JANUARY 2002 ISR DIRECTORY

-COMMERCIAL BOILERS

Boiler Fuel Boiler Nameplate Input Gas Oil I=B=R Net I=B=R Gross Comb. Output Effie Stea Rating

m Steam Vent

Water Size Manufacturer AXEMAN TypslSaries

STEEL Typo Model MBE gph MBh % Sq

.Ft. MBh MBh (Oil) Notes
ANDERSON COMPANY

BUDERUS PO-2 Seres

CAST IRON Light Oil 189PO 2.4 277 82

.7 867 208 241 8012x15 The above ratings are based on 12

.0%C02 and -0

.02 in. tealerdratt.

HYORONIC SYSTEMS G215 sense Light Oil G215-7 2,5 294 867 2568,12,15 I The above rabegs are based an 13

.0% C02 and-0

.005 draft at the vent.

11 G334X Series Inter Ign , Natural or propene G334 -73 301 240 827 217 03340-92 378 314 83.1 273 G334-116 476 396 83.2 344 G334X-132 541 450 012 391 315 Series Power Burner, Natural Gas G315-5 433 350 84.2 304 8,12x15 G315-6 556 454 84.3 395 12x12.15 G315-7 678 559 84.4 466 12,12x15 G310.6 801 663 84

.4 57712,16x15 G3t5.9 924 768 84

.5 668 12,16x15 The above ratings are based ad 10.0% C02 ie -0

.02 dell at the vent. Light Oil G3153 3 350 86.8 304 8,12x15 G319.6 3

.85 454 86

.9 39512,12x15 G315.7 4.7 559 87 486 12x12'15 0315-8 5.6 663 87.1 57712,16x15 0315-9 6

.4 768 87.1 66812x16'15 The above ratings are based an 13

.0% C02 and .0

.02 draft at the vent. 515 Series Light Oil G515-7 6.9 818 88.2 71112x16015 G515-8 8

.4 1009 88

.2 8]] 16,16x15 G515-9 10 1201 86.1 1044 16,16x15 G515-10 11

.6 1392 88.1 121016,20x15 G515-11 13 1563 88.1 1377 16x20,15 G515-12 14

.6 1775 88.1 1543 16,20x15 The above ratings are based on 13.0% C02 and -0.02 draftat the went. Power 8umer, Natural Gas 0515-7 995 818 85.6 711 12,16x15 G515-8 1216 1009 65.5 877 16,16x15 0515-9 1438 1201 e5
.5 1044 16,16x15 G515-10 1660 1392 85.5 1210 16,20x15 0515-11 1881 1583 85 4 137716X2 x1l G515-12 2103 1775 854 154316,20x15 The above ralmgs are based en 10.0% C02. G615 Series Power Burner, Natural Gas G615-9 2309 1951 84
.1 1697 14 G615-10 2670 2242 84,1 1950 14 G615-11 3031 2532 84 2202 14 G615-12 3392 2822 84 2454 16 G615-13 3753 3112 83
.9 2706 16 G615-14 4113 3402 83.9 2958 18 G615-15 4474 3692 83
.9 3210 18 G615-16 4835 3982 83

.9 3463 18 The above ratings am based on 10

.0% C02 and +0.10" at the vent. Light Oil G615-9 16 1951 86.7 1697 14 G615-10 18
.5 2242 86
.7 1950 14 G615-11 21 2532 86
.6 2202 14 G615-12 23.5 2822 86
.6 2454 16 G615-13 26 3112 86
.5 2706 16 G615-14 28

.5 3402 86

.5 2958 18 G615-15 31 3692 86
.5 3210 18

8URNHAM CAST IRON G615-16 33

.5 3982 86

.5 3463 18 The above ratings are based on 130% C02 and +0.10" at the vent.

CORPORATION It Independence Series Nalual Gas N10 315 259.87 83.5 226 Ntt 349 287.92 836 250 N 12 385 317.62 83.5 276 N10 315 259.87 82.5 812 i95 N11 349 28792 82.5 900 216 612 385 31762 82.5 996 239 S Races 8 Natural or Propane 06 330 264 80 230 07 396 316 8 00 275 06 462 309 6 60 32^. 09 528 4224 60 367 10 594 4752 60 413 Also approved with Suffi. I & ID. Senas 5 Natural Gas 5006 401 320.8 60 1004 241 279 5007 468 374 4 60 1171 281 326 5008 546 436.8 80 1367 328 380 5009 624 499.2 80 1558 374 434 5010 702 561 6 80 1754 421 488 5011 780 62.1 80 1950 408 543 5012 858 MA 80 2146 515 597 5013 936 748.8 80 2:412 562 651 5014 1014 8112 80 2538 " 009 705 5015 '092 873.6 80 2720 615 7.JANUARY 2002 ISR DIRECTORY . COMMERCIAL BOILERS

Boiler Fuel Boiler Nameplate Input Gas Oil 1=B=R Net I=B= Gross Comb. Output Elf.. SteR Rating

am Steam Vent Water Size Manufacturer TypelSeries Type Model MBh gph MBE % Sq.Ft. MBh MBh (Oil) Notes 5016 5017 1170

1248 936 998.4 80

80 2925

1121, 702

749 814

868 5018 1326 1060.8 80 3317 796 922 5019 1404 1123.2 80 3513 843 977 5020 1482 1185.6 30 3704 889 1031 5021 15000 1248 30 3900 936 1085 5022 1638 13104 80 4113 987 1139 5024 1794 1435.2 80 4546 1091 1248 5026 1950 1560 80 4975 1194 1357 O Series 5 Propane 5006 375.9375 30075 80 942 226 262 5007 438.75 351 80 1096 263 305 5008 511.875 409.5 80 1279 307 356 5009 585 468 80 1463 351 407 5010 658.125 526.5 80 1646 395 458 5011 731.25 585 80 1829 439 509 5012 804.375 643 5 80 2013 483 560 5013 11 877.5 702 80 2196 527 610 10 4 950 760 5 80 2379 571 661 5015 1023.75 819 80 2558 614 712 5016 1096.875 877.5 80 2742 658 763 5017 1170 936 80 2925 702 814 5018 1243.125 994.5 80 3106 746 865 5019 131625 1053 80 3292 790 916 5020 1389375 1111.5 80 3475 834 967 5021 1462.5 1170 80 3658 8]8 1017 5022 1535 625 1228.5 80 3842 922 1068 5024 1681.875 1345.5 80 4233 1016 1170 5026 1828 125 1462.5 80 4642 1114 1272 The above ratings are also approved far bailers with the Prefix K, P, PH. and SuffixW. S, I, M. V8 Seres LightOil V8 8W 2.35 275 84,2 239 8,12015 589W 2

.6 299 84.1 2608,12x15 V885 2.35 266 84.2 833 200 8,12015 V89S 2.6 298 841 933 224 8012015 The above ratings are based on 13.0% C02 and .0,02' water draftovertire. V9A Sees Netual Gas, Forced Draft V903 447 346 82

.6 1083 260 301 7"Venl V904 606 483 83.4 1508 362 420 7"Vent V905 808 646 82.9 2021 485 562 8"Vent V906 1010 808 82.7 2525 606 703 8"Venl 907 1198 959 82.5 2996 719 e 3M8 It V908 1386 1110 82.4 3471 833 965 10"Vent V909 1674 1342 82.3 4225 1014 1167 1056e11 V910 1905 1528 82.2 4867 1168 1329 10" Vent V911 2136 1714 82.2 5513 1323 1490 12"Vent V912 2367 190D 82.1 6142 1474 1652 12"Vent The above ratings are based on 9.7% CO2 and 0010 in water daft at the vent. Light 04, Forced Draft V903 31 346 85

.2 1083 260 301 1"V, 1 V904 4,2 483 86 1508 362 420 7" Vent V905 5.6 646 85.5 2021 485 5628"Vent V906 7 808 85.2 2525 606 703 8" Vent V907 8.3 959 85.1 2996 719 834 8" Vent V908 9

.6 1110 04.9 3471 833 965 10- Vent V909 ITS 1342 84

.8 4225 1014 116710" Vent 910 13.2 1528 84.8 4667 1168 1329 10" Vont 8911 148 1714 84

.7 5513 1323 149012" Vent 6912 16.4 1900 84.7 6142 1474 1652 12" Vent The above ratings are based on 12

.5% C02 and +0.10 in, water draft at the vent.
V11 Sanes Nalurl Gas, Forced Draft V1104 837 667 82.8 2083 500 580 8"Vent V1105 1068 857 82.6 2679 643 745 856ent V1106 1328 1069 82.5 3342 802 930 856ent V1107 1588 1281 82.4 4013 963 1114 10"Vent 1108 1876 1517 82.3 4829 1159 1319 10"Vent 1109 2136 1729 82.3 5563 1335 1503 10'Vent 1110 2396 1941 822 6279 1507 1688 12"Vent 1111 2656 2154 82,2 6967 1672 1873 12-Vent V1112 2887 2334 82.1 7550 1612 2030 12"Vent 1113 3103 2503 82 6096 1943 2177 12"Venl V1114 3392 2730 81.9 8833 2120 2374 14" Vent 1115 3680 2957 81.8 9567 2296 2571 1456e11 1116 3897 3129 81.7 10113 2427 2718 14"Vent V1117 4186 3353 81
.7 10846 2603 2916 14" Vent V1118 4474 3560 81.6 11583 2780 3113 16"Vent V1119 4691 3739 81.4 12096 2903 3251 1656e111 V1120 4979 3957 61.2 12800 3072 3441 16JVent 1121 5266 4174 81 13501 3241 3630 6' ant V1122 5485 4334 80.8 14021 3365 1 3769 18"Vent V1123 5733 4551 80.7 14721 3533 3957 18"Vent The above ratings are based on 10.0% C02and +0.10.8

. wafer draft. V11 Series Light Oil, Forced Draft 11 04 5.8 667 85.3 2083 500 580 8"Vent 1105 7.4 857 85.1 2679 843 745 856e11 1106 9.2 1069 85 3342 802 930 856e11 11 07 11 1281 84.9 4013 963 1114 1056e11ANUARY 2002 OR DIRECTORY - COMMERCIAL BOILERS

Boiler Fuel Boiler Nameplate Input Gas Oil I=B=R Net I=B= Gross Comb. Output Ethic. SteR Rating

am Steam Vent Water Size Manufacturer Type/Series Type Model MBh gph MRS % Sq,FI. MBh Mah (Oil) Notes 1108 1109 13 14,8 1517

1729 84.9

84.8 4829

5563 1159

1335 1319 1070ent

150310' Veer 1110 16 6 1941 84.8 0279 1507 1688 12"Vent 1111 18 4 2154 84.8 6967 1672 1873 12"Vent 1112 20 2334 64.6 7550 1012 2030 12"Veel 1113 21
.5 2503 64.5 8096 1943 2177 17V in 1114 23.5 2730 84.4 8833 2120 2374 1491en1 1115 25.5 2957 84,3 9567 2296 2571 14 Vert 1116 27 3129 84.3 10113 2427 2718 14 lent 1117 29 3353 84.2 10846 2603 2916 14"Vent t 118 31 3580 64,1 11583 2780 3113 16"Vent 11l9 32.5 3739 83.9 12096 2903 3251 r6"Vent 1120 34.5 3957 83.7 12800 3072 3441 16'Vent 1121 36.5 4174 83,5 13504 3241 3630 i6" Vent 1122 38 4334 83.3 14021 3365 3769 18"Vent 1123 40 4551 83.2 14721 3533 3957 18"Venl The above ratings are based on 13

.0% C02 and +0

.10 in. water draft. STEEL Opus 01 Senes Light Oil 1-3-225 2.25 267 86.5 232 8.12015 The above ratings are based an 13.5% C02 and 0 in

. water at vent. RSA Series Light Oil 04240 2.4 268 84,2 233 8x12:20 SA285 2,85 318 83.2 277 ex12020 The above ratings are based on 12.5% C02 and -002 in. water draft. Senes E Light Oil, Forced Draft 20 6.1 684 83

.7 2138 513 59510"Voel 30 Si . 1043 64.2 3258 782 907 10" Vent 40 12 1402 84,8 4429 1063 1219 t0"Venl 50 15.2 1743 83,7 5613 1347 1516 t2"Vent 60 18,2 2102 84,1 6800 1632 1828 12"Vent 70 21 2461 84.6 7963 1911 2140 12"Vent 80 24 2821 851 9125 2190 2453 12"Vent The above ratings are based on 12.5% C02 and -1-10 in

. water at the vent. Natural Gas, Farted Droll 20 877 684 81.2 2138 513 595 10"Vent 30 1308 1043 81.7 3258 782 907 10Wont 40 1738 1402 823 4429 1063 1219 10"Venl 50 2207 1743 81.2 5613 1347 1516 12"Venl 60 2630 2102 81.6 6800 1632 1828 12"Venl 70 3053 2461 82,1 7963 1911 2140 12"Vent 80 3475 2821 82.6 9125 2190 2453 12"Vent The abeve ratings are based on 9,7% CO2 and +,10 in. water at the vent,

CROWN BOILER CAST IRON

U Jamaica If Inter Ign._ Natural Gas SE 10E 310 245 80 767 104 COMPANY SE 45E 345 273 80 864 205

' ' SE379E 379 209 80 933 24 2 Pilot, Natural Gas SE 310 245 80 767 184 SE 45S 345 273 80 854 205 0E3790 379 299 80 933 224 Freeport Tones Light Oil, Forced Draft TO 2.5 286 85.3 249 8x12015 The above ratings are based an 13.0°'GOS ..d .0.02 in. atTh. vent.
F Series Light Oil, Forced Draft 4 3 355 85 309 7"Vent 4 478 85 416 7"Vent 5 600 84,9 522 8"Vent 6 723 84,9 629 9"Vent 7.5 907 84

.8 7891070e01 9 9 1091 84.7 949 10"Vent The above ratings are based an 12.5% C02 and - 1 0 . 1 0 1 1 water draft atThe vent. Natural Gas, Forced Draft 4 433 355 82

.5 309 7"Vee1 5 577 478 82

.5 416 7" Vent 6 722 600 82
.4 522 8"Vent 7 866 723 82,4 629 970e11 8 082

1 907 82.3 789 10" Vent 9 1299 1091 822 949 10"Venl The above ratings are based an 9,7% C02 and +0,10 in. water craft aIThe vent.

O0DIETRICHI MACNA CAST IRON

GT210 Senes Natural Gas GT217A 323 258 84.3 2248 12.15 GT218A 359 287 84.3 250 8x12015 GT210A Light Oil GT217A 2 25 258 86,9 2248 12.15 GT218A 2,5 287 86.9 2508.12x15 The above ratings are based on 13

.0% C02 and -0

.02 at the vent GT300A Senes Natural Gas, Forced Draft GT304A 404 321 80,9 279 6" Vent GT305A 599 498 82.4 4337"Vent GT306A 810 662 63 576 9"Vent GT307A 1021 826 83.4 718 10" Vont GT308A 1232 990 83.6 861 10"V ent GT309A 1443 1154 83.7 1003 1 0" Vent The above ratings are based on 10.0% C02 and 0.01 In. water draft. Light Oil, Forced Draft GT304A 2.8 321 83.5 279 6" Vent IGT305A 4.15 498 85 433 7" VentJANUARY 2002 tSR DIRECTORY - COMMERCIAL BOILERS

Boiler Fuel Nameplate Input Boiler Gas Oil 1=B=R Net 1=B= Gross Comb, Output Elfin

. Stea R Rating

m Steam Vent

Water Sloe Manufacturer TypelSories Type Model MBh gph MBh % Sq,FI. MBh MBh (Oil( Notes GT306A 5.6 662 85

.6 576 9' Vent GT307A GT308A 7.1 8 5 826

990 85

.9

862 718 10' Venl 66 0" V GT309A . 10 1154 . 86.3 1 1 ent 100310' Vent The above ratings are based on 13,0%C02 and 0,01 In. water draft. GT400A Series Natural Gas

. Forced Draft GT408A 1732 1420 81.6 1235 12' Vent GT409A 2009 1658 82 1442 12" Vent GT410A 2285 1895 82.3 1648 14 Venl GT411A 2562 2133 82.5 1855 14' Vent GT412A 2836 2370 82.7 2061 14 Vent GT413A 3115 2608 82.9 2268 14 Vent GT414A 3392 2845 63 2474 16" Venn The above ratings are based on 10.0% C02 and 0.01 In. water droll. Light Oil. Forced Draft GT408A 12 1420 84,1 123512" Vent GT409A 14 1658 84,5 1442 12" Vent GT410A 15.8 1895 84,8 164814 Vent GT411A 17.8 2133 85,1 185514 Vent GT412A 19.0 2370 85.3 2061 14" Vent GT413A 21.5 2608 854 226814 Vent GT414A 23.5 2645 85.6 2474 16" Vent The shave ratings are based on 130% C02 and 0.01 In. water draft. GT500A Series Natural Gas, Forced Draft GT515A 3753 3153 83.1 2742 :V nt GT516A 3996 3348 83.1 1: 2911 Vent GT517A 4243 3544 83.1 3082 16' Venl GT518A 4489 3739 83.1 3251 16" Vent GT519A 4734 3935 83.1 3422 18 Vent GT520A 4979 4130 83 3591 18 Vent GT521A 5225 4326 83 3762 18" Vent GT522A 5470 4521 83 3931 18" Vent 5T5236 5715 4717 63 4102 18' Vont 5T524A 5961 4912 63 4271 18" Vent GT525A 6206 5108 83 4442 20" Vent The above ratings are based on 10.0%C02 and 001 In

.wale, draft. GT515ASeries Light Oil, Forced Draft GT515A 26 3153 85,7 2742 16" Vant 5T5166 27.5 3348 85.7 2911 1 6" Vent GT517A 29,5 3544 85.6 3082 16" Vent GT518A 31 3739 85.6 3251 16' Venl GT519A 33 3935 85.6 3422 18' Vent GT520A 34.5 4130 85.6 3591 18" Vent GT521A 36 4326 85.6 3762 18" Vent GT522A 38 4521 85.6 3931 18" Vent 5T5236 39.5 4717 85.6 410218" Vent 5T524A 41,5 4912 85.6 4271 18" Vent

DUNKIRK CAST IRON GT525A 43 5108 85.6 4442 20" Vent The above ratings are based on 13

.0% C02 and 0

.01 In, water daft.

