.

Extensive details are found in the 42 companion reports. The final report on the collapse of WTC 7 will appear in a separate report. -

Also in this report is a description of how NIST reached its conclusions. NIST complemented in-house

expertise with private sector technical experts; accumulated copious documents, photographs, and videos

of the disaster; established baseline performance of the WTC towers; performed computer simulations of

the behavior of each tower on September 1 1, 2001; combined the knowledge gained into a probable

collapse sequence for each tower; conducted nearly 1,200 first-person interviews of building occupants

and emergency responders; and analyzed the evacuation and emergency response operations in the two

high-rise buildings.

The report concludes with a list of 30 recommendations for action in the areas of increased structural

integrity, enhanced fire endurance of structures, new methods for fire resistant design of structures, enhanced active fire protection, improved building evacuation, improved emergency response, improved

procedures and practices, and education and training.

Keywords: Aircraft impact, building evacuation, emergency response, fire safety, human behavior,

structural collapse, tall buildings, wind engineering, World Trade Center.

NISTNCSTAR 1, WTC Investigation xiii
Abstract

This page intentionally left blank.

xiv NIST NCSTAR 1, WTC Investigation
Table of Contents

National Construction Safety Team for the Federal Building and Fire Safety Investigation of the World Trade Center Disaster iii

Contributors to the Investigation v

Dedication xi

Abstract xiii

List of Figures xxi

List of Tables xxv

List of Acronyms and Abbreviations xxvii

Preface xxix

Executive Summary xxxv

Part I: September 11, 2001 1

Chapter 1 New York City's World Trade Center 1

1 . 1 The Origination 1

1 .2 The World Trade Center Complex 2

1.2.1 The Site 2

1.2.2 The Towers 5

Chapter 2 The Account of World Trade Center 1 19

2.1 8:46:30 a.m. EDT 19

2.2 The Aircraft 20

2.3 The Immediate Damage 20

2.4 The Jet Fuel 24

2.5 8:47 a.m. to 9:02 a.m. EDT 24

2.6 9:02:59 a.m. EDT 27

2.7 9:03 a.m. to 9:57 a.m. EDT 27

2.8 9:58:59 a.m. EDT 32

2.9 9:59 a.m. to 10:28 a.m. EDT 32

2.10 The Outcome 34

NISTNCSTAR 1, WTC Investigation xv
Table of Contents

Chapters

The Account of World Trade Center 2 37

3.1 8:46:30 a.m. EDT 37

3.2 9:02:59 a.m. EDT 38

3.3 The Immediate Damage 38

3.4 The Jet Fuel 42

3.5 9:03 a.m. to 9:36 a.m. EDT 42

3.6 9:36 a.m. to 9:58 a.m. EDT 44

3.7 The Outcome 45

Chapter 4

The Toll 47

Part II: Reconstructing the Disaster 49

Chapters

The Design and Construction of the Towers 51

5.1 Building and Fire Codes 51

5.2 The Codes and the Towers 52

5.2.1 The New York City Building Code 52

5.2.2 Pertinent Construction Provisions 53

5.2.3 Tenant Alteration Process 54

5.3 Building Design 55

5.3.1 Loads 55

5.3.2 Aircraft Impact 55

5.3.3 Construction Classification and Fire Resistance Rating 55

5.3.4 Compartmentation 56

5.3.5 Egress Provisions 57

5.3.6 Active Fire Protection 61

5.4 Building Innovations ....64

5.4.1 The Need for Innovations 64

5.4.2 Framed Tube System 64

5.4.3 Deep Spandrel Plates 64

5.4.4 Uniform External Column Geometry 65

5.4.5 Wind Tunnel Test Data to Establish Wind Loads 65

5.4.6 Viscoelastic Dampers 65

xvi NISTNCSTAR 1, WTC Investigation
Table of Contents

5.4.7 Long-Span Composite Floor Assemblies 66

5.4.8 Vertical Shaft Wall Panels 66

5.5 Structural Steels 67

5.5.1 Types and Sources 67

5.5.2 Properties 67

5.6 Fire Protection of Structural Steel 69

5.6.1 Thermal Insulation 69

5.6.2 Use of Insulation in the WTC Towers 69

5.7 Concrete 75

5.8 The Tenant Spaces 75

5.8.1 General 75

5.8.2 Walls 76

5.8.3 Flooring 76

5.8.4 Ceilings 76

5.8.5 Furnishings 76

Chapter 6 Reconstruction of the Collapses 81

6.1 Approach 81

6.2 Development of the Disaster Timeline 82

6.3 Learning from the Visual Images 84

6.4 Learning from the Recovered Steel 86

6.4. 1 Collection of Recovered Steel 86

6.4.2 Mechanical and Physical Properties 88

6.4.3 Damage Analysis 89

6.5 Information Gained from Other WTC Fires 91

6.6 The Building Structural Models 92

6.6. 1 Computer Simulation Software 92

6.6.2 The Reference Models 92

6.6.3 Building Structural Models for Aircraft Impact Analysis 94

6.6.4 Building Structural Models for Structural Response to Impact Damage and Fire and

Collapse Initiation Analysis 97

6.7 The Aircraft Structural Model 105

6.8 Aircraft Impact Modeling 107

6.8.1 Component Level Analyses 107

6.8.2 Subassembly Impact Analyses 108

NIST NCSTAR 1, WTC Investigation xvii
Table of Contents

6.8.3 Aircraft Impact Conditions 108

6.8.4 Global Impact Analysis 109

6.9 Aircraft Impact Damage Estimates 112

6.9.1 Structural and Contents Damage 112

6.9.2 Validity of Impact Simulations 1 16

6.9.3 Damage to Thermal Insulation 119

6.9.4 Damage to Ceiling System 120

6.9.5 Damage to Interior Walls and Furnishings 120

6.10 Thennal Environment Modeling 121

6.10.1 Need for Simulation 121

6.10.2 Modeling Approach 121

6.10.3 The Four Cases 126

6.10.4 Characterization of the Fires 127

6.10.5 Global Heat Release Rates 130

6.11 Data Transfer 131

6.12 Thennal Mapping 131

6.12.1 Approach 131

6.12.2 The Fire-Structure Interface 131

6.12.3 Thermal Insulation Properties 132

6.12.4 FSl Uncertainty Assessment 133

6.12.5 The Four Cases 138

6.12.6 Characterization of the Thermal Profiles 141

6.13 Measurement of the Fire Resistance of the Floor System 141

6.14 Collapse Analysis of the Towers 143

6.14.1 Approach to Determining the Probable Collapse Sequences 143

6.14.2 Results of Global Analysis of WTC 1 144

6.14.3 Results of Global Analysis of WTC 2 145

6.14.4 Events Following Collapse Initiation 146

6. 14.5 Structural Response of the WTC Towers to Fire without Impact or Thermal

Insulation Damage 146

6.14.6 Probable WTC 1 Collapse Sequence 150

6.14.7 Probable WTC 2 Collapse Sequence 151

6.14.8 Accuracy of the Probable Collapse Sequences 152

6.14.9 Factors that Affected Building Performance on September 1 1, 2001 154

xviii NISTNCSTAR 1, WTC Investigation
Table of Contents

Chapter 7 Reconstruction of Human Activity 1 55

7 . 1 Building Occupants 155

7.1.1 Background 155

7. 1 .2 The Building Egress System 155

7.1.3 The Evacuation—Data Sources 1 57

7. 1 .4 Occupant Demographics 158

7.1.5 Evacuation of WTC 1 158

7.1.6 Evacuation of WTC 2 160

7.2 Emergency Responders 163

7.2.1 Data Gathered 163

7.2.2 Operation Changes following the WTC 1 Bombing on February 26, 1993 164

7.2.3 Responder Organization 1 66

7.2.4 Responder Access 169

7.2.5 Communications 170

7.2.6 The Overall Response 172

7.3 Factors That Contributed to Enhanced Life Safety 172

7.3.1 Aggregate Factors 172

7.3.2 Individual Factors 172

Part III: The Outcome of the Investigation 173

Chapter 8 Principal Findings 175

8.1 Introduction 175

8.2 Summary 175

8.3 Findings on the Mechanisms of Building Collapse 179

8.3.1 Summary of Probable Collapse Sequences 179

8.3.2 Structural Steels 180

8.3.3 Aircraft Impact Damage Analysis 1 82

8.3.4 Reconstruction of the Fires 183

8.3.5 Structural Response and Collapse Analysis 185

8.4 Findings on Factors Affecting Life Safety 186

8.4.1 Active Fire Protection 186

8.4.2 Evacuation 188

8.4.3 Emergency Response 191

NISTNCSTAR 1, WTC Investigation xix
Table of Contents

8.5 Findings on Operational Codes, Standards, and Practices 194

8.5.1 General 194

8.5.2 Structural Safety 195

8.5.3 Fire Safety 196

8.6 Future Factors That Could Have Improved Life Safety 199

8.6. 1 Building Perfonnance Factors 200

8.6.2 Human Performance Factors 200

Chapters

Recommendations 201

9. 1 Building Regulations 201

9.2 NIST's Recommendations for Improving the Safety of Buildings, Occupants, and

Emergency Responders 202

9.2.1 Group 1. Increased Structural Integrity 205

9.2.2 Group 2. Enhanced Fire Endurance of Structures 208

9.2.3 Group 3. New Methods for Fire Resistant Design of Structures 211

9.2.4 Group 4. Improved Active Fire Protection 213

9.2.5 Group 5. Improved Building Evacuation 214

9.2.6 Group 6. Improved Emergency Response 218

9.2.7 Group 7. Improved Procedures and Practices 220

9.2.8 Group 8. Education and Training 222

9.3 Next Steps 223

Appendix A

National Construction Safety Team Act

Appendix B

World Trade Center Investigation Publications

Appendix C

Subject Index of Supporting Investigation Reports

XX NISTNCSTAR 1, WTC Investigation
List OF Figures

Figure P-1 . The eight projects in the federal building and fire safety investigation of the WTC

disaster xxxi

Figure 1-1. The World Trade Center in Lower Manhattan 3

Figure 1-2. Lower Manhattan and the World Trade Center towers 4

Figure 1-3. Tower floor plans with column numbers 7

Figure 1^. Perimeter column/spandrel assembly and floor structure 8

Figure 1-5. Plan of the 96* floor of WTC 1 showing the core and tenant spaces. 9

Figure 1-6. Schematic of composite floor truss system 10

Figure 1-7. Schematic of a hat truss 11

Figure 1-8. Photograph of insulated WTC trusses 12

Figure 1-9. Schematic of the three-tier elevator system 14

Figure 1-10. Orientation of the three stairwells 16

Figure 1-11. Views of typical WTC office floors 17

Figure 1-12. A WTC trading floor 17

Figure 2-1. Simulated impact of American Airlines Flight 1 1 with WTC 1 19

Figure 2-2. Aircraft entry hole on the north side of WTC 1, photographed 30 s after impact 21

Figure 2-3. South face damage of WTC 1 with key aircraft component locations marked 22

Figure 2-A. Simulation of cumulative aircraft impact damage to floors 93 through 98 in WTC 1 23

Figure 2-5. Representation of exterior views of the fires on the four faces of WTC 1 from 8:47

a.m. to about 9:02 a.m 25

Figure 2-6. Firefighters on the scene at about 9:07 a.m 27

Figure 2-7. Representation of exterior views of the fires on the four faces of WTC 1 from about

9:38 a.m. to 9:58 a.m 28

Figure 2-8. Steel surface temperatures on the bottom chords of fire-exposed trusses, uninsulated

and insulated with 'A in. of BLAZE-SHIELD DC/F 29

Figure 2-9. Temperature dependence of yield strength of structural steel as a fraction of the value

at room temperature 30

Figure 2-10. Simulated temperatures of two adjacent trusses (left) and two adjacent perimeter

columns (right) exposed to the fires in WTC 1 30

Figure 2-1 1 . Temperature contours (°C) on the top and bottom faces of the concrete slab (96*

floor, WTC 1 ) at 100 min after impact. A portion of the concrete slab on the north

face (top) was damaged by the impact of the aircraft 31

NIST NCSTAR 1, WTC Investigation xxi
List of Figures

Figure 2-12. South face of WTC 1 at 10:23 a.m., showing inward buckling (in inches) of

perimeter columns 33

Figure 3-1 . Imminent impact of United Airlines Flight 1 75 with WTC 2 38

Figure 3-2. South face damage of WTC 2 with key aircraft component locations marked 39

Figure 3-3. Simulation of aircraft impact damage to the 78* through 83^'' floors in WTC 2 40

Figure 3^. Representation of exterior views of the fires on the four faces of WTC 2 at about

9:20 a.m 43

Figure 3 5. Photograph of WTC 2 tilting to the southeast at the onset of collapse 45

Figure 4-1. The WTC site on September 17, 2001 47

Figure 5-1 . Fire Command Desk in WTC 1, as seen from a mezzanine elevator, looking west 61

Figure 5-2. Schematic of sprinkler and standpipe systems 63

Figure 5-3. Diagram of floor truss showing viscoelastic damper 66

Figure 5^. Ratio of measured yield strength (Fy) to specified minimum yield strength for steels used in WTC perimeter columns 69

Figure 5-5. Irregularity of coating thickness and gaps in coverage on SFRM-coated bridging

trusses 71

Figure 5 6. Thermal insulation for perimeter columns 72

Figure 5-7. Temperature-dependent concrete properties 75

Figure 5-8. A WTC workstation 76

Figure 6-1. 9:26:20 a.m. showing the east face of WTC 2 85

Figure 6-2. Close-up of section of Figure 6-1 86

Figure 6 3. Examples of a WTC 1 core column (left) and truss material (right) 88

Figure 6^. WTC 1 exterior panel hit by the fuselage of the aircraft 88

Figure 6-5. WTC 1 exterior panel hit by the nose of the aircraft 89

Figure 6-6. Structural model of the 96"' floor of WTC 1 95

Figure 6-7. Model of the 96"" floor of WTC 1, including interior contents and partitions 95

Figure 6-8. Multi-floor global model of WTC 1, viewed from the north 96

Figure 6-9. Multi-floor global model of WTC 2, viewed from the south 96

Figure 6-1 0. Finite element model of an exterior truss seat 98

Figure 6 1 1 . Vertical displacement at 700 °C 98

Figure 6 12. ANSYS model of 96"^ floor of WTC 1 99

Figure 6-13. Finite element model of the Boeing 767-200ER 105

xxii NISTNCSTAR 1, WTC Investigation
List of Figures

Figure 6-14. Pratt & Whitney PW4000 turbofan engine model 106

Figure 6-15. Boeing 767-200ER showing the jet fuel distribution at time of impact 106

Figure 6-16. Calculated impact on an exterior wall by a fuel-laden wing section 107

Figure 6-1 7. Response of a tower subassembly model to engine impact 108

Figure 6-18. Side view of simulated aircraft impact into WTC 1, Case B 1 10

Figure 6-19. Column damage levels 112

Figure 6-20. Case B damage to the slab of floor 96 of WTC 1 112

Figure 6-2 1 . Case B simulation of response of contents of 96"' floor of WTC 1 113

Figure 6-22. Combined structural damage to the floors and columns of WTC 1, Case A 114

Figure 6-23. Combined structural damage to the floors and columns of WTC 1, Case B 114

Figure 6-24. Combined structural damage to the floors and columns of WTC 2, Case C 115

Figure 6-25. Combined structural damage to the floors and columns of WTC 2, Case D 115

Figure 6-26. Observed and Case A calculated damage to the north face of WTC 1 117

Figure 6-27. Schematic of observed damage (top) and Case A calculated damage (lower) to the north face of WTC 1 118

Figure 6-28. Schematic of observed damage (above) and Case C calculated damage (right) to the south face of WTC 2 118

Figure 6-29. Ceiling tile system mounted on the shaking table 120

Figure 6-30. Eight floor model of WTC 1 prior to aircraft impact 122

Figure 6-3 1 . Fire test of a single workstation 123

Figure 6-32. Interior view of a three-workstation fire test 124

Figure 6-33. Rubblized workstations 124

Figure 6-34. Three-workstation fire test, 2 min after the start 125

Figure 6-35. Measured and predicted heat release rate from the burning of three

office workstations 125

Figure 6-36. Upper layer temperatures on the 94"" floor of WTC 1,15 min after impact 127

Figure 6-37. Direction of simulated fire movement on floors 94 and 97 of WTC 1 128

Figure 6-38. Predicted heat release rates for fires in WTC 1 and WTC 2 130

Figure 6-39. Simple bar dimensions (in.) 134

Figure 6-40. Tubular column dimensions (in.) 134

Figure 6-41. Truss Dimensions (in.) 135

Figure 6^2. SFRM-coated steel components prior to a test 135

Figure 6-43. Finite element representation of the insulated steel truss (blue), the SFRM (violet),

and the ceiling (red) 136

Figure 6-44. Comparison of numerical simulations with measurements for the steel surface

temperature at four locations on the top chord of a bare truss 137

NIST NCSTAR 1, WTC Investigation xxiii
List of Figures

Figure 6-45. Comparison of numerical simulations with measurements for the temperature of the

steel surface at four locations on the top chord of an insulated truss 137

Figure 6^6. Temperatures (°C) on the columns and trusses of the 96"" floor of WTC 1 at 6,000 s after aircraft impact, Case B 139

Figure 6-47. Temperatures (°C) on the columns and trusses of the ST' floor of WTC 2 at 3,000 s after aircraft impact, Case D 139

Figure 6-48. Frames from animation of the thennal response of columns on the 96"' floor of WTC

1, Case A 140

Figure 7-1. Simulated impact damage to 95'*' floor of WTC 1, including stairwells, 0.7 s after impact 156

Figure 7-2. Simulated impact damage to WTC 2 on floor 78, 0.62 s after impact 156

Figure 7 3. Observations of building damage after initial awareness but before beginning

evacuation in WTC 1 161

Figure 7^. Observations of building damage from tenant spaces in WTC 2 162

Figure 7-5. Location of the radio repeater 165

Figure 7 6. Timing of FDNY unit arrivals 166

Figure 7-7. Fire Command Board located in the lobby of WTC 1 168

xxiv NISTNCSTAR 1, WTC Investigation
List of Tables

Table P-1 . Federal building and fire safety investigation of the WTC disaster xxx

Table P-2. Public meetings and briefings of the WTC Investigation xxxiii

Table E-1 . Topics of NIST recommendations for improved public safety in tall and high-risk

buildings xliv

Table 1-1. Use of floors in the WTC towers 5

Table 2-1 . Locations of occupants of WTC 1 26

Table 3-1 . Tenants on impact floors in WTC 2 39

Table 3-2. Location of occupants of WTC 2 42

Table 4-1 . Likely locations of WTC decedents at time of impact 48

Table 5-1 . Specified steel grades for various applications 67

Table 5-2. Types and locations of SFRM on fire floors 74

Table 5-3. Floors of focus 78

Table 6-1. Times for major events on September 11,2001 84

Table 6-2. Indications of major structural changes up to collapse initiation 87

Table 6-3. Measured and calculated natural vibration periods (s) for WTC 1 93

Table 6-4. Summary of aircraft impact conditions 108

Table 6-5. Input parameters for global impact analyses 109

Table 6-6. Values of WTC fire simulation variables 126

Table 6-7. Summary of insulation on steel components 136

Table 6-8. Regions in WTC 1 in which temperatures of structural steel exceeded 600 °C 141

Table 6-9. Regions in WTC 2 in which temperatures of structural steel exceeded 600 °C 141

Table 6-10. Comparison of global structural model predictions and observations for WTC 1, Case B 153

Table 6-11. Comparison of global structural model predictions and observations for WTC 2, CaseD 153

NIST NCSTAR 1, WTC Investigation xxv
List of Tables

This page intentionally left blank.

xxvi NISTNCSTAR 1, WTC Investigation
List of Acronyms and Abbreviations

Acronyms

AA American Airlines

ARA Application Research Associates

ASTM ASTM International

BOCA Building Officials and Code Administrators

BPS Building Performance Study

FCD Fire Command Desk

FDNY The Fire Department of the City of New York

FDS Fire Dynamics Simulator

FEMA Federal Emergency Management Agency

FSI Fire Structure Interface IBC International Building Code

LERA Leslie E. Robertson Associates

NFPA National Fire Protection Association

NIST National Institute of Standards and Technology

NYC New York City

NYPD New York City Police Department

NYS New York State PANYNJ The Port Authority of New York and New Jersey

PAPD Port Authority Police Department

SFRM sprayed fire-resistive material

SGH Simpson Gumpertz & Heger, Inc. SOM Skidmore, Owings and Merrill

UA United Airlines

use United States Code

WSHJ Worthington, Skilling, Helle and Jackson

WTC World Trade Center

WTC 1 World Trade Center 1 (North Tower)

NISTNCSTAR 1, WTC Investigation xxvii
List of Acronyms and Abbreviations

WTC2 World Trade Center 2 (South Tower)

WTC7 World Trade Center 7

Abbreviations and Conversion Factors

°C degrees Celsius T (T) = 5/9 [T (T) - 32]

°F degrees Fahrenheit

ft feet

gal gallon ' 1 gal = 3.78 x

10"^

GJ gigajoule

GW gigawatt

in. inch

kg kilogram

kip 1,000 lb

ksi l,000 1b/in.-

Ib pound 1 lb = 0.453 kg

m meter 1 m = 3.28 ft

jim micrometer

min minute

MJ megajoule

MW megawatt

psi pounds per square inch

s second

T temperature

xxviii NISTNCSTAR 7, WTC Investigation
Preface

Genesis of This Investigation

Immediately following the terrorist attack on the World Trade Center (WTC) on September 11, 2001, the Federal Emergency Management Agency (FEMA) and the American Society of Civil Engineers began

planning a building performance study of the disaster. The week of October 7, as soon as the rescue and

search efforts ceased, the Building Perfonnance Study Team went to the site and began its assessment. This was to be a brief effort, as the study team consisted of experts who largely volunteered their time

away from their other professional commitments. The Building Performance Study Team issued its report in May 2002, fulfilling its goal "to determine probable failure mechanisms and to identify areas of

future investigation that could lead to practical measures for improving the damage resistance of buildings

against such unforeseen events."

On August 21. 2002, with funding from the U.S. Congress through FEMA, the National Institute of

Standards and Technology (NIST) announced its building and fire safety investigation of the WTC

disaster. On October 1, 2002, the National Construction Safety Team Act (Public Law 107-231), was

signed into law. (A copy of the Public Law is included in Appendix A). The NIST WTC Investigation was conducted under the authority of the National Construction Safety Team Act.

The goals of the investigation of the WTC disaster were:

• To investigate the building construction, the materials used, and the technical conditions that contributed to the outcome of the WTC disaster.

• To serve as the basis for: - Improvements in the way buildings are designed, constructed, maintained, and used; - Improved tools and guidance for industry and safety officials; - Recommended revisions to current codes, standards, and practices; and - Improved public safety.

The specific objectives were:

1. Determine why and how WTC 1 and WTC 2 collapsed following the initial impacts of the

aircraft and why and how WTC 7 collapsed;

2. Determine why the injuries and fatalities were so high or low depending on location,

including all technical aspects of fire protection, occupant behavior, evacuation, and

emergency response;

3. Determine what procedures and practices were used in the design, construction, operation,

and maintenance of WTC 1, 2, and 7; and

4. Identify, as specifically as possible, areas in current building and fire codes, standards, and

practices that warrant revision.

NISTNCSTAR 1, WTC Investigation xxix
Preface

NIST is a nonregulatory agency of the U.S. Department of Commerce's Technology Administration. The

purpose of NIST investigations is to improve the safety and structural integrity of buildings in the United

States, and the focus is on fact finding. NIST investigative teams are authorized to assess building

perforaiance and emergency response and evacuation procedures in the wake of any building failure that has resulted in substantial loss of life or that posed significant potential of substantial loss of life. NIST

does not have the statutory authority to make findings of fault nor negligence by individuals or organizations. Further, no part of any report resulting from a NIST investigation into a building failure or from an investigation under the National Construction Safety Team Act may be used in any suit or action

for damages arising out of any matter mentioned in such report (15 USC 281a, as amended by Public

Law 107-231).

Organization of the Investigation

The National Construction Safety Team for this Investigation, appointed by the then NIST Director, Dr. Arden L. Bement, Jr., was led by Dr. S. Shyam Sunder. Dr. William L. Grosshandler served as Associate Lead Investigator, Mr. Stephen A. Cauffman served as Program Manager for Administration,

and Mr. Harold E. Nelson served on the team as a private sector expert. The Investigation included eight

interdependent projects whose leaders comprised the remainder of the team. A detailed description of

each of these eight projects is available at http://wtc.nist.gov. The purpose of each project is summarized

in Table P-1, and the key interdependencies among the projects are illustrated in Fig. P-1.

Table P-1. Federal building and fire safety investigation of the WTC disaster.

Technical Area and Project Leader Project Purpose

Analysis of Building and Fire Codes and

Practices; Project Leaders: Dr. H. S. Lew

and Mr. Richard W. Bukowski

Document and analyze the code provisions, procedures, and

practices used in the design, construction, operation, and

maintenance of the stmctural, passive fire protection, and

emergency access and evacuation systems of WTC 1, 2, and 7. Baseline Structural Performance and

Aircraft Impact Damage Analysis; Project Leader: Dr. Fahim H. Sadek

Analyze the baseline performance of WTC 1 and WTC 2 under

design, service, and abnormal loads, and aircraft impact damage on

the stmcmral, fire protection, and egress systems.

Mechanical and Metallurgical Analysis of

Structural Steel; Project Leader: Dr. Frank

W. Gayle

Detennine and analyze the mechanical and metallurgical properties

and quality of steel, weldments, and connections from steel recovered from WTC 1, 2, and 7. Investigation of Active Fire Protection Systems; Project Leader: Dr. David

D. Evans; Dr. William Grosshandler

Investigate the perfomiance of the active fire protection systems in WTC 1, 2, and 7 and their role in fire control, emergency response, and fate of occupants and responders.

Reconstmction of Thermal and Tenability

Environment; Project Leader: Dr. Richard

G. Gann

Reconstruct the time-evolving temperature, thermal environment,

and smoke movement in WTC 1, 2, and 7 for use in evaluating the stmctural performance of the buildings and behavior and fate of

occupants and responders.

Structural Fire Response and Collapse

Analysis; Project Leaders: Dr. John

L. Gross and Dr. Therese P. McAllister

Analyze the response of the WTC towers to fires with and without

aircraft damage, the response of WTC 7 in fires, the perfomiance

of composite steel-tmssed floor systems, and determine the most

probable stmcmral collapse sequence for WTC 1, 2, and 7. Occupant Behavior, Egress, and Emergency

Communicadons; Project Leader: Mr. Jason D. Averill

Analyze the behavior and fate of occupants and responders, both

those who survived and those who did not, and the perfomiance of

the evacuation system.

Emergency Response Technologies and

Guidelines; Project Leader: Mr. J. Randall

Lawson

Document the activities of the emergency responders from the time

of the terrorist attacks on WTC 1 and WTC 2 until the collapse of

WTC 7, including practices followed and technologies used.

XXX NISTNCSTAR 1, WTC Investigation
Preface

Figure P-1. The eight projects in the federal building and fire safety

Investigation of the WTC disaster.

National Construction Safety Team Advisory Committee

The NIST Director also established an advisory committee as mandated under the National Construction

Safety Team Act. The initial members of the committee were appointed following a public solicitation. These were:

• Paul Fitzgerald, Executive Vice President (retired) FM Global, National Construction Safety

Team Advisory Committee Chair

• John Barsom, President, Barsom Consulting, Ltd.

• John Bryan, Professor Emeritus, University of Maryland

• David Collins, President, The Preview Group, Inc.

• Glenn Corbett, Professor, John Jay College of Criminal Justice

• Philip DiNenno, President, Hughes Associates, Inc.

NISTNCSTAR 1, WTC Investigation xxxi
Preface

• Robert Hanson, Professor Emeritus, University of Michigan

• Charles Thornton, Co-Chairman and Managing Principal, The Thomton-Tomasetti Group,

Inc.

• Kathleen Tiemey, Director, Natural Hazards Research and Applications Information Center,

University of Colorado at Boulder

• Fonnan Williams, Director, Center for Energy Research, University of California at San

Diego

This National Construction Safety Team Advisory Committee provided technical advice during the

Investigation and commentary on drafts of the Investigation reports prior to their public release. NIST

has benefited from the work of many people in the preparation of these reports, including the National

Construction Safety Team Advisory Committee. The content of the reports and recommendations,

however, are solely the responsibility of NIST.

Public Outreach

During the course of this Investigation, NIST held public briefings and meetings (listed in Table P-2) to

solicit input from the public, present preliminary findings, and obtain comments on the direction and

progress of the Investigation from the public and the Advisory Committee.

NIST maintained a publicly accessible Web site during this Investigation at http://wtc.nist.gov. The site contained extensive infonnation on the background and progress of the Investigation.

NIST's WTC Public-Private Response Plan

The collapse of the WTC buildings has led to broad reexamination of how tall buildings are designed,

constructed, maintained, and used, especially with regard to major events such as fires, natural disasters,

and terrorist attacks. Reflecting the enhanced interest in effecting necessary change, NIST, with support

from Congress and the Administration, has put in place a program, the goal of which is to develop and

implement the standards, technology, and practices needed for cost-effective improvements to the safety

and security of buildings and building occupants, including evacuation, emergency response procedures,

and threat mitigation.

The strategy to meet this goal is a three-part, NIST-led, public-private response program that includes:

• A federal building and fire safety investigation to study the most probable factors that contributed to post-aircraft impact collapse of the WTC towers and the 47-story WTC 7

building, and the associated evacuation and emergency response experience.

• A research and development (R&D) program to (a) facilitate the implementation of

recommendations resulting from the WTC Investigation, and (b) provide the technical basis

for cost-effective improvements to national building and fire codes, standards, and practices

that enhance the safety of buildings, their occupants, and emergency responders.

xxxii NISTNCSTAR 1, WTC Investigation
Preface

Table P-2. Public meetings and briefings of the WTC Investigation.

Date Location Principal Agenda

June 24, 2002 New York City, NY Public meeting: Public comments on the Draft Plan for the pending WTC Investigation.

August 21, 2002 Gaithersburg, MD Media briefing announcing the formal start of the Investigation.

December 9. 2002 Washington. DC Media briefing on release of the Public Update and NIST request

for photographs and videos. April 8. 2003 New York City, NY Joint public forum with Columbia University on first-person interviews. Apnl 29-30. 2003 Gaithersburg, MD NCST Advisory Committee meeting on plan for and progress on WTC Investigation with a public comment session. May 7, 2003 New York Cit>', NY Media briefing on release of May 2003 Progress Report.

August 26-27, 2003 Gaithersburg, MD NCST Advisory Committee meeting on status of the WTC

investigation with a public comment session. September 17. 2003 New York City, NY Media and public briefing on initiation of first-person data

collection projects.

December 2-3. 2003 Gaithersburg, MD NCST Advisory Committee meeting on status and initial results and release of the Public Update with a public comment session. February 12, 2004 New York City, NY Public meeting on progress and preliminary findings with public

comments on issues to be considered in fonnulating final recommendations.

June 18.2004 New York City, NY Media/public briefing on release of June 2004 Progress Report. June 22-23, 2004 Gaithersburg, MD NCST Advisory Committee meeting on the status of and

preliminary findings from the WTC Investigation with a public

comment session. August 24, 2004 Northbrook, IL Public viewing of standard fire resistance test of WTC floor system at Underwriters Laboratories, Inc. October 19-20, 2004 Gaithersburg, MD NCST Advisory Committee meeting on status and near complete

set of preliminary findings with a public comment session. November 22, 2004 Gaithersburg, MD NCST Advisory Committee discussion on draft annual report to Congress, a public comment session, and a closed session to discuss pre-draft recommendations for WTC Investigation.

April 5, 2005 New York City, NY Media and public briefing on release of the probable collapse sequence for the WTC towers and draft reports for the projects on

codes and practices, evacuation, and emergency response. June 23. 2005 New York City, NY Media and public briefing on release of all draft reports for the WTC towers and draft recommendations for public comment.

September 12-13. 2005Gaithersburg. MD NCST Advisory Committee meeting on disposition of public

comments and update to draft reports for the WTC towers. September 13-15,

2005

Gaithersburg, MD WTC Technical Conference for stakeholders and technical community for dissemination of findings and recommendations

and oppormnity for the public to make technical comments.

• A dissemination and technical assistance program (DTAP) to (a) engage leaders of the construction and building community in ensuring timely adoption and widespread use of

proposed changes to practices, standards, and codes resulting from the WTC Investigation

and the R&D program, and (b) provide practical guidance and tools to better prepare facility owners, contractors, architects, engineers, emergency responders, and regulatory authorities

to respond to fiiture disasters. The desired outcomes are to make buildings, occupants, and first responders safer in future disaster events.

NISTNCSTAR 1, WTC Investigation xxxiii
Preface

National Construction Safety Team Reports on the WTC Investigation

This report covers the WTC towers, with a separate report on the 47-story WTC 7. Supporting

documentation of the techniques and technologies used in the reconstruction are in a set of companion

reports that provide more detailed documentation of the Investigation findings and the means by which

these technical results were achieved. As such, they are part of the archival record of this Investigation.

The titles of the full set of Investigation publications are listed in Appendix B.

xxxiv NISTNCSTAR 1, WTC Investigation
Executive Summary

E.1 GENESIS OF THIS INVESTIGATION

On August 21, 2002, the National Institute of Standards and Technology (NIST) announced its building

and fire safety investigation of the World Trade Center (WTC) disaster.' This WTC Investigation was

then conducted under the authority of the National Construction Safety Team (NCST) Act, which was

signed into law on October 1, 2002. A copy of the Public Law is included in Appendix A.

The goals of the investigation of the WTC disaster were:

• To investigate the building construction, the materials used, and the technical conditions that contributed to the outcome of the WTC disaster after terrorists flew large jet-fuel laden

commercial airliners into the WTC towers.

• To serve as the basis for:

- Improvements in the way buildings are designed, constructed, maintained, and used;

- Improved tools and guidance for industry and safety officials;

- Recommended revisions to current codes, standards, and practices; and

- Improved public safety

The specific objectives were:

1 . Determine why and how WTC 1 and WTC 2 collapsed following the initial impacts of the

aircraft and why and how WTC 7 collapsed;

2. Determine why the injuries and fatalities were so high or low depending on location,

including ail technical aspects of fire protection, occupant behavior, evacuation, and

emergency response;

3. Determine what procedures and practices were used in the design, construction, operation,

and maintenance of WTC 1, 2, and 7; and

' NIST is a nonregulatory agency of the U.S. Department of Commerce. The purpose of NIST investigations is to improve the

safety and structural integrity of buildings in the United States, and the focus is on fact finding. NIST investigative teams are authorized to assess building perfomiance and emergency response and evacuation procedures in the wake of any building

failure that has resulted in substantial loss of life or that posed significant potential of substantial loss of life. NIST does not have the statutory authority to make findings of fault nor negligence by individuals or organizations. Further, no part of any

report resulting from a NIST investigation into a building failure or from an investigation under the National Construction

Safety Team Act may be used in any suit or action for damages arising out of any matter mentioned in such report

( 1 5 use 28 1 a, as amended by P.L. 1 07-23 1 ).

NISTNCSTAR 1, WTC Investigation XXXV
Executive Summary

4. Identify, as specifically as possible, areas in current building and fire codes, standards,

and practices that warrant revision.

E.2 APPROACH

To meet these goals. NIST complemented its in-house expertise with an array of specialists in key

technical areas. In all, over 200 staff contributed to the Investigation. NIST and its contractors compiled

and reviewed tens of thousand of pages of documents; conducted interviews with over a thousand people

who had been on the scene or who had been involved with the design, construction, and maintenance of

the WTC; analyzed 236 pieces of steel that were obtained from the wreckage; performed laboratory tests, measured material properties, and performed computer simulations of the sequence of events that happened from the instant of aircraft impact to the initiation of collapse for each tower.

Cooperation in obtaining the resource materials and in interpreting the results came from a large number

of individuals and organizations, including The Port Authority of New York and New Jersey and its contractors and consultants; Silverstein Properties and its contractors and consultants; the City of New

York and its departments; the manufacturers and fabricators of the building components; the companies

that insured the WTC towers; the building tenants; the aircraft manufacturers; the airlines; the public,

including survivors and family members; and the media.

The scarcity of physical evidence that is typically available in place for reconstruction of a disaster led to the following approach:

• Accumulation of copious photographic and video material. With the assistance of the media,

public agencies and individual photographers, NIST acquired and organized nearly

7,000 segments of video footage, totaling in excess of 150 hours and nearly

7,000 photographs representing at least 185 photographers. This guided the Investigation

Team's efforts to determine the condition of the buildings following the aircraft impact, the

evolution of the fires, and the subsequent deterioration of the structure.

• Establishment of the baseline perfonnance of the WTC towers, i.e., estimating the expected

perfomiance of the towers under nonnal design loads and conditions. The baseline

perfonnance analysis also helped to estimate the ability of the towers to withstand the unexpected events of September 1 1

, 2001 . Establishing the baseline performance of the

towers began with the compilation and analysis of the procedures and practices used in the design, construction, operation, and maintenance of the structural, fire protection, and egress systems of the WTC towers. The additional components of the performance analysis were

the standard fire resistance of the WTC truss-framed floor system, the quality and properties

of the structural steels used in the towers, and the response of the WTC towers to the design

gravity and wind loads.

• Simulations of the behavior of each tower on September 1 1, 2001, in four steps:

1 . The aircraft impact into the tower, the resulting distribution of aviation fuel, and the damage to the structure, partitions, thermal insulation materials, and building contents.

2. The evolution of multi-floor fires.

xxxvi NISTNCSTAR 1, WTC Investigation
Executive Summary

3. The heating and consequent weakening of the structural elements by the fires.

4. The response of the damaged and heated building structure, and the progression of

structural component failures leading to the initiation of the collapse of the towers.

For such complex structures and complex thermal and structural processes, each of these steps stretched

the state of the technology and tested the limits of software tools and computer hardware. For example,

the investigators advanced the state-of-the-art in the measurement of construction material properties and

in structural finite element modeling. New modeling capability was developed for the mapping of fire- generated environmental temperatures onto the building structural components.

The output of the four-step simulations was subject to uncertainties in the as-built condition of the towers,

the interior layout and furnishings, the aircraft impact, the internal damage to the towers (especially the thermal insulation for fire protection of the structural steel, which is colloquially referred to as fireproofing), the redistribution of the combustibles, and the response of the building structural components to the heat from the fires. To increase confidence in the simulation results, NIST used the visual evidence, eyewitness accounts from inside and outside the buildings, laboratory tests involving

large fires and the heating of structural components, and formal statistical methods to identify influential parameters and quantify the variability in analysis results.

• Combination of the knowledge gained into probable collapse sequences for each tower,'^ the

identification of factors that contributed to the collapse, and a list of factors that could have

improved building performance or otherwise mitigated the loss of life.

• Compilation of a list of findings that respond to the first three objectives and a list of

recommendations that responds to the fourth objective.

E.3 SUMMARY OF FINDINGS

Objective 1: Determine why and how WTC 1 and WTC 2 collapsed following the initial impacts of

the aircraft.

• The two aircraft hit the towers at high speed and did considerable damage to principal

structural components (core columns, floors, and perimeter columns) that were directly

impacted by the aircraft or associated debris. However, the towers withstood the impacts and

would have remained standing were it not for the dislodged insulation (fireproofing) and the subsequent multi-floor fires. The robustness of the perimeter frame-tube system and the large

size of the buildings helped the towers withstand the impact. The structural system

redistributed loads from places of aircraft impact, avoiding larger scale damage upon impact.

The hat truss, a feature atop each tower which was intended to support a television antenna,

prevented earlier collapse of the building core. In each tower, a different combination of

impact damage and heat-weakened structural components contributed to the abrupt structural collapse.

^ The focus of the Investigation was on the sequence of events from the instant of aircraft impact to the initiation of collapse for each tower. For brevity in this report, this sequence is referred to as the "probable collapse sequence," although it includes

little analysis of the structural behavior of the tower after the conditions for collapse initiation were reached and collapse

became inevitable.

NCSTAR 1, WTC Investigation xxxvii
Executive Summary

• In WTC 1 , the fires weakened the core columns and caused the floors on the south side of the building to sag. The floors pulled the heated south perimeter columns inward, reducing their capacity to support the building above. Their neighboring columns quickly became

overloaded as columns on the south wall buckled. The top section of the building tilted to the south and began its descent. The time from aircraft impact to collapse initiation was largely

determined by how long it took for the fires to weaken the building core and to reach the

south side of the building and weaken the perimeter columns and floors.

• In WTC 2, the core was damaged severely at the southeast comer and was restrained by the

east and south walls via the hat truss and the floors. The steady burning fires on the east side

of the building caused the floors there to sag. The floors pulled the heated east perimeter

columns inward, reducing their capacity to support the building above. Their neighboring

columns quickly became overloaded as columns on the east wall buckled. The top section of

the building tilted to the east and to the south and began its descent. The time from aircraft impact to collapse initiation was largely determined by the time for the fires to weaken the perimeter columns and floor assemblies on the east and the south sides of the building.

WTC 2 collapsed more quickly than WTC I because there was more aircraft damage to the

building core, including one of the heavily loaded comer columns, and there were early and

persistent fires on the east side of the building, where the aircraft had extensively dislodged

insulation from the stmctural steel.

• The WTC towers likely would not have collapsed under the combined effects of aircraft impact damage and the extensive, multi-floor fires that were encountered on September 1 1

,

2001 , if the themial insulation had not been widely dislodged or had been only minimally

dislodged by aircraft impact.

• In the absence of stmctural and insulation damage, a conventional fire substantially similar to or less intense than the fires encountered on September 1 1, 2001, likely would not have led to the collapse of a WTC tower.

• NIST found no corroborating evidence for altemative hypotheses suggesting that the WTC

towers were brought down by controlled demolition using explosives planted prior to September 1 1

, 2001 . NIST also did not find any evidence that missiles were fired at or hit the towers. Instead, photographs and videos from several angles clearly showed that the collapse initiated at the fire and impact floors and that the collapse progressed from the

initiating floors downward, until the dust clouds obscured the view.

Objective 2: Determine why the injuries and fatalities were so high or low depending on location,

including all technical aspects of fire protection, occupant behavior, evacuation, and emergency

response.

• Approximately 87 percent of the estimated 17,400 occupants of the towers, and 99 percent of

those located below the impact floors, evacuated successfully. In WTC 1 , where the aircraft destroyed all escape routes, 1,355 people were trapped in the upper floors when the building

collapsed. One hundred seven people who were below the impact floors did not survive.

Since the flow of people from the building had slowed considerably 20 min before the tower

collapsed, the stairwell capacity was adequate to evacuate the occupants on that moming.

xxxviii NISTNCSTAR 1, WTC Investigation
Executive Summary

• In WTC 2. before the second aircraft strike, about 3,000 people got low enough in the building to escape by a combination of self-evacuation and use of elevators. The aircraft destroyed the operation of the elevators and the use of two of the three stairways. Eighteen

people fi-om above the impact zone found a passage through the damaged third stairway

(Stairwell A) and escaped. The other 619 people in or above the impact zone perished.

Eleven people who were below the impact floors did not survive. As in WTC 1, shortly

before collapse, the flow of people from the building had slowed considerably, indicating that the stairw ell capacity was adequate that morning.

• About 6 percent of the survivors described themselves as mobility impaired, with recent

injury and chronic illness being the most common causes; few, however, required a wheelchair. Among the 1 1 8 decedents below the aircraft impact floors, investigators

identified seven who were mobility impaired, but were unable to detennine the mobility

capability of the remaining 111.

• A principal factor limiting the loss of life was that the buildings were one-third to one-half

occupied at the time of the attacks. NIST estimated that if the towers had been fully occupied

with 20,000 occupants each, it would have taken just over 3 hours to evacuate the buildings

and about 14,000 people might have perished because the stairwell capacity would not have

been sufficient to evacuate that many people in the available time. Egress capacity required

by current building codes is determined by single floor calculations that are independent of

building height and does not consider the time for fiill building evacuation.

• Due to the presence of assembly use spaces at the top of each tower (Windows on the World

restaurant complex in WTC 1 and the Top of the World observation deck in WTC 2) that were designed to accommodate over 1 ,000 occupants per floor, the New York City Building

Code would have required a minimum of four independent means of egress (stairs), one more

than the three that were available in the buildings. Given the low occupancy level on September 1 1. 2001, NIST found that the issue of egress capacity from these places of

assembly, or from elsewhere in the buildings, was not a significant factor on that day. It is conceivable that such a fourth stairwell, depending on its location and the effects of aircraft impact on its functional integrity, could have remained passable, allowing evacuation by an unknown number of additional occupants from above the floors of impact. If the buildings

had been filled to their capacity with 20,000 occupants, the required fourth stairway would

likely have mitigated the insufficient egress capacity for conducting a full building

evacuation within the available time.

• Evacuation was assisted by participation in fire drills within the previous year by two-thirds

of survivors and perhaps hindered by a Local Law that prevented employers from requiring

occupants to practice using the stairways. The stairways were not easily navigated in some

locations due to their design, which included "transfer hallways," where evacuees had to traverse from one stairway to another location where the stairs continued. Additionally,

many occupants were unprepared for the physical challenge of fiill building evacuation.

• The functional integrity and survivability of the stairwells was affected by the separation of

the stairwells and the structural integrity of stairwell enclosures. In the impact region of

WTC 1, the stairwell separation was the smallest over the building height—clustered well

NCSTAR 1, WTC Investigation XXXIX
Executive Summary

within the building core—and all stairwells were destroyed by the aircraft impact. By

contrast, the separation of stairwells in the impact region of WTC 2 was the largest over the

building height—located along different boundaries of the building core—and one of three

stairwells remained marginally passable after the aircraft impact. The shaft enclosures were

fire rated but were not required to have structural integrity under typical accidental loads: there were numerous reports of stairwells obstructed by fallen debris from damaged

enclosures.

• The active fire safety systems (sprinklers, smoke purge, fire alarms, and emergency occupant

communications) were designed to meet or exceed current practice. However, with the

exception of the evacuation announcements, they played no role in the safety of life on

September 1 1 because the water supplies to the sprinklers were damaged by the aircraft impact. The smoke purge systems operated under the direction of the fire department after

fires were not turned on, but they also would have been ineffective due to aircraft damage.

The violence of the aircraft impact served as its own alarm. In WTC 2, contradictory public

address announcements contributed to occupant confusion and some delay in occupants

beginning to evacuate.

• For the approximately 1 ,000 emergency responders on the scene, this was the largest disaster

they had even seen. Despite attempts by the responding agencies to work together and

perfonTi their own tasks, the extent of the incident was well beyond their capabilities.

Communications were erratic due to the high number of calls and the inadequate performance

of some of the gear. Even so, there was no way to digest, test for accuracy, and disseminate

the vast amount of information being received. Their jobs were complicated by the loss of

command centers in WTC 7 and then in the towers after WTC 2 collapsed. With nearly all elevator service disrupted and progress up the stairs taking about 2 min per floor, it would

have taken hours for the responders to reach their destinations, assist survivors, and escape

had the towers not collapsed.

Objective 3: Determine what procedures and practices were used in the design, construction,

operation, and maintenance of WTC 1 and WTC 2.

• Because of The Port Authority's establishment under a clause of the United States Constitution, its buildings were not subject to any state or local building regulations. The

buildings were unlike any others previously built, both in their height and in their innovative

structural features. Nevertheless, the actual design and approval process produced two

buildings that generally were consistent with nearly all of the provisions of the New York

City Building Code and other building codes of that time that were reviewed by NIST. The

loads for which the buildings were designed exceeded the New York City code requirements.

The quality of the structural steels was consistent with the building specifications. The

departures from the building codes and standards identified by NIST did not have a

significant effect on the outcome of September 1 1

.

• For the floor systems, the fire rating and insulation thickness used on the floor trusses, which

together with the concrete slab served as the main source of support for the floors, were of

concern from the time of initial construction. NIST found no technical basis or test data on which the thermal protection of the steel was based. On September 1 1 , 2001, the minimum

xl NISTNCSTAR 1, WTC Investigation
Executive Summary

specified thickness of the insulation was adequate to delay heating of the tmsses; the amount

of insulation dislodged by the aircraft impact, however, was sufficient to cause the structural

steel to be heated to critical levels.

• Based on four standard fire resistance tests that were conducted under a range of insulation

and test conditions, NIST found the fire rating of the floor system to vary between 3/4 hour

and 2 hours; in all cases, the floors continued to support the full design load without collapse

for over 2 hours.

• The wind loads used for the WTC towers, which governed the structural design of the external columns and provided the baseline capacity of the structures to withstand abnormal

events such as major fires or impact damage, significantly exceeded the requirements of the New York City Building Code and other building codes of the day that were reviewed by

NIST. Two sets of wind load estimates for the towers obtained by independent commercial

consultants in 2002, however, differed by as much as 40 percent. These estimates were based on wind tunnel tests conducted as part of insurance litigation unrelated to the Investigation.

E.4 RECOMMENDATIONS

The tragic consequences of the September 11, 2001, attacks were directly attributable to the fact that

terrorists flew large jet-ftiel laden commercial airliners into the WTC towers. Buildings for use by the general population are not designed to withstand attacks of such severity; building regulations do not

require building designs to consider aircraft impact. In our cities, there has been no experience with a

disaster of such magnitude, nor has there been any in which the total collapse of a high-rise building

occurred so rapidly and with little warning.

While there were unique aspects to the design of the WTC towers and the terrorist attacks of

September 1 1, 2001, NIST has compiled a list of recommendations to improve the safety of tall buildings,

occupants, and emergency responders based on its investigation of the procedures and practices that were

used for the WTC towers; these procedures and practices are commonly used in the design, construction,

operation, and maintenance of buildings under normal conditions. Public officials and building owners

will need to determine appropriate performance requirements for those tall buildings, and selected other

buildings, that are at higher risk due to their iconic status, critical function, or design.

The topics of the recommendations in eight groups are listed in Table E-1. The ordering does not reflect any priority.

The eight major groups of recommendations are:

• Increased Structural InteRrity: The standards for estimating the load effects of potential

hazards (e.g., progressive collapse, wind) and the design of structural systems to mitigate the

effects of those hazards should be improved to enhance structural integrity.

• Enhanced Fire Endurance of Structures: The procedures and practices used to ensure the fire endurance of structures should be enhanced by improving the technical basis for construction

classifications and fire resistance ratings, improving the technical basis for standard fire resistance testing methods, use of the "structural frame" approach to fire resistance ratings.

NCSTAR 1, WTC Investigation xli
Executive Summary

and developing in-service performance requirements and conformance criteria for sprayed

fire-resistive material.

• New Methods for Fire Resistant Design of Structures: The procedures and practices used in the fire resistant design of structures should be enhanced by requiring an objective that uncontrolled fires result in burnout without local or global collapse. Performance-based

methods are an alternative to prescriptive design methods. This effort should include the development and evaluation of new fire resistive coating materials and technologies and

evaluation of the fire performance of conventional and high-perfonnance structural materials.

• Improved Active Fire Protection: Active fire protection systems (i.e., sprinklers, standpipes/

hoses, fire alanns, and smoke management systems) should be enhanced through

improvements to design, perfomiance, reliability, and redundancy of such systems.

• Improved Building Evacuation: Building evacuation should be improved to include system

designs that facilitate safe and rapid egress, methods for ensuring clear and timely emergency

communications to occupants, better occupant preparedness for evacuation during

emergencies, and incorporation of appropriate egress technologies.

• Improved Emergencv Response: Technologies and procedures for emergency response

should be improved to enable better access to buildings, response operations, emergency

communications, and command and control in large-scale emergencies.

• Improved Procedures and Practices: The procedures and practices used in the design,

construction, maintenance, and operation of buildings should be improved to include

encouraging code compliance by nongovernmental and quasi-governmental entities, adoption

and application of egress and sprinkler requirements in codes for existing buildings, and

retention and availability of building documents over the life of a building.

• Education and Training: The professional skills of building and fire safety professionals

should be upgraded though a national education and training effort for fire protection

engineers, structural engineers, architects, and building regulatory and fire service personnel.

The recommendations call for action by specific entities regarding standards, codes and regulations, their adoption and enforcement, professional practices, education, and training; and research and development.

Only when each of the entities carries out its role will the implementation of a recommendation be

effective.

The recommendations do not prescribe specific systems, materials, or technologies. Instead, NIST

encourages competition among alternatives that can meet performance requirements. The

recommendations also do not prescribe specific threshold levels; NIST believes that this responsibility

properly falls within the purview of the public policy setting process, in which the standards and codes

development process plays a key role.

NIST believes the recommendations are realistic and achievable within a reasonable period of time. Only

a few of the recommendations call for new requirements in standards and codes. Most of the recommendations deal with improving an existing standard or code requirement, establishing a standard

xlii NISTNCSTAR 1, WTC Investigation
Executive Summary

for an existing practice without one, establishing the technical basis for an existing requirement, making a

current requirement risk-consistent, adopting or enforcing a current requirement, or establishing a performance-based alternative to a current prescriptive requirement.

NIST strongly urges that immediate and serious consideration be given to these recommendations by the building and fire safety communities in order to achieve appropriate improvements in the way buildings

are designed, constructed, maintained, and used and in evacuation and emergency response procedures

with the goal of making buildings, occupants, and first responders safer in future emergencies.

NIST also strongly urges building owners and public officials to ( 1) evaluate the safety implications of

these recommendations to their existing inventory of buildings and (2) take the steps necessary to mitigate

any unwarranted risks without waiting for changes to occur in codes, standards, and practices.

NIST further urges state and local agencies to rigorously enforce building codes and standards since such

enforcement is critical to ensure the expected level of safety. Unless they are complied with, the best

codes and standards cannot protect occupants, emergency responders, or buildings.

NCSTAR 1, WTC Investigation xliii
Executive Summary

Unrelated

« ON "5 I O Related^

Selected Other

High-Risk

Buildings a

a< All Tall Buildings

Education &

Training

R&D/Further

Study

oU

Adoption &

Enforcement

Standards,

Codes,

Regulations

Practices

u

'a, eH

ao

s

VS

S

ew

X

0.

fao

u

c

i2

c

CO

0)^ C

3 O

'-a

> -aa

_o ad's o =

o

<

o

S «

o i^ ^ o

C O

•3 o

o g

OB 2

•S '5

.2 3

E a-

<u

D

T3o

.9 o

t2 2

=2 ^

o

S3 '3?

<i3 <U

COo

15

_o

o

"cO

CO

"3o

8^

3 5

-ao

1)Q.X

>^ 3

a. M

> X>

CO u

to

3 y o -z:

• s 00

Ji CO 0 S

^ P

-T3 O

'i i

a- -2

c 8

to co

1

1

0 0) c

01) to _3

is CO> '5 o 5i

112 o

"O to S > CO c«

c« Ml

"5 O

^ CO

CO^ CJ p CO ^ CO

CJ (U

CO x> > .2 <

O G

CD 2 OX)

I- 3

g

I

2 .2

iy5 CO

CO

-a o

u

> OJ O Ofll to S 2

s

^ i- I £

£ O

o

u 3 .t:^ CO -3 C

CJ OB h 5

3 2 3

CO 3 o

-§ s

uj [2

? <U c« 3

(L> 13 (U & Z u- Q 00

OJ p <

tj 2

't^ > uh O Oh & y

S

xliv NISTNCSTAR 1, WTC Investigation
Executive Summary

.2 —

Unrelated

Related'

Selected Other

High-Risk

Buildings

All Tall Buildings

Education &

Training

R&D/Further

Studv

Adoption &

Enforcement

Standards,

Codes,

Regulations

Practices

a.3H

Bo

-aM

TtB

V

E

E

o

BO

'S

Si o la

91 Pi

C 3

c —

C3>y

_>> a

D- O

o ^

o

Cl

CJ O

•i: o

5 «

O. _3 5 «

LU

£ m tu

UJ

01)

UJ _

00 o

p c u ^ UJ

O C3 11

C«J CTl

c

_ C3 5 :f

00

o

2^—

I

c1 i

.S bo 2 c

S 2

.2 ^ I-^ o

35 Ji

T3C

o

<U

1) T3o •£ oo a>

03 >° a s

O O

O ^

c3 o

c 'S .2 3

<u -a

oj o

o 3

>^ "> U 3 (U O D S o o

p p 5 ol!

ob-2

O <U

c op

'c3 .S

•3 T3

oJ g

o oo

f—

OJ p

CO -s

° B

OJ o

1) Ic> 00 (u C J5

CO -c -a

'-> o

<u ao > S

T3 "

D

3 > O <j3 O J=

.S §

NISTNCSTAR 1, WTC Investigation xlv
Executive Summary

This page intentionally left blank.

xlvi NISTNCSTAR 1, WTC Investigation
Part I: September 11, 2001
This page intentionally left blank.

NISTNCSTAR 1, WTC Investigation
Chapter 1 New York City's World Trade Center

1.1 THE origination

In 1960, American technology was on the rise, and internationalism was a prominent theme. It was in this technical and global political context and this year that the planning began for a World Trade Center

(WTC) to be located in lower Manhattan. From its first conception during the 1939 World's Fair in New

York, it now emerged under the powerful advocacy of the Chase Manhattan Bank's David Rockefeller.

Here was a grand plan that would embody the concept of New York City as a center of world commerce

and provide a home for numerous international trade companies.

The organization that would build the World Trade Center was The Port of New York Authority, later to be renamed as The Port Authority of New York and New Jersey (The Port Authority, PANYNJ). Created

in 1921, under a clause in the United States Constitution, to run the multijurisdictional commercial zones

in the region. The Port Authority built and operated facilities on the banks of the Port of New York's

waterways, the bridges to cross them, and the major metropolitan airports. It had the authority to obtain

land by eminent domain and to raise funds for its projects. Now, under the leadership of its Executive

Director, Austin Tobin, the concept for the World Trade Center grew from the grand plan of David

Rockefeller to the grandeur of the world's largest office complex.

To fulfill all the functional, aesthetic, and economic desires for this concept, innovative architecture was

needed. In 1962, the firm of Minoru Yamasaki & Associates was hired to perform the architectural

design, which was first unveiled in 1964. The team also involved Emory Roth & Sons, P.C., as the

architect of record.' The structural engineering was by Worthington, Skilling, Helle and Christiansen.

(Some time after completion of the construction, Skilling, Helle, Christiansen, and Robertson, and then

Leslie E. Robertson Associates (LERA) assumed that role.) Jaros, Baum & Bolles were hired as the mechanical engineers, and Joseph R. Loring & Associates were the electrical engineers. Tishman

Construction Corporation was the general contractor.

In 1966, the formal groundbreaking for the towers took place. Construction began in 1968, with the first occupancy in 1970. These dates establish the historical context for the building codes and the state of

practice under which the complex was designed and constructed. This will be discussed further in Part II.

The functions of these entities are as follows. In New York City, a permit, issued by the building commissioner, is required to construct, alter, repair, demolish or remove any building. The architect who signs and generally files the plans (as part of the process for securing the permit) and takes the lead role of a project is the architect-of-record. Specific subsets of plans may be

signed by the structural, electrical, and mechanical engineers, representing the separate disciplines involved in those subsets. The filed plans are reviewed and approved for compliance with the building code requirements by the building commissioner

before issuance of the permit.

The City of New York had no jurisdiction. However, The Port Authority required that all the WTC tower plans be submitted

for their review and approval for code compliance and other architectural requirements. The responsibility of technical correctness rested with the architect of record and the engineers of record.

NISTNCSTAR 1, WTC Investigation 1
Chapter 1

The expected tenancy by companies involved in international trade did not materialize as conceived, so

the State of New York, the City of New York, and The Port Authority became the principal WTC tenants

in the 1970s. As the years passed, however, the prestige of the address grew, and the requirement that occupants be involved in international trade was relaxed. At the end of the twentieth century, the World

Trade Center was nearly fully occupied by a diverse mixture of large and small businesses and federal,

state, and city government organizations.

1 .2 THE WORLD TRADE CENTER COMPLEX

1.2.1 The Site

By 2001, the WTC complex had become an integral part of Manhattan. It was composed of seven

buildings (here referred to as WTC 1 through WTC 7) on a site toward the southwest tip of Manhattan

Island (Figures 1-1 and 1-2). Whether viewed from close up, from the Statue of Liberty across the Upper

Bay or from an aircraft descending to LaGuardia Airport, the towers were a sight to behold. The two

towers, WTC 1 (North Tower) and WTC 2 (South Tower), were each 1 10 stories high, dwarfing the other

skyscrapers in lower Manhattan and seemingly extending to all Manhattan the definition of "tall" previously set by midtown's Empire State Building. WTC 3, a Marriott Hotel, was 22 stories tall, WTC 4

(South Plaza Building) and WTC 5 (North Plaza Building) were each 9-story office buildings, and

WTC 6 (U.S. Customs House) was an 8-story office building. These six buildings were built around a 5-acre Plaza named m honor of Austin Tobin. WTC 7 was a 47-story office building on Port Authority

land across Vesey Street on the north side of the Plaza complex. Built over the ConEd substation serving

the WTC complex, it was completed in 1987 and was operated by Silverstein Properties, Inc.

2 NISTNCSTAR 1, WTC Investigation
New York City's World Trade Center

Figure 1-1. The World Trade Center in Lower Manhattan.

NISTNCSTAR 1, WTC Investigation 3
Chapter 1

Source: The Imagers Team, NASA/GSFC.

Figure 1-2. Lower Manhattan and the World Trade Center towers.

Below the 1 1 western acres of the site, underneath a large portion of the Plaza and WTC 1, WTC 2,

WTC 3, and WTC 6, was a 6-story underground structure. The structure was surrounded by a wall that extended from ground level down 70 ft to bedrock. Holding back the waters of the Hudson River, this wall had enabled rapid excavation for the foundation and continued to keep groundwater from flooding

the underground levels.

Commuter trains brought tens of thousands of workers and visitors to Manhattan from Brooklyn and

New Jersey into a new underground station below the plaza. A series of escalators and elevators took the WTC employees directly to an underground shopping mall and to the Concourse Level of the towers.

4 NISTNCSTAR 1, WTC Investigation
New York City's World Trade Center

1.2.2 The Towers

The Buildings

The focus of the complex was on the two towers, each taller than any other building in the world at that time. The roof of WTC 1 was 1,368 ft above the Concourse Level, 6 ft taller than WTC 2, and supported

a 360 ft tall antenna mast for television and radio transmission. The footprint of each tower was a square, about 210 ft on a side (approximately an acre), with the comers of the tower beveled 9 ft 9 in. Internally,

each floor was a square, about 206 ft on a side."

The superb vistas from the top of such buildings virmally demanded public space from which to view

them, and The Port Authority responded. The 1 0?"" floor of WTC 1 housed a gourmet restaurant and bar

with views of the Hudson River and New Jersey to the west, the skyscrapers of midtown Manhattan to the

north, the East River and Queens and Brooklyn to the east, the Statue of Liberty to the southwest, and the

Atlantic Ocean to the south. Similar views could be seen from observation decks on the 107"' floor and

the roof of WTC 2.

Table 1-1 shows the use of the floors, which was similar but not identical in the two towers.

Table 1-1. Use of floors in the WTC towers.

Floor(s) WTC 1 WTC 2 Roof Antenna space and window washing

equipment

Outdoor observation deck and window

washing equipment

110 Television studios Mechanical equipment

108. 109 Mechanical equipment Mechanical equipment

107 Windows on the World restaurant Indoor observation deck

106 Catering Tenant space 79 through 105 Tenant space Tenant space 78 Skylobby, tenant space Skylobby, tenant space 77 Tenant space Tenant space

75, 76 Mechanical equipment Mechanical equipment

45 through 74 Tenant space Tenant space 44 Skylobby, cafeteria, tenant space Skylobby, tenant space 43 Port Authority space Tenant space 41,42 Mechanical equipment Mechanical equipment

9 through 40 Tenant space Tenant space

7, 8 Mechanical floors Mechanical floors Concourse through 6 6-stor>' lobby 6-story lobby

Extensive details regarding all aspects of this report are found in the supporting Investigation reports listed in Appendix B. A

subject index of those reports appears as Appendix C to this report. Those reports, in turn, cite the numerous documents made

available to the Investigation Team. To maintain continuity, citations of the source documents are not included in this report. They are found in the supporting Investigation reports.

NISTNCSTAR 1, WTC Investigation 5
Chapter 1

The Port Authority had managed the operation of the two towers since their opening three decades earlier. Silverstein Properties acquired a 99-year lease on the towers in July 2001.

The Structures

Each of the tenant floors of the towers was intended to offer a large expanse of workspace, virtually

uninterrupted by columns or walls. This called for an innovative structural design, lightweight to minimize the total mass of 1 10 stories, yet strong enough to support the huge building with all its furnishings and people. Structural engineers refer to the building weight

as the dead load; the people and furnishings are called the live load. Collectively, these are referred to as gravity loads. The buildings would

also need to resist lateral loads and excessive swaying, principally from

the hurricane force winds that periodically strike the eastern seaboard of

the United States. An additional load, stated by The Port Authority to have been considered in the design of the towers, was the impact of a Boeing 707, the largest commercial airliner when the towers were

designed, hitting the building at its full speed of 600 mph.

Skilling and his team rose to the challenge of providing the required load capacity within Yamasaki's

design concept. They incorporated an innovative framed-tube concept for the structural system. The

columns supporting the building were located both along the external faces and within the core. The core

also contained the elevators, stairwells, and utility shafts. The dense array of columns along the building

perimeter was to resist the lateral load due to hurricane-force winds, while also sharing the gravity loads

about equally with the core columns. The floor system was to provide stiffness and stability to the

framed-tube system in addition to supporting the floor loads. Extensive and detailed studies were

conducted in wind tunnels, instead of relying on specific, prescriptive building code requirements, to estimate the wind loads used in the design of these buildings.^ This

approach took advantage of the allowance by most state and local building codes for alternative designs and construction if evidence were presented that ensured equivalent performance.

