### Name: Chris Heintz

Title: Environmental Scientist Company: Nevada Energy Sign Date: Name: Kevin Donahoe Title: Project Manager Company: The Avogadro Group Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date 

## NV 2324 Reid Gardner Unit 1 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Saturday, February 26, 2011 Page 1 of 19

### NV 2324 Reid Gardner Unit 1

Facility Information:
NV 2324 Reid Gardner Unit 1 501 Wally Kay Way

Moapa NV 89025 Contact: Chris Heintz
Phone: 702-402-2048
Fax:
Email: Testing Company: The Avogadro Group
2825 Verne Roberts Circle

Antioch CA 94509 Contact: Kevin M. Donahoe
Phone: 877-602-1023
Fax:
Email: kdonahoe@avogadrogroup.com

Air Permit Number: 2324 Permitted Source ID/Name: Reid Gardner Station 1
Permitted Maximum Process Rate: 111 Mwe Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Pulverized Coal: Dry Bottom (Bituminous Coal)

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
NV 2324 Unit 1 161.16 0 0 4 0 24 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 120 0 NV 2324 Unit 1 Total organic compounds

(TOC) as Propane Method 25A 3 120 0 NV 2324 Unit 1 Hydrogen Chloride Method 26A 3 60 0 NV 2324 Unit 1



### Saturday, February 26, 2011 Page 2 of 19

### NV 2324 Reid Gardner Unit 1

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

Hydrogen Fluoride Method 26A 3 60 0 NV 2324 Unit 1 Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 380 0 NV 2324 Unit 1 Filterable PM2.5 OTM - 27/28 3 380 0 NV 2324 Unit 1 Total PM2.5 OTM - 27/28 3 380 0 NV 2324 Unit 1 Organic Condensible

Particulate OTM - 27/28 3 380 0 NV 2324 Unit 1 Nickel Method 29 3 240 0 NV 2324 Unit 1 Cadmium Method 29 3 240 0 NV 2324 Unit 1 Manganese Method 29 3 240 0 NV 2324 Unit 1 Lead Method 29 3 240 0 NV 2324 Unit 1 Antimony Method 29 3 240 0 NV 2324 Unit 1 Filterable Particulate Method 29 3 240 0 NV 2324 Unit 1 Arsenic Method 29 3 240 0 NV 2324 Unit 1 Cobalt Method 29 3 240 0 NV 2324 Unit 1 Chromium Method 29 3 240 0 NV 2324 Unit 1 Beryllium Method 29 3 240 0 NV 2324 Unit 1 Selenium Method 29 3 240 0 NV 2324 Unit 1 Sulfur Dioxide Method 6C 3 120 0 NV 2324 Unit 1 Nitrogen oxides (NOx) Method 7E 3 120 0 NV 2324 Unit 1



### Saturday, February 26, 2011 Page 3 of 19

### NV 2324 Reid Gardner Unit 1

Sampling / Stack Data Results Summary



### Location NV 2324 Unit 1 - Method 10 Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location NV 2324 Unit 1 - Method 25A Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Saturday, February 26, 2011 Page 4 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 26A Average Run Number M26A-1 M26A-2 M26A-3
Test Date 5/6/2010 5/6/2010 5/8/2010
Run Start Time 7:20:00 AM 1:41:00 PM 8:11:00 AM
Run Finish Time 9:57:01 AM 2:51:01 PM 9:26:00 AM Net Run Time, minutes 60 60 60 Dry Gas Meter Volume Sampled, dscf 38.988 35.460 33.812 36.087 Moisture Content of Stack Gas, % 12.01 12.01 12.30 12.107 Moisture Saturation at Stack Gas Temperature, % 18.37 19.22 18.88 18.823 Carbon Dioxide, % 10.89 10.71 11.76 11.120 Oxygen, % 8.78 8.95 7.75 8.493 Average Stack Gas Temperature, °F 135.25 136.92 136.04 136.070 Dry Volumetric Flow Rate, dry scfm 282,270.5 278,300.8 274,953.7 278,508.333 Actual Wet Volumetric Flue Gas Flow Rate, acfm 382,901.6 379,246.8 377,376.9 379,841.767 Percent Isokinetic of Sampling Rate, % 109.2 104.3 97.2 103.567 F-Factor, dscfm/MMBtu @ %O2 9368 9595 9602 9,521.667
Fw 10640 10640 10640 10,640.000
Fc 1744 1781 1771 1,765.333



