Name: Chris Heintz

Title: Environmental Scientist

Company: Nevada Energy

Sign Date:

Name: Kevin Donahoe

Title: Project Manager

Company: The Avogadro Group

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

NV 2324 Reid Gardner Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Saturday, February 26, 2011 Page 1 of 19
NV 2324 Reid Gardner Unit 1

Facility Information:

NV 2324 Reid Gardner Unit 1

501 Wally Kay Way

Moapa NV 89025

Contact: Chris Heintz

Phone: 702-402-2048

Fax:

Email:

Testing Company:

The Avogadro Group

2825 Verne Roberts Circle

Antioch CA 94509

Contact: Kevin M. Donahoe

Phone: 877-602-1023

Fax:

Email: kdonahoe@avogadrogroup.com

Air Permit Number:

2324

Permitted Source ID/Name:

1 Reid Gardner Station

Permitted Maximum Process Rate:

111 Mwe

Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

NV 2324 Unit 

1

161.16 0 0 0 0 0 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

NV 2324 Unit Carbon Monoxide Method 10 3 120 0

1

Total organic compounds 

(TOC) as Propane

NV 2324 Unit Method 25A 3 120 0

1

NV 2324 Unit Hydrogen Chloride Method 26A 3 60 0

1

Saturday, February 26, 2011 Page 2 of 19
NV 2324 Reid Gardner Unit 1

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

NV 2324 Unit Hydrogen Fluoride Method 26A 3 60 0

1

Inorganic (Aqueous) 

Condensible Part.

NV 2324 Unit OTM - 27/28 3 380 0

1

NV 2324 Unit Filterable PM2.5 OTM - 27/28 3 380 0

1

NV 2324 Unit Total PM2.5 OTM - 27/28 3 380 0

1

Organic Condensible 

Particulate

NV 2324 Unit OTM - 27/28 3 380 0

1

NV 2324 Unit Nickel Method 29 3 240 0

1

NV 2324 Unit Cadmium Method 29 3 240 0

1

NV 2324 Unit Manganese Method 29 3 240 0

1

NV 2324 Unit Lead Method 29 3 240 0

1

NV 2324 Unit Antimony Method 29 3 240 0

1

NV 2324 Unit Filterable Particulate Method 29 3 240 0

1

NV 2324 Unit Arsenic Method 29 3 240 0

1

NV 2324 Unit Cobalt Method 29 3 240 0

1

NV 2324 Unit Chromium Method 29 3 240 0

1

NV 2324 Unit Beryllium Method 29 3 240 0

1

NV 2324 Unit Selenium Method 29 3 240 0

1

NV 2324 Unit Sulfur Dioxide Method 6C 3 120 0

1

NV 2324 Unit Nitrogen oxides (NOx) Method 7E 3 120 0

1

Saturday, February 26, 2011 Page 3 of 19
NV 2324 Reid Gardner Unit 1

Sampling / Stack Data Results Summary

Location NV 2324 Unit 1 - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location NV 2324 Unit 1 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 4 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 26A

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 5/6/2010 5/6/2010 5/8/2010

Run Start Time 7:20:00 AM 1:41:00 PM 8:11:00 AM

Run Finish Time 9:57:01 AM 2:51:01 PM 9:26:00 AM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 38.988 35.460 33.812 36.087

Moisture Content of Stack Gas, % 12.01 12.01 12.30 12.107

Moisture Saturation at Stack Gas Temperature, % 18.37 19.22 18.88 18.823

Carbon Dioxide, % 10.89 10.71 11.76 11.120

Oxygen, % 8.78 8.95 7.75 8.493

Average Stack Gas Temperature, °F 135.25 136.92 136.04 136.070

Dry Volumetric Flow Rate, dry scfm 282,270.5 278,300.8 274,953.7 278,508.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 382,901.6 379,246.8 377,376.9 379,841.767

Percent Isokinetic of Sampling Rate, % 109.2 104.3 97.2 103.567

F-Factor, dscfm/MMBtu @ %O2 9368 9595 9602 9,521.667

Fw 10640 10640 10640 10,640.000

Fc 1744 1781 1771 1,765.333

Location NV 2324 Unit 1 - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Saturday, February 26, 2011 Page 5 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location NV 2324 Unit 1 - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 6 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Saturday, February 26, 2011 Page 7 of 19
NV 2324 Reid Gardner Unit 1