There were four major structural subsystems in the towers, referred to as the exterior wall, the core, the floor system, and the hat truss. The

first, the exterior structural subsystem, was a vertical square tube that consisted of 236 narrow columns, 59 on each face from the lO"" floor

to the 107"" floor (Figure 1-3). There were also columns on alternate

stories at each of the beveled comers, but these carried none of the gravity loads. (There were fewer, wider-spaced columns below the

7"' floor to accommodate doorways.) Each column was fabricated by

welding four steel plates to fonn a tall box, nominally 14 in. on a side. The space between the steel columns was 26 in., with a narrower.

The studies showed that each tower affected the wind loads on the other. This effect was not accounted for in the prescriptive

wind load requirements found in building regulations.

In 1945, a B-25 aircraft had

become lost in the fog and

struck the 78'^ and 79'^

floors of the Empire State

Building. The building

withstood the impact and

ensuing fire and was ready

for reoccupancy the

following week.

A grade of steel is characterized by its yield

strength, expressed in ksi, or thousands of pounds per

square inch. This is the

force per unit area at which

the steel begins to undergo

a permanent deformation.

Different steel strengths, or grades, are manufactured by

varying the chemistry and

processing of the alloy.

Higher strength steel is used

when the design calls for more strength per weight of the steel column or beam.

6 NISTNCSTAR 1, WTC Investigation
New York City's World Trade Center N

A

101 103 10E loe 112 11S lie 121 12' 1Z7 ix 133 i3e 139 142 i<s i^s ist \st 1S7 is9 i....L.L.LJ„l_.i„[„L,L,l.,l„i.,L,[„i„LJ

501

h601

503 504 SOS 507

602 603

1 701

601

1001

702

802

703 rSd 704 705

603 804 805

707

806

902 903 904 905 906

1002 1003 1004 1005 1006 1007

L

6O81

708 •

807"

908<

10081

> 2

-215

-218

<-WTC 1

WTC2

i

3E« 367 3M 3S1 3U 3U »2 2B 33e 333 230 327 324 321 318 31s 312 309 306 303 XI

200 i

15g r

201 203 20e 20s 212 2IS 2tS 221 224 227 230 233 236 239 242 245 248 251 2S4 257 259

Figure 1-3. Tower floor

plans with column

numbers.

506 606

-

sa

7^

L.1..1..1..1..1.

508 608 ~r—

708 607 908 1008

906 1006

•706 80S

505 605 705 804 98s 100b

504 604 704

703 803

904 1004

503 603 903 1003

502

1

602 902 1002

601 701 801 901 1001

X -303

-306

-309

-312

-315

-319

-333

-396

rTTTTTin'^nnM-TTTTTl

-357 -359

459 457 4M 451 44a 445 *«2 438 436 433 430 427 424 421 41B 416 412 409 406 403 401

NISTNCSTAR 1, WTC Investigation 7
Chapter 1

framed plate glass window in each gap. Adjacent columns were connected at each floor by steel spandrel

plates, 52 in. high. The upper parts of the buildings had less wind load and building mass to support.

Thus, on higher floors, the thickness of the steel plates making up the columns decreased, becoming as

thin as % in. near the top. There were 10 grades of steel used for the columns and spandrels, with yield

strengths ranging from 36 ksi to 100 ksi. The grade of steel used in each location was dictated by the calculated stresses due to the gravity and wind loads.

All the exterior columns and spandrels were prefabricated into welded panels, three stories tall and three columns wide. The panels, each numbered to identify its location in the tower, were then bolted to adjacent units to form the walls (Figure 1^). The use of identically shaped prefabricated elements was

itself an innovation that enabled rapid construction. The high degree of modularization and prefabrication

used in the construction of these buildings and the identification, tracking, and logistics necessary to ensure that each piece was positioned correctly was unprecedented.

Source: Unknown. Enhanced by NIST. Figure 1-4. Perimeter column/spandrel assembly and floor structure.

A second structural subsystem was located in a central service area, or core (Figure 1-5), approximately

135 ft by 87 ft, that extended virtually the full height of the building. The long axis of the core in WTC 1 was oriented in the east-west direction, while the long axis of the core in WTC 2 was oriented in the

north-south direction (Figure 1-3). The 47 columns in this rectangular space were fabricated using

primarily 36 ksi and 42 ksi steels and also decreased in size at the higher stories. The four massive comer

columns bore nearly one-fifth of the total gravity load on the core columns. The core columns were

interconnected by a grid of conventional steel beams to support the core floors.

8 NISTNCSTAR 1, WTC Investigation
New York City's World Trade Center

120 130 innnnnnnnn

O

O ^ CO q

o ^

CM :

o :

o

140 150

nnnnnnnnnnnnnnnnn

159

501 508

J

V

\- '

i A- ''/\

— = H\ ~H

100 IP

i '89 ' '90'

91

'

L 1

50

! 88

87

X

1

. 1. 1008

Ir

VJUJ^ _l IJJJJL_I UJ

359 350

- L L'U JU _j1_J'„UULJUUUIjUUUuUULiuIJULJLJuuuuui_juuLJu u uu

340 330 320 310 301 WTC1 96

Note: Column numbers are shown around the perimeter. The four corner core columns (501, 508, 1001, and 1008)

are marked for orientation. Stairwells A, B, and C are shown in red stripes. The fourth red-striped area is the

tenant's convenience stairwell that connected the 95'^ through 97'^ floors in WTC 1 ; it was not considered part of the egress system. The remaining numbers denote specific elevators. Much of the rest of the floor was open space

suited for offices, conference rooms, or office cubicles. The arrangement and size of the core varied among the

different floors. Figure 1-5. Plan of the 96"" floor of WTC 1 showing the core and tenant spaces.

NISTNCSTAR 1, WTC Investigation 9
Chapter 1

The third major structural subsystem was the floors in the tenant spaces. These floors supported their own weight, along with live loads, provided lateral stability to the exterior walls, and distributed wind

loads among the exterior walls. The floor constmction was an innovation for a tall building. As shown in Figure 1-6, each tenant floor consisted of 4 in. thick, lightweight cast-in-place concrete on a fluted steel deck, but that is where "ordinary" ended. Supporting the slab was a grid of lightweight steel bar trusses. The top bends (or "knuckles") of the main truss webs extended 3 in. above the top chord and were embedded into the concrete floor slab. This concrete and steel assembly thus functioned as a composite

unit, that is, the concrete slab acted integrally with the steel trusses to carry floor loads. The primary truss pairs were either 60 ft or 35 ft long and were spaced at 6 ft 8 in. There were perpendicular bridging

trusses every 1 3 ft 4 in. The floor trusses and fluted metal deck were prefabricated in panels that were

typically 20 ft wide and that were hoisted into position in a fashion similar to the exterior wall panels.

Concrete Metal Deck

Main Truss

Figure 1-6. Schematic of composite floor truss system.

The bottom chords were connected to the spandrel plates by devices that were called viscoelastic

dampers. Experiments on motion perception, conducted with human subjects, had shown a high potential

for occupant discomfort when the building swayed in a strong wind. When the tower was buffeted by

strong winds, these dampers absorbed energy, reducing the sway and the vibration expected from a building that tall. The use of such vibration damping devices in buildings was an innovation at that time.

The fourth major structural subsystem was located from the 107"' floor to the roof of each tower. It was a

set of steel braces, collectively referred to as the "hat truss" (Figure 1-7). Its primary purpose had been to support a tall antenna atop each tower, although only WTC 1 had one installed. The hat truss provided

additional connections among the core columns and between the core and perimeter columns, providing

additional means for load redistribution.

10 NISTNCSTAR 1, WTC Investigation
New York City's World Trade Center

Figure 1-7. Schematic of a hat truss.

Fire Resistance

High-rise buildings in the United States are designed to meet requirements intended, among other

objectives, to enable the building to suffer a sizable fire and still remain standing. The requirements are expressed in terms of fire resistance ratings, given in units of time.

The fire resistance of a column, wall, or floor design is rated by subjecting the assembly to standard

heating conditions. A sample section of a wall to be tested is installed as one face of a furnace; a floor becomes the top of the furnace. Beams are normally rated as a part of the floor test. Floor systems are always tested while carrying their full design load. Walls are similarly loaded if they are intended to be

load bearing, but are not loaded if the only load they are intended to support is their own weight. In the United States, columns are required to be loaded during the test, however, an alternative is often used,

whereby the columns is not loaded and the temperature of the steel is used as a limiting criterion.

It is widely recognized in the building profession that fire resistance ratings, although expressed in hours,

do not mean that the structure will sustain its performance for that length of time in a real fire. Actual fire performance may be greater or less than that achieved in the test furnace, depending on the severity of the

actual fire exposure. Rather, these are taken as relative ratings, e.g., a wall rated at 2 hours will block the spread of a fire longer than a wall rated at I hour.

Fire Protection Systems

Bare structural steel components, when exposed to a large and sustained fire, can heat rapidly to the point

where their ability to support their load is compromised. Thus, insulation is usually employed to encapsulate the steel and thus delay the heating of the steel. In the WTC towers, a major fraction of the core columns were enclosed or protected on several sides by sheets of gypsum wallboard. The trusses, perimeter columns, spandrels, and one or more surfaces of the core columns were coated with one of

NISTNCSTAR 1, WTC Investigation 11
Chapter 1

three different sprayed fire-resistive material (SFRM). In this report, these materials are collectively

referred to as "insulation."'' The thickness of the wallboard or the SFRM was selected to provide an

intended level of thennal protection. Figure 1-8 shows the appearance of a floor truss with sprayed

insulation.

Figure 1-8. Photograph of insulated WTC trusses.

Further protection of the building against a fire was provided in part by internal, nonstructural, fire-rated walls. These floor-slab-to-floor-slab partitions, called demising walls, separated the tenant spaces from

each other and from the core area. Their function was to keep a fire from spreading long enough for the

fire to be extinguished. In a 1975 fire in WTC 1, these walls significantly confined the fire.

There were three types of nonstructural walls in the towers. The stairwells and elevator shafts were

surrounded by 2 in. thick, tongue-and-groove, cast gypsum panels, covered with two or three sheets of 5/8

in. gypsum board. The demising walls were made of two sheets of 5/8 in. thick gypsum wallboard on

each side of steel studs. These are often regarded as providing a 2 hour fire separation. Walls in the

interior of the tenant spaces generally extended from the floor slab to the bottom of the drop ceiling and were made of single sheets of 5/8 in. gypsum wallboard over steel studs. These walls were not fire-rated. For some conference rooms and other spaces where sound barriers were desired, the walls extended to bottom of the floor slab above, in which case they were regarded as providing a 1 hour fire separation.

In addition to these methods of passive fire protection, there were components that would be activated in the event of a fire. Automatic fire sprinklers had been installed in all of the office spaces. NIST

The materials used to insulate structural steel are sometimes colloquially referred to as "fireproofmg," referring to the intent of

the material, rather than the property it imparts. Since an important facet of this Investigation was the determination of the sufficiency of the insulation in protecting the steel from the heat of the fires, this report does not pre-judge the quality of the material by using the colloquial term.

12 NIST NCSTAR 1, WTC Investigation
New York City's World Trade Center

calculations showed that the installed automatic sprinkler system was capable of delivering the minimum

required water flow for control of office fires up to 4,500 ft". This was a small fraction of the 40,000 ft" size floors in the towers. In addition, in the stairwells, there were standpipes (for firefighters to connect

their hoses) that were supplied with water by gravity feed from 5,000 gal tanks and by large fire pumps. A

multifunction fire alarm system was intended to alert staff at the Fire Command Station within the building and provide voice and strobe alerts throughout. When turned on after the building had been

cleared of people, a smoke purge system was intended to purge the hot, opaque fire gases from the building.

However, buildings were not (and still are not) required by the building codes or designed to withstand

the impact of a fuel-laden jetliner. Although the impact of a Boeing 707 was stated by the Port Authority

to have been considered in the original design of the towers, only one three-page document, in a format

t>'pically used for talking points was found that addressed the issue. This document stated that such a

collision would result in only local damage and could not cause collapse or substantial damage to the

building. NIST was unable to locate any evidence to indicate consideration of the extent of impactinduced structural damage or the size of a fire that could be created by thousands of gallons ofjet fiiel.

The Workplace

At the beginning of the workday, many of the roughly 40,000 people who worked in the towers and

visited to conduct business or to tour emerged from trains in the massive subterranean station. They

would take escalators and elevators to a one-story shopping mall, then pass through revolving doors to enter a spacious, 6-story-high lobby on the Concourse Level. There, they would cross paths with those

who arrived on foot or by bus or cab.

Getting tens of thousands of people from the Concourse to their offices was no small task. This was

accomplished by a combination of express and local elevators located within each of the building cores (Figure 1-9) that was novel at the fime of construction.

• People traveling to floors 9 through 40 entered a bank of 24 local elevators at the Concourse

Level. These were divided into four groups, with each stopping at a different set of eight or nine floors (9 through 16, 17 through 24, 25 through 31, and 32 through 40).

• Those going to floors 44 through 74 took one of eight express elevators to the 44* floor skylobby before transferring to one of 24 local elevators. These 24 were stacked on top of

the lower bank of 24, providing additional transport without increasing the floor space

occupied by the elevators.

• Those going to floors 78 through 107 took one of 1 1 express elevators from the Concourse

Level to the 78"" floor skylobby before transferring to one of 24 local elevators. These were

also stacked on the lower banks of 24 local elevators.

While providing the desired high rate of people movement, this three-tier system used roughly 25 percent

less of the building footprint than the conventional systems in which all elevators would have run from

the Concourse to the top of the building, resulting in a building core that took up as much as one-half of

the floor area. In addition, there was even more rentable space to be gained. At the top of each elevator

bank, the machinery to lift the cabs occupied one additional floor. From the next floor up to the bottom of

NISTNCSTAR 1, WTC Investigation 13
Chapter 1

the next bank, there was no need for an elevator shaft. The concrete floor was extended into this space, providing additional rentable floor area.

Mechanical Equipment

Room

Skylobby

l\yiechanical Equipment

Room

SI<ylobby

Mechanical Equipment

Room

Express Elevators

Mechanical Equipment

Room

Plaza Level

Local Elevators

Express Elevators

Local Elevators

Figure 1-9. Schematic of the three-tier elevator system.

There were two additional express elevators to the Windows on the World restaurant (and related conference rooms and banquet facilities) in WTC 1 and to the observation deck in WTC 2. There were

also five local elevators: three that brought people from the subterranean levels to the lobby, one that ran between floors 106 and 110, and one that ran between floors 43 and 44 (in WTC 1), serving the cafeteria

14 NISTNCSTAR 1, WTC Investigation
New York City's World Trade Center

from the skylobby. There were also eight freight elevators, one of which served all floors. All elevators

had been upgraded to incorporate firefighter emergency operation requirements.

Also within the core were three sets of stairs that extended nearly the full height of the tower (Figure 1-10). However, the stairwell at an upper

floor did not continuously descend to the lobby, but rather to horizontal

corridors in the vicinity of the mechanical floors. These enclosed

corridors ranged in length from about 10 ft to about 100 ft. (As a result of these and the tiered elevator system, the core arrangements varied

substantially from floor to floor.) After fraversing each of these, the pedestrians would resume their descent, eventually reaching the tower

lobby, from which they could exit the building. The advantages of

moving stairwell locations included reclaiming core space for occupant

use above terminated elevator shafts and overcoming obstructions posed

by equipment installed on mechanical floors.

Upon exiting the elevators or stairs, the interior view was typical of highrise buildings. Surrounding the rectangular core corridor was a mixture

of walls, entry doors to firms, and glass-front reception areas. Above was a drop ceiling.

Many of the floors were occupied by a single tenant. Some of these tenants occupied multiple floors. By

2001, most of these companies had moved in after the installation of automatic sprinklers, which had

allowed the absence of internal partitions. These companies largely took advantage of Yamasaki's design

concept of a vast space that was nearly free of obstructions. The open arrangement often included as many as 200 or more individual modular workstations or office cubicles, generally clustered in groups of

six or eight (Figure 1-1 1 ). Trading floors had arrays of tables with multiple computer screens (e.g.. Figure 1-12, of a trading floor in WTC 4). Some of these floors had a few executive offices in the comers and along the perimeter. Many also had walled conference rooms. It was common for the tenants occupying multiple floors to create openings in the floor slabs and install convenience stairs between their

floors.

Some floors were subdivided to accommodate as many as 20 firms. Some of the smaller firms occupied

space in the core area in the spaces over the elevator shafts.

With thousands of workers and visitors in the buildings, there needed to be food service. The Port Authority maintained a cafeteria on the 43"^ floor of WTC 1. In addition, a number of the companies

maintained kitchen areas on their floors, where catered food was brought in daily, making it unnecessary

for their staff to leave the building for lunch. There was a public cafeteria on the 44"" floor of WTC 1. The visiting public could eat at Windows on the World at the top of WTC 1, at several restaurants on the observation deck of WTC 2, or in the many eateries on the Concourse Level. There were hundreds of

restrooms, in both the tenant and the core spaces.

Following the February

26, 1993, bombing of WTC 1 and in light of the

4 hours needed to evacuate the building,

several improvements

had been made to the

stairwells: battery

operated emergency

lighting, photoluminescent

floor strips indicating the

path to be followed, and

explicit signs on each

doorway to indicate where

it led.

NISTNCSTAR 1, WTC Investigation 15
Chapter 1

16 NISTNCSTAR 1, WTC Investigation
New York City's World Trade Center

NISTNCSTAR 1, WTC Investigation 17
Chapter 1

This page intentionally left blank.

18 NIST NCSTAR 1, WTC Investigation
Chapter 2

The Account of World Trade Center 1

2.1 8:46:30 a m. EOT

On the morning of Tuesday, September 11, 2001, a lot of people were going to be late for work in New

York City, which for many started at 9:00 a.m. or later. It was the first day of school for many local children, and it also was a primary election day in New York. The weather was clear and comfortable

with little wind to speak of, so some took time to do early morning errands. As a result, only about 8,900

of the typical 20,000 people were in World Trade Center (WTC) 1 shortly before 9:00 a.m.

At 8:46:30 a.m. EDT, five hijackers flew American Airlines Flight 1 1 (AA 1 1) with 1 1 crew and

76 passengers into the north face of WTC 1 (Figure 2-1).

[DDI

(CCCDDI 0]

:i::Cddd:3:]

cctoDiiam:

]]:

o::

ii:

im Di:i I

:[:d nmz

'

i[:i[cdd]]]id;ii ;[CD0]]i3;:m

ccnnijii:::!^

tCCDD33]13:i«

:i:c:[Dn3:]ii:ii ::t:cDD]3i]j:B

i:CD D]]l]]IEi3

] 0]]] I

Figure 2-1. Simulated impact of American Airlines Flight 11 with WTC 1.

What follows is the result of an extensive, state-of-the-art reconstruction of the events that accompanied

and followed the aircraft impact. Numerous facts and data were obtained, then combined with validated

computer modeling to produce an account that is believed to be close to what actually occurred.

However, the reader should keep in mind that the building and the records kept within it were destroyed,

and the remains of the towers were disposed of before congressional action and funding was available for

this Investigation to begin. As a result, there are some facts that could not be discerned, and thus there are uncertainties in this accounting. Nonetheless, the National Institute of Standards and Technology (NIST) was able to gather sufficient evidence and documentation to conduct a full investigation upon which to reach firm findings and recommendations. The reconstruction effort, the uncertainties, the assumptions

made, and the testing of these assumptions are documented in Part 11 of this report.

NISTNCSTAR 1, WTC Investigation 19
Chapter 2

2.2 THE AIRCRAFT

The Boeing 767-200ER was a twin-engine, wide-body aircraft, 159 ft 2 in. long, with a wingspan of 156 ft 1 in. Empty, it weighed 183,500 lb. It could

carry 181 passengers in its three-class seating configuration and 23,980 gal

(158,200 lb) ofjet fuel as it covered its maximum cruising range of

6,600 miles. The maximum total weight the plane could carry was specified at 395,000 lb; the typical cruising speed was 530 mph.

On that day, AA Flight 1 1 was much lighter. Bound from Boston for Los

Angeles, some 3,000 miles away, it carried only about half the full load ofjet

fuel. When it hit the north tower, it likely contained about 10,000 gal

(66,000 lb), evenly distributed between the right and left wing tanks. Because

of the tight maneuvers as the plane approached the tower, the baffles in both tanks had directed the ftiel toward the inboard side of each wing. The passenger cabin was more than half empty. The cargo bay,

carrying less than a full load of luggage, contained 5 tons of luggage, mail, electronic equipment, and

food. The total weight of the aircraft was estimated to be 283,600 lb.

2.3 THE IMMEDIATE DAMAGE

The aircraft flew almost straight toward the north tower, banked approximately 25 degrees to the left (i.e., the right wing elevated relative to the left wing) and descended at an angle of about 10 degrees at impact.

Moving at about 440 mph, the nose hit the exterior of the tower at the 96"^ floor. The aircraft cut a gash

that was over half the width of the building and extended from the 93'^'' floor to the 99"" floor (Figures 2-2

and 2-3). All but the lowest of these floors were occupied by Marsh & McLennan, a worldwide

insurance company, which also occupied the 100* floor. Marsh & McLennan shared the 93^^*^ floor with

Fred Alger Management, an investment portfolio management company.

There was relatively little impact damage to the 93"^*^ floor, hit only by the outboard 10 ft of the left wing.

Containing no jet ftiel, the wing tip was shredded by the perimeter columns. The light debris did minimal

damage to the columns or to the thermal insulation on the trusses of the composite floor system

supporting the 94* floor.'' The trusses supporting the 94* floor were impacted by flying debris on the

93'*^ floor.

The 94* floor was more severely damaged. The midsection of the left wing, laden with jet ftael, and the

left engine cut through the building facade, severing 1 7 of the perimeter columns and heavily damaging

four more. The pieces of the aircraft continued inward, severing and heavily damaging core columns.

The insulation applied to the floor trusses above and the columns was scraped off by shrapnel-like aircraft debris and building wall fragments over a wedge almost 100 ft wide at the north face of the tower and

50 ft wide at the south end of the building core.

The 767-200ER

aircraft had two fuel tanks that extended

through most of the

interior of the wings

and a center tank

between the wings

In the bottom of the

fuselage. A full fuel load would have

filled all three tanks.

The reader should bear in mind that the described damage to the building exterior was derived from eyewitness and

photographic evidence. The described damage to the aircraft and the building interior was deemed most likely from the computer simulations and analysis carried out under the Investigation. ,

20 NISTNCSTAR 1, WTC Investigation
The Account of WTC 1

Figure 2-2. Aircraft entry hole on the north side of WTC 1, photographed 30 s

after impact.

The aircraft did the most damage to the 95"' and 96* floors. The fuel-heavy inner left wing hit the 95* floor slab, breaking it over the fiall 60 ft depth of tenant space and another 20 ft into the building core. The fuselage was centered on the 96* floor slab and filled the 95* and 96* floors top to bottom. The

severity of the impact was clear. A wheel from the left wing landing gear flew through multiple

partitions, through the core of the building, and became embedded in one of the exterior column panels on

the south side of the tower. The impact severed the bolts connecting the panel to its neighbors, and the panel and tire landed on Cedar Street, some 700 ft to the south. A second wheel landed 700 ft further south. Within the two floors, 15 to 18 perimeter columns and five to six core columns were severed, and

an additional one to three core columns were heavily damaged. A 40 ft width of the 96* floor slab was

broken 80 ft into the building. TTie insulation was knocked off nearly all the core columns and over a 40

ft width of floor trusses from the south end of the core to the south face of the tower.

NISTNCSTAR 1, WTC Investigation 21
Chapter 2

Figure 2-3. South face damage of WTC 1 with key aircraft component locations marked.

The right wing of the aircraft was fragmented by the perimeter columns on the 97 ' floor. In the process, 12 of those columns were severed. The debris cut a path through the west and center array of trusses and

core columns, stripping the insulation over a 90 ft wide path. The insulation was stripped from a 50 ft wide path on the south side of the floor space.

On the 98"' and 99"^ floors, the outboard 30 ft of the starboard wing was sliced by the perimeter columns,

of which five were severed. The debris cut a shallow path through the west and center array of trusses, damaging the insulation up to the north wall of the building core.

This devastation took 0.7 s. The structural and insulation damage was considerable (Figure 2-4) and was

estimated to be:

• 35 exterior columns severed, 2 heavily damaged.

• 6 core columns severed, 3 heavily damaged.

22 NISTNCSTAR 1, WTC Investigation
The Account of WTC 1

43 of 47 core columns stripped of insulation on one or more floors.

Insulation stripped from trusses covering 60.000 ft' of floor area.

Severe Floor Damage

Fireproofing and I I partitions on floor '—

'

Floor system i—

>

structural damage | | Floor system

removed

Column Damage

Severed ^)

Heavy damage Q

Moderate damage Q

Light damage

112 115 118 121 124 127 130 1 33 136 139 142 145 148 151 154 157 la

0 S>^^ "J>7

9^-: Qft^ i 608'

902 i,C.> W-C:. 906 907

1002 1003 1004 1005 1006 1007

TTT

9081

y—^

I I

3:13 330 327 324 321 318 315 312 309 306 303 301

Figure 2-4. Simulation of cumulative aircraft impact damage to floors 93 through 98

in WTC 1.

Even with all this damage, the building still stood. The acceleration from the impact had been so severe

that people even on lower floors were knocked down and furniture was thrown about. Some survivors

reported fallen ceiling tiles throughout the building, all the way down to the Concourse Level. The pipes

that fed the automatic fire sprinkler system were severed. At least 166 windows were broken. Damage to

interior walls was reported from the Lobby to the 92"'' floors. However, the building was designed with

reserve capacity: it could support significantly more load than the weight of the structure and its people

and contents. The building redistributed the load from the severed perimeter columns, mainly to their neighboring columns. The undamaged core columns assumed the remaining load, as well as the load

from their damaged neighbors. WTC 1 still stood, and would have continued to do so, if not for the fires that followed.

NIST could not determine how many occupants were in the path of the aircraft as it entered the tower. Those in the direct collision path were almost certainly killed instantly. Many more would have lost their

lives from the burst of heat from the burning jet fuel. Fatal injuries were reported on floors as low as the Concourse Level, where a fireball swept through the lobby.

NISTNCSTAR 1, WTC Investigation 23
Chapter 2

In the impact region was further damage that would cost the lives of all the 1,355 people from the 92

floor to the 1 10''^ floor. The crash and flying debris had collapsed the walls of all three stairwells and

interrupted all elevator service to the upper 60 floors. All opportunity for escape had been eliminated.

To the wings of the 767-200ER, the perimeter columns acted like knife blades, slashing the aluminum

fuel tanks and atomizing much of the 10,000 gal ofjet fuel liquid into a spray of fuel droplets. Atomized

jet fuel is highly flammable (similar to kerosene), so both the hot debris and the numerous pieces of

electrical and electronic gear in the offices were more than sufficient as ignition sources. A surge of

combusting fuel rapidly filled the floors, mixing with dust from the pulverized walls and floor slabs. The

pressure created by the heated gases forced the ignited mist out the entrance gash and blown-out windows

on the east and south sides of the tower. The resulting fireballs could be seen for miles, precipitating

many 9-1-1 calls.

Less than 15 percent of the jet fuel burned in the spray cloud inside the building. A roughly comparable

amount was consumed in the fireballs outside the building. Thus, well over half of the jet fuel remained

in the building, unbumed in the initial fires. Some splashed onto the office furnishings and combustibles

from the aircraft that lodged on the impacted floors, there to ignite (immediately or later) the fires that would continue to bum for the remaining life of the building. Some of the burning fuel shot up and down

the elevator shafts, blowing out doors and walls on other floors all the way down to the basement. Flash

fires in the lobby blew out many of the plate glass windows. Fortunately, there were not enough

combustibles near the elevators for major fires to start on the lower floors.

The burning of the jet fuel cloud had consumed much of the oxygen within the 94 and 96 floors,

although photographs showing survivors indicated there were some zones with breathable air. The

oxygen-starved fires died down, but didn't quite go out. Within the first 2 min after the impact, fires could be seen in the north side windows on the 93"^ through 9?"^ floors, the 96"^ floor of the south face,

and the 94"^ floor of the east face. As fresh air entered the perforated facades, there began the steady

burning of the office furnishings and the 1 3 tons of combustibles from the aircraft that would eventually

overwhelm the already damaged building. By 9:00 a.m., these fires had grown and spread to the extent shown in Figure 2-5. In addition to burning around the aircraft entrance hole, there was intense burning on the north, east, and west faces of the 97"' floor. Large fires burned on the south side of the 96'*^ floor and the east side of the 94* floor. At 8:52 a.m., a stream of smoke emerged from the south side of the

1 04''^ floor, although there was no evidence of a significant fire there yet.

There was no way to fight the fires. The piping providing the water supply to the automatic sprinklers

had been broken, and water was flowing down the stairwells. Even had this not happened, the system was designed to supply water to about 8 sprinkler heads at one time, enough to control the flames from as much as 1,500 ft" of burning material. The water supply was likely sufficient to control fires up to triple that size. The fires, however, had already grown far larger than that.

2.4 THE JET FUEL

2.5 8:47 A.M. TO 9:02 a.m. EDT

24 NISTNCSTAR 1, WTC Investigation
The Account of WTC 1

WTC 1 , North Face 8:47 a. m. to 9:00 a.m. WTC 1 , East Face 8:48 a.m. to 9:02 a.m.

WTC 1 , South Face 8:47 a.m. to 9:02 a.m. WTC 1 , West Face 8:47 a.m. to 9:02 a.m.

Note: Color coding—white, no fire; yellow, spot fire; red, fire visible inside; orange, external flaming.

Figure 2-5. Representation of exterior views of the fires on the four faces of WTC 1 from 8:47 a.m. to about 9:02 a.m.

There was also no way to abate the opaque, hot, and toxic smoke that quickly began accumulating. The

manually activated smoke purging system was intended for smoke removal during fire department

operations following a fire. Thus, it was not turned on during the 102 min that the tower would remain

standing. It would not likely have helped anyway. Neither the World Trade Center Safety Director nor

the arriving firefighters knew where the fires were located, so they could not have known how to direct the intake and exhaust flows. Furthermore, the integrity of the vent shafts on the upper floors had been

compromised by the aircraft impact, making it unlikely that the system could have functioned as intended.

Most of the people in WTC 1 were aware of the possibility of an emergency. A quarter of them had been

working in the building since before the 1993 bombing, and most of those had been in the building on

that day. Half the people had been working in the building for at least two years; many had heard the

stories and had participated in the emergency drills.

The building occupants knew that something serious had happened. A third of the survivors had heard

the roar of the plane. Nearly two thirds reported feeling the violent movement of the building. Half

sensed that they were in a life-threatening situation. At the Concourse Level, a fatal fireball filled the space from the elevators to the exit toward WTC 3. Almost immediately, people began calling 9-1-1,

both for help and to find out more about what was going on.

Within 5 min to 8 min of the strike, most of the 7,545 people below the floors of impact began to evacuate. Their progress is tracked in Table 2-1 . Water and debris were in the three stairwells. The air smelled ofjet fuel and was becoming gray with smoke and pulverized gypsum, thermal insulation, and

NISTNCSTAR 1, WTC Investigation 25
Chapter 2

concrete. Nonetheless, perhaps due to the guidance they had received since the 1993 bombing, for the most part the people moved in an orderly maimer down the stairs, helping those who needed assistance.

Within 1 5 min of the strike, nearly all of the people below the impact floors had descended about

10 floors from their original location.

Table 2-1 . Locations of occupants of WTC 1

.

Time Evacuated Lobby to 91" Floor 92"" to no*" Floor

8:46 0 7,545 1,355

9:03 1,250 6,300 1,355

9:59 6,700 850 1,355

10:28 7,450 107 1,355

Note: The numbers in the rows do not add to the estimated total of 8,900 due to rounding errors in the less certain values.

At the time, there were some survivors from the 92"'' through 99^' floors. Most of those who were able moved to the areas where the fires had not

yet spread. Some were seen looking out from the former window spaces

and even standing on the defonned structural steel. At 8:52 a.m., the first of at least 1 1 1 people was observed falling from the building.

Hundreds of people were on the floors above the impact zone. They soon

realized that they were unable to go downward to get away from the smoke and heat that were building up around them. At 8:54 a.m., occupants began breaking windows to provide access to fresh air. By

9:02 a.m., 26 calls, representing hundreds of people, had been made to 9-1-1, asking for help and seeking more information about what was

happening. Some of the people went toward the roof. However, there was no hope because roof evacuation was neither planned nor practical,

and the exit doors to the roof were locked.

Outside the building, a flurry of activity was beginning. Personnel of the Fire Department of the City of

New York (FDNY) were several blocks away, investigating a gas leak at street level, and observed the

aircraft impact. Within a minute, FDNY had notified its communications center and requested additional

alarms for the WTC. A Port Authority Police Department (PAPD) unit had reported to its Police Desk

that there had been an explosion with major injuries. By 8:50 a.m., the first fire engines had arrived, and

an Incident Command Post had been established in the WTC 1 lobby. An Emergency Medical Service

(EMS) Command was established 3 min later. More and more reports of damage, injuries, and deaths

flooded the communications channels, and knowledge of the extent of the catastrophe was emerging. At

8:52 a.m., the first New York City Police Department (NYPD) aviation unit arrived to evaluate the

possibility of roof rescue, but reported they were unable to land on the roof due to the heavy smoke. At

8:55 a.m., the firefighters entering WTC 1 began climbing the stairs (Figure 2-6). Their objectives were

to evacuate and rescue everyone below the fires, then to cut paths through the fires and rescue all those

above the fires.

At 8:59 a.m., a senior PAPD official called for evacuation of the entire WTC complex, although that call was not heard nor heeded by others. By 9:00 a.m., 66 FDNY units had been dispatched to the scene, and

While the occupants were

not advised in advance

that roof evacuation was

not a viable option, there was, and is, no

requirement in the NYC

Building Code for the roof

to be accessible for emergency evacuation or rescue, and roof rescue was not contemplated in the WTC evacuation

plans. Even had the roof been accessible, the

helicopters could not have

landed due to the severe

heat and smoke.

26 NISTNCSTAR 1, WTC Investigation
The Account of WTC 1 \ © Goldfish Pic:l

Figure 2-6. Firefighters on the scene at about 9:07 a.m.

the FDNY had called a fifth alarm for the dispatch of additional department personnel and equipment to the WTC. Spectators had begun converging on the complex, but were advised to stand clear.

The aircraft impact also did damage to the communications in the tower. The capability for buildingwide broadcast from the Fire Command Desk was knocked out. Emergency responder radio traffic peaked at about five times its normal traffic volume during the 20 min period after to the attack. This

peak gradually tapered off, but still continued at a sustained level three times the normal traffic volume.

The radio systems were not adequate to handle the high flow of emergency communications required for

this scale of operations. Many of the radio messages were unintelligible because many individuals were

trying to talk on the same radio channel at the same time.

At 9:02:59 a.m., five hijackers flew United Airlines Flight 175 with 9 crew and 51 passengers into the

east side of the south face of WTC 2. For the most part, there was little awareness of this among the people below the 92"'' floor of WTC 1 . Almost one-fifth of these had already left the building, and nearly

all the 6,300 others were already in the stairwells.

A fire needs a continuing supply of both gaseous fuel and oxygen to keep burning, and the initially

burning combustibles in WTC 1 were being consumed. The additional fuel came from the office

furnishings next to those that were reaching the end of their burning life. The themial radiation from the flames and from the hot gases heated the nearby combustibles, creating flammable vapors. These vapors

needed a source of nearby air to continue the burning. The same flames and hot ceiling layer gases heated

the windows and window frames in the vicinity. The hot gases pushed on the weakened aluminum

NISTNCSTAR 1, WTC Investigation 27

2.6 9:02:59 a.m. EDT

2.7 9:03 A.M. TO 9:57 a.m. EDT
Chapter 2

frames, sending some windows outward to fall to the Plaza below. Other windows were sucked into the

building. The fires now had both new fuel and fresh air.

And so the fires continued to spread, likely aided by as-yet unbumed jet fuel that had soaked into some of

the furnishings and flooring. The coating of (non-combustible) gypsum and concrete fragments slowed

the burning rate by as much as half, but could not halt the fire from spreading. The overall movement of

the fires was toward the south side of the tower. By 9:15 a.m., the fires on the 97* floor had intensified

and filled most of the fioor. Large fires had erupted on the east sides of the 92"'' and 96"^ floors.

Seventy-five minutes after the impact, approaching 10:00 a.m., the fire on the 97"" floor had begun to bum

itself out, but the fire on the 94* floor had intensified and filled much of the north half of the floor (Figure 2-7). Starting about 9:30 a.m., there were vigorous fires on nearly the full perimeter of the

98* floor. There was still almost no burning on the 99* floor or above.

WTC 1 , North Face 9:38 a. m. to 9:58 a.m. WTC 1 , East Face 9:38 a.m. to 9:58 a.m.

WTC 1 , South Face 9:38 a.m. to 9:58 a.m. WTC 1 , West Face 9:36 a.m. to 9:58 a.m.

.159 555 aSO 340 3^5 'Ao 325 320 J15 310 305 3D1 455* 45'"' 450 445 vlo 435 i^Cl 12:" -520 J15 410 405 4D1 Note: Color coding—white, no fire; yellow, spot fire; red, fire visible inside; orange, external flaming.

Figure 2-7. Representation of exterior views of tlie fires on tlie four faces of WTC 1 from

about 9:38 a.m. to 9:58 a.m.

The hot smoke from the fires now filled nearly all the upper part of the tenant space on the impact floors. Aside from isolated areas, perhaps protected by surviving gypsum walls, the cooler parts of this upper

layer were at about 500 °C, and in the vicinity of the active fires, the upper layer air temperatures reached

1,000 °C. The aircraft fragments had broken through the core walls on the 94* through the 97* fioors,

and temperatures in the upper layers there were similar to those in the tenant spaces.

28 NISTNCSTAR 1, WTC Investigation
The Account of WTC 1

The perimeter columns, floors, and core coluinns were immersed in these hot gases and began to weaken.

Where the insulation was dislodged, the temperature of the steel rose rapidly, in contrast to steel members

where insulation was intact (Figure 2-8). The heaviest core columns with damaged insulation heated

slowly, as the absorbed heat was dissipated through their massive cross sections. The temperatures of the

lighter columns and the floor slabs rose more quickly, and those of the stripped trusses even more so.

Figure 2-8. Steel

surface temperatures on

the bottom chords of

fire-exposed trusses,

uninsulated and

insulated with Y4 in. of

BLAZE-SHIELD DC/F.

0 10 20 30 40 50

Time (min)

As a steel column is heated, its ability to support gravity loads and resist

lateral loads decreases. At temperatures of about 300 °C, steel loses about

20 percent of its yield strength (Figure 2-9). Under modest loads, steel is elastic, that is, it can compress, or shorten, but will recover when loads are removed. As the load increases, the steel becomes plastic, and the shortening is unrecoverable. At still higher loads, the column buckles. At

temperatures above 500 °C, the steel further weakens, the loss of strength

and stiffness become significant, and the column's ability to carry its share

of the building loads decreases. It shortens due to a combination of plastic

deformation and an additional, time-dependent defonnation called creep that can increase column

shortening and hasten buckling. Figure 2-10 indicates the rates at which structural steel could have been

heated by the WTC fires and the effect of the thermal insulation in slowing the heating process.''

At this point, the core of WTC 1 could be imagined to be in three sections. There was a bottom section

below the impact floors that could be thought of as a strong, rigid box, structurally undamaged and at almost normal temperature. There was a top section above the impact and fire floors that was also a heavy, rigid box. In the middle was the third section, partially damaged by the aircraft and weakened by

heat from the fires. The core of the top section tried to move downward, but was held up by the hat truss. The hat truss, in turn redistributed the load to the perimeter columns.

Structural steels do not need to melt to lose

strength. Their melting

points are about

1 ,600 °C, well above

the 1,100 °C typical

peak value reached by

fires of common

building combustibles.

* Chapter 6 contains an explanation of how these temperature profiles were developed.

NIS T NCSTAR1. WTC Investigation 29
Chapter 2

Figure 2-9. Temperature dependence of

yield strength of structural steel as a

fraction of the value at room temperature.

800

1000 -

3000 4000 Time (s) 6000

Note: The red data are for structural steel components without insulation; the blue data are for steel components that are still insulated. Figure 2-10. Simulated temperatures of two adjacent trusses (left) and two adjacent

perimeter columns (right) exposed to the fires in WTC 1.

Simultaneously, the fires were creating another problem for the tower. The floors of the 93'^'' through the

97"' stories were being heated both by the hot gases from below and by thennal radiation from the fires on

the floor above (Figure 2-1 1). On the south side of the building, where the fires were heating the longspan trusses whose SFRM had been dislodged, the floors began to sag. In so doing, they began pulling

inward on their connections to the south face and to the core columns. Pull-in forces due to the sagging

floors did not fail the floor connections in most areas.

30 NISTNCSTAR 1. WTC Investigation
The Account of WTC 1

Top surface Bottom surface

Figure 2-11. Temperature contours {°C) on the top and bottom faces of the concrete slab

(96'^ floor, WTC 1) at 100 min after impact. A portion of the concrete slab on the north

face (top) was damaged by the impact of the aircraft.

Meanwhile, the occupants from below the impact floors were moving steadily down the stairs at roughly

a floor per minute. Although they encountered firefighters climbing upward, this did not slow the downward progress much. Within 75 min of the impact, 90 percent of the people who would survive had

left WTC 1 . At 9:37 a.m., a Port Authority official instructed all units to direct the evacuees over the bridge on West Street to the Financial Center. However, this change in evacuation route actually began w ith the collapse of WTC 2.

Conditions on floors 92 and above continued to deteriorate. The presence of the fires and the resulting

high smoke and radiant heat levels made the 92"'' floor through the 99"' floor uninhabitable except in small areas. Above the impact zone, there were only seven calls to 9-1-1 between 9:03 a.m. and

9:10 a.m.; and then, more than a half hour later, three last calls from floors 104 and 105 between

9:43 a.m. and 9:57 a.m. More people jumped through windows they broke or that had been broken by the

fires.

By 9:15 a.m., 30 FDNY units had signaled their arrival, and by 9:59 a.m., the number had grown to 74. They had been told to stop short of the site because of the large number of ambulances already there and the debris

falling from the buildings. Many of the firefighters proceeded into WTC 1

.

Once inside, they found that only one of the 99 upward elevators was

working, one that went as far as the 16"^ floor. Most of the firefighters then

proceeded to ascend the three stairways, intending to help evacuate the occupants, cutting paths through the fires as necessary. Because the

firefighters were carrying as much as a hundred pounds of bulky firefighting gear, their progress was slow and was impeded by the flow of evacuees coming down the stairs. A few reached as high as floors in the 40s and 50s.

Since the Command

Boards were

destroyed in the

collapse, it is unknown

just how many

firefighters went into WTC 1 , when they

went in, or, In most

cases, what level they

reached.

NISTNCSTAR 1, WTC Investigation 31
Chapter 2

2.8 9:58:59 a.m. EDT

With no warning that could be discerned in WTC 1 , WTC 2 collapsed. The shudder as the more than

250,000 tons of steel, concrete, and furnishings hit the ground was felt well beyond the site. Seismic

sensors located 100 miles away recorded the time and intensity of the event.

The gigantic concussion was felt by some of the nearly 800 people still in the stairwells in WTC 1. The

evacuation rate slowed to half its prior level as a new cloud of dust, smoke, and debris filled the

Concourse and the stairwells, and the lights went out. Higher up, no more calls to 9-1-1 originated from

above the 9 r' floor. .

At 10 a.m., NYPD and FDNY ordered all emergency responders out of WTC 1 and away from the WTC

site.

2.9 9:59 a.m. TO 10:28 a.m. EDT

For the next half hour, the last 690 of the eventual survivors worked their way down the last flights of stairs, across West Street to the west and

across Vesey Street to the north and to safety. By 10:28 a.m., all but 107

of the roughly 7,500 people who had been below the impact floors were

able to escape.

Having heard over their radios the orders that they should evacuate, some

of the responders inside the tower headed down the stairwells and out of

the building, telling their comrades on the way. Others did not, having not received the message, having climbed too high to now get out in time, or continuing on the missions to help others still in the building.

A pressure pulse generated by the collapse of WTC 2 appeared to intensify

the fires in WTC 1 . Within 4 s of the collapse of WTC 2, flames burst

from the south side windows of the 98"^ floor. The fires on the north faces of the 92"'', 94'", and 96'" floors brightened noticeably. Flames near the south end of the east face of the 92"'' and 96"' floors also flared. The fires on the east and south faces of the 98"' floor already extended out the windows. Those in the WTC 1 stairwells felt a gush of wind.

At 10:01 a.m., flames began coming out of the south side of the west face of the 104"' floor, three floors higher than any floor where fire had been previously observed and five floors above the highest floor with

a major fire. After a rapid growth period, this fire burned intensely up to the time the tower collapsed.

By 10:18 a.m., a substantial pressure pulse inside the building ejected jets of smoke from the 92"'^ and 94''' through 98"' floors of the north faces and the 94"' and 98"' floors of the west face. Fires raged on the south

side of the 96"' through 99"' floors.

The sagging of the floors had increased. Although the floors on the north side of the tower had sagged

first, they contracted due to cooling when the fires moved toward the south. Now, the south side floors had sagged to the point where the south perimeter columns bowed inward (Figure 2-12). By 10:23 a.m., the south exterior wall had bowed inward as much as 55 in.

At 10:06 a.m., an NYPD

aviation unit advised that WTC 1 would conne down and that all emergency vehicles

should be moved away

from it. At 10:20 a.m., observers in NYPD

helicopters said that the

top of the building was

leaning; and at 10:21 a.m., they said

that WTC 1 was buckling on the southwest corner and leaning to the south.

32 NISTNCSTAR 1, WTC Investigation
The Account of WTC 1

Note: Enhanced by NIST. Figure 2-12. South face of WTC 1 at 10:23 a.m., showing inward bucl<ling (In inches) of

perimeter columns.

The tower was being overwhelmed. Three of the four major structural systems—the core, the floors, and

the perimeter walls—were weakening. The south wall became unstable and tried to transfer its remaining

load to the weakened core via the hat truss and to adjacent perimeter columns via the spandrels. The

entire section of the building above the impact zone began tilting as a rigid block toward the south. The

upper section of the building then collapsed onto the floors below. Within 12 s, the collapse of WTC 1 had left nothing but rubble.

NISTNCSTAR 1, WTC Investigation 33
Chapter 2

2.10 THE OUTCOME

Seven major factors led to the collapse of WTC 1

:

• Structural damage from the aircraft impact;

• Large amount ofjet fuel sprayed into the building interior, that ignited widespread fires over

several floors;

• Dislodging of SFRM from stmctural members due to the aircraft impact, that enabled rapid

heating of the unprotected structural steel;

• Open paths for fire spread resulting from the open plan of the impact floors and the breaking

of partition walls by the impact debris;

• Weakened core columns that increased the load on the perimeter walls;

• Sagging of the south floors, that led to pull-in forces on the perimeter columns; and

• Bowed south perimeter columns that had a reduced capacity to carry loads.

After the building withstood the initial aircraft damage, the timing of the collapse was largely determined

by the time it took for the fires to weaken the core and to reach the south side of the building and weaken

the columns and floor assemblies there.

There were no survivors among the 1,355 people who were on or above the 92"'' floor. The aircraft had

destroyed all egress paths downward, and roof rescue was impossible.

Of the roughly 7,545 building occupants who started that morning below

the 92"'' floor, all but 107 escaped the building. Those left behind were

trapped by debris, awaiting assistance, helping others, or were just too late in starting their egress. For the most part, the evacuation was steady and

orderly.

Six percent (almost 500) of the survivors from WTC 1 had a limitation that impaired their ability to evacuate. Many of these were able to evacuate,

often with assistance; others were less fortunate. About 40 to 60 mobilityimpaired occupants were found on the 12"' floor, where they had been

placed in an attempt to clear the stairways. Just before the collapse of

WTC 1, emergency responders were assisting about 20 of these people down the stairwell. It remains

unclear how many of these people survived.

Those emergency responders who entered the building and the emergency personnel who were already in the building were helpful in assisting the evacuation of those below the impact floors. However, there was insufficient time and no path to reach any survivors on the impact floors and above. Any attempts to mitigate the fires would have been fruitless due to the lack of water supply and the difficulty in reaching

the fire floors within the time interval before the building collapse. It is not known precisely how many

Had the building been

significantly more than

one-third to one-half

occupied, the casualties

would likely have been

far higher, since the

exiting population would

have exceeded the

capacity of the stairwells

to evacuate them in the

time available.

34 NISTNCSTAR 1, WTC Investigation
The Account of WTC 1

emergency responders entered the building nor how many of the 421 responder casualties occurred in WTC 1. NIST estimated that approximately 160 FDNY fatalities occurred outside the WTC towers.

NISTNCSTAR 1, WTC Investigation 35
Chapter 2

This page intentionally left blank.

36 NISTNCSTAR 1, WTC Investigation
Chapter 3

The Account of World Trade Center 2

3.1 8:46:30 a m. EOT

The nature of the events leading to the collapse of World Trade Center (WTC) 2 had a number of

important features distinct from those of WTC 1 . Those contrasts led to a larger overall fraction of the occupants surviving despite the building collapsing in a shorter period. As was the case with WTC 1, what follows is the result of an extensive, state-of-the-art reconstuiction of the events that accompanied

and followed the aircraft impact. Numerous facts and data were obtained, then combined with validated

computer modeling to produce an account that is believed to be close to what actually occurred. The

reader should again keep in mind that the building and the records kept within it were destroyed and the remains of the towers were disposed of before this Investigation began. As a result, there are some facts that could not be discerned, and there are uncertainties in this accounting. Nonetheless, the National

fristitute of Standards and Technology (NIST) was able to gather sufficient evidence and documentation

to conduct a full investigation upon which to reach firm findings and recommendations. The

reconstruction effort, the uncertainties, the assumptions made, and the testing of these assumptions are documented in Part II of this report.

The ordeal for the occupants of WTC 2 began at the same time as it did for those in WTC 1 , when

American Airlines (AA) Flight 1 1 struck WTC 1 at 8:46 a.m. Nearly all of the roughly 8,600 people in WTC 2 were well aware that something serious had occurred in the other tower. Half the people heard

the terrible sound of the aircraft hitting WTC 1 , just a few hundred feet away. One-fifth of the people saw

the flames, smoke, or the debris ejected from the south side of WTC 1, over 10 percent felt WTC 2

moving, and another fifth in WTC 2 were quickly alerted to the seriousness of what had happened by

co-workers, phone calls, or the morning news. Over half believed they were personally at risk.

Many began talking to each other, gathering personal items, and helping others. Fortunately, they began

to get out of the building. Within 5 min, half the people had left their floor, and that fraction grew

rapidly. About one-sixth used the elevators, with more of these people starting on the higher floors. The

remainder divided themselves evenly among the three stairways. NIST estimated that approximately

3,000 people escaped because of the actions they took in the 16 min following the aircraft impact on WTC I, especially their use of the elevators.

At 9:00 a.m. came the first building-wide public address system announcement that there was a fire in WTC 1, that WTC 2 was secure, and that people should return to their offices. This added confusion to an already tense situation, a situation that became even more turbulent when at 9:02 a.m., a contradictory

announcement said that people may wish to start an orderly evacuation if conditions on their floor warranted.

NISTNCSTAR 1. WTC Investigation 37
Chapter 3

3.2 9:02:59 a.m. EDT

Sixteen and a half minutes after the first impact, five hijackers flew United AirHnes (UA) Flight 175, with

9 crew and 5 1 passengers, into WTC 2 at about 540 mph, about 100 mph faster than AA Flight 1

1

(Figure 3-1). UA 175 was also a Boeing 767-200ER and had also left Boston, bound for Los Angeles. It flew into WTC 2 carrying about 9,100 gal (62,000 lb) ofjet fiiel, evenly distributed between the inboard

portions of the left and right wing tanks. The cargo bay held about 9 tons of luggage, mail, electrical equipment, and food. Combining this with the combustible cabin materials and luggage, the plane

brought about 1 4 tons of solid combustibles into the tower with it.

Figure 3-1. Imminent impact of United Airlines Flight 175 with WTC 2.

3.3 THE IMMEDIATE DAMAGE

The aircraft completely disappeared into the building in a fifth of a second. In response to the force of the

collision, the top of the tower swayed 27 in. to the north, taking 2.6 s to reach the maximum

displacement. UA Flight 175 was heading approximately 15 degrees east of Plan North^ when it hit the

south face of WTC 2 about 23 ft east of the center. The off-center impact twisted the upper part of the tower in a counterclockwise movement. The building vibrated in the north-south direction, along with a

twisting motion, with the amplitude decreasing steadily with each oscillation.

The center of the nose of the plane struck at the 81" floor slab. The plane was banked 38 degrees to the

left (right wing upward) and was heading slightly (6 degrees) downward from the horizontal. Since the

^ Plan North was approximately 29 degrees clockwise from True North.

38 NISTNCSTAR 1, WTC Investigation
The Account of WTC 2

bank angle was steeper than that of AA Flight 11, this entry wound stretched over nine floors, from 77 to 85, rather than eight in WTC 1 (Figure 3-2). The occupancy of those floors is shown in Table 3-1.

Damage in shaded area cannot be accurately determined Figure 3-2. South face damage of WTC 2 with key aircraft component locations marked.

Table 3-1 . Tenants on impact floors in WTC 2. Floors Tenant Business

85 Harris Beach Legal

84 Eurobrokers Brokerage

83 Mitsui; IQ Banking; Financial Software

79 through 82 Fuji Bank Banking

77 and 78 Baseline Investment Services

The bulk of the impact damage was confined to six floors. Figure 3-3 shows the combined damage.

Floors 77, 84, and 85 were struck only by the outer extent of the wings. Empty of fuel, the light framing

NISTNCSTAR 1, WTC Investigation 39
Chapter 3

and aluminum sheet of the wing did Uttle damage to the building structure or the SFRM on the columns

and trusses on these floors. There were 433 broken windows on the north, east, and south facades.

201 203 20e 209 212 215 216 221 224 227 230 233 236 239 242 245 24a 251 254 257 259

Severe Floor Damage

Fireproofing and I I partitions on floor '—

Floor system .—

.

structural damage | | Floor system

removed

Column Damage

Severed Q

Heavy damage Q

Moderate damage Q

Light damage

TTTTT'I 459^7 454 451 446 445 442 439 436 433 430 427 424 421 418 415 412 409 406 403 401 Figure 3-3. Simulation of aircraft impact damage to the 78"" through 83"^° floors in WTC 2.

The middle of the left wing hit the 78* floor, severing nine perimeter columns and breaking 19 windows

on the south face. The SFRM was stripped from the floor trusses over the same width as the building

core. The stripping of insulation from the trusses continued inward across the tenant space and about two

thirds of the way into the core. There was no direct core column damage from the debris on this floor. However, the southeast comer core column was so damaged on the 80"' floor that it broke at its splices on

the 77* and 83''' floors.

>rd

There was heavier damage to the 79* floor. The left engine and the inboard section of the left wing

shattered a 25 ft wide section of the center of the floor slab all the way to the core of the building and

severed 15 perimeter columns. Reaching the building core, the debris severed nine columns, heavily

damaged another, and abraded the SFRM from the eastern two thirds of the columns and trusses all the

way to the north end of the core.

The damage was most severe on the 80* and 81" floors, hit directly by the fuselage. On the lower floor, a chunk of the floor slab was broken, just above the affected piece of the 79"^ floor. In addition, a 70 ft deep strip along the east side of the core floor was crushed. The north side floor slab sagged along its eastern end. Ten of the perimeter columns severed on the 79* floor were displaced here also. Within the building core, ten columns were severed, including many that were severed on the 79* floor. The SFRM

was stripped not only from the eastern two thirds of the core structural elements, nearly to the north wall,

but also from most of the trusses on the east tenant space, all the way to the north fa9ade.

40 NISTNCSTAR 1, WTC Investigation
The Account of WTC 2

On the Sr' floor, the fuselage pulverized a section of the floor 40 ft wide that extended into the southeast comer of the core. The SFRM and gypsum fire protection on the full depth of the east side of the core and in the entire east side of the tenant space was stripped. The structural damage to the core columns was limited to near the southeast comer, but as mentioned above, the impulses felt here caused damage to the key comer column all the way down to the 78"" floor. The right engine passed all the way through the Sr' floor, exited from the northeast comer, and damaged the roof of a building on Church Street, before

coming to rest some 1,500 ft northeast of WTC 2 near the comer of Murray and Church Streets. The right

landing gear assembly passed through the ST' floor at the east side of the north face and landed near the engine on the roof of a building on Park Place. (See Figure 1-1 for the street locations relative to the towers.)

The right engine hit the 82'"* floor spandrels about 50 ft from the east edge of the building, cmshing part

of the 82"'' floor slab. Along with the inboard section of the right wing, it severed eight to nine perimeter

columns, including some to the east of those severed on the lower floors. The wing caused tmss damage

up to the southeast comer of the core and severed five columns. As on the 8r' floor, the fire protection on the east side of the tenant space and the east side of the core was dislodged.

The 83"* floor caught the middle of the starboard wing. The east side floor slab appeared to be dislodged

and sagged at least half of the way into the building.

The result of the core column damage was that the building core leaned slightly to the southeast above the impact zone. The tendency of the core to lean was resisted by the floors and the hat tmss.

The direct impact of the aircraft was over in about 0.6 s. The stmctural and insulation damage, summed

over all floors, was estimated to be:

• 33 exterior columns severed, 1 heavily damaged.

• 10 core columns severed, 1 heavily damaged.

• 39 of 47 core columns stripped of insulation on one or more floors.

• Insulation stripped from tmsses covering 80,000 ft" of floor area

The tower swayed more than one foot back and forth in each direction on the impact floors, about onethird the sway under the high winds for which the building was designed. Nonetheless, just like WTC 1 across the Plaza, WTC 2 absorbed the aircraft strike and remained standing.

By 9:03 a.m., most of the people in WTC 2 had already left their usual work floors. Nearly 40 percent of

all the occupants had left the building, (Table 3-2), and 90 percent of those who would survive had begun

their evacuation. Many of those still on the east side of the impact floors were likely killed or seriously

injured by the impact. The same was true for many of those on the 78"' floor skylobby, who were

deciding on a course of action, waiting for the express elevators to transport them to the ground floor, or attempting to return to their offices. Those on the west side of the building were less seriously affected. In calls to 9-1-1, they reported fallen ceiling tiles, collapsed walls, jet fuel, heat, smoke, and fire.

NISTNCSTAR 1, WTC Investigation 41
Chapter 3

Table 3-2, Location of occupants of WTC 2. Time Escaped LODDy 10 /o rioor / / to 1 iU r loor

8:46 0 5,700 2,900

9:03 3,200 4,800 637

9:36 6,950 1,050 619

9:59 8,000 11 619

Note: The numbers in the rows do not add to the estimated total of 8,600 occupants due to rounding in the less certain values.

This aircraft had also severed the pipes that fed the automatic sprinklers and

destroyed all elevator service to the impact floors. But, unlike AA Flight 11,

the off-center strike of UA Flight 1 75 had left one of the three stairways

passable, Stairway A on the north side of the building core.

When the aircraft struck WTC 2, emergency responders had already been

dispatched to the WTC site, and the initial surge of emergency responder radio

had subsided to a level approximately three times that of normal operations.

However, the radio traffic volume was still at a level where approximately

one-third to one-half of the radio communications was not understandable.

3.4 THE JET FUEL

Within about one half of a second, dust and debris flew out of windows on the east and north faces. Several small fireballs of atomized jet fuel burst from windows on the east face of the 81^' and 82"'* floors,

coalescing into a single, large fireball that spanned the entire face. A tenth of a second later, fire appeared

in the dust clouds ejected from the south face of the 79*, 81^', and 82"'' floors. Almost simultaneously,

three fireballs came from the east side of the north face. The largest came from the 80* through 82"''

floors. A second, somewhat smaller one came from the same floors on the northeast comer of the

building. The smallest emerged from the 79* floor. No dust or fireballs came from the west face.

As in WTC 1, less than 15 percent of the jet fuel burned in the spray cloud inside the building. Roughly

10 percent to 25 percent was consumed in the fireballs outside the building. Thus, well over half of the

jet fuel remained after the initial fireballs.

The rapid burning of the jet fuel inside the building created an overpressure that was estimated at 2 psi to 3 psi for 0.5 s to 2 s. For a window and frame of over 10 ft", this amounts to over 3,000 pounds of force, more than enough to break windows. Photographs of the north and east faces appeared to show hanging

floor slabs where the fireballs had been ejected from the building. Based on the failure of the truss seat connections, NIST estimated that the static capacity of an undamaged floor was 4.8 psi against uplift pressure and 4.4 psi against downward pressure over the entire floor. It is not unreasonable that a combination of physical damage from the impact and overpressure from the fireballs caused the partial

collapse of these floor slabs.

3.5 9:03 a.m. TO 9:36 a.m. EDI

The fireballs burned for 10 s, extending almost 200 ft out from the north, east, and south faces. Having

consumed the aerosol fuel, the flames then receded.

Stairwell A remained

passable because It was well west of the

aircraft strike center and partially

protected by

elevator machinery

and the long

dimension of the

building core.

42 NIST NCSTAR t WTC Investigation
The Account of WTC 2

For the next half hour, small fires were burning in and near the aircraft impact cavity on the south side of

the building. There were vigorous fires on the east side of the 80"" through 83"* floors (Figure 3-^),

especially on the northeast end of the ST' and 82"'' floors, where the aircraft had bulldozed the office

desks and chairs and added its own combustibles. In addition to the ample supply of fuel, these fires had

access to plenty of air, as numerous windows on the east face had been blown out by the impact or

fireball. They would continue to bum as long as the building stood.

WTC 2. North Face 9:16 a. m.to 9:28 a.m.

»:: :: I

iiiiiiiiiii 'I

iiiiiiiiii

:S iiiiiii iiiKi

IIIIIIIIII

2M » ac 2ti m: i> WTC 2. South Face

220 215 210 m 201

9:16 a. m. to 9:28 a.m.

WTC 2, East Face

" mM

9:16 a. m. to 9:28 a.m

iiiiill

]» 3S9 3M 34S MO us 3M 325 320 315 310 306 301 WTC 2, West Face 9:16 a. m.to 9:28 a.m.

43C 425 420 415 410 405 401 159 155 1 50 145 140 13S 130 125 120 115 110 10S 101 Note: Color coding—white, no fire; yellow, spot fire; red, fire visible inside; orange, external flaming.

Figure 3-4. Representation of exterior views of the fires on the four faces

of WTC 2 at about 9:20 a.m.

Between 9:30 a.m. and 9:34 a.m., there were several large bursts of smoke from the 79"' and 80"' floors of

the north face, possibly resulting from the ignition of pools ofjet fuel that had settled there, or from

shifting of dislodged floor slabs elsewhere.

Dire structural changes were occurring in the building interior. Core columns, including the massive

southeast comer column, had been severed by the aircraft. The loads from these columns had been

redistributed to other, intact core columns and to the east exterior wall. The core leaned to the south and

east, restrained from further movement by the east and south walls through the floors and the hat tmss.

The fires were weakening the stmcture in a manner different from WTC 1 . First, the severed core columns in the southeast comer led to the failure of some column splices to the hat tmss. Nonetheless,

the hat tmss continued to transfer loads from the core to the perimeter walls. Second, the overall load

redistribution increased the loads on the east wall. Third, the increasing temperatures over time on the long-span floors on the east side had led to significant sagging on the 79"" through 83"* floors, resulting in an inward pull force. Fourth, within 18 min of the aircraft impact, there was inward bowing of the east perimeter columns as a result of the floors sagging. As the exposure time to the high temperatures

lengthened, these pull-in forces from the sagging floors increased the inward bowing of the east perimeter

columns.

NISTNCSTAR 1, WTC Investigation 43
Chapter 3

Meanwhile, people continued their evacuation. By 9:36 a.m., almost 7,000 of the 8,600 occupants had

left the building. From the impact floors and above, 18 occupants had discovered that the hot, smokefilled, debris-laden Stairway A was not fully blocked and had made their way to survival. It is not known

how many more of the 6 1 9 other people who had been on or above the impact floors became aware of

this, but none made it out of the building. There are no records of infomation regarding this escape route having been collected and transmitted to others who might have been able to use it.

The PAPD, NYPD, and FDNY centers were now being inundated with calls from the two buildings. In

the confusion, some of the callers did not identify which building they were in. At 9:12 a.m., PAPD was

notified that the WTC 2 floor warden phones were not working. Other calls alerted them to trapped and

injured people. At 9: 1 8 a.m., FDNY reported that they had a single elevator working to floor 40. A

simultaneous call indicated that FDNY was relocating its command post across West Street. At

9:30 a.m., EMS set up a triage desk in the lobby of WTC 2.

3.6 9:36 a.m. TO 9:58 a.m. EDT

By 9:58 a.m., all but eleven of the occupants who had been below the impact floors had left the building

and crossed the street to safety.

The fires continued to bum in the east half of the building.

At 9:55 a.m., firefighters communicated that they had reached floor 55 of WTC 2, one of the few calls for which a record survived indicating how high the responders had reached. Before WTC 2 collapsed,

firefighters had reached the 78"' floor by using the single functioning elevator to the 40* floor and then

climbing the stairs.

