- About NRC           - The Commission
      - Statutory Authority
      - Strategic Plan
      - Budget & Performance
      - Organization & Functions
      - Locations
      - History
      - Values
      - Policymaking
      - Radiation Protection
      - Fire Protection
      - Regulation
      - Emergency Preparedness   and Response
      - Public Affairs
      - Congressional Affairs
      - International Programs
      - State and Tribal Programs
      - Alternative Dispute   Resolution Programs
      - Contact Us
      - Employment
      - Contracting
      - Grants
      - Civil Rights
      -     
    - NuclearReactors           - Power Reactors
      - Research and Test Reactors
      - Operating Reactors
      - Operator Licensing
      - New Reactors
      - Advanced Reactors
      - Operator Licensing for New Reactors
      -     
    - NuclearMaterials           - Special Nuclear Material
      - Source Material
      - Byproduct Material
      - Med, Academic & Ind Uses
      - Source Materials Facilities
      - Uranium Recovery Facilites
      - Fuel Cycle Facilities
      - Materials Transportation
      -     
    - RadioactiveWaste           - Low-Level Waste
      - Waste Incidental to Reprocessing
      - High-Level Waste
      - Uranium Mill Tailings
      - LLW Disposal
      - HLW Disposal
      - Storage of Spent Nuclear Fuel
      - Transporation of Spent Nuclear Fuel
      -     
    - NuclearSecurity           - Domestic Safeguards
      - Information Security
      - Radioactive Material
      - &;   
    - Public Meetings& Involvement           - Open Government
      - Public Meeting Schedule
      - Commission Schedule
      - Conferences & Symposia
      - Documents for Comment
      - Involving Stakeholders
      - Info Quality Guidelines
      - Subscribe to E-mail Notices 
      -     

```
                                 UNITED STATES
                         NUCLEAR REGULATORY COMMISSION
               OFFICE OF NUCLEAR MATERIAL SAFETY AND SAFEGUARDS
                            WASHINGTON, D.C.  20555

                                 May 24, 1996


NRC INFORMATION NOTICE 96-33:  ERRONEOUS DATA FROM DEFECTIVE THERMOCOUPLE
                               RESULTS IN A FIRE


Addressees

All material and fuel cycle licensees that monitor temperature with
thermocouples.

Purpose

The U.S. Nuclear Regulatory Commission (NRC) is issuing this information
notice to alert addressees to an incident where a defective thermocouple
caused an evaporator to run at an excessively high temperature, resulting in a
fire.  It is expected that recipients will review the information for applica-
bility to their facilities and consider actions, as appropriate, to avoid
similar problems.  However, suggestions in this information notice are not NRC
requirements; therefore, no specific action nor written response is required.

Description of Circumstances

On February 21, 1996, a licensee had a fire in the ventilation system of its
liquid waste process.  The licensee's investigation determined that the fire
was caused by a type-J thermocouple manufactured with reverse polarity.  The
type-J thermocouple was part of a Pulse Combustion Drier put into operation in
1985 to evaporate waste water.  The drier operates with natural gas that
ignites inside the drier combustion chamber.  Waste water is pumped into the
hot gases being expelled from the combustion chamber within an evaporation
cone.  The temperature is controlled by regulating the amount of waste water
being fed into the system.  This is based on temperature readings from a
thermocouple in the duct work.

The licensee had replaced the thermocouple with a spare unit while trouble-
shooting a lead wire problem on February 15, 1996.  The spare thermocouple was
found to have reverse polarity during a test run, and the licensee believed it
had corrected the problem by reversing the lead wire polarity at the
instrument.  The system appeared to read correctly during a 10-minute test
run.  However, approximately an hour into a full run the next day, the
temperature reading began to behave erratically.  The temperature readings
dropped even though the actual temperature was increasing.  By the time the
licensee identified the discrepancy, a fire had started in the dust collector
filter cartridges.

The defective type-J thermocouple was purchased in 1985 (as a spare part),
along with the Pulse Combustion Drier from Sonodyne Industries in Portland,
Oregon.  The thermocouple had been manufactured for Sonodyne Industries by 


9605220019.                                                            IN 96-33 
                                                            May 24, 1996
                                                            Page 2 of 2


Gulton Measurement and Control Systems Division (a division of Gulton
Industries) in East Greenwich, Rhode Island.  The licensee reported that
Sonodyne Industries is out of business and Gulton Industries is no longer
manufacturing thermocouples.

Discussion

NRC is not aware of any other Sonodyne driers currently being used by NRC
licensees.  Licensees that operate waste water evaporators or other heat-
generating systems using thermocouples may wish to consider reviewing the
source of the thermocouples and testing the polarity of thermocouples in
stock.

This information notice requires no specific action nor written response.  If
you have any questions about the information in this notice, please contact
the technical contact listed below or the appropriate regional office.


      signed by                                 signed by

Elizabeth Q. Ten Eyck, Director           Donald A. Cool, Director
Division of Fuel Cycle Safety             Division of Industrial and 
   and Safeguards                            Medical Nuclear Safety
Office of Nuclear Material Safety         Office of Nuclear Material Safety
   and Safeguards                            and Safeguards

Technical contact:  Kevin M. Ramsey, NMSS
                    (301) 415-7887
                    Internet:[email protected]

Attachments:
1.  List of Recently Issued NMSS Information Notices
2.  List of Recently Issued NRC Information Notices
```