BOILERS 1 Seres D247 Inter. gn. 80111181 Gas D247.300 300 240 80 750 180 209 Division of ECR D247.400 400 320 80 1000 240 278 International, Inc. 0247-500 500 400 80 1250 300 348 D247-600 600 480 80 1500 360 417 D247-700 700 560 80 1750 420 467 D247.000 800 040 80 2000 480 557 D247-900 900 720 80 2250 540 626 0247-1000 1000 800 80 2500 600 696 D247-1100 100 880 80 2750 660 765 D247-1200 1200 960 80 3000 120 835 D247-1300 1300 1040 80 3260 780 904 D247-1400 1400 1120 80 3500 840 974 D247-1500 1500 1200 80 3750 900 1043 D247-1600 1600 1280 80 4008 962 1113 D247-1700 1700 1360 80 4283 1028 1183 D247-1800 1800 1440 80 4563 1095 1252 0247-1900 1900 1520 80 4838 116' 1322 D247-2000 2000 1600 00 5117 1228 1391 D247-2100 2100 1680 80 5392 1294 1461 0247.2200 2200 1760 80 5671 1361 1530 0247-2300 2300 1840 80 5912 1426 1600 D247-2400 2400 1920 80 6213 1401 1670 0247-2500 2500 2000 80 6471 1553 1739 D247.2600 2600 2080 80 6729 1615 1809 02472700 2700 2166 80 6988 1677 1878 D247.2900 2800 2240 80 7246 1739 1948 D247.29OD 2900 2320 80 7504 1801 2017 D247-3000 3000 2400 80 7763 1863 2087 Al.. appavad it, sufbc 5 0, W. EV Series Forced Draft. Light Oil PFO-7-2.35 2,35 277 85.2 2417"0e01 PFO.9.3.00 3 354 85.2 308 e"Vent PFO-8T-2.75 2.75 325 85.2 283 8'Vent The above ratings are based on 12,5% C02 and +0.1 inch water over Ore

HYDROTHERM CAST IRONJANUARY 20021BR DIRECTORY - COMMERCIAL BOILERS

Boiler Fuel Boiler Nameplate Input Gas Oil 1=B=R Net 1=B=R Gross Comb. Output Effie. Stea Rating

m Steam Vent

Water Size Manufacturer Type/Series Type Model MBA gph MBA % Sq.Ft. MBh MBA (Oil) Nolen Division of Advanced Thermal N R-B Series Pant, Natural or Propane 0-3006 300 240 80 209 Hydrenico, Inc, Inter Ign , Nalural or Propane R-3008-P 300 240 80 209 Damper, Inter Ign , Nalural or R-30OB-PV 300 240 80 209 p MULTITEMP Series PllOt, Nalural Gas MR-3000 360 298 828 2.58 MR 420C 420 342 814 297 MR-5000 500 412 824 358 MR-6008 600 480 80 417 MR 750C 750 618 824 537 MR 900B 900 720 80 626 MR 10000 1000 824 824 717 MR 1200B 1200 000 80 835 MR 1500B 1500 1200 00 1043 MR 1800B 1800 1440 80 1252 MR 2100B 2100 1680 00 1461 00-24006 2400 1920 80 1675 Inter Ign., Natural Gus MR-360GP 360 298 828 258 MRa20C-P 420 342 61.4 297 MR -5000-P 500 412 62 4 358 MR -6008-P 600 480 80 417 MR-TOOT-P 750 618 82 4 537 1,1R-9008-P 900 720 80 626 01R -10000-F 1000 82.1 82.4 717 MR -12006-F 1200 960 80 035 MR-1500e-F 1500 1200 80 1043 MR-10006-F 1800 1440 30 1252 MR -21008-F 2100 1680 80 1461 MR-24006-F 2400 1920 80 1675 Damper, Inter Ign , Nalural Ge NIR-3600.P\ 300 298 828 258 MR 20C-P\ 420 342 814 297 MR-500C-P\ 500 412 824 358 MR 6003-P\ 600 480 80 417 MR-7500-P\ 750 618 82A 537 MR 900B-P\ 900 720 80 626 h1R-1000C-F 1000 824 824 717 MR -12008-F 1200 960 80 835 MR-150OB-F r500 1200 00 1043 MR-18008-F 1800 1440 80 1252 MR -'21008-F 2100 1600 00 1461 00-24006-1` 2400 1920 110 1675 MR60C 360 302 83.9 263 MR-420C 400 332 83 280 MR-5000 470 390 82.9 339 145-7500 705 585 82.8 500 MR-1000C 940 780 82.0 678 Inter. Ign . Prnpane MR-360C-P 360 302 839 263 010-0200-6 400 332 83 269 MR -5000-P 470 390 82.9 339 MR-750C-P 705 585 829 509 MR-10000-F 940 780 829 678 Damper, Inter Ign , Propane MR-360C-P\ 360 302 83 9 263 MR-4200 P\ 400 332 83 289 MR-500C P1 470 390 82.9 339 MR-7500-P\ 705 565 82.9 509 MR-10000-F 940 780 82.9 678
0 VGA-B Senes Pilot, Nalural Gas VGA-30085 300 240 00 750 180 000-35065 350 280 80 875 210 VGA-40OBS 400 320 80 1000 240 Inter Ign, Nalural Gas 000-30000. 300 240 60 750 180 VGA-35005' 350 200 60 875 210 VGA-40085. 400 320 80 :000 240 Damper. Infer. Ign.. Natural Ga VGA-30085. 300 240 80 750 180 VGA-3500S 350 260 80 875 210 VGA-40065. 400 320 80 1000 240 P.I.I. Propane I000-30065 300 240 00 750 180 00-35065 350 280 80 075 210 700-40065 360 288 80 900 216 Inter Ign, Propane GA-30085. 300 240 80 750 180 GA-35OBS. 350 280 80 875 210 'GA-400BS. 360 288 80 900 216JANUARY 20021BR DIRECTORY

- COMMERCIAL BOILERS

anufacturer Boiler

TypelSaris. Fuel Type Boiler

Model Nameplate

Input Gas MBA Oil

gph 1=B=R

Gross Output MBA Net 1=B=R Rating

Comb. Eftic

. Steam ° Sq.FL Steam MBh Water

MBh Vent

Size (Oil) otes Damper, Inter. Ign. Propane VGA-300BS' 300 240 80 750 (80 GA-350BS' 350 280 80 875 210 GA-400BS- 360 288 60 900 216 The above ratings are also approved for boilers with suffix (T) S (C). It VGAM-B Series Pilot, Natural or Popane GAM-5008 500 400 80 1250 300 'GAM -6005 600 480 80 

## 1505 360 050-7008 700 560 80 1750 420 Pilot, Natural Gas VGAM-800B 800 640 80 2000 480 VGAM1200 1200 960 80 3000 720 VGAM-1600: 1800 280 80 4008 962 VGAM-2000: 2000 600 8D 5117 1223 VGAM-2400 2.100 1920 80 6313 1491 Pilot, Propane VGAM-8008 720 576 80 1800 432 VGAM-12001 1080 864 80 2700 64B VGAM-16001 1440 152 80 3600 864 VGAM-20001 1800 1440 8U 411,3 1095 VGAM-24001 2160 1728 80 5558 1334 Inter Igo„ NaWral or Propane VGAM-500B 500 400 80 1250 300 VGAM-6008 600 480 80 1500 360 VGAM-7008 700 560 80 1750 420
Inter hr, Natural Gas GM-11113 800 640 2000 480 GA81-1208 1200 060 3000 720 [
080-10001 1600 1280 4008 962 GAM-20001 2000 1600 80 5117 1223 rGA81-24001 2400 1920 80 6313 1491 Inter Ign, Propane VGAM-8008 720 576 80 1800 .132 0881.1-1200 1080 864 80 2700 648 VGAM-16001 1440 1152 80 3600 864 VGAM-2000! 1600 1440 80 4563 1095 VGAM-24001 2160 1728 80 5558 1334 Damper, Inter Ign.. Natural or VGAIrt-5008 500 400 80 1250 300 VGAM-6008 600 480 80 1500 360 VGAM-7008 700 560 80 1750 420 tlVGAhf-6 Series Inter thin, Natural Gas VGAM-17008 800 640 80 2000 480 VG M-120(1 1200 000 80 3000 720 VGAM.160C 1600 1280 80 4098 962 00001-20001 2000 1600 80 5117 1223 VGAM.240D 2400 1920 80 6313 1491 Inter Ign Propane GAM-8008 720 576 80 1800 432 GAM-12001 1080 864 80 2700 648 [GAM-1600, 1440 1152 80 3600 861 GAM-2000 1800 1440 80 4563 1095 GAM-2400: 2160 1]28 80 5558 1334 OR Sanes Light Oil OR 330A 2.35 266 83.5 231 8912.15 OR-385A 2.75 306 83.9 266 8x12.15 The aoove ratings are based on 13,0% C02 and

-0 02 in. water draft. MG Series Natural Gas ORP-385 397 305 81.3 265 8.12x15 MG-770 794 610 81.3 530 12.16x20 MG -1155 1191 915 81.3 796 16.16x20 MG-1540 1588 1220 81.3 1061 16.20x25 MG-1925 1985 1525 81.3 1326 20x20"25 MG-2310 2382 1830 81.3 1591 20x20.25 MG-2695 2779 2135 81.3 185] 20x20"25 MG-3080 3176 2440 81.3 2122 20"24"25 MG M65 3573 2745 81.3 2387 2 20-24 5 MIS 3850 3970 3050 81.3 2652 24,24 5 2 ME 235 4367 3355 81.3 2917 21,24.25 MG-4620 4764 3660 81.3 3183 24x26025 MG-5005 5161 3965 61.3 .4. 24.2 8.30 MG-5390 5558 4270 81.3 3714 24x28.30 MG-5775 5955 4575 81.3 3978 28028030 MG-6160 6352 4880 81.3 4243 28028030 MG-6545 6749 5185 81.3 4509 28x28030 MG-6930 7146 5490 81.3 4774 28x28030 MO Series Light Oil 110 20 3 338 64.5 294 1,12,2 0 MO 560 4 454 83,5 395 12x12,20 MO 660A 4.7 532 83,5 463 12.12x20 MO-770A 5.5 612 83.9 532 12.12x20 MO 8`10 6 676 84.5 588 12.16x20 MID990A 7,05 798 63.5 694 12.16x20 MO-1155A 8,25 918 83

.9 798 16x16920 MO-1320A 9,4 1064 83

.5 925 16x16920JANUARY 2002 188 DIRECTORY - COMMERCIAL BOILERS

Boiler Fuel Boiler Nameplate Input Gas Oil 1=B=R Net 1=B= Grass Comb. Output Effio. Stea R Rating

m Steam Vent

Water Size Manufacturer TypelSerios Type Model MBh gph MBh % Sq

.Ft. MBh MBh (Oil) Notes MO-1540A 11 1224 83.9 1064 16020x25 MO-1925A 13.75 1530 83

.9 133020020x25 MO-2310A 16.5 1836 83,9 159620020x25 M0-2695A 19,25 2142 83,9 1862 20x20025 MO-3080A 22 2448 83,9 2129 20.242 MO 3465A 24.75 2754 83,9 2395 20X24x2 MO-3850A 27,5 3060 83.9 266 20x24a2 MO 235A 30

.25 3366 83,9 292; 2424a MO-4620A 33 3672 83,9 3193 24.242 MO 5005A 35

.75 3978 83.9 3459 24x28025 MO.5390A 38

.5 4284 83,9 3725 24x28830 MO-5775A 41.25 4590 83

.9 399128x28030 00.6160A 44 4896 83.9 4257 28028030 MO-6545A 46

.75 5202 83

.9 4523 28028030 MO-6930A 49.5 5508 83.9 479028.28x30 The above ratings are based on 13.2% C02 and -0,02 in. wafer dralt, except M0-420 whose ratings are based on 13 .7% C02 MOP Senes Natural Gas 0 RP-385 397 306 81 ,3 266 8012.15 MOP-770 794 612 81.3 53212016020 MOP-1155 1191 918 81,3 79816x16820 MOP-1540 1588 1224 81,3 106416820x25 MOP-1925 1985 1530 81 ,3 133020x20025 MOP-2310 2382 1836 81,3 1596 20020x25 MOP-2695 2779 2142 81 ,3 186220020x25 MOP-3080 3176 2448 81

.3 212920-24x25 MOP-3465 3573 2754 81

.3 239520,24x25 MOP-3850 3970 3060 81 ,3 2661 24x24 MOP-4235 4367 3366 81 ,3 2927 24x24025 MOP-4620 4764 3672 81 ,3 319324.24x25 MOP-5005 5161 3978 81

.3 345924028x30 MOP-5390 5558 4264 81.3 3725 24X2 X30 MOP-5775 5955 4590 81

.3 399128x28.30 MOP-6160 6352 4896 81.3 425728x28030 MOP-6545 6749 5202 81,3 452328x28030 MOP-6930 7146 5508 81.3 479028028x30 Light Oil ORP-385 2.75 306 83.9 266 8x12015 MOP 770 5.5 612 83.9 53212016x20 MOP 1155 8

.25 918 83.9 79816016x20 MOP 1540 11 1224 83.9 1064 16x20025 MOP 1925 13

.75 1530 83

.9 1330 20,2W MOP-2310 16.5 1836 83.9 159620x20025 MOP2695 19

.25 2142 83

.9 1862 2DX20^ MOP-3080 22 2448 83.9 2129 20x2402 MOP-3465 24

.75 2754 83

.9 2395 2W4a2 MOP-3850 27

.5 3060 83.9 2661 2424 2 MOP-4235 30,25 3366 83,9 292724x24025 MOP-4620 33 3672 83,9 319324824x25 MOP-5005 35,75 3978 83,9 345924x28030 MOP-5390 38

.5 4284 83

.9 372524x28030 MOP-5775 41 ,25 4590 83.9 399128x28.30 MOP-6160 44 4896 83

.9 425728x28.30 MOP-6545 46

.75 5202 83.9 4523 28028.30

NEW YORKER STEEL MOP-6930 49

.5 5508 839 479028x28030 The above 2tings based on 13.2% C02 (Oil) or10.2% C02 (Gas, and -0

.02 in, water draft.

BOILER FR Senes Light 0,1 FR265W 2.35 265 84.9 2308812815 COMPANY 18305W 2,6 305 83.3 2658x12018 FIR 50W 3 350 85 304 8012020 FR 400W 3,5 400 83.8 3488012x20 PR462W 4 462 841 4028012.25 Th above ratings are basedo0 122% C02 and -002 in. water droll. SAP Senes Light 06 9 284AP 2.6 284 84.3 247 8012x20 S339AP 3

.1 339 84.2 295 8x12020 The above ratings are based on 12,2% C02 and -0

.02 in. water droll

PEERLESS 051 Senes

CAST IRON Outdoor Boiler, Light Si OS2701 155 270 82,5 235 The above wings are based on 12.2% C02.

HEATER fl Senes GM Inter lgn. Natural Gas GM-07-SV 342 280 82 243 COMPANY GM-08-SV 399 327 82 284

Y Senes 62 Plot or Inter Ign, Natural or P 62.09-WIS 320 256 80 600 192 223 62-10-WIS 360 288 80 900 216 250 62-11-WIS 400 320 80 1000 240 278 52-12-WIS 440 352 80 1100 239 'Co 62-l3-WIS 480 384 80 1200 286 334 62-14-WlS 520 416 80 1300 312 362 62-15-W!S 500 448 80 1400 366 390 Ratings approved with sugi. STDG or SPRK Y Sores 211A Pd.t or Inter ten, Natural G 211 A-04 630 504 80 1575 378 438 211 0-05 340 672 80 2100 504 584JANUARY 200218R DIRECTORY - COMMERCIAL BOILERS

Boiler Feel Boiler Nameplate Input Gas oil I=B=R Net I=B= Gross Comb. output Emc

. SteR Rating

am Sloem Vent Water Size Manufacturer Type/Series Type Model MBh gph MBh % Sq.Ft. MBh MBh (Oil) Notes 2116-06 211 A-07 1050

1260 840 1008 80

80 2625

3150 630

756 730

077 2116-08 1470 1175 8U 3675 882 1023 211 A-09 1680 1344 80 4229 1015 1169 211 6-10 1890 1512 80 4008 1154 1315 211 All 2100 1680 80 5392 1294 1461 211 A-12 2310 184!1 8U 59]1 1433 1607 211 A-13 2520 2016 80 6521 1565 1753 211 A-14 2730 2184 80 7067 1696 1899 211 A-15 2940 2352 80 7808 1826 2045 211 A-16 3150 2520 80 8154 1957 2191 211 A-17 3360 2688 80 86900 2087 2337 211A-18 3570 2856 80 9238 22 17 2483 211A-19 3780 3024 80 9783 2348 2630 211A-20 3990 3192 80 10325 2478 2776 211A-21 4200 3360 80 10871 2609 2922 211A-22 4410 3528 80 11413 2739 3058 2113423 4620 3696 80 11958 2870 3214 211A-24 4830 3864 80 12500 3000 3360 2116-25 5040 4032 80 13042 3130 3506 2116-26 5250 4200 80 13588 3261 3652 211A-27 5400 4368 80 14129 3391 3798 211A-28 5670 4536 80 14675 3522 3944 211 A-29 5880 4701 80 15217 30052 4090 211A-30 6090 4872 80 15763 3783 4237 211A-31 630D 5040 80 16304 3013 4383 211A-32 6510 5206 to 16846 4043 4529 211A-33 6720 5376 80 17392 4174 4675 211A-34 6930 5544 80 17933 4304 4821 211 A-35 7140 5712 80 470 8 4435 4967 211 A-36 7350 5880 80 19021 4585 5113 211 A-37 7560 6048 80 19567 4696 5259 211 A-38 7770 6216 80 20108 4826 5405 211 A-39 7980 6364 80 20654 4957 5551 211A-00 8190 6552 80 21196 5087 5697 211A-41 8400 6720 80 21738 5217 5843 211A-t2 8610 6888 80 22283 5348 5990 211A-43 8820 7056 80 22825 5478 6136 211A-44 9030 7224 80 23371 5609 6282 211A-45 9240 7392 80 23913 5739 6428 211 A.46 9450 7560 80 24458 5870 6574 Pilot or Inter. Ign., Propan 211A-04 615 492 80 1536 369 426 2116.05 820 656 80 2050 492 570 211A-V6 1025 820 80 2563 615 713 2116-07 1230 984 80 3075 738 856 211A-08 1435 1148 to 3508 861 998 211A-09 1640 1312 80 4121 989 1141 1116 40 1845 1476 60 4688 1125 1283 211 A-11 2050 1640 00 5258 1262 1426 2116 42 2255 1804 60 5821 1397 1569 211 A-13 2460 1968 80 6367 1528 1711 211 A-14 2665 2132 80 6!196 1655 1854 211A-15 28]0 2296 80 742.9 1783 1997 211A-16 3075 2480 80 7958 1910 2139 211A 17 3280 2624 80 8488 2037 2282 211 6-10 3485 2788 80 9021 2165 2424 211 A-19 3690 2952 80 9550 2292 2557 211 A-20 3895 3116 80 10079 2419 2710 211A-21 4100 3280 80 10613 2547 2852 211 A-22 4305 3444 80 11142 2674 2995 211A-23 4510 3608 80 11671 2601 3137 211A-24 4715 3772 80 12204 2929 3280 211A-25 4920 3936 80 12733 3356 3123 211A-26 5125 4100 80 13263 3183 3565 211A-27 5330 4264 80 13796 3311 3708 211A-28 5535 4428 80 14325 3438 3850 211 A-29 5740 4592 80 14851 3565 3993 2116 30 5945 4756 80 15388 3693 4136 211A-31 6150 4920 80 15917 3820 4278 211A-32 6355 5084 80 16440 3947 4421 2116-33 6560 5248 80 10979 4075 4563 2116-34 6765 5412 80 11608 4202 4706 211A-35 6970 5576 80 18038 4329 4849 21 IA-36 7175 5740 80 18571 4457 4991 211A-37 7380 5904 80 19100 4584 5134 Wafer and Steam Sends Light Oil ECIECT-05-250-WI5 2.5 286 84
.1 896 215 249 8.12x20 ECIECT-06-275-WIS 2.75 321 84.4 1004 241 279 8x12020 ECIECT-06

-300-WIS 3 347 833 1083 261 302 8x12.20 The above ratings are based on 13

.5% C02 and -0

.02m. water craft. Senes SCISCT Natural Gas, Forced Draft SCISCT-05-1 433 343 80

.8 1071 257 298 7" VentJANUARY 200218R DIRECTORY - COMMERCIAL BOILERS

Boiler Fuel Nameplate Input Boiler Gas Oil 1=B=R Net 1=B= Gross Comb. Output Effie
- SteR Rating

am Steam Vent Water Size Manufacturer Type/Series Type Model MBh gph MBh % Sq

.FL MBh MBh (Oil) Nates SCISCT-06-1 505 405 81

.2 1267 304 352 9" Vent SCISCT-07-1 577 462 81 1446 347 402 9"Vent SC CT-081 649 519 809 1621 369 451 9' Vent SC CT-091 722 575 807 1796 431 50010' Vert SC/SCT-10-1 794 632 60