The physical condition of the tower had deteriorated seriously. The inward bowing of columns on the

east wall spread along the east face. The east wall lost its ability to support gravity loads, and,

consequently, redistributed the loads to the weakened core through the hat truss and to the adjacent north

and south walls through the spandrels. But the loads could not be supported by the weakened structure, and the entire section of the building above the impact zone began tilting as a rigid block to the east and

south (Figure 3-5). Column failure continued from the east wall around the comers to the north and

south faces. The top of the building continued to tilt to the east and south, as, at 9:58:59 a.m., WTC 2

began to collapse.

44 NISTNCSTAR 1, WTC Investigation
The Account of WTC 2

Figure 3-5. Photograph of WTC 2 tilting to the southeast at the onset of collapse.

3.7 THE OUTCOME

Seven factors led to the collapse of WTC 2:

• Direct structural damage from the aircraft impact, which included more severe damage to the core columns than in WTC 1

;

• Jet fuel sprayed into the building interior, that ignited widespread fires over several floors;

• Dislodging of SFRM from structural members due to the aircraft impact and aircraft and

building debris, which enabled rapid heating of the unprotected structural steel;

• Sustained fires on the east side of the tower and an ample air supply;

• Weakened core columns that increased the loads on the perimeter walls;

NISTNCSTAR 1, WTC Investigation 45
Chapter 3

• Sagging of the east floors, that led to pull-in forces on the east perimeter columns; and

• Bowed east perimeter columns that had a reduced capacity to carry loads.

After the building withstood the initial aircraft damage, the timing of the collapse was largely determined

by the time for the fires to weaken the perimeter columns and floors on the east and south sides of the building. That the aircraft impact damage to the core was more severe in WTC 2 than in WTC 1 contributed to the shorter time to collapse.

The loss of life in WTC 2 was significantly reduced by the prompt

start of evacuation activity before the tower was hit by the aircraft. Only a quarter of those initially on or above the impact floors died

when the building collapsed, as contrasted with 100 percent in WTC 1. Eighteen people on those upper floors found that one stairwell was

passable in time to evacuate. Whether others found this escape route is unknown.

Of the roughly 6,000 people who started the morning below the

77"^ floor, all but 1 1 evacuated the building, indicating sufficiently

efficient movement within the three stairwells within the time available.

Even more than in WTC 1 , those emergency responders who entered WTC 2 and the emergency

personnel who were already in the building were helpful in assisting the evacuation of those below the

impact floors. However, there was insufficient time to reach any survivors on the impact floors and

above. Any attempts to mitigate the fires were fruitless due to the lack of water supply and the difficulty

in reaching the fire floors within the time interval before the building collapse. It is not known precisely

how many emergency responders entered the building nor how many of the 42 1 emergency responder

casualties occurred in WTC 2.

As with WTC 1 , had the

building been more than

one-third occupied, the

casualties would have been

far higher as the population

would have exceeded the

capacity of the stairwells to evacuate them in the time

available.

46 NISTNCSTAR 1, WTC Investigation
Chapter 4

The Toll

By sunset on September 11, 2001, all seven buildings on the World Trade Center (WTC) site lay in ruins

(Figure 4—1). Table 4—1 compiles the likely locations of the decedents.

Source: National Oceanographic and Atmospheric Administration. Figure 4-1. The WTC site on September 17, 2001.

NISTNCSTAR 1. WTC Investigation 47
Chapter 4

Table 4-1. Likely locations of WTC decedents at time of impact.

Location" Number

WTC 1 Occupants (Total) 1,462 At or Above the Impact Floors 1,355 Below the Impact Floors 107 WTC 2 Occupants (Total) 630

At or Above the Impact Floors 619 Below the Impact Floors 11 Confirmed Below Impact Zone in WTC 1 or WTC 2 30"

Unknown Location Inside WTC 1 or WTC 2 24^ Emergency Responders (Total) 421"

FDNY 343 NYPD 23 PAPD 37

Hospital/Paramedic 7

Federal 2

Volunteer Responders 9 Bystander/Nearby Building Occupant 18

American Airlines Flight 11 United Airlines Flight 175 60* No Information 17 Total 2,749

a. Where possible, NIST used eyewitness accounts to place individuals. Where no specific accounts existed, NIST used employer and floor infonnation to place individuals.

b. These individuals were typically security guards and fire safety staff who were observed perfonning activities below the

floors of impact after the aircrafts struck.

c. These 24 individuals were largely performing maintenance, janitorial, delivery, safety, or security functions.

d. Emergency responders were defined to be people who arrived at the site from another location. Thus, security staff and Port Authority staff (different from PA Police Officers) were not defined as emergency responders.

e. Does not include the five hijackers per aircraft.

48 NISTNCSTAR 1, WTC Investigation
Part II: Reconstructing the Disaster
This page intentionally left blank.

50 NISTNCSTAR 1, WTC Investigation
Chapter 5

The Design and Construction of the Towers

5.1 BUILDING AND FIRE codes

Codes for the design, construction, operation, and maintenance of buildings are the blueprints by which a

society manifests its intent to provide public safety and welfare. They incorporate the knowledge,

experience, procedures and practices of the applicable engineering disciplines, the values of the contemporary society, the experiences from prior successes and failures, and knowledge of the commercial products, services, and technologies available for the tasks at hand.

In the United States, building and safety regulations of state and local jurisdictions are most frequently

based on national "modef" building codes (model codes). Developed under the auspices of private sector organizations in an open process, the model codes include minimum requirements for public health,

safety, and welfare. The model codes are traditionally organized into volumes according to the official responsible for their enforcement and include a building code, fire code, plumbing code, electrical code,

mechanical code, etc. The model codes adopt by reference voluntary consensus standards developed by a large number of private sector standards development organizations. These standards include

measurement methods; calculation methods; data sets; and procedures and practices for design,

construction, operation, and maintenance.

The model codes and referenced standards do not become law until they are adopted legislatively or administratively by a jurisdiction empowered to enforce regulations, for example, a state or city. These

jurisdictions may modify specific provisions of the models codes and referenced standards to suit local conditions or traditional practices. Once legally adopted, the totality of the modified model codes and

standards are referred to as building regulations.

Proposals to modify the model codes, offered by individuals or organizations, are discussed in open

forums before being accepted or rejected by a voting process. Localities adopting model codes update

their versions periodically as well, but typically not on the same schedule. To a lesser and decreasing

extent, some jurisdictions have generated their own building codes to reflect specialized local conditions

and preferences. The Federal government's role in determining specific codes is minimal and not mandatory (except for federally owned, leased, regulated, or financially assisted properties).

There are also key stakeholder groups that are responsible for or influence the practices used in the design, construction, operation, and maintenance of buildings in the United States through the code

development process. These include organizations representing building owners and managers, real

estate developers, contractors, architects, engineers, suppliers, and insurers. (Infrequently, members of

the general public and building occupants participate in this process.) These groups also provide training,

especially as it affects the ability to implement code provisions in practice, since lack of adequate training

programs can limit the application of improved code provisions.

NISTNCSTAR 1, WTC Investigation 51
Chapter 5

5.2 THE CODES AND THE TOWERS

5.2.1 The New York City Building Code

The New York City (NYC) Building Code was and is part of the Administrative Code of New York City.

Until recently, the various versions of the Code were not based on any model code, but rather were

written by local code development committees. However, there are many similarities between the

versions of the NYC Code and the model codes of the same time, since they all reflected accepted

practice.

The NYC Code has been amended from time to time by Local Laws to update safety requirements or to incorporate technological advances. These Local Laws were enacted by the New York City Council. To

aid the implementation of and to clarify building code requirements. New York City issued mandatory

"rules" that were typically initiated by City Government offices and issued under authority of the

Building Commissioner.

At the time the WTC project began in the early 1960s, the 1938 NYC Building Code was in effect. In 1960, reflecting growing dissatisfaction with the failure of the Code to keep pace with changes that had

occurred in the building industry, the Building Commissioner requested the New York Building Congress

to form a working committee to study the problem. On December 6, 1968, Local Law 76 repealed the 1938 code and replaced it with the 1968 code. As is the general custom with changes to building codes,

the new provisions did not apply to buildings approved under the prior code, provided they did not

represent a danger to public safety and welfare, or until they underwent a major renovation or change in primary use.

The 1968 NYC Building Code also included "Reference Standards." These included standard test methods and design standards published by standards development organizations. Some of these

Reference Standards included modifications to the published standards, as well as stand-alone standards

developed by New York City.

Through 2002, 79 Local Laws had been adopted that modified the 1968 Building Code. The major Local

Law affecting the structural design of buildings dealt with seismic provisions. Five of the Local Laws

had provisions that pertained to fire protection and life safety that were of interest to the WTC

Investigation:

• Local Law 5 (1973) added, among other specifications, requirements for:

- Compartmentation (subdivision) within upper story, unsprinklered, large floor areas. Its provisions applied retroactively to existing office buildings.

- Signs regarding the use of elevators and stairs, also retroactive.

- A fire alann system for buildings more than 100 ft in height.

• Local Law 55 (1976) added a requirement for inspection of all sprayed fire protection,

effective immediately but not retroactive.

• Local Law 33 (1978) added a requirement for trained fire wardens on each floor.

52 NISTNCSTAR 1, WTC Investigation
The Design and Construction oftlie Towers

• Local Law 86 (1979), among other provisions, required full compliance with Local Law 5 by

February 7, 1988, and exempted fully sprinklered buildings from compartmentation

requirements.

• Local Law 16 (1984) added requirements for sprinklers in new and existing buildings taller than 100 ft. Since Local Law 5 only required compartmentation of non-sprinklered spaces,

this negated the compartmentation requirements from Local Law 5.

The World Trade Center (WTC) was located in Manhattan and would normally have been designed and

constructed according to the NYC Building Code of 1938. However, the WTC was constructed by The

Port Authority of New York and New Jersey (The Port Authority or PANYNJ) on land that it owned. As

an interstate agency established under a clause of the United States Constitution permitting compacts

between states, The Port Authority's construction projects were not required to comply with any building

code. Nonetheless, The Port Authority instructed its consultants to design the two towers to comply with

the 1938 NYC Code. In 1965, The Port Authority directed the architect and consulting engineers to revise their designs for the towers to comply with the second and third drafts of what would become the 1968 NYC Code. The rationale for this step was that the new Code allowed the use of advanced

techniques in the design of the WTC, as well as more lenient provisions regarding exit stairs and the reduced fire ratings. To reaffirm a "long standing policy" of The Port Authority that its facilities meet or exceed NYC Building Code requirements, a formal memorandum of understanding between The Port Authority and the New York City Department of Buildings was established after the bombing in 1993.

5.2.2 Pertinent Construction Provisions

To gain perspective on the conditions under which the WTC towers were constructed, the rationale for the design, and the building structures themselves, the National Institute of Standards and Technology (NIST)

and its contractors reviewed tens of thousands of pages of documents provided by The Port Authority and

its contractors and consultants, Silverstein Properties and its contractors and consultants, the Fire

Department of the City of New York, the NYC Police Department, the NYC Law Department, the NYC

Department of Design and Construction, the NYC Department of Buildings, the NYC Office of

Emergency Management, the manufacturers and fabricators of the building components, the companies

that insured the WTC towers, and the building tenants.

NIST deemed it important to understand how the provisions under which the WTC was constructed and

maintained compared to equivalent provisions in place elsewhere in the United States at that time. The

Investigation selected three codes for comparison:

• The 1 964 New York State (NYS) Building Code, which governed construction outside the New York City limits

• The 1965 Building Officials and Code Administrators (BOCA) Basic Building Code, a model

building code typically adopted by local jurisdictions in the northeastern region of the United

States

• The 1967 Municipal Code of Chicago, under which the Sears Tower (1 10 stories) and the John Hancock Center (100 stories) were buih

NISTNCSTAR 1, WTC Investigation 53
Chapter 5

For the most part, the provisions in the various codes were similar, if not identical, indicating that there was a common understanding of the essentials of building safety and that the codes were at similar stages

of evolution:

• There were only modest differences among the codes in the provisions for gravity loads.

• All three of the contemporaneous building codes had provisions for wind loads that were less stringent than those used for the tower design.

• None of the codes had provisions for design against progressive collapse.

• For alterations or additions to a building, there were criteria to determine whether the whole

building or only the alterations needed to comply with the current code requirements. The

"trigger" was either the fraction of the building cost involved in the renovation or the fraction

of the building dimensions. The 1968 NYC Building Code was slightly less conservative

than the Chicago Code and the BOCA Code. The NYS Code required that any addition or

alteration conform to the contemporary code.

• The 1968 NYC Building Code required inspection of sprayed fire protection, but did not

specify if testing was required.

• Only the NYC Building Code contained provisions for bracing (lateral support to prevent

buckling of columns and walls) and stresses associated with transverse deflections of

structural members.

NIST examined the 2001 edition of the NYC Building Code to detennine the extent to which Local Laws

had modified the code provisions between the times of construction and collapse of the towers. The 2001

edition of the NYC Building Code was essentially the same as the 1968 edition, as amended by the

intervening Local Laws.

5.2.3 Tenant Alteration Process

With hundreds of tenants. The Port Authority realized that many would want extensive modifications to

their space, both before they moved in and during the course of their occupancy. In anticipation, The Port

Authority:

• Set up a special office to review and approve plans, issue variances, and conduct inspections.

• Developed a formal tenant alteration process for any modifications to leased spaces in WTC 1 and WTC 2 to maintain structural integrity and fire safety. The Tenant Construction

Review Manual, first issued in 1971, contained the technical criteria, standards, and review

criteria for use in planning alterations (architectural, structural, mechanical, electrical, and

fire protection). Alteration designs were to be completed by registered design professionals,

and as-built drawings were to be submitted to The Port Authority. The 1 968 NYC Building

Code was referenced. The review manual was updated four times and supplemented, in 1998, by the Architectural and Structural Design Guidelines, Specifications, and Standard

Details.

54 NISTNCSTAR 1, WTC Investigation
The Design and Construction of the Towers

The interiors of the towers had been heavily modified over the years due to tenant turnover, same-tenant space usage changes, the addition of sprinklers, and asbestos abatement.

5.3 BUILDING DESIGN

5.3.1 Loads

The NYC Building Code specified minimum design values for both dead and live gravity loads and for

lateral (wind) loads.

• Each tower was designed to support dead loads (its own weight) consistent with the provisions in the 1968 NYC Building Code. The dead loads included the weight of the

structural system and loads associated with architectural, mechanical, plumbing, and

electrical systems.

• Each tower was designed to support live loads (the combined weights of the people and the building contents) exceeding those specified in the 1968 NYC Building Code.

• The design wind loads used in the towers were higher than those required by the 1968 NYC

Building Code and the three other codes identified earlier.

5.3.2 Aircraft Impact

The accidental 1945 collision of a B-25 aircraft with the Empire State Building sensitized designers of

high-rise buildings to the potential hazards of such an event. However, building codes did not then, and

do not currently, require that a building withstand the impact of a fuel-laden commercial jetliner. A Port Authority document indicated that the impact of a Boeing 707 aircraft flying at 600 mph was analyzed

during the design stage of the WTC towers. However, the investigators were unable to locate any

documentation of the criteria and method used in the impact analysis and were thus unable to verify the

assertion that "...such collision would result in only local damage which could not cause collapse or

substantial damage to the building and would not endanger the lives and safety of occupants not in the immediate area of impact." Since the ability for rigorous simulation of the aircraft impact and of the ensuing fires are recent developments and since the approach to structural modeling was developed for

this Investigation, the technical capability available to The Port Authority and its consultants and

contractors to perform such an analysis in the 1 960s would have been quite limited.

5.3.3 Construction Classification and Fire Resistance Rating

Building codes classify building constructions into different "Types" or "Classes." The Class pertinent to the WTC towers was Class 1 (fire resistive). The 1938 NYC Building Code had no subdivisions of

Class 1 construction, which required a 4 hour fire resistance rating for columns and a 3 hour rating for

floors. The 1968 version of the Code subdivided Class 1 for office occupancies into 1 A, with

requirements identical to the 1938 Class 1, and IB. Class IB specified a 3 hour rating for columns and

Letter with an attachment dated November 13, 2003, from John R. Dragonette (Retired Project Administrator, Physical

Facilities Division, World Trade Department) to Saroj Bhol (Engineering Department, PANYNJ).

NiSTNCSTAR 1, WTC Investigation 55
Chapter 5

girders supporting more than one floor and a 2 hour rating for floors including beams. There were no

height or area requirements that differentiated between Class 1 A and Class IB, and the towers could have

been classified as either one. The Port Authority elected to provide the fire protection in the WTC towers

with Class IB standards.

Achieving a specified rating for a truss-supported floor using a sprayed fire-resistive material (SFRM)

was an innovation at the time of the WTC design and construction. NIST was not able to find any

evidence that there was a technical basis to relate SFRM thickness to a fire resistance rating, nor was

there sufficient prior experience to establish such thickness requirements by analogy. NIST did find

documentation that the Architect of Record and the Structural Engineer of Record had each written to The

Port Authority, stating that the fire rating of the WTC floor system could not be determined without

testing. NIST was unable to find any indication that such tests were performed nor any technical basis for the specification of the particular SFRM product selected or its application thickness.

The NYC Building Code required inspection at the time of application of the SFRM, to be conducted under the supervision of a building inspector or a licensed design professional who assumed responsibility for compliance.

This inspection included verification of the thickness of the material, its density, and its adhesion, each using a specific ASTM test method. The

Code contained a requirement that SFRM installed in areas where it was

subject to mechanical damage be protected and maintained in a serviceable

condition.

5.3.4 Compartmentation

Both the 1 968 NYC Building Code and The Port Authority practice required partitions to separate tenant spaces from each other and from common spaces, such as the corridors that served the elevators, stairs, and other common spaces in the building core. These were intended to limit fire spread on a floor and to prevent the spread of a fire from one tenant space to that of another.

• The Port Authority specified partitions separating tenant spaces from exit access corridors to have a 2 hour rating. This allowed dead end hallways to extend to 1 00 ft (rather than 50 ft with 1 hour partitions), which pennitted more flexibility in tenant layouts. Above the ceiling,

penetrations for ducts or to allow for return airflow were fitted with rated fire dampers to preserve the fire rating. This 2 hour rated construction was not used in the original design,

but was specified later by The Port Authority as tenant spaces were altered.

• For walls separating tenant spaces to achieve a 1 hour rating, they needed to continue through

any concealed spaces below the floor and above the ceiling. The Port Authority chose to stop

these demising walls at the bottom of the suspended ceiling and use 10 ft strips of 1 hour

rated ceiling on either side of the partition. There was no precedent for this approach and,

after a warning from the general contractor, the tenant alteration guidelines required that tenant partitions have a continuous fire barrier from top of floor to bottom of slab.

• There were no requirements in the 1 968 NYC Building Code or in The Port Authority

guidelines for partitions wholly within tenant spaces. As mentioned in Section 1.2.2, these

There were no code

requirements nor

general practice by

which sprayed fire- resistive material was

to be inspected over

the life of the building.

56 NISTNCSTAR 1, WTC Investigation
The Design and Construction of tfie Towers

gypsum board walls generally ran from the floor slab to just above the suspended ceiling,

although some extended to the slab above when the tenant desired additional sound

attenuation. For these partitions to be fire rated, the ceiling would have had to be rated as well but were not required to be so.

• Enclosures for vertical shafts, including stairways and transfer corridors, elevator hoistways,

and mechanical or utility shafts were required to be of 2 hour fire rated construction. These

innovative walls are further described below.

There was a conflict regarding the number of partitions within a tenant space. On the one hand, the design of the WTC towers was intended to provide about 30,000 ft" per floor of nearly uninterrupted

space and access to views of the Manhattan panorama. On the other hand. Local Law 5 dictated

compartmentation into no more than 7,500 ft' areas for unsprinklered spaces. These areas could be

increased to 15,000 ft' if protected by 2 hour fire resistive construction and smoke detectors. The

compartmentation limit was removed when complete sprinkler protection was provided. Following a 1975 fire. The Port Authority began installing sprinklers at the time a new tenant moved in. By

September 11, 2001, the installations had been completed throughout the towers, and, in general, the tenants on the impact floors had few internal partitions except for those surrounding conference rooms

and executive offices.

Firestopping materials are used to fill gaps in walls and floors through which smoke and flames might

pass. Such passage could negate the fire endurance value of the wall or floor. The 1 968 NYC Building

Code included comprehensive requirements identifying when and where firestopping was required. The

1964 New York State Building Code addressed the issue in less detail, and the Chicago Building Code

had no requirements. The National Fire Protection Association (NFPA) Life Safety Code had

firestopping requirements for exterior and interior partitions at floor levels, and did allow a trade-off for sprinklered concealed spaces. In the towers, unlike many buildings, the exterior wall was connected with

the floors without gaps.

5.3,5 Egress Provisions

The primary egress system for the office spaces was the three stairways

located in the building core. There were four main requirements for these

stairways: number, width (including separate width requirements for the doors), separation of the doors to the stairways, and travel distance to the stairway doors.

The number of stairways and the width of the doors resulted from the

implementafion of the 1 968 edition of the NYC Building Code, whose

provisions were less restrictive than those in the 1938 edition. The

1968 code eliminated a fire tower (an enclosed staircase accessed through

a naturally ventilated vestibule) as a required means of egress and reduced

The NYC Building Code

used the "units of exit width" method for specifying exit capacity,

in which each 22 in. unit of exit width provided

the capacity for 60 people. Thus each

44 in. stairwell provided

for 120 people and the

56 in. stairwell provided

2y2 units, or 150 people,

for a total occupant load

per floor of 390.

NISTNCSTAR 1, WTC Investigation 57
Chapter 5

the number of required stairwells from six to three^ and the width of the doors leading to the stairs from

44 in. to 36 in.

Of the three staircases, two (designated A and C) were 44 in. wide; stairway B was 56 in. wide. The

largest occupant load in the office spaces was 365 people per floor (36,500 ft" on the largest floor, with

100 ft" per person). Neither the 1968 NYC Building Code nor any of the contemporaneous codes

mandated consideration of the number of building stories in determining the number and widths of the

stairwells.

For the floors classified in the office use group (all floors except the observation deck and

restaurant/meeting spaces), a minimum of two stairwells would have been required to serve the occupants, each equally sized. The three modem building codes considered in this report [International

Building Code (IBC) (2000), NYC Building Code (2003), and NFPA 5000 (2003)], as well as the 1968 NYC Building Code, were consistent in this requirement, each regardless of building height.

However, the resulting width of these minimum requirements would differ. Two 44 in. stairwells would

have satisfied IBC minimum requirements, two 65 in. stairwells would have satisfied NFPA 5000

requirements, and two 78 in. stairwells would have satisfied the 1968 and 2003 NYC Building Code

requirements. Alternatively, as was built at WTC 1 and WTC 2, three stairwells of narrower construction,

but equivalent or greater total required width, would also satisfy the egress requirements in the modem

building codes.

The 1968 NYC Building Code contained a requirement that the stairwells be "as far apart as practicable."

Since the stairwells on the impact floors of WTC 1 were substantially closer together than those on the impact floors of WTC 2, it certainly was possible to have designed a greater separation in WTC 1. Local

Law 16 (1984) added a quantitative requirement that the separation between exit door openings be at least one-third of the maximum travel distance of the floor. For the WTC towers, this maximum distance was

1 80 ft, and the smallest separation of stairwell doors was 70 ft. The towers were consistent with this requirement.

NFPA 5000 (2003) and IBC (2000) incorporate a requirement that the separation of the stairwells be no

less than one-third the overall diagonal length of the building. For the towers this length was 294 ft, and

one-third was 98 ft. Thus, the stairwell separafions on some floors would have been inconsistent with the

later codes (with which the buildings in New York City were not required to comply).

At the top of the two towers were floors that were classified as public assembly floors: the Windows on

the World restaurant complex in WTC 1 (floors 106 and 107) and the Top of the World observation deck

in WTC 2 (floor 107). The design number of occupants on each of these floors was over 1,000. On

September 11, 2001, there were about 188 people in the Windows on the World and few in the Top of the World since it was before the opening hour. Thus, had the stairwells remained passable through the

impact region, the capacity would have been sufficient for the occupant load observed on that mom.ing.

Nonetheless, the egress requirements for assembly occupancy were more stringent than for business

occupancy in both the NYC Building Code in 1968 and in 1996, when the Windows on the World

re-opened after refurbishment following the 1993 bombing in the basement. NIST found documentation

that, in 1996, The Port Authority created areas of reftige consistent with the provisions of the 1968 NYC

See discussion of the required number of stairwells later in this section.

58 NISTNCSTAR 1, WTC Investigation
The Design and Construction of tlie Towers

Building Code, but NIST was unable to find evidence indicating that the requirements for the number of

exits for the evacuation of over 1 ,000 people from each of these floors had been considered in the design

or operation of the buildings. In 1995, the NYC Department of Buildings, however, had reviewed the egress capacity from these floors and apparently concurred that the proposed remodel to these spaces

would meet the intent of the NYC Building Code.

Subsequently, NIST communications in 2005 with The Port Authority and the NYC Department of

Buildings identified a difference of interpretation regarding the number of exits required to serve these

floors. The Port Authority stated that a fourth exit was not required since the assembly use space in question constituted less than 20 percent of the area of principal use, with principal use area defined as the

entire building. The Department of Buildings stated that the 20 percent rule did not apply to assembly

spaces such as restaurants and observation decks that are open to the public, and therefore exit reduction

cannot be applied and a fourth exit was required.

The Department further clarified that areas of refuge and horizontal exits are not to be credited for required means of egress (unless the spaces are used non-simultaneously) and that for places of assembly,

with occupant load in excess of 1,000, the floor shall have a minimum of four independent means of

egress (stairs) to street. If the floor were divided into areas of refuge with rated walls, as was the case for the WTC towers, each area is to be considered an independent place of assembly that needs its own

access to two means of egress (stairs) without going through another assembly space if they have an occupant load of less than 500 each (or three means of egress if the area of refuge had an occupant load

between 500 and 999). Further, since the only means of egress from the roof-top deck was through the space on the observation floor, the Department clarified that occupant load from the deck would need to be added to the occupant load of the observation floor and that the travel distance from the roof deck

along the connecting stairs to the required means of egress at the observation floor shall be within the maximum permitted by the NYC Building Code. The Department, however, did not raise the issue of a fourth stairwell in its December 1 994 meeting with The Port Authority and when it subsequently

concurred with The Port Authority's proposal to remodel the spaces.

Given the low occupancy level on September 1 1, 2001, NIST found that the issue of egress capacity from

these places of assembly, or from elsewhere in the buildings, was not a significant factor on that day. It is conceivable that such a fourth stairwell, depending on its location and the effects of aircraft impact on its functional integrity, could have remained passable, allowing evacuation by an unknown number of

additional occupants from above the floors of impact. If the buildings had been filled to their capacity

with 20,000 occupants, the required fourth stairway would likely have mitigated the insufficient egress capacity for conducting a full building evacuation within the available time.

The elevator system was described in Chapter 1 . These were not to be used for emergency evacuation

except under the control of the fire department. Roughly 3,000 of the people who were initially at or above the impact floors in WTC 2 and were warned by the attack on WTC 1 survived, however, in large

part by taking the elevators downward before the aircraft struck WTC 2.

Following the 1993 bombing, The Port Authority instituted the following changes to reduce egress time,

in addition to those stairwell improvements mentioned in Section 1.1.2:

• Construction of new egress corridors, north (to Church Street and Vesey Street) and south (to

Liberty Street) for faster evacuation from the Concourse (mall), and of two escalators from

NISTNCSTAR 1, WTC Investigation 59
Chapter 5

the Concourse (mall), one to the plaza at WTC 5 and one up to WTC 4 and onto Church

Street.

• Semiannual fire drills in conjunction with the FDNY.

• Appointment of Fire Wardens, specially trained and equipped with flashlights, whistles, and

identifying hats.

Building Communications

WTC emergency procedures specified that all building-wide announcements were to be broadcast from the Fire Command Desk (FCD), located in the lobby of each WTC tower (Figure 5-1), using prepared text. A situation

requiring evacuation for any reason, including fire or smoke, would have led

to the following announcement, enabling a phased evacuation:

"Your attention please. We are experiencing a smoke condition in the vicinity of your floor. Building personnel have been dispatched

to the scene and the situation is being addressed. However, for precautionary reasons, we are conducting an orderly evacuation of

floors . Please wait until we announce your floor number over

the public address system. Then follow the instructions of your fire safety team. We will continue to keep you advised. We apologize

for the inconvenience and we thank you for your cooperation."'"

The announcement to be used when a particular floor required an evacuation was:

"Your attention please. It is now time for your floor to be evacuated. In accordance with the

directions from your fire safety team, please take the exit stairs nearest to your location. We

remind you that communications, emergency lighting and other essential services are in service. We will continue to keep you advised. We apologize for the inconvenience and we thank you for your cooperation.

At the discretion of the Fire Safety Director, the information and instructions broadcast to the building

occupants could be modified to suit the nature of the emergency.

A Fire Command Desk

(Figure 5-1) was

located in the lobby of each tower. The

computer screen

monitored the fire alarms, smoke

sensors, sprinkler

water flow, elevator

lobby smoke

detectors, fire signal

activation, air handling

fans, status of elevators, and troubles

with the fire systems.

The Port Authority of New York and New Jersey. World Trade Center Emergency Procedures Manual 2001.

60 NIST NCSTAR 1. WTC Investigation
The Design and Construction of the Towers

Figure 5-1. Fire Command

Desk in WTC 1, as seen from a mezzanine elevator, looking

west.

5.3.6 Active Fire Protection

The provision of fire safety in the WTC towers revolved around a Fire Safety Plan that provided direction

for fire emergency response and was organized around a hierarchy of staff trained in its implementation.

In charge in each tower was the Fire Safety Director, who oversaw emergency response until the arrival of the Fire Department of the City of New York (FDNY), gathered necessary infonnation, and relayed it to the Fire Chief upon arrival. In an emergency, the Fire Safety Director proceeded to the FCD or the fire scene. He/she had one or more Deputy Fire Safety Directors located at the FCD and at the sky lobbies.

The front line w as a set of Floor Wardens and Deputy Floor Wardens who were responsible for assessing

conditions and assisting the evacuation of occupants on their respective floors. The Floor Wardens had

their own communications system.

Built into each tower were four resources to mitigate the effects of a fire: an alarm system to alert people

to the presence of the fire, an automatic sprinkler system and a standpipe system for controlling the fire by the application of water, and a smoke venting system to improve visibility as people proceeded toward

exits. The primary documentation of the design, installation, maintenance, and modification of these

systems was stored on the 81" floor of WTC 1 and was lost when that building collapsed. Contractors to the Investigation Team were able to re-create descriptions of the physical systems and their capabilities

from limited duplicate information provided by The Port Authority, Silverstein Properties, Inc, and

contractors, consultants, and operators involved with the systems.

The original fire alarm system used the technology current at the time and was engineered exclusively for the World Trade Center towers. The 1993 bomb explosion in WTC 1 destroyed the communications to the Operations Control Center, and the alarm system was revealed to be vulnerable to a single point of

failure. Repair was problematic, since spare parts for the 25-year-old system were unavailable, and the software was no longer supported. The Port Authority immediately commissioned a new state-of-the-art system for WTC 1, WTC 2, WTC 4, WTC 5, and the subterranean levels. This retrofit involved the

installation of over 10,000 detectors, pull stations, and monitors; 30,000 notification devices (speakers

NISTNCSTAR 1, WTC Investigation 61
Chapter 5

and strobe lights); 150 miles of conduit; and 1,000 miles of wiring. Redundant Operations Control

Centers were located in the basements of both towers.

The primary monitoring and control of the fire alarm system was performed at the FCD located in the lobby of each building. The new system included:

• Numerous intercoimected microprocessors located in each of the four WTC buildings.

• Smoke sensors located throughout the tenant spaces, at each elevator landing, in return air ducts, and in electrical and mechanical rooms.

• At least one manual fire alarm station installed in each story in the evacuation path.

• Emergency voice and alarm speakers for notification and communication in all areas within

the buildings, designed to ensure system function in the event 50 percent of the system

became inoperable.

• Automatic notification of the fire department upon fire alarm activation.

• Two-way communications stations at the remote fire panels, at the Floor Warden stations,

and at the standpipes.

• A two-way telephone system for the firefighters to make announcements.

• Emergency voice and alarm communication capability, both under manual control at the FCD.

• Strobe lights to provide alarm indications for the hearing impaired.

• Water flow indicators for the fire sprinkler system, including indicators for disabled systems.

No documentation of the status of the replacement system survived the 2001 attack. However, a 2002

analysis estimated that over 80 percent of the towers had been retrofitted and that about 25 percent of the

original system was still in use.

Although there were localized carbon dioxide and halon systems within the towers, the Safety Plan

predominantly relied on water for containing and suppressing a fire (Figure 5-2). By

September 11, 2001, automatic sprinklers had been installed throughout WTC 1 and WTC 2." The New

York City water distribution system supplied water to the complex from two independent connections

located under Liberty Street to the south and Vesey Street to the north. Within each tower were six 5,000 gal water storage tanks, three located on the 1 lO"' floor and one each on the 20"\ 41", and 75"'

floors. These were filled from the domestic water supply in the building. In the event of a fire, the

gravity-fed water would flow to as many of the thousands of installed sprinklers as had been activated.

The WTC engineering staff would supply additional water upward from the city mains using manually

The exceptions to this were the computer rooms (protected with halon and carbon dioxide systems), kitchens (protected with

dry chemical and steam smothering systems), mechanical spaces on the 108"' through 1 lO"' floors, and the electrical rooms

throughout the buildings, for which the application of water would have been inappropriate.

62 NISTNCSTAR 1, WTC Investigation
The Design and Construction oftlie Towers

started pumps located in the towers; the FDNY could augment the supply using fire department

connections and truck-based pumps. While there were redundant vertical supply pipes, there was only a

single connection to the array of sprinklers on any given floor.

110th Floor

75lh Floor

41 St Floor

20th Floor

1st Floor (Concourse)

High Pressure Standpip* -

B-1 Level

WTC 1 2x5000 gal Storage Tanks 5 & 6 SOOOgal

Storage Tank 3

Pump 5 -^<^

Sprinkier <KI>

Control '

5000 sal Storage Tank 2

Pump 4

5000 gal Storage Tank 1

Pump 3 -

5000 gal Storage Tank 4

Pump2

-Pimipl

Figure 5-2. Schematic of sprinkler and standpipe systems.

The WTC towers were constructed with a manually activated (by Port Authority staff at the direction of

FDNY) smoke purge system, use of which was integrated into The Port Authority's WTC Fire Safety

Plan. The system was designed to meet the 1968 NYC Building Code and was functional by

September 1 1, 2001. The non-dedicated system used the existing building ventilation system, in contrast with an alternative dedicated system that would have been used only for smoke management. Each tower was divided into three zones, with the blowers located on the mechanical equipment floors (7, 41, 75, and

108). In the smoke purge mode, the mechanical system was aligned so that an entire zone was vented;

there was no provision to vent an individual floor. The smoke from the impact floors in WTC 1 would

have been drawn upward to the 108"^ floor, while the smoke from the impact floors in WTC 2 would have

been drawn downward to the 75"^ floor. The system was designed to clear the zone of smoke after the fire was extinguished, perhaps during post-fire cleanup operations, lest the forced air increase the burning

intensity.

NISTNCSTAR 1, WTC Investigation 63
Chapter 5

5.4 BUILDING INNOVATIONS

5.4.1 The Need for Innovations

Had the towers been built according to conventional design, they would have been heavier and would

have had less usable space on each floor. Thus, a resourceful approach was taken in translating The Port Authority's needs and Yamasaki's design into practice.

The Investigation Team identified six innovations incorporated in the lateral-load-resisting system and the

gravity-load-carrying system of the towers. Their roles were discussed in Chapter 1. In addition, there were two innovations in achieving the required fire resistance ratings. The innovative, tiered elevator

system was also discussed in Chapter 1 . The following sections describe these new technologies. The

use of sprayed fire-resistive material is discussed in more detail in Section 5.6.

5.4.2 Framed Tube System

WTC 1 and WTC 2 were among the first steel-structure, high-rise buildings built using the framed-tube

concept to provide resistance to lateral (wind) loads. The framed-tube system had previously been used

in the concrete-framed, 43-story DeWitt-Chestnut and the 38-story Brunswick buildings, both in Chicago

and both completed in 1965.

In the framed-tube concept, the exterior frame system resists the force of the wind. The exterior columns

carry a portion of the building gravity loads, and in the absence of wind, are all in compression, i.e., the

loads push down on and shorten the columns. Under the effect of a strong wind alone, columns on the windward side are in tension, i.e., they elongate as the top of the building bends away from the wind. The

columns on the leeward side are compressed. The columns on the walls parallel to the wind are half in tension (on the windward side) and half in compression (on the leeward side). The net effect of combined

gravity and wind loads is larger compression on the leeward side and reduced compression, or in rare instances even tension, on the windward side.

Prior to final design, tests had been performed at the University of Western Ontario to assess the stiffness of the wall panels, which consisted of three columns, each three stories high, and the associated spandrel

plates as shown in Figure 1^. These tests used quarter-scale thermoplastic models of panels planned for the 20"\ 47"\ and 74"^ floors. (Recall that the structural members became lighter at the higher floors.)

The tests also examined the effect of the spandrel thickness, the width of the box columns, and the presence and thickness of stiffeners. Forces were applied to the models, and the resuhing deflections

measured. The results of these tests guided the final design of the wall panels and provided support for The Port Authority's acceptance of the resulting structural design. This included the innovations

described in Sections 5.4.3 and 5.4.4.

5.4.3 Deep Spandrel Plates

The standard approach to construction of the framed tube would have used spandrel beams or girders to connect the columns. The towers used a band of deep plates as spandrel members to tie the perimeter

columns together.

64 NISTNCSTAR 1, WTC Investigation
The Design and Construction of the Towers

5.4.4 Uniform External Column Geometry

In a U'pical high-rise building, the columns would have been larger near the base of the building and

would have become smaller toward the top as they bore less wind and gravity loads. However, the Yamasaki design called for the appearance of tall, uniform columns (Figure 1-2). This was achieved by

varying both the strength of the steels and the thickness of the plates that made up the perimeter columns.

5.4.5 Wind Tunnel Test Data to Establish Wind Loads

To determine the extreme wind speeds that could be expected at the top of the towers, Worthington,

Skilling, Helle & Jackson (WSHJ) collected data on the wind speeds and directions recorded in the New

York area over the prior 50 years. From these data, a design wind speed for the buildings was determined

for a 50 year wind event, defmed as the wind speed, averaged over a 20 min duration at 1,500 ft above the ground. The estimated value was just under 100 mph in all directions.

To estimate how the buildings would perform under wind loads, both during construction and upon

completion, WSHJ conducted a then unique wind tunnel testing program at Colorado State University

(CSU) and the National Physical Laboratory (NPL) in the United Kingdom. In each wind tunnel, a physical model of Lower Manhattan, including the towers, was subjected to steady and turbulent winds

consistent with the estimated design wind speeds. The model scale was 1/500 for the CSU tests and

1/400 for the NPL tests. The tower models were thus about 3 ft tall. Separate tests were conducted for the single tower and for the two towers at various spacings, with various values of the tower stiffness and

damping, and for various wind directions. The two laboratories obtained similar results. Tests on the two- tower models showed that the wind response of each tower was significantly affected by the presence of

the other tower.

WSHJ also conducted experiments to determine the wind-induced conditions that would be tolerated by

the people who would work in and visit the towers. Breaking new ground in human perception testing, the investigators found that surprisingly low building accelerations caused discomfort.

The test results led to changes in the building design, including stiffer perimeter columns, and the addition of viscoelastic dampers described in the next section. The dampers were used to reduce the building vibrations due to winds.

5.4.6 Viscoelastic Dampers

The tower design included the first application of damping units to supplement the framed-tube in limiting wind-induced oscillations in a tall building. Each tower had about 10,000 dampers.

On most truss-framed floors (tenant floors), a damper connected the lower chord of a truss to a perimeter

column. A depiction of the units is shown in Figure 5-3. On beam-framed floors (generally the

mechanical floors with their heavier loads), a damper connected the lower flange of a wide-flange beam

(that sparmed between the core and the perimeter wall) to a spandrel.

NISTNCSTAR 1, WTC Investigation 65
Chapter 5

(

J

3usset plate / Truss upper chord / n ^1 rRv

^ Truss seatangle^^^^^^^^^^

Standoff

plate ^"'''^v::;;;;;^...^^

12 y/* 1 1 A ^ v—v V—w—' ijk

, ' Splice plate Truss lower J'\ Viscoelastic gaddle chord Spandrel damper

Figure 5-3. Diagram of floor truss showing viscoelastic damper.

Two sets of experiments, conducted by the 3M Company (the manufacturer of the viscoelastic material)

and by the Massachusetts Institute of Technology, respectively, examined the damping characteristics of

the units. Both studies found that the units provided significant supplemental damping under design

conditions.

5.4.7 Long-Span Composite Floor Assemblies

The floor system in the towers (as shown in Figure 1-6) was novel in two respects:

• The use of open-web, lightweight steel trusses topped with a slab of lightweight concrete

• The composite action of the steel and concrete that resulted from the "knuckles" of the truss diagonals extending above the top chord and into the poured concrete

Tests conducted in 1964 by Granco Steel Products and Laclede Steel Company (the manufacturer of the

trusses for WTC 1 and WTC 2) determined the effectiveness of the knuckles in providing composite

action. Another set of tests, performed by Laclede Steel Company, detennined that any failure of the knuckles occurred well beyond the design capacity. A third set of tests, performed at Washington

University in 1968, confirmed the prior results and indicated that failure was due to crushing of the concrete near the knuckles.

5.4.8 Vertical Shaft Wall Panels

While similar to other gypsum shaft wall systems and firewalls, the compartmentation system used in the

vertical shafts (e.g., for elevators, stairs, utilities and ventilation) was unique in that it eliminated the need

for any framing. The walls consisted of gypsum planks placed into metal channels at the floor and ceiling

slabs. The planks were 2 in. thick (2/4 in. on floors with 16ft ceiling heights) and 16 in. wide, with metal

tongue and groove channels attached to the long sides that served as wall studs. An assembled wall was

66 NISTNCSTAR 1, WTC Investigation
The Design and Construction of the Towers

then covered with gypsum wallboard. The planks were Hkely custom fabricated for this job, as the investigators found no mention of similar products in gypsum industry Uterature of the time or since.

5.5 STRUCTURAL STEELS

5.5.1 Types and Sources

Roughly 200,000 tons of steel were used in the construction of the two WTC towers. The building plans

called for an unusually broad array of steel grades and multiple techniques for fabricating the structure from them. The NIST team obtained the information needed to characterize the steels from stmctural

drawings provided by The Port Authority, copies of correspondence during the fabrication stages, steel mill test reports, interviews with fabrication company staff, search of the contemporaneous literature, and

measurements of properties at NIST. Sorting through this immense amount of information was made

difficult by the large number of fabricators and suppliers, the use of proprietary grades by some of the manufacturers; and the fact that the four fabricators of the impact and fire floor structural elements no

longer existed at the time of this Investigation.

Fortunately, the potential for confusion had led the building designers to a tracking system whereby the

steel fabricators stamped and/or stenciled each structural element with a unique identifying number. The

structural engineering drawings included these identifying numbers as well as the yield strengths of the individual steel components. Thus, when NIST found the identifying number on an element such as a perimeter column panel, the particular steel specified for each component of the element was known, as well as the intended location of the steel in the tower.

In all, 14 grades of steel were specified in the structural engineering plans, having yield strengths from

36 ksi to 100 ksi. Twelve were actually used, as the fabricators were permitted to substitute 100 ksi steel where yield strengths of 85 ksi and 90 ksi were specified. Table 5-1 indicates the elements for which the various grades were used. The higher yield strength steels were used to limit building weight while

providing adequate load-carrying capacity.

Table 5-1. Specified steel grades for various applications.

Application

Yield Strength (ksi)

36 42 45 46 50 55 60 65 70 75 80 100

Perimeter columns •/ -/

Spandrel plates / /

Core columns •/ (a) (a)

Floor trusses

a. About 1 percent of the wide flange core columns were specified to be of these higher grades.

5.5.2 Properties

The Port Authority required a thorough and detailed quality assurance programs to ensure compliance

with the specifications for the steel, welds, and bolts. The steel data went beyond the minimum yield

strength (the property of greatest importance) to include tensile strength and ductility. The quality assurance program included unannounced inspections and confirming tests.

NISTNCSTAR 1, WTC Investigation 67
Chapter 5

NIST perfonned confirmatory tests on samples of the 236 pieces of recovered steel to determine if the

steel met the structural specifications. Making a definitive assessment was complicated by overlapping

specifications from multiple suppliers, differences between the NIST test procedures and the test procedures that originally qualified the steel, the natural variability of steel properties, and damage to the

steel from the collapse of the WTC towers. Nonetheless, the NIST investigators were able to determine

the following:

• There were 14 grades (strengths) of steel that were specified. However, a total of 32 steels in the impact and fire floors were sufficiently different (grade, supplier, and gage) to require

distinct models of mechanical properties.

• The steels in the perimeter columns met their intended specifications for chemistry,

mechanical properties, yield strengths, and tensile properties. The steels in the core columns

generally met their intended specifications for both chemical and mechanical properties.

• Roughly 1 3 percent of the measured strength values for the perimeter and core columns were

at or below the specified minimums (Figure 5-4). The strength variation was consistent with

the historical variability of steel strength and with the effects from damage during the collapse of the towers. The measured values were within the typical design factor of safety.

• The yield strengths of many of the steels in the floor trusses were above 50 ksi, even when

they were specified to be 36 ksi.

• Tests on a limited number of recovered bolts showed they were much stronger than expected

based on reports from the contemporaneous literature.

The mechanical properties of steel are reduced at elevated temperatures. Based on measurements and

examination of published data, NIST determined that a single representation of the elevated temperature

effects on steel mechanical properties could be used for all WTC steels. Separate values were used for the yield and tensile strength reduction factors for bolt steels.

68 NISTNCSTAR 1, WTC Investigation
The Design and Construction of the Towers

LL

DCD

1.8

1.6

0.8

oinner webs

^ Other plates

40 60 80

Specified F ksi

100

Note: The ratio values less than 1 arose from natural variation in the steel and did not affect the safety of the towers on September 1 1 , 2001 . The bars represent maximum and

minimum values from multiple measurements. Figure 5-4. Ratio of measured yield strength (Fy) to specified minimum

yield strength for steels used in WTC perimeter columns.

5.6 FIRE PROTECTION OF STRUCTURAL STEEL

5.6.1 Thermal Insulation

When steel is heated it loses both strength and stiffness. Thus, measures must be taken to protect the steel

in a structure from temperature rise (and consequent loss of strength) in case of fire.

Bare structural steel components can heat quickly when exposed to a fire of even moderate intensity.

Therefore, some sort of thermal protection, or insulation, is necessary. This insulation can be in direct contact with the steel, such as a sprayed fire-resistive material (SFRM), or can be a fire resistant enclosure

surrounding a structural element.

5.6.2 Use of Insulation in the WTC Towers

The thermal protection of the steel structures in the WTC towers included a combination of SFRM and

enclosures of gypsum wallboard. The use of SFRM for floor truss protection was new in high-rise

buildings, and the requirements evolved during the construction and life of the towers. By examining

documents supplied by The Port Authority, LERA, and the SFRM manufacturers, NIST was able to

NISTNCSTAR 1, WTC Investigation 69
Chapter 5

document much of the sequence of these changing requirements and arrive at an estimation of the passive

protection in place on September 1 1, 2001.

Floor Systems

At the time the WTC was designed, the ASTM E 1 19 test method had been used for nearly 50 years to determine the fire resistance of structural members and assemblies. However, The Port Authority

confimied to the Investigation Team that there was no record of fire endurance testing of the innovative

assemblies representing the thennally protected floor system used in the towers. The floor assembly was

not tested despite the fact that the Architect of Record and the Structural Engineer of Record stated that the fire rating of this novel floor system could not be determined without testing.

Prior to construction, the Architect of Record had used infonnation from (unidentified) manufacturers to recommend a 1 in. thickness of SFRM around the top and bottom chords of the trusses and a 2 in. thickness for the web members of the trusses. This was to achieve the fire endurance requirements for Class 1 A construction (Section 5.3.3).

In 1969, The Port Authority directed that a Vi in. thick coatmg of BLAZE-SHIELD Type D

(BLAZE-SHIELD D), a mixture of cement and asbestos fibers, be used to insulate the floor trusses. This was to achieve a Class 1 A rating, even though the preponderance of evidence suggests that the towers were chosen to be Class IB, the minimum required by the NYC Building Code. NIST found no evidence

of a technical basis for selection of the Vi in. thickness. This coating had been installed as high as the 38*

floor of WTC 1 when its use was discontinued due to recognition of adverse health effects from

inhalation of asbestos fibers. The spraying then proceeded with BLAZE-SHIELD DC/F, a similar

product in which the asbestos was replaced by a glassy mineral fiber and whose insulating value was

reported by Underwriters Laboratories, Inc., to be slightly better than that of BLAZE-SHIELD D. On the lower floors, the BLAZE-SHIELD D was encapsulated with a sprayed material that provided a hard coat

to mitigate the dispersion of asbestos fibers into the air.

In 1994, The Port Authority measured the SFRM thickness on trusses on floors 23 and 24 of WTC 1. In

all, average thicknesses were reported for 32 locations, and the overall average thickness was found to be

0.74 in. NIST performed a further evaluation of the SFRM thickness using photographs taken in the

1990s of floor trusses on (non-upgraded) floors 22, 23, and 27 of WTC 1 (Figure 5-5). By measuring

dimensions on the photographs, NIST estimated the insulation thicknesses on the diagonal web members

of trusses. (The thickness of chord member insulation could not be measured.) The average thickness

and standard deviation of web members was 0.6 in. ± 0.3 in. on the main trusses, 0.4 in. + 0.25 in. on the bridging trusses, and 0.4 in. + 0.2 in. on the diagonal struts. These numbers indicated that there were

areas where the coating thickness was less than the specified 0.5 in.

70 NISTNCSTAR 1, WTC Investigation
The Design and Construction of the Towers

It

r

I 1993 Reproduced with permission of U S. Mineral Products Co.

dba Isolatek International and Morse Zehnter Associates

Note: Enhancement by NIST. Figure 5-5. Irregularity of coating thickness and gaps in coverage on SFRM-coated bridging trusses.

In 1995, The Port Authority performed a study to estabUsh requirements for retrofit of sprayed insulation

to the floor trusses during major alterations when tenants vacated spaces in the towers. Based on design

information for fire ratings of a similar, but not identical, composite floor truss system contained in the Fire Resistance Directory published by Underwriters Laboratories, Inc., the study concluded that a VA in. thickness of sprayed mineral fiber material would provide a 2 hour fire rating, consistent with the

Class IB requirements. In 1999, the removal of existing SFRM and the applicafion of new material to

this thickness became Port Authority policy for full floors undergoing new construction and renovation.

For tenant spaces in which only part of a floor was being modified, the SFRM needed only to be patched

to y4 in. thickness or to match the 1 Vi in. thickness, if it had previously been upgraded. In the years between 1995 and 2001, thermal protection was upgraded on 18 floors of WTC 1, including those on which the major fires occurred on September 1 1, 2001, and 13 floors of WTC 2 that did not include the

fire floors. The Port Authority reported that the insulation used in the renovations was BLAZE-SHIELD II.

In July 2000, an engineering consultant to The Port Authority issued a report on the requirements of the

fire resistance of the floor system of the towers. Based on calculations and risk assessment, the consultant

concluded that the structural design had sufficient inherent fire performance to ensure that the fire condition was never the critical condition with respect to loading allowances. The report recommended

that a 1 .3 in. thickness be used for the floor trusses.

In December 2000, another condition assessment concluded that the structural insulation in the towers had an adequate 1 hour rating, considering that all floors were now fitted with sprinklers. The report also noted the ongoing Port Authority program to upgrade the fire-resistive material thickness to 1 Vi in. in order to achieve a 2 hour fire rating.

NISTNCSTAR 1, WTC Investigation 71
Chapter 5

The Port Authority provided NIST with the records of measurements of SFRM thickness on upgraded

floors in both towers. The average thickness and standard deviation on the main trusses was 2.5 in. +

0.6 in., based on 18 data sets with a total of 256 measurements. NIST analysis of several Port Authority

photographs from the 1 990s of the upgraded 3 1

^' floor of WTC 1 indicated an average thickness and

standard deviation on the main trusses of 1.7 in. + 0.4 in., based on 52 measurements from five web

members in two photographs. NIST gave more weight to the measured data, which were taken according

to a standard procedure in ASTM E 605, than to the data scaled fi^om photographs, for which there was

neither standard procedure nor calibration of the method.

Perimeter Columns

In 1966, the contractor responsible for insulating the perimeter columns proposed applying a 1 3/16 in. thick coating of BLAZE-SHIELD D to the three external faces (Figure 5-6) to achieve a 4 hour rating,

which is a Class 1 A rating requirement ( 1 hour more than Class IB). NIST found evidence of a technical

basis for this decision. In the construction drawings prepared by the exterior cladding contractor, the following SFRM thicknesses were specified:

• 7/8 in. of vermiculite plaster on the interior face and 13/16 in. of BLAZE-SHIELD D on the

other three faces.

• Vi in. of venniculite plaster on the interior surfaces of the spandrels and Vi in. of

BLAZE-SHIELD D on the exterior surfaces.

I r-6"

Panel

^V.^ Typical Column

Aluminum Cover Figure 5-6. Thermal insulation for perimeter columns.

Vermiculite plaster had a higher thermal conductivity and thereby increased heat migration from the room

air to the column steel and, thus, could keep the steel temperature at 70 °F when the temperature was 0 °F

outside.

72 NISTNCSTAR 1. WTC Investigation
The Design and Construction of the Towers

In October 1969, The Port Authority provided the following instructions to the contractor applying the sprayed fire protection, in order to maintain the Class 1-A Fire Rating of the NYC Building Code:

• 2 3/16 in. of BLAZE-SHIELD D for columns smaller than 14WF228'- and 1 3/16 in. for columns equal to or greater than 14WF228.

• Vi in. covering of BLAZE-SHIELD D for beams, spandrels and bar joists.

NIST's review of available documents has not uncovered the reasons for selecting BLAZE-SHIELD

fire-resistive material or the technical basis for specifying Vi in. thickness of SFRM for the floor trusses. As with the trusses. BLAZE-SHIELD DC/F was applied to the perimeter columns above the 38"^ floor of

WTC 1 and all the perimeter columns in WTC 2.

Core Columns and Beams

Multiple approaches were used to insulate structural elements in the core:

• Those core columns located in rentable and public spaces, closets, and mechanical shafts were enclosed in boxes of gypsum wallboard (and thus were inaccessible for inspection).

The amount of the gypsum enclosure in contact with the column varied depending on the location of the column within the core. SFRM (BLAZE-SHIELD D and DC/F) was applied on those faces that were not protected by the gypsum enclosure. The thicknesses specified in the construction documents were 13/16 in. for the heavier columns and 23/16 in. for the

lighter columns.

• Columns located at the elevator shafts were protected using the same SFRM thicknesses.

They were not enclosed and thus were accessible for routine inspections.

Inspection of the columns within the elevator shaft spaces in 1993 indicated some loss of SFRM

coverage. As a result, new insulation was applied to selected columns within the elevator shaft space. Information provided to NIST indicated that a different SFRM, Monokote Type 2-106, was used.

Thickness measurements for columns and beams below the 45"^ floor indicated average thicknesses of

0.82 in. and 0.97 in., respectively. Information from The Port Authority indicated that the minimum

required thickness of the re-applied SFRM was Vi in. for the columns and Va in. for the beams.

NIST w as unable to locate information from which to characterize the insulation of the core columns and

beams that were not accessible. Except as noted above, once completed, the core was generally not

inspected. NIST was not able to locate any post-collapse core beams or columns with sufficient insulation still attached to make pre-collapse thickness measurements.

Summary of SFRM on September 11, 2001

Table 5-2 summarizes the types and thicknesses of the SFRMs used in the towers. According to Port Authority documents, in the upper part of the towers, trusses on floors 92 through 100 and 102 in WTC 1

This designation indicates that the column is a 14 in. deep wide flange section and weighs 228 pounds per foot.

NIST NCSTAR 1, WTC Investigation 73
Chapter 5

had upgraded insulation by September 11, 2001. In WTC 2, truss insulation had been upgraded on

floors 77, 78, 85, 88, 89, 92, 96, 97, and 99.

Table 5-2. Types and locations of SFRM on fire floors.

Building Component Material

Thicl<ness (in.)

Specified" Installed Used in Analysis'*

FLOOR SYSTEM

Original

Main trusses and diagonal struts BLAZE-SHIELD DC/F 0.5 0.75 0.6

Bridging trusses (one-way zone)^ BLAZE-SHIELD DC/F 0.5 0.38'' 0.3

Bridging trusses (two-way zone)' BLAZE-SHIELD DC/F 0.5 0.38'' 0.6 Upgraded

Main tmsses BLAZE-SHIELD 11 1.5 2.5 2.2 Main truss diagonal struts BLAZE-SHIELD II 1.5 2.5 2.2

Bridging trusses BLAZE-SHIELD II 1.5 2.5 2.2 EXTERIOR WALL PANEL

Box columns

Exterior face BLAZE-SHIELD DC/F 1 3/16 (e) 1.2

Interior face Vemiiculite plaster 7/8 (e) 0.8

Spandrels

Exterior face BLAZE-SHIELD DC/F 0.5 (e) 0.5

Interior face Vermiculite plaster 0.5 (e) 0.5 CORE COLUMNS

Wide flange columns

Light BLAZE-SHIELD DC/F 2 3/16 (e) 2.2 Heavy BLAZE-SHIELD DC/F 1 3/16 (e) 1.2 Box columns

Light BLAZE-SHIELD DC/F (0 (e) 2.2<8' Heavy BLAZE-SHIELD DC/F (f) (e) 1.2'^» CORE BEAMS BLAZE-SHIELD DC/F 0.5 (e) 0.5

a. "Specified" means material and thicknesses detennined from correspondence among various parties.

b. The analysis is described in Chapter 6.

c. Not expressly specified. SFRM was required for the areas where the main trusses ran in both directions and, while not required, was

also applied in the areas where they ran in one direction only.

d. Analysis of photographs indicated that the thickness was approximately one half that on the main trusses.

e. Not able to detennine. f Not specified. '

g. Thickness assumed equal to wide flange columns of comparable weight per foot.

74 NISTNCSTAR 1, WTC Investigation
The Design and Construction of tlie Towers

5.7 CONCRETE

Two types of concrete were used for the floors of the WTC towers: lightweight concrete in the tenant

office areas and normal weight concrete in the core area. Because of differences in composition and

weight, the two types of concrete respond differently to elevated temperatures, as shown in Figure 5-7.

While their tensile strengths degrade identically, lightweight concrete retains more of its compressive

strength at higher temperatures. The degradation of concrete mechanical properties with temperature was

included in the structural response analysis of the floor systems.

6000 400

Figure 5-7. Temperature-dependent concrete properties.

5.8 THE TENANT SPACES

5.8.1 General

About 80 percent of the floors had a single tenant. Many of these floors were filled with arrays of

modular office cubicles, their low partitions affording sightlines to the windows, with perhaps an

occasional perimeter conference room or executive office in the way (Figure 1-11). Trading floors (Figure 1-12) had tables and computers throughout and food service areas to minimize time away from

the non-stop transactions. The remaining 20 percent of the floors were each subdivided among as many

as 25 tenants. Some of the approximately 25 tenants that occupied two or more contiguous floors

installed convenience stairways within their own space.

Certain floors were of special interest to the Investigation. These were the floors on which there was

structural damage from the aircraft and/or on which extensive fires were observed. These floors,

designated as focus floors, and the information NIST obtained regarding them are characterized in Table 5-3. Additional information, obtained from the tenant finns and The Port Authority, is summarized in the remainder of this chapter.

NISTNCSTAR 1. WTC Investigation 75
Chapter 5

5.8.2 Walls

The plans for the tenant spaces in WTC 1 showed no interior walls whose sole function was to subdivide

the floors. There were a number of partitioned offices and conference areas. Although NIST was not

able to obtain layout drawings for the fire floors in WTC 2, the verbal descriptions of those floors indicated similarly open space. The types of interior walls were described in Section 5.3.4.

5.8.3 Flooring

Truss-supported concrete slabs formed the floors in the office areas of the towers. Some tenants had

installed slightly raised (6 in.) floors on top of the slab under which communication cables were run. This was especially true on trading floors. There was a wide range of floor coverings in use. Inlaid wood and

marble were used in some reception areas. Most commonly, the expanse of the floor was covered with

nylon carpet.

5.8.4 Ceilings

There were two different ceiling tile systems originally installed in the towers under Port Authority

specification. The framing for each was hung from the bottom of the floor trusses, resulting in an

apparent room height of 8.6 ft and an above-ceiling height of about 3.4 ft. The tiles in the tenant spaces were 20 in. square, Va in. thick, lay-in pieces on an exposed tee bar grid system. The tiles in the core area were 12 in. square, V4 in. thick, mounted in a concealed suspension system. Neither system was specified

to be fire-rated, and it was estimated that in a fire they might provide only 10 min to 15 min of thermal

protection to the trusses before the ceiling frame distorted and the tiles fell. Chemically, the tiles were

similar, and their combustible content, flame spread, and smoke production were all quite low.

5.8.5 Furnishings

The decorating styles of the tower tenants ranged from simple, modular trading floors to customized office spaces. The most common

layout of the focus floors was a continuous

open space populated by a large array of

workstations or cubicles (Figure 1-11). The

number of different types of workstations in the two towers was probably large. However,

discussions with office furniture distributors

and visits to showrooms indicated that, while

there was a broad range of prices and

appearances, the cubicles were fundamentally

similar to that shown in Figure 5-8.

The workstations were typically 8 ft square, bounded on all four sides by privacy panels,

with an entrance opening in one side only.

Within the area defined by the panels was a

76 NISTNCSTAR 1. WTC Investigation
The Design and Construction of tlie Towers

self-contained workspace: desktop (almost always a wood product, generally with a laminated finish), file storage, bookshelves, carpeting, chair, etc. Presumably there were a variety of amounts and locations of

paper, both exposed on the work surfaces and contained within the file cabinets and bookshelves. The

cubicles were grouped in clusters or rows, with up to 2 1 5 units on a given floor.

NIST estimated the combustible fuel loading on these floors to have been about 4 lb/ft' (20 kg/m"), or about 60 tons per floor. This was somewhat lower than found in prior surveys of office spaces. The

small number of interior walls, and thus the minimal amount of combustible interior finish, and the limited bookshelf space account for much of the differences. While paper in the filing cabinets might

have been significant in mass, it did not bum readily due to the limited oxygen available within the drawers.

NISTNCSTAR 1, WTC Investigation 77
Chapter 5

o

St

(A3

O

O

o

(Ao

o

^ :2

.^2 <u £ u£

OJ-J

c« O

O "3

^ . o

r- t> O

E o ^

1/2 O

ao —

t/) OJ -3.

S 2 ^

CO ^03 a ^ ^ 3 -p o

O O

o IO o

o 3

2

« OS

t; S

^ ^ •£ 5 <^ O s„ (U

1/3 ti O 1) 1- tr- aj O

O S

. =

i/3 C

00 , S !3

=^ -J 13

•r' 1/3

oo

« _ o ,^

2 ^

(u o

ON

to "O

CO G

(U CO

o ~

CO

^ O

t/3 O

s ^

o ^ P

ON

aj ^

1> (U CO

C ON o 2 C/3 OJ r-

?3 H

O 'T3CO

CJ

.CO dj & 5

s ^

O _

CO S

CX O

>^ "3

"cO :2 3 -co U C c/3

CO

<U rON

ON

.2 o ON

(D </3

J1

"53

O

c« CO ijj U c« o

5^ 2 c

. n, ^

GO 5J l-c C c« <D .2 o -fi ^ . •£ O -r-J c/3

o C aj C

CJ VCO o

G.O C

"cO5 .s

C3N ^ o

o o 2-0

^ 2 co c O CO

^ -E

t^JZ S 2 o

.2 w n

g

§^^'

O V- ON

o O 5

D ~

o S «i rS ^ CO CO D

1/3 . S

t2 (u o

O -O cj > CO —

& 6

<U CO

CO -5

c« O

a. o

-3 .2 a § CO !^

CO

CO ac O CO

o 22

o u

-2 £

O

O c

O

o

cc

o

CJ

'—

CO GO

CO c2

o

co

r2

C/3 cn

we: oor co

CO o

CO o "2

-2

lo

00

C3N 00

CO "r- ON

c« ? 5

^ jg o

CO O

> ^

s ^

U3O

CO GO

1/3 u

go

)-i o

'Cu

to— 1«

C/3 QJ o £

^ o

-O O «J

>-

(D SO

^ o o

CO

i: 1/1 S ^ CO o

c/3 O

00 ON !'§

CO "3

c/1 ^

'

to -

' -2S;

X)S o

o -S U o

c/3 CO -O o 2

CO

o

o

00n

-3

CO

CO

I in

C) SI

to Ii- c 4, .- >

>

Cfi

CO u

s <^ Si

^ 2 ^

CO S 00

u

CJ

si

2"cO(UODN

O

n

CO U

78 NISTNCSTAR 1, WTC Investigation
The Design and Construction of the Towers

.2 ij

51

j: O

^3 O

5X) u

a o

>

O

. 3

-O o

g. COo

o —

o 1

-O O

'3 Oo

t/3 „

>

CQ O

>

>-

a

-J

5 J

o

/1J ^ ^

cu B ^ O X to >, " «

t« C«

5i S o

S g O S «

>

>

>

>

O

o

C3O

1 'i

•= a

.t: cij

° 1

>

I i

oc

>

>-

of

>

o

-o«

o

cpQ

"3

O

•a5

o

C3

CJ o CO

U

o

>

2

y «5 E

•- a ,? u ^ ^ -o °

u c

p C o I ^1

^ c/i (L) g

o i

5 1) o

-2 > o ^ '3; -a

5i S a a11

CJ o

'3 '-5 c C

C/5 Q. "H.