### Location NV 2324 Unit 1 - Method 29 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Saturday, February 26, 2011 Page 5 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 6C Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location NV 2324 Unit 1 - Method 7E Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Saturday, February 26, 2011 Page 6 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - OTM - 27/28 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Saturday, February 26, 2011 Page 7 of 19

### NV 2324 Reid Gardner Unit 1

Emissions Summary



### Location: NV 2324 Unit 1 - Method 10 Compound: Carbon Monoxide Average Run M10-1 M10-2 M10-3 lb/mmBtuO2 2.66E-02 9.07E-02 3.88E-02 0.052 ppm 2.30E+01 7.94E+01 3.38E+01 45.400 ppm@7%O2 2.54E+01 8.68E+01 3.68E+01 49.667



### Location: NV 2324 Unit 1 - Method 25A Compound: Total organic compounds (TOC) as Average Run M25A-1 M25A-2 M25A-3 lb/mmBtuO2 1.64E-03 2.95E-03 3.50E-03 0.003 ppm 9.00E-01 1.64E+00 1.94E+00 1.493 ppm@7%O2 9.94E-01 1.79E+00 2.11E+00 1.631



### Location: NV 2324 Unit 1 - Method 26A Compound: Hydrogen Chloride Average RunNumber M26A-1 M26A-2 M26A-3 Mass_mg 5.962 5.199 6.3 5.820 lb/mmBtuO2 5.45E-03 5.42E-03 6.27E-03 0.006


### Compound: Hydrogen Fluoride Average RunNumber M26A-1 M26A-2 M26A-3 Mass_mg 0.528 0.53 0.551 0.536 lb/mmBtuO2 4.82E-04 5.53E-04 5.48E-04 0.001



### Location: NV 2324 Unit 1 - Method 29 Compound: Antimony Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.000027 0.000063 0.000026 0.000 lb/mmBtuO2 6.81E-09 1.55E-08 7.05E-09 0.000


### Compound: Arsenic Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00015 0.00015 0.000172 0.000 lb/mmBtuO2 3.78E-08 3.70E-08 4.67E-08 0.000


### Compound: Beryllium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.000024 0.000024 0.000024 0.000 lb/mmBtuO2 6.06E-09 5.92E-09 6.51E-09 0.000



### Saturday, February 26, 2011 Page 8 of 19

### NV 2324 Reid Gardner Unit 1

Compound: Cadmium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.000093 0.000079 0.000061 0.000 lb/mmBtuO2 2.35E-08 1.95E-08 1.65E-08 0.000


### Compound: Chromium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00115 0.0009 0.00117 0.001 lb/mmBtuO2 2.90E-07 2.22E-07 3.17E-07 0.000


### Compound: Cobalt Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00033 0.01231 0.000105 0.004 lb/mmBtuO2 8.33E-08 3.04E-06 2.85E-08 0.000


### Compound: Filterable Particulate Average RunNumber M29-1 M29-2 M29-3 Mass_mg 10.02 3.17 9.08 7.423 lb/mmBtuO2 2.53E-03 7.82E-04 2.46E-03 0.002


### Compound: Lead Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.0002799 0.00043 0.0003499 0.000 lb/mmBtuO2 7.06E-08 1.06E-07 9.49E-08 0.000


### Compound: Manganese Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00093 0.00117 0.00093 0.001 lb/mmBtuO2 2.35E-07 2.89E-07 2.52E-07 0.000


### Compound: Nickel Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00212 0.00155 0.00101 0.002 lb/mmBtuO2 5.35E-07 3.83E-07 2.74E-07 0.000


### Compound: Selenium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00078 0.00066 0.00065 0.001 lb/mmBtuO2 1.97E-07 1.63E-07 1.76E-07 0.000



### Location: NV 2324 Unit 1 - Method 6C 

### Compound: Sulfur Dioxide Average Run M6C-1 M6C-2 M6C-3 lb/mmBtuO2 1.06E-01 3.82E-02 4.19E-02 0.062


### Saturday, February 26, 2011 Page 9 of 19

### NV 2324 Reid Gardner Unit 1

Process Run Data ppm 4.02E+01 1.46E+01 1.60E+01 23.600 ppm@7%O2 4.44E+01 1.60E+01 1.74E+01 25.933