.5 1975 474 55010" Vent Light Oil, Forced Draft SC/SCT-05-W/S 3 343 03

.3 1071 257 2:17"1 t SC/SCT-06-W/5 3,5 405 63,7 1267 304 32 9" Venl SC/500-07-W/S 4 462 83.5 1446 347 402 9"Vent SC/SCT-08-W/6 4.5 519 83

.4 1621 389 451 '"V"' SC/SC-09-W/S 5 575 83,2 1796 431 500 10" Vent SC/SCT-10-W1S 5.5 632 83 1975 474 550 10" Vent The above ratings are based on 12

.5% C02 and +1110 in water draft at vent Series LC/LCE Natuml Gas, Forced Draft LC -4 686 547 81,2 1708 410 476 9"Vent LC 5R 808 649 81.2 2029 487 564 9'Vent LOS 881 707 81.2 2208 530 615 9" Vent LC6 1077 868 81.1 2713 651 755 10"Vont LC-7 1273 1029 81.1 3217 772 895 10"Vent LC-8 1469 1189 81.1 3717 892 1034 10"Vont LC -9 1664 1350 81.1 4250 1020 1174 12"Vent
LC10 1860 1511 81
.1 4804 1153 1314 12"0ent
LC 11 2056 1672 81.1 5367 1288 1454 12' Vent LC-12 2252 1832 81
.1 5917 1420 1593 12'Vent LCE-13 2464 1966 tit 6358 1526 1710 14"Vent LCE-14 2657 2125 81 6875 1650 1848 14"Vent LCE-15 2850 2284 81 7388 1773 1986 14"Vent LCE-16 3043 2444 81 7908 1898 2125 14' Vent LCE-17 3236 2603 81 8421 2021 2263 14"Vent
LC .18 3429 2763 81 8938 2145 2403 16"Vont
LC .19 3622 2922 81 8454 2269 2541 16" Vont LCE-20 3815 3082 81 9971 2393 2680 16" V.2 LCE-21 4027 3256 811 10533 2528 2831 16"Vont LCE-22 4239 3430 81,1 11096 2663 2983 16"Vent LCE-23 4451 3604 81.2 11658 2798 3134 16"Vent LCE-24 4663 3777 81.2 12217 2932 3284 16"Vent Light Oil, Forced Draft LG4 4,75 547 83,7 1708 410 476 9"V at LC-5R 5 6 649 83,7 2029 487 564 9"V It LG5 6,1 707 83,7 2208 530 615 9" Vent LG5 7.5 868 83.7 2713 651 755 10" Vent LC-7 8.8 1029 83.6 3217 772 895 10" Vent LC-8 10.2 1189 83.6 3717 892 1034 10" Vent LG9 11.6 1350 83.6 4250 1020 1174 12" Vent G10 12.8 1511 83

.6 4804 1153 1314 12' Vent LC 11 14,2 1672 83.6 5367 1288 1454 12'Vent LC-12 15.6 1832 83.6 5917 1420 1593 12"Vent LCE-13 17 1966 83.5 6358 1526 1710 14' Vent LCE-14 18.4 2125 83.5 6875 1650 1648 14'Vent LCE-15 19.8 2284 83.5 7388 1773 1986 14" Vent LCE-16 21 2444 83.5 7908 1898 2125 14' Vent LCE-17 22,5 2603 83,5 8421 2021 226314' Vent LCE-18 24 2763 83.5 8938 2145 2403 16'V at LCE-19 25 2922 83.5 9454 2269 2541 16'V at LCE-20 26.5 3082 83.5 9971 2393 268016" Vent LCE-21 28 3256 83.6 10533 2528 2831 16' Vent LCE-22 29,5 3430 83,6 11096 2663 298316' Vent LCE-23 31 3604 83,7 11658 2798 3134 16'0e11

PENNCO, INC. CAST IRON LCE-24 32.5 3777 83.7 12217 2932 3284 16' Vent The above ratings are based on 13,0% CO2 (oil) and -0.1 'water draft at the vent.

ii Series 41 H nlet. Ign , Natural Gas 1H-0300 300 240 60 750 180 209 41H-0400 400 320 80 1000 240 278 411H-0500 10(1 400 00 1250 300 348 ?H-0600 600 480 80 1500 360 417 1H-0700 700 560 80 175D 420 487 1H-0800 800 640 80 2000 480 557 11H-0900 900 720 80 2250 540 626 41H-1000 1000 800 80 2500 600 696 41H--1100 1100 680 80 2750 860 765 1H-1200 1200 900 80 3000 720 835 1H-1300 1300 1040 80 3250 780 904 lH-1400 1400 1120 80 3500 840 974 1 H11500 1500 1200 80 3750 900 1043 iH-1600 1600 1200 80 4008 082 1113 1H-1700 1700 1360

' 80 4283 1020 1.183 iH-1800 1800 144 80 4563 1095 1252 1H-1900 1900 1520 80 4838 11a1 1322 1H-2000 2000 1600 80 5117 1228 1391 1H-2100 2100 1680 80 5392 1294 1481 1H-2200 2200 1760 80 5671 1361 1530 1H-2300 2300 1840 80 5942 1426 1600JANUARY 20021BR DIRECTORY

- COMMERCIAL BOILERS

anulastsroe Boiler

TypolSorios Fuel Typo Boiler

Model Nameplate

Input Gas Oil MBh gph 1=B=R Gross Comb. Output Effie

. MBh % Not 1=B=R Rating
Steam Sq

.Ft. Steam

MBh Rant

Water Size MBh (Oil) otes 14-2400 111-2500 2400

2500 1920 2000 80

60 6213

6471 1491

1553 1670

1739 )H-2800 2600 2080 80 6729 1015 1809 111-2700 2700 2100 80 6988 1677 1878 1H-2800 2800 2240 80 7246 1739 1948 1H-2900 2900 2320 80 7504 1801 2017 iH-3000 3000 2400 80 7763 1853 2087 Also approved with suite SI ar WI
RAYPAK, INC. COPPER

n HI DelI. Inter. Ign Natural or Propane H(3,4)302(P 300 252 84 219 H(3,4)402(P 399 335 61 291 H(3,4)502(P 506 420 84 365 H(3,4)652(P; 60 5 546 84 475 14(3 4)752(P 7511 630 04 548 H(34)902(P, 900 756 04 657 H(8 4)992(P 990 831 84 723 4(9.4)1282(1 1260 1058 84 920 H(9 4)1532(1 1530 1285 84 1117 4(9.4)1802(1 1800 1512 84 1315 0119A)2002t1 1099 1679 64 1460 4(981207211 2070 1]38 84 1511 4(9.4)234211 2340 19005 64 1709 N ADS Series nter Ign Natural or Propane 4500 500 420 84 365 11750 750 630 84 548 41000 9995 840 84 730
H5000SH 500 485 97 422 H750GSH 750 728 97 633 410011058 999.5 970 97 (143
• Indoor & Ould00r Inter tgn., Natural Gas H-033 0B 331 273.0 82 237 H040 0B 399 327.2 82 264 4.03318 334 273.9 B2 237 H-04018 399 327.2 82 284 H-05148 5119 419.4 82 365 H-0624A 627 514.1 02 447 H-072 4A 726 595.3 82 518 0-0824A 825 6765 82 588
4 Indoor Inter.Ign.,N alural G- H-09628 961.7 7886 112 686 H 11258 11247 9223 82 802 H-12238 1222.5 1002 5 82 872 H-13368 1336.6 1096 82 953 H -68A 1467 1202.9 82 1046 H=i631A 1630 1336.6 82 1162 H•1826A 4-21008 1825.6

2100 1497 1722 82

82 1302 1497 H-21008 1999 1639.2 82 1425 4-25008 2499 2049.2 82 1782 H-30018 3000 2460 82 2139 4-35008 3500 2870 82 2496 H -4001A 4000 3280 82 2852
0 Indoor & Outdoor Inter Ign Propane 4-03308 333 273.9 82 237 H-04008 399 327.2 82 284 1-05148 481 394.4 82 343 H-0624A 589 483 82 420 H-0724A H-0824A 882

775 5,92 035.5 82

82 486 553
n Indoor ntor. Ign., Propane H-0962A 685 7262 82 631 H-1125A 1035 840 7 82 738 H-1223A 1125 922 9 82 802 H-13368 1233 1011 1 82 879 4-14688 1350 1107 82 963 H-16318 1500 1230 02 1070 H-1826A H-21008 1680

2100 1377 6 1722 02

82 1198 1497 H-21008 1.999 1630 2 62 1425 6-25098 2499 2049.2 82 1782 H-30018 3000 2460 82 2139 11-35008 3500 287. 82 2406 H1001A 4000 3280 82 2852
II Oultloor Inlur, Ign., Natural Gas 1 H-0926A 926 759.3 82 660 H-1083A 1083 888.1 82 772 4-11788 1178 966 82 840 H-12878 1287 1755.3 82 918 H-14148 1413 1158.7 82 1008 44-1571A 1570 1207A 82 1119JANUARY 2002 ER DIRECTORY - COMMERCIAL BOILERS

Boiler Fool Bailer Nameplate Input Gas Oil 1=B=R Nat I=B=R Gross Comb. Output Effie. Stea Rating

m Steam Vent

Water Size Manufacturer TypelSeries Type Model MBh gph MBh % Sq.Ft. MBh MBh (Oil) Solos H-1758A 1758 1441.6 82 1254 N Outdoor nter Ign. Propano H-0926A 885 725,7 82 631 H-1083A 1035 818,7 82 738 H-1178A 1125 922.5 82 802 H-129712 1230 1000,6 82 077 H-1414A 1350 1107 82 9163 H-1571A 1500 1230 82 1070

RBI WATER COPPER H-1758A 1680 1377.6 82 1198 Also approvedwilh prefix H1 • H6

HEATERS d Spectrum Sores Damper, Inter Ign, Natural or P w 300 300 250 63 218 Division of M SBIW)350 350 290 83 252 Mestek, Inc SB(W)400 400 331 83 289

1, Fulcra tl Senes Forced Draft, Naluml or Propa FH(W)500 500 425 OS 370 FH(W)750 750 638 85 555 FH(W)1000 1000 850 85 740 FH(W}t250 1250 1062 85 924 FHIW)1500 1500 1275 85 1109 FHIW)1750 1750 1488 85 1295

SLANTIFIN CAST IRON FHlW)1950 1950 1658 85 '442

CORPORATION NConcopt 21 Senes Modulating Dunce Vent, Nalor CBM-399 399 341 85.5 297

4 Galaxy Series Damper Pilot, Natural or Propa GG-300DP 300 240 80 209 ConhnuouS Clrcute6an. Damp GG300DS 300 2,10 80 209 Cont. Ciro. Damper, GG-300EDS 300 240 80 209 GG-325EDS 325 260 80 226 GG-350EO5 350 280 80 243 a Galaxy Series Carl. Cnc., Dantpor,Inlerlgn,N GG-350HED 350 291 83 253 GG-375HED 375 304 81 264 GG-399HED 399 32] 82 284 Damper. Inter tyn„ Natural, Pr GG-300EOP 300 240 80 209 G5-325EDP 325 260 80 226 GG-350E0P 350 280 80 243 00-3504E0 350 291 83 253 00-3750E0 375 304 81 264 00-3994E0 390 327 82 264 it Galaxy Senes Damper, Pilot, Natural or Prop GXH-300D 300 240 80 209 GXH-300HD 300 243 8' 211 Campa, Into, 191, Naluml or GXH-300HE 300 243 81 211 Danpor Pilot. Natural or Propa GXH-30011D 300 243 81 758 182 Dapper, Inter Ign , Natural or', GXH-300HE 300 2,13 81 758 182 " Ratings are for Naluml Gas N GXHT Caravan SenesPlot, Natural or Propane GXHT-3802 380 304 80 950 228 GXHT-5002 GXHT 750Z 561

756 403 605 80

80 1258

1892 302

454

- itGET Caravan Series Priot or Inter Igo Natural or Pr GGT-0400 400 322 82 280 GGT-0500 500 402 804 350 GGT-0600 600 480 80 417 GGT-0900 900 720 80 626 GGT-1200 1200 960 80 634 GGT-':500 1500 1200 80 1043 Infer lge, Natural or Propane GGT-0OOE 400 322 82 260 GGT-500E 500 402 80.4 350 htlatake777 =___> GGT-BOOE 600 600 80 417 GGT-900E 900 720 80 626 GGT-1200E 1200 960 80 634 GGT-1500E 1500 1200 80 1043 GGHT Caravan Series Inter 19n. Natural or Propane GGHT-700E 700 501 83 505 GGHT-750E 750 008 81 529 GGHT-800E 798 654 82 569 004T-10501 1050 072 83 758 0081-11251 1125 912 81 793 GGHT-12001 1197 981 82 853 GGHT-14001 1400 1162 83 1010 0541-15001 1500 1216 81 1057 GGHT-16001 1596 1308 82 1137JANUARY 20021BR DIRECTORY - COMMERCIAL BOILERS

Boiler Furl Nameplate Input Boiler Gas Oil 1=B=R Net 1=B= Gross Comb. Output Effie Slea R Rating

m Steam Vent

Water St.. Manufacturer TyprlSeries Type Model MBh gph MBh % Sq.Ft. MBh MBh (Oil) Notes GGHT-17501 1750 1453 83 1263 GGHT-18751 1875 1520 81 1321 GGHT-200111 1995 1635 62 1422 GGHT-21001 2100 1743 83 1516 GGHT-22501 2250 1824 81 1586 3007-24001 2394 1962 82 1706 GGHT-25401 2450 2043 83 1768 GGHT-26251 2625 2128 81 1850 GGHT-28001 GGHT 2600 2793

2600 2289 2324 82

63 1990 202

- GGHT-30001 3000 2432 01 1 2115 0001-31501 3150 2615 63 2273 0007-32001 3192 2616 82 2275 0001-33751 3375 2736 fl1 2379 GGHT-35001 3500 2905 83 2526 0601-36001 3591 2943 82 2559 0 061-37501 3750 3040 81 2643
Y GXHT-HZ Steam Cara Pilot, Natural Gas GGHT-40001 3990 3270 82 2843 Ratings are for Naluml Gas

0080-6006, 600 486 81 1521 365 0061-9004, 12001 0061 900

1200 729 972 81

81 2279

3038 547

729

- GXHT-15001 1500 1215 81 3796 911 Liberty Sanes Model L Light Oil LD-50 2.15 250 859 783 188 2178X12%15 LD-50 2,35 272 85.2 2378812%15 LD-60 2.6 298 85.8 933 224 2598 MIS LD-60 2.85 326 04.7 2838%12X15 LD-70 3.1 354 85,5 1108 266 308 8X12X15 LD-70 3,35 361 64.2 3318X12%15 LD-70 3 339 83.5 294 8012215 LD-70 3 337 84.8 1054 253 8012815 The above ratings are based on 13,0% C02 and -0.02 in. wat.(raft. Liberty Dual Fuel Light Oii OF-50 2.15 250 85 7 783 188 217 8x121 15 DF-50 2.35 271 . 84.8 236 8012x15 DF-60 2
.6 296 85.2 925 222 2578,12,15 DF-60 2

.85 324 84.2 282 8x12015 DF-70 3 337 84.8 1054 253 293 6x22015 DF-70 3.1 348 84.8 1088 261 303 8012x15 OF-70 3.35 378 83.5 329 8012015 Power Burner, Natural Gas 0 F-50 310 250 83.1 783 188 217 8112015 DF-50 339 271 82.3 236 8012.15 DF-60 375 296 82.6 925 222 257 8112015 DF-60 411 324 81.7 282 8112015 DF-70 400 311 82.3 971 233 270 8112x15 DF-70 447 348 82,3 1088 261 303 Bx12x15 DF-70 484 378 81 329 8x12.15 The above ratings are based on 12.25% C02 (Oil) or 9.5% C02 (Gas) and -0

.02 in water draft. LDZO Co.- Series Light Oil DZ0.600.2-5 4.3 500 85,9 1563 375 12112x20 DZ0-750.2-6 5.2 596 85.8 1863 447 12112x20 DZO.850.2-7 6 664 85.5 2138 513 12olRe20 DZO-900-3-5 6.4 750 85S 2346 563 12116x20 DZ0-1100-3-6 7.8 894 85
.8 2796 671 16x16.20 DZO-1300-3

-7 9 1026 85
.5 3208 770 16x16.20 DZO-1 700-4-7 12 1368 85

.5 4313 1035 1 6120025 DZO.2100.5.7 15 1710 85
.5 5496 1319 16.20x2S The above ratings are based on 13,008 C02 and -0.02 in. water draft. LOWO Caravan Series Light Oil DW0-600-2.5 4.3 500 85.9 43512x12.20 DW0-750.2-6 5.2 596 85,8 51812112x20 DW0-850-2-7 6 684 89.S 59512.16.20 0 WO.900.3.5 6.4 750 85.9 05212016020 DWO-11003.6 7.8 894 85,8 77716x16020 0 W0-1300-3.7 DWO 1700-4 7 9 2 1026

368 85,5

5 89216016120

- - DW0-2100-5-7 1 15 1

1710 8
.5

05.5 119016x20025 1487 16020025 DWO-2500-6

-7 18 2052 85.5 1784 20x20025 DW0-2900-7

-7 21 2394 85
.5 2062 20x20025 DWO-3400-8-7 24 2736 85.5 2379 20.24.25 The above rulings are based on 13.0% C02 and -0 ,02 in. water draft. LWDF Caravan Sanes (I Light Oil WDF-600.2-5 43 500 85.7 43512112x20 WDF-750.2-6 5.2 592 85,2 51,512x12.20 WDF-850.2-7 6 674 84.8 566 12.16x20 WDF-900-3-5 6.4 750 85

.7 65212x16020 WDF-1100-3-6 7.8 088 85.2 77216, : 0,20 WDF-1300-3-7 9 1011 84,8 879 16x16620 WDF-1700.4-7 12 1348 84,8 1172 16x20025 WDF-2t 00-5

-7 15 1685 84
.8 1465 16120x25 WDF-2500-6

-7 18 2022 84
.8 1758 20120x25 -W W F-2900-7-7 21 2359 84
.8 2051 20x20625 WDF-3400-8-7 24 2696 84.8 2344 20020625JANUARY 20021 BR DIRECTORY

- COMMERCIAL BOILERS Nameplate Input 1=B=R Net 1=B= Gross Comb. R Rating Vent Boiler Fast Bailer Gas Oil Output Effie. Steam Steam Water Si.. Manufacturer TypalSeries Type Model MBh gph MBh % Sq.FL MRS MBh (Oil) Notes Power Burner, Natural Gas WDF-600-2 620 500 83
.1 435 12x12520 WDF-750-2 750 592 82.6 515 12x12020 WDF-850-2 800 622 82.3 541 12016x20 60DF-900-3 930 750 83.1 652 12x16020 WDF-1100 1125 886 82.6 77216x16.20 WDF-1300. WDF 1700 1200

1600 933 1244 82.3

82 3 811 16616x20 1082 16 20 25

- ' WDF-2100. 2000 1555 . 82.3 0 x 1352 16x20025 WDF-2500. 2400 1866 82
.3 1628 20x20025 WDF-2900. 2800 2177 82.3 1893 20020x25 WDF-3400' 3200 2488 82.3 2163 20020x25 Above ratings based on 1125% C02 (Oil) or 9.5% C02 (Gas) and -0.02 in. wafer draft LZDF Caravan Series (DLighl Oil LZDF-600-2-5 4.3 500 85.7 1563 375 12.12.20 LZDF-750-2-6 5.2 592 85.2 1850 444 12012x20 LZDF-650-2
.7 6 674 84.8 2106 506 12016520 LZDF-900-3

-5 6.4 750 85
.7 2346 563 12.16.20 LZDF-1 100

-3-6 7.8 688 85
.2 2775 666 16.16820 LZDF-1 300.3-7 9 1011 64
.8 3158 758 16x16820 LZDF-1 700-4-7 12 1348 84.8 4242 1018 16x20025 LZOF-2100-5-7 15 1685 84
.8 5408 1298 16020x25 Power Bumer, Natural Gas ZOF-600-2- 620 500 83.1 1563 375 12012x20 ZDF-750-2- 750 592 82.6 1850 444 12x12020 ZDF-850-2- 800 622 82.3 1946 467 12016x20 ZDF-900-3' 930 750 83.1 2346 563 12016x20 ZDF-1 100- 1125 888 82.6 2775 666 16016x20 ZDF-1300: 1200 933 82
.3 2917 700 16016.20 ZD-1700-4 1600 1244 82.3 3888 933 16020x25 ZD-2100-5- 2000 1555 82.3 4963 1191 16020x25 Above ratings based on 12.2590 C02 (Oil) or 9.5°0 C02 (Gas) and -0 021n

. walerdrallSMITH CAST IRON BOILERS CAST IRON

if G250 Series Pilot, Natural Gas 66250-5-7-( 300 240 80 750 180 Divi n of 66250.5.8-( 350 200 80 8]5 210 West- t, Inc. 56250-9.8-( 400 320 80 1000 240 Inter Igo.. Natuml Gas GB50-S-7-1 300 240 00 750 160 G6 90-S-8-1 3,90 280 80 875 210 66250-S-9-I 400 320 80 1000 240 Pilot. Propane PG6250-5-7 300 240 80 750 180 PG6250-S-8 350 200 80 875 210 PG6250-S-9 360 208 80 900 216 Inter. Ign,, Propane P06250-S-] 300 240 80 750 180 PG6250-S-8 350 280 80 875 210 PG6250-S-9 360 286 80 900 216 The above m6ngs also approved with the suffix D (o.. a.k damper N GB300-W Genes Piln1 ur Inter. Ign. Natural or P 68300-W-5 400 326 81 5 283 G6300-W-6 500 400 81 5 355 GB300-W-7 600 489 81 6 425 GB300-W-8 700 571 81 5 487 GB 300-W-9 800 652 81 5 567 09300?N 1( 900 70-1 81 5 635 68300-W 1" 1000 815 81 5 709 G6300-W-1i 110D 897 81 5 780 68300-W-It 1200 978 

### 81 5 850 GBs00-W 1. 1300 1060 81 55 922 GB300-W 1( 1400 1141 815 992 68300-4V--1f 1500 1223 81 5 1083 G8300-W i7 1600 1304 8iS 1134 G6300-W-i1 1700 1366 81.5 1205 663110 -W-1t 1800 1467 815 1276

16300-S Series Pilot or triter. Ign. Na)ural or P GB300-W-2( 68300-W-2'.