CO a

eb O o

O o

Q. Q. O o

1)

><

UJ

1) ~ u f f

C c o o

o o

_o _o E u. d

NISTNCSTAR 1, WTC Investigation 79
This page intentionally left blank.

NIST NCSTAR 1, WTC Investigation
Chapter 6

Reconstruction of the Collapses

6.1 APPROACH

The following presents an oven iew of the methods used to reach the accounts in Part 1. The details may

be foimd in the companion reports to this document, which are indexed in Appendix C. A substantial effort was directed at establishing the baseline perfonnance of the WTC towers, i.e., estimating the expected performance of the towers under normal design loads and conditions. This

enabled meeting the third objective of the Investigation, as listed in the Preface to this report. The

baseline performance analysis also helped to estimate the ability of the towers to withstand the unexpected events of September 11, 2001. Establishing the baseline performance of the towers began

with the compilation and analysis of the procedures and practices used in the design, construction,

operation, and maintenance of the structural, fire protection, and egress systems of the WTC towers. The

additional components of the performance analysis were:

• The standard fire resistance of the WTC truss-fi^amed floor system,

• The quality and properties of the structural steels used in the towers, and

• The response of the WTC towers to design gravity and wind loads.

The second substantial effort was the simulation of the behavior of each tower on September 1 1, 2001,

providing the basis for meeting the first and second objectives of the Investigation. This entailed four

modeling steps:

1. The aircraft impact into the tower, the resulting distribution ofjet fuel, and the damage to the

structure, partitions, insulation materials, and building contents.

2. The spread of the multi-floor fires.

3. The heating of the structural elements by the fires.

4. The response of the damaged and heated building structure, and the progression of structural component failures leading to the initiation of the collapse of the towers.

For such complex structures and complex thermal and structural processes, each of these steps stretched

the state of the technology and tested the limits of software tools and computer hardware. For example,

the investigators advanced the state-of-the-art in the measurement of construction material properties and

in structural finite element modeling. New modeling capability was developed for the mapping of fire- generated environmental temperatures onto the building structural components.

For the final analyses, four cases were used, each involving all four of the modeling steps. Case A and

Case B were for WTC 1 , with Case B generally involving more severe impact and fire conditions than

NISTNCSTAR 1, WTC Investigation 81
Chapter 6

Case A. For WTC 2, Case D involved more severe impact and fire conditions than Case C. The results of the two cases for each tower provided some understanding of the uncertainties in the predictions.

There were substantial uncertainties in the as-built condition of the towers, the interior layout and

furnishings, the aircraft impact, the internal damage to the towers (especially the insulation), the

redistribution of the combustibles, and the response of the building structural components to the heat from

the fires. To increase confidence in the simulation results, NIST used information from an extensive

collection of photographs and videos of the disaster, eyewitness accounts from inside and outside the

buildings, and laboratory tests involving large fires and the heating of structural components. Further,

NIST applied formal statistical methods to identify those parameters that had the greatest effect on the model output. These key inputs were then varied to detemiine whether the results were reasonably

robust.

The combined knowledge from all the gathered data and analyses led to the development of a probable

collapse sequence for each tower,' the identification of factors that contributed to the collapses, and a list of factors that could have improved building performance or otherwise mitigated the loss of life.

6.2 DEVELOPMENT OF THE DISASTER TIMELINE

Time was the unifying factor in combining photographic and video information, survivor accounts,

emergency calls from within the towers, and communications among emergency responders. The visual

evidence was the most abundant and the most detailed.

The destruction of the WTC towers was the most heavily photographed disaster in history. The terrorist attacks occurred in an area that is the national home base of several news organizations and has several

major newspapers. New York City is also a major tourist destination, and visitors often carry cameras to record their visits. Further, the very height that made the towers accessible to the approaching aircraft also made them visible to photographers. As a result there were hundreds of both professional and

amateur photographers and videographers present, many equipped with excellent equipment and the

knowledge to use it. These people were in the immediate area, as well as at other locations in New York

and New Jersey.

There was a surprisingly large amount of photographic material shot early, when only WTC 1 was

damaged. By the time WTC 2 was struck, the number of cameras and the diversity of locations had

increased. Following the collapse of WTC 2, the amount of visual material decreased markedly as people

rushed to escape the area and the huge dust clouds generated by the collapse obscured the site. There is a

substantial, but less complete, amount of material covering the period from the tower collapses to the

collapse of WTC 7 late the same afternoon.

' The focus of the Investigation was on the sequence of events from the instant of aircraft impact to the initiation of collapse for each tower. For brevity in this report, this sequence is referred to as the "probable collapse sequence," although it does not

actually include the structural behavior of the tower after the conditions for collapse initiation were reached and collapse

became inevitable.

82 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

There were multiple sources of visual material:

• Recordings of newscasts from September 1 1 and afterward, documentaries, and other

coverage pro\ ided information and also pointed toward other potential sources of material.

• Web sites of the major photographic clearinghouses.

• Local print media.

• NYPD and FDNY.

• Collections of visual material assembled for charitable or historical purposes.

• lndi\ iduals' photographs and videos that began appearing on the World Wide Web as early

as September 11, 2001.

• Responses to public appeals for visual material by the Investigation Team.

Investigation staff contacted each of the sources, requested the material, made arrangements for its transfer, and addressed copyright and privacy issues. Emphasis was placed on obtaining material in a form as close as possible to the original in order to maintain as much spatial and timing information as possible: direct digital copies of digital photographs and videos, high resolution digitized copies of film or

slide photographs, and direct copies from the original source of analog video.

The assembled collection included:

• 6,977 segments of video footage, totaling in excess of 300 hours. The media videos included

both broadcast material and outtakes. Additionally, NIST received videotapes recorded by more than 20 individuals.

• 6,899 photographs from at least 200 photographers. As with the videos, many of the photographs were unpublished.

This vast amount of visual material was organized into a searchable database in which each frame was

characterized by a set of attributes: photographer (name and location), time of shot/video, copyright

status, content (including building, face(s), key events (plane strike, fireballs,

collapse), the presence of FDNY or NYPD people or apparatus, and other

details, such as falling debris, people, and building damage).

The development of a timeline for fire growth and structural changes in the WTC buildings required the assignment of times of known accuracy to each

video frame and photograph. Images were timed to a single well-defined

event. Due to the large number of different views available, the chosen event was the moment the second plane struck WTC 2, established from the time

stamps in the September 1 1 telecasts. Based on four such video recordings,

the time of the second plane impact was established as 9:02:59 a.m.

The TV network clocks were quite close to the

actual time since they were regularly

updated from highly accurate

geopositioning

satellites or the

precise atomic-clockbased timing signals

provided by NIST as a

public service.

NISTNCSTAR 1, WTC Investigation 83
Chapter 6

Absolute times were then assigned to all frames of all videos that showed the second plane strike. By

matching photographs and other videos to specific events in these initially assigned videos, the time

assignments were extended to visual materials that did not include the primary event. Times were also

cross-matched using additional characteristics, such as the appearance and locations of smoke and fire plumes, distinct shadows cast on the buildings by these plumes, the occurrence of well-defined events such as a falling object, and even a clock being recorded in an image. By such a process, it was possible

to place photographs and videos extending over the entire day on a single timeline. As the time was

assigned to a particular photograph or video, the uncertainty in the assignment was also logged into the

database. In all, 3,032 of the catalogued photographs and 2,673 of the video clips in the databases were

timed with accuracies of + 3 s or better.

This process enabled establishing the times of four major events of September 11, listed in Table 6-1.

The building collapse times were defined to be the point in time when the entire building was first observed to start to collapse.

6-1. Times for major events on September 11

Event Time

First Aircraft Strike 8:46:30 a.m. Second Aircraft Strike 9:02:59 a.m.

Collapse ofWTC2 9:58:59 a.m.

Collapse ofWTC 1 10:28:22 a.m.

There were additional sources of timed infonnation. Phone calls from people within the building to

relatives, friends, and 9-1-1 operators conveyed observations of the structural damage and developing

hazards. Communications among the emergency responders and from the building fire command centers contributed further information about the areas where the external photographers had no access.

6.3 LEARNING FROM THE VISUAL IMAGES

The photographic and video images were rich sources of information on the condition of the buildings

following the aircraft impact, the evolution of the fires, and the deterioration of the structure. To enable

analysis of this information, a shorthand notation (based on the building design drawings) was used to label the exterior columns and windows of the buildings:

• First, the faces of the towers were numbered in a manner identical to those used in the

original plans:

WTC 1: north:! east: 2 south: 3 west: 4

WTC 2: west: 1 north: 2 east: 3 south: 4

• The 59 columns across each tower face were assigned three-digit numbers. Following the

floor number, the first digit was that of the face, and the remaining two digits were assigned

consecutively from right to left as viewed from outside the building. Thus, the fourth column

from the right on the east face of the 81'' floor of WTC 1 was labeled 81-204.

84 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

• Each of the 58 windows on each floor and tower face was assigned the number of the column

to its right as viewed from the outside of the building and was also identified by its floor. Thus the rightmost window on the east face of the 94"' floor of WTC 1 was labeled 94-201

.

As an example of information that was extracted, Figure 6-1 shows an enhanced image of the east face of

WTC 2. Figure 6-2 expands a section of interest. The amount of detail available is evident. For

instance, large piles of debris are present on the north side of the tower on the 80* and 81^' floors, and

locations where fires are visible or where missing windows are easily identified. Many details of each

frame were important in tracking the evolution of the fires and the damage to the buildings.

I n 1 1 1 1 1 1 1 1 1 1 1 ( I n I Ml / IT 1 1 j 1 1 1 i ll 1 1 ) H I

Note: Enhancements by NIST

Figure 6-1 . 9:26:20 a.m. showing the east face of WTC 2.

In each photograph and each video frame, each window was also coded to indicate whether the window

was still in place or not and the extent to which flames and smoke were visible. Color-coded graphics of

the four facades of the two towers were then constructed. Examples of these graphics were shown in Chapters 2 and 3.

The results of the visual analysis included:

• The locations of the broken windows, providing information on the source of air to feed the

fires within.

• Observations of the spread of fires.

• Documentation of the location of exterior damage from the aircraft impact and subsequent

structural changes in the buildings.

NISTNCSTAR 1, WTC Investigation 85
Chapter 6

Note: Enhancements by NIST.Figure 6-2. Close-up of section of Figure 6-1.

• Identification of the presence or absence of significant floor deterioration at the building

perimeter.

• Observations of certain actions by building occupants, such as breaking windows.

The near-continuous observations of the externally visible fires provided input to the computer

simulations of fire growth and spread. The discrete observations of changes in the displacement of

columns and, to a far lesser degree, floors became validation data for the modeling of the approach to structural collapse of the towers. Table 6-2 lists the most important observations.

6.4 LEARNING FROM THE RECOVERED STEEL

6.4.1 Collection of Recovered Steel

NIST had two reasons for obtaining specimens of structural steel from the collapsed towers. The primary

objective was characterizing the quality of the steel and determining its properties for use in the structural modeling and analysis of the collapse sequences. The second reason was obtaining infomiation regarding

the behavior of the steel in the aircraft impact zone and in areas which had major fires.

86 NISTNCSTAR 1. WTC Investigation
Reconstruction of the Collapses

Table 6-2. Indications of major structural changes up to collapse initiation.

Tower Time (a.m.) Observation

WTC 1

10:18 Smoke suddenly expelled on the north face (floors 92, 94, 95 to 98) and west face (92, 94 to 98).

10:23 Inward bowing of perimeter columns on the east side of the south face from floors 94

to 100; maximum extent: 55 in. ± 6 in. at floor 97.

10:28:22

First exterior sign of collapse (downward movement of building exterior). Tilting of the building section above the impact and fire area to due south as the strucmral collapse initiated. First exterior sign of downward movement of building at floor 98.

WTC2

9:02:59

Exterior fireball from the east face of floor 82 and from the north face from floors 79

to 82. The deflagration prior to the fireballs may have caused a significant pressure pulse to act on floors above and below.

9:21 Inward bowing of exterior wall columns on most of the east face from floors 78 to 83; maximum extent: 7 in. to 9 in. at floor 80.

9:58:59

First exterior sign of collapse (downward movement of building exterior). The northeast comer tilted counterclockwise around the base of floor 82. Column

buckling was then seen progressing across the north face and nearly simultaneously on

the east face. Tilting of the building section above the impact and fire area to the east and south

prior to significant downward movement of the upper building section. The tilt to the south did not increase any further as the upper building section began to fall, but the

tilt to the east did increase until dust clouds obscured the view.

Within weeks of the destruction of the WTC. contractors of New York City had begun cutting up and

removing the debris from the site. Members of the FEMA-sponsored and ASCE-led Building

Performance Assessment Team, members of the Structural Engineers Association of New York, and

Professor A. Astaneh-Asl of the University of California, Berkeley, CA, with support from the National

Science Foundation, had begun work to identify and collect WTC structural steel from various recycling

yards where the steel was taken during the clean-up effort. The Port Authority of New York and New

Jersey (Port Authority) also collected structural steel elements for future exhibits and memorials.

Over a period of about 1 8 months, 236 pieces of steel were shipped to the NIST campus, starting about

six months before NIST launched its Investigation. These samples ranged in size and complexity from a nearly complete three-column, three-floor perimeter assembly to bolts and small fragments. Figures 6-3

through 6-5 show some of the recovered steel pieces. Seven of the pieces were from WTC 5. The

remaining 229 samples represented roughly 0.25 percent to 0.5 percent of the 200,000 tons of structural

steel used in the construction of the two towers.

The collection at NIST included samples of all the steel strength levels specified for the construction of

the towers. The locations of all structural steel pieces in WTC 1 and WTC 2 were uniquely identified by

stampings (recessed letters and numbers) and/or painted stencils. NIST was successful in finding and

deciphering these identification markings on many of the perimeter panel sections and core columns, in many cases using metallurgical characterization to complete missing identifiers. In all, 42 exterior panels were positively identified: 26 from WTC 1 and 16 from WTC 2. Twelve core columns were positively

identified: eight from WTC 1 and four from WTC 2. Twenty-three pieces were identified as being parts

of trusses, although it was not possible to identify their locations within the buildings.

NISTNCSTAR 1, WTC Investigation 87
Chapter 6

Source: NIST. Figure 6-3. Examples of a WTC 1 core column (left) and truss material (right).

Source: NIST. Figure 6-4. WTC 1 exterior panel hit by the fuselage of the aircraft.

Overlaying the locations of the specimens with photographs of the building exteriors following the

aircraft impact (for perimeter columns and spandrels) and the extent-of-damage estimates (Section 6.8)

(for core columns) enabled the identification of steel pieces near the impact zones. These included five specimens of exterior panels from WTC 1 and two specimens of core columns from each of the towers.

6.4.2 Mechanical and Physical Properties

NIST determined the properties of many of the recovered pieces for comparison with the original

purchase requirements, comparison with the quality of steel from the WTC construction era, and input to the structural models used in the Investigation. Structural steel literature and producers' documents were

used to establish a statistical basis for the variability expected in steel properties.

88 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

The properties of the steel samples tested were

consistent with the specifications called for in the

steel contracts. In particular, the yield strengths of

all samples of the floor trusses were higher than

called for in the original specifications. This was in part because the truss steels were supplied as a higher grade than specified. Overall, approximately

87 percent of all perimeter and core column steel tested exceeded the required minimum yield

strengths specified in design documents. Test data

for the remaining samples were below specifications,

but were within the expected variability and did not

affect the safety of the towers on

September 11, 2001. Furthermore, lower strength

values measured by NIST could be expected due to

(a) differences in test procedures from those used in the qualifying mill tests and (b) the damaged state of

the samples. The values of other steel properties were similar to typical construction steels of the WTC construction era. The limited tests on bolts indicated that their strengths were greater than the specified minimum, and they were stronger than

contemporaneous literature would suggest as typical.

The tested welds performed as expected.

NIST measured the stress-strain behavior at room

temperature (for modeling baseline performance),

high temperature strength (for modeling structural response to fire), and at high strain rates (for

modeling the aircraft impact). Based on data from

published sources, NIST estimated the thermal

properties of the steels (specific heat, thermal conductivity, and coefficient of thermal expansion) and

creep behavior for use in the structural modeling of the towers' response to fire.

6.4.3 Damage Analysis

NIST performed extensive analyses of the recovered steel specimens to determine their damage

characteristics, failure modes, and (for those near the fire zones) fire-related degradation. In some cases, assessment of enhanced photographic and video images of the towers enabled distinguishing between

damage that occurred prior to the collapse and damage that occurred as a result of the collapse. Because

the only visual evidence was from the outside of the buildings, this differentiation was only possible for the perimeter panel sections. The observations of fracture and failure behavior, confirmed by an

Investigation contractor, were also used to guide the modeling of the towers' performance during impact

and subsequent fires and to evaluate the model output.

Source: NIST. Figure 6-5. WTC 1 exterior panel hit by

the nose of the aircraft.

NISTNCSTAR 1, WTC Investigation 89
Chapter 6

For two of the five exterior panels from the impact zone of WTC 1 , the general shape and appearance of

the recovered pieces matched photographs taken just before the building collapse. Thus, NIST was able

to attribute the observed damage to the aircraft impact. NIST also made determinations regarding the connections between structural steel elements:

• There was no evidence to indicate that the joining method, weld materials, or welding

procedures were inadequate. Fractures of the columns in areas away from a welded joint were the result of stretching and thinning. Perimeter columns hit by the plane tended to fracture along heat-affected zones adjacent to welds.

• The failure mode of spandrel connections varied. At or above the impact zone, bolt hole tear- out was more common. Below the impact zone, it was more common for the spandrels to be

ripped from the panels. There was no evidence that fire exposure changed these failure modes.

• The exterior column splices at the mechanical floors, which were welded in addition to being

bolted, generally did not fail. The column splices at the other floors generally failed by bolt

fracture. :

• The perimeter truss connectors (or seats) below the impact zone in WTC I were

predominantly bent down or torn off completely. Above the impact zone, the seats were as

likely to be bent upward as downward. Core seats could not be categorized since their asbuilt locations could not be detennined.

• Failure of core columns was a result of both splice connection failures and fracture of the

columns themselves.

Examination of photographs showed that 1 6 of the exterior panels recovered from WTC 1 were exposed

to fire prior to the building collapse. None of the nine recovered panels from within the fire floors of

WTC 2 were directly exposed to fire. NIST used two methods to estimate the maximum temperatures

that the steel members had reached:

• Observations of paint cracking due to thermal expansion. Of the more than 170 areas examined on 16 perimeter column panels, only three columns had evidence that the steel reached temperatures above 250 °C: east face, floor 98, inner web; east face, floor 92, inner

web; and north face, floor 98, floor truss connector. Only two core column specimens had

sufficient paint remaining to make such an analysis, and their temperatures did not reach

250 °C. NIST did not generalize these results, since the examined columns represented only

3 percent of the perimeter columns and 1 percent of the core columns from the fire floors.

• Observations of the microstructure of the steel. High temperature excursions, such as due to a fire, can alter the basic structure of the steel and its mechanical properties. Using

metallographic analysis, NIST determined that there was no evidence that any of the samples

had reached temperatures above 600 °C.

90 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

These results were for a very small fraction of the steel in the impact and fire zones. Nonetheless, these

analyses indicated some zones within WTC 1 where the computer simulations should not, and did not, predict highly elevated steel temperatures.

6.5 INFORMATION GAINED FROM OTHER WTC FIRES

There had been numerous fires in the towers prior to September 11, 2001. From these, NIST learned

what size fire WTC 1 and WTC 2 had withstood and how the tower occupants and the responders

functioned in emergencies. While The Port Authority's records of prior fires were lost in the collapses,

FDNY provided reports on 342 fires that had occurred between 1970 and 2001.

Most of these fires were small, and occupants extinguished many of them before FDNY arrival. Forty- seven of these fires activated one to three sprinklers and/or required a standpipe hose for suppression.

Only two of the fires required the evacuation of hundreds of people. There were no injuries or loss of life in any of these fires, and the interruptions to operations within the towers were local. A major fire occurred in WTC 1 on February 13, 1975, before the installation of the sprinkler system. A

furniture fire started in an executive office in the north end of an 11 floor office suite in the southeast comer of the building. The fire spread south and west along corridors and entered a file room. The fire flashed over, broke seven windows, and spread to adjacent offices north and south. The air conditioning

system turned on, pulling air into the return air ducts. Telephone cables in the vertical shafts were

ignited, destroying the fire-retarded wood paneling on the closet doors. The fire emerged on the 12"^ and

13"^ floors, but there was little nearby that was combustible. The fire also extended vertically from the 9""

to the 19* floors within the telephone closet. Eventually the fire was confined to 9,000 ft^ of one floor,

about one-fourth of the total floor area. The trusses and columns in this area had been sprayed with

BLAZE-SHIELD D insulation to a specified Yi in. thickness. Four trusses were slightly distorted, but the

structure was not threatened.

Only one major fire incident resulted in a whole-building evacuation. At 12:18 p.m. on February 26,

1993, terrorists exploded a bomb in the second basement underground parking garage in the WTC

complex. The blast immediately killed six people and caused an estimated $300 miUion in damage. An

intense fire followed and, although the flames were confined to the subterranean levels, the smoke spread

into four of the seven buildings in the WTC complex. Most of the estimated 150,000 occupants

evacuated the buildings, including approximately 40,000 from the affected towers. In all, 1,042 people were injured in the incident, including 15 who received blast-related injuries. The evacuation of the towers took over 4 hours. The incident response involved more than 700 firefighters (approximately

45 percent of FDNY' s on-duty personnel at the time).

In addition, there was a fire on the 104* floor of WTC 1 on September 1 1, 2001, that apparently did not

contribute to the eventual collapse, yet was quite severe. At 10:01 a.m., flames were first observed on the west face, and by 10:07 a.m., intense flames were emanating from several windows in the southern third of that face. The fire raged until the building collapsed at 10:28 a.m. Thus, the tower structure was able

to withstand a sizable fire for about 20 min, presumably with the ceiling tile system heavily damaged and

the truss system exposed to the flames. The 104* floor was well above the aircraft impact zone, so there should have been little damage to the sprayed fire-resistive material, which was the same (Table 5-3) as

NISTNCSTAR 1, WTC Investigation 91
Chapter 6

on the floors where the fires led to the onset of the collapse. The photographic evidence showed no signs

of column bowing or a floor collapse.

6.6 THE BUILDING STRUCTURAL MODELS

6.6.1 Computer Simulation Software

Structural modeling of each tower was required in order to:

• Establish the capability of the building, as designed, to support the gravity loads and to resist wind forces;

• Simulate the effects of the aircraft impacts; and

• Reconstruct the mechanics of the aircraft impact damage, fire-induced heating, and the

progression of local failures that led to the building collapse.

The varied demands made different models necessary, and different software packages were used for each

of these three functions. The reason for the choice in each case is presented in the next three sections of

the report.

6.6.2 The Reference Models

Under contract to NIST, Leslie E. Robertson Associates (LERA) constructed a global reference model of

each tower using the SAP2000, version 8, software. SAP2000 is a software package for performing finite element calculations for the analysis and design of building structures. These global, three-dimensional

models encompassed the 110 stories above grade and the six subterranean levels. The models included

primary structural components in the towers, resulting in tens of thousands of computational elements.

The data for these elements came from the original structural drawing books for the towers. These had

been updated through the completion of the buildings and also included most of the subsequent,

significant alterations by both tenants and The Port Authority. LERA also developed reference models of

a truss-framed floor, typical of those in the tenant spaces of the impact and fire regions of the buildings,

and of a beam-framed floor, typical of the mechanical floors.

LERA's work was reviewed by independent experts in light of the firm's earlier involvement in the WTC

design. It was that earlier work, in fact, that made LERA the only source that had the detailed knowledge

of the design, construction, and intended behavior of the towers over their entire 38-year life span. The

accuracy of the four models was checked in two ways:

• The two global models were checked by Skidmore, Owings & Merrill (SOM), also under

contract to NIST, and by NIST staff This entailed ensuring consistency of the models with

the design documents, and testing the models, for example, to ensure that the response of the models to gravity and wind loads was as intended and that the calculated stresses and

deformations under these loads were reasonable.

• The global model of WTC 1 was used to calculate the natural vibration periods of the tower. These values were then compared to measurements from the tower on eight dates of winds

92 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

ranging from 1 1.5 mph to 41 mph blowing from at least four different directions. As shown

in Table 6-3, the N-S and E-W values agreed within 5 percent and the torsion values agreed

within 6 percent, both within the combined uncertainty in the measurements and calculations.

• SOM and NIST staff also checked the two floor models for accuracy. These reviews

involved comparison with simple hand calculations of estimated deflections and member

stresses for a simply supported composite truss and beam under gravity loading. For the

composite truss sections, the steel stress results were within 4 percent of those calculated by

SAP2000 for the long-span truss and within 3 percent for the short-span truss. Deflections

for the beams and trusses matched hand calculations to within 5 percent to 1 5 percent. These

differences were within the combined uncertainty of the methods.

Table 6-3. Measured and calculated natural vibration periods (s) for WTC 1. Direction of Motion

N-S E-W Torsion

Average of Measured Data 11.4 10.6 4.9

Original Predicted Values 11.9 10.4 Reference Global Model Predictions 1 1.4 10.7 5.2

The few discrepancies between the developed models and the original design documents, as well as the areas identified by NIST and SOM as needing modification, were corrected by LERA and approved by

NIST. The models then serv ed as references for more detailed models for aircraft impact damage

analysis and for theraial-structural response and collapse initiation analysis.

NIST also used these global reference models to establish the baseline performance of the towers under

gravity and wind loads. The two key perfonnance measures calculated were the demand-to-capacity ratio (DCR) and the drift.

• Demand is defined as the combined effects of the dead, live, and wind loads imposed on a

structural component, e.g., a column. Capacity is the permissible strength for that component. Normal design aims at ensuring that DCR values for all components be I.O or lower. A value of DCR greater than 1 .0 does not imply failure since designs inherently

include a margin of safety.

• Drift is the extent of sway of the building under a lateral wind. Excessive deflection can

cause cracking of partitions and cladding, and, in severe cases, building instability that could

affect safety.

Using SAP2000, NIST found that, under original WTC design loads, a small fraction of the structural components had DCR values greater than 1.0. (Most DCR values of that small fraction were less than

1 .4. with a few as high as 1 .6.) For the perimeter columns, DCR values greater than 1.0 were mainly near

the comers, on floors near the hat truss, and below the 9"' floor. For the core columns, these members

were on the 600 line between floors 80 and 106 and at core perimeter columns 901 and 908 for much of

their height. (See Figure 1-5 for the column numbers.) One possible explanation to the cause of DCRs in excess of 1 .0 may lie in the computer-based structural analysis and software techniques employed for this

NISTNCSTAR 1, WTC Investigation 93
Chapter 6

baseline perfonnance study in comparison with the relatively rudimentary computational tools used in the

original design nearly 40 years ago.

As part of its wind analysis, NIST calculated the drift at the top of the towers to be about 5 ft in a nearly

100 mph wind—the wind load used in the original design. Common practice was, and is, to design for substantially smaller deflections; but drift was not, and still is not, a design factor prescribed in building

codes.

The estimation of wind-induced loads on the towers emerged as a problem. Two sets of wind tunnel tests and analyses were conducted in 2002 by independent laboratories as part of insurance litigation unrelated

to the NIST Investigation. The estimated loads differed by as much as 40 percent. NIST analysis found

that the two studies used different approaches in their estimations. This difference highlighted limitations

in the current state of practice in wind engineering for tall buildings and the need for standards in the field of wind tunnel testing and wind effects estimation.

6.6.3 Building Structural Models for Aircraft Impact Analysis

Ideally, the Investigation would have used the reference global models of the towers as the "targets" for the aircraft. However, this was not possible. The impact simulations required inclusion of both a far higher level of detail of the building components and also the highly nonlinear behavior of the tower and

aircraft materials, and the larger model size could not be accommodated by the SAP2000 program. There were also physical phenomena for which algorithms were not available in this software. Another finite element package, LS-DYNA, satisfied these requirements and was used for the impact simulations.

Early in the effort, it became clear to both NIST and to ARA, Inc., the NIST contractor that performed the

aircraft impact simulations, that the model had to "fit" on a state-of-the-art computer cluster and to run

within weeks rather than months. To minimize the model size while keeping sufficient fidelity in the impact zone to capture the building deformations and damage distributions, various tower components

were depicted with different meshes (different levels of refinement). For example, tower components in the path of the impact and debris field were represented with a fine mesh (higher resolution) to capture the

local impact damage and failure, while components outside the impact zone were depicted more coarsely,

simply to capture their structural stiffness and inertial properties. The model of WTC 1 included floors 92

through 100; the model of WTC 2 extended from floor 77 through floor 85. The combined tower and

aircraft model of more than two million elements, at time steps ofjust under a microsecond, took

approximately two weeks of computer time on a 12-noded computer cluster to capture the needed details of the fraction of a second it took for the aircraft and its fragments to come to rest inside the building.

The structural models, partially shown in Figures 6-6 through 6-9, included:

• Core columns and spliced column connections;

• Floor slabs and beams within the core;

• Exterior columns and spandrels, including the bolted connections between the exterior panels

in the refined mesh areas; and

• Tenant space floors, composed of the combined floor slab, metal decking, and steel trusses.

94 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

They also included representations of the interior partitions and workstations. The live load mass was

distributed between the partitions and cubicle workstations.

Figure 6-6. Structural model of the 96*'' floor of WTC 1.

Workstations Modeled

over Truss Floor Area

Figure 6-7. Model of the 96*^ floor of WTC 1, including interior contents and partitions.

NISTNCSTAR 1, WTC Investigation 95
Chapter 6

^ Side 100 Figure 6-8. Multi-floor global model of WTC 1, viewed from the north.

Figure 6-9. Multi-floor global model of WTC 2, viewed from the south.

96 NISTNCSTAR 7, WTC Investigation
Reconstruction of the Collapses

Within these models, it was critical that the structural and furnishing materials behaved correctly when

impacted by the aircraft or debris. For each grade of steel, the stress-strain behavior and the yield strength were represented using data from tests conducted at NIST. The weakening and failure of the concrete

floor slabs were simulated using material models embedded in LS-DYNA. The primary influence of the nonstructural components on the impact behavior was their inertial contribution. Values for the resistance

to rupture of gypsum panels and the fracture of the wood products in the workstations were obtained from

published studies.

fri order to complete the global models of the two towers, models of sections of the buildings were

developed. As shown in Section 6.8.1, these submodels enabled efficient identification of the principal features of the interaction of the buildings with specific aircraft components.

6.6.4 Building Structural Models for Structural Response to Impact Damage and Fire

and Collapse Initiation Analysis

The structural response and collapse analysis of the towers was conducted in three phases by NIST and

Simpson Gumpertz & Heger, Inc. (SGH), under contract to NIST. The first phase included component

and detailed subsystem models of the floor and exterior wall panels. The objectives of Phase 1 were to gain understanding into the response of the structure under stress and elevated temperatures, identify

dominant modes of failure, and develop reductions in modeling complexity that could be applied in Phase 2. The second phase analyzed major subsystem models (the core framing, a single exterior wall,

and full tenant floors) to provide insight into their behavior within the WTC global system. The third phase was the analysis of global models of WTC 1 and WTC 2 that took advantage of the knowledge

gained from the more detailed and subsystem models. A separate global analysis of each tower helped

determine the relative roles of impact damage and fires with respect to structural stability and sequential

failures of components and subsystems and was used to determine the probable collapse initiation sequence.

Phase 1: Component and Detailed Subsystem Analyses

Floor Subsystem Analysis

The floors played an important role in the structural response of the WTC towers to the aircraft iinpact

and ensuing fires. Prior to the development of a floor subsystem model, three component analyses were

conducted, as follows:

• Truss seats. Figure 6-10 shows how an exterior seat connection was represented in the finite element structural model. The component analysis determined that failure could occur at the bolted connection between the bearing angle and the seat angle, and the truss could slip off

the seat. Truss seat connection failure from vertical loads was found to be unlikely, since the needed increase in vertical load was unreasonable for temperatures near 600 °C to 700 °C.

• Knuckles. The "knuckle" was formed by the extension of the truss diagonals into the concrete slab and provided for composite action of the steel truss and concrete slab. A model was developed to predict the knuckle performance when the truss and concrete slab acted

compositely.

NISTNCSTAR 1, WTC Investigation 97
Figure 6-10. Finite element model of an exterior truss seat.

Single composite truss and concrete slab section. A floor section was modeled to investigate

failure modes and sequences of failures under combined gravity and thermal loads. The floor section was heated to 700 °C (with a linear thennal gradient through the slab thickness from

700 °C to 300 °C at the top surface of the slab) over a period of 30 min. Initially the thermal

expansion of the floor pushed the columns outward, but with increased temperatures, the

floor sagged and the columns were pulled inward. Knuckle failure was found to occur mainly at the ends of the trusses and had little effect on the deflection of the floor system.

Figure 6-1 1 shows that the diagonals at the core (right) end of the truss buckled and caused an increase in the floor system deflection, ultimately reaching approximately 42 in. Two

possible failure modes were identified for the floor-truss section: sagging of the floor and loss of truss seat support.

-42.11 -32.603 -23.095 -13.588 -4.081 -37.357 -27.849 -18.342 -8.834 .673211

Figure 6-11. Vertical displacement at 700 °C.

NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

A finite element model of the full 96' floor of WTC 1 was translated from the SAP2000 reference models

into ANSYS 8.1 for detailed structural evaluation (Figure 6-12)'^. The two models generated comparable

predictions of the behavior under dead or gravity loads.

Figure 6-12. ANSYS model

of 96'^ floor of WTC 1.

The model was used to evaluate structural response under dead and live loads and elevated temperatures,

identify failure modes and associated temperatures and times to failure, and identify reductions in modeling complexity for global models and analyses. The structural response included thennal expansion

of steel and concrete members, temperature-dependent properties of steel and concrete that affected

material stiffness and strength, and bowing or buckling of structural members. The deformation and

failure modes identified were floor sagging between truss supports, floor sagging resulting from failure of

a seat at either end of the truss, and failure of the floor subsystem truss supports.

Exterior Wall Subsystem

The exterior walls played an important role in each tower's reaction to the aircraft impact and the ensuing

fires. Photographic and video evidence showed inward bowing of large sections of the exterior walls of

both towers just prior to the time of collapse.

A finite element model of a wall section was developed in ANSYS for evaluation of structural response

under dead and live loads and elevated structural temperatures, determination of loads that would have

caused buckling, and identification of reductions of modeling complexity for global models and analyses.

The modeled unit consisted of seven full column/spandrel panels (described in Section 1.2.2) and portions

of four other panels. The model was validated against the reference model developed by LERA

(Section 6.6.2) by comparing the stiffness for a variety of loading conditions.

ANSYS allowed including the temperature-varying properties of the structural materials, a necessary feature not available in SAP 2000.

NISTNCSTAR 1, WTC Investigation 99
Chapter 6

The model was subjected to several gravity loads and heating conditions, several combinations of

disconnected floors, and pull-in from sagging floors until the point of instability. In one case, the simulation assumed three disconnected floors, and the top of the wall subsystem was subjected to "pushdown" analysis, i.e., an increasing force to provide a measure of remaining capacity in the wall section.

The model captured possible failure modes due large lateral deformations, column buckling from loss of

support at floor truss seats and diagonal straps, failure of column splice bolts, and failure of spandrel

splice bolts or tearing of spandrel or splice plates at boh holes. The model also showed:

• Large deformations and buckling of the spandrels could be expected at high temperatures, but

they did not significantly affect the stability of the exterior columns and generally did not need to be precisely modeled in the tower models.

• Partial separations of the spandrel splices could be expected at elevated temperatures, but

they also did not significantly affect the stability of the exterior columns.

• Exterior column splices could be expected to fail at elevated temperatures and needed to be

accurately modeled.

• Plastic buckling of columns, with an ensuing rapid reduction of load, was to be expected at extremely high loads and at low temperatures.

• The sagging of trusses resulted in approximately 14 kip of inward pull per truss seat on the

attached perimeter column.

Phase 2: Major Subsystem Analyses

Building on these results, ANSYS models were constructed of each of the three major structural subsystems (core framing, a single exterior wall, and full composite floors) for each of the towers. The

models were subjected to the impact damage and elevated temperatures from the fire dynamics and

thermal analyses to be described later in this chapter.

Core Framing

The two tower models included the core columns, the floor beams, and the concrete slabs from the impact

and fire zones to the highest floor below the hat truss structure: from the 89'*' floor to the 106"' floor for WTC 1 and from the 13"^ floor to the 106"' floor for WTC 2. Within these floors, aircraft-damaged

structural components were removed. Below the lowest floors, springs were used to represent the

stiffness of the columns. In the models, the properties of the steel varied with temperature, as described in Section 5.5.2. This allowed for realistic structural changes to occur, such as thennal expansion, buckling,

and creep.

The forces applied to the models included gravity loads applied at each floor, post-impact column forces

applied at the top of the model at the 106"' floor, and temperature histories applied at 10 min intervals with linear ramping between time intervals.

100 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

Under these conditions, the investigators first detennined the stability of the core under impact conditions

and then its response under thermal loads:

• In WTC 1 , the core was stable under Case A (base case) impact damage, but the model could

not reach a stable solution under Case B (more severe) impact damage.

• The WTC 1 core became unstable under Case A impact damage and Case B thermal loads as

it leaned to the northwest (due to insulation dislodged from the northwest comer column); the core model was restrained in horizontal directions at floors above the impact zone half way

through the thermal loads.

• The WTC 2 core was stabilized for Case C (base case) by providing horizontal restraint at all floors representing the restraint provided by the perimeter wall to resist leaning to the southeast. A converged, stable solution was not found for Case D (more severe) impact

damage.

• The WTC 2 stabilized core model for Case C impact damage was subjected to Case D

thermal loads.

Following each simulation, a pushdown analysis was performed to determine the core's reserve capacity.

The analysis results showed that:

• The WTC 1 isolated core structure was most weakened from thermal effects at the center of

the south side of the core. (Smaller displacements occurred in the global model due to the

constraints of the hat truss and floors.)

• The WTC 2 isolated core was most weakened from thennal effects at the southeast comer

and along the east side of the core. (Larger displacements occurred in the global model as the

isolated core model had lateral restraints imposed that were somewhat stiffer than in the global model.)

Composite Floor

The composite floor model was used to determine the response of a full floor to Case A and B thermal

loads for WTC 1 floors and Case C and D thermal loads for WTC 2 floors. It included:

• A reduced complexity truss model, validated against the single tmss model results.

• Primary and bridging trusses, deck support angles, spandrels, core floor beams, and a concrete floor slab.

• Fire-generated local temperature histories applied at 10 min intervals with linear ramping

between time intervals.

• Temperature-dependent concrete and steel properties, except for creep behavior.

NISTNCSTAR 1. WTC Investigation 101
Chapter 6

• Restraint provided by exterior and core columns, which extended one floor above and below

the modeled floor. The potential for large deflections and buckling of individual structural members and the floor system were included.

The results showed that: a

• At lower elevated temperatures (approximately 100 °C to 400 °C), the floors thermally

expanded and displaced the exterior columns outward by a few inches; horizontal

displacement of the core columns was insignificant. None of the floors buckled as they

thermally expanded, even with the exterior columns restrained so that no horizontal

movement was allowed at the floors above and below the heated floor, which maximized

column resistance to floor expansion. Even with this level of column restraint, the exterior

columns did not develop a sufficient reaction force (push inward to resist the expansion

outward) to buckle any of the floors.

• At higher elevated temperatures (above 400 °C), the floors began to sag as the floors'

stiffness and strength were reduced with increasing temperature, and the difference in thermal

expansion between the trusses and the concrete slab became larger. As the floor sagging

increased, the outward displacement of the exterior columns was overcome, and the floors exerted an inward pull force on the exterior columns.

• Floor sagging was caused primarily by either buckling of truss web diagonals or disconnection of truss seats at the exterior wall or the core perimeter. Except for the truss seat failures near the southeast comer of the core in WTC 2 following the aircraft impact,

web buckling or truss seat failure was caused primarily by elevated temperatures of the

structural components.

• Analysis results from the detailed truss model found that the floors began to exert inward pull

forces when floor sagging exceeded approximately 25 in. for the 60 ft floor span.

• Sagging at the floor edge was due to loss of vertical support at the truss seats. The loss of

vertical support was caused in most cases by the reduction in vertical shear capacity of the

truss seats due to elevated steel temperatures.

• Case B impact damage and thermal loads for WTC 1 floors resulted in floor sagging on the

south side of the tower over floors that reasonably matched the location of inward bowing

observed on the south face. Case A impact damage and thermal loads did not result in sagging on the south side of the floors.

• Cases C and D impact damage and thermal loads for WTC 2 both resulted in floor sagging on

the east side of the tower over floors that reasonably matched the location of inward bowing

observed on the east face. However, Case D provided a better match.

102 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

Exterior Wall

Exterior wall models were developed for the south face of WTC 1 (floors 89 to 106) and the east face of

WTC 2 (floors 73 to 90). These sections were selected based on photographic evidence of column

bowing.

Many of the simulation conditions were similar to those for the isolated core modeling: removal of

aircraft-damaged structural components, representation of lower floors by springs, temperature-varying

steel properties, gravity loads applied at each floor, post-impact column forces applied at the 106"^ floor,

and temperature histories applied at 10 min intervals with linear ramping between time intervals.

The analysis results showed that:

• Inward pull forces were required to produce inward bowing consistent with the displacements

measured from photographs. The inward pull was caused by sagging of the floors. Heating of

the inside faces of the exterior columns also contributed to inward bowing.

• Exterior wall sections bowed outward in a pushdown analysis when several consecutive

floors were disconnected, the interior face of the columns was heated, and column gravity

loads increased (e.g., due to load redistribution from the core and hat truss). At lower

temperatures, thermal expansion of the inside face was insufficient to result in inward bowing

of the entire exterior column. At higher temperatures, outward bowing resulted from the combined effects of reduced steel strength on the heated inside face, which shortened first under column gravity loads, and the lack of lateral restraint from the floors.

• The observed inward bowing of the exterior wall indicated that most of the floor connections

must have been intact to cause the observed bowing.

• The extent of floor sagging observed at each floor was greater than that predicted by the ftill floor models. The estimates of the extent of sagging at each floor was governed by the combined effects of insulation damage and fire; insulation damage estimates were limited to areas subject to direct debris impact. Other sources of floor and insulation damage from the

aircraft impact and fires (e.g., insulation damage due to shock and subsequent vibrations as a

result of aircraft impact or concrete slab cracking and spalling as a result of thennal effects) were not included in the floor models.

• Case B impact damage and thermal loads for the WTC 1 south wall, combined with pull-in

forces from floor sagging, resulted in an inward bowing of the south face that reasonably

matched the observed bowing. The lack of floor sagging for the Case A impact damage and

thermal loads resulted in no inward bowing for the south face.

• Cases D impact damage and thermal loads for the WTC 2 east wall, combined with pull-in

forces from floor sagging, resulted in an inward bowing of the east face that reasonably

matched the observed bowing.

NISTNCSTAR 1, WTC Investigation 103
Chapter 6

Phase 3: Giobai Modeling

The global models were used for the two final simulations and provided complete analysis of results and

insight into the subsystem interactions leading to the probable collapse sequence. Based upon the results of the major subsystem analyses, impact damage and thennal loads for Cases B and D were used for WTC 1 and WTC 2, respectively. The models extended from floor 91 for WTC 1 and floor 77 for WTC 2

to the roof level in both towers. Although the renditions of the structural components had been reduced in complexity while maintaining essential nonlinear behaviors, based on the findings from the component

and subsystem modeling, the global models included many of the features of the subsystem models:

• Removal of aircraft-damaged structural components.

• Application of gravity loads following removal of aircraft damaged components and prior to thermal loading.

• Temperature-dependent concrete and steel properties.

• Creep strains for column components.

• Representation of lower floors by springs.

• Local temperature histories applied at 10 min intervals with linear ramping between time

intervals.

There were several adjustments to the models based on the findings from the subsystem modeling:

• Removal of theraial expansion from the spandrels and equivalent slabs in the tenant area to avoid local buckling that affected convergence but had little influence on global collapse

initiation.

• Representing the WTC 2 structure above the 86'*^ floor as a single "super-element" to reduce

model complexity. The floors above the impact zone had only exhibited linear behavior in the previous analyses. This modification assumed linear behavior of the hat truss, which was

checked as part of the review of analysis results.

• Representation of the lower part of the tower (starting several floors below the impact

damage) as a super-element. This prevented the use of construction sequence in applying

gravity loads to the model (where loads are applied in stages to simulate the construction of

the building). The lack of construction sequence increased the forces on the exterior columns

slightly, and decreased those on the core columns slightly.

The inclusions of creep for column components was necessary for the accuracy of the models, but its addition also greatly increased the computation time. As a result, the simulations of WTC 1 took 22 days

and those of WTC 2 took 14 days on a high-end computer workstation. The results of these simulations

are presented in Section 6.14.

104 NISTNCSTAR 1. WTC Investigation
6.7 THE AIRCRAFT STRUCTURAL MODEL

Reconstruction of the Collapses

Due to their similarity, the two Boeing 767-200ER aircraft were represented by a single, finite element

model, two views of which are shown in Figure 6-13. The model consisted of about 800,000 elements.

The typical element dimensions were between 1 in. and 2 in. for small components, such as spar or rib flanges, and 3 in. to 4 in. for large parts such as the wing or fuselage skin. Structural data on which to base the model were collected fi-om the open literamre, electronic surface models and CAD drawings, an

inspection of a 767-300ER. Pratt and Whitney Engine Reference Manuals, American Airlines and United

Airlines, and the Boeing Company website.

Figure 6-13. Finite element model of the Boeing 767-200ER.

NISTNCSTAR 1, WTC Investigation 105
Chapter 6

More detailed models of subsections of the aircraft were constructed for the component level analyses

described below. Special emphasis was placed on modeling the aircraft engines, due to their potential to produce significant damage to the tower components. The element dimensions were generally between

1 in. and 2 in., although even smaller dimensions were required to capture some details of the engine

geometry. The various components of the resulting engine model are shown in Figure 6-14. Fuel was

distributed in the wing as shown in Figure 6-15 based on a detailed analysis of the fuel distribution at the time of impact.

Figure 6-14. Pratt & Whitney PW4000

turbofan engine model.

106 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

6.8 AIRCRAFT IMPACT MODELING

6.8.1 Component Level Analyses

Prior to conducting the full simulations of the aircraft impacting the towers, a series of smaller scale simulations was performed to develop understanding of how the aircraft and tower components

fragmented and to develop the simulation techniques required for the final computations. These

simulations began with finely meshed models of key components of the tower and aircraft structures and

progressed to relatively coarsely meshed representations that could be used in the global models.

Examples of these component-level analyses included impact of a segment of an aircraft wing with an

exterior column, impact of an aircraft engine with exterior wall panels, and impact of a fuel-filled wing

segment with exterior wall panels.

Figure 6-16 shows two frames from the last of these analyses, with the wing segment entering from the

left, being fragmented as it penetrates the exterior columns, and spraying jet fuel downstream.

t = O.Os t = 0.04 s

Figure 6-16. Calculated impact on an exterior wall by a fuel-laden wing section.

The Investigation Team gained valuable knowledge from these component impact analyses, for example:

• Moving at 500 mph, an engine broke any exterior column it hit. If the engine missed the

floor slab, the majority of the engine core remained intact and had enough residual

momentum to sever a core column upon direct impact.

• The impact of the inner half of an empty wing significantly damaged exterior columns but did

not result in their complete failure. Impact of the same wing section, but filled with fuel, did

result in failure of the exterior columns.

NISTNCSTAR 1, WTC Investigation 107
Chapter 6

6.8.2 Subassembly Impact Analyses

Next, a series of simulations were perfonned for intennediate-sized sections of a tower. These

subassembly analyses investigated different modeling techniques and associated model sizes, run times,

numerical stability, and impact response. Six simulations were performed of an aircraft engine impacting

a subassembly that included structural components from the impact zone on the north face of WTC 1, exterior panels, truss floor structures, core framing, and interior contents (workstations). One response of

the structure to the engine impact is shown in Figure 6-17.

Figure 6-17. Response of a tower subassembly model to engine impact.

Typical knowledge gained from these simulations were:

• The mass of the concrete floor slab and nonstructural contents had a greater effect on the

engine deceleration and subsequent damage than did the concrete strength.

• Variation of the failure criteria of the welds in the exterior columns did not result in any

noticeable difference in the damage pattern or the energy absorbed by the exterior panels.

6.8.3 Aircraft Impact Conditions

From the NIST photographic and video collection, the speed and orientation of the aircraft (Table 6-^) were estimated at the time of impact. The geometry of the wings, different in flight from that at rest, was

estimated from the impact pattern in the photographs and the damage documented on the exterior panels

by NIST. United Airlines and American Airlines provided information on the contents of the aircraft, the mass ofjet fuel, and the location of the fuel within the wing tanks.

Table 6-4. Summary of aircraft impact conditions.

Condition AA 11 (WTC 1) UAL 175 (WTC 2) Impact Speed (mph) 443 + 30 542 ± 24

Vertical Approach Angle 10.6° ± 3° below horizontal (heading downward)

6° + 2° below horizontal (heading

downward)

Lateral Approach Angle 180.3° + 4° clockwise from Plan

North'

13° ± 2° clockwise from Plan

North'

Roll Angle (left wing downward) 25° + 2° 38° ±2°

a. Plan North is approximately 29 degrees clockwise from True North.

108 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

6.8.4 Global Impact Analysis

From the component and subassembly simulations, it became apparent that each computation of the full tower and aircraft would take weeks. Furthennore, the magnitude and location of damage to the tower

structure were sensitive to a large number of initial conditions, to assumptions in the representation of the

collision physics, and to any approximations in the numerical methods used to solve the physics

equations. Thus, it was necessary to choose a manageable list of the factors that most influenced the outcome of a simulation. Careful screening was conducted at the component and subassembly levels,

leading to identification of the following prime factors:

• Impact speed,

• Vertical approach angle of the aircraft,

• Lateral approach angle of the aircraft,

• Total aircraft weight,

• Aircraft materials failure strain,

• Tower materials failure strain, and

• Building contents weight and strength.

Guided by these results and several preliminary global simulations, two global simulations were selected

for inclusion in the four-step simulation of the response of each tower, as described in Section 6.1. The

conditions for these four runs are shown in Table 6-5. The computers simulate the aircraft flying into the

tower, calculated the fragments that were formed from both the aircraft and the building itself, and then

followed the fragments. The jet fuel, atomized upon impact into about 60,000 "blobs" averaging one

pound, dispersed within and outside the building. Each simulation continued until the debris motion had

reduced to a level that was not expected to produce any significant further impact damage.

Table 6-5. Input parameters for global Impact analyses.

Analysis Parameters

WTC 1 WTC 2

Case A Case B Case C Case D

Flight Parameters

Impact Speed 443 mph 472 mph 542 mph 570 mph

Vertical Approach

Angle 10.6° 7.6° 6.0° 5.0°

Lateral Approach

Angle

180.0° 180.0° 13.0° 13.0°

Aircraft Parameters Weight 100% 105 % 100% 105 %

Failure Strain 100% 125 % 100% 115 %

Tower Parameters

Failure Strain 100 % 80% 100% 90%

Live Load Weight" 25 % 20% 25 % 20%

Contents Strength 100% 100 % 100% 80%

a. Live load weight expressed as a percentage of the design live load.

NISTNCSTAR 1, WTC Investigation 109
Chapter 6

These simulations each took about 2 weeks on a 12-node computer cluster. Figure 6-18 shows six frames

from the animation of one such simulation.

m ED

(a) Time=0.00 s

r nil nn ssi

HimBBIIIiBM UIMU IBBBIIflBI ma in i

HimaBiiiBaii Emra ibbhwhiii

(b) Time=0.10 s

(c) Time=0.20 s Figure 6-18. Side view of simulated aircraft impact into WTC 1, Case B.

110 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

fin mH

\

(d) Time=0.30 s

I Eia HUl • in , ME nm

II m I BIB 1 31 laaciiBHi ib a bib i ai m" " Enni

nnmmnsiiiM

EH in

(e) Time=0.40 s

I nx mi BO . KniBiiiiBiii Emu ftisMM) nn DMOn]

(f) Time=0.50 s Figure 6-18. Side view of simulated aircraft impact into WTC 1, Case

NISTNCSTAR 1, WTC Investigation 111
Chapter 6

6.9 AIRCRAFT IMPACT DAMAGE ESTIMATES

6.9.1 Structural and Contents Damage

Each of the four global simulations generated infonnation about the state of the structural components

following the impact of the aircraft. The four degrees of column damage are defined as follows and

shown graphically in Figure 6-19. The unstrained areas are blue and the highly strained areas are red.

• Lightly damaged column: column impacted, but without significant structural deformation;

• Moderately damaged column: visible local distortion, but no deformation of the column

centerline;

• Heavily damaged column: Permanent deflection of the column centerline; and

• Failed column: Column severed. \

(a) Light (b) Moderate (c) Heavy (d) Severed

Figure 6-19. Column damage levels.

Figure 6-20 shows the calculated damage to a floor slab. Figure 6-21 shows the response of the

furnishings and the jet fuel to the impact. Figures 6-22 through 6-25 show the combined damage for all floors for the four global simulations. The latter proved usefiil in visualizing the extent of aircraft impact

in one graphic image.

Impact I Colu I 1

Figure 6-20. Case B damage to the slab of floor 96

ofWTCI.

112 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

(c) Calculated impact response (fuel removed)

Figure 6-21 . Case B simulation of response of contents of 96"" floor of WTC 1

.

NISTNCSTAR 1. WTC Investigation 113
Chapter 6

101 103 106 1 09 112 115 118 121 12« 127 1 30 1 33 1 36 1 39 142 145 148 151 154 157 159

Severe Floor Damage

Floor fireproofing

[ |

Floor system

structural damage

Floor system

removed

Column Damage

Severed Q

Heavy damage Q

Moderate damage

Light damage

1

701

801 Q0OQ Q 803 804

70 r

801

I 9081

902 903 904 905 906 107

1002 1003 1004 1005 1006

7081

807

rrr

-251

-254

-257

359 357 354 351 348 345 342 339 336 333 330 327 324 321 318 315 312 309 306 303 301 Figure 6-22. Combined structural damage to the floors and columns of WTC 1, Case A.

101 103 106

9 T

Figure 6-23. Combined

structural damage to the

floors and columns of WTC

Case B.

1,

112 115 lie 121 124 1 27 130 1 33 1 36 1 39 142 145 148 1 51 154 157 169

>01

f(s^ QQ Q L sol

1701

1801

901 902

DO 707

806

1002 1003 1004 1005 1006 1007

JL. , „ % J

807'

908<

10081

I I It It r

-206

-208

-245

-248

-251

rTTTTTT

3 2

359 357 3S4 351 a4S 342 339 336 333 330 327 .124 321 318 315 312 309 306 303 301

114 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

201 203 206 209 212 215 21S 221 224 227 230 233 236 239 2<2 245 248 251 2S4 257 259

Severe Floor Damage

Floor fireproofing

| [

Floor system i—

i

structural damage | | Floor system

removed

Column Damage

Severed ^)

Heavy damage Q

Moderate damage

Light damage

45S 457 454 451 448 445 442 430 436 433 430 427 424 421 418 415 412 Figure 6-24. Combined structural damage to the floors and columns of WTC 2, Case C.

201 203 206 209 212 215 213 221 224 227 230 233 236 239 242 245 248 251 254 257 259

Figure 6-25. Combined

structural damage to the

floors and columns of

WTC 2, Case D.

459 4S7 454 451 448 445 442 439 436 133 430 427 424 421 416 415 412 409 406 4C3 401

NISTNCSTAR 1, WTC Investigation 115
Chapter 6

6.9.2 Validity of Impact Simulations

Assessment of the aircraft impact simulations of exterior damage to the towers involved comparing the

predicted perimeter wall damage near the impact zone with post-impact photographs of the walls. Figure 6-26 shows a photograph of the north face of WTC 1 after impact and the results of the Case A

simulation. The calculated silhouettes capture both the position and shape of the actual damage.

Figures 6-27 and 6-28 depict more detailed comparisons between the observed and calculated damage.

The aircraft hole is shown in white. The colored dots characterize the mode in which the steel or connection failed (e.g., severed bolt, ripped weld) and the magnitude of the deformation of the steel:

• Green: proper match of failure mode and magnitude

• Yellow: proper match in the failure mode, but not the magnitude

• Red: neither the failure mode nor the magnitude matched

• Black: the observed damage was obscured by smoke, fire, or other factors

The predominance of green dots and the scarcity of red dots indicate that the overall agreement with the observed damage was very good. The agreement for Cases B and D was slightly lower.

Assessment of the accuracy of the predictions of damage inside the buildings was more difficult, as NIST

could not locate any interior photographs near the impact zones. Three comparisons were made:

• The Case A simulation for WTC 1 predicted that the walls of all three stairwells would have

been collapsed. This agreed with the observations of the building occupants. The Case A

simulation for WTC 2 showed that the walls of stairwell B would have been damaged, but

that Stairwell A would have been unaffected. Stairwell C was not included in the WTC 2

model, but is adjacent to where damage occurred. The building occupants reported that Stairwells B and C were impassable; Stairwell A was damaged but passable.

• The two simulations of WTC 2 showed accumulations of fijmishings and debris in the

northeast comer of the 80th and 8 1 st floors. These piles were observed in photographs and

videos.

• Two pieces of landing gear penetrated WTC 1 and landed to the south of the tower. The Case

B prediction showed landing gear penetrating the building core, but stopping before reaching

the south exterior wall. For WTC 2, a landing gear fragment and the starboard engine

penetrated the building and landed to the south. The Case D prediction correctly showed the main landing gear emerging from the northeast comer of WTC 2. However, Case D showed

that engine not quite penetrating the building. Minor modifications to the model (all within

the uncertainty of the input data) would have resulted in the engine passing through the north

exterior wall of the tower.

116 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

(a) Observed Damage

(b) Calculated damage

Figure 6-26. Observed and Case A calculated damage to the north face of WTC 1.

NISTNCSTAR 1. WTC Investigation 117
Chapter 6

U f M f f f f . .

.

orinuonfflnnoni:

]DD[DDfflGDO]D

Figure 6-27.

Schematic of

observed

damage (top)

and Case A

calculated

damage (lower)

to the north

face ofWTC 1.

P Incorrect mode

^ Obscured on images

lllllllllllllllllllllllllllllllillllllllEIIIII

Figure 6-28.

Schematic of

observed

damage (above)

and Case C

calculated

damage (right) to

the south face of

WTC 2.

mum

mm

# Correct mode and magnitude

Correct mod«3. magnitu^de insufficient

~1 ~| # Incorrect mode

LJJii 0 Obscured on images

118 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

Not all of the observables were closely matched by the simulations due to the uncertainties in exact impact conditions, the imperfect knowledge of the interior tower contents, the chaotic behavior of the

aircraft breakup and subsequent debris motion, and the limitations of the models. In general, however,

the results of the simulations matched these observables sufficiently well that the Investigation Team

could rely on the predicted trends.

Simulations of the damage to the core columns had been performed previously by staff of Weidlinger

Associates, Inc. (WAI) and the Massachusetts Institute of Technology (MIT). Each developed a range of

numbers of failed and damaged columns, as did NIST. The range of the MIT results straddled the NIST

results. WAFs analysis resulted in more failed and damaged coluinns, with WTC 2 being unstable

immediately following impact.

6.9.3 Damage to Thermal Insulation

The dislodgement of thermal insulation from structural members could have occurred as a result of

(a) direct impact by debris and (b) inertial forces due to vibration of structural members as a result of the

aircraft impact. The debris from the aircraft impact included the fragments that were formed from both

the aircraft (including the contents and fuel) and the building (structural members, walls, and furnishings).

In interpreting the output of the aircraft impact simulations, NIST assumed that the debris impact

dislodged insulation if the debris force was strong enough to break a gypsum board partition immediately

in front of the structural component. Experiments at NIST confirmed that an array of 0.3 in. diameter

pellets traveling at approximately 350 mph stripped the insulation from steel bars like those used in the WTC trusses.

Determining the adherence of SFRM outside the debris zones was more difficult. There was

photographic evidence that some fraction of the SFRM was dislodged from perimeter columns not

directly impacted by debris.

NIST developed a simple model to estimate the range of accelerations that might dislodge the SFRM

from the structural steel components. As the SFRM in the towers was being upgraded with BLAZESHIELD II in the 1990s, The Port Authority had measured the insulation bond strength (force required to pull the insulation from the steel). The model used these data as input to some basic physics equations.

The resulting ranges of accelerations depended on the geometry of the coated steel component and the SFRM thickness, density and bond strength. For a flat surface (as on the surface of a column), the range was from 20g to 530g, where g is the gravitational acceleration. For an encased bar (such as used in the WTC trusses), the range was from 40g to 730g. NIST estimated accelerations from the aircraft impacts of

approximately lOOg.

In determining the extent of insulation damage in each tower, NIST only assumed damage where

dislodgement criteria could be established and supported through observations or analysis. Thus, NIST

made the conservative assumption that insulation was removed only where direct debris impact occurred

and did not include the possibility of insulation damage or dislodgement from structural vibration. This

assumption produced a lower bound on the bared steel surface area, thereby making it more difficult to heat the steel to the point of failure.

NISTNCSTAR 1, WTC Investigation 119
Chapter 6

6.9.4 Damage to Ceiling System

The aircraft impact modeling did not include the ceiling tile systems.

To estimate whether the tiles would survive the aircraft impact, the University at Buffalo, under contract to NIST, conducted tests of

WTC-like ceiling tile systems using their shake table (Figure 6-29)

and impulses related to those induced by the aircraft impact on the towers. The data indicated that accelerations of approximately 5g

would most likely result in substantial displacement of ceiling tiles. Given the estimated impact accelerations of approximately lOOg,

NIST assumed that the ceiling tiles in the impact and fire zones were

fully dislodged. This was consistent with the multiple reports of

severely damaged ceilings (Chapter 7).

Source: NIST

Figure 6-29. Ceiling tile system mounted on the shaking table.

6.9.5 Damage to Interior Walls and Furnishings

As shown in Figure 6-18, the aircraft impact simulations explicitly included the fracture of walls in the debris path and the "bulldozing" of furnishings. Damage to the impacted furnishings was not modeled.

Walls and furnishings outside the debris paths were undamaged in the simulations.

An intact ceiling tile system

could have provided the floor trusses with approximately

1 0 min to 1 5 min of thermal

protection from ceiling air temperatures near 1,000 °C. These temperatures would

quickly heat steel without

thermal insulation to temperatures for reduction of the strength of structural

steels.

120 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

6.10 THERMAL ENVIRONMENT MODELING

6.1 0.1 Need for Simulation

Following the impact of the aircraft, the jet-fuel-ignited fires created the sustained and elevated

temperatures that heated the remaining building structure to the point of collapse initiation. The

photographic evidence provided some information regarding the locations and spreading of the fires. However, the cameras could only see the periphery of the building interior. The steep viewing angles of

nearly all of the photographs and videos further limited the depth of the building interior for which fire information could be obtained. NIST could not locate any photographic evidence regarding the fire exposure of the building core or the floor assemblies.

The simulations of the fires were the second computational step in the identification of the probable

sequences leading to the collapse of the towers. The required output of these simulations was a set of

three-dimensional, time varying renditions of the thermal and radiative environment to which the

structural members in the towers were subjected from the time of aircraft impact until the onset of

building collapse. The rigor of the Investigation placed certain requirements on the computational tool (model) used to generate these renditions:

• Resolution of the varying thermal environment across key dimensions, e.g., the truss space;

• Representation of the complex combustibles;

• Computation of flame spread across the large expanses of the WTC floors; and

• Confidence in the accuracy of the predictions.

6.10.2 Modeling Approach

The time frame of the Investigation and the above requirements led to the use of the Fire Dynamics

Simulator (FDS). Under development at NIST since 1978, FDS was first publicly released in February

2000 and had been used worldwide on a wide variety of applications, ranging from sprinkler activation to residential and industrial fire reconstructions. However, it had never before been applied to spreading

fires in a building with such large floor areas.

Figure 6-30 shows how FDS represented the eight modeled floors (92 through 99) of the undamaged

WTC 1. A similar rendition was prepared for floors 78 through 83 of WTC 2. The layout of each floor was developed from architectural drawings and from the information described in Section 5.8. There was

a wide range of confidence in the accuracy of these floor plans, varying from high (for the floors occupied

by Marsh & McLennan in WTC 1, for which recent and detailed plans were obtained) to low (for most of

the space in WTC 2 occupied by Fuji Bank, for which floor plans were not available).

The effects of the aircraft impact were derived from the simulations described in Section 6.8. The

portions of walls and floors that were "broken" in those simulafions were simply removed from the FDS

models of the towers. The furnishings outside the aircraft-damaged regions were assumed to be unmoved

and undamaged. The treatment of furnishings within the impact zone is discussed later in this section.