### Location: NV 2324 Unit 1 - Method 7E Compound: Nitrogen oxides (NOx) Average Run M7E-1 M7E-2 M7E-3 lb/mmBtuO2 3.37E-01 3.17E-01 3.20E-01 0.325 ppm 1.77E+02 1.69E+02 1.70E+02 172.000 ppm@7%O2 1.95E+02 1.85E+02 1.85E+02 188.333



### Location: NV 2324 Unit 1 - OTM - 27/28 Compound: Filterable PM2.5 Average RunNumber OTM27-1 OTM27-2 OTM27-3 Mass_mg 4.25 3.85 3.3 3.800 lb/mmBtuO2 1.13E-03 1.01E-03 9.56E-04 0.001


### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber OTM27-1 OTM27-2 OTM27-3 Mass_mg 6.21 9.24 7.5 7.650 lb/mmBtuO2 1.65E-03 2.44E-03 2.17E-03 0.002


### Compound: Organic Condensible Particulate Average RunNumber OTM27-1 OTM27-2 OTM27-3 Mass_mg 2.13 0.63 0.8 1.187 lb/mmBtuO2 5.64E-04 1.66E-04 2.32E-04 0.000


### Compound: Total PM2.5 Average RunNumber OTM27-1 OTM27-2 OTM27-3 Mass_mg 12.59 13.72 11.6 12.637 lb/mmBtuO2 3.34E-03 3.62E-03 3.36E-03 0.003



### Saturday, February 26, 2011 Page 10 of 19

### NV 2324 Reid Gardner Unit 1

Process Run Data

APCD Run Data 

### Run Name Value UOM Comments Target Value 1 Heat Input 884.8 Million Btus/million BTU using O2 5-5-10 07:00 - 10:00 0



### 1 Unit Load 99.7 MW 0
1 Steam Rate 633.1 1000 lbs/hr 0


### 1 Fuel Input Rate 78.817 1000 lbs/hr 0
2 Heat Input 926.3 Million Btus/million BTU using O2 05-05-10 10:00 - 13:00 0

2 Unit Load 99.9 MW 0


### 2 Steam Rate 646.8 1000 lbs/hr 0
2 Fuel Input Rate 82.33 1000 lbs/hr 0
3 Heat Input 941.6 Million Btus/million BTU using O2 5-5-10 13:00 - 16:00 0

3 Unit Load 100.1 MW 0
3 Steam Rate 649.6 1000 lbs/hr 0


### 3 Fuel Input Rate 80.65 1000 lbs/hr 0
4 Heat Input 953.5 Million Btus/million BTU using O2 5-6-10 07:00-14:00 0
4 Unit Load 99 MW 0


### 4 Steam Rate 632.9 1000 lbs/hr 0
4 Fuel Input Rate 81.1 1000 lbs/hr 0
5 Heat Input 1002.3 Million Btus/million BTU using O2 05-07-10 07:00- 14:00 0