G13300-S-5 1900 2000

400 1549 1630

322 91.5

111.5

80.5 008 42 13 41 477 Also approved with Prelio "P" for Propane

GB300-S-6 500 403 80.5 1258 302 GB300 S-7 600 483 805 1508 382 GB300-S-8 700 564 WS 1763 423 68300-S-9 800 844 80.5 2013 483 48300-S Series Pilot or triton. Ign. Natural or P G 6300-5--10 900 725 80.5 2267 544 68300-5-11 1000 805 80.5 2517 604 GB300-S--12 1100 886 805 2771 665 66300-0-13 1200 996 80.5 3113 747 68300-5--14 1300 1047 80.5 3271 785 063(01-515 1400 1127 805 3521 845 08300-5-16 1500 1208 80 5 3775 906 66300-5-17 1600 1288 80 5 4033 968 68300-6-18 Vol) 1368 805 4313 1035JANUARY 20021 BR DIRECTORY

- COMMERCIAL BOILERS

Boiler Fuel Nameplate Input Boiler Gas Oil 1=B=R Net I=B= Gross Comb. Output Effic

. SteR Rating

am slam Vent Water Size Manufactcrar Type/Series Type Model MBh gph MBh % Sq.Ft. MBh MBh (Oil) Notes 56300-0i9 G6300-S-20 1000

1900 1449 1530 80.5

805 4592

4875 1102

1170 GB300-S-21 2000 1610 805 5154 1237 Also approved with Prefix"P"for Propane 8614A Series Light Oil BB14A-SfW-6L 2.5 279 84,1 871 209 243 8812x15 BB14A-SIW-6H 2.75 305 83.5 954 229 265 8812x15 BBI4A-SlW-7L 3 337 844 1054 253 293 8012x15 BBI4A.SIW

-7H 3,4 377 83.8 1179 283 328 8x12015 BB14A-SAN-8L 3,5 396 84,8 1238 297 344 8012.20 BB14A-SIW

-BH 4 449 84 1404 337 390 8x12.20 The above ratings are based oa 12

.5% C02 and -0,02 in. water draft. 19S ... a Nature] Gas, Forced Draft 19-SIW-03 375 297 81.6 929 223 258 6 Vent 19-SNV-04 520 413 827 1292 310 359 7" Vent 19-5/W-05 660 529 826 1654 397 460 Want 19-51W-06 801 644 82.6 2013 483 560 8" car 19-SIW-07 942 760 02,6 2375 570 661 9"Vent 19-SIW-08 1082 878 82.6 2738 657 762 10"Vent 19-SIW-09 1223 992 82.6 3100 744 863 10"Vent 1'_S-10 1364 1107 826 3456 830 963 10"Vent 19.s -11 1505 1223 82,6 3821 917 1063 10'Venl 19-SIW-12 1645 1339 82.6 4213 1011 1164 1234e11 Light Oil, Forced Draft 19-SM'-03 2

.6 297 84.2 929 223 2586"Vent 19-SIW.04 3

.6 413 85.2 1292 310 359 7'Venl 19-S/W-05 4,6 529 85,2 1654 397 4608"Von[ 19-SIW-06 5.5 644 85,2 2013 483 560 8"Venl 19SIW-07 6.5 760 85.2 2375 570 661 9'Vent 19-SIW-08 7.5 878 85,1 2738 657 762 ID Vent 19-SIW-09 8.5 992 85.1 3100 744 863 10'Veni 12 W-10 9.5 1107 85.1 3456 830 963 10'Venl 19-SIW-11 10
.4 1223 85.1 3821 917 1063 1PVen1 19-SIW

-12 11.4 1339 851 4213 1011 1164 12'Vent The above ratings are based an 12

.515 (Oil) or 9

.7% C02 (Gas) and +10 in. water at the vent. 19A Series Natural Gas, Forced Draft 19A-8AW-03 375 297 61,6 929 223 258 7" Vent 19A-SIW-04 520 413 82,7 1292 310 359 7" Vent 19A-SAN-05 725 575 82.1 1796 431 500 8" Vent 19A-SAN-06 931 738 811 2308 554 642 8"Vent 19A-SW-07 1137 901 814 2817 676 783 9" Vent 19A-SIW-08 1342 1063 81.3 3321 797 924 10"Vent 19A-SIW-09 1548 1226 81.2 3883 920 1066 10"Vent 19A-01W-10 1754 1388 81,1 4384 1052 1207 10"Vent 19A-SNV-t1 1959 1551 81,1 4946 1187 1349 12" V2 19A-SAW-12 2165 1713 81 5508 1322 1490 12' Vent Light Oil Forced Draft A-SAV-03 2 6 297 84 2 929 223 258 7" Vent , j:A-M-04 . 3.6 413 . 85.2 1292 310 359 7" Vent 19A-SM7-05 5 575 84,6 1796 431 500 8" Vent 19A- Was 6.5 738 84.2 2308 554 642 8"V ni 19A-SN4-07 7.9 901 84 2817 676 783 9" Vent 19A-SIW-08 9,3 1063 83.8 332, 797 924 1 0" Vent 19A-SMJ-09 10.8 1226 83.7 3883 920 1066 10" Vent 19A-SlW-10 12.2 1388 83,6 4383 1052 1207 10"Vent 19NSMJ-11 13.6 1551 83.6 4946 1187 1349 IT Vent 19A-SIW-12 15 1713 83,5 5508 1322 149012' Vent The above ratings are base 0n 12

.5% C02 Oil at

.97% C02 (Gas) and +.10 in water at the ve. 28A Series Nalurai Gas, Forced Draft 28A-SAN-04 1154 900 2813 675 783 11" ant 280-51W-05 1491 1166 3646 875 101 10"Vent 28A. W-06 1827 1433 4538 1089 1246 1234e01 28A.W

-07 2163 1699 5458 1310 1477 1234e91 28A-SAW-08 2499 1965 81 6358 1526 1709 14"Vent 28A-SIW-09 2836 2232 81 7221 1733 1941 14"Venl 28A_IW-10 3172 2498 81 8079 1939 2172 14 Vent 28A-SNV-11 3508 2764 81 8942 2146 2403 16"Vent 28A- M-12 3844 3031 81 9804 2353 2636 16"Vent 28A-SAW-13 4180 3297 81 10667 2560 2867 16"Vent 28A_ NV-14 4517 3563 81 11525 2766 3098 18"Vent 28A_ NV-15 4853 3830 81 12392 2974 3330 1834e01 28A-SAV-16 5189 4096 81 13250 3180 3562 18"Vent 280-57.5-17 5525 4362 81 14113 3387 3793 1834e11 28A-SIW-18 5862 4629 81 14975 3594 4025 20"Vent Light Oil, Forced Draft 28A-SM'-04 8 900 83

.5 2813 675 783 t0"Vent 28A-SM-05 10
.4 1166 83
.5 3646 875 1014 10"Vent 28A. M-06 12.6 1433 83
.5 4538 1089 1246 12"Venl 28A_ NV-07 15 1699 83,5 5458 1310 1477 12"Vent 280-SM-08 17,4 1965 83
.5 6358 1526 1709 1434e11 28A-SIW-09 19 6 2232 83
.5 7221 1733 1941 14"Vent 28A-SM'-10 22 2498 83.5 8079 1939 217214Vent 28A-SM'-11 24.5 2764 83.5 8942 2146 240316"Vent 28A-SIW-12 26
.5 3031 83,5 9804 2353 2636 16"Vent 28A-SM'-13 29 3297 83,5 10667 2560 2867 16"Vent 28A-SAN-14 31.5 3563 83
.5 11525 2766 3098 18"VentJANUARY 20021BR DIRECTORY - COMMERCIAL BOILERS Nameplate Input leBeR Net I=B= Gross Comb. R Rating Vent Boiler Fuel Boiler Gas Oil Output Effie. Steam Steam Water Size Menufagluror TypolSOries Type Model MBh gph MBh % Sq.Ft. MBh MBh (Oil) Notes 28A-SIW-15 33.5 3830 83.5 12392 2974 3330 18"Vent 28ASIW.16 36 4096 83.5 13250 3180 3562 18"Vent 28A-SIW-17 28A-S1i11-18 38.5 40.5 4362

4629 83.5

83.5 14113

14975 3387

3594 4092 VV

4025 20"Vent The above Rungs are based on 12.25% C02 (Oil) or 9.5% C02 (Gas) and +.10 in. water at vent.

The above ratings arealso approved for bailers with prefix G, GO or LO. 350A Mills Seres Power Bumar, Natural Gas 350A-'-06 1290 1001 80,9 3129 751 87016016017 350A-•-07 1585 1235 81 3858 926 1074 16,16020 350A •-06 1879 1470 81 4667 1120 1278 16x20x23 350A -09 2174 1705 81 5483 1316 1483 16x20x26 350A-10 2469 1939 81 6271 1505 1 686 20,20x29 350A -11 2763 2174 81 7033 1688 1890 20x20032 350A---12 3057 2474 et 7792 1870 2095 20,20x35 350A-13 3352 2643 81 8550 2052 2298 20x24,38 350A•-14 3646 2878 81 9308 2234 2503 20,2441 Light Oil 350A-'-06 8.9 1001 83.4 3129 751 87016x16017 350A-'-07 11 1235 83.5 3858 926 1074 16016x20 350A-'-08 13 1470 83.5 4667 1120 1278 16020023 350A.-09 15 1705 83,5 5483 1316 1483 16020026 350A -10 17.2 1939 83,5 6271 1505 1686 20820029 350A-11 19.2 2174 83.5 7033 1688 1890 20020.32 350A=-12 21 2474 83.5 7792 1870 2095 20020035 350A •-13 23 2643 83.5 8550 2052 2298 2082438 The above selings are based on 13% C02 (Oil) and -002 in. water draft. 350A'-14 25.5 2878 83,5 9308 2234 2503 20,24x41 Insert S for Steam, W for water boilers. 3500A Mills Sends Power Bumer, Natural Gas 3500A-'-06 1499 1165 80,7 3642 874 1013 16,16,1 9 3500A •-07 1889 1478 80.7 4696 1127 1285 16,20x23 3500A •-08 2278 1790 80.8 5771 1385 1557 20020,26 3500A-'-09 2668 2103 60.8 6804 1633 1829 20,20x30 3500A-'-t0 3057 2415 80.8 7813 1875 2100 20x20033 3500A-'-11 3447 2727 80.8 8821 2117 2371 20x24037 3500A-'-12 3836 3040 W. 9833 2360 2643 20x24040 3500A •-13 4226 3352 80.8 10842 2602 2915 24.2444 3500A-'-14 4615 3665 80,8 11854 2845 3187 24124,47 Light Oil 3500A•-06 10.4 1165 83.2 3692 874 101316x16 x19 3500A--'-07 13 1478 83.2 4696 1127 1285 16x20123 3500A-'-05 15.8 1790 83.3 5771 1385 1557 20,20x26 3500A 09 18.4 2103 83,3 6804 1633 1829 20020430 3500A -10 21 2415 83.3 7813 1875 2100 20x2Ox33 3500A -11 24 2727 83.3 8821 2117 2371 20024.37 3500A'-12 26.5 3040 83.3 9833 2360 2643 20024040 The above m1ngs are based on 13.0% C02 (Oil) or 10,0% C02 (Gas) and -0.02 in. wafer draft, 3500A'-13 29.5 3352 83.3 10842 2602 2915 24024.44 The above mlings are also approved far boilerswith prefix G or GO 3500A'-14 32 3665 83.3 11854 2845 3187 24,24047 • insect S for steam. W for water bailers. 4500A Mills Series Natural Gas 500A -10 3920 3080 82.1 9963 2391 267820x24.30 500A -11 4404 3467 81.8 11217 2692 3015 24,24037 SODA-'-12 4888 3853 81,6 12463 2991 331124 24,44 SOMA-'-13 5372 4240 81,4 13717 3292 3687 24,26x51 SODA-'-14 5856 4627 81.3 14967 3592 4023 24x28.58 SOOA -15 6341 5014 81.1 16221 3893 4360 24028x65 500A -16 6825 5400 81 17471 4193 4696 28x28,72 500A `-17 7309 5787 80,9 18721 4493 5032 28028x79 SODA •-18 7793 6174 80.9 19971 4793 5369 28,28x86 500A-'-t9 8277 6560 80.8 21221 5093 5704 30x30093 500A -20 8761 6947 80,7 22475 5394 6041 300300100 500A-'-2t 9246 7334 80.7 23725 5694 6377 30036,107 500A •-22 9730 7720 80.6 24975 5994 6713 300360114 Light Oil 500A -10 27 3080 84.6 9963 2391 2678 20x24030 500A-'-11 30.5 3467 84,3 11217 2692 3015 24x24,37 500A -12 34 3853 84,1 12463 2991 3350 24x24,44 500A -13 37 4240 83.9 13717 3292 3687. x28051 SODA -14 40.5 4627 63.8 14967 3592 4023 24x28058 500A-15 44 5014 837 16221 3893 4360 24028,65 SODA •-16 475 5400 83.5 17471 4193 4696 28028072 SDOA-'-17 51 5787 83.5 18721 4493 5032 28528x19 S00A=-18 54 6174 83A 19971 4793 5369 28x28086 SODA •-19 57 6560 83.3 21221 5093 5704 30x30093 500A=-20 61 6947 83.2 22475 5394 6041 30x300100 The above ratings are based on 12,5% C02 (Oil) or 9.7% C02 (Gas) and -0.02m, water droll. 500A-21 64 7334 83,2 23725 5694 6377 30,36x107 The above ratings are also approved for boilers with prefix G, LO. and GLO. 500A "-22 67 7720 83.2 24975 5994 6713 30x365114 ' Insert S for Steam, W for water boilers 4500A Mills Seems Heavy Oil 500A---10 25 3045 84.4 9850 2364 2648 20024,30 5WA-11 28 3435 84.3 11113 2667 298724x24537 500A-M2 31 3825 84.3 12375 2970 3326 24024044 500 A-1,13 34.5 4214 84.3 13633 3272 3664 24,28x51 500A-M4 37.5 4604 84.2 14896 3575 4003 24028058 500A-M5 40.5 4994 84,2 16154 3877 4343 24x28065 500A-M6 43.5 5384 84.2 17417 4180 4682 28028x72 500A-M7 46.5 5774 84.2 18679 4483 5021 28028x79 500A-MB 50 6163 84.2 19938 4785 5359 28528086JANUARY 200216R DIRECTORY - COMMERCIAL BOILERS

Boiler Fuel Boiler Nameplate Input Gas oil I=B=R Net I=B= Gross Comb. Output Effie. SteR Rating

am Steam Vent Wader Size Manufacturer Type/Series Type Model MBA gph MBA % Sq

.Ft. MBh MBh (011) Notes 500A •-19 53 6553 84.2 21200 5088 5698 30x30.93 500A •-20 56 6943 84
.1 22463 5391 6037 300300100 ...A •-21 59 7333 84.1 23721 5693 6377 30x36,107 The abave ratings are based on 12.25% C02 and -0.10 in. water draft. 5000--'-22 62 7723 64.1 24983 5966 671630x36

.114 'Insert S (ar steam, Wfor wafer boilers.
M450A Mills Series Power Sumer, Natural Gas M450A'-10 3031 2449 831 7921 1901 2130 20.20029 M4SOA-'-11 3380 2733 83A 8642 2122 2377 20024.33 M450A-'-12 3729 3016 83.2 9758 2342 2623 20024.37 M450A'-13 4077 3300 83 10675 2562 2870 24%24x40 M450A---14 M450A '-15 4426

4775 3583 3867 82
.9

a2:1 11592

112 2782

3002 3116 24%24x44

3363 24.24x47 M450A•-16 5124 4151 82
.6 13429 3223 3610 24028053 M450A-17 5473 4434 82.5 14346 3443 3856 241,28859 M450A-'-18 5821 4718 82A 15263 3663 4103 24028.65 M450A'.19 6170 5001 .2A 16179 3883 4349 28028.71 M450A-20 6519 5285 823 17096 4103 4596 28%28x77 M450A-21 6868 5568 82.2 18013 4323 4842 28%28x82 M45OA=-22 7216 5852 82
.2 18929 4543 5089 28x28.88 Light Oil M450A-'-10 21 2449 86.3 7921 1901 2130 20x20029 M450A-'-11 23.5 2733 86 8842 2122 2377 20x24.33 M450A'-t2 26 3016 85
.8 9758 2342 2623 20.24x37 M450A-'-13 28.5 3300 85.6 10675 2562 2870 24%24x40 M450A'-14 30.5 3583 854 11592 2782 3116 24 24,44 M4 A--'-15 33 3867 853 12508 3002 3363 24.24x47 M450A---16 35.5 4151 852 13429 3223 3610 24%28x53 M450A'-17 38 4434 85
.1 14346 3443 3856 24%28x59 M450A'-18 40,5 4718 85 15263 3663 4103 24.28.65 M4SOA-19 43 5001 84
.9 16179 3883 4349 28.28.71 M450A'-20 45 5285 84
.8 17096 4103 4596 28x28.77 M450A •-21 47.5 5568 84
.8 18013 4323 4842 28028x82 M450A'-22 50 5852 64
.8 18929 4543 5089 28.28088 Heavy Oil M450A-10 19.6 2449 85.9 7921 1901 2130 20020029 M45OA-11 22 2733 85
.9 8842 2122 2377 20%24x33 M45OA-12 24 3016 86 9758 2342 2623 20024x37 M450A-13 26 3300 86 10675 2562 2870 24%24x40 M450A'-14 28.5 3583 86 11592 2782 3116 24024044 M450A -15 30.5 3867 86 12508 3002 3363 24%24x47 M4SOA-16 33 4151 86 13429 3223 3610 24.28x53 M450A-17 35 4434 86 14346 3443 3856 24x28059 M450A-t8 37.5 4718 86
.1 15263 3663 4103 24x28165 M450A-19 39.5 5001 86.1 16179 3883 4349 28028.71 M450A •.20 41.5 5285 86.1 17096 4103 4596 28%2807 M460A -21 44 5568 86.1 18013 4323 4842 28%28x82 The above raorgs are based an 12,5% C02 (o9) or 9.5% C02 (gas) and -0