NISTNCSTAR 1. WTC Investigation 121
Chapter 6

FDS represented the spaces in which the fires and their effluent were to be modeled as a grid of

rectangular cells. These grids included the walls, floors, ceilings, and any other obstructions to the

movement of air and fire. In the final simulations, the grid size was 0.5 m x 0.5 m x 0.4 m high

(1 .6 ft X 1.6 ft X 1.3 ft.). Each floor contained about 125,000 grid cells, and the nature of each cell was

updated every 10 ms (100 times every second). The computations were performed using parallel

processing, in which the fires on each floor were simulated on a different computer. At the end of each

1 0 ms update, the processors exchanged information and proceeded to the computations for the next time

interval. Each simulation of 105 min of fires for WTC 1 took about a week on eight Xeon computers

with a combined 16 GB of memory. The simulations for WTC 2, with fewer floors and 60 min of real time fires, took about half the time.

Figure 6-30. Eight floor model of WTC 1 prior to aircraft impact.

The fires were started by ignition of the jet fuel, whose distribution was provided by the aircraft impact

simulations. The radiant energy from these short-lived fires heated the nearby combustibles, creating

flammable vapors. When these mixed with air in the right proportion within a grid cell, FDS burned the

mixture. This generated more energy, which heated the combustibles further, and continued the burning.

122 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

The floors of the tower on which the dominant burning occurred were

characterized by large clusters of office

workstations (Figure 1-11). NIST

determined their combustion behavior

from a series of single-workstation fire

tests (Figure 6-3 1 )• In these highly

instrumented tests, the effects of

workstation type, the presence ofjet fuel,

and the presence of fallen inert material

(such as pieces of ceiling tiles or gypsum

board walls) on the burning surfaces were

all assessed. While FDS properly captured

the gross behavior of these fires, the state of modeling the combustion of real fiamishings was still primitive. Thus, the

results of this test series were used to refine the combustion module in FDS.

The accuracy of FDS predictions was then assessed using two different

types of fire tests. In each case, the model predictions were generated prior

to conducting the test.

The first series provided a measure of the ability of FDS to predict the

thermal environment generated by a steady state fire. A spray burner

generating 1 .9 MW or 3.4 MW of power was ignited in a 23 ft by 1 1 .8 ft by

12.5 ft high compartment. The temperatures near the ceiling approached

900 °C. FDS predicted:

• Room temperature increases near the ceiling to within 4 percent.

• Gas velocities at the air inlet to the compartment (and thus the air drawn into the compartment by the fire) within the uncertainty in the experimental measurements.

• The leaning of the fire plume due to the asymmetry of the objects within the compartment.

The extent of the leaning was underestimated.

• Radiant heat flux near the ceiling to within 10 percent, within the uncertainty of the experimental measurements.

The second series was a preamble to the modeling of the actual WTC fires. Arrays of three WTC

workstations were burned in a 35.5 ft by 23 ft by 1 1 ft high compartment (Figure 6-32). The tests examined the effects of the type of workstation, the presence ofjet fuel, and the presence of fallen inert material on the burning surfaces. In one of the tests, the workstations were rubblized (Figure 6-33).

Figure 6-34 depicts the intensity of the test fires. Figure 6-35 shows the measured and predicted heat

release rate data from one of the tests in which there was no jet ftiel nor inert material present.

Source: NIST. Figure 6-31 . Fire test of a single workstation.

The large fires discussed in this report are characterized by

heat release rate, or burning intensity, (in MW), by total energy

released (in GJ), and

by the heat flux, or radiant intensity

(in kW/m^).

NISTNCSTAR 1, WTC Investigation 123
Chapter 6

Source: NIST.

124 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

Source: NIST

Figure 6-34. Three-workstation fire test, 2 min after the start.

3000

Figure 6-35. Measured and predicted heat release rate from the burning of three

office workstations.

The differences in the fire behavior under the different experimental conditions were profound in these

roughly hour-long tests. The jet fuel greatly accelerated the fire growth. Only about 60 percent of the

NISTNCSTAR 1. WTC Investigation 125
Chapter 6

combustible mass of the rubblized workstations was consumed. The near-ceiling temperatures varied

between 800 °C and 1,100 °C. Nonetheless, FDS successfully replicated:

• The general shape and magnitude of the time-dependent heat release rate.

• The time at which one half of the combustion energy was released to within 3 min.

• The value of the heat release rate at this time to within 9 percent.

• The duration of the fires to within 6 min.

• The peak near-ceiling temperature rise to within 10 percent.

All these predictions were within the combined uncertainty in the model input data and the experimental

measurements.

Combined, these results led to the assessment that the uncertainty in the thermal environment predictions

of the WTC fires would be dominated less by the FDS errors and more by the unknowns in such factors as the distribution of the combustibles, ventilation, and building damage.

6.10.3 The Four Cases

Four fire scenarios (Case A and Case B for WTC 1 and Case C and Case D for WTC 2) were

superimposed on the four cases of aircraft-driven damage of the same names (Section 6.9). A number of preliminary simulations had been performed to gain insight into the factors having the most

influence on the severity of the fires. The most influential was the mass of combustibles per unit of floor area (fuel load); second was the extent of core wall damage, which affected the air supply for the fires. The aforementioned workstation fire tests had also indicated that the damage condition of the furnishings

also played a key role. The scenario variables and their values are shown in Table 6-6.

Table 6-6. Values of WTC fire simulation variables.

Variable

WTC 1 WTC 2 Case A Case B CaseC CaseD

Tenant combustible

fuel load"

4 Ib/ft- 5 Ib/ft- 4 Ib/ft- 5 Ib/ftDistribution of

disturbed combustibles

Even Weighted toward

the core

Heavily

concentrated in the northeast comer

Moderately

concentrated, in the northeast comer

Condition of

combustibles

Undamaged except

in impact zone

Displaced furniture mbblizedAll mbblized Undamaged except

in impact zone

Representation of

impacted core walls''

Fully removed Soffit remained Fully removed Soffit remained

a. In addition, approximately 27,000 lb of solid combustibles from the aircraft were distributed along the debris path.

b. In Cases A and C, the walls impacted by the debris field were fully removed. This enabled rapid venting of the upper layer into the core shafts and reduced the burning rate of combustibles in the tenant spaces. In Cases B and D, a more severe

representation of the damage was to leave a 4 ft gypsum wallboard soffit that would maintain a hot upper layer on each fire floor. This produced a fire of longer duration near the core columns and the attached floor membranes.

126 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

FDS contained no algorithm for breaking windows from the heat of the fires. Thus, during each

simulation, windows were removed at times when photographs indicated they were first missing.

Damage to the ventilation shafts was derived from the aircraft impact simulations. For undamaged floors,

all the openings to the core area were assumed to total about 50 ft" in area.

6.10.4 Characterization of the Fires

For each of the four scenarios, FDS was used to generate a time-dependent gas temperature and radiation

environment on each of the floors. The results of the FDS simulations of the perimeter fire were compared with the fire duration and spread rate as seen in the photographs and videos. For ease of

visualization, contour plots of the room gas temperature 1.3 ft below the ceiling slab (in the "upper layer"

of the compartment) were superimposed on profiles of the photographed fire activity. An example is shown in Figure 6-36. The stripes surrounding the image represent a summary of the visual observations

of the windows, with the black stripes denoting broken windows, the orange stripes denoting external

flaming, and the yellow stripes denoting fires that were seen inside the building. Fires deeper than a few

meters inside the building could not be seen because of the smoke obscuration and the steep viewing

angle of nearly all the photographs.

0:15:00.0 I

Figure 6-36. Upper layer temperatures on the 94*" floor of WTC 1, 15 min after impact.

NISTNCSTAR 1. WTC Investigation 111
Chapter 6

Given the uncertainties in some of the floor plans, the damage to the internal walls, and movement of the

office furnishings, the intent of the simulations was to capture the magnitudes of the fires and the broad

features of their locations and movement; and they did so.

The following sections summarize the simulated behavior of the fires (which was used in the following

stages of the disaster reconstruction) and their correlation with the analysis of the photographic evidence.

WTC 1

Much of the fire activity was initially in the vicinity of the impact area in the north part of the building.

As a result of the orientation of the impacting aircraft and its fuel tanks, the early fires on the 92"'^ through

94"^ floors tended toward the east side of the north face, while the early fires on the 97"" through

99"^ floors tended toward the west side of the north face. The fires on all the floors spread along the east and west sides and were concentrated in the south part of the building at the time of collapse, as depicted

in Figure 6-37. . . ^

WTC 1 , Floor 97

Figure 6-37. Direction of simulated fire movement on floors 94 and 97 of WTC 1.

128 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

The fire simulation results for Case A and Case B were similar, indicating only a modest sensitivity to the

fuel load and the degree of aircraft-generated damage. This was because, in general, the size and

movement of the fires in WTC 1 were limited by the supply of air from the exterior windows. Since the window breakage pattern was not changed in Case B, the additional and re-distributed combustibles

within the building did not contribute to a larger fire. The added fuel did slow the spread slightly because

the fires were sustained longer in any given location.

Although there was generally reasonable agreement between the simulated and observed fire spread rates, there were instances where the fires burned too quickly and too near the windows. This resulted from an

artifact of the model: the combustible vapors burned immediately upon mixing with the incoming oxygen.

Simulations performed with doubled fuel loads slowed the fire spread well below the observed rates. Combined with the above results, this suggested that the estimated overall combustible load of 4 Ib/fP was reasonable.

The simulations showed high temperatures in some of the elevator shafts. The late fire observed on the west face of the 1 04'*^ floor may have started from fuel gases in the core shafts that had accumulated over

the course of the first hour of fires below. The presence of fire in the shafts on the 99''^ floor provided some support for this hypothesis, but no simulations were performed for floors higher than the 99*.

The predictions of maximum temperatures (e.g., red zones in Figure 6-37) were consistent with those in the three-workstation fire tests.

The use of an "average" gas temperature was not a satisfactory means of assessing the thermal

environment on floors this large and would also have led to large errors in the subsequent thermal and

structural analyses. The heat transferred to the structural components was largely by means of thermal

radiation, whose intensity is proportional to the fourth power of the gas temperature. At any given

location, the duration of temperatures near 1,000 °C was about 15 min to 20 min. The rest of the time, the calculated temperatures were near 500 °C or below. To put this in perspective, the radiative intensity onto

a truss surrounded by smoke-laden gases at 1 ,000 °C was approximately 7 times the value for gases at 500 °C.

WTC 2

Simulating the fires in WTC 2 posed challenges in addition to those encountered in simulating the fires in WTC 1. The aircraft, hitting the tower to the east of center, splintered much of the furnishings on the east side of the building and plowed them toward the northeast comer. Neither the impact study nor the validation experiments performed at NIST could be completely relied upon to predict the final

distribution, condition, and burning behavior of the demolished furnishings. In addition, only the layouts

of the 78'^ and 80"^ floors were available to the Investigation; the other floors were only roughly described

by former occupants. As a result of these unknowns, the uncertainty in these calculations was distinctly

greater than in those for WTC 1 . To help mitigate gross differences between the simulations and the observables, NIST made floor-specific adjustments, based on the results of preliminary computations. In

particular, the fuel load and volatility on the SO"" floor were reduced, and the fuel load on the ST' and

82"" floors was increased.

NISTNCSTAR 1, WTC Investigation 129
Chapter 6

In contrast with WTC 1, in WTC 2 there was less movement of the fires. The major burning occurred

along the east side, with some spread to the north. There was no significant burning on the west side of

the tower.

Also unlike WTC 1, changing the combustible load in WTC 2 had a noticeable effect on the outcome of

the simulations. Because so many windows on the impact floors in WTC 2 were broken out by the

aircraft debris and the ensuing fireballs, there was an adequate supply of air for the fires. Thus, the

burning rate of the fires was determined by the fuel supply. In the Case D simulation, the office

furnishings and aircraft debris were spread out over a wider area, and the furnishings away from the

impact area were undamaged. Both of these factors enabled a higher burning rate for the combustibles.

In general, the Case D simulations more closely approximated the observations in the photographs and

videos, although there was still some prediction of burning too close to the perimeter, especially on the

east side of the 78'^ 79'^ 81" and 83"* floors. The burning in the northeast comer of the ST' and

82"'' floors was more intense in Case D than in Case C. The fire in the east side of the 79* floor burned more intensely and reached the south face sooner.

Nothing in the simulations explained the absence of fires in the "cold spot," the 10-window expanse

toward the east of the north face of the 80"\ 81'', and 82"'' floors.

6.10.5 Global Heat Release Rates

Much of the information needed to simulate the fires came from laboratory-scale tests. While some of

these involved enclosures several meters in dimension and fires that reached heat release rates of 10 MW

and 12 GJ in total heat output, they were still far smaller than the fires that burned in the WTC towers. Figure 6-38 shows the heat release rates from the FDS simulations of the WTC fires. The peak plateau

heat release rates were about 2 GW for WTC 1 and 1 GW for WTC 2. Integrating the areas under these curves produced total heat outputs from the simulated fires of about 8,000 GJ from WTC 1 and 3,000 GJ

from WTC 2.

3 0

2 5

- WTC 1, Case A

WTC 2, Case C

WTC 1, Case B WTC 2, Case D

X

0 0

0 20 40 60 80 100

Time (min)

Figure 6-38. Predicted heat release rates for fires in WTC 1 and WTC 2.

130 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

6.11 DATA TRANSFER

The following data from FDS were compiled for use as boundary conditions for the finite-element

calculation of the structural temperatures:

• The upper and lower layer gas temperatures, time-averaged over 100 s and spatially averaged

over 3 ft. The upper layer gas temperatures were taken 1 .3 ft (one grid cell) below the

ceiling. The lower layer temperatures were taken 1.3 ft above the floor.

• The depth of the smoke layer.

• The absorption coefficient of the smoke layer 1 .3 ft below the ceiling.

Simulating the effect of a fire on the structural integrity of a building required a means for transferring the heat generated by the fire to the surfaces of the insulation on structural members and then conducting the heat through those members. In the Investigation, this meant mapping the time- and space-varying gas temperatures and radiation field generated by FDS onto and throughout the (insulated) columns, trusses and other elements that made up the tower structure.

This process was made difficult for these large, geometrically complex buildings by the wide disparity in length and time scales that had to be accounted for in the simulations. FDS generated thennal maps with

dimensional resolution of the order of a meter and temperatures fluctuating on a time scale of

milHseconds. The finite element models for thermal analysis resolved length of the order of Vi in. on a time scale of seconds. Devising a computation scheme to accommodate the finest of these scales, while

simulating the largest of these scales, presented a software challenge in order to avoid unacceptably long

computation times.

6.12.2 The Fire-Structure Interface

NIST developed a computational scheme to overcome this difficulty, FZT ' ~ ', ~.

6.12 THERMAL MAPPING

6.12.1 Approach

These computations began with the structural models of each WTC

tower as described in Section 6.6.4, damaged by the aircraft as described in Section 6.8.4 and exposed to fire-generated heat, as described in Section 6.10.4. For a particular tower and damage

scenario, FSl "bathed" each small section of each structural member in an air envirormient that had been generated by FDS. For efficiency of

computation, two simplifications were made:

the Fire Structure Interface (FSI).

• The fluctuating environment was averaged over 30 s intervals, and

The transfer of radiant

energy from a hot mass to a

cool mass is proportional to the absolute temperature

(Kelvin) to the fourth power.

Thus, the contribution of the

hot upper layer dominates

the overall radiative heat

transfer. Convective heat

transfer is linearly

proportional to the difference

in temperature between the

hot gas and the cool solid.

NISTNCSTAR 1, WTC Investigation 131
Chapter 6

• The local environment was represented by a hot, soot-laden upper layer and a cooler,

relatively clear lower layer.

FSl then calculated the radiative and convective heat transfer to each of these small sections using

conventional physics. Finally, the temperature data were read into the ANSYS 8.0 finite element

program, which applied the temperature distribution to the structural elements.

6.12.3 Thermal Insulation Properties

Equivalent Uniform Thickness of SFRM

Preliminary simulations with FSl explored the extent to which bare steel structural elements would heat more rapidly than the same elements would if they were well insulated. In one such calculation

experiment, one of the largest columns in the tower structure was immersed in a furnace at 1,100 °C.

Uninsulated, it took just 13 min for the steel surface temperatures to reach 600 °C, in the range where

substantial loss of strength occurs. When insulated with 1 1/8 in. of SFRM, the same column had not reached that temperature in 10 hours. This established that the fires in WTC 1 and WTC 2 would not be

able to significantly weaken the insulated core or perimeter columns within the 102 min and 56 min,

respectively, after impact and prior to collapse. Thus, it was important to know whether the insulation was present or removed and much less important to know the exact thickness of the SFRM.

It was likely that the thinner steel bars and angles in the floor trusses would be more sensitive to the condition of the insulation. If the insulation were present, but too thin or imperfectly applied, these

components might have been heated to failure in times on the order of an hour.

NIST performed additional simulations to probe the effect of gaps in the truss insulation and of variations

in the thickness, similar to those observed in real SFRM application (Figure 5-6). It was evident that incorporation of these small-scale variations into the description of the structural members would have

lengthened the FSl computations to an extreme. Furthennore, there was insufficient information to determine how the thickness varied over the length of the structural members. NIST combined the

measured variations in the SFRM thickness (as described in Section 5.6.2) with simulations of the heat

transfer through the uneven material. This led to the identification of a unifonn thickness that provided

the same insulation value as did the measured coatings. These values, shown in Table 5-3, were used in the thermal calculations. They were found to be greater than the specified thicknesses but slightly smaller

than the average measured thicknesses, as they should be.

SFRM Thermophysical Properties

When the Investigation began, there were few published data on the insulating properties of SFRMs,

especially at elevated temperatures. It was expected, and soon confinned, that the fires could generate

temperatures up to 1,100 °C. Therefore, NIST contracted for measurement of the key SFRM

thermophysical properties that, along with coating thickness, determine the insulating effect of the

coatings. These properties included thennal conductivity, specific heat capacity, and density. These were

measured for each SFRM at temperatures up to 1,200 °C. Since there were no ASTM test methods

developed specifically for characterizing the thennophysical properties of SFRMs as a function of

temperature, ASTM test methods developed for other materials were used. Samples were prepared by the

132 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

manufacturers of the fire-resistive material, which included BLAZE-SHIELD DC/F and

BLAZE-SHIELD II.

• The thermal conductivity measurements were performed according to ASTM C 1113,

Standard Test Method for Thermal Conductivity of Refractories by Hot Wire (Platinum

Resistance Thermometer Technique). The room temperature values were in general

agreement with the manufacturer's published values for both materials. The thermal

conductivities increased with temperature.

• Specific heat capacity was measured in accordance with ASTM E 1269, Standard Test Method for Determining Specific Heat Capacity by Differential Scanning Calorimetry (DSC).

By including DSC measurement of a NIST Reference Material (sapphire), the measured

SFRM quantities were directly traceable to NIST standards.

• The densities of the SFRMs were calculated from measurements of changes in the mass and

dimensions of samples as their temperatures were increased. The length-change

measurements were performed according to ASTM E 228, Standard Test Method for Linear

Thermal Expansion of Solid Materials. The mass loss measurements were performed

according to ASTM E 1131, Standard Test Method for Compositional Analysis by

Thermogravimetry

.

It was not known which type(s) of gypsum wallboard were used to enclose the core columns. Therefore,

the thermophysical properties of four types of gypsum panels were examined.

• Thermal conductivity was measured using the heated probe technique described in ASTM

D 5334, Standard Test Method for Determination of Thermal Conductivity of Soil and Soft

Rock by Thennal Needle Probe Procedure. In general, the thermal conductivity initially

decreased as the temperature increased to 200 °C and then increased with increasing

temperature above 300 °C.

• Specific heat capacities of the cores of the four gypsum panel samples were measured using a

differential scanning calorimeter at NIST according to ASTM E 1269, Standard Test Method

for Determining Specific Heat Capacity by Differential Scanning Calorimetry. The four

panels had nearly identical specific heat capacities as a function of temperature.

• The variation of density with temperature was determined from the change in volume of the gypsum material and the mass loss. The linear expansion was determined using a dilatometer

and the mass loss from thermogravimetric analysis. All four materials showed the same trend

as a function of temperature.

6.12.4 FSI Uncertainty Assessment

As was done for FDS, it was necessary to establish the quality of FSI' s predictions of temperature profiles

within insulated and bare structural steel components. This was accomplished using data from a series of

six tests in which assorted steel members were exposed to controlled fires of varying heat release rate and

radiative intensity. The steel members, depicted in Figures 6-39 through 6-41, were either bare or coated

with sprayed BLAZE-SHIELD DC/F in two thicknesses. The fibrous insulation was applied by an

NISTNCSTAR 1, WTC Investigation 133
Chapter 6

experienced applicator, who took considerable care to apply an even coating of the specified thickness.

As such, the insulated test subjects represent a best case in terms of thickness and unifonnity.

Figure 6-42 shows some of the coated components.

Figure 6-39. Simple bar dimensions (in.).

Figure 6-40. Tubular column dimensions (in.).

134 NISTNCSTAR 1. WTC Investigation
Reconstruction of the Collapses

NISTNCSTAR 1. WTC Investigation 135
Chapter 6

Table 6-7 shows the dnnensions and variabiHty of the insulation for the two successful tests involving

coated steel. The thickness measurements were taken at numerous locations along the perimeter and

length of each specimen using a pin thickness gauge specifically designed for this type of insulation.

Table 6-7. Summary of insulation on steel components.

Applied Thickness (in.) Test Item Specified Thickness (in.) Mean Std. Deviation

5 Bar 0.75 0.91 0.22 Column 1.50 1.61 0.12 Truss A 0.75 1.06 0.28

Truss B 1.50 1.59 0.32

6 Bar 0.75 1.00 0.18 Column 0.75 0.84 0.14

Truss A 0.75 1.02 0.27

Truss B 0.75 1.01 0.27

Temperatures were recorded at multiple locations on the surfaces of the steel, the insulation, and the compartment. As an example, Figure 6^3 shows the finite element representation of the coated truss.

Figure 6-43. Finite element representation of the Insulated steel truss (blue), the

SFRM (violet), and the ceiling (red).

Figure 6-44 compares the measured and predicted temperatures on the steel surface of the top chord of a bare truss. Figure 6^5 is the analogous plot of the measured and predicted temperatures on the steel surface of the top chord of a truss insulated with 3/4 in. of BLAZE-SHIELD DC/F. Similar curves were

generated for each of the steel pieces, bare and insulated.

136 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

550

500

450 -

400 -

350 -

3 300 E-

|_250f- ^ 200 -

150 -

100 r

50 -

i00

Experimental Data

TU-1

TU-2

TU-3

TU-4

TU-1

TU-2

TU-3

TU-4

500 1000 1500

Time(s)

2000 2500 3000

Figure 6-44. Comparison of numerical simulations witli measurements for the steel

surface temperature at four locations on the top chord of a bare truss.

600

0^400

o

q3Q.

§ 200

Experi mental Data

TU-1

TU-2

TU-3

TU-4

Numerical Results

TU-1

TU-2

TU-3

TU-4

X X

1000 2000 3000

Time (s) 4000 5000 6000

Figure 6-45. Comparison of numerical simulations with measurements for the

temperature of the steel surface at four locations on the top chord of an insulated truss.

NISTNCSTAR 1, WTC Investigation 137
Chapter 6

Examination of the graphs for the insulated steel pieces indicated the following:

• FSI captured the shape of the temperature rise at the steel surfaces and the significant

decrease in the rate of temperature rise when the SFRM was present.

• The times to the peak temperature (or a near-plateau) were predicted to within about a minute

in all cases.

• There was no consistent pattern of overprediction or underprediction of the surface

temperatures.

• On the average, the numerical predictions of the steel surface temperature were within

7 percent of the experimental measurements for bare steel elements and within 17 percent for the insulated steel elements. The former was within the combined uncertainty in the

temperature measurements and the heat release rate in the fire model. The increase in the

latter was attributed to model sensitivity to the SFRM coating thickness and thermal

conductivity.

In general, the FSI added little to the overall uncertainty in the simulation of the temperatures at the outer

surfaces of bare steel elements and, more importantly, at the SFRM-steel interface.

An additional, important outcome of the experiments was the demonstration of the insulating effect of even 3/4 in. of SFRM. Trusses, made of relatively thin steel, were far more susceptible to heating than

the perimeter and core columns. As shown in Figure 2-10, in 15 min, a bare truss reached a temperature

at which significant loss of strength was imminent. An identical, but insulated truss had not reached that temperature in 50 min.

6.12.5 The Four Cases

FSI imposed the thermal environment from each of the four FDS fire scenarios (Cases A and B for WTC 1 and Cases C and D for WTC 2) on the four damaged structures from the aircraft simulations,

which carried the same case letters. The FSI output files carried the same case letters as the input files.

The FSI calculations were performed at time steps ranging from 1 ms to 50 ms. Use of the resulting data

set for stnictural analysis would have required a prohibitive amount of computation time. Thus, for each

case, the instantaneous temperature and temperature gradient for each grid volume was provided at 10 min intervals after aircraft impact. For WTC I, there were 10 such intervals, ending at 6,000 s; for WTC 2 there were 6 intervals, ending at 3,600 s. Comparison of these coarsely timed output files with

files at 1 min resolution showed any differences to be within the combined uncertainty.

Each floor in the FSI simulation provided thermal information for the floor assembly above. Thus, there was not sufficient information for FSI to model the lowest floor in the FDS simulations. For WTC 1, the

global thermal response generated by FSI included floors 93 through 99; for WTC 2, the included floors were 79 through 83.

138 NISTNCSTAR 1. WTC Investigation
Reconstruction of the Collapses

For ease of visualization, two graphic representations were developed. Figure 6-A6 shows an example of

the temperature map for the 96"" floor of WTC 1 . Severed columns and broken floor segments are not shown. Figure 6^7 shows a similar map for the 81^' floor of WTC 2.

North Tower : 96th Floor

Figure 6-47. Temperatures (°C) on the columns and trusses of the 81 floor of WTC 2 at 3,000 s after aircraft impact, Case D. A third visualization tool was animation of the evolving temperatures of the columns. Frames from an example, again of the 96"^ floor of WTC I, Case A, are shown in Figure 6-48. The size of the square

representing a column represents its yield strength. Columns may have been heated when the fire was

nearby and then cooled after the local combustibles were consumed.

NISTNCSTAR 1. WTC Investigation 139
Chapter 6

140 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

6.12.6 Characterization of the Thermal Profiles

Tables 6-8 and 6-9 summarize the regions of the floors in which the structural steel reached temperatures

at which their yield strengths would have been significantly diminished. Instances of brief heating of one

or two columns early in the fires were not included.

Even in the vicinity of the fires, the columns and trusses for which the insulation was intact did not heat to temperatures where significant loss of strength occurred.

Unlike the simulations of the aircraft impact and the fires, there was no evidence, photographic or other, for direct comparison with the FSl results.

Table 6-8. Regions in WTC 1 in which temperatures of structural steel exceeded 600 °C.

Floor

Number

Trusses Perimeter Columns Core Columns

Case A CaseB Case A Case B Case A CaseB

9394 N, S NE, S

95 N N, S S NW. S 96 N N, S S s w, s 97 N, S N, S S N w, s 98 N N, S 99

Key: N. north; NE, northeast; NW, northwest; S, south: W, west.

Table 6-9. Regions in WTC 2 in which temperatures of structural steel exceeded 600 °C.

Floor

Number

Trusses Perimeter Columns Core Columns

Case C Case D CaseC Case D CaseC CaseD

79

80

81 NE NE NE NE NE

82 E E E E E E

83 E E E E

Key: E, east; NE, northeast.

6.13 MEASUREMENT OF THE FIRE RESISTANCE OF THE FLOOR SYSTEM

As described in Section 5.4.7, the composite floor system, composed of open-web, lightweight steel trusses topped with a slab of lightweight concrete, was an innovative feature. As further noted in Section 5.6.2, the approach to achieving the specified fire resistance for these floors was the use of a SFRM. Documents indicated that the fire performance of the composite floor system of the WTC towers was an issue of concern to the building owners and designers. However, NIST found no evidence

regarding the technical basis for the selection of insulation material for the floor trusses or for the

insulation thickness to achieve a 2 hour rating. Further, NIST has found no evidence that fire resistance

tests of the WTC floor system were conducted.

NISTNCSTAR 1, WTC Investigation 141
Chapter 6

Most of the possible building collapse sequences included some contribution from the floors, ranging

from their ability to transfer load to their initiating the collapse by their failure. Thus, it became central to the Investigation to obtain data regarding the limits of the insulated floors in withstanding the heat from

the fires. The standard test for determining the fire endurance of floor assemblies is ASTM E 119,

"Standard Test Methods for Fire Tests of Building Construction and Materials." The conduct of the test

is described in Section 1.2.2 under "Fire Protection Systems."

Accordingly, NIST contracted with Underwriters Laboratories, Inc. to conduct tests to obtain information on the fire endurance of trusses like those in the WTC towers. The objective was to understand the

effects of three factors:

• Scale of the test. There were no established facilities capable of testing the 60 ft lengths of

the long spans that were used in the towers, but there is a history of testing reduced-scale

assemblies and scaling them to practical dimensions. In the Investigation's tests, the full- scale test specimens were 35 ft long, equal to the shorter span between the core and the perimeter of the WTC towers. Their construction replicated, as closely as possible, the

original short-span floors. The reduced-scale specimens were half that length and height. All

assemblies were 14 ft wide. The simulation of a "maximum load condition," as required by

ASTM E 1 1 9, involved placing a combination of concrete blocks and containers filled with

water on the top surface of the floor. The load on the shorter truss was double that of the longer truss to achieve the same state of stress in both trusses. Traditionally, relatively smallscale assemblies have been tested and results have been scaled to practical floor system

spans.

• SFRM thickness. The Port Authority originally specified BLAZE-SHIELD D as the SFRM,

applied to a Vi in. covering. The average measured thicknesses were found to be

approximately 0.75 in. These two thicknesses of BLAZE-SHIELD D were used in the

Investigation tests.

• Test restraint conditions. In 1971, well after the design of the towers was completed, the ASTM E 1 19 Standard began differentiating between thermally restrained and unrestrained

floor assemblies. An unrestrained assembly is free to expand thermally and to rotate at its supports; a restrained assembly is not. It is customary in the United States to conduct

standard fire tests of floor assemblies in the restrained condition. The current standard

describes a means to establish unrestrained ratings for floor assemblies from restrained test

results. In practice, a floor assembly such as that used in the WTC towers is neither

restrained nor unrestrained but is likely somewhere in between. Testing under both restraint conditions, then, is thought to bound perfonnance under the standard fire exposure. In

addition, it provided a comparison of unrestrained ratings developed from both restrained and

unrestrained test conditions.

The test plan included four tests, which varied the three factors:

Test 1: 35 ft floor, y4 in. insulation, restrained

Test 2: 35 ft floor, in. insulation, unrestrained

142 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

Test 3: 17 ft floor, y4 in. insulation, restrained

Test 4: 17 ft floor, Vi in. insulation, restrained

The results of the four tests are summarized as follows:

• All four test assemblies were able to withstand standard fire conditions for between Va hour

and 2 hours without exceeding the limits prescribed by ASTM E 1 19.

• All four test specimens sustained the maximum design load for approximately 2 hours

without collapsing.

• The restrained full-scale floor system obtained a fire resistance rating of 1 Vi hours, while the unrestrained floor system achieved a 2 hour rating. Past experience with the ASTM E 1 19

test method led investigators to expect the unrestrained floor assembly to receive a lower

rating than the restrained assembly.

• For assemblies with a Va in. SFRM thickness, the 17 ft assembly's fire rating was 2 hours; the 35 ft assembly's rating was 1 Vi hours. This result raised the question of whether or not a fire rating of a 17 ft floor assembly is scalable to the longer spans in the WTC towers.

• The specimen in Test 4, with a fire rating of Va hour, would not have met the 2 hour

requirement of the NYC Building Code.

The Investigation Team was cautious about using these results directly in the formulation of collapse

hypotheses. In addition to the scaling issues raised by the test results, the fires in the towers on September 1 1 , and the resulting exposure of the floor systems, were substantially different from the conditions in the test furnaces. Nonetheless, the results established that this type of assembly was capable

of sustaining a large gravity load, without collapsing, for a substantial period of time relative to the duration of the fires in any given location on September 1 1

.

6.14 COLLAPSE ANALYSIS OF THE TOWERS

6.14.1 Approach to Determining the Probable Collapse Sequences

At the core of NIST's reconstruction of the events of September 11, 2001, were the archive of

photographic and video evidence, the observations of people who were on the scene, the assembled

documents describing the towers and the aircraft, and Investigation-generated experimental data on the properties of construction and furnishing materials and the behavior of the fires. Information from all of

these sources fed the computer simulations of the towers, the aircraft impacts, the ensuing fires and their heating of the structural elements, and the structural changes that led to the collapse of the towers. To the extent that the input information was complete and accurate, the output of the simulations would have

provided definitive responses to the first three objectives of the Investigation. However, the available

information, as extensive as it was, was neither complete nor of assured precision. As a result, the Investigation Team took steps to ensure that the conclusions of the effort were credible explanations for how the buildings collapsed and the extent to which the casualties occurred.

NISTNCSTAR 1, WTC Investigation 143
Chapter 6

One principal step was the determination of those variables that most affected the outcome of the various

computer simulations. Sensitivity studies and examination of components and subsystems were carried out for the modeling of the aircraft impact, the fires, and the structural response to impact damage and

fires. For each of the most influential variables, a central or middle value and reasonable high and low

values were identified. Further computations refined the selection of these values. The computations also were improved to include physical processes that could play a significant role in the structural degradation of the towers.

The Investigation Team then defined three cases for each building by combining the middle, less severe, and more severe values of the influential variables. Upon a preliminary examination of the middle cases,

it became clear that the towers would likely remain standing. The less severe cases were discarded after the aircraft impact results were compared to observed events. The middle cases (which became Case A

for WTC 1 and Case C for WTC 2) were discarded after the structural response analysis of major

subsystems were compared to observed events. The more severe case (which became Case B for WTC 1 and Case D for WTC 2) was used for the global analysis of each tower.

Complete sets of simulations were then performed for Cases B and D. To the extent that the simulations

deviated from the photographic evidence or eyewitness reports, the investigators adjusted the input, but

only within the range of physical reality. Thus, for instance, the observed window breakage was an input

to the fire simulations and the pulling forces on the perimeter columns by the sagging floors were

adjusted within the range of values derived from the subsystem computations.

The results were a simulation of the structural deterioration of each tower from the time of aircraft impact

to the time at which the building became unstable, i.e., was poised for collapse. Cases B and D

accomplished this in a manner that was consistent with the principal observables and the governing

physics.

6.14.2 Results of Global Analysis of WTC 1

After the aircraft impact, gravity loads that were previously carried by severed columns were redistributed

to other columns. The north wall lost about 7 percent of its loads after impact. Most of the load was

transferred by the hat truss, and the rest was redistributed to the adjacent exterior walls by spandrels. Due

to the impact damage and the tilting of the building to the north after impact, the south wall also lost gravity load, and about 7 percent was transferred by the hat truss. As a result, the east and west walls and

the core gained the redistributed loads through the hat truss.

Structural steel and concrete expand when heated. In the early stages of the fire, temperatures of

structural members in the core rose, and the resulting thermal expansion of the core columns was greater

than the thermal expansion of the (cooler) exterior walls. The floors also thermally expanded in the early

stages of the fires. About 20 min after the aircraft impact, the difference in the thermal expansion

between the core and exterior walls, which was resisted by the hat truss, caused the core columns' loads

to increase. As floor temperatures increased, the floors sagged and began to pull inward on the exterior

wall. As the fires continued to heat areas of the core that were without insulation, the columns weakened

and shortened and began to transfer their loads to the exterior walls through the hat truss until the south

wall started to bow inward due to the inward pull of the sagging floors. At about 100 min, approximately

20 percent of the core loads had been transferred by the hat truss to the exterior walls due to weakening of

144 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

the core, the loads on the north and south walls had each increased by about 10 percent, and those on the

east and west walls had about a 25 percent increase. The increased loads on the east and west walls were

due to their relatively higher stiffness compared to the impact damaged north wall and bowed south walls.

The inward bowing of the south wall caused failure of exterior column splices and spandrels, and these

columns became unstable. The instability spread horizontally across the entire south face. The south

wall, now unable to bear its gravity loads, redistributed these loads to the thermally weakened core through the hat truss and to the east and west walls through the spandrels. The building section above the impact zone began tilting to the south as the columns on the east and west walls rapidly became unable to carry the increased loads. This further increased the gravity loads on the core columns. The gravity loads

could no longer be redistributed, nor could the remaining core and perimeter columns support the gravity

loads from the floors above. Once the upper building section began to move downwards, the weakened

structure in the impact and fire zone was not able to absorb the tremendous energy of the falling building

section and global collapse ensued.

6.14.3 Results of Global Analysis of WTC 2

Before aircraft impact, the load distribution across the exterior walls and core was symmetric with respect

to the centerline of each exterior wall. After aircraft impact, the exterior column loads on the south side

of the east and west walls and on the east side of south wall increased. This was due to the leaning of the building core towards the southeast. After aircraft impact, the core carried 6 percent less load. The north

wall load reduced by 6 percent and the east face load increased by 24 percent. The south and west walls

carried 2 percent to 3 percent more load.

In contrast to the fires in WTC 1 , which generally progressed from the north side of the building to the south side over approximately 1 hour, the fires in WTC 2 were located on the east side of the core and

floors from the time of impact until the building collapsed, with the fires spreading somewhat from south

to north. With insulation dislodged over much of the same area, the structural temperatures became

elevated in the core, floors, and exterior walls at similar times. During the early stages of the fires, columns with dislodged insulation elongated due to thermal expansion. As the structural temperatures

continued to rise, the columns thermally weakened and consequently shortened. Thennal expansion of

the floors also occurred early in the fires, but as floor temperatures increased, the floors sagged and began

to pull inward on the exterior columns.

The south exterior wall displaced downward following the aircraft impact, but did not displace fiirther

until the east wall became unstable 43 min later. The inward bowing of the east wall, due to the inward

pull of the sagging floors, caused failure of exterior column splices and spandrels and resulted in the east wall columns becoming unstable. The instability progressed horizontally across the entire east face. The

east wall, now unable to bear its gravity loads, redistributed them to the thermally weakened core through

the hat truss and to the east and west walls through the spandrels.

The building section above the impact zone began tilting to the east and south as column instability

progressed rapidly from the east wall along the adjacent north and south walls, and increased the gravity

load on the weakened east core columns. The gravity loads could no longer be redistributed, nor could

the remaining core and perimeter columns support the gravity loads from the floors above. As with

WTC 1, once the upper building section began to move downwards, the weakened structure in the impact

NISTNCSTAR 1. WTC Investigation 145
Chapter 6

and fire zone was not able to absorb the tremendous energy of the falling building section and global

collapse ensued.

6.14.4 Events Following Collapse Initiation

Failure of the south wall in WTC 1 and east wall in WTC 2 caused the portion of the building above to tilt in the direction of the failed wall. The tilting was accompanied by a downward movement. The story

immediately below the stories in which the columns failed was not able to arrest this initial movement as evidenced by videos from several vantage points.

The structure below the level of collapse initiation offered minimal resistance to the falling building mass

at and above the impact zone. The potential energy released by the downward movement of the large

building mass far exceeded the capacity of the intact structure below to absorb that through energy of

deformation.

Since the stories below the level of collapse initiation provided little resistance to the tremendous energy

released by the falling building mass, the building section above came down essentially in free fall, as seen in videos. As the stories below sequentially failed, the falling mass increased, further increasing the demand on the floors below, which were unable to arrest the moving mass.

The falling mass of the building compressed the air ahead of it, much like the action of a piston, forcing

material, such as smoke and debris, out the windows as seen in several videos.

NIST found no corroborating evidence for alternative hypotheses suggesting that the WTC towers were

brought down by controlled demolition using explosives planted prior to September 11, 2001. NIST also did not fmd any evidence that missiles were fired at or hit the towers. Instead, photographs and videos

from several angles clearly show that the collapse initiated at the fire and impact floors and that the collapse progressed from the initiating floors downward, until the dust clouds obscured the view.

6.14.5 Structural Response of the WTC Towers to Fire without Impact or Thermal

Insulation Damage

To complete the assessment of the relative roles of aircraft impact and ensuing fires, NIST examined

whether an intense, but conventional, fire, occurring without the aircraft impact, could have led to the

collapse of a WTC tower, were the tower in the same condition as it was on September 10, 2001. NIST

used the observations, information, and analyses developed during the Investigation to enable the formulation of probable limits to the damage from such a fire. Since a complete analysis beyond the

actual collapse times of the towers was not conducted, the findings in this section represent NIST's best

technical judgment based on the available observations, information, and analyses:

• Ignition on a single floor by a small bomb or other explosion. If arson were involved, there might have been multiple small fires ignited on a few floors.

• Air supply determined by the building ventilation system.

• Moderate fire growth rate. In the case of arson, several gallons of an accelerant might have

been applied to the building combustibles, igniting the equivalent of several workstations.

146 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

• Water supply to the sprinklers and standpipes maliciously compromised.

• Intact structural insulation and interior walls.

The four cases described in this chapter represented fires that were far more severe than this:

• About 10,000 gallons ofjet fuel were sprayed into muhiple stories, quickly and

simultaneously igniting hundreds of workstations and other combustibles.

• The aircraft and subsequent fireballs created large open areas in the building exterior through

which air could flow to support the fires.

• The impact and debris removed the insulation from a large number of structural elements that were then subjected to the heat from the fires.

Additional findings from the Investigation showed that:

• Both the results of the multiple workstation experiments and the simulations of the WTC fires showed that the combustibles in a given location, if undisturbed by the aircraft impact, would

have been almost fully burned out in about 20 min.

• In the simulations of Cases A through D, none of the columns and trusses for which thermal

insulation was intact reached temperatures at which significant loss of strength occurred.

Thermal analyses showed that steel temperatures in areas where the insulation remained

intact rarely exceeded 400 °C in WTC 1 and 500 °C in WTC 2.

• In WTC 1, if fires had been allowed to continue past the time of building collapse, complete

burnout would likely have occurred within a short time since the fires had already traversed

around the entire floor and most of the combustibles would already have been consumed (see

Figure 6-38). During the extended period from collapse to burnout, the steel temperatures

would likely not have increased very much. The installed insulation in the fire-affected floors of this building had been upgraded to an average thickness of 2.5 in.

• In a fire simulation of WTC 2, that was extended for 2 hours beyond Case D and with all windows broken during this period, the temperatures in the truss steel on the west side of the building (where the insulation was undamaged) increased for about 40 min before falling off

rapidly as the combustibles were consumed. Results for a typical floor (floor 8 1 ) showed that temperatures of 700 °C to 760 °C were reached over approximately 15 percent of the west

floor area for less than 10 min. Approximately 60 percent of the floor steel had temperatures

between 600 °C and 700 °C for about 15 min. Approximately 70 percent of the floor steel had temperatures that exceeded 500 °C for about 45 min. At these temperatures, the floors would be expected to sag and then recover a portion of the sag as the steel began to cool. Based on results for Cases C and D, the temperatures of the insulated exterior and core columns would not have increased to the point where significant loss of strength or stiffness would occur during these additional 2 hours. With intact, cool core columns, any inward

bowing of the west exterior wall that might occur would be readily supported by the adjacent

exterior walls and core columns.

NISTNCSTAR 1, WTC Investigation 147
Chapter 6

• Both WTC 1 and WTC 2 were stable after the aircraft impact, standing for 102 min and

56 min, respectively. The global analyses with structural impact damage showed that both

towers had considerable reserve capacity. This was confirmed by analysis of the post-impact

vibration of WTC 2, the more severely damaged building, where the damaged tower

oscillated with a peak amplitude that was between 30 percent and 40 percent of the sway

under hurricane force winds for which the towers were designed and at periods nearly equal

to the first two translation and torsion mode periods calculated for the undamaged structure.

• Computer simulations, supported by the results of large-scale fire tests and furnace testing of

floor subsystems, showed that insulated structural steel, when coated with the average

installed insulation thickness of y4 in., would not have reached high temperatures (i.e., greater

than 650 °C) from nearby fires for a longer time than the burnout time of the combustibles

(approximately 20 min for 4 lb/ft" of combusted material). Simulations also showed that variations in thickness resulting from normal application, even with occasional gaps in coverage, would not have changed this result.

• Inward bowing of the exterior walls in both WTC 1 and WTC 2 was observed only on the

face with the long-span floor system. In WTC 1, this was found to be the case even though

equally extensive fires were observed on all faces. In WTC 2, fires were not observed on the long-span west face and were less intense on the short-span faces than on the east face.

• Inward bowing was a necessary but not sufficient condition to initiate collapse. In both

WTC I and WTC 2, significant weakening of the core due to aircraft impact damage and

thermal effects was also necessary to initiate building collapse.

• The tower structures had significant capacity to redistribute loads (a) from bowed walls to adjacent exterior walls with short-span floors via the arch action of spandrels, and

(b) between the core and exterior walls via the hat truss and, to a lesser extent, the floors.

In evaluating how the undamaged towers would have performed in an intense, conventional fire, NIST

considered the following factors individually and in combination:

• The temperatures that would be reached in structural steel components with intact insulation.

• The extent ofthe area over which high temperatures (e.g., greater than 600 °C where

significant thermal weakening of the steel occurs) would be reached at any given time.

• The duration over which the high temperatures would be sustained concurrently in any given

area.

• The length ofthefloor span (long or short) where high temperatures would be reached.

• The number offloors with areas where high temperatures would be sustained concurrently in the long-span direction.

148 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

• The potentialfor inward bowing ofexterior walls (i.e., magnitude and extent of bowing over

the \\ idth of the face and the number of floors involved) due to thermally induced floor sagging of long-span floors and associated inward pull forces.

• The capacity- ofthe structure to redistiibiite loads (e.g., via the spandrels, hat truss, and

floors) if the thermal conditions were sufficiently intense to cause inward bowing of the exterior walls.

In addition, NIST considered the following known facts:

• WTC 1 did not collapse dtiring the major fire in 1975, which engulfed a large area (about

one-fourth of the floor area or 9,000 ft') on the southeast quadrant of the 1 1th floor. At the time, office spaces in the towers were not sprinklered. The fire caused minimal damage to the floor system with the Vi in. specified insulation thickness applied on the trusses (four

trusses were slightly distorted), and at no time was the load-carrymg capacity compromised

for the floor system or the structure as a whole.

• Four standard fire resistance tests of floor assemblies like those in the WTC towers conducted

as part of this Investigation showed that (a) it took about 90 min of sustained heating in the furnace for temperatures to exceed 600 °C on steel truss members with either Vi in. or in. insulation thickness, and (b) in no case was the load-carrying capacity compromised by

heating of the floor system for 2 hours at furnace temperatures, with applied loads exceeding

those on September 11 by a factor of two.

From these findings, factors, and observed performance, NIST concluded:

• In the absence of structural and insulation damage, a conventional fire substantially similar to or less intense than the fires encountered on September 1 1, 2001, likely would not have led to the collapse of a WTC tower.

• The condition of the insulation prior to aircraft impact, which was found to be mostly intact,

and the insulation thickness on the WTC floor system contributed to, but did not play a governing role, in initiating collapse of the towers.

• The towers likely would not have collapsed under the combined effects of aircraft impact and

the subsequent multi-floor fires encountered on September 1 1 if the thermal insulation had

not been widely dislodged or had been only minimally dislodged by aircraft impact.

These findings apply to fires that are substantially similar to or less intense than those encountered on September 11, 2001 . They do not apply to a standard fire or an assumed fire exposure which has

(a) uniform high temperatures over an entire floor or most of a floor (note that the WTC floors were

extremely large) and concurrently over multiple floors, (b) high temperatures that are sustained

indefinitely or for long periods of time (greater than about 20 min at any location), and (c) combusted fire loads that are significantly greater than those considered in the analyses. They also do not apply if the capacity of the undamaged structure to redistribute loads via the spandrels, hat truss, and floors is not accounted for adequately in a fiiU 3 -dimensional simulation model of the structure.

NISTNCSTAR 1, WTC Investigation 149
Chapter 6

6.14.6 Probable WTC 1 Collapse Sequence

Aircraft Impact Damage

• The aircraft impact severed a number of exterior columns on the north wall from the 93"^ to the 98"" floors, and the wall section above the impact zone moved downward.

• After breaching the building's perimeter, the aircraft continued to penetrate into the building,

severing floor framing and core columns at the north side of the core. Core columns were

also damaged toward the center of the core. Insulation was damaged from the impact area to the south perimeter wall, primarily through the middle one-third to one-half of the core width.

Finally, the aircraft debris removed a single exterior panel at the center of the south wall

between the 94"' and 96"' floors.

• The impact damage to the exterior walls and to the core resulted in redistribution of severed

column loads, mostly to the columns adjacent to the impact zones. The hat truss resisted the

downward movement of the north wall.

• Loads on the damaged core columns were redistributed mostly to adjacent intact core columns and to a lesser extent to the north perimeter columns through the core floor systems

and the hat truss.

• As a result of the aircraft impact damage, the north and south walls each carried about

7 percent less gravity load after impact, and the east and west walls each carried about

7 percent more load. The core carried about 1 percent more gravity load after impact.

Thermal Weakening of the Structure

• Under the high temperatures and stresses in the core area, the remaining core columns with

damaged insulation were thennally weakened and shortened, causing the columns on the

floors above to move downward. The hat truss resisted the core column shortening and

redistributed loads to the perimeter walls. The north and south walls' loads increased by

about 10 percent, and the east and west walls' loads increased by about 25 percent, while the core's loads decreased by about 20 percent.

• The long-span sections of the 95* to 99* floors on the south side weakened with increasing

temperatures and began to sag. Early on, the floors on the north side had sagged and then

contracted as the fires moved to the south and the floors cooled. As the fires intensified on

the south side, the floors there sagged, and the floor connections weakened. About

20 percent of the connections on the south side of the 97"' and 98"' floors failed.

• The sagging floors with intact floor connections pulled inward on the south perimeter

columns, causing them to bow inward.

150 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

Collapse Initiation

• The bowed south wall columns buckled and were unable to carry the gravity loads. Those

loads shifted to the adjacent columns via the spandrels, but those columns quickly became

overloaded as well. In rapid sequence, this instability spread all the way to the east and west

walls.

• The section of the building above the impact zone (near the 98"^ floor), acting as a rigid block,

tilted at least 8 degrees to the south.

• The downward movement of this structural block was more than the damaged structure could

resist, and global collapse began.

6.14.7 Probable WTC 2 Collapse Sequence

Aircraft Impact Damage

• The aircraft impact severed a number of exterior columns on the south wall from the 78* floor to the 84''^ floor, and the wall section above the impact zone moved downward.

• After breaching the building's perimeter, the aircraft continued to penetrate into the building,

severing floor framing and core columns at the southeast comer of the core. Insulation was damaged from the impact area through the east half of the core to the north and east perimeter

walls. The floor truss seat connections over about one-fourth to one-half of the east side of

the core were severed on the 80'*" and 81" floors and over about one-third of the east perimeter wall on the 83'^'' floor. The debris severed four columns near the east comer of the north wall between the 80"" and 82"'* floors.

• The impact damage to the perimeter walls and to the core resulted in redistribution of severed

column loads, mostly to the colurrms adjacent to the impact zones. The impact damage to the core columns resulted in redistribution of severed column loads, mainly to other intact core columns and the east exterior wall. The hat truss resisted the downward movement of the south wall.

• As a result of the aircraft impact damage, the core carried about 6 percent less gravity load. The north wall carried about 10 percent less, the east face carried about 24 percent more, and

the west and south faces carried about 3 percent and two percent more, respectively.

• The core was then leaning slightly toward the south and east perimeter walls. The perimeter

walls restramed the tendency of the core to lean via the hat tmss and the intact floors.

Thermal Weakening of the Structure

• Under the high temperatures and stresses in the core area, the remaining core columns with

damaged insulation were thermally weakened and shortened, causing the columns on the

floors above to move downward.

NISTNCSTAR 1. WTC Investigation 151
Chapter 6

At this point, the east wall carried about 5 percent more of the gravity loads, and the core

carried about 2 percent less. The other three walls carried between 0 percent and 3 percent

less.

The long-span floors on the east side of the 79"^ to 83'^'' floors weakened with increasing

temperatures and began to sag. About one-third of the remaining floor coimections to the

east perimeter wall on the 83'^'' floor failed.

Those sagging floors whose seats were still intact pulled inward on the east perimeter

columns, causing them to bow inward. The inward bowing increased with time.

Collapse Initiation

As in WTC 1 , the bowed columns buckled and became unable to carry the gravity loads. Those loads shifted to the adjacent columns via the spandrels, but those columns quickly

became overloaded. In rapid sequence, this instability spread all across the east wall.

Loads were transferred from the failing east wall to the weakened core through the hat truss and to the north and south walls through the spandrels. The instability of the east face spread

rapidly along the north and south walls.

The building section above the impact zone (near the 82"'' floor) tilted 7 degrees to 8 degrees

to the east and 3 degrees to 4 degrees to the south prior to significant downward movement of

the upper building section. The tilt to the south did not increase any further as the upper

building section began to fall, but the tilt to the east was seen to increase to 20 degrees until dust clouds obscured the view.

The downward movement of this structural block was more than the damaged structure could

resist, and the global collapse began.

6.14.8 Accuracy of the Probable Collapse Sequences

Independent assessment of the validity of the key steps in the collapse of the towers was a challenging

task. Some of the photographic information had been used to direct the simulations. For example, the timing of the appearance of broken windows was an input to the fire growth modeling. However, there were significant observables that were usable as corroborating evidence, as shown in Tables 6-10 and

6 11. Some of these were used to establish the quality of the individual simulations of the aircraft impact

and the fire growth, as described in Sections 6.9 and 6.10. While the agreement between observations

and simulation was not exact, the differences were within the uncertainties in the input information. The

generally successfiil comparisons lent credibility to the overall reconstruction of the disaster.

There remained a small, but important number of observations against which the structural collapse

sequences could be judged. The comparisons are for Cases B and D impact damage and temperature

histories, for which the better agreement was obtained.

152 NISTNCSTAR 1, WTC Investigation
Reconstruction of the Collapses

Table 6-10. Comparison of global structural model predictions and

observations for WTC 1, Case B. Observation Simulation

Following the aircraft impact, the tower still stood. The tower remained upright with significant reserve

capacity.

The south perimeter wall was first observ ed to have

bowed inward at 10:23 a.m. The bowing appeared over

nearly the entire south face of the 94"' to 100* floors. The maximum bowing was 55 in. on the 97''' floor. (The

central area in available images was obscured by

smoke.)

The inward bowing of the south wall at 10:28 a.m. It extended from the 94"' to the lOO"' floor, with a maximum of about 43 in.

As the strucmral collapse began, the building section abov e the impact and fire zone tilted at least 8 degrees to the south with no discemable east or west component in the tilt. Dust clouds obscured the view as the building

section began to fall dowTiward.

The south side bowed and weakened. The analysis

stopped as the initiation of global instability was

imminent.

The time to collapse initiation was 102 min from the

aircraft impact.

There was significant weakening of the south wall and

the core columns. Instability was imminent at 100 min.

Table 6-11. Comparison of global structural model predictions and

observations for WTC 2, Case D. Observation Simulation

Following the aircraft impact, the tower still stood. The tower remained upright with significant resewe

capacity.

The east perimeter wall was first observed to have

bowed inward approximately 10 in. at floor 80 at 9:2 1 a.m. The bowing extended across most of the east face between the 78"' and 83''' floors.

The inward bowing of the east wall had a maximum

value of about 9.5 in. at 9:23 a.m. The bowing extended

from the 78"' floor to the 83"^ floor.

The building section above the impact and fire area tilted to the east and south as the structural collapse initiated. The angle was approximately 3 degrees to 4 degrees to the south and 7 degrees to 8 degrees to the east prior to significant downward movement of the upper building

section. The tilt to the south did not increase as the upper building section began to fall, but the tilt to the

east rose to approximately 25 degrees before dust clouds obscured the view.

At point of instability, there was tilting to the south and

east.

TTie time to collapse initiation was 56 min after the

aircraft impact.

The analysis predicted global instability after 43 min.

The agreement between the observations and the simulations is reasonably good, supporting the validity

of the probable collapse sequences. The exact times to collapse initiation were sensitive to the factors that controlled the inward bowing of the exterior columns. The sequence of events leading to collapse

initiation was not sensitive to these factors.

NISTNCSTAR 1. WTC Investigation 153
Chapter 6

6.14.9 Factors that Affected Building Performance on September 11, 2001

• The unusually dense spacing of perimeter columns, coupled with deep spandrels, resulted in a robust building that was able to fragment the aircraft upon impact and redistribute loads from

severed perimeter columns to adjacent, intact columns.

• The wind loads used for the WTC towers, which governed the design of the framed-tube

system, significantly exceeded the requirements of the building codes of the era and were

consistent with the independent NIST estimates that were based on current state-of-the-art considerations.

• The robustness of the perimeter framed-tube system and the large lateral dimension of the

towers helped the buildings withstand the impact of the aircraft.

• The composite floor system enabled the floors to redistribute loads from places of aircraft impact damage to other locations, avoiding larger scale collapse upon impact.

• The hat truss resisted the significant weakening of the core by redistributing loads form the

damaged columns to intact columns.

As a result of these factors, the buildings would likely not have collapsed under the combined effects of

the aircraft damage and subsequent fires if the insulation had not been widely dislodged. The thickness

and the condition of the insulation prior to aircraft impact did not play a governing role in the initiation of

building collapse.

154 NISTNCSTAR 1, WTC Investigation
Chapter 7

Reconstruction of Human Activity

7.1 BUILDING OCCUPANTS

7.1.1 Background

While much attention has properly focused on the nearly three thousand people who lost their lives at the World Trade Center (WTC) site that day, the circumstances and efforts that led to the successful

evacuation of five times that many people from the WTC towers also have been given attention. Understanding why the loss of life was high or low was one of the four objectives of the Investigation.

Success in clearing a building in an emergency can be characterized by two quantities: the time people

need to evacuate and the time available to them to do so. For the WTC towers, the times available for escape were set by the collapse of the buildings. Neither the building occupants nor the emergency

responders knew those times in advance. Moreover, the times were also three or four times shorter than

the time needed to clear the tenant spaces of WTC 1 following the 1993 bombing.

The investigators examined the design of the buildings, the behavior of the people, and the evacuation

process in detail to ascertain the factors that figured prominently in the time needed for evacuation. In analyzing these factors, NIST recognized that there were inherent uncertainties in constructing a valid

portrayal of human behavior on that day. These included limitations in the recollections of the people, the need to derive fmdings from a statistical sampling of the building population, the lack of information

from the decedents on the factors that prevented their escape, and the limited knowledge of the damage to the interior of the towers. NIST carefully considered these uncertainties in developing its fmdings and is confident in those findings and related recommendations.

7.1.2 The Building Egress System

Examination of drawings, memoranda, and calculations showed that the standard emergency evacuation

procedures required using the three stairwells. The elevators were not to be used, and the doors to the roof were to be kept locked. Under most circumstances, a local evacuation would be ordered. The people on the floors near the threat would move to three floors below the incident. Under more severe circumstances, a full building evacuation would be ordered, requiring all occupants to leave the building

by way of the stairwells.

As noted in Section 1.2.2, the locations of the stairwells differed at various heights in the buildings. This,

combined with the aircraft impacting different floors in the two towers, the different aircraft impact

location relative to the center of the building, and the different orientation of the core (Section 1.2.2), led

to different damage to the stairwells. As shown in Figure 7-1, a frame from a simulation from a NIST

contractor. Applied Research Associates (Section 6.9), the stairwell separation in this region of WTC 1 was the smallest in the building—clustered together well within the building core—and American

Airlines Flight 1 1 destroyed all three stairwells from the 92"'^ floor upward. By contrast, the separation of

the stairwells in the impacted region of WTC 2 was the largest in the building, i.e., they were located

NISTNCSTAR 1, WTC Investigation 155
Chapter 7

along different boundaries of the building core. United Airlines Flight 175 destroyed Stairwells B and C,

but not Stairwell A (Figure 7-2).

Figure 7-1. Simulated impact damage to 95 floor of WTC 1, including stairwells, 0.7 s

after impact.

Figure 7-2. Simulated impact

damage to WTC 2 on floor 78,

0.62 s after impact.

©

156 NISTNCSTAR 1, WTC Investigation
Reconstruction of Human Activity

7.1.3 The Evacuation—Data Sources

To document the egress from the two towers as completely as possible, NIST:

• Contracted with the National Fire Protection Association and the National Research Council

of Canada to index a collection of over 700 previously published interviews with WTC

survivors.

• Listened to and analyzed 9-1-1 emergency phone calls made during the morning of

September 1 1

.

• Analyzed transcripts of emergency communication among building personnel and emergency

responders.

• Examined complaints filed with the Occupational Safety and Health Administration by

surviving occupants and families of victims regarding emergency preparedness and

evacuation system perfonnance.

In addition NIST. in conjunction with NuStats, Partners, LLP as a NIST contractor, conducted an

extensive set of interview s with survivors of the disaster and family members of occupants of the

buildings. First, telephone interviews were conducted with 803 survivors, randomly selected from the list of approximately 100,000 people who had badges to enter the towers on that morning. The results enabled a scientific projection of the population and distribution of occupants in WTC 1 and WTC 2, as well as exploration of factors that affected evacuation. Second, 225 face-to-face interviews, averaging

2 hours each, gathered detailed, first-hand accounts and observations of the activities and events inside

the buildings on the morning of September 1 1 . These people included occupants near the floors of

impact, witnesses to fireballs, mobility-impaired occupants, floor wardens, building personnel with

emergency response responsibilities, family members who spoke to an occupant after 8:46 a.m., and

occupants from regions of the building not addressed by other groups. Third, six complementary focus

groups, a total of 28 people, were convened, consisting of:

1 . Occupants located near the floors of impact, to explore the extent of the building damage and

how the damage influenced the evacuation process.

2. Floor wardens, to explore the implementation of the floor warden procedures and the effect those actions had on the evacuation of the occupants on a floor and the evacuation of the floor warden.

3. Mobility-impaired occupants, to explore the effect of a disability on the evacuation of the occupant and any other individuals who may have assisted or otherwise been affected by the evacuee.

4. Persons with building responsibilities, to capture the unique perspective of custodians,

security, maintenance, or other building staff.

NISTNCSTAR 1, WTC Investigation 157
Chapter 7

5. Randomly selected evacuees in WTC 1, to explore further the variables that best explained

evacuation delay and normalized stairwell evacuation time, including environmental cues,

floor, and activities.

6. Randomly selected evacuees in WTC 2, for the same purpose as the preceding group.

The following sections describe the key findings from this large data set.

7.1.4 Occupant Demographics

The following were estimated from statistical analysis of the telephone interview data:

• There were 17,400 ± 1,180 occupants inside WTC 1 and WTC 2 at 8:46 a.m. Of these,

8,900 ± 750 were inside WTC 1 and 8,540 ± 920 were inside WTC 2.

• Men outnumbered women roughly two to one.

• The mean and median ages were both about 45, with the distribution ranging from the early

20s to the late 80s.

• The mean length of employment at the WTC was almost six years, but the median was only

two years tenure within WTC 1 and three years within WTC 2.

• Sixteen percent of the evacuees were present during the 1993 bombing, although many others

knew of the evacuation.

• Two-thirds had participated in at least one fire drill in the 12 months prior to the 2001

disaster. Eighteen percent did not recall whether they had participated or not; 1 8 percent

reported that they had not. New York City law prohibited requiring full evacuation using the

stairs during fire drills.

• Six percent reported having a limitation that constrained their ability to escape. (This

extrapolated to roughly 1,000 of the WTC 1 and WTC 2 survivors.) The most common of

these limitations, in decreasing order, were recent injury, chronic illness, and use of

medications.

Estimates based on the layouts of the tenant spaces indicated that approximately 20,000 people worked in each tower. Relatively few visitors would have been present at 8:46 a.m. Thus, the towers were between

one-third and one-half full at the time of the attack.

7.1.5 Evacuation of WTC 1

The number of survivors evacuated from WTC 1 was large, given the severity of the building damage and

the unexpectedly short available time. Of those who were below the impact floors when the aircraft struck, 99 percent survived. About 84 percent of all the occupants of the tower at the time survived. The

aircraft impact damage left no exit path for those who were above the 9r' floor. It is not known how

many of those could have been saved had the building not collapsed. While it is possible that a delayed

158 NISTNCSTAR 1, WTC Investigation
Reconstruction of Human Activity

or avoided collapse could have improved the outcome, it would have taken many hours for the FDNY to reach the 92"'' floor and higher and then to conduct rescue and fire suppression activity there.

The general pattern of the evacuation was described in Chapter 2. The following are specific facts derived from the interviews:

• The median time to initiate evacuation was 3 min for occupants from the ground floor to floor

76, and 5 min for occupants near the impact region (floors 77 through 91). The factors that best explained the evacuation initiation delays were the floor the respondent was on when

WTC 1 was attacked, whether the occupant encountered smoke, damage or fire, and whether

he or she sought additional information about what was happening.

• Occupants throughout the building observed various types of impact indicators throughout

the building, including wall, partition, and ceiling damage and fire and smoke conditions.

The filled-in squares in Figure 7-3 indicate the floors on which the different observations were reported.

• Damage to critical communications hardware likely prevented announcement transmission,

and thus occupants did not hear announcements to evacuate, despite repeated attempts from

the lobby fire command station.