Emissions Summary

Location: NV 2324 Unit 1 - Method 10

Compound: Carbon Monoxide

Average

Run M10-1 M10-2 M10-3

lb/mmBtuO2 2.66E-02 9.07E-02 3.88E-02 0.052

ppm 2.30E+01 7.94E+01 3.38E+01 45.400

ppm@7%O2 2.54E+01 8.68E+01 3.68E+01 49.667

Location: NV 2324 Unit 1 - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run M25A-1 M25A-2 M25A-3

lb/mmBtuO2 1.64E-03 2.95E-03 3.50E-03 0.003

ppm 9.00E-01 1.64E+00 1.94E+00 1.493

ppm@7%O2 9.94E-01 1.79E+00 2.11E+00 1.631

Location: NV 2324 Unit 1 - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 5.962 5.199 6.3 5.820

lb/mmBtuO2 5.45E-03 5.42E-03 6.27E-03 0.006

Compound: Hydrogen Fluoride

Average

RunNumber M26A-1 M26A-2 M26A-3

Mass_mg 0.528 0.53 0.551 0.536

lb/mmBtuO2 4.82E-04 5.53E-04 5.48E-04 0.001

Location: NV 2324 Unit 1 - Method 29

Compound: Antimony

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.000027 0.000063 0.000026 0.000

lb/mmBtuO2 6.81E-09 1.55E-08 7.05E-09 0.000

Compound: Arsenic

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00015 0.00015 0.000172 0.000

lb/mmBtuO2 3.78E-08 3.70E-08 4.67E-08 0.000

Compound: Beryllium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.000024 0.000024 0.000024 0.000

lb/mmBtuO2 6.06E-09 5.92E-09 6.51E-09 0.000

Saturday, February 26, 2011 Page 8 of 19
NV 2324 Reid Gardner Unit 1

Compound: Cadmium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.000093 0.000079 0.000061 0.000

lb/mmBtuO2 2.35E-08 1.95E-08 1.65E-08 0.000

Compound: Chromium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00115 0.0009 0.00117 0.001

lb/mmBtuO2 2.90E-07 2.22E-07 3.17E-07 0.000

Compound: Cobalt

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00033 0.01231 0.000105 0.004

lb/mmBtuO2 8.33E-08 3.04E-06 2.85E-08 0.000

Compound: Filterable Particulate

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 10.02 3.17 9.08 7.423

lb/mmBtuO2 2.53E-03 7.82E-04 2.46E-03 0.002

Compound: Lead

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.0002799 0.00043 0.0003499 0.000

lb/mmBtuO2 7.06E-08 1.06E-07 9.49E-08 0.000

Compound: Manganese

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00093 0.00117 0.00093 0.001

lb/mmBtuO2 2.35E-07 2.89E-07 2.52E-07 0.000

Compound: Nickel

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00212 0.00155 0.00101 0.002

lb/mmBtuO2 5.35E-07 3.83E-07 2.74E-07 0.000

Compound: Selenium

Average

RunNumber M29-1 M29-2 M29-3

Mass_mg 0.00078 0.00066 0.00065 0.001

lb/mmBtuO2 1.97E-07 1.63E-07 1.76E-07 0.000

Location: NV 2324 Unit 1 - Method 6C

Compound: Sulfur Dioxide

Average

Run M6C-1 M6C-2 M6C-3

lb/mmBtuO2 1.06E-01 3.82E-02 4.19E-02 0.062

Saturday, February 26, 2011 Page 9 of 19
NV 2324 Reid Gardner Unit 1

Process Run Data

ppm 4.02E+01 1.46E+01 1.60E+01 23.600

ppm@7%O2 4.44E+01 1.60E+01 1.74E+01 25.933

Location: NV 2324 Unit 1 - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run M7E-1 M7E-2 M7E-3

lb/mmBtuO2 3.37E-01 3.17E-01 3.20E-01 0.325

ppm 1.77E+02 1.69E+02 1.70E+02 172.000

ppm@7%O2 1.95E+02 1.85E+02 1.85E+02 188.333

Location: NV 2324 Unit 1 - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 4.25 3.85 3.3 3.800