.02 in wafer draft (light oil) or-O6 in water(heavy ail). M45OA-22 46 5852 86
.1 18929 4543 5089 28x28088 ' Insed S for Steam

. W for Water Boilers 650A Mills Seres Power Burner, Natural Gds 690A--15 7732 6247 82.1 20208 4850 5432 28028047 650A--'-t6 8258 6672 82.2 21583 5180 5802 28%28x50 650A '-17 8784 7098 823 22983 5511 6172 30030.52 6500-18 9309 7523 82
.3 24338 5841 6542 30x30'54 650AV-19 9835 7949 82
.3 25717 6172 6912 30036x56 6500--20 10361 8374 82 4 27092 6502 7282 30%36x58 6500-21 10887 8799 82
.4 28467 6832 7651 30x36.61 6500-22 11412 9225 82.4 29842 7162 8022 30x36064 650A -23 11938 9650 82,5 31217 7492 8391 36%36x67 650A--24 12464 10076 82
.5 32596 7823 8762 36e36x69 650A-'-25 12990 10501 82
.6 33971 8153 9131 36x36071 Heavy Oil 650A--t5 50 6247 84
.7 20208 4850 5432 28028.47 650A-M6 53 6672 84
.7 21583 5180 5802 28x28150 50A M7 57 7098 84
.8 22963 5511 6172 30x30,52 50A MB 60 7523 84
.8 24338 5841 654230. 0.54 50A-'-19 64 7949 84.9 25717 6172 6912 30x36056 50A-•-20 67 8374 84
.9 27092 6502 7282 30x36,58 ""500=-21 ]0 0 8799 85 28467 6832 7651 30036x61 ;4 922 85 29842 7162 8022 30036x64 50A--23 77 9650 85 31217 7492 8391 36036,67 640A-24 81 10076 85 32596 6 7823 8762 36036.69 6500'-25 84 10501 85
.1 33971 a 9131 36036.71 The above ratings ate based on 12

.4C02 (ail) and .0.02 in. water droll. 6500A Mills Series Power Burner, Natural Gas 500A-'-15 8936 7194 81
.9 23271 5585 6256 30x30055 II6OOA--16 9805 7872 81.7 25467 6112 6845 30%36x61 515000--17 6500A-18 10674

11543 8550 9228 81
.6

81.4 27656

29854 6638

7165 7435 30x36066

8024 30.36x72 5000'-19 12412 9906 81.3 32046 7691 8614 36%36x77 500A-20 13281 10584 81.3 34238 8217 9203 36%36x83 6500A-'-21 14150 11262 81 .2 36433 8744 9793 36036088 5000'-22 15019 11940 81
.1 38625 9270 10383 36036094 5000-'-23 15888 12618 81
.1 40821 9797 0 097236.4 99 5000

-24 16758 13297 81 43017 10324 11563 366420105 65000'-25 17627 13975 81 45208 10850 12152 36x42%110Boiler Fuel Boiler Nameplato Input Gas Oil I=B=R Net 1=B= Gross Comb. Output Effie. SteR Rating

am Steam Vent Water Size Manufacturer TypelSerios Type Model MBh gph MBh % Sq.Ft

. MBh MBh (Oil)

L6500A Light Oil 16504•'-15 62 7194 84
.4 23271 5585 05 625630.3 5 6500-'-16 6B 7872 84.2 25467 6112 6845 30136961 6500-'-17 74 8550 84
.1 27658 6638 7435 30036,66 6500-'-18 80 9228 84 29854 7165 8024 30x36072 6500-'-19 86 9906 83.9 32046 7691 8614 36x36077 6500=-20 92 10585 83
.8 34242 8218 9204 36x36083 6500-21 96 11263 83.7 36438 8745 9794 36036x88 6500=-22 104 11941 83,6 38629 9271 10383 36036.94
" 6500-'-23 110 12619 83
.6 40821 9797 10973 36042099 6500-24 116 13297 83.5 43017 10324 x10 1156336.4 5 6500=-25 122 13975 83,5 45208 10850 12152 36.420110 Heavy Oil 16500A -M5 58 7194 84.4 23271 5585 6256 30030655 500A-16 63 7872 84.2 25467 6112 6845 30036061 SODA-M7 69 8550 84.1 27658 6638 7435 30.36.66 500A'-18 75 9228 84 29854 7165 8024 30036072 500A--19 80 9906 83.9 32046 7691 8614 36036177 6500A -20 86 10584 83.8 34236 8217 9203 36036.83 500A-'-21 92 11262 83.7 36433 8744 9793 36036088 50OA-22 97 11940 83.6 38625 9270 10383 36036094 6500A-'-23 103 12618 83
.6 40821 9797 10972 36042.99 6500A-24 108 13297 83,5 43017 10324 11563 36,42,105 6500A-25 114 13975 83 5 45208 10850 12152 36x420110
A.O. SMITN WATER COPPER

II Genesis Series Naloral or Propane GB 500 500 425 85 370 PRODUCTS GB650 650 052.5 85 440 COMPANY GB-750 750 6375 85 554 GB-1000 990 8415 85 732 G8-1300 1300 1105 85 961 G8-1500 1500 1275 85 1100 G8-1850 1850 1572.5 85 1367 G8-2100 2100 1785 85 1552 58-2590 2490 2116.5 85 1840 G80-500 500 425 85 370 G80-650 650 052.5 85 480 G80-750 750 637.5 85 55.1 G80-1000 990 8415 85 732 G80.1300 1300 1105 85 961 G80-1500 1500 1275 65 1109 080.1850 1850 1572 5 85 1367 G80-2100 2100 1785 85 1552 080-2500 2490 2116 5 85 1840 a Legend 20DO Natural Gas LO -500 500 450 90 301 L8-750 750 675 90 587 LS-1000 1000 900 90 783

THERMO. STEEL DYNAMICS HT Series Forced Drag, Light Oil BOILER COMPANY

ULTIMATE CAST IRON ENGINEERING Series PFO and PFO-T Forced Draft, Light Oil CORPORATION

UTICA CAST IRON BOILERS Y J-B Sones Pilot, Natural Gas Division of ECR Intemaianal, Inc

. Notes

The above ratings are based on 12.4% C02 and -0.02 in waterdraft.

The above ratings are based on 12.4% C02 (oil) and +0.10 in water draft. ' Insert "S" for Steam or "W" for Water

HT-225 2.25 264 85.6 230 HT-250 2.5 291 85.2 253 HT-275 2.75 319 84,9 277 The above are based on 13.2% C02 for the HT-225.13.4% C02 for the HT-250, and 13.6-,C02 for the HT-275 a1
-0 The above rating is based an 12

.25% C02 and

-002 in wafer draft. 02 in waterdraS ofthe vent.

PFO-7-2.35 2

.35 277 85

.2 241 7"Vent PFO-9-3.00 3 354 85,2 3088"Vent PFO-8T-215 2,75 325 85.2 2838"Vent The above ratings are based on 12 5% C02 and +0.1 inch water over fire.

J-30081 300 240 80 750 180 209 J-39961 399 319 2 60 996 239 277 J-40081 400 320 60 11100 240 278 J-50081 500 375 75 1171 281 326 J-60081 600 480 80 1500 360 417 J-70081 700 560 50 1750 420 487 J-00081 800 040 80 2000 480 557 J-90081 900 720 80 2250 540 626 J-400081 11100 800 80 2500 0 000 695 J-110081 1100 880 80 2750 060 765 J-120081 1200 960 80 0 30 720 835 1-130061 1300 1 040 80 3250 780 904ANUARY 200216R DIRECTORY - COMMERCIAL BOILERS

Boiler Foal Boiler Nameplate Input Gas Oil 1=B=R Not 1 =B=R Rating Gross Cemb. Output Eflic. Steam Steam Vent Water Staa Manufacturer Type/Sari.. Type Model MBA gph MBh % Sq.Ft. MBh M8h (Oil) Notes -140081 J-150061 1400

1500 1120 1200 80 3500 640

60 3750 goo 974 1043 -160081 1600 1280 80 4008 962 1113 -170081 1700 1360 80 4203 1026 1183 0-185551 10 1440 80 4563 1005 1252 -190081 1900 1520 80 4838 1161 1322 J-200081 2000 1600 80 5117 1228 1391 J-210081 2100 1680 80 5392 1294 1461 J-220081 2200 1760 80 5671 1361 1530 1-230061 2300 1040 80 5943 1426 1600 -240061 2400 1920 80 6213 1491 1670 -250081 2500 1999 80 64667 1552 1738 Stadia, Steam Sends Light Oil SF06225 2
.25 251 83.3 783 188 218 8,12,15 S FH7275 2.75 307 83.3 958 230 267 8,12,15 he above ratings are based en 13,10% C02 and -0.02 inches water draft. Stertire Water Series Light Oil SF 6225W 2.25 251 83
.3 218 8,12,15 56407275W 2.75 307 83

.3 267 8,12,15 he above ratings are based on 130°i1COS and -0.01 in, water draft

IESSMANN STAINLESS STEEL IANUFACTURING It Veoomat Farcrnl Draft, Natural or P.P. 050-10 398 358.2 89.9 310 OMPANY VSB-":3 488 439.1 89,5 382 VSB-17 638 575.6 90.2 501 006-22 846 763.3 90.2 664 VSB-28 1071 9663 902 840 056-37 1389

1 1252 5 90.1 1080 006-46 000-57 7200

2100 1557.2 1948.8 902

902 1354 1695 VSB-72 2702 2437.7 90 2 2120 VSB-89 3301 3032.3 90 2 2637 CAST IRON it Vibgas 100-GS10 Sor Two Stage, Natural or Propene 0010-72 300 257 856 223 GS10-S4 G510 96 340

380 291 325 856

85 6 253 283

- o Vitopus 50-RS Natural or Propane 95.08 550 465.5 83 397 RS-11 800 664 83 577 95-14 1050 8715 83 758 itAlola-RN Sans Two Stage. Natural or Propane RN315 315 268 85 233 RN350 350 298 85.1 250 RN-385 385 328 85.2 285 l: Randomal 4W0 Farrar! Pratt, Natural or Propan RMT-125 508 427 84.1 371 901-160 650 546 84 475 RMT-195 792 665 04 578 RMT-230 034 785 64 883 RMT-270 1096 921 04 801 N Rondoma15000 Forced Draft, Natural or Prope 951-320 1300 1092 84 950 RMT-380 1544 1297 84 1128 RMT'-140 1787 1501 04 1305 507-500 2031 1706 84 1483 953-560 2275 1911 84 1662 Rid -630 2559 2150 ITT 1070 901-700 2843 2388 84 2077 401-780 3168 2661 84 2314 RMT-860 3493 2934 84 2551 001-910 3696 3105 84 2700 8511-1060 4387 3685 8- 3204
WATERPIK COPPER TECHNOLOGIES, o MighlyThemr Songs C Indoor 804c,; Natural or Props HH325 325 263 25 01 229 INC. HH400 400 324 81 282 Leers Healing Systems OutdoorBOiler, NaturaI., Prop HH325 325 260 80 226 HIT 00 400 320 80 278 Al. approved wall PreOo'PH". 7 MightyThemt Series C Indoorl0uldoor. Natural Gas HH04000 400 333 83.4 290 0 MightyThemt Series E Outdoor, Natural or Propane HH050D 500 410 82 357 11HO60D 600 492 82 428 HH0715 715 586, 3 82 510 HH0850 850 697 82 606 HH0999 999 819.19 82 712 0H1010 1010 828,2 82 720 881200 1200 984 82 856 0H1400 1430 1172.6 82 1020 HH1670 1670 1369A 82 1191ANUARY 2002 ISR DIRECTORY - COMMERCIAL BOILERS Nameplate Input I=B=R Gross Net I=B=R Rating

Comb. Vent Monu(aclurer Boiler Fuel TypelSeries Type Boiler Model Gas Oil

MBh gph Output MBh Effic. Steam

Ce Sq.Ft. Steam MBh Water Si.

MBh (Oil) Notes HH1825 1825 1496.5 82 1301 0H2200 2205 1786.05 81 1553 HH2800 2745 2223,45 81 1903 HH3200 3150 2551.5 81 2219 HH3600 3845 205224 81 2567 HH4770 4050 3280.5 81 2853 HH4500 4500 3845 81 3170 Also approved with Prefix'PH' far sizes 500 lhm 1325, II MightyTherm Series 1 Indoor Boiler, Natural or Props HH0500 500 405 81 352 000600 600 486 81 423 HH0715 715 579.15 81 504 480860 850 8 x88.5 81 599 HH099S 999 809.19 81 704 HH':010 1010 818.1 81 711 001200 1200 972 81 845 HIT' .430 1430 1158 3 81 1007 HH1670 1670 13527 81 1176 HH1825 11125 !47825 81 1285 Iso approved with Prefix'PH' Indoor. Inter Ign. Naluml or P HH2000 1999.9 1639 918 82 1426 H02450 2450 2009 82 1747 HH3050 3050 2501 82 2175 H03500 14H4050 3500

4050 2870 3321 82

82 2400 2888 0H4500 4500 3090 02 3209 HHS000 5000 4100 82 3565 N Mighty Therm Senes 8lndoar Boiler, Natural or Props HH0500 600 410 82 357 HH0GOD 600 402 82 428 H00715 715 586.3 82 510 H00850 850 697 82 606 400999 999 81910 82 712 H01010 1010 828.2 82 720 HH1200 1200 984 82 850 H H1430 1430 11726 82 1020 991670 1670 1369 4 82 1191 HH1025 1825 149'0.5 82 1301 Iso approved with Prefix "PH" (or sizes 500 Bra 1825. S lAghty Man Senns Indoor Boiler, Natural or Pmpal HH0320 320 272 85 237 H00400 400 339.2 85 295 H00520 520 442 85 384 000625 625 531 3 HS 462 H00775 775 8568 85 573 HH1000 1000 650 85 739 Outdoor Boller, Natural or Prop HH0320 320 2656 83 231 060400 400 331.17 83 288 060520 520 431.9 83 375 000625 625 518.75 83 451 080775 775 643.25 83 559 H81.000 1000 830 83 722 Also approved adh Prop, 'PH'

EIL-MCLAIN SPX Company CAST IRON

N PFG Seres 6 Pilot, Natural or Propane PFG-6-SPN 305 247 61 215 PFG-7-SPN 360 206 81 257 Inter. Ign, Natural Gas JPFG-6-PIN 305 247 81 215 PFG-7-PIN 366 296 81 257 Inter Ign , Naluml or Propane PFG-8-PIN 427 346 81 301 It EG Senes 4 Pilot, Natural or Propane EG-75-S 300 240 80 750 180 209 Into Ign„ Natural Gas EG-75-PI 300 240 00 760 180 209 Damper, Inter. Ign., Natural Go EG-75-PIDN 300 240 80 750 180 209 Damper. Pilot Natural or Prop EG-75-SPD 300 240 80 750 180 209 Above ratings are also approved for boilers with prefix P and Seth, SPN

. 0 EGH Senes 4 Pilot, Natural or Propane 1 H,11' 350 280 80 875 210 243 EGH-95' 400 320 80 1000 240 278 1
EGH-105' 450 360 80 1125 270 313 EGH-115-Pll 500 400 80 1250 300 348 EGH-125-PI 550 440 80 1375 330 383 'The above ratings are approved for boilers with suffix PIN, SPN and SPL. N LGB Sen.., 2 Pilot, Natural or Propane 1 11 400 324 61 1013 243 282 LGB-5 520 421.2 81 1317 316 366 1LOB-6 050 526.5 81 11145 395 4.58 LGB-7 780 631 fl 61 975 474 549 LGB-8 910 737.1 81 2305 553 0141 LGB-9 1040 6.424 81 2635 032 733 SPL, N and LJANUARY 20021 BR DIRECTORY - COMMERCIAL BOILERS Nameplate GB=R Net luB=R Rating Input Gross Comb. Vent Boiler Fuel Boiler Gas Oil Output Effie. Steam Steam Water Size Manufacturer TypelSeries Type Model MBh gph Mill, 56 Sq,Ft. Main MBh (Oil) LGB-10 11]0 977,7 81.1 2965 711 824 LOS-11 1300 1053 81 3290 790 916 LGB-112 1430 1150.3 81 3620 869 1007 LGS-13 1500 1263.6 E1 3955 949 1099 LOS -14 1690 1368.9 E1 4315 1035 1190 LGB-1S 1820 1474.2 81 4680 1123 1282 LGB-16 1950 1579.5 81 5645 1211 13]3 LGB-17 2080 1684.8 81 5410 1298 1465 L0 B-18 2210 1790.1 81 5775 1386 1557 L0B-19 2340 1895.4 81 6125 1410 1648 LGB-20 2470 2000.7 81 6470 1553 1740 LGB-21 2600 2106 81 6815 1635 1831 LGB-22 2730 2211.3 81 155 11717 1923 LOB-23 2860 7 2319.6 81 7495 799 2014 WGOIWTGO Gold Serie Light O8 IWTM/G0-8 2 3 266 65 2318x12,20 WTIWGO-9 2 55 295 65 257 8.12.20 SGO Gold Series 3 Light Oil ISGO.BW 2 3 266 85 231 8,12,20 500-9W 2. 55 295 85 257 8,1240
500-8 2 3 266 85 833 200 8,12,20 500-9 2. 55 295 85 921 221 8,12,20 78S.... 1 Forced Draft, Nalual Gas 378 346 278 82 871 209 242 8' Vent 78 494 400 81.9 1250 300 348 8' Venl 578 641 521 81,9 1629 391 453 8" Vent 676 789 643 81.9 2008 482 559 8'Vent 778 937 764 81.9 2388 573 664 10 Vent 878 1084 886 81.9 2771 665 770 10 Vent 978 1232 1007 81.9 3146 755 876 10"Vent 1 078 1379 1129 81.9 3529 847 982 1 0"Vent 1178 1527 1250 81.9 3908 938 1087 10"Vent 1278 1674 1372 81.9 4329 1039 1193 12' Vora Forced Draft, Light Oil 378 2

.4 278 84

.5 871 209 242 8" Vent 78 3.4 400 84

.5 1250 300 348 81 Vent 578 4.45 521 84.5 1629 391 453 6" Vent "78 5.5 643 84

.4 2008 482 559 8" Vent 778 6

.5 764 84,4 2388 573 664 t0" Vent 878 7.5 886 84.4 2771 665 770 10" Vent 978 8,5 1007 84.4 3146 755 876 10" Vent 1 078 9.6 1129 84.4 3529 847 982 1 0' Vent 1178 10.6 1250 84.4 3908 938 1087 10" Vent 1278 11.6 1372 84.4 4329 1039 1193 12"Vent 811 Series I Forced Draft, Nalual Gas 4880 996 794 81.9 2483 6596 690 1(i Vent 88 1010 810 61,9 2533 08 704 10Vent 588 1357 1084 81.6 3388 813 943 10Vent 688 1703 1358 81.4 4275 1026 1181 10'Venl 788 2049 1632 81.3 5225 1254 1419 12' Vent 868 2396 1904 81.2 6154 1477 1656 12 "Vent 9888 2482 1991 81.2 6442 1546 1731 14"Vent 988 2713 2176 81.2 7038 1689 1892 14"Vent 10880 2887 2304 81.1 7454 1789 2003 14"Vent 1088 3103 2452 81.1 7933 1904 2132 14"Vent 1188 3392 2724 81.1 8613 2115 2369 14'Vent 1288 3753 3000 81 9704 2329 2609 14"Vent 1388 4113 3270 81 10579 2539 2843 14"Vent 1488 4474 3550 81 11483 2756 3087 16ent 1588 4763 3820 81 12358 2966 3322 16Venl 16880 4979 3980 81 12875 3090 3461 16Vent 1688 5124 4090 81 13229 3175 355716 Van' 1788 5485 4370 80.9 14138 3393 3800 18"Vent 1888 5845 4640 80
.9 15008 3602 4035 18"Vent Light Oil, Forced Draft 88R 6.9 794 84.4 2483 596 690 10'Vent 88 7 810 84
.4 2533 608 704 10"Vent 588 9
.4 1084 84
.1 3388 813 943 10"Vent 688 11.8 1358 83.9 4275 1026 1181 10"Vent 788 14
.2 1632 83
.8 5225 1254 1419 12 "Vent 888 16
.6 1904 83 .7 6154 1477 1656 12"Vent 988R 17.2 1991 83,7 6442 1546 1731 14"Vent 988 18.8 2176 83.7 7038 1689 1892 14"Vent 10880 20 2304 83.6 7454 1789 2003 14"Vent 1088 21.5 2452 83.6 7933 1904 2132 14"Vent 1188 23
.5 2724 83.6 8813 2115 2369 14"Vent 1288 26 3000 83.5 9704 2329 2609 14"Vent 1388 28.5 3270 83.5 10579 2539 2843 14"Vent 1488 31 3550 83.5 11483 2756 3087 16"Vent 1588 33 3820 83.5 12358 2966 3322 t6"Vent 16880 34
.5 3980 83
.5 12875 3090 3461 16"Vent Noles

The aboveralings are based on 13,0% CO2 and-0,02 in waterdralL 'Also approved in, area. P,B orA.