• Evacuation rates reached a maximum in approximately 5 min, and remained roughly constant

until the collapse of WTC 2, when the rate in WTC 1 slowed to about 20 percent of the maximum.

• The maximum downward travel rate was just over one floor per minute, slower than the slowest speed measured for non-emergency evacuations. This was in part because:

- Occupants encountered smoke and/or damage during evacuation.

- Occupants were often unprepared for the physical challenge of frill building evacuation.

- Occupants were not prepared to encounter transfer hallways during the descent.

- Mobility-impaired occupants were not universally identified or prepared for frill building

evacuation.

- Occupants interrupted their evacuation.

• The mobility-impaired occupants did not evacuate as evenly as the general population.

- Those who were ambulatory generally walked down the stairs with one hand on each

handrail, taking one step at a time. They were typically accompanied by another

occupant or an emergency responder. Combined, they blocked others behind them from

moving more rapidly.

- On the 1 2'^ floor, FDNY personnel found 40 to 60 people, some of whom were mobility

impaired. The emergency responders were assisting about 20 of these mobility-impaired

NISTNCSTAR 1, WTC Investigation 159
Chapter 7

people down the stairs just prior to the collapse of the building. It is unknown how many

of this group survived.

- Some mobility-impaired occupants requiring assistance to evacuate were left by

coworkers, thereby imposing on strangers for assistance.

7.1 .6 Evacuation of WTC 2

The evacuation from WTC 2 was markedly different from that from WTC 1 . Over 90 percent of the occupants had started to self-evacuate before the second aircraft stmck, and three-quarters of those from

above the 78"' floor had descended below the impact region prior to the second attack. (Nearly 3,000

occupants were able to survive due to self-evacuation and the use of the still-functioning elevators.) As a

result, 91 percent of all the occupants survived. Eleven people from below the impact floors perished,

about 0. 1 percent. Eighteen people in or above the impact zone when the plane struck are known to have

found the one passable stairway and escaped. It is not known how many others from the impact floors or above found their way to the passable stairway and did not make it out or how many could have been

saved had the building not collapsed. A delayed or avoided collapse could have provided the additional

time for more people to learn about and use the passable stairway.

The general pattern of the evacuation was described in Chapter 3. The following are specific facts derived from the interviews:

• The median time to initiate evacuation was 6 min, somewhat longer than in WTC 1

.

• As in WTC I, occupants observed various types of impact indicators throughout the building,

including wall, partition, and ceiling damage and fire and smoke conditions (Figure 1—4).

• Building announcements were cited by many as a constraint to their evacuation, principally

due to the 9:00 a.m. announcement instructing occupants to return to their work spaces. Crowdedness in the stairways, lack of instructions and information, as well as injured or disabled evacuees in the stairwells were the most frequently reported obstacles to evacuation.

• Evacuation rates from WTC 2 showed three distinct phases:

(1) Before WTC 2 was attacked, occupants used elevators, as well as stairs, to evacuate,

resulting in approximately 40 percent of the eventual survivors leaving the building during

that 1 6 min window.

(2) After WTC 2 was attacked and the elevators were no longer operational, the evacuation

rate slowed down to a steady rate equivalent to the rate observed in WTC I , which also had

only stairs available to occupants.

(3) About 20 min prior to building collapse, the rate in WTC 2 slowed to approximately

20 percent of the stairwell-only evacuation rate.

160 NISTNCSTAR 1. WTC Investigation
Reconstruction of Human Activity

NISTNCSTAR 1. WTC Investigation 161
Chapter 7
Reconstruction of Human Activity

7.2 EMERGENCY RESPONDERS

7.2.1 Data Gathered

The attack on the World Trade Center produced a massive response from the emergency services within

New York City. As a resuh, copious information was produced concerning the attack and the emergency

response. Although some key information was lost when the buildings collapsed, an extensive amount was obtained from three organizations that contributed to the emergency response: The Port Authority of

New York and New Jersey (Port Authority), FDNY, and the New York City Police Department (NYPD).

There also was a significant amount of information available through the various media services. Some

of the items were transferred to NIST; the Investigation Team examined others at locations in the New

York City area. The data fell into four categories.

Documentary Data

This included procedures for conducting operations at the WTC, records generated during the WTC

operations, and records generated following the event. The last group of documents included detailed

investigative reports of the FDNY and NYPD operations by McKinsey and Company, documents of

investigative first-person interviews, and lists of decedents.

Electronic Data

These were recordings of radio and telephone communications. Some were already in digital format;

those on tape were digitized and/or transcribed. Some recordings required sound enhancement to improve comprehension.

First-Person Interviews

In October 2003, NIST entered into a three-party agreement between NIST, New York City (NYC), and

the National Commission on Terrorist Acts Upon the United States (the 9/1 1 Commission). The

agreement provided procedures under which NIST and the 9/1 1 Commission would interview a maximum of 125 NYC emergency responders, 100 from FDNY and 25 from NYPD. In December 2003,

NIST officially requested and the Port Authority agreed to interviews with 1 5 Port Authority personnel,

including emergency responders, safety, security, and management personnel. In addition to the interviews conducted under the agreements described above, NIST interviewed eight people who

contacted NIST directly and volunteered. The first-person interviews were conducted beginning in October 2003 and were completed in December 2004.

The organizations and the number of interviews conducted were:

• FDNY (68 interviews): Senior management and officers, mid-level officers, company

officers, firefighters, emergency medical personnel, and dispatchers

• NYPD (25 interviews): Senior management and officers, mid-level officers, Emergency

Service Unit personnel, aviation personnel, and dispatchers

NISTNCSTAR 1, WTC Investigation 163
Chapter 7

• PANYNJ/PAPD (15 interviews): Senior management personnel, facility safety personnel,

building security personnel, facility communications personnel, building vertical transportation personnel, senior PAPD officers, mid-level PAPD officers, and line PAPD

officers

• Other (8 interviews): A building security guard, dispatcher, firefighters, WTC building

engineer, and a fire safety director

Each interview generally took from 1 hour to 4 hours to complete, depending on the person's job and the

complexity of their involvement in emergency operations.

An interview included a self-narrative regarding the emergency responder's experience at the WTC and

follow-up questions by staff from NIST and the 9/1 1 Coimnission.

Visual Data

These still photographs and video footage became part of the collection described in Section 6.3.

7.2.2 Operation Changes following the WTC 1 Bombing on February 26, 1993

This unprecedented act had provided insight into the complex nature of responding to a large incident at the WTC towers. As a result, numerous issues were raised concerning the WTC buildings in relationship

to the emergency response. A multiagency study identified issues of security, occupant safety, and

emergency responder operations and safety. The following changes made by The Port Authority and the

FDNY had a direct impact on emergency responder operations on September 11, 2001.

The Port Authority

• Improved egress from the towers at the Concourse Level.

• Made improvements to the stairwells: battery operated emergency lighting, photoluminescent

floor strips indicating the path to be followed, and explicit signs on each doorway to indicate

where it led.

• Established a PAPD Command Center inside of WTC 5.

• Installed Fire Command Desks in the lobbies of WTC 1 and WTC 2.

• Installed in WTC 5 a radio repeater that operated on the FDNY city-wide high-rise frequency.

(The radio repeater's function was to receive FDNY radio communication on a specified

radio frequency, amplify the signal power, and retransmit the radio communications on

another specified radio frequency that the FDNY radios could receive. This could enhance

communications in buildings made of steel and reinforced concrete that pose challenges to radio-frequency communication.) The antenna was located on the top of WTC 5 and was

directed at WTC I and WTC 2 (Figure 7-5). On September 1 1, 2001, the controls for operating the repeater were located at the Fire Command Desks in the tower lobbies.

164 NISTNCSTAR 1, WTC Investigation
Reconstruction of Human Activity

Upgraded the elevator intercom system to be

monitored at the lobby Fire Command Desks.

Constructed an Operations Control Center on

the Bl level of WTC 2 with the capability to monitor all HVAC systems and elevators.

Installed a decentralized fire alarm system,

with three separate data risers to transponders

located every three floors, redundant control

panels and electronics, and multiple control

station announcement capability.

Conducted fire drills in conjunction with

FDNY.

Published a new Incident Command System

manual in May 1997.

Source: Original artwork by Marco Crupi.

Enhanced by NIST. Figure 7-5. Location of the radio

repeater.

Purchased eighty 800 MHz radios for use by deputy fire commissioners, each staff chief, and

the Field Communications Unit. Twenty of the radios were to be distributed by the Field

Communications unit at an incident, if needed.

• Issued Port Authority radios to those FDNY companies located near the WTC that often

responded to the WTC, allowing them to communicate with the building's Deputy Fire

Safety Directors and with PAPD.

In addition, The Port Authority and New York City signed two agreements applying to the fire safety of

Port Authority facilities located in New York City. The first agreement was for the implementation of

fire safety recommendations that would be made by FDNY after they had inspected Port Authority

facilities located in New York City. The second recognized the agreement that FDNY could conduct fire safety inspections of Port Authority properties in New York City. It provided guidelines for FDNY to communicate needed corrective actions to The Port Authority, and it assured that new or modified fire safety systems were to be in compliance with local codes and regulations. It also required a third party

review of the systems by a New York State licensed architect or engineer.

NIST NCSTAR 1, WTC Investigation 165
Chapter 7

7.2.3 Responder Organization

The emergency response to the attack was

immediate. Within 3 min of the aircraft impact on WTC 1 , PAPD was providing infomiation on the attack to the pohce desk, FDNY had

dispatched 26 units to the scene, and NYPD

had called a department mobilization that included dispatching aviation units to the WTC

for visual assessment. Within 10 min, PAPD

had called a chemical mobilization; NYPD had

dispatched five Emergency Service Unit (ESU)

teams and had two aviation units at the scene providing observations. Within 30 min,

121 FDNY units had been dispatched to the scene and 30 units had signaled their arrival at the scene by pushing the "10-84" button on the vehicle's communications console (Figure 7-6)

FDNY

Under New York City policy, since this was identified as a fire incident, FDNY was to be in control of

the site. By 8:50, FDNY was operating from the Fire Command Desk in the lobby of WTC 1. Within

minutes, the Incident Command Post was moved outside to West Street. The FDNY also maintained the

lobby Command Post inside WTC 1 and established one in WTC 2. Additional command posts were

established in the lobby of the Marriott Hotel (WTC 3) and on the comer of West and Liberty Streets.

Some of the first FDNY personnel on the scene had actually seen the aircraft hit the building and knew

that the upper floors were badly damaged, including the building safety systems. They also saw the victims burned by the fireball that came into the building lobby. Upon meeting with Port Authority

personnel and the previous WTC 1 Deputy Fire Safety Director, who had recently trained the new Fire

Safety Director, to learn more about building conditions, FDNY personnel quickly made judgments

related to building conditions and emergency response operations that were, in retrospect, highly accurate,

for example:

• There were large fires burning on multiple floors at and above the impact zone.

• Smoke, fire, and structural damage in the buildings prevented many building occupants from

evacuating floors above the impact zones.

• Many of the people trapped above the impact zones were already dead or would likely die

before emergency responders could reach them.

• Localized collapses within and above the impact zones were possible due to the structural damage and fires.

166 NISTNCSTAR 1, WTC Investigation
Reconstruction of Human Activity

• The elevators, some with people trapped inside, were generally not working and/or were not

safe for use during the WTC operations.

• Firefighters would have to gain access to the injured and trapped occupants by climbing the

stairs and carrying the equipment needed up the stairs.

• It would take hours to accumulate sufficient people and equipment to access the impact

zones.

• The sprinkler and standpipe systems were compromised at the impact zone and firefighting

would not be an option until a reliable water supply was established and equipment was

carried up.

• Jet fuel had flowed into the elevator shafts and into other parts of the buildings and presented

a danger to building occupants and emergency responder personnel.

Those in command decided that the response strategy was to enable the evacuation of those below the impact and fire zones. However, those directing initial operations inside the buildings followed an

additional strategy: get sufficient people and equipment upstairs to cut a path through the fire and debris

to rescue occupants above the fires. The strategy of company-level personnel, who were trained to fight

fires and perceived this as a conventional, large high-rise fire, was to get to the fire floors and extinguish

the fires.

Overlaying this trinity of operational strategies was the fact that this was the largest emergency response

in FDNY history, with roughly 1,000 firefighters on the scene. Even the singularly large response to the 1993 bombing involved about 700 emergency personnel. A typical two-alarm fire might have involved

about 100 personnel.

Thus, keeping track of what all these people were doing, where there were located, where they were

going, and what they would do when they got there was a task without precedent. The principal tools for

this were three 1 8 in. x 28 in. magnetic boards known as Fire Command Boards (Figure 7-7). They were

located in the lobbies of WTC 1 and WTC 2 and at the Incident command Post on West Street. On each

Board, magnetic identifiers of different colors identified engines, ladder and tower ladders, battalions,

special units, and sectors. Unit numbers were written on the identifiers with marking pens. These Boards

became overwhelmed after about 30 min due to the large number of people and units arriving at the scene. Some emergency personnel that arrived at the site did not report to the Command Posts or were

not logged in on the Command Board. A formal analysis of arrivals and missions of the various units was compromised by the loss of the Boards in the collapse of the towers; there were no backup records.

NYPD

The roles of the NYPD were to establish traffic control and perimeter security at the site, provide security

for the command posts, and conduct evacuation and rescue operations within the towers. Their aviation

units supplied observation capability and assessed the potential for roof rescue.

The primary mobilization point for the NYPD Special Operations Division (SOD) that sent Emergency

Service Unit (ESU) rescue teams into the WTC was at the comer of Church and Vesey Streets at the

NISTNCSTAR 1. WTC Investigation 167
Chapter 7

Figure 7-7. Fire Command Board located in the lobby of WTC 1.

northeast comer of the WTC tract. The post was managed by a SOD detective who had just gone off of

duty and was still at his office when the attack occurred. He dispatched six ESU teams, each consisting

of about five people. Records for each team were written on paper attached to a clipboard.

A second SOD mobilization point was established at the comer of West and Vesey Streets at the northwest comer of the WTC tract. The armed NYPD officers and ESU teams provided security for the

FDNY Incident Command Post.

Since there were few NYPD units and since they typically arrived with all members, keeping track of the

units was less problematic than for the FDNY. However, with the collapse of WTC 2, all written records were lost as the high winds and debris blew through the mobilization points. Since NYPD had only about

50 personnel operating in or near the towers, the managers of the mobilization points were able to easily

reconstmct the lost data on their personnel.

Although The Port Authority had not endorsed a plan for roof rescue from the towers, it appeared to be one of the few options available for occupants trapped above the fires. NYPD helicopters reached the scene by 8:52 to assess the possibility of roof rescue. They were unable to land on the roof due to heavy

smoke conditions. During the first hour, FDNY did not consider the option of roof rescue. When the

aircraft stmck WTC 2, it was clear that this was criminal activity, and the decision regarding roof top

operations became the responsibility of NYPD. The NYPD First Deputy Commissioner ordered that no

roof rescues were to be attempted, and at 9:43 a.m., this directive was passed to all units.

Roof rescue was not intended to be an option, and The Port Authority reported that it never advised

tenants to evacuate upward. The Port Authority's standard full-building occupant evacuation procedures

and drills required the use of stairways to exit at the bottom of the WTC towers. The standard procedures were to keep the doors to the roof locked. Roof access required use of an electronic swipe card to get

through the first two doors and a security officer watching a closed-circuit camera on the 22nd floor of

WTC 1 to open the third door via a buzzer. (The 1 968 NYC Building Code required access to roofs like these, most likely to provide FDNY access. The 2003 code does not intend roof access to be used for evacuation and has no prohibition on locking this access.)

168 NISTNCSTAR 1, WTC Investigation
Reconstruction of Human Activity

The NYPD and FDNY did not consider roof rescue a viable strategy for general evacuation. First, the NYPD and FDNY policies for roof operations were focused mainly on providing emergency responders

with access into the building above the fire floors for firefighting, conventional rescue, and comforting

occupants. Roof rescue was considered a measure of last resort to be used, for example, to assist occupants with medical emergencies. Second, although on September 1 1, an NYPD aviation unit was

early on the scene to consider the possibility, smoke and heat conditions at the top of the towers prevented

the conduct of safe roof operations, despite repeated attempts. Even if it had been possible for a helicopter to gain access to the roof, only a very small fraction of the large number of people trapped

above the impact zone could have been rescued before the towers collapsed. Nonetheless, perhaps as an

indication of the dire situation in the top floors of the towers, at least two decedents tried to get to the roof

and found the roof access locked in both the WTC towers. Personnel at the WTC 1 Security Control

Center on the 22"^ floor attempted to electronically release the doors to the roof, but were unsuccessful

due to damage to the computerized control system.

PAPD

The roles of the PAPD were to establish security at the WTC and to conduct evacuation operations.

PAPD officers were performing their normal law enforcement duties at the WTC site when the attack on WTC 1 occurred. Several additional PAPD teams were dispatched from various locations from around

the city and from Jersey City, with some arriving before the collapse of WTC 2 and reporting to PAPD

personnel at the WTC 1 lobby Fire Command Desk. There were dozens of PAPD officers on site and on

orders to report to the site. With the collapse of WTC 2, the PAPD Police Desk (in WTC 5) and the Command Center were evacuated. Many of the emergency response records were lost initially, but were

recovered some days later.

Interdepartmental Interactions

The coordination of communications and operations between the responding authorities at the WTC site was a challenge for all emergency responders working that morning. The short time duration between the

initial attack and the collapse of the towers, coupled with the large number of responders and their staggered arrivals, compounded the difficulty of establishing a unified operation.

FDNY (and the Emergency Medical Services), NYPD, PAPD, The Port Authority, and OEM were

attempting to work together. These efforts were stymied by a lack of existing protocols that clearly

defined authorities and responsibilities, communications systems problems, and multiple major attacks and threats. Although there was- merit to having the FDNY and NYPD Command Posts separated, there was no uniform means for communicating between the two Command Posts at the time when WTC 2

collapsed. FDNY and NYPD were primarily operating as independent organizations based on their operational responsibilities.

7.2.4 Responder Access

Fighting fires in the upper levels of tall buildings is not the same as fighting fires in buildings that are less than 100 ft high. In the case of the WTC towers, the people needing assistance were mostly many stories above the ground, and climbing tens of flights of stairs was the only way upward for the emergency

NISTNCSTAR 1. WTC Investigation 169
Chapter 7

responders. In the time available, they were not able to get very far. For example, emergency responders

wearing police unifonns, not wearing Self-contained Breathing Apparatus (SCBA), and not carrying extra equipment, were able to climb the stairs at a rate of approximately 1.4 min per floor while climbing to floors in the 40s inside of WTC 1. The climbing rate for firefighters wearing protective clothing and

SCBA and carrying extra firefighting and rescue equipment was about 2 min per floor. The downward

flow of evacuees, especially those who had physical disabilities or were obese, also slowed the responders' progress, especially in the 44 in. wide stairwells. The flow of the evacuees caused teams of

emergency responders to become separated, further disrupting team operations.

Neither the number of responders who entered the towers nor the floors they reached are known, due to the incompleteness of the Command Boards and their eventual destruction. From radio communications

and first-person interviews, it appears that there were responders as high as floors in the 50s in WTC 1 and the 78"' floor in WTC 2.

7.2.5 Communications

There were multiple equipment systems for command-to-field communications, for responders to communicate among themselves, and for contact to and from building occupants:

• Landline telephone system (including access to the 9-1-1 system),

• Emergency armouncement systems within WTC 1 and WTC 2,

• Cellular systems (including access to the 9-1-1 system),

• Warden phones (tower stair landings to Command Post),

• Firefighter phones, called standpipe phones, in the WTC towers, and

• FDNY handie-talkies, with booster support from a repeaters on WTC 5 and a Battalion car repeater located inside WTC 2.

Within WTC 1 , the system used to make the emergency announcements was disabled by the first aircraft impact, communications to the elevators in the upper third of the buildings were lost, the Warden phones

did not work, and attempts to use the landline phones to contact people upstairs were unsuccessful due to the failure of some phones in the building.

Little is known about the function of the internal communications inside WTC 2 after the aircraft struck

the building. This is because all of the key emergency responders working inside WTC 2 died when the building collapsed. However, interviews with some occupants who evacuated from the building and

interviews with emergency responders who communicated with counterparts inside WTC 2 indicated the

following: some of the building's public address systems were working, some of the elevator phone

systems were working, and some of the landline telephones were working. It is not known if the Warden

Phone system was fully operational or if the standpipe phones were operational. Emergency responder

communications inside WTC 2 primarily depended on radio and face-to-face communications.

170 NISTNCSTAR 1, WTC Investigation
Reconstruction of Human Activity

The collapse of WTC 2 caused the cellular phone system in Lower Manhattan to fail. However, there were still landlines working in the city blocks adjacent to the WTC site, and calls were still emanating

from inside WTC 1

.

All of the radio systems analyzed were working well just before the attack on the WTC. However,

PAPD, FDNY, and NYPD were aware that radio communications had not fared well in high-rise

buildings, including WTC 1 following the 1993 bombing. The vast amount of metal and steel-reinforced concrete in high-rise buildings was known to attenuate and block radio signals, especially the low output

power emergency responder handie-talkies. This was again a problem on September 11, 2001, when all three agencies encountered difficulties with their hand-held units.

Thus, there was a heavy burden placed on the FDNY repeater to boost the weak signals to a discemable

level. The repeater was functional during operations at the WTC; apparently the antenna was not damaged by debris from the aircraft impacts. However, within WTC 1 , the system did not function

correctly. The cause of this malfrinction could not be determined since the unit was destroyed in the

collapse of WTC 1. Repeater recording communications suggest that it was used within WTC 2. The

radio recordings showed that communications readability using the repeater channel was generally good

to excellent. Where readability levels were poor, it was generally caused by multiple people attempting to communicate over the radio at one time. The heavy traffic continued until the repeater failed with the collapse of WTC 2.

Had communications using the repeater been adequate in WTC 1 , there would have been opposing effects on the quality of operations and life safety. On the positive side, the emergency personnel in the tower

would have been in at least some contact with the Command Posts. However, two serious counterpoints

would have occurred. First, if the responders in both towers were using the same repeater at the same

time, the traffic would have been heavier, and more of the calls would have been indecipherable. Second,

a firefighter in either tower would have had difficulty discerning which communications related to operations in his tower. Given the inadequate markings within the towers and the unfamiliarity of some

emergency responders with the site, there was already a high degree of confusion as to which tower a responder was in.

The poor radio communications at the WTC had a serious impact on the FDNY Command Post's attempts to maintain command and control in general. All emergency responders struggled with the high

volume and low quality of radio communications traffic at the WTC, described as "radio gridlock." NIST

estimates that one-third to one-half of the emergency responder radio communications were

undecipherable or incomplete.

The poor communications had a critical effect on the conveyance of evacuation instructions. As early as 8:48, there was an order to WTC personnel to clear WTC 1. At 8:59 a.m., a senior PAPD officer called

for the evacuation of the two towers. At 9:01 a.m., this was extended to the entire complex. This was

before the second aircraft struck. At 9:04 a.m., WTC Operations told people to evacuate an unidentified

building. At 10:06 a.m., an NYPD aviation unit reported that it wouldn't be much longer before WTC 1 would come down. Some survivors reported not having received any of these messages. It is not known

how many others did not, nor whether their locations were such that they could have made it out of the buildings in time.

NISTNCSTAR 1. WTC Investigation 171
Chapter 7

7.2.6 The Overall Response

It was difficult to quantify the responders' degree of success. There were multiple reports of FDNY,

NYPD, and PAPD efforts making the difference between death and survival. There were reports of

assistance where the survival of the occupants was not detennined. There were reports of firefighters

quenching small fires on the lower floors of the towers and at the impact point in WTC 2. However, it would have been impossible for them to have had any significant effect on the fires that eventually led to the collapse of the structures.

7.3 FACTORS THAT CONTRIBUTED TO ENHANCED LIFE SAFETY

7.3.1 Aggregate Factors

• Reduced number of people in the buildings at the times of aircraft impact.

• Functioning elevators in WTC 2 for the 16 min prior to 9:02:59 a.m.

• Remoteness of Stairwell A from the impact zone and debris field.

• Participation of two-thirds of surviving occupants in recent fire drills.

• Upgrades to the life safety system components after the 1993 bombing.

• Evacuation assistance provided by emergency responders to evacuees.

7.3.2 Individual Factors

• Location below the floor of impact.

• Shortness of delay in starting to evacuate.

172

/

NISTNCSTAR 1, WTC Investigation
Part III: The Outcome of the Investigation
This page intentionally left blank.

NIST NCSTAR 1, WTC Investigation
Chapter 8

Principal Findings

8.1 INTRODUCTION

This chapter presents the findings of the National Institute of Standards and Technology (NIST),

organized according to the first three of the Investigation objectives for the World Trade Center (WTC)

towers. The fourth objective is the subject of Chapter 9. WTC 7 is the subject of a companion report.

The findings were derived fi^om the extensive documentation summarized in the preceding chapters and

described in detail in the accompanying reports. While NIST was not able to compile a complete

documentation of the history of the towers, due to the loss of records over time and due to the collapses,

the Investigators were able to acquire information adequate to support the findings and recommendations

compiled in this chapter and the next. The chapter begins with summary statements and continues with

the listing of the full set of principal findings.

Objective 1: Determine why and how WTC 1 and WTC 2 collapsed following the initial impacts of

• The two aircraft hit the towers at high speed and did considerable damage to principal

structural components (core columns, perimeter columns, and floors) that were directly

impacted by the aircraft or associated debris. However, the towers withstood the impacts and

would have remained standing were it not for the dislodged insulation and the subsequent

multi-floor fires. The robustness of the perimeter fi^ame-tube system and the large size of the buildings helped the towers withstand the impact. The structural system redistributed loads

in places of aircraft impact, avoiding larger scale damage upon impact. The hat truss, which was intended to support a television antenna atop each tower, prevented earlier collapse of the building core. In each tower, a different combination of impact damage and heat-weakened

structural components contributed to the abrupt structural collapse.

• In WTC 1 , the fires weakened the core columns and caused the floors on the south side of the building to sag. The floors pulled the heated south perimeter columns inward, reducing their capacity to support the building above. Their neighboring columns quickly became

overloaded as the south wall buckled. The top section of the building tilted to the south and

began its descent. The time from aircraft impact to collapse initiation was largely determined

by how long it took for the fires to weaken the building core and to reach the south side of the building and weaken the perimeter columns and floors.

• In WTC 2, the core was damaged severely at the southeast comer and was restrained by the

east and south walls via the hat truss and the floors. The steady burning fires on the east side

of the building caused the floors there to sag. The floors pulled the heated east perimeter

columns inward, reducing their capacity to support the building above. Their neighboring

8.2 SUMMARY

the aircraft.

NISTNCSTAR 1, WTC Investigation 175
Chapter 8

columns quickly became overloaded as the east wall buckled. The top section of the building

tilted to the east and to the south and began its descent. The time from aircraft impact to collapse initiation was largely determined by the time for the fires to weaken the perimeter

columns and floor assemblies on the east and south sides of the building. WTC 2 collapsed more quickly than WTC 1 because there was more aircraft damage to the building core, including one of the heavily loaded comer columns, and there were early and persistent fires on the east side of the building where the aircraft had extensively dislodged insulation from

the structural steel.

• The WTC towers would likely not have collapsed under the combined effects of aircraft impact damage and the extensive, multi-floor fires that were encountered on September 1 1, 2001 , if the thennal insulation had not been widely dislodged or had been only minimally

dislodged by aircraft impact.

• In the absence of structural and insulation damage, a conventional fire substantially similar to or less intense than the fires encountered on September 1 1, 2001, likely would not have led to the collapse of a WTC tower.

• NIST found no corroborating evidence for alternative hypotheses suggesting that the WTC

towers were brought down by controlled demolition using explosives planted prior to September 1 1, 2001. NIST also did not find any evidence that missiles were fired at or hit the towers. Instead, photographs and videos from several angles clearly showed that the

collapse initiated at the fire and impact floors and that the collapse progressed from the

initiating floors downward, until the dust clouds obscured the view.

Objective 2: Determine why the injuries and fatalities were so high or low depending on location,

including all technical aspects of fire protection, occupant behavior, evacuation, and emergency

response.

• Approximately 87 percent of the estimated 17,400 occupants of the towers, and 99 percent of

those located below the impact floors, evacuated successfully. In WTC 1, where the aircraft destroyed all escape routes, 1,355 people were trapped in the upper floors when the building

collapsed. One hundred seven people who were below the impact floors did not survive.

Because the flow of people from the building had slowed considerably 20 min before the

tower collapsed, the stairwell capacity was adequate to evacuate the occupants on that morning.

• In WTC 2, before the second aircraft strike, about 3,000 people got low enough in the

building to escape by a combination of self-evacuation and use of elevators. The aircraft destroyed the operation of the elevators and the use of two of the three stairways. Eighteen

people from above the impact zone found a passage through the damaged third stairway

(Stairwell A) and escaped. The other 619 people in or above the impact zone perished.

Eleven people who were below the impact floors did not survive. As in WTC 1 , shortly

before collapse, the flow of people from the building had slowed considerably, indicating that the stairwell capacity was adequate that morning. It is presumed that the 1 1 people did not escape for the same reasons as the victims in WTC I

.

176 NISTNCSTAR 1, WTC Investigation
Principal Findings

• About 6 percent of the survivors described themselves as mobihty impaired, with recent

injury and chronic illness being the most common causes; few, however, required a wheelchair. Among the 118 decedents below the aircraft impact floors, investigators

identified seven who were mobility impaired, but were unable to determine the mobility

capability of the remaining 111.

• A principal factor limiting the loss of life was that the buildings were one-third to one-half

occupied at the time of the attacks. NIST estimated that if the towers had been fully occupied

with 20.000 occupants each, it would have taken just over 3 hours to evacuate the buildings

using the stairs and about 14,000 people might have perished because the stairwell capacity

would not have been sufficient to evacuate that many people in the available time. Egress

capacity required by current building codes is determined by single floor calculations that are independent of building height and does not consider the time for fiill building evacuation.

• Due to the presence of assembly use spaces at the top of each tower that were designed to accommodate over 1 ,000 occupants per floor for the Windows on the World restaurant complex and the Top of the World observation deck, the New York City (NYC) Building

Code would have required a minimum of four independent means of egress (stairs), one more

than the three that were available in the buildings. Given the low occupancy level on

September 1 1, 2001, NIST found that the issue of egress capacity from these places of

assembly, or from elsewhere in the buildings, was not a significant factor on that day. It is conceivable that such a fourth stairwell, depending on its location and the effects of aircraft impact on its functional integrity, could have remained passable, allowing evacuation by an unknown number of additional occupants from above the floors of impact. Moreover, if the buildings had been filled to their capacity with 20,000 occupants, the required fourth stairway

would likely have mitigated the insufficient egress capacity for conducting a ftill building

evacuation within the available time.

• Evacuation was assisted by participation in fire drills within the previous year by two-thirds

of survivors and perhaps hindered by a Local Law that prevented employers from requiring

occupants to practice using the stairways. The stairways were not easily navigated in some

locations due to their design, which included "transfer hallways" where evacuees had to traverse from one stairway to another location where the stairs continued. Additionally,

many occupants were unprepared for the physical challenge of full building evacuation.

• The ftanctional integrity and survivability of the stairwells was affected by the separation of

the stairwells and the structural integrity of stairwell enclosures. In the impact region of

WTC 1 , the stairwell separation was the smallest over the building height—clustered well

within the building core—and all stairwells were destroyed by the aircraft impact. By

contrast, the separation of stairwells in the impact region of WTC 2 was the largest over the building height—located along different boundaries of the building core—and one of three

stairwells remained passable after the aircraft impact. The shaft enclosures were fire rated

but were not required to have structural integrity under typical accidental loads—there were numerous reports of stairwells obstructed by fallen debris from damaged enclosures.

• The active fire safety systems (sprinklers, smoke purge, fire alarms, and emergency occupant

communications) were designed to meet or exceed current practice. However, with the

NISTNCSTAR 1. WTC Investigation 177
Chapter 8

exception of the evacuation announcements, they played no role in the safety of life on September 1 1 because the water supplies to the sprinklers were damaged by the aircraft impact. The smoke purge systems, operated under the direction of the fire department after the fires, were not turned on, but they also would have been ineffective due to aircraft damage. The violence of the aircraft impact served as its own alarm. In WTC 2, contradictory public address announcements contributed to occupant confusion and some

delay in occupants beginning to evacuate.

• For the approximately 1,000 emergency responders on the scene, this was the largest disaster

they had ever seen. Despite attempts by the responding agencies to work together and

perform their own tasks, the extent of the incident was well beyond their capabilities.

Communications were erratic due to the high number of calls and the inadequate performance

of some of the gear. Even so, there was no way to digest, test for accuracy, and disseminate

the vast amount of infomiation being received. In the opinion of some first responders,

communications and infomiation sharing cost the lives of some emergency responders. Their

jobs were complicated by the loss of command centers in WTC 7 and then in the towers after WTC 2 collapsed. With nearly all elevator service disrupted and progress up the stairs taking

about 2 min per floor, it would have taken hours for the responders to reach their destinations,

assist survivors, and escape before the towers collapsed.

Objective 3: Determine what procedures and practices were used in the design, construction,

operation, and maintenance of WTC 1 and WTC 2.

• Because of The Port Authority of New York and New Jersey's (Port Authority's)

establishment under a clause of the United States Constitution, its buildings were not subject

to any state or local building regulations. The buildings were unlike any others previously

built, both in their height and in their innovative structural features. Nevertheless, the actual

design and approval process produced two buildings that generally were consistent with

nearly all of the provisions of the NYC Building Code and other building codes of that time

that were reviewed by NIST. The loads for which the buildings were designed exceeded the New York City code requirements. The quality of the structural steels was consistent with

the building specifications. The departures from the building codes and standards identified

by NIST did not have a significant effect on the outcome of September 1 1

.

• For the floor systems, the fire rating and insulation thickness used on the floor trusses were of

concern from the time of initial construction. NIST found no technical basis or test data on which the thennal protection of the steel was based. However, on September 1 1, 2001, the

minimum specified thickness of the insulation was adequate to delay heating of the trusses and the amount of insulation dislodged by the aircraft impact was sufficient to enable the

critical heating of the structural steel.

• Based on four standard fire resistance tests that were conducted under a range of insulation

and test conditions, NIST found the fire rating of the floor system to vary between 3/4 hour

and 2 hours; in all cases, the floors continued to support the fiill design load without collapse

for over 2 hours.

178 NISTNCSTAR 1, WTC Investigation
Principal Findings

• The wind loads used for the WTC towers, which governed the design of the external

columns, significantly exceeded the requirements of the NYC Building Code and other

building codes of the day that were reviewed by NIST. Two sets of wind load estimates for the towers obtained by independent commercial consultants in 2002, however, differed by as much as 40 percent. These estimates were based on wind tunnel tests conducted as part of

insurance litigation unrelated to the Investigation.

The tragic consequences of the September 11, 2001, attacks were largely a result of the fact that terrorists flew large jet-fuel laden commercial airliners into the WTC towers. Buildings for use by the general

population are not designed to withstand attacks of such severity; building regulations do not require

building designs to consider aircraft impact. In our cities, there has been no experience with a disaster of

such magnitude, nor has there been any in which the total collapse of a high-rise building occurred so

rapidly and with little warning.

While there were unique aspects to the design of the WTC towers and the terrorist attacks of

September 11, 2001, there are several possibilities to improve the safety of tall buildings, occupants, and

emergency responders that result from this investigation of commonly used procedures and practices that were used in the design, construction, operation, and maintenance of the WTC towers. There also are possible improvements for selected buildings that owners may determine to be at higher risk due to their iconic status, critical function, or design. The recommendations in Chapter 9 suggest a variety of ways in which to achieve these safety improvements.

8.3 FINDINGS ON THE MECHANISMS OF BUILDING COLLAPSE

8.3.1 Summary of Probable Collapse Sequences

WTC 1 was struck by a hijacked aircraft at 8:46:30 a.m. and began to collapse at 10:28:22 a.m. WTC 2 was struck by a hijacked aircraft at 9:02:59 a.m. and began to collapse at 9:58:59 a.m. The specific

factors in the collapse sequences relevant to both towers (the sequences vary in detail for WTC 1 and

WTC 2) are:

• Each aircraft severed exterior columns, damaged interior core columns and knocked off

insulation from steel as the planes penetrated the buildings. The weight carried by the severed

columns was distributed to other columns.

• Subsequently, fires began to grow and spread. They were initiated by the aircraft's jet ftiel, but were fed for the most part by the building contents and the air supply resulting from

breached walls and fire-induced window breakage.

• These fires, in combination with the dislodged insulation, were responsible for a chain of

events in which the building core weakened and began losing its ability to carry loads.

• The floors weakened and sagged from the fires, pulling inward on the exterior columns.

• Floor sagging and exposure to high temperatures caused the exterior columns to bow inward

and buckle—a process that spread across the faces of the buildings.

NISTNCSTAR 1, WTC Investigation 179
Chapter 8

• Collapse then ensued.

Seven major factors led to the collapse of WTC 1 and WTC 2:

• Structural damage from the aircraft impact;

• Large amount ofjet fuel sprayed into the building interior, that ignited widespread fires over

several floors;

• Dislodging of SFRM from structural members due to the aircraft impact, that enabled rapid

heating of the unprotected structural steel;

• Open plan of the impact floors and the breaking of the partition walls by the impact debris

that resulted in increased ventilation;

• Weakened core columns that increased the load on the perimeter walls;

• Sagging of the floors, that led to pull-in forces on the perimeter columns; and

• Bowed perimeter columns that had a reduced capacity to carry loads.

8.3.2 Structural Steels

• Fourteen different strengths of steel were specified in the structural engineering plans, but

only 1 2 steels of different strength were actually used in construction due to an upgrade of

two steels. Ten different steel companies fabricated stnictural elements for the towers, using

steel supplied from at least eight different suppliers. Four fabricators supplied the major

structural elements of the 9"' to the 107"^ floors. Material substitutions of higher strength

steels were not uncommon in the perimeter columns and floor trusses.

• About 87 percent of the tested steel specimens (columns, trusses and bolts) met or exceeded

the required yield strengths specified in design documents. About 13 percent had NISTmeasured strengths that were slightly lower than the design values, but this may have arisen

from mechanical damage during the collapse, the natural variability of structural steel, and

slight differences between the NIST and original mill test report testing protocols.

• The safety of the WTC towers on September 1 1, 2001, was most likely not affected by the

fraction of steel that, according to NIST testing, was modestly below the required minimum

yield strength. The typical factors of safety in allowable stress design were capable of

accommodating the measured property variations below the minimum.

• The pre-collapse photographic analysis showed that 16 recovered exterior panels were

exposed to fire prior to collapse of WTC 1 . None of the nine recovered panels from within

the fire floors of WTC 2 were observed to have been directly exposed to fire.

• None of the recovered steel samples showed evidence of exposure to temperatures above

600 °C for as long as 1 5 min. This was based on NIST annealing studies that established the

180 NISTNCSTAR 1. WTC Investigation
Principal Findings

set of time and temperature conditions necessary to alter the steel microstructure. These

results provide some confirmation of the thermal modeling of the structures, since none of the samples were from zones where such heating was predicted.

• Only three of the recovered samples of exterior panels reached temperatures in excess of

250 °C during the fires or after the collapse. This was based on a method developed by NIST

to characterize maximum temperatures experienced by steel members through observations

of paint cracking.

• Perimeter columns exposed to fire had a great tendency for local buckling of the inner web; a

similar correlation did not exist for weld failure.

• Observations of the recovered steel provided significant guidance for modeling the damage

from the aircraft impact with the towers.

• For the perimeter columns struck by the aircraft, fractures of the plates in areas away from a welded joint exhibited ductile behavior (necking and thinning away from the fracture) under

very high strain rates. Conversely, fractures occurring next to a welded joint exhibited little or no ductile characteristics.

• There was no evidence to indicate that the type ofjoining method, materials, or welding

procedures were improper. The welds appeared to perform as intended.

• The failure mode of spandrel connections on perimeter panels differed above and below the impact zone. Spandrel connections on exterior panels at or above the impact zone were more

likely to fail by bolt tear out. For those exterior panels below the impact zone, there was a higher propensity for the spandrels to be ripped off from the panels. This may be due to shear

failures as the weight of the building came down on these lower panels. There was no

difference in failure mode for the spandrel connections whether the exterior panels were

exposed to fire or not.

• With the exception of the mechanical floors, the perimeter panel column splices failed by

fracture of the bolts. At mechanical floors, where splices were welded in addition to being

bolted, the majority of the splices did not fail.

• Core columns failed at both splice connection and by fracture of the columns themselves.

• The damage to truss seats on perimeter panels differed above and below the impact zone in both towers. The majority of recovered perimeter panel floor truss connectors (perimeter

seats) below the impact floors were either missing or bent downward. Above this level, the

failure modes were more randomly distributed.

• In the floor trusses, a large majority of the electric resistance welds at the web-to-chord

connections failed. The floor truss and the perimeter panel floor truss connectors typically

failed at welds and bolts.

NISTNCSTAR 1, WTC Investigation 181
The NIST-measured properties of the steels (strain rate, impact toughness, high-temperature

yield and tensile strengths) were similar to literature values for other construction steels of the

WTC era.

The creep behavior of the steels could be modeled by scaling WTC-era literature data using room temperature tensile strength ratios.

Aircraft Impact Damage Analysis

Both towers withstood the significant structural damage to the exterior walls, core columns,

and floor systems due to the aircraft impact. WTC 2 was the more severely damaged

building and the first to collapse. WTC 2 displayed significant reserve capacity, as evidenced

by a post-impact rooftop sway that was more than one-third of that under the hurricane force

winds for which the building was designed. The oscillation period of this swaying was nearly

equal to that calculated for the undamaged structure. (Such an analysis was not possible for the less severely damaged WTC 1 due to the absence of equivalent video footage for the

analysis.)

American Airlines Flight 1 1 impacted the north wall of WTC 1 at a speed of 443 mph ±

30 mph, banked 25 degrees ± 2 degrees to the left (left wing downward) and with the nose

tilted slightly downward. United Airlines Flight 175 impacted the south wall of WTC 2 at a speed of 542 mph ± 24 mph, banked 38 degrees ± 2 degrees to the left (left wing downward)

and with the nose pointed slightly downward and to the right.

The aircraft impact on WTC 1 caused extensive damage to the north wall of the tower,

principally in the regions impacted by the fuselage, engine, and fuel-filled wing sections.

Photographic evidence showed that 34 perimeter columns were completely severed, while

four columns were heavily damaged, and two columns were moderately damaged.

The impact simulations of WTC 1 indicated that three to six core columns were severed, and

three to four columns were heavily damaged. The floor trusses, core beams, and floor slabs experienced significant impact-induced damage on floors 94 through 96, particularly in the

path of the fuselage. The wing structures were fragmented at the exterior wall, and aircraft fuel was dispersed on multiple floors. Aircraft debris substantially damaged the nonstructural

interior partitions and the workstations and dislodged insulation in its path. The bulk of the

fuel and aircraft debris was deposited in floors 93 through 97 with the largest concentration on floor 94.

The aircraft impact on WTC 2 caused extensive damage to the south wall of the tower and to the regions impacted by the fuselage, engine, and fuel-filled wing sections. Photographic

evidence showed that 29 perimeter columns were completely severed, one was heavily

damaged, and three were moderately damaged. Four perimeter columns on the north wall

also were severed.

The impact simulations of WTC 2 indicated that five to ten core columns were severed and

up to four columns were heavily damaged. The rupture of some column splices on floors 77,

80, and 83 contributed significantly to the failure of the core columns. The floor trusses, core

NISTNCSTAR 1, WTC Investigation
Principal Findings

beams, and floor slabs experienced significant impact-induced damage on floors 79 to 8 1

,

particularly in the path of the fuselage. The analyses indicated that the wing structures were

fragmented due to the interaction with the exterior wall and, as a result, aircraft fuel was

dispersed on multiple floors. The aircraft debris substantially damaged the building's contents and also dislodged insulation in its path. The bulk of the fuel was concentrated on

floors 79, 81, and 82, while the bulk of the aircraft debris was deposited in floors 78 through

80, with the largest concentration on floor 80.

• Other effects of the aircraft impacts included (a) severing of the sprinkler and fire hose water

supply systems, negating any possible fire suppression efforts; (b) dispersing ofjet fuel and

ignition of building contents over large areas; (c) increasing the air supply into the damaged

buildings that permitted very large fires; and (d) damaging ceilings, enabling unabated heat

transport to the floor structure above and over the floor-to-ceiling partition walls to the next compartment. These effects were consistent with photographic evidence and with the accounts of building occupants and emergency responders.

• The simulations fairly closely matched the exterior wall damage patterns from each of the

aircraft impacts and correctly predicted the collapse of five of the six stairwell walls and the

lesser damage to the sixth, the trajectories of the engine and wheels that penetrated the buildings, and the accumulation of furnishings and debris in the northeast comer of the 80"^ andSr' floors ofWTC2.

8.3.4 Reconstruction of the Fires

• In each tower, the fires were initiated simultaneously on multiple floors by ignition of some

of the jet fuel from the aircraft. The initial jet fuel fires themselves lasted at most a few

minutes.

• The principal combustibles on the fire floors were workstations. The total combustible fiiel load on the WTC floors was about 4 lb/ft". Higher combusted fiael loadings resulted in slower fire spread rates that did not match the patterns observed in the photographic evidence.

Under these higher combusted fuel loadings, the fires likely would not have reached the south

side of WTC 1 in the time needed to cause inward bowing and collapse initiation.

• The aircrafts added significant combustible material to their paths (and the paths of their breakup fragments) through the buildings.

• It is possible to reconstruct a complex fire in a large building, even if the building is no longer

standing. However, this requires extraordinary information to replace what might have been

gleaned from an inspection of the post-fire premises. In the case of the WTC tower, this information included floor plans of the fire zones, burning behavior of the combustibles,

simulations of damage to the building interior, and frequent photographic observations of the

fire progress from the building exterior.

• The fires in WTC 1 were generally ventilation limited, i.e., they burned and spread only as

fast as windows broke. Where the combustibles were not significantly relocated by the

aircraft debris, they tended to bum out in about 20 min. This was consistent with the results

NISTNCSTAR 1, WTC Investigation 183
of workstation fire tests conducted by NIST, in which the fuel load was 4 lb/ft". Although

there were multiple fires on some of the impact floors, the general trend was for the fires to move toward the south side of the tenant spaces.

The fires in WTC 2 had sufficient air to bum at a rate detemiined by the properties of the

combustibles. This was in large part due to the extensive breakage of windows in the fire zone by the aircraft impact. In contrast with WTC 1, there was little spread in WTC 2. The

early fires persisted on the east side of the tower and particularly in the northeast comer of the

80''^ and ST' floors, where the aircraft debris had pushed a lot of fractured combustibles

The Fire Dynamics Simulator can predict the room temperatures and heat release rate values

for complex fires to within 20 percent, when the building geometry, fire ventilation, and

combustibles are properly described.

The Fire Stmcture Interface, developed for this Investigation, mapped the fire-generated

temperature and thennal radiation fields onto and through layered stmctural materials to within the accuracy of the fire-generated fields and the thermophysical data for the stmctural

components.

Conventional office workstations reached a peak buming rate in about 10 min and continued

buming for a total of about a half hour. Partial covering of surfaces with inert material

reduced the peak buming rate proportional to the fraction covered, but did not affect the total amount of heat release during the entire buming.

Jet fuel sprayed onto the surfaces of typical office workstations burned away within a few

minutes. The jet fuel accelerated the buming of the workstation, but did not significantly

affect the overall heat released.

In the simulations, none of the columns with intact insulation reached temperatures over 300 °C. Only a few isolated tmss members with intact insulation were heated to temperatures over 400 °C in the WTC 1 simulations and to temperatures over 500 °C in the WTC 2

simulations. In WTC 1, if the fires had been allowed to continue past the time of building

collapse, complete bumout would likely have occurred within a short time since the fires had

already traversed around the entire floor, and most of the combustibles would already have

been consumed. In WTC 2, if the fire simulation were extended for 2 hours past the time of

building collapse with all windows broken, the temperatures in the tmss steel on the west side

of the building (where the insulation was undamaged) would likely have increased for about

40 min before falling off rapidly as the combustibles were consumed. Temperatures of

700 °C to 760 °C were reached over approximately 15 percent of the west floor area for less than 10 min. Approximately 60 percent of the floor steel had temperatures between 600 °C

and 700 °C for about 15 min. Approximately 70 percent of the floor steel had temperatures

that exceeded 500 °C for about 45 min. At these temperatures, the floors would be expected

to sag and then recover a portion of the sag as the steel began to cool. The temperatures of

the insulated exterior and core columns would not have increased to the point where they

would have experienced significant loss of strength or stiffness.

NISTNCSTAR 1. WTC Investigation
Principal Findings

8.3.5 Structural Response and Collapse Analysis

• The core columns were weakened significantly by the aircraft impact damage and thermal

effects. Thermal effects dominated the weakening of WTC 1 . As the fires moved from the north to the south side of the core, the core was weakened over time by significant creep

strains on the south side of the core. Aircraft impact damage dominated the weakening of

WTC 2. With the impact damage, the core subsystem leaned to the southeast and was

supported by the south and east perimeter walls via the hat truss and floors. As the core weakened, it redistributed loads to the perimeter walls through the hat truss and floors. Additional axial loads redistributed to the exterior columns from the core were not significant

(only about 20 percent to 25 percent on average) as the exterior columns were loaded to approximately 20 percent of their capacity before the aircraft impact.

• The primary role of the floors in the collapse of the towers was to provide inward pull forces

that induced inward bowing of perimeter columns (south face of WTC 1 ; east face of

WTC 2). Sagging floors continued to support floor loads as they pulled inward on the perimeter columns. There would have been no inward pull forces if the floors connections

had failed and disconnected.

• Column buckling over an extended region of the perimeter face ultimately triggered the global system collapse as the loads could not be redistributed through the hat tmss to the already weakened building core. As the exterior wall buckled (south face for WTC 1 and east face for WTC 2), the column instability propagated to adjacent faces and caused the initiation of the building collapse. Perimeter wall buckling was induced by a combination of thennal

weakening of the columns, inward pull forces from sagging floors, and to a much lesser degree, additional axial loads redistributed from the core.

• The WTC towers would likely not have collapsed under the combined effects of aircraft impact damage and the extensive, multi-floor fires that were encountered on September 11,

2001, if the thermal insulation had not been widely dislodged or had been only minimally

dislodged by aircraft impact.

• In the absence of structural and insulation damage, a conventional fire substantially similar to or less intense than the fires encountered on September 11, 2001, likely would not have led to the collapse of a WTC tower.

• The insulation damage estimates were conservative as they ignored possibly damaged and

dislodged insulation in a much larger region that was not in the direct path of the debris but was subject to strong vibrations during and after the aircraft impact. A robust criterion to generate a coherent pattern of vibration-induced dislodging could not be established to estimate the larger region of damaged insulation.

• For WTC 1 , partitions were damaged and insulation was dislodged by direct debris impact over five floors (floors 94, 95, 96, 97, and 98) and included most of the north floor areas in

front of the core, the core, and central regions of the south floor areas, and on some floors,

extended to the south wall.

NISTNCSTAR 1, WTC Investigation 185
Chapter 8

• For WTC 2, partitions were damaged and insulation was dislodged by direct debris impact

over six floors (floors 78, 79, 80, 81, 82, and 83) and included the south floor area in front of

the core, the central and east regions of the core, and most of the east floor area, and extended

to the north wall.

• The adhesive strength of BLAZE-SHIELD D to steel coated with primer paint was found to be one-third to one-half of the adhesive strength to steel that had not been coated with primer

paint. The SFRM products used in the WTC towers were applied to steel components with

primer paint.

• The average thickness of the original thermal insulation on the floor trusses was estimated to be 0.75 in. with a standard deviation of 0.3 in. The average thickness of the upgraded thermal

insulation was estimated to be 2.5 in. with a standard deviation of 0.6 in. Based on finite- element simulations, the thermal analyses for determining temperature histories of structural components used a thermally equivalent thickness of 0.6 in. and 2.2 in. for the original and

upgraded insulation, respectively. For thermal analyses of the perimeter columns, spandrel

beams, core beams, and core columns, the insulation on these elements was set to the

specified thickness, due to a lack of field measurements.

• Based on four Standard Fire Tests conducted for various length scales, insulation thickness,

and end restraints, the floor assemblies were shown to be capable of sagging without

collapsing and supported their fiill design load under standard fire conditions for 2 hours or more without failure.

• For assemblies with a in. SFRM thickness, the 17 ft assembly's fire rating was 2 hours; the

35 ft assembly's rating was 1 Vi hours. This result raised the question of whether or not a fire rating of a 1 7 ft floor assembly is scalable to the longer spans in the WTC towers.

• The specimen with Vi in. SFRM thickness and a 17 ft span would not have met the 2 hour

requirement of the NYC Building Code.

• There is far greater knowledge of how fires influence structures in 2005 than there was in the 1960s. The analysis tools available to calculate the response of structures to fires are also far better now than they were when the WTC towers were designed and built.

• Active fire protection systems for many buildings are designed to the same perfonnance

specifications, regardless of height, size, and threat profile.

• The active fire protection systems (alarms, suppression, and smoke purging) in the WTC

towers were designed to meet or exceed then-current practice. However, the successful

operation of these systems depended upon the fire threat being consistent with what had been

anticipated based upon previous experience and best engineering practices of the day.

1 86 NIST NCSTAR 1, WTC Investigation

8.4 FINDINGS ON FACTORS AFFECTING LIFE SAFETY

8.4.1 Active Fire Protection
Principal Findings

• The fire alarm systems in the towers provided for automatic fire detection, but required

manual activation of notification devices. On September 1 1, 2001, the impact of the aircraft

itself alerted occupants in the WTC buildings to the unfolding danger when the first aircraft

hit.

• Soon after the first aircraft impact, an overwhelming number of alanns were displayed at the Fire Command Station in WTC 1 . The alarm systems were only capable of detemiining and

displaying (a) areas that had at some time reached alarm point conditions and (b) areas that had not. The quality and reliability of infonnation available to emergency responders at the Fire Command Station was not sufficient to understand the fire conditions.

• Although the fire alarm systems used multiple communication path risers, the systems

experienced performance degradation, especially in WTC 1 where all fire alann notification

and communication functions appear to have been lost above the floors of impact.

• There was no means at the Fire Command Stations to determine whether or not announcements reached and could be heard on the intended floors.

• Alarm systems store information that is valuable for understanding the fire and smoke

development in a building, but no information from the fire alarm systems was located, and

there was no indication that anyone looked for it during the cleanup of the WTC site. Survivability of alarm systems data on computer hard drives, memory modules, or printouts

in building fires and collapse enviroimients is not addressed in present installation standards.

• Transmission of critical data outside the building to a monitoring station would provide means to preserve event data.

• Except for specific areas that were exempted from required sprinkler coverage, sprinkler

systems were installed throughout the towers. As designed, the water supplies (storage tanks

and pumped city water), automatic sprinklers, and standpipe/pre-connected hose systems met

or exceeded the applicable installation requirements in the NYC Building Code. There were

other design features that were considered inconsistent with engineering best practices, but no

evidence was found to indicate that these features affected the events that occurred on

September 1 1

.

• All the fires that occurred in sprinklered spaces in the towers prior to September 11, 2001, were controlled with three or fewer sprinklers, in some cases supplemented by manual fire fighting.

• On the floors where the major fires occurred on September 11, 2001, the sprinkler system

played no part since their water supply was damaged by the aircraft impact. The typical

sprinkler system was installed with one connection to the sprinkler riser, providing a single

point of failure of the water supply to the floor level sprinklers.

• The sprinkler systems could have provided fire control at coverage areas up to two or three times the specified design area of 1,500 ft'. However, 4,500 ft" constituted less than

15 percent of the area of a single floor in these buildings, and estimates of the extent of the

NISTNCSTAR 1, WTC Investigation 187
Chapter 8

initial fires in WTC 1 and WTC 2 in 2001 were considerably greater than three times the specified design areas.

There were redundant and sufficient supplies of water for the standpipe and sprinkler systems

for control of nonnally expected fires on the floors where the September 1 1 fires occurred.

Activating the secondary water supplies required manual operation of electric fire pumps by a

sizable number of people at various locations.

No information was available at the Fire Command Desk about the water supply in areas that were burning, leading to a Port Authority employee being sent up to assess the status.

There was no infonnation available regarding the perfonnance of the non-aqueous fire suppression systems on September 1 1, 2001. The manually operated smoke purge systems were designed to be activated by the fire department after a fire was suppressed, and,

therefore, were not initiated on September 11. It is unlikely the systems would have

functioned as designed, due to loss of electrical power and damage to the HVAC shafts and

other structural elements in the impact zone that were integral parts of the systems.

Analysis indicated that the aircraft impact rupture of large return air shafts and related ductwork created a major path for vertical smoke spread in the towers.

8.4.2 Evacuation

Approximately 87 percent of WTC occupants, and over 99 percent of those below the floors of impact, were able to evacuate successfully.

At the time of the aircraft impacts, the towers were only about one-third to one-half occupied.

Had they been at the full capacity of 20,000 workers and visitors per tower, computer egress modeling indicated that a full evacuation would have required just over 3 hours. Under those

circumstances, about 14,000 occupants might have perished in the building collapses.

There were 8,900 ± 750 people in WTC 1 at 8:46 a.m. on September 1 1, 2001. Of those,

7,470 (or 84 percent) survived, while 1,462 to 1,533 occupants died.'^ At least 107 occupants were killed below the aircraft impact zone. No one who was above the floor in WTC 1 after the aircraft impact survived. This was due to the fact that the stairwells and elevators were destroyed and helicopter rescue was impossible.

There were 8,540 ± 920 people in WTC 2 at 8:46 a.m. on September 1 1, 2001. Of those,

7,940 (or 93 percent) survived, while 630 to 701 occupants were killed.'"^ Eleven of those

killed were employed on floors located below the aircraft impact zone. Approximately 75

percent of the occupants above the 78"" floor at 8:46 a.m. had successfully descended below

the 78"' floor prior to the aircraft impact at 9:03 a.m. The use of elevators and self-initiated evacuation during this period saved roughly 3,000 lives.

As shown in Table 4-1, there were a total of 71 decedents whose initial locations in the towers were not certain: 30 below the impact zone in either WTC 1 or WTC 2, 24 at an unknown location in WTC 1 or WTC 2, and 17 people for whom no location information was available.

188 NISTNCSTAR 1, WTC Investigation
Principal Findings

• The evacuation from WTC 2 occurred in spite of conflicting announcements, first urging

people to return to their offices around 9:00 a.m., and then infonning them around 9:02 a.m.

that they may initiate an evacuation if conditions warranted. A subsequent announcement at 9:20 a.m., after the second aircraft strike, informed occupants that they could use the

Concourse if they wished to leave the building. An announcement at 9:37 a.m. instructed

occupants to go down the stairs.

• Stairwell A in WTC 2 remained passable for at least some period of time after the aircraft impact because (1) only the end of the left wing, empty ofjet fuel, was in line with the

stairwell; (2) Stairwell A was behind the structural/architectural core in the area of impact;

and (3) the aircraft debris had to travel through the longer dimension of the core and thus was

slowed by a greater number of columns, shafts, walls, and mechanical equipment, and (4)

Stairwell A was widely separated from Stairwells B and C.

• Eighteen people successfully used the debris-cluttered Stairwell A in WTC 2 to leave the building after being on or above the 78"^ floor when United Airlines Flight 175 hit the building. It is possible that additional occupants from above the impact floors were making

their way down the stairwell some minutes before building collapse.

• Two-thirds of the WTC 1 occupants and half of the WTC 2 occupants had started working at the WTC in the previous 4 years.

• Two-thirds of the WTC 1 and WTC 2 occupants participated in at least one fire drill in the twelve months prior to September 1 1, 2001 . Nearly all (93 percent) of these occupants were

instructed about the location of the nearest stairwell. However, only half of the survivors had

previously used a stairwell, in part since NYC Local Law 5 prohibited requiring occupants to practice stairwell evacuation.

• The NIST Investigation found no evidence that the occupants of WTC 1 heard public address

system announcements, although the fire command station was attempting to make such

announcements.

• The delays of about 5 min in starting evacuation were largely spent trying to obtain additional

information, trying to make sense of the situation, and generally preparing to evacuate.

• People who started their evacuation on higher floors took longer to start leaving and

substantially increased their odds of encountering smoke, damage or fire. These encounters,

along with interruption for any reason, had a significant effect on increasing the amount of

time that people spent to traverse their evacuation stairwell.

• The WTC occupants were inadequately prepared to encounter horizontal transfers during the evacuation process and were occasionally delayed by the conftision as to whether a hallway

led to a stairwell and conftision about whether the transfer hallway doors would open or be

locked.

• The WTC occupants were often unprepared for the physical challenge of ftiU building

evacuation. Numerous occupants required one or more rest periods during stairwell descent.

NISTNCSTAR 1, WTC Investigation 189
Chapter 8

• In WTC 1, the average surviving occupant spent approximately 48 seconds per floor in the

stairwell, about twice that observed in non-emergency evacuation drills. The 48 seconds does

not include the time prior to entering the stairwell, which was often substantial. Some

occupants delayed or interrupted their evacuation, either by choice or instruction.

• Downward traveling evacuees reported slowing of their travel due to ascending emergency

responders, but this counterflow was not a major factor in determining the length of their evacuation time. Emergency responders reported trouble ascending the stairs because of the volume of evacuees in the stairwells.

• During the last 20 min before each building collapsed, the evacuation rate in each building

had slowed to about one-fifth the immediately prior evacuation rate. This suggests that for those seeking and able to reach and use the undamaged exits and stairways, the egress capacity was adequate to accommodate survivors.

• Many opportunities to communicate important information in a timely manner were missed,

such as the general location of the impact region or whether to evacuate or not. As a result,

building occupants, 9-1-1 operators, fire department dispatch, WTC building officials, and

Port Authority personnel lacked necessary information about the situation.

• Faced with an uncertain situation, occupants of both buildings received conflicting feedback / advice from a variety of sources (including 9-1-1 operators, FDNY, family and friends, and

The Port Authority) regarding whether to evacuate, whether to break windows, and the nature of their situation. It is likely that, in many instances, the people giving advice had as little accurate information as those seeking it.

• The decision to establish the primary evacuation route underground through the Concourse

and then up to street level near WTC 5 prevented a significant number of injuries and/or

deaths.

• Approximately 1 ,000 surviving occupants had a limitation that impacted their ability to evacuate, including recent surgery or injury, obesity, heart condition, asthma, advanced age, and pregnancy. The most frequently reported disabilities were recent injuries and chronic

illnesses. The fraction of occupants requiring use of a wheelchair was very small.

• Mobility-impaired occupants were not universally accounted for by existing evacuation

procedures, as some were left by colleagues (later rescued by strangers), some in WTC 1 were temporarily removed from the stairwells in order to allow more able occupants to evacuate the building, and others chose not to identify their mobility challenge to any

colleagues.

• Most mobility-impaired individuals were able to evacuate successfully, often with assistance

from co-workers or emergency responders, and it is not clear how many were among the

1 18 from below the impact floors who did not survive. It does not appear that mobilityimpaired individuals were significantly over-represented amongst the decedents. As many as 40 to 60 mobility-impaired occupants and their companions were found on the 1 2*'' floor of

190 NISTNCSTAR 1, WTC Investigation
Principal Findings

WTC 1 by emergency responders. About 20 of these were making their way down the stairs shortly before the building collapsed. It is not known how many from this group survived.

• Due to the presence of assembly use spaces at the top of each tower that were designed to accommodate over 1 .000 occupants per floor for the Windows on the World restaurant complex and the Top of the World observation deck, the NYC Building Code would have

required a minimum of four independent means of egress (stairs), one more than the three

that were available in the buildings. Given the low occupancy level on September 11, 2001,

NIST found that the issue of egress capacity from these places of assembly, or from

elsewhere in the buildings, was not a significant factor on that day. It is conceivable that such

a fourth stairwell, depending on its location and the effects of aircraft impact on its frinctional

integrity, could have remained passable, allowing evacuation by an unknown number of

additional occupants form above the floors of impact. Moreover, if the buildings had been

filled to their capacity with 20,000 occupants, the required fourth stairway would likely have

mitigated the insufficient egress capacity for conducting a full building evacuation within the available time.

8.4.3 Emergency Response

• New York City's emergency responders had never experienced an operation of the size presented by the attack on the WTC. They typically followed their department policies and

procedures for the operations they were required to carry out. Under these procedures,

almost all emergency responder departments established their command posts within the potential collapse zone of the buildings.

• In general, all departments attempted to work together to save as many lives as possible. This was done with no fonnal structure of unified command between departments below the Commissioner level of operations.

• Unified operations were hindered by the FDNY and NYPD command posts being separated.

Department Chiefs could not directly communicate with each other using their handie-talkies

and did not formulate unified orders and directions for their departments. Neither FDNY nor NYPD had liaison officers working with the other department's command posts until after WTC 1 collapsed.

• The first emergency responders were colleagues and regular building occupants. Acts of

individual heroism saved many people whom traditional emergency responders would have

been unable to reach in time.

• The initial fire department assessment of the situation was correct regarding the general

magnitude of damage, the status of the water supply, and the further limitations imposed on

firefighting by the height of the impact. FDNY command personnel learned from 9-1-1 dispatch operators that smoke, fire, and structural damage in the buildings prevented many

building occupants from evacuating floors above the impact zones. The decision was quickly

made that fire department efforts should be directed toward evacuation and rescue of building

occupants and should not focus on firefighting.