lb/mmBtuO2 1.13E-03 1.01E-03 9.56E-04 0.001

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 6.21 9.24 7.5 7.650

lb/mmBtuO2 1.65E-03 2.44E-03 2.17E-03 0.002

Compound: Organic Condensible Particulate

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 2.13 0.63 0.8 1.187

lb/mmBtuO2 5.64E-04 1.66E-04 2.32E-04 0.000

Compound: Total PM2.5

Average

RunNumber OTM27-1 OTM27-2 OTM27-3

Mass_mg 12.59 13.72 11.6 12.637

lb/mmBtuO2 3.34E-03 3.62E-03 3.36E-03 0.003

Saturday, February 26, 2011 Page 10 of 19
NV 2324 Reid Gardner Unit 1

Process Run Data

APCD Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 884.8 5-5-10 07:00 - 

10:00

0

1 Unit Load 99.7 MW 0

1 Steam Rate 633.1 1000 lbs/hr 0

1 Fuel Input Rate 78.817 1000 lbs/hr 0

2 Heat Input Million Btus/million BTU using O2 926.3 05-05-10 10:00 - 

13:00

0

2 Unit Load 99.9 MW 0

2 Steam Rate 646.8 1000 lbs/hr 0

2 Fuel Input Rate 82.33 1000 lbs/hr 0

3 Heat Input Million Btus/million BTU using O2 941.6 5-5-10 13:00 - 

16:00

0

3 Unit Load 100.1 MW 0

3 Steam Rate 649.6 1000 lbs/hr 0

3 Fuel Input Rate 80.65 1000 lbs/hr 0

4 Heat Input Million Btus/million BTU using O2 953.5 0 5-6-10 07:00-14:00

4 Unit Load 99 MW 0

4 Steam Rate 632.9 1000 lbs/hr 0

4 Fuel Input Rate 81.1 1000 lbs/hr 0

5 Heat Input Million Btus/million BTU using O2 1002.3 05-07-10 07:00-

14:00

0

5 Unit Load 104.6 MW 0

5 Steam Rate 674.8 1000 lbs/hr 0

5 Fuel Input Rate 84.58 1000 lbs/hr 0

6 Heat Input Million Btus/million BTU using O2 945.5 05-08-10 07:00 - 

14:00

0

6 Unit Load 98.7 MW 0

6 Steam Rate 635.8 1000 lbs/hr 0

6 Fuel Input Rate 78.33 1000 lbs/hr 0

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 0 0

2 LOW NOX BURNERS 0 0

3 LOW NOX BURNERS 0 0

Saturday, February 26, 2011 Page 11 of 19
NV 2324 Reid Gardner Unit 1

Process Lab Run Data

4 LOW NOX BURNERS 0 0

1 OVERFIRE AIR 0 0

2 OVERFIRE AIR 0 0

3 OVERFIRE AIR 0 0

4 OVERFIRE AIR 0 0

1 FABRIC FILTER 6.43 in. H2O 0

2 FABRIC FILTER 6.44 in. H2O 0

3 FABRIC FILTER 6.25 in. H2O 0

4 FABRIC FILTER 6.31 in. H2O 0

1 VENTURI SCRUBBER 0.89 in. H2O 0

2 VENTURI SCRUBBER 1.03 in. H2O 0

3 VENTURI SCRUBBER 0.84 in. H2O 0

4 VENTURI SCRUBBER 0.95 in. H2O 0

Saturday, February 26, 2011 Page 12 of 19
NV 2324 Reid Gardner Unit 1

Sampling / Stack Data Results Detail

Location NV 2324 Unit 1 - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 13 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 14 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 26A

Average

Run Number M26A-1 M26A-2 M26A-3

Test Date 5/6/2010 5/6/2010 5/8/2010

Run Start Time 7:20:00 AM 1:41:00 PM 8:11:00 AM

Run Finish Time 9:57:01 AM 2:51:01 PM 9:26:00 AM

Net Traversing Points 24 24 24

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.234 0.23 0.234 0.233

Pitot Tube Coefficient 0.8083 0.801 0.8083 0.806

Dry Gas Meter Calibration Factor 0.977 0.994 0.977 0.983

Barometric Pressure, inches of Mercury 28.28 28.23 28.08 28.197

Average Orifice Meter Differential, inches H2O 1.37 1.23 1.11 1.237

Dry Gas Meter Volume Sampled, cubic feet 41.854 39.158 36.557 39.190

Average Dry Gas Meter Temperature, °F 65.29 88.58 64.96 72.943

Dry Gas Meter Volume Sampled, dscf 38.988 35.460 33.812 36.087

Total Moisture Liquid collected, g 113.1 102.9 100.6 105.533

Volume of Water Vapor, standard cubic feet 5.32 4.84 4.74 4.967

Moisture Content of Stack Gas, % 12.01 12.01 12.30 12.107

Moisture Saturation at Stack Gas Temperature, % 18.37 19.22 18.88 18.823

Dry Mole Fraction 0.8799 0.8799 0.877 0.879

Carbon Dioxide, % 10.89 10.71 11.76 11.120

Oxygen, % 8.78 8.95 7.75 8.493

Carbon Monoxide & Nitrogen, % 80.33 80.34 80.49 80.387

Fuel Factor 1.11 1.12 1.12

Dry Molecular Weight, lb/lb-Mole 30.09 30.07 30.19 30.117

Wet Molecular weight, lb/lb-Mole 28.64 28.62 28.69 28.650

Flue Gas Static Pressure, inches of H2O -0.25 -0.23 -0.25 -0.243

Absolute Flue Gas Pressure, inches of Mercury 28.26 28.21 28.06 28.177

Average Stack Gas Temperature, °F 135.25 136.92 136.04 136.070

Average Velocity Head, inches of H2O 0.5780226737

58838

0.574247692

583764

0.557529066

970306

0.570

Average Stack Gas Velocity, feet/second 45.05 44.62 44.40 44.690

Stack Cross-Sectional Area, square feet 141.658 141.658 141.658 141.658

Dry Volumetric Flow Rate, dry scfm 282,270.5 278,300.8 274,953.7 278,508.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 382,901.6 379,246.8 377,376.9 379,841.767

Percent Isokinetic of Sampling Rate, % 109.2 104.3 97.2 103.567

Percent Excess Air, % 70.7 73.0 57.4 67.033

F-Factor, dscfm/MMBtu @ %O2 9368 9595 9602 9,521.667

Round Duct Diameter, inches 161.16 161.16 161.16

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1744 1781 1771 1,765.333

Saturday, February 26, 2011 Page 15 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, February 26, 2011 Page 16 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 17 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 18 of 19
NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, February 26, 2011 Page 19 of 19