The above ratings are based an 13,0% CO2 and -0.02 in wafer draft, 'Al.. eppmved with pref,P.B orA

The above ratings are based on 13.0% CO2 oil or 10% CO2 gas and -0.10 in al vent.JANUARY 20021 BR DIRECTORY . COMMERCIAL BOILERS Nameplate 1=B=R Net I=B=R Rating Input Gross Comb. Vent Boller Fuel Boiler Gas Oil Output ER.. Steam Steam Water Size Manufacturer Type/Series Type Model MBh gph MBh % Sq.Ft. MBh MBh (Oil) 1688 35.5 4090 83,5 13229 3175 3557 16"Vent 1788 38 4370 83,4 14138 3393 3800 1Vent 1888 40.5 4640 83.4 15008 3602 4035 18"Vent 94 Sans 3 Nalunl Gas, Forced Draft 894 2540 2028 81.2 6563 1575 1763 14"Vent 994 2887 2320 81.2 7504 1801 2017 14"Vent 1094 3247 2612 81.3 8450 2028 2271 16"Vent 1194 3608 2904 81.4 9396 2255 2525 16"Vent 1294 3969 3190 81,4 10321 2477 2774 r&Vent 1394 4330 3480 81.4 11258 2702 3026 18'Vent 1494 4691 3770 81.4 12196 2927 3278 18"Vent 1594 5052 4070 81.5 13167 3160 3539 18" Vent 1694 5412 4360 81.5 14104 3385 3791 18" Vent 1794 5773 4650 81.5 15042 3610 4043 20 Vent 1894 6134 4940 81.5 15979 3835 4296 20 Vert 1994 6495 5230 81.5 16921 4061 4548 2034001 2094 6856 5520 81.5 17858 4286 480020 Vent 2194 7216 5810 81.5 18796 4511 505220 Vent 2294 7649 6100 81.5 19733 4736 5304 22 Vent 2394 7938 6390 81.5 20671 4961 5557 22 Vent 2494 8371 6680 81 5 21608 5186 5809 22Venl 2594 8660 6970 81.5 22546 5411 6061 22"Vent Light Oil, Forced Draft 894 17.6 2028 83.7 6563 1575 17631434ent 994 20 2320 83.8 7504 1801 2017 14"Vent 1094 22.5 2612 83.8 8450 2028 2271 1634e81 1194 25 2904 83.9 9396 2255 2525 WWII 1294 27.5 3190 83.9 10321 2477 2774 1634en1 1394 30 3480 83.9 11258 2702 3026 l8Went 1494 32,5 3770 83.9 12196 2927 3278 18"4001 1594 35 4070 84 13167 3160 3539 t8"Vent 1694 3].5 4360 84 14104 3385 3791 18'Venl 1794 40 4650 84 15042 3610 4043 2034en1 1684 42.5 4940 84 15979 3835 4296 2034001 1994 45 5230 84 16921 4061 454820W' l 2094 47.5 5520 84 17658 4286 4800 2034001 2194 50 5810 84 18796 4511 5052 2034e11 2294 53 6100 84 19733 4736 5304 2234e11 2394 55 6390 84,1 20671 4961 55572234001 2494 58 6680 84.1 21608 5186 5809 22"Vent 2594 60 6970 84.1 22546 5411 6061 22 "Vent Heavy Oil, Forced Draft 894 16.6 2028 83,6 6563 1575 176314"Vent 994 19 2320 83,6 7504 1801 2017 1434e11 1094 21.5 2612 83.6 8450 2028 2271 16"Venl 1194 24 2904 83.6 9396 2255 2525 16"Vent 1294 26 3190 836 10321 2477 2774 16"Vent 1394 28.5 3480 83,6 11258 2702 3026 1834e11 1494 31 3770 83,6 12196 2927 3278 1834e51 1594 33 4070 83.6 13167 3160 3539 18"Vent 1694 35.5 4360 83.6 14104 3385 3791 18"Vent 1794 38 4650 83.6 15042 3610 4043 2034001 1894 40.5 4940 83.6 15979 3835 4296 20"Vent 1954 42.5 5230 83.6 16921 4061 4548 20"Vent 2094 45 5520 63,6 17858 4286 4800 20"Vent

AVERAGES 82.50 Notes The above ratings are basedon 12.5% C02 (oil) or 9.5% C02 (Gas) andl• 0

.10 in at the veni The above raliI's are also approved (or boilers with prefix BL. BG, BGL, ABL, ABG, ABGL, PG, PL and PGL and suffix WF and SF.

The above ratings are based an 12.25% C02 (oil) or 9.5% C02 (ga)s and 0 0,10 in at the went. The above ratings are also approved far bailers with piefit ABG, ABGL, ABL, BL, BGL, SO, PL, PG and PGL and suffix WF and SFiuARY 200216R DIRECTORY -COMMERCIAL -LEND

uel Manufaclumr TypelSeriea Typa A%EMAN STEEL ANDERSON P025enes Ligh1011 COMPANY

BBDERUS CASTIRON HYDRONIC 315 Series Power earner. NaluralGaz SYSTEMS

.e...., Oil 3153enes (Canes 050(04

15Senes Light Oil

ower BUmar, Natural Gas meplalo alaput Thermal Biller Gas .11 EMC. Medoff MBh gDh Y•

109770 2.4

4,1.1 80
.

G15-7 678 2 GII I 01 02

. G3139 934 3.1

. 2, Ell

G315_5 3 833 G3156 -1 84 2 3t5-> 47 05

. G31 8 56 04

. G31S9 6 057

17 G51 I S 84 B56 GSii9 05.6 G5t S10 116 85] 0315 t3 07.

.. 17

12 140 e6

.117 991 821 G11. 1216 83. G5159 1438 035 1660 83 EfOC Thomlai Ez. "1 11, TIEIf'rCi11 OlRerenco EMC

. Oft-- .. ,. % ..

82 .4 03

ED 1 34 817 2.6 824 2

. 0 82.8 16 83 .1 14

i 27

833 35 21 05.0 20 846 25 5] 14

847 1 858 4 2.3 8 ) 2.4 808 3 1.1 06 13

82

. 2 3.4 03

.0 25 835 9 26 83 B=R the=RR 9 Gross Comb. a Vent Output EMC

. Steam Steam Water SMe MBh % S9.Ft. MBh MBh (Oil)
2]7 827 867 200 2418.12.15

350 84.2 3048xi2x15 454 843 39512x12x1x 59 04

. 4 48612.2x15 3 84.4 S 1211615 760 045 66012,16x15
"1 h5] vo 8.92.

350 866 3048,12x15 454 069 39512x12.15 15 87 61212.15 663 0I1 5]712.16x15 ]fib 07.1 66812x16,15

18,2 711 12xt6a1x .,1 1009 802 077 16x16.15

1 -1 1392 121016.20x15 583 80 .1 137]16x20,15 1 00.1 154316.20x15 775

01 056 ]1112x1fix15 1009 05 877 t6xtfixts 5 6x15 392 85 5 21016 20 1x

615Genes Power Burner. Natural G. . GSi S11 881 842 .515-12 2103 844
G111 23119 "1 .15 2671 - 0031 . 84.2 12 844 10
84.5 -14 840 83. 1 O 83.2 0.0

0 :2S . 1 x x 1583 05.4 13]]16.20x15 1775 054 154316.20x15
1951 1950 1

14 4 2242 84
. 1 1950 4 2532 84 2202 14 2E22 I 2454

'

lghl Od

RNNAM CAST IRON CORPORATION Va 18nes Light Oll G6'15-I' 47; 11 G615-16 ^0?J n

iA 7.1 G615-10 10

. 5 21 Gfi15-it 861 G615-12 23. 5 05.0 G115 t3 Gfi15t4 28

. 5 853 G61511 31 851 GOO 16 33 .1

235 835 VS9W 2. 6 82.1 B0 2,35 80

. V89S 26 I, 1 1. 02] 1.2 025 024 1.5

81.1 -04 866 0 .1 86.1 .1 850 85x 10 85.3 12 831 84.9

836 11

111 31 019 22 2706 3112 I3 P 3402 83 2958 18 3592 83 3210 8 3902 83

.9 3963 18
1911 efi.> 169] 2242 86.7 19x0 2532 86.6 2202 14 2454 16 3112 86.1 2706 16 3402 865 2958 18 3210 18 3902 06.5 3463 18

275 84.2 299 R4 1 2600.12x15 266 84.2 833 200 Sxi2x15 290 84

. 1 933 224 8.12x15 VIA Senes Nat..' Gas, ForcM Ora11

gltl il. Fbrcetl Oran

t Senes Naluai Gas. Forced Orall V90J 447 ]7.4 V504 606 79. V. 1.. 111 1010 V506 80

. V907 1198 80

.1
11 ED V909 1674 910 1905 002 236 802 V912 236]
V903 3.1 79.7 4.2 82.1 V905 56 906 7 824 V. 8. 3 82.5 V540 909 111 132 S27 911 14.8 827 912 16

.4 02.8
V 117 797 1105 1068 1. 2 J 106 328 5 77.4 12 ]B] 17 80

.0 2.9 80.0 2] 00.1 2

.4 1 23 80.2 2.1 802 2. 0 802 0 803 1.0
797 5 82.1 3 824 3.1 82.4 2.8 825 28 826 2.3 826 22 027 21 027 21 828 19
79.7 3.1 002 2.4 6 820 260 301 7Neh1 41 3 4 100 362 420 7' Vent 646 029 2021 405 Sfi28Nl 808 027 2525 606 ]038Nen en 959 21 2996 719 8311- 1110 024 34]1 833 965IO-- 1342 02

.3 4225 101 116]10- 1528 022 48fi> 111 32910'Venl 1]14 822 5513 9012Nenl 900 02.1 6142 14]4 165212-Vent 34 85 .2 250 Venl 483 6 1508 HE 42D Venl 696 855 2021 485 5628Ve1 800 852 2525 7030'Ve1 959 85 .1 7,E 834 Venl 1310 84

.9 3471 833 96510 LI 1342 84

.0 4221 1014 tt6]10'Vent 1528 13290Vent 1714 84> 1323 100 ' 1' 2: 1900 847 6142 14N 1--Veal IS 82.8 2083 1. 0 -1 SE 026 2671 643 74-1 1 1 80 807 vi 103 1076 BO

. 1109 2136 80

. 1110 2396 S Bt 1 285 vi 3 805 1 80] 1.7 89 809 81.0 14

81.1 1.1
80] 80.5 14 1069 02 .45 334 802 9308N0n1 1281 12 4 1517 1729 023 5563 1335 150310-11 1941 02

.2 62]9 1507 1608 12'Venl 2154 822 596] 1672 10]312Nenl 2334 082 75x0 1012 2130 12Nen1 2513 82 8096 1943 2177 12"' 2]30 819 8833 21. 2374 14' ", 111 J 11'S ?991 c91

' r t'. 20 71
11L'. if`. 112.: X7.1 71 804 1

.4 903 to 80.1 11 SoI 16 797 1] 9 79.2 18 790 18 -4 13 2957 81

.8 956] 2296 257114Nen1 3129 01.7 10113 2421 211814Nenl 3311 Si] ICS46 2603 916142 3500 11583 2]00 3111 3]39 2903 3251 I-Z 395] 81

.2 128011 30]2 3441 16JVeal 41 )4 3241 36011-1 4334 1. S 14021 3365 3]69 18 t 45x1 80.7 14721 3533 395]8- Ill, bove ratngs nre I,-- 12 0°%C02 and .002 ia wale, draft

he above al- ore based -10 0%C02 s
-002 daft al I-- Th. aLC.^. a..eu an 30:x C0 1. tl 01 oats t?n vev

fne above ralings are based Ca 13 0%C02 and 0 02 droll ai the vent

fhe above alings are based on 13.0%402 and .002 droll aI the wens

fhe above .I-era 0.-- 10 o%C02

he above ratings are based on 10 .0%C02 - W 10' at ft veal

he above slings are based on 130°%C02 an0 0

.177 al the veal

above ratings are -d on 13 0%C02 and-0 02' water doll ovedae

he above .finis are based oa 9 7% C02 aM+010 in water d.ft al Ne vent



### above, g re baaaa an us%eoz and .amm. wme,drnnaune .em.

above l.trq. are based on 10.0%C02 aM W.10.n. weler denV11 series Light Od, Forced D.ft

STEEL Op-ol Series Light 0i1 R1AGeees L1gM11011
Series E L1gh1011, Forced Dab

Natural Gas. F-d Dra11

CROWN -11.0. BOILER I,—. Series Li9M11 Oil. Forced D.11 COMPANY F Series Li081 Oil, Forced Doe 101-3325 225 8481
RP240 78 1 -.1 2 05 7 . 6 .1 B E30 91 019 650 1 E. 83.5 at 81. E t 6p 0 .5 E71 21 ' 3a E0p 24 14.
E20 8)8 100 E30 )) E40 8 80

.7 150 9 6'i

25 81]
3 845 S 854 Ffi 85] 6 804

1 2.5 9 86.6

33 30 577 :2 72 831 35 8 02 1299 84.0 Natural Gas FO![M-It S f6

F9

1311 RICW STIRON MAGNA GT210 Series NalaralGas G217A

GT210A Light 0.1 GT21M
4112171
GT300A I.,- N.1-1 Gas, Forced D.Q

L1gM1t .0, Forced -ift GT21M

!JiI

G304A 4113051 361 GT30)A GT30 GT3010

9A 323 359 ]9.

2,21 25 82
4044 795
5 03.1
ID^ 23

1 411 1)32 '2 1 GT AA '009 025 GT .5 829 GT411A 2562

1 411 .T4 9A GT410A GT411A
GT413A GT416A GT516d 821 82 ) 667 85> 85.3 2083 500

111 2619 643 5808Venl 7458Nen1 830 20 834 1069 1201 05 334 802

84

.9 4013 963 306Venl 10Ven

83.4 835 51] 1729
1 ' ' 86 .9 4829 1159

84

.0 5563 1335 84 17 731910Nen 1503 10•Vel 1688 12 11 834 54 21 2334 84 B 196> 1672

66 7550 1812 1073 12Nen1 203012Ne1 832 2503 86.5 8096 1943 21P 12Vel 830 23D 644 8633 2120 23]414Nenl 828 828 2157 3129 84.3 9161 2297

84 .3 10113 242] 2518 140241 271814Venl 82 16 82 6 3363
3580 842

I, I 18583 2)80 3113 IIZ2 822 18 3739 395] 83.9 12096 2903

637 281` 3072 325 16Ven1 3441 16Nen1 81] 15 4174 4334 83.5 13504

3.3 14021 3365 3>6918Ven1 81.3 19 451 83.2 14721 3533 3957 18Nen1 M1e above ratings are b-d on 13D%C02 arN .0.101x. water-It

ed_e 6] 865 2320212x15 M1e above .11495 are based on 13.5%.02 aM O In wale, al vent
]9.0 26 84.2 233 0212x0 7911 31 83.2 2 821220 be above ralieol are based on 12.5%C02 antl-NO in. wafer doll.
80.1 38 684 83) 2130 513 59510Ven1 819 2.3 835 1 3 42 80 1402 86. 2 3258 782

84 8 4429 1063 907 104741 121910Nen1

. 19 18 1 ]4 . 837 5613 1347 156 12Nen1 0
' l S 18 10 09 70 2 2661 86 .1 fi8W 1632 86 6 7963 1911 Ill. 12-1 21012Ven1 1 1 2821 5 .1 9125 2190 245312-1 be above, g re ba^tlan 12.5% C02 aM I.tOin. -1-1 lM1event. ]00 66 61.2 2136 513 1111 1- 79.7 007 p2 1) 321 702 3 44 p63 8 . 9D] tNenl 21910N l 79.0

H 1743 3. -1 56 3 347 en 151612Ven1 790 2 1" 2461 8

82 ]63 11 2' V11



# 114 1
12 2621 .1 28 9125 2190 

# Nen

0 121
N5312Nen M1e abaver rig are basetl on 0]°b C02 arM+. 10 n. wafer al M1e vent.