NISTNCSTAR 1, WTC Investigation 191


Only one elevator in each building was of use to the responders. To gain access to the injured

and trapped occupants, firefighters had to climb the stairs, carrying the equipment with them.

NIST estimated that emergency responder climbing rates varied between approximately

1.4 min per floor for personnel not carrying extra equipment to approximately 2.0 min per

floor for personnel wearing protective clothing and carrying extra equipment.

Intense smoke and heat conditions on the top of the two WTC buildings prevented the NYPD

helicopters from conducting roof evacuations.

NYPD aviation unit personnel reported critical information about degrading building

conditions before WTC 2 collapsed and critical information about the impending collapse of

WTC 1 several minutes prior to its collapse. No evidence has been found to suggest that the information was further communicated to all emergency responders at the scene.

There were roughly 1,000 emergency responders on the site. The Command Board approach

to managing operations became overwhelmed with this large number of personnel and units

reporting in for operations. The responding units generally followed good practices as related

to accountability of staff. However, there were cases where individuals and ambulances did

not report to the Command Posts. There was no way to locate or track units and individuals once they had departed to accomplish their tasks.

Generally, the equipment used by the emergency responders was adequate for the operations

being carried out. Flashlights were valuable, since the stairwells were generally dark and

many areas were opaque with smoke and dust, especially in WTC 1 after the collapse of

WTC 2. Self-contained breathing apparatus enabled responders to breathe when they were in the zones where the air was contaminated.

For PAPD and NYPD, radio equipment did not appear to be a major problem during the operations. The PAPD's new radio antenna system provided it with a reasonable quality of

radio communications until the collapse of WTC 2, at which time personnel were forced to switch to point-to-point communications. NYPD experienced successful operations with its radio equipment, mainly since only a few entered the WTC towers and the location of the mobilization point (a city block or more away from the towers) provided an unobstructed line of sight route for radio signals to enter and exit the building's windows.

The overall emergency response was hampered by the loss of the Office of Emergency

Management Command Center.

The FDNY Incident Command Desk was hampered by the lack of a fully functional Field

Communications unit, poor radio communications, and limited access to shared information

critical to operations.

The FDNY radio system was inadequate for locating and tracking the large number of

persormel at the site. The FDNY relied heavily on hand-held units and knew that even the new handie-talkie radios did not work well in high-rise buildings where the signals were

attenuated by the large amounts of metal and steel-reinforced concrete. Thus, the location of

NISTNCSTAR 1, WTC Investigation
Principal Findings

Command Posts inside the buildings made calls to them subject to attenuation. Nonetheless,

there were reports by emergency responders that their radios played a part in saving their

lives.

• Radio communications overload quickly became a problem. After the first aircraft strike, there was a factor-of-five increase in emergency responder radio communications. This

resulted in situations where the base station radio operators were unable to relay important

information. Approximately 1/3 to 1/2 of the emergency radio conmiunications were not complete messages or were not understandable.

• Communications within, fi-om, and to WTC 1 were problematic. The building emergency

communications system used to make the emergency announcements inside was inoperable

as a result of the aircraft impact. The warden and standpipe phone systems were also not

operating. The radio repeater in WTC 5, though found to be operational, was not effective in WTC 1. Eventually, only about half of the responders located in WTC 1 heard radio

messages calling for the immediate evacuation of the building. Emergency responders who

had the evacuation information told others.

• The WTC 5 repeater appeared to be effective in WTC 2. The Battalion Car Cross-band

Repeater, recently developed by the FDNY and taken to the lobby of WTC 2, was used as a backup.

• Information overload led to an inability to pool and analyze information in real time and to distribute it to the emergency responders and the WTC occupants in a timely fashion. As a

result, many emergency responders did not get the critical information they needed to maintain good situational awareness. Some occupants did not get information that potentially

could have saved their lives, such as notification that Stairwell A was possibly passable from

above the impact zone.

• A preponderance of evidence indicted that lack of timely information sharing and inadequate

communication capabilities likely contributed to the loss of emergency responder lives.

• The collapse of WTC 2 totally disrupted the ongoing Incident Command System Operations

being carried out by FDNY, NYPD, and PAPD.

• The private ambulances and Emergency Medical Service teams that responded to the WTC

had limitations to their effectiveness. They had no protective clothing. They did not have the same radios, so the other agencies could not communicate with them. Only paper records were kept of patients being treated by official and self-dispatched emergency medical units. These records were lost when the buildings collapsed.

• Communications between the emergency response agencies and the media were problematic.

Critical life safety and evacuation information from the WTC towers was not communicated

to the news media so that it could be broadcast to people trapped inside the WTC towers above the building fires. By bypassing the appropriate emergency response agency contact

points, some media firms interfered with the on-site operations.

NISTNCSTAR 1, WTC Investigation 193
Chapter 8

8.5 FINDINGS ON OPERATIONAL CODES, STANDARDS, AND PRACTICES

8.5.1 General

• Although not required to conform to NYC codes, The Port Authority adopted the provisions

of the proposed 1968 edition of the NYC Building Code, more than three years before it went

into effect. The proposed 1968 edition allowed Port Authority to take advantage of less restrictive provisions and of technological advances compared with the 1938 edition, which was in effect when design for the WTC towers began in 1962.

• The NYC Department of Buildings reviewed the WTC tower drawings in 1 968 and provided

comments to The Port Authority concerning the plans in relation to the 1938 NYC Building

Code. The architect-of-record submitted to The Port Authority responses to those comments,

noting how the plans conformed to the 1968 NYC Building Code

• In 1993, The Port Authority and the NYC Department of Buildings entered into a memorandum of understanding that restated The Port Authority's longstanding policy to ensure that its facilities in the City of New York meet and, where appropriate, exceed the

requirements of the NYC Building Code.

• The Port Authority was not required to yield, and appears not to have yielded, jurisdictional

authority for regulatory and enforcement oversight to the New York City Department of

Buildings. The Port Authority was created as an interstate entity, under a clause of the U.S.

Constitution permitting compacts between states, and is not bound by the authority of any

local or state jurisdiction.

• It was remarkable that the Investigation Team was able to obtain the large quantity of

documentation of the construction and subsequent modification of the WTC towers. Such

documents are nonnally not archived for more than about 6 years to 7 years, with no

requirements for storage remote from the building. In the case of the WTC towers. The Port Authority and its contractors and consultants maintained an unusually comprehensive set of

documents, a dominant portion of which had not been destroyed in the collapse of the buildings but was assembled and provided to the Investigation Team.

• The Architect of Record was responsible for specifying the fire protection and designing the

evacuation system. There was not, and still is not, a requirement for a fire protection

engineer to be part of the process. In the case of the WTC towers, the building owner played

a significant role in specifying the fire protection and evacuation systems.

• The current state-of-practice is not sufficiently advanced for engineers to routinely analyze

the performance of a whole structural system under a prescribed design-basis fire scenario.

• Buildings were not (and still are not) specifically designed to withstand the impact of fuel- laden commercial aircraft, and building codes in the United States do not require building

designs to consider aircraft impact.

194 NISTNCSTAR 1, WTC Investigation
Principal Findings

• While two documents from The Port Authority indicated that the safety of the WTC towers and their occupants in an aircraft collision was a consideration in the original design, it appears that the effect of the subsequent fires was not considered. NIST was unable to locate any documentary evidence on the aircraft impact analysis considered by The Port Authority.

8.5.2 Structural Safety

• At the time of the design and construction of the WTC towers, there were no explicit structural integrity provisions to mitigate progressive collapse. U.S. Federal agencies and the United Kingdom have since developed and implemented such guidelines. New York City

adopted by rule in 1973 a requirement for buildings to resist progressive collapse under

extreme local loads. The rules apply specifically to buildings that used precast concrete wall

panels and not to other types of buildings.

• At the time of the design and construction of the WTC towers, there were no explicit

minimum structural integrity provisions for the means of egress (stairwells and elevator

shafts) in the building core that were critical to life safety. The building core, generally

designed to be part of the vertical gravity load-carrying system of the structure, need not be

part of the lateral load-carrying system of the structure. In this case, the structural designer

may have preferred the use of partition walls rather than structural walls in the core area to reduce building weight. In the case of the WTC towers, the core had 2 hour fire-rated,

gypsum partition walls with little structural integrity, and the core framing was required to carry only gravity loads. Had there been a minimum stmctural integrity requirement to satisfy normal building and fire safety considerations, it is conceivable that the damage to stairways, especially at the floors of impact, may have been less extensive.

• Wind loads were a major factor in the design of structural components that made up the frame-tube steel framing system. Building codes allow the determination of wind forces

from wind tunnel tests for use in design, but there were not (and still are not) standards for conducting wind tunnel tests and for the methods used in practice to estimate design wind

loads from test results. Results of two sets of wind tunnel tests conducted for the WTC

towers in 2002 by independent commercial laboratories as part of insurance litigation, and

voluntarily provided to NIST by the parties to the litigation, show up to 40 percent

differences in resultant forces on the structures. There were also significant differences

among various specified design wind speeds. Such disparities are indicative of the

limitations associated with the current state of practice in wind engineering for tall buildings.

• The original design wind loads on the towers exceeded those established in the prescriptive

provisions of the NYC Building Code from 1968 through 2001. These wind loads were also higher than those required by other selected building codes and the relevant model building

code of the time. Note, however, that the approach in these codes was oversimplified, and as

a result, these codes may not be applicable for super-tall building design.

• In the original design of the towers, the calculated drift (the maximum sway of the building) was significantly larger than what is currently used in practice. However, drift was not, and

is not, a design factor prescribed in building codes.

NISTNCSTAR 1, WTC Investigation 195
Chapter 8

• The demand/capacity ratios (DCRs) of the columns, estimated from the original WTC design

loads, were in general close to those obtained under current wind design practice. The DCRs

for over 99 percent of the floor trusses and beams were less than unity as they should have

been. The safety of the WTC towers on September 11, 2001 was most likely not affected by

the fraction of structural members for which the demand exceeded allowable capacity due to: (1) the factor of safety in the allowable stress design method, (2) the load redistribution

capability of the steel structures, and (3) the towers having been subjected to lighter than

routine live loads and minimal wind loads at the time of the attacks.

• Under a combination of the original WTC design dead and wind loads, tension forces were

developed in the exterior walls of both towers. The forces were largest at the base of the building and at the comers. The Investigation showed that the DCRs for the exterior wall

splice connections were less than 1.0.

• For the towers' resistance to shear sliding under wind loads, the factor of safety was between

1 0 and 1 1 .5, while the factor of safety against overturning ranged from 1 .9 to 2.7 for both

towers.

• The period of natural building oscillations calculated from the reference global model of the

WTC 1 matched well those detennined from accelerometers located atop the tower. This lent credence to the global models of the towers.

8.5.3 Fire Safety

• By being consistent with the proposed 1968 edition of the NYC Building Code, rather than

the requirements of the 1938 Code, the tower design:

- Eliminated a fire tower (also called a smoke-proof stairway) as a required means of

egress;

- Reduced the number of required stairwells from 6 to 3 (see discussion in Section 5.35)

and the size of doors leading to the stairs from 44 in. to 36 in.;

- Reduced the fire rating of the shaft walls in the building core from 3 hours to 2 hours; and

- Pennitted a 1 hour reduction in fire rating for all structural components (columns from

4 hours to 3 hours and floor framing members from 3 hours to 2 hours) by allowing the

owner/architect to select Class 1 B construction for business occupancy and unlimited

building height.

Many of these allowances in the 1968 NYC Building Code are contained in current codes.

A fire tower (also called a smoke-proof stair) is a stairway that is accessed through an enclosed vestibule that is open to the outside or to an open ventilation shaft providing natural ventilation that prevents any accumulation of smoke without the need

for mechanical pressurization.

196 NISTNCSTAR 1, WTC Investigation
Principal Findings

• In 1993, The Port Authority adopted a poHcy providing for implementation of fire safety

recommendations made by local government fire departments after a fire safety inspection of

a Port Authority facility and for the prior review by local fire safety agencies of fire safety

systems to be introduced or added to a facility. Later that year, The Port Authority entered

into an agreement with FDNY that reiterated the policy adopted by The Port Authority,

recognized the right of FDNY to conduct fire safety inspections of Port Authority properties

in the City of New York, provided guidelines for FDNY to communicate needed corrective

actions to The Port Authority, ensured that new or modified fire safety systems are in compliance with local codes and regulations, and required third-party review of such systems

by a New York State licensed architect or engineer.

• Compartmentation of spaces is a key building fire safety requirement to limit fire spread. . The WTC towers initially had 1 hour fire-rated partitions separating tenants (demising walls)

that extended from the floor to the suspended ceiling, not the floor above (the ceiling tiles were not fire rated). Over the years, these partitions were replaced with partitions that were

continuous fi^om floor to floor (separation wall), consistent with the 1968 NYC Building

Code. Some partitions had not been upgraded by 1997, and a consultant recommended to The Port Authority that it develop and implement a survey program to ensure that the remediation process occurred as quickly as possible. It appears that with few exceptions,

nearly all of the floors not upgraded were occupied by a single tenant. The Port Authority

adopted guidelines in 1998 that required such partitions to provide a continuous fire barrier

from top of floor to underside of slab.

• No technical basis was found for selecting the sprayed fire-resistive material (SFRM) used or

its thickness for the large-span open-web floor trusses of the WTC towers. The assessment of

the insulation thickness needed to meet the 2 hour fire rating requirement for the untested

WTC floor system evolved over time:

- In October 1969, The Port Authority directed the insulation contractor to apply 1/2 in. of

insulation to the floor trusses.

- In 1999, The Port Authority issued guidelines requiring that insulation be upgraded to 1 1/2 in. for full floors undergoing alterations.

- Unrelated to the WTC buildings, an International Conference of Building Officials

(ICBO) Evaluafion Service report (ER-1244), re-issued June 1, 2001, using the same SFRM recommends a minimum thickness of 2 in. for "unrestrained steel joists" with

"lightweight concrete" slab.

• There was no code provision that specifically required the conduct of a fire resistance test if adequate data did not exist from other building components and assemblies to qualify an

untested building element. Instead, several alternate methods were permitted, with limited

guidance on detailed procedures to be followed. Both the Architect of Record (in 1966) and

the Structural Engineer of Record (in 1975) stated that the fire rating of the floor system of

the WTC towers could not be determined without testing. NIST did not fmd evidence

indicating that such a test was conducted to determine the fire rating of the WTC floor system. The Port Authority informed NIST that there are no such test records in its files.

NISTNCSTAR 1, WTC Investigation 197
Neither the 1968 edition of the NYC Building Code, which was used in the design of the

WTC towers, nor the 2001 edition of the code, adopted the "structural frame" requirement.

Use of the "structural frame" approach, in conjunction with the prescriptive fire rating, would

have required the floor trusses, the core floor framing, and perimeter spandrels in the WTC

towers to be 3 hour fire-rated, like the columns for Class 1 B construction in the 1 968 NYC

Building Code. This approach, which appeared in the Unifonn Building Code (a model

building code) as early as 1953, was carried into the 2000 International Building Code (one

of two current model codes). The WTC floor system was essential to the stability of the building as a whole since it provided lateral stability to the columns and diaphragm action to distribute wind loads to the columns of the frame-tube system.

There was, and is, no technical basis to establish whether the construction classification and

fire rating requirements were risk-consistent with respect to the design-basis hazard and the

consequences of that hazard. For tall buildings, the likely consequences of a given threat to an occupant on the upper floors are more severe than the consequences to an occupant on the

first floor, especially considering more difficult access by firefighters and increased time

required for stairwell evacuation. There were, and are, no additional categories for tall buildings, where different building classification and fire ratings requirements may be

appropriate.

There were no field application and inspection requirements to ensure that the as-built condition of the passive fire protection, such as SFRM, confonned to conditions found in fire resistance tests of building components and assemblies. This includes determination of

whether the as-applied average insulation thickness and variability was thermally equivalent

to the specified minimum fire proofing thickness. (Currently, the NYC Building Code and

the IBC require inspection of the SFRM, although self-certification is becoming common. NFPA 5000 requires a quality assurance program.) In addition, requirements were not

available for in-service inspections of passive fire protection during the life of the building.

The adequacy of the insulation of the WTC towers posed an issue of some concern to The

Port Authority over the life of the buildings.

Structural design did not, and does not, consider fire as a design condition, as it does the

effects of dead loads, live loads, wind loads, and earthquake loads. Current prescriptive code

provisions are based on tests that provide relative ratings of fire resistance. These may be

adequate for simple structures and for comparing the relative performance of structural components in more complex structures. The state-of-the-art did not enable evaluation of the

actual performance (i.e., load-carrying capacity) in a real fire of the structural components, or

the structure as a whole system, including the connecfions between components.

The provisions that were used for the WTC towers did not require specification of a fire- rating requirement for connections separate from those for the connected elements. The

Investigation Team was unable to determine the fire rating of a connection where the connected elements had different fire ratings, and whether the applied insulation achieved

that rating.

There was, and is, no technical basis to establish whether the minimum mechanical and

durability related properties of SFRM were sufficient to ensure acceptable in-service

NISTNCSTAR 1. WTC Investigation
Principal Findings

performance in buildings. This includes the ability of such materials to withstand typical

shock, impact, vibration, or abrasion effects over the life of a building. There are now

measurement methods for many of these properties, but the relationship of the results to serviceability requirements is in need of technical support.

• There were no validated tools to analyze the dynamics of building fu-es and their effects on

the structural system that would have allowed engineers to evaluate structural perfomiance

under alternative fire scenarios and fire protection strategies. While considerable progress has been made in recent years, significant work remains to be done before adequate tools are available for use in routine practice. NIST had to further develop and validate tools to in\'estigate the fire performance of the WTC towers.

• Building code provisions for sprinkler installation in office buildings were an option in lieu of

compartmentation. NYC has since promulgated local laws to encourage installation of

sprinklers in new buildings, and is now considering a law to require sprinklers in existing

buildings. The WTC towers were fully sprinklered by 2001, about 30 years after their construction.

• Active smoke management systems and/or combination fire/smoke dampers were not required in fully sprinklered buildings by the 1 968 NYC Building Code or any subsequent,

retroactive provisions.

• With a few special exceptions, building codes in the United States did not, and do not, require

the use of fire-protected elevators for routine emergency access by first responders or as a secondary method (after stairways) for full building evacuation of occupants in emergencies.

• Firefighters moving up the stairs did not significantly lengthen the average time evacuees

spent in the stairways. However, the climbing rate of the firefighter was hampered by the presence and movement of the evacuees.

• The separation of the three stairwells in each tower exceeded the requirements of the 1968

NYC Building Code. On some floors, the separation distances were not as large as the current model building codes require, while on other floors, the separation distances

significantly exceeded the provisions in those codes.

8.6 FUTURE FACTORS THAT COULD HAVE IMPROVED LIFE SAFETY

In the course of the Investigation, NIST and its contractors were aware that there were modem, emerging,

or even imagined capabilities that could have increased the survival rate of those in the WTC towers, had

they been in place on September 11, 2001. These are listed here, not posed as recommendations for implementation, but presented for completeness in the portrayal of the findings of the Investigation.

NIST has not conducted studies to evaluate the degree to which building perfonnance and human factors could have been improved on September 11, 2001, had the capabilities been available.

NISTNCSTAR 1, WTC Investigation 199
Chapter 8

8.6.1 Building Performance Factors

• Thennal insulation that bonds more firmly to structural steel.

• Perimeter column and floor framing with greater mass to enhance thermal and buckling

resistance.

• Improved compartmentation and stairwell enclosures.

• Thermally resistant window assemblies to limit the air supply and retard fire growth.

• Steels with improved high temperature properties, especially with regard to creep.

• Fire protected and structurally hardened elevators for use in occupant evacuation and

responder access.

• More accurate and reliable communications among emergency responders and building

occupants.

• Better management of large-scale emergency incidents.

• Better evacuation training.

• Self-evacuation capability for the mobility impaired.

8.6.2 Human Performance Factors

200 NISTNCSTAR 1, WTC Investigation
Chapter 9

Recommendations

9.1 BUILDING REGULATIONS

As described in Chapter 5. codes and standards for the design, construction, operation, and maintenance

of buildings are the documents by which a society states its intent to provide public safety and

functionality. In the United States, building and fire safety regulations, promulgated and enforced by

state and local jurisdictions, are based on model codes developed by private sector organizations—the

International Code Council (ICC) and the National Fire Protection Association (NFPA). At present (June

2005), all or parts of 45 states plus the District of Columbia use the ICC's International Building Code,

while 36 states plus the District of Columbia use the ICC's International Fire Code. Similarly, NFPA's

National Electrical Code is used in virtually all jurisdictions. With the exception of standards for manufactured housing, the federal government's role in determining specific codes is mandatory only for federally owned, leased, regulated, or financed facilities.

The model codes adopt by reference voluntary consensus standards that are developed by a large number

of private sector standards development organizations (SDOs). The SDOs include NFPA, ASTM

International, the American Society of Civil Engineers (ASCE), the American Institute of Steel Construction (AISC), the American Concrete Institute (ACI), and the American Forest & Paper

Association (AF&PA). The processes used by these organizations are accredited by the American

National Standards Institute (ANSI), which administers and coordinates the U.S. voluntary

standardization and conformity assessment system.

In addition to standards and codes organizations, there are other key stakeholder groups that either are responsible for or influence the practices used in the design, construction, operation, and maintenance of

buildings in the United States. These typically include organizations representing building owners and

managers (e.g., Building Owners and Managers Association, Construction Industry Institute), real estate developers (e.g., Real Estate Board of New York), contractors (e.g.. Associated General Contractors,

Associated Builders and Contractors), architects (e.g., American Institute of Architects), engineers (e.g.. National Society of Professional Engineers, Society of Fire Protection Engineers, Structural Engineering

Institute, National Council of Structural Engineering Associations), suppliers, and insurers. These groups

also provide training, especially as it affects the ability to implement code provisions in practice. Lack of

adequate training programs can Hmit the usefulness or widespread acceptance of improved code

provisions. Very few members of the general public and building occupants participate in this process.

The National Conference of States on Building Codes and Standards (NCSBCS)—a body of the National

Governors Association and the Council of State Governments—includes members representing chief

building regulatory officials of the states and local code officials from across the nation. While NCSBCS

does not develop or implement building codes, it provides a national forum to discuss issues related to codes, standards, and practices that cut across jurisdictional boundaries.

NISTNCSTAR 1, WTC Investigation 201
Chapter 9

The National Institute of Standards and Technology (NIST) is a nonregulatory agency of the U.S. Department of Commerce. NIST does not set building codes or standards, but provides technical support

to the private sector and to other government agencies in the development of U.S. building andfire

practice, standards and codes. NIST provides this support by conducting research which helps to form

the technical basis for such practice, standards, and codes; disseminating research results to practicing

professionals; having its staff participate on technical and standards committees; and, providing technical

assistance to the building and fire safety communities.

Rigorous enforcement ofbuilding codes and standards by state and local agencies, well trained and

managed, is critical in orderfor standards and codes to ensure the expected level ofsafety. Unless they are complied with, the best codes and standards cannot protect occupants, emergency responders, or

buildings. ^

9.2 NIST'S RECOMMENDATIONS FOR IMPROVING THE SAFETY OF

BUILDINGS, OCCUPANTS, AND EMERGENCY RESPONDERS

NIST conducted its building and fire safety investigation of the World Trade Center (WTC) disaster of

September 11, 2001, under the authority of the National Construction Safety Team Act (15 USC 7301 et

seq.). The National Construction Safety Team's final report is required by the Act to include

recommendations that address ( 1 ) specific improvements to building standards, codes, and practices,

(2) changes to, or the establishment of, evacuation and emergency response procedures, and (3) research

and other appropriate actions needed to help prevent future building failures.

As part of its WTC Investigation, NIST is issuing 30 recommendations that identify specific

improvements in the way buildings are designed, constructed, maintained, and used and in evacuation and

emergency response procedures.

• NIST believes that these recommendations are both realistic and achievable within a reasonable period of time and that their implementation would make buildings safer for occupants and emergency responders in future emergencies.

• NIST strongly urges that immediate and serious consideration be given to these

recommendations by the building and fire safety communities—especially designers, owners,

developers, codes and standards development organizations, regulators, fire safety

professionals, and emergency responders.

• NIST also strongly urges building owners and public officials to (1) evaluate the safety

implications of these recommendations to their existing inventory of buildings, and (2) take

the steps necessary to mitigate any unwarranted risks without waiting for changes to occur in codes, standards, and practices.

NIST has assigned top priority to work vigorously with these communities to ensure that there is a complete understanding of the recommendations and their technical basis and to provide needed technical

assistance. As part of this effort, NIST will develop and maintain a web-based system with infomiation on the status of NIST's recommendations that will be available to the public so that progress in implementing them can be tracked.

202 NISTNCSTAR 1, WTC Investigation
Recommendations

In formulating its recommendations from the WTC Investigation, NIST considered:

• The relevant commonly used procedures and practices'' and established baseline performance

for the buildings, evacuation, and emergency response;

• The performance on September 11, 2001, compared to the baseline performance;

• Findings related to building performance, evacuation and emergency response, and to procedures and practices used in the design, construction, operation, and maintenance of the buildings;

• Whether these findings relate to the unique circumstances surrounding the terrorist attacks of

September 11, 2001, or to nonnal building and fire safety considerations (including

evacuation and emergency response);

• Technical solutions that are needed to address potential risks to buildings, occupants, and

emergency responders, considering both identifiable hazards and the consequences of those

hazards; and

• Whether the risks apply to all buildings or are limited to certain building types (e.g., buildings

that exceed a certain height and floor area or that employ a specific type of structural system),

buildings that contain specific design features, iconic/signature buildings, or buildings that house critical functions.

The 30 recommendations resulting from the NIST Investigation were prepared by the Investigation Team

with benefit of review by the National Construction Safety Team Advisory Committee and the public.

These improvements are to be achieved both by complying with existing codes and through provisions

that address new requirements. Table 9-1 (which follows the recommendations) shows a crosswalk

between the recommendations in each of eight groups and three categories. The topics addressed in each

group of recommendations are:

1 . Increased structural integrity, including methods for preventing conditions that could result in progressive collapse (when a building or a significant portion of a building collapses due to disproportionate spread of an initial local failure), standardizing the estimation of wind loads that frequently govern the design of tall buildings, and enhancing the stability of tall buildings.

2. Enhanced fire endurance of structures, including the technical basis for determining construction

classification and fire resistance ratings, improvements to the technical basis for standard fire resistance testing methods, adoption of the "structural frame" approach to fire resistance ratings,

and in-service performance requirements and conformance assessment criteria for spray-applied

fire-resistive materials.

3. New methods for designing structures to resist fires, including the objective of burnout without

collapse, the development of performance-based methods as an alternative to current prescriptive

While there were unique aspects to the design of the WTC towers and the terrorist attacks of September 11, 2001, the design, construction, operation, and maintenance of the WTC towers—and the emergency response to the WTC towers—were based on procedures and practices that were commonly used for normal conditions.

NISTNCSTAR 1, WTC Investigation 203
Chapter 9

design methods, the development and evaluation of new fire-resistive coating materials and

technologies, evaluation of the fire performance of conventional and high-performance structural materials, and elimination of technical and standards barriers to the introduction of new materials

and technologies.

4. Improved active fire protection, including the design, performance, reliability, and redundancy of

sprinklers, standpipes/hoses, fire alarnis, and smoke management systems.

5. Improved building evacuation, including system designs that facilitate safe and rapid egress, methods for ensuring clear and timely emergency communications to occupants, better occupant

preparedness for evacuation during emergencies, and incorporation of appropriate egress

technologies.

6. Improved emergency response, including better access to the buildings and better operations,

emergency communications, and command and control in large-scale emergencies.

7. Improved procedures and practices, including encouraging code compliance by nongovernmental

and quasi-governmental entities, adoption and application of egress requirements in available

code provisions for existing buildings, and retention and availability of building documents over

the life of a building.

8. Education and training programs for fire protection engineers, structural engineers, architects, and

building regulatory and fire service personnel.

Each recommendation has been assigned a number (1, 2, 3, etc.) for easy reference. The numerical

ordering does not reflect any priority.

The three categories and their subdivisions (also included in Table 9-1) are:

• Responsible Community:

- Professional practices

- Provisions in standards, codes, and regulations

- Adoption and enforcement of the provisions

- Research and development or requiring further study

- Education and training

204 NISTNCSTAR 1, WTC Investigation
Recommendations

• Affected Population of Buildings:

- All tall buildings'^; building owners and public officials will need to determine

appropriate performance requirements for buildings that are at risk due to types of

structural, fire safety, or egress systems used, location, use, historic/iconic status, nature of occupancy, etc.

- Selected other buildings (buildings that are at risk due to types of systems used, location, use. historic/iconic status, nature of occupancy, etc.).

• Relation to the outcome on September 1 1, 2001

:

- If in place, could have changed the outcome on September 11, 2001

- Would not have changed the outcome, yet is an important building and fire safety issue

that was identified during the course of the Investigation

In its recommendations, NIST does not prescribe:

• Specific systems, materials, or technologies. NIST encourages competition among different systems, materials, and technologies that can meet performance requirements.

• Specific threshold levels. NIST believes that the responsibility for the establishment of

threshold levels properly belongs in the public policy setting process, in which the standards

and codes development process plays a key role.

Only a few of the recommendations call for new requirements in standards and codes. Most of the recommendations deal with improving an existing standard or code requirement, establishing a standard

for an existing practice without one, establishing the technical basis for an existing requirement, making a current requirement risk-consistent, adopting or enforcing a current requirement, or establishing a performance-based alternative to a current prescriptive requirement.

9.2.1 Group 1. Increased Structural Integrity

The standards for estimating the load effects of potential hazards (e.g., progressive collapse, wind)

and the design of structural systems to mitigate the effects of those hazards should be improved to enhance structural integrity.

Recommendation 1. NIST recommends that: (1) progressive collapse be prevented in buildings

through the development and nationwide adoption of consensus standards and code provisions,

along with the tools and guidelines needed for their use in practice; and (2) a standard

methodology be developed—supported by analytical design tools and practical design

' NIST has found that the physiological impacts on emergency responders of climbing numerous (e.g., 20 or more) stories makes it difficult to conduct effective and timely firefighting and rescue operations in building emergencies without

functioning elevators. Consideration and better knowledge of factors such as ladder height, physiological factors involving emergency responders and building occupants, use of working elevators, and installation and use of protected elevators could

refine the currently used definition of tall buildings to include multiple threshold levels.

NISTNCSTAR 1, WTC Investigation 205
Chapter 9

guidance—to reliably predict the potential for complex failures in structural systems subjected

to multiple hazards.

a. Progressive collapse''^ should be prevented in buildings. The primary structural systems should

provide alternate paths for carrying loads in case certain components fail (e.g., transfer girders or columns). This is especially important in buildings where structural components (e.g., columns,

girders) support unusually large floor areas. Progressive collapse is addressed only in a very

limited way in practice and by codes and standards. For example, the initiating event in design to prevent progressive collapse may be removal of one or two columns at the bottom of the

structure. Initiating events at multiple locations within the structure, or involving other key

components and subsystems, should be analyzed commensurate with the risks considered in the design. The effectiveness of mitigation approaches involving new system and subsystem design

concepts should be evaluated with conventional approaches based on indirect design (continuity,

strength, and ductility of connections), direct design (local hardening), and redundant (alternate)

load paths. The capability to prevent progressive collapse due to abnormal loads should include:

(i) comprehensive design rules and practice guides; (ii) evaluation criteria, methodology, and

tools for assessing the vulnerability of structures to progressive collapse; (iii) performance-based

criteria for abnormal loads and load combinations; (iv) analytical tools to predict potential

collapse mechanisms; and (v) computer models and analysis procedures for use in routine design

practice. The federal government should coordinate the existing programs that address this need:

those in the Department of Defense; the General Services Administration; the Defense Threat

Reduction Agency; and NIST. Affected Standards'^- ASCE-7, AISC Specifications, and

ACl 318. These standards and other relevant committees should draw on expertise from

ASCE/SFPE 29 for issues concerning progressive collapse under fire conditions. Model Building

Codes: The consensus standards should be adopted in model building codes (i.e., the

International Building Code and NFPA 5000) by mandatory reference to, or incorporation of, the

latest edition of the standard. State and local jurisdictions should adopt and enforce the improved

model building codes and national standards based on all 30 WTC recommendations. The codes

and standards may vary from the WTC recommendations, but satisfy their intent.

b. A robust, integrated predictive capability should be developed, validated, and maintained to routinely assess the vulnerability of whole structures to the effects of credible hazards. This

capability to evaluate the perforaiance and reserve capacity of structures does not exist and is a

significant cause for concern. This capability also would assist in investigations of building

failure—as demonstrated by the analyses of the WTC building collapses carried out in this Investigation. The failure analysis capability should include all possible complex failure phenomena that may occur under multiple hazards (e.g., bomb blasts, fires, impacts, gas

explosions, earthquakes, and hurricane winds), experimentally validated models, and robust tools

for routine analysis to predict such failures and their consequences. This capability should be

developed via a coordinated effort involving federal, private sector, and academic research

organizations in close partnership with practicing engineers.

Progressive collapse (or disproportionate collapse) occurs when an initial local failure spreads from structural element to structural element resulting in the collapse of an entire structure or a disproportionately large part of it. ^° While the WTC towers eventually collapsed, they had the capacity to redistribute loads from impact and fire damaged

structural components and subsystems to undamaged components and subsystems. However, the core columns in the WTC

towers lacked sufficient redundant (alternate) paths for carrying gravity loads. A full listing of the affected standards, including the complete names of these standards, is provided in Table 9-2, which is located following the recommendations.

206 NISTNCSTAR 1, WTC Investigation
Recommendations

Recommendation 2. NIST recommends that nationally accepted performance standards be

developed for: (1) conducting wind tunnel testing of prototype structures based on sound

technical methods that result in repeatable and reproducible results among testing laboratories;

and (2) estimating wind loads and their effects on tall buildings for use in design, based on wind

tunnel testing data and directional wind speed data. Wind loads specified in current prescriptive

codes may not be appropriate for the design of very tall buildings since they do not account for building-specific aerodynamic effects. Further, a review of wind load estimates for the WTC towers

indicated differences by as much as 40 percent from wind tunnel studies conducted in 2002 by two

independent commercial laboratories. Major sources of differences in estimation methods currently

used in practice occur in the selection of design wind speeds and directionality, the nature of

hurricane wind profiles, the estimation of "component" wind effects by integrating wind tunnel data

with wind speed and direction information, and the estimation of "resultant" wind effects using load

combination methods. Wind loads were a major factor in the design of the WTC tower structures and were relevant to evaluating the baseline capacity of the structures to withstand abnormal events such

as major fires or impact damage. Yet, there is lack of consensus on how to evaluate and estimate

winds and their load effects on buildings.

a. Nationally accepted standards should be developed and implemented for conducting wind tunnel

tests, estimating site-specific wind speed and directionality based on available data, and

estimating wind loads associated with specified design probabilities from wind tunnel test results and directional wind speed data.

b. Nationally accepted standards should be developed for estimating wind loads in the design of tall buildings. The development of performance standards for estimating wind loads should consider

(1) appropriate load combinations and load factors, including performance criteria for static and

dynamic behavior, based on both ultimate and serviceability limit states, and (2) validation of

wind load provisions in prescriptive design standards for tall buildings, given the universally

acknowledged use of wind-tunnel testing and associated performance criteria. Limitations to the use of prescriptive wind load provisions should be clearly identified in codes and standards.

The standards development work can begin immediately to address many of the above needs. The

results of those efforts should be adopted in practice as soon as they become available. The research

that will be required to address the remaining needs also should begin immediately and results should

be made available for standards development and use in practice. Affected National Standard:

ASCE-7. Model Building Codes: The standard should be adopted in model building codes by

mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 3. NIST recommends that an appropriate criterion be developed and

implemented to enhance the performance of tall buildings by limiting how much they sway

under lateral load design conditions (e.g., winds and earthquakes). The stability and safety of tall buildings depend upon, among other factors, the magnitude of building sway or deflection, which

tends to increase with building height. Conventional strength-based design methods, such as those

used in the design of the WTC towers, do not limit deflections. The deflection limit state criterion,

which is proposed here is in addition to the stress limit and serviceability requirement; it should be

adopted either to complement the safety provided by conventional strength-based design or independently as an alternate deflection-based approach to the design of tall buildings for life safety.

The recommended deflection limit state criterion is independent of the criterion used to ensure occupant comfort, which is met in current practice by limiting accelerations (e.g., in the 15 to 20 milli-g range). Lateral deflections, which already are limited in the design of tall buildings to

NISTNCSTAR 1, WTC Investigation 207
Chapter 9

control damage in earthquake-prone regions, should also be limited in non-seismic areas.""^ Affected

National Standards: ASCE-7, AISC Specifications, and ACI 318. Model Building Codes: The

standards should be adopted in model building codes by mandatory reference to, or incorporation of, the latest edition of the standard.

9.2.2 Group 2. Enhanced Fire Endurance of Structures

The procedures and practices used to ensure the fire endurance of structures be enhanced by

improving the technical basis for construction classifications and fire resistance ratings, improving

the technical basis for standard fire resistance testing methods, use of the "structural frame"

approach to fire resistance ratings, and developing in-service performance requirements and

conformance criteria for sprayed fire-resistive materials.

Recommendation 4. NIST recommends evaluating, and where needed improving, the technical

basis for determining appropriate construction classification and fire rating requirements

(especially for tall buildings)—and making related code changes now as much as possible—by

explicitly considering factors including:^^

• timely access by emergency responders and full evacuation of occupants, or the time

required for burnout without partial collapse;

• the extent to which redundancy in active fire protection (sprinkler and standpipe, fire alarm, and smoke management) systems should be credited for occupant life safety;^"*

• the need for redundancy in fire protection systems that are critical to structural integrity;^^

• the ability of the structure and local fioor systems to withstand a maximum credible fire scenario^^ without collapse, recognizing that sprinklers could be compromised, not

operational, or non-existent;

• compartmentation requirements (e.g., 12,000 ft^'^^^) to protect the structure, including fire rated doors and automatic enclosures, and limiting air supply (e.g., thermally resistant

window assemblies) to retard fire spread in buildings with large, open floor plans;

^' Analysis of baseline performance under the original design wind loads indicated that the WTC towers would need to have been between 50 percent and 90 percent stiffer to achieve a typical drift ratio used in current practice for non-seismic regions,

though not required by building codes. Limiting drift would have required increasing exterior column areas in lower stories and/or significant additional damping.

The construction classification and fire rating requirements should be risk-consistent with respect to the design-basis hazards and the consequences of those hazards. The fire rating requirements, which were originally developed based on experience with buildings less than 20 stories in height, have generally decreased over the past 80 years since historical fire data for buildings suggests considerable conservatism in those requirements. For tall buildings, the likely consequences of a given

threat to an occupant on the upper floors are more severe than the consequences to an occupant on the first floor or the lower

floors. For example, with non-functioning elevators, both the time requirements are much greater for full building evacuation from upper floors and emergency responder access to those floors. It is not clear how the current height and areas tables in building codes consider the technical basis for the progressively increasing risk to an occupant on the upper floors of tall buildings that are much greater than 20 stories in height.

Occupant life safety, prevention of fire spread, and structural integrity are considered separate safety objectives.

The passive fire protection system (includes fireproofing insulation, compartmentation, and firestopping) and the active sprinkler system each provide redundancy for maintaining structural integrity in a building fire, should one of the systems fail to perform its intended function. A maximum credible fire scenario includes conditions that are severe, but reasonable to anticipate, conditions related to building construction, occupancy, fire loads, ignition sources, compartment geometry, fire control methods, etc., as well as adverse, but reasonable to anticipate operating conditions.

208 NIST NCSTAR 1, WTC Investigation
Recommendations

• the effect of spaces containing unusually large fuel concentrations for the expected

occupancy of the building; and

• the extent to which fire control systems, including suppression by automatic or manual

means, should be credited as part of the prevention of fire spread.

Adoption of this recommendation will allow building codes to distinguish the risks associated with

different building heights, fuel concentrations, and fire protection systems. Research is needed to develop the data and evaluate alternative proposals for construction classifications and fire ratings.

Model Building Codes: A comprehensive review of current construction classification and fire rating

requirements and the establishment of a uniform set of revised thresholds with a firai technical basis

that considers the factors identified above should be undertaken."^

Recommendation 5. NIST recommends that the technical basis for the century-old standard

for fire resistance testing of components, assemblies, and systems be improved through a national effort. Necessary guidance also should be developed for extrapolating the results of

tested assemblies to prototypical building systems. A key step in fulfilling this recommendation

is to establish a capabilit> for studying and testing the components, assemblies, and systems

under realistic fire and load conditions.

This effort should address the technical issues listed below:"^

a. Criteria and test methods for determining: o structural limit states, including failure, and means for measurement; o effect of scale of test assembly versus prototype application, especially for long-span

structures that significantly exceed the size of testing furnaces; o effect of restraining thermal expansion (end-restraint conditions) on test results, especially for long-span structures that have greater flexibility;

o fire resistance of structural connections, especially the fire protection required for a loaded

connection to achieve a specified rating:^'^ o effect of the combination of loading and exposure (time-temperature profile) required to adequately represent expected conditions; o the repeatability and reproducibility of test results (typically results from a single test are used

to determine rating for a component or assembly); and

Or a more appropriate limit, which represents a reasonable area for active firefighting operations.

The National Fire Protection Association fNFPA) 5000 model code and the International Building Code (IBC) both recognize

the risks associated with different building heights and accepted changes in 2001 and 2004, respectively. Both model codes now require that buildings 420 feet and higher have a minimum 4 hour structural fire-resistance rating. The previous

requirement was 2 hours. The change provides increased fire resistance for the structural system leading to enhanced

tenability of the structure and gives firefighters additional protection while fighting a fire. While NIST supports these changes

as an interim step, NIST believes that it is essential to complete a comprehensive review that will establish a firm technical

basis for construction classification and fire rating requirements.

The technical issues were identified from the series of four fire resistance tests of the WTC floor system and the review and

analysis of relevant documents that were conducted as part of this Investigation. There is a lack of test data on the fire resistance ratings of loaded connections. The fire resistance of structural connections is not rated in current practice. Also, standards and codes do not provide guidance on fireproofing requirements for structural connections when the connected members have different fire resistance ratings.

NISTNCSTAR 1, WTC Investigation 209
Chapter 9

o realistic ratings for structural assemblies made with materials that have improved elevated

temperature properties (strength, modulus, creep behavior).

b. Improved procedures and guidance to analyze and evaluate existing data from fire resistance tests of building components and assemblies for use in qualifying an untested building element.

c. Relationships between prescriptive ratings and performance of the assembly in real fires.

Affected National and International Standards '^': ASTM E 119, NFPA 251, UL 263, and ISO 834.

Model Building Codes: The standards should be adopted in model building codes by mandatory

reference to, or incorporation of, the latest edition of the standard.

Recommendation 6. NIST recommends the development of criteria, test methods, and

standards: (1) for the in-service performance of sprayed fire-resistive materials (SFRM, also

commonly referred to as fireproofing or insulation) used to protect structural components; and

(2) to ensure that these materials, as-installed, conform to conditions in tests used to establish

the fire resistance rating of components, assemblies, and systems. This should include:

• Improved criteria and testing methodology for the performance and durability of SFRM (e.g.,

adhesion, cohesion, abrasion and impact resistance) under in-service exposure conditions (e.g.,

temperature, humidity, vibration, impact, with/without primer paint on steef^") for use in acceptance and quality control. The current test method to measure the bond strength, for example, does not distinguish the cohesive strength from the tensile and shear adhesive strengths.

Nor does it consider the effect of primer paint on the steel surface. Test requirements that explicitly consider the effects of abrasion, vibration, shock, and impact under normal service

conditions are limited or do not exist. Also, the effects of elevated temperatures on thermal

properties and bond strength are not considered in evaluating the performance and durability

ofSFRM.

• Inspection procedures, including measurement techniques and practical conformance criteria, for SFRM in both the building codes and fire codes for use after installation, renovation, or modification of all mechanical and electrical systems and by fire inspectors over the life of the building. Existing standards of practice (AIA MasterSpec and AWCI Standard 12), often

required by codes for some buildings need to be broadly applied to both new and existing

buildings. These standards may require improvements to address the issues identified in this recommendation.

• Criteria for detennining the effective uniform SFRM thickness—thermally equivalent to the

variable thickness of the product as it actually is applied—that can be used to ensure that the

product in the field conforms to the near uniform thickness conditions in the tests used to establish the fire resistance rating of the component, assembly, or system. Such criteria are needed to ensure that the as-installed SFRM will provide the intended performance.

' While the WTC recommendations are focused mainly on U.S. national standards, each U.S. standard has counterpart

international standards. In a recent report (ISO/TMB AGS N 46), the International Organization for Standardization (ISO), through its Advisory Group for Security (AGS), has recommended that since many of the ISO standards for the design of

buildings date to the 1980s, they should be reviewed and updated to make use of the studies done by NIST on the World Trade

Center disaster, the applicability of new technology for rescue from high buildings, natural disasters, etc. ISO's Technical Advisory Group 8 coordinates standards work for buildings.

'^ NIST tests showed that the adhesive strength of SFRM on steel coated with primer paint was a third to half of the adhesive

strength on steel that had not been coated with primer paint. The SFRM products used in the WTC towers were applied to

steel components coated with primer paint. ^.

210 NISTNCSTAR 1, WTC Investigation
Recommendations

• Methods for predicting the effectiveness of SFRM insulation as a function of its properties, the application characteristics, and the duration and intensity of the fire.

• Methods for predicting service life performance of SFRM under in-service conditions.

Affected Standards: AIA MasterSpec and AWCI Standard 12 for field inspection and conformance

criteria; ASTM standards for SFRM performance criteria and test methods. Model Building Codes:

The standards should be adopted in model building codes by mandatory reference to, or incorporation

of, the latest edition of the standard. (See Recommendation 10 for more on this issue.)

Recommendation 7. NIST recommends the adoption and use of the "structural frame"

approach to fire resistance ratings. This approach requires that structural members—such as

girders, beams, trusses and spandrels having direct connection to the columns, and bracing members

designed to carry gravity' loads—be fire protected to the same fire resistance rating as columns. This

approach is currently required by the International Building Code (IBC), one of the model codes, and

is in the process of adoption by NFPA 5000, the other model code. This requirement ensures consistency in the fire protection provided to all of the structural elements that contribute to overall

structural stability. State and local jurisdictions should adopt and enforce this requirement.

9.2.3 Group 3. New Methods for Fire Resistant Design of Structures

The procedures and practices used in the fire resistant design of structures should be enhanced by

requiring an objective that uncontrolled fires result in burnout without partial or global (total)

collapse. Performance-based methods are an alternative to prescriptive design methods. This

effort should include the development and evaluation of new fire-resistive coating materials and

technologies and evaluation of the fire performance of conventional and high-performance

structural materials.

Recommendation 8. NIST recommends that the fire resistance of structures be enhanced by

requiring a performance objective that uncontrolled building fires result in burnout without

partial or global (total) collapse. Such a provision should recognize that sprinklers could be

compromised, nonoperational, or nonexistent. Current methods for determining the fire resistance

rating of structural assemblies do not explicitly specify a perfomiance objecdve. The rating resulting

from current test methods indicates that the assembly (component or subsystem) continued to support

its superimposed load (simulating a maximum load condition) during the test exposure without

collapse. Model Building Codes: This recommendation should be included into the national model

codes as an objective and adopted as an integral part of fire resistance design for structures. The issue

of non-operational sprinklers could be addressed using the existing concept of Design Scenario 8 of

NFPA 5000, where such compromise is assumed and the result is required to be acceptable to the Authority Having Jurisdiction. Affected Standards: ASCE-7, AISC Specificafions, ACl 318, and

ASCE/SFPE 29.

Recommendation 9. NIST recommends the development of: (1) performance-based standards

and code provisions, as an alternative to current prescriptive design methods, to enable the

design and retrofit of structures to resist real building fire conditions, including their ability to achieve the performance objective of burnout without structural or local floor collapse: and

(2) the tools, guidelines, and test methods necessary to evaluate the fire performance of the

Had this requirement been adopted by the 1968 New York City building code, the WTC floor system, including its connections, would have had the 3 hour rating required for the columns since the floors braced the columns.

NISTNCSTAR 1, WTC Investigation 211
Chapter 9

structure as a whole system. Standards development organizations, including the American

Institute of Steel Construction, have already begun developing performance-based provisions to consider the effects of fire in structural design.

This perfonnance-based capability should include the development of, but not be limited to:

a. Standard methodology, supported by perfonnance criteria, analytical design tools, and practical

design guidance; related building standards and codes for fire resistance design and retrofit of

structures, working through the consensus process for nationwide adoption; comprehensive

design rules and guidelines; methodology for evaluating thermostructural perfonnance of

structures; and computational models and analysis procedures for use in routine design practice,

b. Standard methodology for specifying multi-compartment, multi-floor fire scenarios for use in the

design and analysis of structures to resist fires, accounting for building-specific conditions such

as geometry, compartmentation, fuel load (e.g., building contents and any flammable fuels such

as oil and gas), fire spread, and ventilation; and methodology for rating the fire resistance of

structural systems and barriers under realistic design-basis fire scenarios.

c. Publicly available computational software to predict the effects of fires in buildings—developed,

validated, and maintained through a national effort—for use in the design of fire protection

systems and the analysis of building response to fires. Improvements should include the fire behavior and contribution of real combustibles; the performance of openings, including door

openings and window breakage, that controls the amount of oxygen available to support the growth and spread of fires and whether the fire is fuel-controlled or ventilation-controlled; the

floor-to-floor flame spread; the temperature rise in both insulated and uninsulated structural members and fire barriers; and the structural response of components, subsystems, and the total building system due to the fire.

d. Temperature-dependent thermal and mechanical property data for conventional and innovative

construction materials

e. New test methods, together with associated confomiance assessment criteria, to support the perfonnance-based methods for fire resistance design and retrofit of structures. The perfonnance

objective of burnout without collapse will require the development of standard fire exposures that

differ from those currently used.

Affected National and International Standards: ASCE-7, AISC Specifications, ACI 318, and

ASCE/SFPE 29 for fire resistance design and retrofit of structures; NFPA, SFPE, ASCE, and

ISO TC92 SC4 for building-specific multi-compartment, multi-floor design basis fire scenarios; and

ASTM, NFPA, UL, and ISO for new test methods. Model Building Codes: The performance

standards should be adopted as an alternate method in model building codes by mandatory reference

to, or incorporation of, the latest edition of the standard.

Recommendation 10. NIST recommends the development and evaluation of new fire-resistive

coating materials, systems, and technologies with significantly enhanced performance and

durability to provide protection following major events. This could include, for example,

technologies with improved adhesion, double-layered materials, intumescent coatings, and more

energy absorbing SFRMs.^'* Consideration should be given to pre-treatment of structural steel

Other possibilities include encapsulation of SFRM by highly elastic energy absorbing membranes or commodity grade carbon

fiber or other wraps. The membrane would remain intact under shock, vibration, and impact but may be compromised in a

fire, yet allowing the SFRM to perfonn its thermal insulation function. The carbon wrap would remain intact under shock,

vibration, and impact and, possibly, under fire conditions as well.

212 NIST NCSTAR 1. WTC Investigation
Recommendations

members with some type of mill-applied fire protection to minimize the uncertainties associated with

field application and in-use damage. If such an approach was feasible, only connections and any fire protection damaged during construction and fit-out would need to be field-treated. Affected

Standards: Technical barriers, if any, to the introduction of new structural fire resistance materials,

systems, and technologies should be identified and eliminated in the AIA MasterSpec, AWCI

Standard 12 and ASTM standards for field inspection, conformance criteria, and test methods. Model

Building Codes: Technical barriers, if any, to the introduction of new structural fire resistance

materials, systems, and technologies should be eliminated from the model building codes.

Recommendation 11. NIST recommends that the performance and suitability of advanced

structural steel, reinforced and pre-stressed concrete, and other high-performance material

systems be evaluated for use under conditions expected in building fires. This evaluation should

consider both presently available and new types of steels, concrete, and high-performance materials to establish the properties (e.g., yield and ultimate strength, modulus, creep behavior, failure) that are important for fire resistance, establish needed test protocols and acceptance criteria for such materials

and systems, compare the performance of newer systems to conventional systems, and the cost- effectiveness of alternate approaches. Technical and standards barriers to the introduction and use of

such advanced steel, concrete, and other high-performance material systems should be identified and

eliminated, or at least minimized, if they are found to exist. Affected Standards: AISC Specifications

and ACI 318. Technical barriers, if any, to the introduction of these advanced systems should be

eliminated in ASTM E 1 19, NFPA 251, UL 263, ISO 834. Model Building Codes: Technical

barriers, if any, to the introduction of these advanced systems should be eliminated from the model

building codes.

9.2.4 Group 4. Improved Active Fire Protection

Active fire protection systems (i.e., sprinklers, standpipes/hoses, fire alarms, and smoke

management systems) should be enhanced through improvements to design, performance,

reliability, and redundancy of such systems.

Recommendation 12. NIST recommends that the performance and possibly the redundancy of

active fire protection systems (sprinklers, standpipes/hoses, fire alarms, and smoke

management systems) in buildings be enhanced to accommodate the greater risks associated

with increasing building height and population, increased use of open spaces, high-risk building

activities, fire department response limits, transient fuel loads, and higher threat profile. The

performance attributes should deal realistically with the system design basis, reliability of

automatic/manual operations, redundancy, and reduction of vulnerabilities due to single point

failures. Affected Standards: NFPA 13, NFPA 14, NFPA 20, NFPA 72, NFPA 90A, NFPA 92A,

NFPA 92B, and NFPA 101. Model Building Codes: The perfonnance standards should be adopted in model building codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 13. NIST recommends that fire alarm and communications systems in buildings be developed to provide continuous, reliable, and accurate information on the status of life safety conditions at a level of detail sufficient to manage the evacuation process in building fire emergencies; all communication and control paths in buildings need to be designed

and installed to have the same resistance to failure and increased survivability above that

specified in present standards. This should include means to maintain communications with

evacuating occupants that can both reassure them and redirect them if conditions change. Preinstalled fire warden telephone systems in buildings can serve a useful purpose and may be installed

in buildings, and if so. they should be made available for use by emergency responders. All

NISTNCSTAR 1. WTC Investigation 213
Chapter 9

communication and control paths in buildings need to be designed and installed to have the same

resistance to failure and increased survivability above that specified in present standards. Affected

Standards: NFPA 1, NFPA 72, and NFPA 101. Model Building and Fire Codes: The performance

standards should be adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 14. NIST recommends that control panels at fire/emergency command

stations in buildings be adapted to accept and interpret a larger quantity of more reliable

information from the active fire protection systems that provide tactical decision aids to fireground commanders, including water flow rates from pressure and flow measurement

devices, and that standards for their performance be developed. Affected Standards: NFPA 1, NFPA 72, and NFPA 101. Model Building and Fire Codes: The performance standards should be

adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 15. NIST recommends that systems be developed and implemented for:

(1) real-time off-site secure transmission of valuable information from fire alarm and other

monitored building systems for use by emergency responders, at any location, to enhance

situational awareness and response decisions and maintain safe and efficient operationsr^^ and

(2) preservation of that information either off-site or in a black box that will survive a fire or other building failure for purposes of subsequent investigations and analysis. Standards for the

performance of such systems should be developed, and their use should be required. Affected

Standards: NFPA 1, NFPA 72, and NFPA 101. Model Building and Fire Codes: The performance

standards should be adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard.

9.2.5 Group 5. Improved Building Evacuation

Building evacuation should be improved to include system designs that facilitate safe and rapid

egress, methods for ensuring clear and timely emergency communications to occupants, better

occupant preparedness regarding their roles and duties for evacuation during emergencies, and

incorporation of appropriate egress technologies.^*

Recommendation 16. NIST recommends that public agencies, non-profit organizations

concerned with building and fire safety, and building owners and managers develop and carry

out public education and training campaigns, jointly and on a nationwide scale, to improve

building occupants' preparedness for evacuation in case of building emergencies. This effort

The alarm systems in the WTC towers were only capable of determining and displaying: (a) areas that had at some time reached alann point conditions; and (b) areas that had not. The quality and reliability of information available to erriergency

responders at the Fire Command Station was not sufficient to understand the fire conditions. The only information transmitted

outside the building was the fact that the building had gone into alarni. Further, the fire alarm system in WTC 7, which was

transmitted to a monitoring service, was on "tesf the morning of September 1 1, 2001, because routine maintenance was being

perfonned. Under test conditions ( 1 ) the system is typically disabled for the entire building, not just for the area where work is being performed, and (2) alarm signals typically do not show up on an operator console. This effort should include standards and guidelines for the development and evaluation of emergency evacuation plans, including best practices for both partial and full evacuation, and the development of contingency plans that account for expected conditions that may require adaptation, including the compromise of all or part of an egress path before or during

evacuation, or conditions such as widespread power failure, earthquake, or security threat that restrict egress from the building. Evacuation planning should include the process from initial notification of the need to evacuate to the point the occupants

arrive at a place where their safety is ensured. These standards and guidelines should be suitable for assessing the adequacy of

evacuation plans submitted for approval and should require occupant training through the conduct of regular drills.

214 NISTNCSTAR 1, WTC Investigation
Recommendations

should include better training and self-preparation of occupants, an effectively implemented system of

floor wardens and building safety personnel, and needed improvements to standards. Occupant

preparedness should include:

a. Improved training and drills for building occupants to ensure that they know evacuation

procedures for a variety of emergency scenarios (e.g., including evacuation and shelter in place), are familiar with the egress route, and are sufficiently aware of what is necessary if evacuation is required with minimal notice (e.g., footwear consistent with the distance to be traveled, a flashlight/glow stick for pathway illumination, and dust masks).

b. Building owners and managers should educate tenants on the life safety systems present in their building(s), provide training materials explaining egress routes and stairwell and elevator

information, and develop educational programs explaining the most appropriate responses in emergency situations. It is further recommended that the owners and managers of office

buildings implement the necessary systems for collecting and storing the training history of each

building occupant.

c. Improved training and drills that routinely inform building occupants that roof rescue is not (or is) presently feasible as a standard evacuation option, that they should evacuate down the stairs in any fiill-building evacuation unless explicitly instructed otherwise by on-site incident

commanders, and that elevators can be used if they are still in service and haven't been recalled or stopped.

d. Improved codes, laws, and regulations that do not restrict or impede building occupants during

evacuation drills from familiarizing themselves with the detailed layout of alternate egress routes

for a full building evacuation.^^

Affected Standard: ICC/ANSI A II 7- 1 . Model Building and Fire Codes: The standard should be

adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard. Affected Organizations: NFPA, NIBS, NCSBCS, BOMA, and CTBUH.

Recommendation 17. NIST recommends that tall buildings be designed to accommodate timely

full building evacuation of occupants when required in building-specific or large-scale

emergencies such as widespread power outages, major earthquakes, tornadoes, hurricanes

without sufficient advanced warning, fires, explosions, and terrorist attack. Building size,

population, function, and iconic status should be taken into account in designing the egress

system. Stairwell capacity and stair discharge door width' should be adequate to accommodate counterflow due to emergency access by responders.

a. Improved egress analysis models, design methodology, and supporting data should be developed

to achieve a target evacuation performance (e.g., time for full building evacuation^^) for the design building population by considering the building and egress system designs and human

factors such as occupant size, mobility status, stairwell tenability conditions, visibility, and

congestion.

New York City Local Law 5 prohibits requiring occupants to practice stairwell evacuation during drills. Egress capacity should be based on an ail-hazards approach that considers the number and width of stairs (and doors) as well

as the possible use of scissor stairs credited as a single stair. Use of egress models is required to estimate the egress capacity for a range of different evacuation strategies, including full building evacuation. NIST found that the average surviving occupant in the WTC towers descended stairwells at about half

the slowest speed previously measured for non-emergency evacuations.

NISTNCSTAR 1, WTC Investigation 215
Chapter 9

b. To the degree possible, mobility-impaired occupants should be provided a means for self- evacuation in the event of a building emergency. Current strategies (and law) generally require

the mobility impaired to shelter-in-place and await assistance. New procedures, which provide

redundancy in the event that the floor warden system or co-worker assistance fails, should

consider full building evacuation, and may include use of fire-protected and structurally hardened

elevators,''" motorized evacuation technology, and/or dedicated communication technologies for the mobility impaired.

c. If protected/hardened elevators are provided for emergency responders but become unusable

during an emergency, due to a malfunction or a conventional threat whose magnitude exceeds the magnitude considered in design, sufficient stairwell capacity should be provided to ensure timely

emergency responder access to buildings that are undergoing full evacuation. Such capacity

could be provided either via dedicated stairways for fire service use or by building sufficient

stairway capacity (i.e., number and width of stairways and/or use of scissor stairs credited as a

single stair) to accommodate the evacuation of building occupants while allowing access to emergency responders with minimal hindrance from occupant counterflow.

d. The egress allowance in assembly use spaces should be limited in state and local laws and

regulations to no more than a doubling of the stairway capacity for the provision of a horizontal

exit on a floor, as is the case now in the national model codes."" The use of a horizontal exit creates an area of refuge with a 2 hour fire rated separation, at least one stair on each side, and

sufficient space for the expected occupant load.

Affected Standards: NFPA 101, ASME A 17. Model Building and Fire Codes: The standards should

be adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 18. NIST recommends that egress systems be designed: (1) to maximize

remoteness of egress components (i.e., stairs, elevators, exits) without negatively impacting the

average travel distance; (2) to maintain their functional integrity and survivability under

foreseeable building-specific or large-scale emergencies; and (3) with consistent layouts,

standard signage, and guidance so that systems become intuitive and obvious to building

occupants during evacuations.

a. Within a safety-based design hierarchy that should be developed, highest priority should be

assigned to maintain the functional integrity, survivability, and remoteness of egress components

and active fire protection systems (sprinklers, standpipes, associated water supply, fire alarms,

and smoke management systems). The design hierarchy should consider the many systems (e.g., stairs, elevators, active fire protection, mechanical, electrical, plumbing, and structural) and

system components, as well as functional integrity, tenant access, emergency responder access, building configuration, security, and structural design.

Elevators should be explicitly designed to provide protection against large, but conventional, building tires. Fire-protected

elevators also should be structurally hardened to withstand the range of foreseeable building-specific or large-scale emergencies. While progress has been made in developing the requirements and technologies for fire-protected elevators, similar criteria and designs for structurally hardened elevators remain to be developed.

The New York City Building Code permits a doubling of allowed stair capacity when one area of refuge is provided on a floor and a tripling of stair capacity for two or more areas of refuge on a floor. In the world of post-September 1 1, 2001, it is difficult to predict ( 1 ) if, and for how long, occupants will be willing to wait in a refuge area before entering an egress

stairway, and (2) what the impact would be of such a large group of people moving down the stairs on the orderly evacuation of lower floors.

216 NISTNCSTAR 1, WTC Investigation
Recommendations

b. The design, functional integrity, and survivability of the egress and other life safety systems (e.g., stairwell and elevator shafts and active fire protection systems) should be enhanced by

considering accidental structural loads such as those induced by overpressures (e.g., gas

explosions), impacts, or major hurricanes and earthquakes, in addition to fire separation

requirements. In selected buildings, structural loads due to other risks such as those due to terrorism may need to be considered. While NIST does not believe that buildings should be

designed for aircraft impact, as the last line of defense for life safety, the stairwells and elevator

shafts individually, or the core if these egress components are contained within the core, should

have adequate structural integrity to withstand accidental structural loads and anticipated risks.

c. Stairwell remoteness requirements should be met by a physical separation of the stairwells that provide a barrier to both fire and accidental structural loads. Maximizing stairwell remoteness,

without negatively impacting the average travel distance, would allow a stairwell to maintain its structural integrity independent of any other stairwell that is subject to accidental loads, even if the stairwells are located within the same structural barrier such as the core. The current "walking

path" measurement allows stairwells to be physically next to each other, separated only by a fire barrier. Reducing the clustering of stairways that also contain standpipe water systems provide

the fire service with increased options for formulating firefighting strategies. This should not preclude the use of scissor stairs"*" as a means of increasing stair capacity—provided the scissor

stair is only credited as a single stair.

d. Egress systems should have consistent layouts with standard signage and guidance so that the systems become intuitive and obvious to all building occupants, including visitors, during

evacuations. Particular consideration should be given to unexpected deviations in the stairwells

(e.g., floors with transfer hallways).

Affected Standard: NFPA 101. Model Building and Fire Codes: The standard should be adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 19. MST recommends that building owners, managers, and emergency

responders develop a joint plan and take steps to ensure that accurate emergency information is communicated in a timely manner to enhance the situational awareness of building occupants

and emergency responders affected by an event. This should be accomplished through better

coordination of information among different emergency responder groups, efficient sharing of

that information among building occupants and emergency responders, more robust design of

emergency public address systems, improved emergency responder communication systems,

and use of the Emergency Broadcast System (now known as the Integrated Public Alert and

Warning System) and Community Emergency Alert Networks.

a. Situational awareness of building occupants and emergency responders in the form of information

and event knowledge should be improved through better coordination of such information among

emergency responder groups (9-1-1 dispatch, fire department or police department dispatch,

emergency management dispatch, site security, and appropriate federal agencies), efficient sharing and communication of information between building occupants and emergency

responders, and improved emergency responder communication systems (i.e., including effective

communication within steel and reinforced concrete buildings, capacity commensurate with the

scale of operations, and interoperability among different communication systems).

Two separate stairways within the same enclosure and separated by a fire rated partition.