### 5 Unit Load 104.6 MW 0
5 Steam Rate 674.8 1000 lbs/hr 0


### 5 Fuel Input Rate 84.58 1000 lbs/hr 0
6 Heat Input 945.5 Million Btus/million BTU using O2 05-08-10 07:00 - 14:00 0

6 Unit Load 98.7 MW 0


### 6 Steam Rate 635.8 1000 lbs/hr 0
6 Fuel Input Rate 78.33 1000 lbs/hr 0

Run Name Value UOM Comments Target Value 

### 1 LOW NOX BURNERS 0 0
2 LOW NOX BURNERS 0 0
3 LOW NOX BURNERS 0 0



### Saturday, February 26, 2011 Page 11 of 19

### NV 2324 Reid Gardner Unit 1

Process Lab Run Data 4 LOW NOX BURNERS 0 0


### 1 OVERFIRE AIR 0 0
2 OVERFIRE AIR 0 0
3 OVERFIRE AIR 0 0


### 4 OVERFIRE AIR 0 0
1 FABRIC FILTER 6.43 in. H2O 0
2 FABRIC FILTER 6.44 in. H2O 0


### 3 FABRIC FILTER 6.25 in. H2O 0
4 FABRIC FILTER 6.31 in. H2O 0
1 VENTURI SCRUBBER 0.89 in. H2O 0


### 2 VENTURI SCRUBBER 1.03 in. H2O 0
3 VENTURI SCRUBBER 0.84 in. H2O 0
4 VENTURI SCRUBBER 0.95 in. H2O 0



### Saturday, February 26, 2011 Page 12 of 19

### NV 2324 Reid Gardner Unit 1

Sampling / Stack Data Results Detail



### Location NV 2324 Unit 1 - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Saturday, February 26, 2011 Page 13 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Saturday, February 26, 2011 Page 14 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 26A Average Run Number M26A-1 M26A-2 M26A-3 Test Date 5/6/2010 5/6/2010 5/8/2010 Run Start Time 7:20:00 AM 1:41:00 PM 8:11:00 AM Run Finish Time 9:57:01 AM 2:51:01 PM 9:26:00 AM Net Traversing Points 24 24 24 Net Run Time, minutes 60 60 60 Nozzle Diameter, inches 0.234 0.23 0.234 0.233 Pitot Tube Coefficient 0.8083 0.801 0.8083 0.806 Dry Gas Meter Calibration Factor 0.977 0.994 0.977 0.983 Barometric Pressure, inches of Mercury 28.28 28.23 28.08 28.197 Average Orifice Meter Differential, inches H2O 1.37 1.23 1.11 1.237 Dry Gas Meter Volume Sampled, cubic feet 41.854 39.158 36.557 39.190 Average Dry Gas Meter Temperature, °F 65.29 88.58 64.96 72.943 Dry Gas Meter Volume Sampled, dscf 38.988 35.460 33.812 36.087 Total Moisture Liquid collected, g 113.1 102.9 100.6 105.533 Volume of Water Vapor, standard cubic feet 5.32 4.84 4.74 4.967 Moisture Content of Stack Gas, % 12.01 12.01 12.30 12.107 Moisture Saturation at Stack Gas Temperature, % 18.37 19.22 18.88 18.823 Dry Mole Fraction 0.8799 0.8799 0.877 0.879 Carbon Dioxide, % 10.89 10.71 11.76 11.120 Oxygen, % 8.78 8.95 7.75 8.493 Carbon Monoxide & Nitrogen, % 80.33 80.34 80.49 80.387 Fuel Factor 1.11 1.12 1.12 Dry Molecular Weight, lb/lb-Mole 30.09 30.07 30.19 30.117 Wet Molecular weight, lb/lb-Mole 28.64 28.62 28.69 28.650 Flue Gas Static Pressure, inches of H2O -0.25 -0.23 -0.25 -0.243 Absolute Flue Gas Pressure, inches of Mercury 28.26 28.21 28.06 28.177 Average Stack Gas Temperature, °F 135.25 136.92 136.04 136.070 Average Velocity Head, inches of H2O 0.5780226737 58838 0.574247692

583764 0.557529066

970306 0.570

Average Stack Gas Velocity, feet/second 45.05 44.62 44.40 44.690 Stack Cross-Sectional Area, square feet 141.658 141.658 141.658 141.658 Dry Volumetric Flow Rate, dry scfm 282,270.5 278,300.8 274,953.7 278,508.333 Actual Wet Volumetric Flue Gas Flow Rate, acfm 382,901.6 379,246.8 377,376.9 379,841.767 Percent Isokinetic of Sampling Rate, % 109.2 104.3 97.2 103.567 Percent Excess Air, % 70.7 73.0 57.4 67.033 F-Factor, dscfm/MMBtu @ %O2 9368 9595 9602 9,521.667 Round Duct Diameter, inches 161.16 161.16 161.16 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10640 10640 10640 10,640.000 Fc 1744 1781 1771 1,765.333



### Saturday, February 26, 2011 Page 15 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Saturday, February 26, 2011 Page 16 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Saturday, February 26, 2011 Page 17 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Saturday, February 26, 2011 Page 18 of 19

### NV 2324 Reid Gardner Unit 1

Location NV 2324 Unit 1 - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Saturday, February 26, 2011 Page 19 of 19