61) 286 033 2498.12x15 Te above ralings are basetl an 13 0% COS antl -0.021x.41112 vent.
355 BS 309 ]Next 1, 4 470 B5 4161Venl 5 7 Bfi 41 Olo ]2 4 9

14 9 5221Nenl 111


# - 1 1 116 Bfi 6 901 i .1 0 7

14 

# 711 949 tOVenl M1e a1ove,47x95 are based oa 121%C02 antl I- fer tlrall atTM1e vent. '2 1 11 355 82 309 )v ^I 820 03 478 02 416 831 831 )

t 723 826 02.6 5228Ve1 6299Ven1 840 -1 50) 1091 023

02.2 76910' Venl 11110Nenl ratings are basetl on 91%C0242+0. 1014 . wafer dra0 tTh. vent 1--

11 44 25 043 2248:12x15 ; 99 4d 287 843 2608.12x15
010 8 224 81 2x15 820 287 069 250821 2x1 5 0e above ralings are based an 13 0%C02 antl -0 02 at I6e vent 711 14 296"Ven1 34 17 498 024 7' Ve41 17 13 12 8 3 )6 9' Vent e19 80.4 5

3.2 826 036

' 6 >10 tD'Venl

l 800 3) 1154 ] :3 -3 10 0"V'd Ire above ralings are Wsed en 10 0%C02 aM 001 In water tlrall

054 321 135 2)1311111 1 Venl 4 062 058 5)6 9"Vnl 83 022 26 990 02

8 71810'Vent 0 Vent 02 E 1154 86.3 006 4 " 4310'Venl Aeabove 140405 are based 1113 )% C02 and 0 01 11 -1111111 2p 04 20 81 .6 1235 12' Venl 025 121 0.5 1 1650 95 02

62 3 14,4 12'Ve91 1 4 14" V t 033 08 2133 . 82.5 0 en 1 55 14• Venl 837 00

OB 2370 1.1 027

821 206114'Vel Venl 22fiB 14 039 0 2.1 83 ]4 16" Veal he above ra rigs are basetl on 10 0%C02 aM 001 Ili water -fl
142 84 1 1235 12"1 1
BST 658 1095 845

848 4
1648 14- 856 2 2133 85.1 185514•Venl II 1 237

8 053 2D61 V111 226814• Ven' 865 2645 54 2474 6 "Vent 

### ne above rmmga are baaetl on tao%eoz and o a1 m. wmer gran. 14 1 3153 03.1 2]4216• Venl 13] 035 04 3348 3544 83

03.1 2911 Vedl 308216"Venl

33 00 3935 3.1 8 83.1 51 16"Ven1 1 22 11' Venl 829

0 01 4328 03 3591 18" Venl 02 1 3 4521 13 1131 18 VenlGT515A Se lies LighI 011

. Forced 0,80

CAST IRON BOILERS EV SMaB F- D.8, L,ghl Oil Oivis-f ECR

H8ROTHERM CASTIRON OrvisiOn of OR Series L,ghl Oil Atlvancetl Thermal HytlrOnics,lx. MG Series NalOral Gas

M0 Sena, I-Ra Oil

MOP Series Natural Gas

Light 011 26 06. 2] 07
. 31 862 33 052

5 39] 760 70 40-0 AG-]]0 794 .1G:1155 1191 08 68 AG 1925 i.s 76.6 AG-2310 2302 as AG-2695 27]5 -30E3

M420 3 00 440 1 MO.660A 41 110. ,117. 55 795 MO 040 60.5 M0:9- 80. M0 155A 825 95 M-132DA 94 8.9 1 79 M0192A 13]5 M2310A 165 >9 M02695A 1925 79. as A 2 79.5 MO 3465A NI 75 79.5 MO350A 275 79. 111235A 3025 79. 110-0620A 79. M0 5005A 3 00540A 385 79. MO s-A 4125 '11 M0 a, am 14 7^ MO 6545A 46.75 79 M.II-A 69.5 79.

111 1 'S 119 '50 90 230 "71:

.1GP56_`0 t7- ^ ]]-1 Mo. .,.A n±1 4)17 4912 B3 4f OZ 18'Venl -I 10' Venl 5108 83 444220'Veal he above ralings are 68866 on 10 0°%C02- 001 In wale,-a

0 2)216'-I 0]0 -1.3 050 -0.2 3348 3564 85)

85 2"116'Ve0 8216'Vent 112 -11 37" a 3251 16' Veal 852 3935 116 %2210' Veal 055 0.1 858 0.2 4130 4326 856

056 359110'Venl 376210'Ve01 05.0 06 053 03 412 1 4717 6 05 31 10'Ve01 4 390210'Veal 045 1.1 4912 85,6 42711a'Vd11 04.9 07 5108 05

.6 446220'V- he above sings are based en 13 0%C02 aatl 001 Ia

.wale, d.R

27 7 85.2 241 7- 1 356 325 05

.2

052 3.B a- I a- he above ralings arc based on 12 s%C02 aa4+O1 inch wale, aver (ire

00 9 211 231812:5 ]9 306 839 2668.12x15 he a0we ratings are bamdon 130%C02 aatl 002 m wale, tlrae
788 4 305 2656x12'15 610 91 01
.3

81
.3 53012x16:20 79616x1640 60 768 45

65 220 1525 81.3 C' 640x25 132 112112' 6 6.0 4 2835 81.3 61
.3 1591 29.20x25 105] 20.20x25 768 011 4 2440 2745 81.3

81

.3 212 20x24.25 2387 2024.25 6.0 fi.e 4 3050 3355 81

.3 2652 -025 291] 24x24.25 760 5 3660 81

.3 3103 24.26x25

5 396 6270 813

81

.3 3]1424x28. a )66 768 45 4- 39] 2-8x30 6263 28x28.30
]6B 5

45 5185 5490 01

.3

013 450928.26x3 4]]428.2800

BOs 338 04S 3948212x0 01.1 45 835 952812x20 80.9 532 835 46312.12x4 79 45 61 17 039

14 53212x124 58812.16x20 809 298 694 12.16x20 }95 91 039 ]9016x16120

44 1066

122 3

.5

83

.9 92516x16:20 106416x2045 }95 79 44 530 036 63

.9

83.9 133020x2045 159620.2x25 >95 44 2142 83

.9 18622040x25 244 03

.9 2129202445 }95 >9 2254 139 2395 20x2625 2661 20.24x25 79 336 039 29)24x2445 )95 ]95 38] 317' 839

31 31324x2445 34592448x25 7as ]95 4284 4590 039

839 3] 52446x30 399126x2640 }95 795 489 5202 039

839 425}20480 452326:28x30 705 5508 839 47a 20.28x30 he 46486, neare based 0a 132% C02 and 002ia wale, d,.R, -pt M0420 -,a 4I- are-d-137%C02 30 81 2868x1285

1 3 532 12x164 224 01 3 %4 0646 1a
. . ' 42 ' 3 . 0

. x2045 77 103 1 3 15 5% 2 20x2045 1 d.2 12 013 106220x2045
77.1 4.2 248 754 813

01

.3 212920x24.25 239520.2425 2 42 3060 81
.3 81.3 2661 24.26x25 2927 24'4 x25 7].i 771 42

.2 3572 390 01

.3

81

.3 319324.24x25 3459 24826x3. 7r_t ))f 42

2 4304 0 81 3

BT3 3725 38 3998 28x20. ]] 42 4096 81

.3 4257 2040x30 77 42 5202 O1 3 4523 21,21,31 77 42 5500 613 4]9020x2040
868.12x15 812 53212x1840 91 1224 039

83
.9 9816.6x20 6d 16:2025 039 1330 20x2045 159620x445 212 244 839

a3 a 166220x205 2129 20x24 5 2]5 2 2395 20x2445 306 3676 03

.9

839 266124x245 292] 24x24825 3672 839 319324.24x25 397 839 345924.28x30 7R R 428 4590 83

03 3)2524.2830 3991 26.2830 542 83a 4257 28.28x0 452326.2830 79.5 5508 839 47902848x30 he 86088181!098 08868 0a 132°1 C02 (011) 01102%C02 1080, 800.00214

. 780e, 01811 .NEW YORKER BOILER STEEL FR Series Light Oll FP265W COMPANY fR305W FR350WMFR962W 

### SAP -- 1,f,' ." 5204AP S339AP 051 S5 a 05125 55,151, LOOt 04 

### OS2701

ESS NEATER CAST IRON Wale, and El-Series Llghl Oil EC/ECTOS258WI5 COMPANY EC/CT RE-275-S EC/ECT O6 .- Sedes SCISCT Natural Gas Forced O,.vll - - SCISCT-OS1 SCT:, SC/SCT,' BGSCT-00\

Light OlL Forces Orao SC/SCT.09^\ SCISCT-10.\

CSCT-OSW/S T-0&WIS SGSC.07-W/5 S

BGSCTS W/S

Series LCILCE Natural Gas, Forced Dall SCIBDT O9 WIS SCISCT-1- LC Le 5N LGS LC LC LCO 9C1 1 LG L"12 LCE-13 CE-'^ CE '^ CE-`6 CE CE'3 q ,C CE -sl



### Light Q1,Foal Daft LC-0 C-SR LGS LCb LCLCLG10 LG11 LC12 LCE1 LCE, 1 2 LE-i5 LCE i6 LCE:ti LCE-10 LCE-1 LC El LCE-1 LCE-2 WE-3 LCE-24
HLAN-N CAST ]RON CORPORATION 1-y nes MadelL Light Oil D50 O50 D4i0 Dfi D-]
D-iO LD 70 DF.50 DF-50 LDEfiO C" LOE]D LDF-]- LO170

6 882 5 LDZO.]506 433 ] 501 82 577 11 9 80 22 J9. ) 9 ]9fi ]92 6 002 0
00 09 8 796 11 196 09 et 1 3.

. 81 T
927 4 02 4 02.4 25 82.6 5 82.1 02.1 55 021 62.1

686 113 191 1 808 803 881 802 80.3 0.9 80.2 1.0 1071 1213 K0 B 8 80 0 93 1469 80

811 809 0.2

s1.1 0.- auz 813 2056 

### --. avz 1
2252 81.3 246 81.3 79.8 1.2 296. - 800 1.0 265. 00.1 09 80.3 07 14 Oo1 4 801 03 08 02 809 02 809 02 BI 810 D2
415 02.3 83 56 82.0 6.1 028 2 11 028 11 827

035 827 06 33 833

83.1 83.1 128 84. 3 142
^ 843 84. 1 166 83 839 7 02 184 02.5 826 023 24 128 83.1 024 03.1 22

.5 02.6 24 022 026 822 25 83 5 835 26.5 83.1 28 03.1 83.1 2P 1 21 83.1
72

.5 83 83 03

215 031 03.1 23 02 02.7 2.6 81..

81.] Ot,} 81.6 31 335 812 016

KII 807 3 00.2 802

0.0 235 031

24 02.4 26 01.3 285 81.2 91 3 80.2 3 02 002
35 8.1 310 006

0.6

411

.1 O 9.9

89 8.0 T.O T.1 78.1 2.9 265 305 04
.9 230 8:11x5 265 812x1 350 309 8:12x20 400 402 038

042 348 0.12x20 402 8.12x25 h above -- are I,- wr 122%C02 aria -002 in wale, daft
3 24] 812,2 339 04 295 8x12:20 he above aen9s are based -12 2%C02 a,A
-0 021n

. wale, daft
69 170 025 he At,- ratings and based on 12 2%C02

28 321 04.1

R4 4 096 215 241 249

279 8:12x20 03] 1003 261 302 8:12x20 he above ratings are based-135%C02 and 002 in wale, daft
806 10]1 257 298 T Venl a 812 217
" 352 9•Vel 462 519 81

809 1446

7621 347

389 402 9'Venl

451 1'Venl .7 7 4 1 1.10 •Vent 632 005 1975 4)4 550 f0• Vent
343 83.3 16]1 257 290 Venl OS 462 637

3.5 1261

1446 304

347 3529'Venl

4029'Venl 579 STS 036

032 161

796 309

431 4519'Ve

500 f0• Venl N 632 83 1975 414 . 0 Venl he abdver l g ,n based-125% C02 and+010in water -1 al vent 17 012 178 4110 476 9'Venl 649 717 012

012 209

2200 4 1

530 5649'Venl

5 'enl 066 2713 651 ]5511:11 1029 1 89 321] 3717 72

892 8951- 'Vet

1034 -'Vem 3 1 s0 4211 ID21 1174 12enl ' V 1511 162 81.1 536, 153 1288 iS1412•Vent

7454 2'Venl 832 81.1 5917 620 1932'Venl 1966 2125 01

III 6350

6015 1520 1650 1] 10 14-Venl

1848 14• Venl 2204 01 73B0 1773 1986 14' Venl 2444 270 8

Bt 790

0421 1898

2021 22125 I4 4• Venl

63 1
3 01 098 2145 V0316•Venl
2 299 9954 2269 2541 16•Venl 3982 3256 Bt

81.1 99]7

10533 2393

2528 2831 tfi'Venl 3439 3694 III 1

81.2 110%

11650 2663

2790 2983 16•Venl

3134 i6•VeI 812 12217 2932 3204 tfi'Veal
541 831 t>O6 411 4719' Venl 7.7 63)

83.7 229

2208 487

530 SE4 9'Venl

615 9' Venl 6 129 837

131 2713

32 651

772 ]5510'Venl

895 tO• Venl 109 83.6 371) 892 t- l()'Venl 1350 -01 1511 K3 16 4258 4- 1020

1153 1174 12•Vel

1314 12•Ven1 -05 16]2 -03 1832 836 83.6 5367

6917 1286

1420 1454 13•Venl

1593 12•Venl
2125 63.5

83.5 6358

66]5 1526

1650 171014'Venl

104814'Venl 2264 0.4 635 63 1360 1773 1898 IS. 14•Venl

212514•Venl 09 2603

3 3.5 0421 2021 21 d5 2d0316'Venl 2922 63.5 ]1 2269 2541 i6• Venl 3202 3256 83.5

83.6 99

10533 2393

2518 2680 16'Veal

213116'-1 3430
] 133 S

1 6 111.

11656 211

2796 i6• Velnl

2903 313 KZ 1
3n .37 12217 2932 3184 16'Veal he above ratio
-s are based ne 130° m Cot (ail) and X01 • wale, salt al the vent

IRK 217 812X15 Z]2 652 23] 60%12X15 29 326 858

041 933 224 259X12%15 2838%12X15 35 381 055

84

.2 1198 266 300 8%12X15 3316%12X15 339 33> 840 IS'I 253 2948%12X15 0%12X5 The.d.ve lacings are based on 130%C. aria 012n wal.frafl
26 50

. ]03 188 217 0:12x15 24 2> 1 4 6 236 0:12x15 39 296 65
.2 925 222 211 2'1' 30 324 84 ; 2028:12x5 337 46 S4 84
.8 84 1054

1000 253

261 293 8,12x15

303 0,)2x15 29 376 835 329 8.12x15

250 83
.1 703 188 211 0,12x15 271 211 2 82.3

82.6 925 222 K: 157 01215 324 81] 182 0:12x15 311 348 823

823 971

1080 233

261 2>9 8,12x15

303 8,12x15 3]0 81 329 0,12x15 The above abnge are bases on 12.25%C02(On) e, 9 5% C02 (Gas) aM -002 in wale, also
500 596 09

5
.0 1563

1083 315

44] 2'220

12:12x20- 04110,01- 41 0L+94p (0e0)003060,0(00)9000100000e90006000, 0900e041

11 P I'O000

- P0e200%SttuO Pase9 a,e s0u0e, 00090041

00000 (000) 000 4,0 (00) 000 USZ 00 00 000e9 00 0001 000001

I1 P 100,01000'0061 0)000%S'6,0(001200%S0Zt00Pas000000600000^



### ae1P-- e. x00 Pee-l et eo -4 a,666w16, -, -

11e,p,ale 01200

- We 200%0 Et00060 0 ae 50000, 00040 a 41 SZxpyxgt SZxUZx9t OZr9lx9t OZr9Lx9t OZx94xZt OZx9LxZt OZrZIxZI OZrZIxZI
SZrOZx9t 0009006) OZx9lx9t aZr94xgt OZrglxtt OZx94xZt 00-0x09 00-11x01 9L9 KS Ill ttBZ

OOfL 49

Z 40 94H L06

l. S't8

lZ0 t8 61 LO'MlSV61 90 96 SVl Z9 S SOM'S' "I I'll ZSg EL4 GL8 M LH Of lA'MNS-tl6l

' - f22 -

fiL6 29B L6Z LB 9Z EO'M/Stl6l UerO Paa1Pd 1^.0146i1

ZZEI 9055 L8 E0 6L ZIMLS'06 LBLt 9464 L P I00 SSL 61 6 1 0600 )

'6L GS64 44'M'S'tl6t 

### ZSot OZ L6L 

### 4ec4

IZEE z L.

ELB 9ZL

E901 

# 11

tZ 4

6L Z6L Z6L OL '5l, 6^-^Stl6t 6L 2911 ^ Sb6t 9L9 955 LLBZ

BOfZ 118

Log 906

01C ZZ 9t Z6L '6L Lfll LO-MNS-tl6t 90-IrV5-tl6t "I 96Lt 6Zt I

I ll .1 BZ EE 66L 6L OL

L SZL

ozs SO-MLS-tlGt

EZZ fiZ6 9Lg L62 2 Z"6L fi sCf 0 NJS tl6t Ue,O Pap,p3 'seO le+nleN saua5 V6l
ll0 E124 t 59 6EEl EB 41L ZL-M/S41

IZeE 'p0 401 9t-^SUt OE8 11L 9S6f

I 11 LSH

SB LOL4

Z16 Z Eg EH E9 S'6

SB 60'NJS51 GS9 HCLZ Sg SL gOM/S-6t .1 1 1 SL oz

oz ZSg

ZSg 091

149 l SEB 9f8 ES S9 5S [0'961549 6 Se 605 t'ZH ZI ZB 99 50'NJS4t
EZZ 2621

fiZ6 59

0'48 L6Z E Gla Z 94H 'l0 l8 9f

2 I^^S4t E 569 Ue'0 Paa103 1.014011 1109 ElZ4 908 6EEt Z I"48 

### Le sI9L ZL-1ws4t ufi OfB uee

951E 9 ze

909 eztt

Lott i'le 9 5^l 11 961559
44L L59 OO tE

OELZ 908

gZ8 09 066

8L8 Sl t'lg

LO lg
g ' l8

'Lg EZLL Z60L 60'MIM 80-MIS6t .1 186 f oz 5 t 1 1611 9 Z

9 Z9
Z 449 Z IOB Og O9 t0H

11 90-M1S41

40 NJ551 fZZ 606 g 8 L6Z II Z4G '6L SLE EO-hVS-6l 110,0 pavo3'se01e1nIeN s aS 6l 0g L6Z 100 OEZI

6909 048

0 9fiE

LLE 8'08 6L 6L 6L S E

4E l0-MLS-tl6189 1L-MMS-V6L89 ESL Kot 01 6 LEE 

### 4 z'09 Og E l88 lL 01)900010096 11 "1

t 11

5 E

"1 L 41 .-I 18g H -MIS- IM o u01s^n10 609 L8 48 6LZ IL 6L z S l9NJStlIL80 0014611 0005 tl9 leB 08X091 NOLI 15b0 15tl0 H11W5

LGtI E966 fZH SSSI 90 BLL 00 0000 -6-0000021 EE6 088E EZB 44ZL 9'I HLL LL 0099 >00LL'0Zl OOL 999 LI6Z

SLL2 E'Zg

900 EE6

000 94 L1 BLL

699 LL 00 )) Sitt :OOi 1-302

600 302 f95 412 10 SZ 1

# 11 6 1 

### oDG 3009

994

SLE 9461

E951 Z0

L. E0 Z9

065 0 SZ 900 'LL aca 9 009

119 D -Z45530Z1

Z Osag (111 zo 3on

8GZ4 gOIS g 11 1091 000 00tr302t 0901 ESL Z0Z9

ES tE 000

8"6B 8000

9904 08

4 Z"OB 08 'OB ZL

6 9-00 9 t-60ZI L-E'OOE 9-3001 s1LL 9912 Z'S0 

# oll, Z Lfe 

### La I 21 N%, an
905 gOtZ

0501 B'60

ZSg 9G9

165 2"OH OB l8 9

ZS G4-050-3021 9-Z-OSL-dOZI SLE E9 5L LSB OOS "E0 E4 S-Z-009-dOZI 11014611 O) 0000 01021

SZH H.Z 9I gLL 096

LLLZ 0'LL 4 :^ 1900
808 SSSI 99 0'4 LL 002 OOSZ 30961 'OOtL-dOMI EZe 41 

### zL 1 

### a-36009 f2H 900 EE6 9'6 GE LL

09 LL

BL 0000 0Zll 401 t-40MI t t30Mt OsL 11 01, 6 1 EZH gZ8 ZZ9

065 96 1E 8'LL

009 "LL

eL 000

os< Z-OS-dOMI

r0sc3aml tEe OOS SZ 900 OB Ol9 Z'009'dOMI s00101a1eN I..- 0d

9692 2"ag ag 

### 4z re00le3oml 84B 6SEZ ti LL 001 898 ZZOL Z OB 'OB Bt [90050 1

- - 10961 49 B 6H SB9l

1E Z Oe Z Og OH 00 SL

Zl L'S00 1-30961 UOLt-30M1 L-
zll ZSg 1tOI

888 Z OB E" B E OB

' 40 6

g'L L-E90Et30M1 'EOat 9-30961 1 [Se 

### see rse O90L 

### z6s 9 ee

roe I0 ae 49 S'E406: 

### L-sase^d - 

### 6m cast-3oml 150 005 

### ^ ee a E 

### e v s'Z009^36M1 110109100100ea5 0000,00 39961

SSH 9ELZ Ito ' L8 9Z L-g'009E-OMOI 558 46£0 9tg 't8 1Z L-L'OO6rOMOl 5EB 0

' ZEOZ 0 t0

' el

L 005rOMOt L^1
-OOl2OMOl -M I

- 00 S Sa 558 090

9919 9201 I LB I l0 LB 't8 Z

6 L OOLI OMO L-E'OOE L'OM01 0 Sg fi58 0

1S 61 GE0 'E8 9'9 9109601 15POD6'OMOI SSB 0 58 6X9

965 ILO 'tH 9 GE458OOI greS1-6M61 559 005 Ee C 4 5'0'009'09601 1.014011 sa,a5 uene1000M01
Glfl 9695 558 OLLt 410 't8 SL L-540LZ0201 SEOt OLL EtE4

BOZE 558

SSe 09Et

900 Zl 10000)00201 101 lL9 E9S 9GG2

9bEZ HSH

6"58 668

OSL 690 [ Eg 06 0209 ELS BE tZ S 58 689 le 9 1Z95E02O1Ligh1Oi1

35001 Mills Series Power SUmer. NaWral Gas [28A )0 5 1491 12 )02

1.1 14 )B4 BA-SM] l07 2163 06 S. 81 ^4N^i :'1130 J6J 7 88 768 189 12-1 1, r,,.. 789( ]8.9 789 ]69 ]99
890

2M- W" 21 M'-OS 104 001 2BA-SMf-W 126 81. 28A SM/-0' t5 80. BASM1V-08 1>4 807 28A1M09 10.6 81.3 2BA.SAN^1p 22 201:SAN^11 24.5 806 26A $M 12 26.5 28AS. 29 31.5 808 2. 215 33.5 81] 2ASMJ-i6 HA SM'-17 305 803 36ASMr 10 405 816

3501'08 60.3 3501'-OB 3501-'-09 01,2 3501'-10 17. 2 80.5 3501--11 19.2 350A -12 21 ,.A'-13 23 82.1 3501 -14 25. 5 80.