NISTNCSTAR 1. WTC Investigation 217
Chapter 9

b. The emergency communications systems in buildings should be designed with sufficient

robustness and redundancy to continue providing pubHc address announcements or instructions in foreseeable building-specific or large-scale emergencies, including widespread power outage,

major earthquakes, tornadoes, hurricanes, fires, and accidental explosions. Consideration should

be given to placement of building announcement speakers in stairways in addition to other

standard locations.

c. The Integrated Public Alert and Warning System (IPAWS) should be activated and used,

especially during large-scale emergencies, as a means to rapidly and widely communicate

infomiation to building occupants and emergency responders to enhance their situational awareness and assist with evacuation.

d. Local jurisdictions (cities and counties or boroughs) should seriously consider establishing a Community Emergency Alert Network (CEAN), within the framework of IPAWS, and make it available to the citizens and emergency responders of their jurisdiction to enhance situational awareness in emergencies.''^ The network should deliver important emergency alerts, information

and real-time updates to all electronic communications systems or devices registered with the CEAN. These devices may include e-mail accounts, cell phones, text pagers, satellite phones,

and wireless PDAs.

Affected Standard: NFPA 101 and/or a new standard. Model Building and Fire Codes: The standard

should be adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard to the extent it is within the scope of building and fire codes.

Recommendation 20. NIST recommends that the full range of current and next generation

evacuation technologies should be evaluated for future use, including protected/hardened

elevators, exterior escape devices, and stairwell descent devices, which may allow all occupants an equal opportunity for evacuation and facilitate emergency response access. Affected

Standards: NFPA 101, ASME A 17, ASTM E 06, ANSI Al 17.1. Model Building and Fire Codes:

The standards should be adopted in model building and fire codes by mandatory reference to, or incorporation of, the latest edition of the standard.

9.2.6 Group 6. Improved Emergency Response

Technologies and procedures for emergency response should be improved to enable better access to buildings, response operations, emergency communications, and command and control in largescale emergencies.

Recommendation 21. NIST recommends the installation of fire-protected and structurally

hardened elevators to improve emergency response activities in tall buildings by providing

timely emergency access to responders and allowing evacuation of mobility-impaired building

occupants. Such elevators should be installed for exclusive use by emergency responders during

emergencies."'* In tall buildings, consideration also should be given to installing such elevators for

Types of emergency communications could include life safety information, severe weather warnings, disaster notifications (including information on ten-orist attacks), directions for self-protection, locations of nearest available shelters, precautionary evacuation infonnation, identification of available evacuation routes, and accidents or obstructions associated with roadways

and utilities. The access time for emergency responders, in tall building emergencies where elevators are not functioning and only stairways can be used, averages between 1 min and 2 min per floor, which, for example, corresponds to between 1 1/2 hour and 2 hours (depending on the amount of gear and equipment carried) to reach the 60"' floor of a tall building. Further, the physiological

218 NISTNCSTAR 1. WTC Investigation
Recommendations

use by all occupants. NIST has found that the physiological impacts on emergency responders of

climbing numerous (e.g., 20 or more) stories makes it difficult to conduct effective and timely

firefighting and rescue operations in building emergencies without functioning elevators. The use of

elevators for these purposes will require additional operating procedures and protocols, as well as a requirement for release of elevator door restrictors by emergency response personnel.

Affected Standards: ASME A 17, ANSI 117.1. NFPA 70. NFPA 101, NFPA 1221, NFPA 1500,

NFPA 1561, NFPA 1620, and NFPA 1710. Model Building and Fire Codes: The standards should be

adopted in model building and fu"e codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 22. NIST recommends the installation, inspection, and testing of emergency

communications systems, radio communications, and associated operating protocols to ensure

that the systems and protocols: (1) are effective for large-scale emergencies in buildings with

challenging radio frequency propagation environments; and (2) can be used to identify, locate,

and track emergency responders within indoor building environments and in the field. The

federal government should coordinate its efforts that address this need within the framework provided

by the SAFECOM program of the Department of Homeland Security.

a. Rigorous procedures, including pre-emergency inspection and testing, should be developed and

implemented for ensuring the operation of emergency communications systems and radio

communications in tall buildings and other large structures (including tunnels and subways), or at locations where communications are difficult.

b. Performance requirements should be developed for emergency cominunications systems and

radio communications that are used within buildings or in built-up urban environments, including

standards for design, testing, certification, maintenance, and inspection of such systems.

c. An interoperable architecture for emergency communications networks—and associated

operating protocols—should be developed for unit operations within and across agencies in large- scale emergencies. The overall network architecture should cover local networking at incident

sites, dispatching, and area-wide networks, considering: (a) the scale of needed communications

in terms of the number of emergency responders using the system in a large-scale emergency and

the organizational hierarchy; (b) challenges associated with radio frequency propagation

especially in buildings; (c) interoperability with existing legacy emergency communications

systems (i.e., between conventional two-way systems and newer wireless network systems); and

(d) the need to identify, locate, and track emergency responders at an incident site.

Affected Standards: FCC, SAFECOM, NFPA Standards on Electronic Safety Equipment, NFPA 70,

NFPA 297, and NFPA 1221. Model Building Codes: The standards should be adopted in model

building codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 23. NIST recommends the establishment and implementation of detailed

procedures and methods for gathering, processing, and delivering critical information through

integration of relevant voice, video, graphical, and written data to enhance the situational awareness of all emergency responders. An information intelligence sector^' should be

established to coordinate the effort for each incident. Affected Standards: National Incident

impact on the emergency responders of climbing more than 10 to 12 floors in a tall building makes it difficult for them to immediately begin aggressive firefighting and rescue operations.

A group of individuals that is knowledgeable, experienced, and specifically trained in gathering, processing, and delivering information critical for emergency response operations and is ready for activation in large and/or dangerous events.

NISTNCSTAR 1. WTC Investigation 219
Chapter 9

Management System (NIMS), NRP, SAFECOM, FCC, NFPA Standards on Electronic Safety

Equipment, NFPA 1500, NFPA 1561, NFPA 1620, NFPA 1710, and NFPA 1221. Model Building

Codes: The standards should be adopted in model building codes by mandatory reference to, or incorporation of, the latest edition of the standard.

Recommendation 24. NIST recommends the establishment and implementation of codes and

protocols for ensuring effective and uninterrupted operation of the command and control

system for large-scale building emergencies.

a. State, local, and federal jurisdictions should implement NIMS. The jurisdictions should work

with the Department of Homeland Security to review, test, evaluate, and implement an effective

unified command and control system. NIMS addresses interagency coordination and establishes

a response matrix—assigning lead agency responsibilities for different types of emergencies and

functions. At a minimum, each supporting agency should assign an individual to provide

coordination with the lead agency at each incident command post.

b. State, local, and federal emergency operations centers (EOCs) should be located, designed, built,

and operated with security and operational integrity as a key consideration.

c. Command posts should be established outside the potential collapse footprint of any building

which shows evidence of large multi-floor fires or has serious structural damage. A continual

assessment of building stability and safety should be made in such emergencies to guide ongoing

operations and enhance emergency responder safety. The infonnation necessary to make these assessments should be made available to those assigned responsibility (see related Recommendations 15 and 23).

d. An effective command system should be established and operating before a large number of

emergency responders and apparatus are dispatched and deployed. Through training and drills, emergency responders and ambulances should be required to await dispatch requests from the incident command system and not to self-dispatch in large-scale emergencies.

e. Actions should be taken via training and drills to ensure a coordinated and effective emergency

response at all levels of the incident command chain by requiring all emergency responders that are given an assignment to immediately adopt and execute the assignment objectives.

f. Command post information and incident operations data should be managed and broadcast to command and control centers at remote locations so that information is secure and accessible by

all personnel needing the information. Methods should be developed and implemented so that any information that is available at an interior information center is transmitted to a emergency

responder vehicle or command post outside the building.

Affected Standards: NIMS, NRP, SAFECOM, FCC, NFPA Standards on Electronic Safety

Equipment, NFPA 1221, NFPA 1500, NFPA 1561, NFPA 1620, and NFPA 1710. Model Building

Codes: The standards should be adopted in model building codes by mandatory reference to,, or incorporation of, the latest edition of the standard.

9.2.7 Group 7. Improved Procedures and Practices

The procedures and practices used in the design, construction, maintenance, and operation of

buildings should be improved to include encouraging code compliance by nongovernmental and

quasi-governmental entities, adoption and application of egress and sprinkler requirements in codes for existing buildings, and retention and availability of building documents over the life of a

building.

220 NISTNCSTAR 1, WTC Investigation
Recommendations

Recommendation 25. Nongovernmental and quasi-governmental entities that own or lease

buildings and are not subject to building and fire safety code requirements of any governmental

jurisdiction are nevertheless concerned about the safety of the building occupants and the

responding emergency personnel. NIST recommends that such entities be encouraged to provide a level of safety that equals or exceeds the level of safety that would be provided by

strict compliance with the code requirements of an appropriate governmental jurisdiction. To

gain broad public confidence in the safety of such buildings, NIST further recommends that as- designed and as-built safet> be certified by a qualified third party, independent of the building

owner(s). The process should not use self-approval for code enforcement in areas including

interpretation of code provisions, design approval, product acceptance, certification of the final

construction, and post-occupancy inspections over the life of the buildings.^^

Recommendation 26. NIST recommends that state and local jurisdictions adopt and

aggressively enforce available provisions in building codes to ensure that egress and sprinkler

requirements are met by existing buildings.^^ Further, occupancy requirements should be

modified where needed (such as when there are assembly use spaces within an office building)

to meet the requirements in model building codes. Provisions related to egress and sprinkler

requirements in existing buildings are available in such codes as the International Existing Building

Code (lEBC), International Fire Code, NFPA 1, NFPA 101, and ASME A17.3. For example, the lEBC defines three levels of building alteration (removal and replacement or covering of existing

materials and equipment, reconfiguration of space or system or installation of new equipment, and

work area in excess of 50 percent of the aggregate area of the building). At the lowest level there are no upgrade implications for sprinklers and the egress system. At the next level, sprinklers are required in work areas serv ing greater than 30 persons if certain other conditions related to building

height and use such as shared exists also are met. There are numerous requirements for means of

egress, including number of exits, specification of doors, dead-end corridors and travel distances,

lighting, signage, and handrails. At the highest level, the sprinkler and egress requirements are

identical to the second level without the minimum 30 person restriction and the other conditions

related to building height and use. The Life Safety Code (NFPA 101) applies retroactively to all buildings, independent of whether any work is currently being done on the building, and ASME 17.3 applies retroactively to all elevators as a minimum set of requirements.

Recommendation 27. NIST recommends that building codes incorporate a provision that

requires building owners to retain documents, including supporting calculations and test data,

related to building design, construction, maintenance and modifications over the entire life of

The long-standing stated policy of The Port Authority of New York and New Jersey (PANYNJ) was to meet and, where

appropriate, exceed the requirements of local building and fire codes, and it entered into agreements with the New York City

Department of Buildings and The Fire Department of the City of New York in accordance with that policy. Although the PAN'YNJ sought review and concurrence from New York City in the areas listed in the recommendation, the PANYNJ was not

required to yield, and appears not to have yielded, approval authority to New York City. The PANYNJ was created as an

interstate entity, a "body corporate and politic," under its charter, pursuant to Article 1, Section 10 of the U.S. Constitution permitting compacts bet^A'een states. Further, there are many other similar nongovernmental and quasi-governmental entities

in the United States. A comprehensive review of documents conducted as part of this Investigation suggests that the WTC

towers generally were designed and maintained consistent with the requirements of the 1968 New York City Building Code. Areas of concern included fireproofmg of WTC floor system, height of tenant separation walls, and egress requirements for the assembly use space for the Windows of the World in WTC I and Top of the World observation deck in WTC 2. These areas of concern did not play a significant role in determining the outcomes related to the events of September 1 1, 2001. The WTC towers were unsprinklered when built. It took nearly 28 years after passage of New York City Local Law 5 in 1973, which required either compartmentation or sprinklering, for the buildings to be fully sprinklered (the Port Authority chose not

to use the compartmentation option in Local Law 5). This was about 1 3 years more than the 1 5-year period for full compliance with Local Law 5 that was set by Local Law 84 of 1979.

NISTNCSTAR 1, WTC Investigation 221
Chapter 9

the building. Means should be developed for offsite storage and maintenance of the

documents. In addition, NIST recommends that relevant building information be made

available in suitably designed hard copy or electronic format for use by emergency responders.

Such information should be easily accessible by responders during emergencies. Model Building

Codes: Model building codes should incorporate this recommendation. State and local jurisdictions

should adopt and enforce these requirements.

Recommendation 28. NIST recommends that the role of the "Design Professional in Responsible Charge"^^ be clarified to ensure that: (1) all appropriate design professionals

(including, e.g., the fire protection engineer) are part of the design team providing the standard

of care when designing buildings employing innovative or unusual fire safety systems,^** and

(2) all appropriate design professionals (including, e.g., the structural engineer and the fire protection engineer) are part of the design team providing the standard of care when designing

the structure to resist fires, in buildings that employ innovative or unusual structural and fire safety systems. Affected Standards: AIA Practice Guidelines. Model Building Codes: The IBC,

which already defines the "Design Professional in Responsible Charge," be clarified to address this recommendation. The NFPA 5000 should incorporate the "Design Professional in Responsible

Charge" concept and address this recommendation.

9.2.8 Group 8. Education and Training

The professional skills of building and fire safety professionals should be upgraded through a national education and training effort for fire protection engineers, structural engineers, and

architects. The skills of the building regulatory and fire service personnel should also be upgraded

to provide sufficient understanding and the necessary skills to conduct the review, inspection, and

approval tasks for which they are responsible.

Recommendation 29. NIST recommends that continuing education curricula be developed and

programs be implemented for (1) training fire protection engineers and architects in structural

engineering principles and design, and (2) training structural engineers, architects, fire protection engineers, and code enforcement officials in modern fire protection principles and

technologies, including fire-resistance design of structures, and (3) training building regulatory

and fire service personnel to upgrade their understanding and skills to conduct the review,

inspection, and approval tasks for which they are responsible. The outcome would further the integration of the disciplines in effective fire-safe design of buildings. Affected Organizations: AIA,

SFPE, ASCE, ASME, AISC, ACI, and state licensing boards. Model Building Codes: Detailed

criteria and requirements should be incorporated into the model building codes under the topic

"Design Professional in Responsible Charge."

The availability of inexpensive electronic storage media and tools for creating large searchable databases make this feasible.

In projects involving a design team, the "Design Professional in Responsible Charge"—usually the lead architect—ensures that the team members use consistent design data and assumptions, coordinates overlapping specifications, and serves as the liaison

to the enforcement and reviewing officials and to the owner. The term is defined in the International Building Code and in the ICC Performance Code for Buildings and Facilities (where it is the Principal Design Professional).

If the fire safety concepts in tall buildings had been sufficiently mature in the 1960s, it is possible that the risks associated with

jet-fuel ignited multi-floor fires might have been recognized and taken into account when the impact of a Boeing 707 aircraft was considered by the structural engineer during the design of the WTC towers.

222 NISTNCSTAR 1, WTC Investigation
Recommendations

Recommendation 30. NIST recommends that academic, professional short-course, and webbased training materials in the use of computational fire dynamics and thermostructural

analysis tools be developed and delivered to strengthen the base of available technical

capabilities and human resources. Affected Organizations: AIA, SFPE, ASCE, ASME, AISC, and

ACI, ICC, NFPA.

9.3 NEXT STEPS

After issuance of the final report, the National Construction Safety Team Act requires NIST to:

• Conduct, or enable or encourage the conducting of, appropriate research recommended by the Team;

• Promote (consistent with existing procedures for the establishment of building standards, codes,

and practices) the appropriate adoption by the Federal Government, and encourage the appropriate adoption by other agencies and organizations, of the recommendations of the Team

with respect to

o Technical aspects of evacuation and emergency response procedures;

o Specific improvements to building standards, codes, and practices; and

o Other actions needed to help present future building failures.

NIST is assigning top priority to work vigorously with the building and fire safety communities to assure

that there is a complete understanding of the recommendations and to provide needed technical assistance

in getting them implemented. NIST has identified specific codes, standards, and practices affected by

each of the recommendations (Tables 9-2a, 9-2b, and 9-2c) and already begun to reach out to the responsible organizations to pave the way for a timely, expedited consideration of the recommendations.

Toward this end, NIST held a conference September 13-15, 2005, that was attended by over 200 people,

including all of the major standards and codes development organizations.

NIST also has awarded a contract to the National Institute of Building Sciences (NIBS) to convene a panel of building code experts to turn appropriate recommendations into code language suitable for submission of code change proposals to the two national model code developers.

In addition, NIST will implement a web-based system so that the public can track progress on

implementing the recommendations. The web site will list each of the recommendations, the specific

organization or organizations (e.g.. standards and code developers, professional groups, state and local authorities) responsible for its implementation, the status of its implementation by organization, and the plans or work in progress to implement the recommendations.

NISTNCSTAR 1. WTC Investigation 223
Chapter 9

Relation

to

9/11

Outcome Unrelated \

Related \

Application

Selected Other

Buildings \ \ \ \ \

All Tall Buildings \ s \ \ \ \ \ \ \ \ \ \ \ \

Responsible

Community

Education &

Training \

R&D/Further

Study \ \ \ \ \ \

Adoption &

Enforcement \ \ \

Standards,

Codes,

Regulations

\ \ \ \ \ \ \

Practices \ \ \ \ \

Recommendation Number in oo ON o 00 o o

Recommendation Group IT)

Recommendation

Area

Increased

Stmctural

Integrity

Enlianced

Fire

Endurance

of

Structures

New

Methods

for

Fire

Resistant

Design

of

StrucUires Improved

Active

Fire

Protection Improved

Building

Evacuation

224 NISTNCSTAR 1. WTC Investigation
Recommendations

Relation

to

9/1 1

Outcome Unrelated \

Related \ \ s \

Application

Selected Other

Buildings \ \ \

All Tall Buildings \ \ s \ \ \ \

Responsible

Community

Education &

Training \ \ \

R«&D/Further

Study \ \ \

Adoption &

Enforcement \ \ \

Standards,

Codes,

Regulations

\ \ s \ \

Practices s \ \ \ \ \ \ S

Recommendation Number r 1 Dri ri rj

IT) ri ri o

Recommendation Group r- 00

u<

s

o

«e

i)E

e

o

u

linpiovod

Emergency

Response Improved

Procedures

and

Practices

Education

and

Training

NISTNCSTAR 1. WTC Investigation 225
Chapter 9

Table 9-2a. Standards Affected by the Recommendations.

Affected Standard Group Number Recommendation

American Concrete Institute, AC I J 1 8 - Buildnig Code Requirements tor Stmctural Concrete1 . Increased Structural Integrity

3. New Methods for Fire Resistant Design of Stnictures

1,3,8,9, 11

American Institute of Architects,

AIA MASTERSPEC - Master Specification

System for Design Professionals and the Building/Construction Industry

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

6, 10

American Institute of Architects

Practice Guidelines

7. Improved Procedures and Practices 28

Amprirjin Tn^stihitp of Stppl

Constmction Specification for Stmctural

Steel Buildings

11 . llIVl^CloV.'W InrrpH'NpH Stni(*tiii".nl .JLlUVlUltll IntppritA/ IlllVt^liLV

3. New Methods for Fire Resistant Design of Structures

1 3, 8, 9 11

/Viiici n^iiii o^JL-ic I y \ji V. 1 V 11 L^iig,iiiv^i ASCE 7 - Minimum Design Loads for Buildings and Other Structures1. lln^lCaoCU ollUL-lUldl lllLC^Iiiy

3. New Methods for Fire Resistant Design of Structures

11 7 ^ 8 Q , z., J), o, y

American Society of Civil Engineers,

ASCE 29 - Standard Calculation Methods

for Structural Fire Protection

1 . Increased Structural Integrity

3. New Methods for Fire Resistant Design of Structures

1,8,9

American Society of Mechanical Engineers,

ASME A 1 7 - Elevators and Escalators, and

A 1 7. 1 - Safety Code for Elevators and

Escalators

5. Improved Building Evacuation

6. Improved Emergency Response

17, 20,21

American Society of Mechanical Engineers,

ASME A 17.3 - Safety Code for Existing Elevators and Escalators

7. Improved Procedures and Practices 26

Association of the Wall and Ceiling Industi^y

AWCI 1 2 - Design Selection UtiHzing

Sprayed Fire-Resistive Materials

AWCI 12-A - Standard Practice for the Testing and Inspection of Field Applied

Fire-Resistive Materials

AWCI 12-B - Standard Practice for the Testing and Inspection of Field Applied

Intumescent Fire-Resistive Materials

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

6, 10

ASTM International Committee E 06,

Performance of Buildings; Subcommittee

E 06.77, High-Rise Building External Evacuation Devices

5. Improved Building Evacuation 20

ASTM International,

ASTM E 1 19 - Standard Test Methods for Fire Tests of Building Construction and

Materials

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

5, 11

Department of Homeland Security,

National Incident Management System

(NIMS)

6. Improved Emergency Response 23,24

226 NISTNCSTAR 1, WTC Investigation
Recommendations

Affected Standard Group Number Recommendation

Department of Homeland Security,

National Response Plan (NRP)

6. Improved Emergency Response 23,24

Department of Homeland Security',

SAFECOM

6. Improved Emergency Response 22, 23, 24

Federal Communications Commission,

Emergency Responder Radio

Communications Regulations

6. Improved Emergency Response 22,23,24

International Code Commission/American

National Standards Instimte, ICC/ANSI

Al 17.1 - Accessible and Usable Buildings

and Facilities

5. Improved Building Evacuation

6. Improved Emergency Response

16, 20,21

International Organization for Standardization. ISO 834 - Fire Resistance Tests

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

5, 1

1

National Fire Protection Association,

NFPA 1 - Fire Prevention Code

4. Enhanced Active Fire Protection

7. Improved Procedures and Practices

12, 13, 14, 15,26

National Fire Protection Association,

NFPA 13 - Installation of Sprinkler Systems

4. Enhanced Active Fire Protection 12

National Fire Protection Association

NFPA 14 - Installation of Standpipe and

Hose Systems

4. Enhanced Active Fire Protection 12

National Fire Protection Association,

NFPA 20 - Installation of Stationary Pumps

for Fire Protection

4. Enhanced Active Fire Protection 12

National Fire Protection Association,

NFPA 70 - National Electrical Code

6. Improved Emergency Response 21,22

National Fire Protection Association,

NFPA 72 - National Fire Alarm Code

4. Enhanced Active Fire Protection 12, 13, 14, 15

National Fire Protection Association,

NFPA 90A - Standard for Installation of Air- Conditioning and Ventilating Systems

4. Enhanced Active Fire Protection 12

National Fire Protection Association,

NFPA 101 - Life Safety Code

4. Enhanced Active Fire Protection

5. Improved Building Evacuation

7. Improved Procedures and Practices

12, 13, 14, 15, 16, 17,

18, 19, 20,21,26

National Fire Protection Association. NFPA 1^1 1 ?S \1 — StanHarH ^ IcLllUul LI iVl^Lll\JUo Methnds nfVJi Tests i Colo nf\J\. Fire Endurance of Building Construction and

Materials

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

5, 11

National Fire Protection Association,

NFPA 297 - Guide on Principles and

Practices for Communications Systems

6. Improved Emergency Response 22

National Fire Protection Association,

NFPA 1221 - Standard for the Installation, Maintenance, and Use of Emergency Service

Communications Systems

6. Improved Emergency Response 21,22, 23,24

NISTNCSTAR 1. WTC Investigation 111
Chapter 9

Affected Standard Group Number Recommendation

National Fire Protection Association,

NFPA 1500 - Standard on Fire Department

Occupational Safety and Health

6. Improved Emergency Response 21,23,24

National Fire Protection Association,

NFPA 1561 - Standard on Emergency

Services Incident Management System

6. Improved Emergency Response 21,23,24

National Fire Protection Association,

NFPA 1620 - Recommended Practice for Pre-Incident Planning

6. Improved Emergency Response 21,23,24

National Fire Protection Association,

NFPA 1 7 10 - Standard for the Organization

and Deployment of Fire Suppression

Operations, Emergency Medical Operations,

allU oUCClal wUCi aLlUllJ> lU lllC JTUUllC UV Career Fire Departments

6. Improved Emergency Response 21, 23, 24

UndeTOriters Laboratories, UL 263 ~ Fire Tests of Building Construction and Materials2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

5,9, 11

Table 9-2b. Model Codes Affected by the Recommendations.

Affected Model Code Group Recommendation

International Building Code 1. Increased Structural Integrity

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

4. Improved Active Fire Protection

5. Improved Building Evacuation

6. Improved Emergency Response

7. Improved Procedures and Practices

8. Education and Training

1-24, 26-29

International Existing Building Code 7. Improved Procedures and Practices 26

International Fire Code 7. Improved Procedures and Practices 26

National Fire Protection Association,

NFPA 5000 - Building Constmction and

Safety Code

1 . Increased Structural Integrity

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

4. Improved Active Fire Protection

5. Improved Building Evacuation

6. Improved Emergency Response

7. Improved Procedures and Practices

8. Education and Training

1-24, 26-29

228 NISTNCSTAR 1, WTC Investigation
Recommendations

Table 9-2c. Organizations Affected by the Recommendations.

Affected Organization Group Recommendation

American Concrete Institute 1 . Increased Structural Integrity

2. Enhanced rire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

O. ILU.U.CallUll ailLl llalllUIg,

1,3,6,8,9, 11,29,

American Institute of Architects 7. Improved Procedures and Practices

o. ILUUCaLlUll allU IXalliJLlX^

28, 29, 30

American Instimte of Steel Construction 3. New Methods for Fire Resistant Design of Structures

8. Education and Training

1,3,8, 9, 29, 30

American National Standards Institute 5. Improved Building Evacuation

6. Improved Emergency Response

16, 20,21

American Society of Civil Engineers 1 . Increased Structural Integrity

3. New Methods for Fire Resistant Design of Structures

8. Education and Training

1,2,3,8,9, 26, 29,

30

American Society of Mechanical Engineers 2. Enhanced Fire Endurance of Structures

5. Improved Building Evacuation

6. Improved Emergency Response

5, 17, 20,21,29,30

rtoaULlallUll Ul Lite Vv till ullLl \^ ^lllU^ lllUUoLiy 5 ASTN4 International z. cnndnceu rire nnuurance oi oliuciuics

3. New Methods for Fire Resistant Design of Structures

5. Improved Building Evacuation

Building OwTiers & Managers Association 5. Improved Building Evacuation 16

Council on Tall Buildings and Urban Habitat 5. Improved Building Evacuation 16

Department of Homeland Security 6. Improved Building Evacuation 22, 23, 24

Federal Communications Commission 6. Improved Emergency Response 22, 23, 24

International Code Council 1 . Increased Structural Integrity

2. Enhanced Fire Endurance of Structures

5. Improved Building Evacuation

8. Education and Training

1,4, 16, 30

International Organization for Standardization

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

5,9, 11

National Conference of States on Building

Codes & Standards, Inc.

5. Improved Building Evacuation 16

NISTNCSTAR 1, WTC Investigation 229
Chapter 9

Affected Organization Group Recommendation

National Fire Protection Association 1 . Increased Structural Integrity

2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

4. Enhance Active Fire Protection

5. Improved Building Evacuation

6. Improved Emergency Response

7. Improved Procedures and Practices

8. Education and Training

1,4,5,8,9, II, 12,

13, 14, 15, 16, 17, 18,

19, 20,21,22,23,24,

26, 30

National Institute of Building Sciences 5. Improved Building Evacuation 16

Society of Fire Protection Engineers 3. New Methods for Fire Resistant Design of Structures

8. Education and Training

8,9,29, 30

State licensing boards 8. Education and Training 29

Underwriters Laboratories 2. Enhanced Fire Endurance of Structures

3. New Methods for Fire Resistant Design of Structures

5, 11

230 NISTNCSTAR 1, WTC Investigation
Appendix A

National Construction Safety Team Act

PUBLIC LAW 107-231—OCT. 1, 2002 116 STAT. 1471

Public Law 107- 107th ConRi-ess231

An Act

To provide for the establishment of investigative teams to assess building perform- ance and emergency response and evacuation procedures in the wake of any

building Eailure that has resulted in substantial loss of life or that posed sig^nificant potential of substantial loss of life. Be it enacted by the Senate and House of Representatives of

the United States ofAmerica in Congress assembled, SECTION 1. SHORT TITLE. This Act may be cited as the "National Construction Safety Team .\ct". SEC. 2. NATIONAL CONSTRUCTION SAFETY TEAIHS.

Oct. 1, 3002 [H.R 46S7]

National

Construction

Safety Team Act

15 use 7301

note.

15 use 730

1

(a) Establishment.—Tlie Director of the National Institute of Standards and Technology (in this Act referred to as the

"Director") is authorized to estabUsh National Construction Safety Teams (in this Act referred to as a "Team',! for deplojonent aft<?r events causing the failure of a building or buildings that has

resulted in substantial loss of life or that posed significant potential

for substantial loss of life. To the maximum extent practicable, the Director shall establish and deploy a Team within 4S hours

after such am event. The Director shall promptly publish in the Federal Register, FedereJ Register notice of the estabhshment of each Team. publication. (b) PtiKPOSE OF In\t:stigation; Duties.—

(1) PtmposE.—The purpose of investigations by Teams is to improve the safety and structural integrity of Buildings in the United States.

(2) Duties. —A Team shall

(A1 establish the likely technical cause or causes of the building failure; (B) evaluate the technical aspects of evacuation and

emergency response procedures;

(C) recommend, as necessary, specific improvements

to building standards, codes, and practices based on the

findings made pursuant to subparagraphs (A) and (B); and

(D) recommend any research and other appropriate

actions needed to improve the structural safety of buildings,

and improve evacuation and emergencv' response proce- dures, based on the findings of the investigation.

(c) Procedukes.—

(1) Development.—Not later than 3 months after tlie date Deadline, of the enactment of this Act. the Director, in consultation with the United States Fire Administration and other appropriate Federal agencies, shall develop procedures for the establishment and deployment of Teams. The Director shall

NISTNCSTAR 1. WTC Investigation 231
Appendix A

116 STAT. 1472 PUBLIC LAW 107-231—OCT. 1, 2002

update such procedures as appropriate. Such procedures shall include pro\isions—

(A) regarding conflicts of interest related to service on tlie Team;

(B) defining the circiimstances under which the

Director wiU estabUsh and deploj' a Team;

(C) prescribing the appropriate size of Teams;

(D) guiding t)ie disclosure of Information under section

8; (E) guiding tlie conduct of investigations under tliis Act, Including procedm-es for providing written notice of inspection authority tmder section 4(a) and for ensming

compliance with any other appUcable law;

(F) identifying and prescribing appropriate conditions

for the provision by the Director of additional resovu-ces and services Teams may need;

(G) to ensm-e that investigations under tliis Act do

not impede and are coordinated with iiny search and rescue

efforts being imdertaken at the site of the building failure; (H) for regular briefings of the pubhc on tlte status

of the investigative proceedings and findinm;

(I) guiding the Teams in moving and preserving evi- dence as described in section 4 (a)(4), (bK2), and (d)(4); (J) providing for coordination with Federal, State, and

local entities that may sponsor research or investigations

of building failiures, including research conducted under

the Earthquake Hazards Reduction Act of 1977; and

(K) regarding such other issues as the Director considers appropriate.

Federal Register, (2) Pliblic,\tion.—The Director shall publish promptly in

publication. the Federal Register final procedures, and subsequent updates

thereof, developed imder paragraph (1).

15 use 7S02. SEC. 3. COMPOSITION OF TEAMS. Each Team shall be composed of individuals selected bv the

Director and led by an individual designated by the Director. Team

members shall include at least 1 employee of the National Institute of Standards and Technologv' and shall include other experts who

are not employees of the National Institute of Standards and Technology, who may include private sector experts, imiversity experts, representatives of professional organizations with appropriate

expertise, and appropriate Federal, State, or local officials. Tecim members who are not Federal employees shall be considered Federal GoveiTunent contractors.

15 use 7303. SEC. 4. AUTHORITIES.

(a) Entry .4ND Inspection.—In investigating a building failure under tlus Act, members of a Team, and any other person authorized by the Director to support a Team, on display of appropriate

credentials provided by the Director and written notice of inspection

authority, may

(1) ent^T property where a biuldiiig failure being inves- tigated has occurred, or where building components, materials, and artifacts with respect to the building faUure are located, and take action necessary, appropriate, and reasonable in Ught

of the natm-e of the property to be inspected to carrv- out

tlie duties of the Team under section 2(b)(2) (A) aitd (B);

232 NISTNCSTAR 1, WTC Investigation
World Trade Center Investigation Publications

PUBLIC LAW 107-231—OCT. 1, 2002 116 STAT. 1473

(2) during reasonable hours, inspect any record (including any desiCTi. construction, or maintenance record), process, or

facility related to the investigation;

(,3^ inspect and test any building components, materials, and artifacts related to the building faiUu-e; and

(4) move such records, components, materials, and artifacts as provided by the procedures developed mider section 2(c)(1). (b) Avoiding Unnecess.\fy Interference .vnd Presebvtno

Evidence.—An inspection, test, or other action taken by a Team

imder this section shall be conducted in a way that

(1) does not interfere unnecess;ully with services pro\'ided

by the owner or operator of the building components, materials,

or artifacts, property, records, process, or facility,'; and

(2) to the maximum extent feasible, presei-ves evidence

related to the building failure, consistent with the ongoing needs of the investigation,

(c) Coordination.—

(1) Wrra SE.\RCH ,00) REsc\"E efforts.—.A Team shaU

not impede, and shall coordinate its investigation with, any

search and rescue efforts being undertaken at the site of the building failure,

(2) With other keseakch.—A Team shall coordinate its investigation, to the extent practicable, with qualified researchers who are conducting engineering or scientific (incluciing social science* research relating to the building

fiailure. (3) Memorajida of l-ndesstanding.—The National

Institute of Standards and Technology shall enter into a memo- randum of understanding with each Federal agency that may

conduct or sponsor a related investigation, providing for coordination of investigations.

(41 With state ant> local authorities.—A Team shaU

cooperate with State and local authorities carrvlng out any

activities related to a Team's investigation.

(d) Interagency' Priorities.—

(1) In general.—Except as provided in paragraph (2) or

(3), a Team investigation shall have priority over any other

investigation of any other Federal agency.

(2) Nation.\l tr.xnsportation safety board.—If the National Transportation Safety Board is conducting an investigation related to an investigation of a Team, the National Transportation Safety Board investigation shall have priority over the Team investigation. Such priority shall not otherwise

affect the authority of the Team to continue its investigation under this Act,

(3) CRijaNAL acts.—If the Attorney General, in consultation with the Director, determines, and notifies the Director, that circumstances reasonably indicate that the building failure being investigated by a Team may have been caused by a criminal act, the Team shall relinquish investigative priority

to the appropriate law enforcement agency. The relinquishment

of investigative prioritv by the Team shall not otherwise affect the authority of the Team to continue its investigation under

this Act.

(4) Preservation of evidence.—If a Federal law enforce- ment agency suspects and notifies the Director that a building

failure being investigated by a Team under this Act may have

NISTNCSTAR 1. WTC Investigation 233
Appendix A

116 STAT. 1474 PUBLIC LAW 107-231—OCT. 1, 2002

been caused by a criminal act, the Team, in consultation with

the Federal law enforcement agency, shall take necessary

actions to ensure that evidence of the criminal act is preserved.

15 use 7304. SEC. 5. BRIEFINGS, HEARINGS, WITNESSES, AND SVnBPOENAS.

(a) Gener.\l Aothority'.—The Director or Im designee, on

behalf of a Team, may conduct hearings, administer oaths, and

require, by subpoena (pursuant to subsection (e)) and otherwise, necessary witnesses and evidence as necessary to carrj' out this

(b) Briefings.—The Du-ector or his designee (who may be

the leader or a member of a Team), on behalf of a Team, shall hold regular pubMc briefings on the status of investigative pro- ceedings and fundings, including a final briefing after the report reqmred by section 6 is issued.

(c) Pliblic He.aeings.—Dming the course of an investigation

bj' a Team, the National Institute of Standards and Technology may, if the Director considers it to be in the public interest, hold

a public hearijig for the purposes of—

(1) gathering t*sttmony fi-om witnesses; and

(2) informijig the pubhc on the progi-ess of the investigation,

(d^ Production of Witnesses.—A witness or evidence in an

investigation mider this Act may be summoned or required to be produced ft-om any place in the Uiut^d States. A witness sum- moned imder this subsection is entitled to the same fee and mileage

the witness would have been paid in a court of the United States.

(e) Issuance of Subpoenas. —A subpoena shall be issued only under the signature of the IXrector but may be sen'ed by ciny person designated by the Director.

(f> Failote To' Obey Subpoen.y—If a person disobeys a sub- poena issued by the Director under tliis Act, the Attorney General,

acting on behalf of the Director, may bring a civil action in a

district court of the United States to enforce the subpoena. An

action under this subsection may be brought in the judicial district in which the person against whom the action is brought resides,

is found, or does business. The coiul may punish a failiu-e t-o obey an order of the court to comply with the subpoena as a contempt of courts

In order to support Teams in carrjing out this Ad, the Director

(1) procure the temporary or intermittent services of experts or consultants imder section 3109 of title 5, United

States Code;

equipment, personnel, and facilities of a department, agency,

or instrumentahty of the United States Government on a reimbursable or other basis;

(3) confer with employees and request the use of services, records, and facilities of State and local governmental authorities; (4) accept voluntary and uncompensated services;

(5) accept and use gifts of money and other property, to the extent provided in advance in appropriations Acts;

(6) make contracts with nonprofit entities to cany out

studies related to purpose, functions, and authorities of the Teams; and

Act

15 use 7305. SEC. e. ADDITIONAL POWERS. may—

234 NISTNCSTAR 1, WTC Investigation
World Trade Center Investigation Publications

PUBLIC LAW 107-231—OCT. 1, 2002 116 STAT. 1475

(7) provide nongovenimental members of the Team reasonable compensation for time spent canning out activities under

this Act. SEC 7. DISCLOSURE OF ESTORMATION. 15 USC 7306.

(a) General Ritj:.—Except as othervvise provided in this sec- Eecotxis. tion, a copy of a record, information, or investigation submitted

or received by a Team shall be made available to the public on

request and at reasonable cost.

(b^ Exceptions.—Subsection (a) does not require the release of—

(1) information described by section 652(b) of title 5, United

States Code, or protected from disclosure by any other law

of the United States; or

(2) information described in subsection (a) by the National

Institute of Standards and Technology- or by a Team mitil the report required by section S is issued-

(c) Protection of Vou-ntafy Sitbmission of Information.—

Notwithstanding any other provision of law. a Team, the National

Institute of Standards and Teclmologv', and any agency receiving information from a Team or the National Institute of Standards £md Technology, shall not disclose voluntarily provided safety- related information if that information is not directly related to the building failure being investigated and the Du^ector finds that

the disclosure of the information would tnliibit the voluntary' provi- sion of that t.vpe of information.

(d> Pltblic SAFETi' INFOR^L4TION.—A Team and the National

Institute of Standards and Teclinology shall not publicly release any iiiformation it receives in the course of an investigation imder

this .Act if the Director finds that the disclosvure of that information might jeopardize public safety. SEC. 8. NATIONAL CONSTRUCTION SAFETTf TEAM REPORT. 15 USC 7307. Not later than 90 days after completing an investigation, a Deadline. Team shall issue a public report which includes

(1) an analysis of the Ukely technical cause or causes of

the building failure investigated;

(2) any technical recormnendations for changes to or the establishment of evacuation and emergency response procedures;

(3) any recommended specific improvements to building standards, codes, and practices; and

(4) recommendations for resesirch and other appropriate

actions needed to help prevent future building failures. SEC. 9. NATIONAL INSnTTUTE OF STANDARDS AND TECHNOLOGY

ACTIONS.

After the issuance of a pubhc report under section 8, the National Institute of Stajidards and Techjiology shall comprehensively review the report and, working with the United States Fire Administration and other appropriate Federal and non-Federal

agencies and organizations

(1) conduct, or enable or encourage the conducting of, appropriate research recommended by the Team; and

(2) promote (consistent with existing procediu-es for the establishment of building standards, codes, and practices) the

15 USC 7303.

NISTNCSTAR 1, WTC Investigation 235
Appendix A

116 STAT. 1476 PUBLIC LAW 107-231—OCT. 1,2002

appropriate adoption by the Federal Government, and encour- age the appropriate adoption by other agencies and organizations, of the recommendations of tlie Team with respect to

(A) technical aspects of evacuation and emergency

response procedures;

(B) specific improvements to building standards, codes, and praclnces; and

(C) other actions needed to help prevent future building

failures.

15 use 7309. SEC. 10. NATIONAI. ES'STITITTE OF STANDARDS AND TECHNOLOGY

ANNUAL REPORT.

Deadline. Not later than Februarj' 15 of each year, the Director shall transmit to the Committ4?e on Science of the House of Representatives and tx) the Committee on Commerce, Science, and Transportation of the Senate a rep>ort tliat includes

(1) a summary of the investigations conducted by Teams

during the prior fiscal year;

(2) a summaiy of recommendations made by the Teams

in reports issued mider section 8 during the prior fiscal year and a description of the extent to which those recommendations

have been implemented; and

(3) a description of die actions taken to improve building

safety and stmctural integrity by the National Institute of Standards and Technologv' during the prior fiscal year in response to reports issued mider section 8. 15USC7310. SEC. 11. ADVISORY COJOnTTEE.

(a) EsTABUsHMENT AND PtTNCTiONS.The Director, in consultation with the United States Fire Administration and other appropriate Federal agencies, shall estabUsh an advisory committee to advise the Director on carrying out tliis Act and to review the procedures developed under section 2(c)(1) and the reports issued under section 8. Deadline. (b) ANNUAL REPORT.—On January 1 of each year, the advisory committee shall tnmsmit to the Committee on Science of the House

of Representatives and to the Committee on Comtmerce, Science, and Transportation of the Senate a report that includes

(1) an evaluation of Team activities, along with rec- ommendations to improve the operation and effectiveness of

Te6UQs; and

(2) an assessment of the implementation of the rec- ommendations of Teams and of the advisory' committee.

(c) DiTKATiON OF Advisory Committee.—Section 14 of the Federal Advisory Committee Act shall not apply to the advisory committee established under this section.

15 use 7311. SEC. 12. ADDITIONAL APPLICABILITY. The authorities and restrictions applicable under tliis Act to the Director and to Teams shall apply to the activities of the National Institute of Standards and Technology in response to the attacks of September 11, 2001. SEC. 13. AMENDMENT.

Section 7 of the National Bureau of Standards Authorization Act for Fiscal Year 19.S6 (15 U.S.C. 281a) is amended by inserting

", or fi-om an investigation under the National Construction Safety

Team Act," after "from such investigation".

236 NISTNCSTAR 1, WTC Investigation
World Trade Center Investigation Publications

PUBLIC LAW 107-231—OCT. 1, 2002 116 STAT. 1477

SEC. 14. CONSTRUCTION. 15 USC 7312. Nothing in this .Act shall be construed to confer any authority on tlie National Institute of Standards and Teclinology to require the adoption of building standards, codes, or practices. SEC. 15. AVTHORIZATION OF APPROPRIATIONS. 15 USC 7313. The National Institute of Standards and Teclinology is authorized to use fiinds otherwise authorized bv law to carrs' out this Act.

Approved October 1, 2002.

LEOISLATnT HISTORY-RR. 4687: HOUSE REPORTS: No. 107-530 (Comm. on ScionceX CONGRESSIONAL RECORD. Vol. 148 ( 2002): July \2. considered and passed House. Sept 9, considered and passed Senate, amended.

Sept. 17, House oorcurred in Senate amendment.

NISTNCSTAR 1, WTC Investigation 237
Appendix A

This page intentionally left blank.

238 NISTNCSTAR 1, WTC Investigation
Appendix B

World Trade Center Investigation Publications

This report, NIST NCSTAR 1, cov ers the WTC towers, with a separate report on the 47-story WTC 7. Supporting documentation of the techniques and technologies used in the investigation are in a set of

companion reports that provide more details of the Investigation findings and the means by which these

technical results were achieved. The titles of the full set of Investigation publications are:

NIST (National Institute of Standards and Technology). 2005. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Final Report on the Collapse ofthe World Trade

Center Towers. NIST NCSTAR 1. Gaithersburg, MD, September.

NIST (National Institute of Standards and Technology). 2006. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Final Report on the Collapse of World Trade Center 7. NIST NCSTAR 1 A. Gaithersburg, MD.

Lew, H. S., R. W. Bukowski, and N. J. Carino. 2005. Federal Building and Fire Safety Investigation of

the World Trade Center Disaster: Design, Construction, and Maintenance ofStructural and Life Safety

Systems. NIST NCSTAR 1-1. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Fanella, D. A., A. T. Derecho, and S. K. Ghosh. 2005. Federal Building and Fire Safety

Investigation of the World Trade Center Disaster: Design and Construction ofStructural Systems.

NIST NCSTAR 1-1 A. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Ghosh, S. K., and X. Liang. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Comparison ofBuilding Code Structural Requirements. NIST

NCSTAR 1-1 B. National Institute of Standards and Technology. Gaithersburg, MD, September.

Fanella, D. A., A. T. Derecho, and S. K. Ghosh. 2005. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Maintenance and Modifications to Structural

Systems. NIST NCSTAR 1-1 C. National Institute of Standards and Technology. Gaithersburg,

MD, September.

Grill, R. A., and D. A. Johnson. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Fire Protection and Life Safety Provisions Applied to the Design and

Construction of World Trade Center 1, 2, and 7 and Post-Construction Provisions Applied after Occupancy. NIST NCSTAR 1 -ID. National Institute of Standards and Technology. Gaithersburg,

MD, September.

Razza, J. C, and R. A. Grill. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Comparison ofCodes, Standards, and Practices in Use at the Time ofthe Design and Construction of World Trade Center 1, 2, and 7. NIST NCSTAR 1-lE. National

Institute of Standards and Technology. Gaithersburg, MD, September.

NIST NCSTAR 1, WTC Investigation 239
Appendix B

Grill, R. A., D. A. Johnson, and D. A. Fanella. 2005. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Comparison ofthe 1968 and Current (2003) New

York Cit)' Building Code Provisions. NIST NCSTAR 1-lF. National Institute of Standards and

Technology. Gaithersburg, MD, September.

Grill, R. A., and D. A. Johnson. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Amendments to the Fire Protection and Life Safety Provisions ofthe New

York City Building Code by Local Laws Adopted While World Trade Center 1, 2, and 7 Were in Use. NIST NCSTAR 1-lG. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Grill, R. A., and D. A. Johnson. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Post-Construction Modifications to Fire Protection and Life Safety Systems

of World Trade Center 1 and 2. NIST NCSTAR 1-1 H. National Institute of Standards and

Technology. Gaithersburg, MD, September.

Grill, R. A., D. A. Johnson, and D. A. Fanella. 2005. Federal Building and Fire Safety Investigation

ofthe World Trade Center Disaster: Post-Construction Modifications to Fire Protection, Life

Safety, and Structural Systems of World Trade Center 7. NIST NCSTAR I-II. National Institute of

Standards and Technology. Gaithersburg, MD, September.

Grill, R. A., and D. A. Johnson. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Design, Installation, and Operation ofFuel System for Emergency Power in World Trade Center 7. NIST NCSTAR I-IJ. National Institute of Standards and Technology.

Gaithersburg, MD, September.

Sadek, F. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center Disaster:

Baseline Structural Performance and Aircraft Impact Damage Analysis ofthe World Trade Center

Towers. NIST NCSTAR 1-2. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Faschan, W. J., and R. B. Garlock. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center Disaster: Reference Structural Models and Baseline Performance Analysis of

the World Trade Center Towers. NIST NCSTAR I-2A. National Institute of Standards and

Technology. Gaithersburg, MD, September.

Kirkpatrick, S. W., R. T. Bocchieri, F. Sadek, R. A. MacNeill, S. Holmes, B. D. Peterson, R. W. Cilke, C. Navarro. 2005. Federal Building and Fire Safety Investigation ofthe World Trade

Center Disaster: Analysis ofAircraft Impacts into the World Trade Center Towers, NIST

NCSTAR 1-2B. National Institute of Standards and Technology. Gaithersburg, MD, September.

Gayle, F. W., R. J. Fields, W. E. Luecke, S. W. Banovic, T. Foecke, C. N. McCowan, T. A. Siewert, and

J. D. McColskey. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center

Disaster: Mechanical and Metallurgical Analysis ofStructural Steel. NIST NCSTAR 1-3. National

Institute of Standards and Technology. Gaithersburg, MD, September.

240 NIST NCSTAR 1. WTC Investigation
World Trade Center Investigation Publications

Luecke, W. E., T. A. Siewert, and F. W. Gayle. 2005. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Contemporaneous Structural Steel

Specifications. NIST Special Publication 1-3 A. National Institute of Standards and Technology.

Gaithersburg, MD, September.

Banovic, S. W. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center

Disaster: Steel Inventory and Identification. NIST NCSTAR 1-3B. National Institute of Standards

and Technology. Gaithersburg, MD, September.

Banovic, S. W., and T. Foecke. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Damage and Failure Modes ofStructural Steel Components. NIST

NCSTAR 1-3C. National Institute of Standards and Technology. Gaithersburg, MD, September.

Luecke, W. E., J. D. McColskey, C. N. McCowan, S. W. Banovic, R. J. Fields, T. Foecke,

T. A. Siewert, and F. W. Gayle. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Mechanical Properties ofStructural Steels. NIST NCSTAR 1-3D.

National Institute of Standards and Technology. Gaithersburg, MD, September.

Banovic, S. W., C. N. McCowan, and W. E. Luecke. 2005. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Physical Properties ofStructural Steels. NIST

NCSTAR 1-3E. National Institute of Standards and Technology. Gaithersburg, MD, September.

Evans, D. D., R. D. Peacock, E. D. Kuligowski, W. S. Dols, and W. L. Grosshandler. 2005. Federal

Building and Fire Safety Investigation ofthe World Trade Center Disaster: Active Fire Protection

Systems. NIST NCSTAR 1-4. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Kuligowski, E. D., D. D. Evans, and R. D. Peacock. 2005. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Post-Construction Fires Prior to September 11,

2001. NIST NCSTAR 1-4A. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Hopkins, M., J. Schoenrock, and E. Budnick. 2005. Federal Building and Fire Safety Investigation

ofthe World Trade Center Disaster: Fire Suppression Systems. NIST NCSTAR 1-4B. National

Institute of Standards and Technology. Gaithersburg, MD, September.

Keough, R. J., and R. A. Grill. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Fire Alarm Systems. NIST NCSTAR 1-4C. National Institute of Standards

and Technology. Gaithersburg, MD, September.

Ferreira, M. J., and S. M. Strege. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center Disaster: Smoke Management Systems. NIST NCSTAR 1-4D. National

Institute of Standards and Technology. Gaithersburg, MD, September.

Gann, R. G., A. Hamins, K. B. McGrattan, G. W. Mulholland, H. E. Nelson, T. J. Ohlemiller,

W. M. Pitts, and K. R. Prasad. 2005. Federal Building and Fire Safety Investigation ofthe World Trade

Center Disaster: Reconstruction ofthe Fires in the World Trade Center Towers. NIST NCSTAR 1-5. National Institute of Standards and Technology. Gaithersburg, MD, September.

NIST NCSTAR 1, WTC Investigation 241
Appendix B

Pitts, W. M., K. M. Butler, and V. Junker. 2005. Federal Building and Fire Safety Investigation of

the World Trade Center Disaster: Visual Evidence, Damage Estimates, and Timeline Analysis.

NISTNCSTAR 1-5 A. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Hamins, A., A. Maranghides, K. B. McGrattan, E. Johnsson, T. J. Ohlemiller, M. Donnelly,

J. Yang, G. MulhoUand, K. R. Prasad, S. Kukuck, R. Anleitner and T. McAllister. 2005. Federal

Building and Fire Safety Investigation ofthe World Trade Center Disaster: Experiments and

Modeling ofStructural Steel Elements Exposed to Fire. NIST NCSTAR 1-5B. National Institute of

Standards and Technology. Gaithersburg, MD, September.

Ohlemiller, T. J., G. W. Mulholland, A. Maranghides, J. J. Filliben, and R. G. Gann. 2005. Federal

Building and Fire Safety Investigation ofthe World Trade Center Disaster: Fire Tests ofSingle

Office Workstations. NISTNCSTAR 1-5C. National Institute of Standards and Technology.

Gaithersburg, MD, September.

Gann, R. G., M. A. Riley, J. M. Repp, A. S. Whittaker, A. M. Reinhom, and P. A. Hough. 2005.

Federal Building and Fire Safety Investigation ofthe World Trade Center Disaster: Reaction of

Ceiling Tile Systems to Shocks. NIST NCSTAR 1-5D. National Institute of Standards and

Technology. Gaithersburg, MD, September.

Hamins, A., A. Maranghides, K. B. McGrattan, T. J. Ohlemiller, and R. Anleitner. 2005. Federal

Building and Fire Safety Investigation ofthe World Trade Center Disaster: Experiments and

Modeling ofMultiple Workstations Burning in a Compartment. NIST NCSTAR 1-5E. National

Institute of Standards and Technology. Gaithersburg, MD, September.

McGrattan, K. B., C. Bouldin, and G. Forney. 2005. Federal Building and Fire Safety

Investigation ofthe World Trade Center Disaster: Computer Simulation ofthe Fires in the World

Trade Center Towers. NIST NCSTAR 1-5F. National Institute of Standards and Technology.

Gaithersburg, MD, September.

Prasad, K. R., and H. R. Baum. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Fire Structure Interface and Thermal Response ofthe World Trade Center

Towers. NIST NCSTAR 1-5G. National Institute of Standards and Technology. Gaithersburg,

MD, September.

Gross, J. L., and T. McAllister. 2005. Federal Building and Fire Safety Investigation ofthe World Trade

Center Disaster: Structural Fire Response and Probable Collapse Sequence ofthe World Trade Center

Towers. NIST NCSTAR 1-6. National Institute of Standards and Technology. Gaithersburg, MD,

September.

Carino, N. J., M. A. Stames, J. L. Gross, J. C. Yang, S. Kukuck, K. R. Prasad, and R. W. Bukowski.

2005. Federal Building and Fire Safety Investigation ofthe World Trade Center Disaster: Passive

Fire Protection. NIST NCSTAR 1-6A. National Institute of Standards and Technology.

Gaithersburg, MD, September.

242 NISTNCSTAR 1, WTC Investigation
World Trade Center Investigation Publications

Gross, J., F. Hervey, M. Izydorek, J. Mammoser, and J. Treadway. 2005. Federal Building and

Fire Safety Investigation ofthe World Trade Center Disaster: Fire Resistance Tests ofFloor Truss

Systems. NIST NCSTAR 1-6B. National Institute of Standards and Technology. Gaithersburg,

MD, September.

Zarghamee, M. S., S. Bolourchi, D. W. Eggers, O. O. Erbay, F. W. Kan, Y. Kitane, A. A. Liepins,

M. Mudlock, W. I. Naguib, R. P. Ojdrovic, A. T. Sarawit, P. R Barrett, J. L. Gross, and

T. P. McAllister. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center

Disaster: Component, Connection, and Subsystem Structural Analysis. NIST NCSTAR 1-6C.

National Institute of Standards and Technology. Gaithersburg, MD, September.

Zarghamee, M. S., Y. Kitane, O. O. Erbay, T. P. McAllister, and J. L. Gross. 2005. Federal

Building and Fire Safety' Investigation ofthe World Trade Center Disaster: Global Structural

Analysis ofthe Response ofthe World Trade Center Towers to Impact Damage and Fire. NIST

NCSTAR 1-6D. National Institute of Standards and Technology. Gaithersburg, MD, September.

McAllister, T., R. W. Bukowski, R. G. Gann, J. L. Gross, K. B. McGrattan, H. E. Nelson, L. Phan,

W. M. Pitts, K. R. Prasad, F. Sadek. 2006. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: Structural Fire Response and Probable Collapse Sequence of World Trade

Center 7. (Provisional). NIST NCSTAR 1-6E. National Institute of Standards and Technology.

Gaithersburg, MD.

Gilsanz, R., V. Arbitrio, C. Anders, D. Chlebus, K. Ezzeldin, W. Guo, P. Moloney, A. Montalva,

J. Oh, K. Rubenacker. 2006. Federal Building and Fire Safety Investigation ofthe World Trade

Center Disaster: Structural Analysis ofthe Response of World Trade Center 7 to Debris Damage

and Fire. (Provisional). NIST NCSTAR 1-6F. National Institute of Standards and Technology.

Gaithersburg, MD.

Kim, W. 2006. Federal Building and Fire Safety Investigation ofthe World Trade Center

Disaster: Analysis ofSeptember 11, 2001, Seismogram Data. (Provisional). NIST NCSTAR I-6G.

National Institute of Standards and Technology. Gaithersburg, MD.

Nelson, K. 2006. Federal Building and Fire Safety Investigation ofthe World Trade Center

Disaster: The Con Ed Substation in World Trade Center 7. (Provisional). NIST NCSTAR 1-6H.

National Institute of Standards and Technology. Gaithersburg, MD.

Averill, J. D., D. S. Mileti, R. D. Peacock, E. D. Kuligowski, N. Groner, G. Proulx, P. A. Reneke, and

H. E. Nelson. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center Disaster:

Occupant Behavior, Egress, and Emergency Communication. NIST NCSTAR 1-7. National Institute of

Standards and Technology. Gaithersburg, MD, September.

Fahy, R., and G. Proulx. 2005. Federal Building and Fire Safety Investigation of the World Trade

Center Disaster: Analysis ofPublished Accounts ofthe World Trade Center Evacuation. NIST

NCSTAR 1-7A. National Institute of Standards and Technology. Gaithersburg, MD, September.

Zmud, J. 2005. Federal Building and Fire Safety Investigation ofthe World Trade Center

Disaster: Technical Documentationfor Survey Administration. NIST NCSTAR 1-7B. National

Institute of Standards and Technology. Gaithersburg, MD, September.

NIST NCSTAR 1, WTC Investigation 243
Appendix B

Lawson, J. R., and R. L. Vettori. 2005. Federal Building and Fire Safety Investigation ofthe World

Trade Center Disaster: The Emergency Response Operations. NIST NCSTAR 1-8. National Institute of

Standards and Technology. Gaithersburg, MD, September.

244 NIST NCSTAR 1. WTC Investigation
Appendix C

Subject Index of Supporting Investigation Reports

The purpose of this index is to direct readers of NIST NCSTAR 1 to the supporting Investigation reports

in which more detailed descriptions of the topics covered in this report can be found. The citations refer

to the NIST NCSTAR report numbers; complete citations are in Appendix B to this report. For a subject

referenced in a report with a number and a letter (e.g., 1-5 A), a summary description of the topic can be

found in the report with the number alone (e.g., 1-5). In most of the citations, the pertinent chapter or section numbers in the report appears in parentheses. The absence of these parenthetical locations

indicates that much of the report is on that topic.

Aircraft Impact

Damage 1-2 (7, 8), 1-2B, 1-3C (2), 1-5 (2), 1-6 (5)

Modeling 1-2 (5), 1-2B

Photographs 1-5A (6, 7), 1-2B (7.2), 1-3C (2)

Speed and direction 1-2 (6), 1-2B (7), 1-5 (2.2, 2.3)

Results and findings 1-2 (7, 8.2), 1-2B (1 1)

Building and Fire Codes

Egress 1-1 (10), 1-lD (5), 1-7 (2.5)

Fire 1-1 (9), 1-lD, 1-lE, 1-lF, 1-lG, 1-IH

Post-construction modifications l-ll (11, 12, 13) Port Authority policies 1-1 A (4) Structural 1-1 (4), 1-1A(2), 1-lB, 1-lC, 1-6(10.2)

Used in WTC design 1-1 (1 to 7)

Collapse

Observations and timeline 1-6 (6), 1-3C (2)

Probable sequences 1-6 (9, 10.9), 1-6D (5)

Combustibles

Aircraft contents 1-5 (3.3)

Jet fuel distribution and locations 1-2, 1-8 (5.3)

Jet fuel quantity 1-5 (3.3)

Workstations 1-5 (3.2), 1-5C, 1-5D

Concrete

Properties 1 -6 (4. 1 ), 1 -6C (3 . 1

)

Elevators (See Evacuation)

Emergency Response

Chronology

Communications and equipment.

Data and interviews

Firefighting

Interagency coordination

Operations

-8 (4) -8 (5.7, 7, 9.2, 9.3)

-8 (2)

-8 (5.6, 9.1)

-8 (8)

-8 (5,9.1,9.4)

NIST NCSTAR 1, WTC Investigation 245
Appendix C

Planning 1-8(6)

Evacuation

Data and interviews 1-7 (3), 1-7 A, 1-7B

Egress system design 1-1 (10), 1-lE (2.8), 1-lH (3, 4, 5)

Elevators 1-1 (10.4), 1-lD (8), 1-lE (2.12), 1-7 (2.2) Factors affecting 1-7(10)

Firefighter interactions 1-8(5.6)

Mobility-impaired people 1-7 (10.3, 1 1.5)

Modeling 1-7(10)

Progression on 9/1 1/01 1-7 (5, 6, 7, 8, 9, 1 1) Stairwells 1-7(2.2)

Fire Alarm System

Codes and standards 1-lD (7), 1-lE (2.1 1), 1-lF (2.6), 1-lH (3, 4, 5)

Design 1-1 (10), 1-4 (4, 6), 1-4C

Operation on 9/1 1/01 1-4 (4.5), 1-4C (6), 1-7 (6, 8, 10), 1-8 (5.3)

Fire Behavior

Characterization 1-5 A (5)

WTC 1 1-5 A (8)

WTC2 1-5A(9)

Firefighting (See Emergency Response)

Fire Simulations

Accuracy 1-5 (4, 5)

Fire Dynamics Simulator (FDS) 1-5 (4), 1-5B (10), 1-5C (4), 1-5F

Fire in an undamaged WTC tower 1-5 (6.15)

Fire Structure Interface (FSl) 1-5 (6), 1-5C (1 1), 1-5G

Results and findings 1-5 (6, 7), 1-5F (7), 1-5G (12)

Fire Suppression Systems

Codes and standards 1-1 (10), 1-lD (6), 1-lE (2.9, 2.10), 1-lF (2.5),

1-1H(3,4, 5), 1-4B(4)

Design 1-4 (3,6), 1-4B

Operation on 9/11/01 1-4 (3), 1-4B (9), 1-8 (5.3)

Fire TestsExposure of structural steel 1-5 (5), 1-5

B

Floor systems 1-6 (3, 10.3), 1-6B

Single office workstations 1-5 (4), 1-5C

Multiple workstations 1-5 (4), 1-5E

Insulation (for Fire Protection of Structural Steel)

Damage 1-2, 1-3C (2), 1-5G (5), 1-6 (2.7), 1-6A

Modeling 1-5G (4,5,7). 1-6 (2)

Properties 1-6 (2), 1-6A (3, 6, 7)

Specifications 1 - 1 H (6, 7, 9), 1 -6 (2, 1 0. 1 ), 1 -6

A

Thickness 1-6A (4,5)

246 NISTNCSTAR 1, WTC Investigation
Subject Index of Supporting Investigation Reports

Jet Fuel (See Combustibles)

Photographs and videos

Collection 1-5 (2), 1-5 A (2)

Timing 1-5 (2), 1-5A(3)

Smoke Management System

Design 1-1 (10). 1-lE (2.5, 2.13), 1-lF (2.8), 1-4 (5, 6), 1-4D

Operation on 9/11/01 1-4 (5.4), 1-4D (7, 8), 1-8 (5.3)

Stairwells (See Evacuation)

Structural Steel

Damage 1-3 (6, 9), 1-3C

Mechanical properties 1-3 (7, 9), 1-3D, 1-6 (4), 1-6C (3)

Recovered pieces 1-3 (5), 1-3B

Specifications 1-3 (3, 4), 1-3

A

Physical properties 1-3 (8), 1-3E

Structure Modeling

For aircraft impact 1-2, 1-2B (2, 3)

Reference models 1-2 (2), 1-2

A

Towers 1-2, 1-5F, 1-6 (4, 7, 8, 10), 1-6C, 1-6D

Results and findings 1-6 (10.8)

Timelines

Aircraft impact

Evacuation

Fires

Structural

1-2, 1-2B, 1-5A

1-7, 1-8

1-5 (2), 1-5

A

1-6 (8, 9)

World Trade Center Towers

Baseline structural performance

Ceiling tile system

Description

Design and construction

Fire safety staff Gravity loads

Iimovative features

Interior layout

Structural maintenance and modifications

Modifications post- 1993 bombing

Occupant demographics

Prior fires Wind loads

1-2 (4, 8), 1-2A(2, 3, 5, 6) 1-5 (3.1), 1-5D, 1-7 (6.1, 7)

1-1 (2), 1-2A(1), 1-5A(4), 1-7 (2.1)

1-1 (5, 7), 1-lA (6, 7, 8), 1-3 (2), 1-5A (4) 1-7 (2.3)

1-lB (4), 1-2 A (4)

1-1 (6), 1-1A(3, 5)

1-1 (10), 1-5 (3.1)

1-1 (8), 1-lC

1-7 (2.4), 1-8 (3) 1-7 (4, 11.1) 1-4 (2), 1-4A

1-1B(4), 1-2 (3), 1-2A (4)

NISTNCSTAR 1. WTC Investigation 247
Appendix C

\

This page intentionally left blank.

248 NISTNCSTAR 1, WTC Investigation