Li9h1 Oil 3500A^'
-O6 35001•-0> 10.4 3 800

Bt2 35001 -OB 15.0 80.

' ' 18.4 21 .1

02

.1 3. '-11 35001 -12 . 265 012
35001'-13 35001'-14 29.5 32 81

.2

81.0

Ligh1O11

-AMills Seees Heavy Oil SOOA -10 i

411

823 818 2 81 2 1226 3663 71 920 924 10' Veal

0fi6 10•Ve1 1386 :16 4383 1052 1211] 10•Ven1 815 2 818 1. 1551 1713 836

83
.5 4 46

55M 1187

1322 1349 12' Vent

1490 12-V- The above ratingsare base on 12.5%C02O4 al 97%C02(Ga1)antlr ID .n wale, al ft ve,

910 81 2013 675 71310Ne1 t fib 01 3648 8)5 pt 10•Ven1 1433 699 01

01 4538

540 1089

310 1246 12Nen l l

14. 12Ne n1 965 01 fi350 152fi 1]09 14Nen1
2498 7221 0079 1733

1939 1941 14Ne1

21]2 14Nenf 4 276 6 81 8942 2146 240316Nent 3 '31 329, 9804 1IS 2353

2560 2636 16Nnt

26116Nent 3563 81 11525 2'. 3090 10Nenf 3830 Bt

Bt 12392

3250 2"

3180 010 11

356210Ne 4.2 4629 81

Bt tdi 13

49]5 338]

3594 3- 1

402120Ne1
3 BO1 90 111 83.5

3.5 2013

116 171

075 713

10,410Nenl 012 03.5 4538 1089 124112- 809 801 1699 1965 83.5 5459 1310 1x26 14T/ 12Nen1

nos 14Ne Il 2, 2232 83.5 7221 17. 1941 1-- 81.1 2. 116 2 2490 2764 835 8079

942 193

2 146 2172 14Nen1

2431-11 81 ] 3031 83.5 98N 2353 23616Nenl 812 329] 83.5 10661 2560 206716Nen 808 2. 83.5 11525 12392 2166

2914 3098 1BNen1

333018Nen1 81.3 809 2 4096 4362 83.5

83. 5 13250

4113 311 3S. 1-1 3]93 1"": The above ralinOS are based on 12.25%CO2 (O4( o, 95%CO2 (Gas( antl « 101n. water at vent. 818 1 4629 93.5 149)5 SS. 4025 201- The above ralinB%are also approvetl 1., boilers vntb prefix G, GO or LO

1001 80
.9 3129 751 87 16:16x. 235 4'0 3858 466) 926

1120 10)4 1fix16z20

12)8 1fi.20x23 .OS 1939 01

01 5483

6271 1316

1505 1483 6. x26

1...20x29 2174 2474 7033 92 1688

18)0 1890 20:20x32

2095 2020x35 2843 01 0550 2052 2296 20x2-I 20]0 81 .06 22. 250320:24x41

1001 834 3129 751 870 16.16.17 802 2 1 1235 1410 83.5

835 3850

4668 926

1120 10)4 1:16x20

12]8 16.20x23 0 2 805 30 1105 1939 835

83.5 5483

6271 1318 4831-0#6 .-20- 28 0.6 21 4

24]4 835

83.5 ]033

-2 1680

1810 18N-20x32

209520.20x35 82.1 14 .1 2 9 2663 2878 835
a 8550

90 2052

22. 29820.24x38 41 250320.26x TM1e above raunps are based on 13%C02 (Oip a74 0021.. wale, tlmft Insert S for Steam

. W for water boilers.
1165 001 382 874 101318.16x19 1478 1790 00]

008 411

5711 1127

1305 120516:2023

5 )20:2026 2103 245 808

808 ..

7013 1633

1015 182920:2030

210020x20.33 2)2] 311 808

111 8021

1133 2117

2111 2371 20x24.3)

204320:24x40 3352 808 10842 2602 291524:24x44 3615 80.0 f854 2- 3187 24. x47
8 32

' 165 3.2 3642 16:1x19 12 28 : 11 24 1478 1790 832 4696 5]1i IT

13' 1365 1205 16.20x23

155920x20#fi 016 17 2103 83.3 6804 1633 1829 20:20x30 021 12 012 2.1 1 14 2415 2]2> 3090 83

.3

13 833 ]813

1121 .33 33 1895

2111 2366 2178 20:20x33

2371 124x31 2643 1 20:2x40 4 above ralirgs are based on 134%CO2(0107, 10.0% CO2(Gas)and-002in water draft 01.2 21 010 1.5 3352 3665 833 6642 111. 2645 310724.4x47 lalirgs are also approvetl for bailee with pre0: G or GO. InseN S for steam, W ferwaler hollers.
3080 82

.1 993 x391 2610 20:24x30
3853 81

.6 12463 2991 315 24:24x37 335024x26:04 4240 462] 813

813 1373)

1496] 3292

3592 3687 24.28:51

402324,28x56 5014 5400 81 1

11 16221

717 3893

411, 43602412x65

4S. 28:2802 5787 80

.9 18721 4493 5032 28x28:]0 6174 656 09

80

.8 1.1 1

21221 4)93

5093 53..28x06

5] 04 30:3093 690 '334 807

807 22675

23725 5344

5699 1.41 3030:100

:3130-107 1120 80

.6 24975 5941 6)1330x36,114
3030 84.6 9963 2391 2678 20,24x30 396] 3853 84

.3

84.1 11217

12463 2692

21. 301524x24 x31

335024:24x44 1 4240 462' 839

63 0 13717

1496' 3292

3592 368'26x28.51

4023 24:26x58 5010 13 7 1.21 HIS 43.24 6x65 540 835 17471 4193 46%28.28x)2 17 7 617 835 18721 19971 4493

4793 503228:28x)9

5369 28.28x66 656 694] 83.3 21221 22485 5093

5394 5'0430:30x93

6041 30.30x100 ratirgs are based ea 12 5% C02 (03) or 97%702 (Gas( antl -102 m. water tlra0
82.3 09 ))20 832 23,25 24975 5699

5994 63. 3D.M.l0'

671330:36x114 ratilajs are N. approved far bailers wish prefix G, LO antl GLO Inserb1818r Steam.Wlor wafer boilers

3435 84.3 11113 2fi67 29872dx24 x17EBxffx9E E0Z6 Lt ZO BEZ9E 898 90501 84 028 9'28 ZL*9CZ0E 4209 99x9[x0E SE4L BEff e6Z B59GZ 4'40 9226 OSSB OZ

S'4 1129

9"LB 49v9fxOf 5909 SSsOfxOE 9529 2t t9 S95S L99S2

14292 2'99

9 99 2494

9614 60

Lt f'f9

429 

### 9e,p o. ,I pee Zoo x424 ee pasep a,p s6eee, a.ppe ay 04 LxZt'9 yS LZt 05801 BOZ59 SE0 SL6Et L"t 8'49
504:29x99 f9S44 66z29v9E fL6ol 92904 4099 12904 51e GGLft 4944 9't t9 611 96x9"ezff EHEOI 00x9Exff96L6 LGZ6 5910 6Zff[

0969E 990

LEO t961t

E9Zlt 9

9't 0'20

920 fez9Er9f roZG CLx9Erff 9194 9120 1694 2924C

9902E Bf9

099 59501

9066 9l Z'Z0 ZLx9ExpE 6208 5914 45862 IZIZ
99x9fxof SC6L t9z9fx, 599 8f99 2119 05942

L995Z 498

2 98 ZLHL

11 9t

t Z0

LZ0 SSzOExff 95 ,9 x955 14291 498 4644 l 620
ll LZbx9C ZSLZI 1 11 00254 40 SLGfI 161 S01zy6xff E9SLL 6ZEOI L40E4 40 L6ZEl E 6L 66zZ6xff ZL601 L6L6

oac 42804

szsae 1'48 01921

Owu 461 964
EBx9"exff EOl6 LtZO BEZ4[ 2te EtH 29241

40504 961 L6L LCx9Exff 9490 4694 9904E ELH 90fi6 B6L ZLx9ExpE 4200 89x9EV0E SE6L 59 tL 9999 4s96Z

9s9LZ 940 OSSe 49x9ExOf 5489 55x0ExpE 9529 Zt t9 SASS 1

IGZEZ 618

64 ZGBL

464[ OB

II P+-w

. 2pe-P..(

"01po924 up parnpale seune+ anppe aV tCx9Cz1 4121 I'll ILfiCE 111 40504 0't f"EB 69x9fxff Z9C EZBL 965LC S0 9400 IEl

19x9Exff LS9L Z9LL ZE89 9862

L90 II 5226 6648 Zt 0EB 8Sx9Ex0E 2824 ZOS9 60LZ 6'68 4LEa 9L 95zgfx0l 2469 K0E0E 2459 ZL 49 1485 LIGSZ

0EE6Z 00

1 6464

EZ54 I Z H"ZB
ZSz-Z ZL l9 OSx8Zx0L ZO5 1155 0015 9622

EBSIZ L 98 LL9 80 pf0 BEH G9x8Zx8L Zf45 0506 00ZOZ 448 L9Z9
"" 1111 69zffx9E_I EIII ELBL 11611

IZ 929

SLB 4054

9LOOl 08

9Z-9Z L6E8

ZZ" Z64L

Z9lC II4962 S ZB

111 0596

11 990 800 1--E 1591 ZE09 948Z bZ. 6618 85x -ZHZL 9sx Z-ZL69 ZW9 ZlI Z6olz

41LSZ 9x0 4490 

### epe
4S -ol ,659 1605 9EEZ Z9 EZ54 2SxOfzOf 2Lt9 OSxBLxeZ 2o8S It SS 0845 ...

0512 'Z8

ZZB 9604

ZG99 900 8'OH --8l ZEES 0504 80ZOZ I. .I a11o9+aleM+O1 M 'wealS+pl S Vasul 9:92x92 68p5 E9sb 61111 150 8"90 Illp eay^+ale e. 9p +o( y610 oe+p+alera w. ZOp' W e (se6) ypp %S 6 +P (110) 20p 9:5 Z1 uo pasey we s6eee+anope aV Z9z8Zz8Z Z98b if ft081 990 8955 449 LCYI- 9656 11:840, 6994 Zoll 99 9fi014

64191 490 SBZS 698 S9t9Z/Z 9044 ERIC E9ZS4 90 B... 6'50 65x92262 959E E5v9Zz6Z t9E EZZE 9f99 S"re fi"E8 1492xbZ Zo. ZOOC BOSZL 90 198E S"re 8"f8 04-4-Z MIZ Lfz4ZzZ fZ9Z -Z

- SG90

9SL6 I.

90 GOEE

940E LZ 9"re 8'90 Efz92zOZ LGf2 ZZLZ 2000 6'SB EELZ 4E BZe 64x.-OE LZ I- 1- 618 6062 92 9
BB:. Iz 6805 LB - `ZCB4 Eb59Zozoll

I-L e 6a 

# I 259 

# I, L . I L 9654 1Lx9ZI, 6bf4 .11 EBBS 96044

64194 8 90

1 SBLS

"1 6'0 6'EB 499 59x82292 Ept4 "I II 9tLb 8"t Z'EB 65xgLx6Z 958E ESxZx4Z Otff 999E EZZE I=

6Z450

250 Zv,

4514 L 4662x42 EeEE Zx4Z 944E ZB[2 80521 96511 fSe

1 498

EB1 9"t

S't L'EB

6'EB 04x6L4Z LEx Z Zl. ZBSZ ZZ 94-

9s<6 11

0 1

9o0E 6Z

fii LZ9

62B I Z Ll. LLEL 2zI

242 4688 90 I'll 6'Z 490 _oz- 6ZxOZOZ OEtZ 1061 4264 990 6902 OE f"f8
99:81x02 695 9954 62681 ZZ8 ZSM Z9xeZx92 299 -ZgL 965 : fZZv

EOL4 I,.,

%041 ZZ0 8955 592 4'48 t- 926999 -.Z.. EOL9 EBBS £91, 6L 194

99254 1 Z9

28 108s

BlG9 448 t'L9 6SZ -Z ff8E 95:82x92 049E 949E EZZE 99961

6Z6E1 5'Z:

9 ZB 15 L4 040 049 "...b, EIEE

4Z 911E 09*bZxZ 29oz 19SZ 905Zt

16544 5(904 [2

fi29
EB L9B

IOSf OOEE 010 0'40
lzol Lfx4Zx0l EL9L EEV4ZZOZ LLf2 2EZ 22 2 BSL6

MI ZE9

9f9 910E

EELZ 609 6ZxO4xOZ OE IZ 1p64 t26C LE9 fi942 BOB
s+al!ee+alem+01 M'weals+e^S Vasul, 

### e69z roe IZI 0EB llwp+alex, e1040-pue ZOp YeSZ Zl uo paseq am s6elle+anpge a41 

### 41114x01 111 111 

### uLez r90 eecL I 6LB oot_ OE LE 09 E6vOfxoZ 695 I.
8005 E94ZZ

OOZ LL Z9 9559 L 19 9

I SeG9 BEG61 248 9919 Z Ze 6GzeLxBZ ZOS ZGx8Lx8Z 2994 1899 0844 6[98

Ll trLl 298

Z 9 4[LS

9995 820
I 59x8ZZ6, ... 95x92262 1009 LGff SS. 45191

9189 Z"90

190 9W6

9099 Z

Z L'

8'40 15v8Zx6Z 999E -9L- 9ZEE ZLZE OL. EEff

SLEZI E b0

E 90 tZ4

SZZZ Z

Z 4te

f"28 848 ZZ4 52-:059 to 944 :..I `tH OLL EZ-:o ZB 904 22:0.o 059 tZ-: 0059 L'ZB
420 1'ZH II

Sig GZB z9 54-:0059

0'98 ZZ--tl.1. 4'98 LZ- .11, 'b8 OZ-.-V054W 908 G4-tl056fY Eg 04'tl0594Y '90 CL-,-V056LV f8 9L-tlOSb4Y tlOs 0f8 9L-.-tlOSMY90 EL-tlo OSWI I-tl

` C0 OL vo-

6ER OS ZZ-: tl059W 

### -: tl054W LE9 II 12 oz "05M Lf0 f4 61-tlOSbW E0 S'Ob -tlOStrW fe Bf LL :-VOS41Y

SSf 9t-.-V056W LEB EE

SbE tl-.-V056W GZ0 SBZ t-.-V054W Z0 9Z l.-VOS6W

9EZ tl-: tl056W OI-.-V054LY CEB IZ

Z2-: 005 ZB IZ : tl00S 'Z8 OZ-: tl00s Z8 BW-tloog z, I. 11 11 ew-boos ze sw-bees 

### 9w-tloos t0 EW'b00s 

### za ,.. zw voos 

# -ol11 11 1 02I 126 1940 83
.7

836 36933

30625 8]44

92]0 9]3 36.36x88

10383 39n36z9-1 SODA-3
00 .4 :.25 81

01. 817

81 1 12618 1319] 139]5 036

835 835 40821

4301 ] 45200 9J9]

10324 10050 109]2 3fix4 .

11563 36.42x105 12152 36x420110 The aboveralilgsare based on 124 % C02 (011) antl 010in walertlralt Inserl'I' far Sfeam or RY I0r Water

THEEMG- DYNAMICS STEEL HT Series Fprcetl DA, Light Oil H-225 225 83 0 21 85 230 BOILER COMPANY T250 HT 2]5 21 03 B2 031 2 1 029 20 91 319 852

84.9 53 277 The above are basetl-132% C02 forthe HT 225 ,134%CO21orthe HT-250, antl 136%C02 ]or 1 HT-275a1 -21 ater tlrall al fhevent VTF Series Gamper. Llghl Oil VTF-1600 25 76 769 41 269 812 - 8
. 12x20 The above rating Is based on 12 25%C02 and -002 in wafertlmll

ULTIMATE ENGINEERING CAST INON Genes PFO aM FFO-T F-d -fl, Light Oil PFO 1-2.35 235 842 2 27] 052 241 l CORPORATION PF09-300 3 09 35 052 OB BNenl PFO 11 1 2 IE 275 844 0 4 OB 325 052 2838-t The above ratings are basetl on 12 5%. C02- I D l inch wafer over Ore.

OTICA BOILERS CAST IRON E1.1- Gleam Seres LGI,l OB SFHfi225 1,11 791 197 36 251 833 783 1114 210 8.12x15 aIal ECR lnlerrmuon
. Ic S.1-Water Seees LI9h100 FH7275

SFHS225W 275
225 7 7

797 797 36 307

251 03
. 3

111 958 230 267 8.12.15

210 8.12.15 The above mlilgs are basetl 0113 0%C02 - 102 inches water dra0

WEN.MCI.AIN A SPX Company CAST IRON WGOAVTGO GOIE Sere: LI9M1I Oil o 8 3 2 2 266 = 0. 55 026 82 2.4 295 85 257 S22- he above ratings are based on 13 0%C02 and ^O 0211 water dra11 'Also approvetl with pre0x PS or A ISO G,ld Sados3 LI,hl 00 SGO BW 2.3 826 82.6 2.0 266 211 0.12x2 5G0 9W 255 826 826 24 295 05 251 0.12.20 SG01 23 826 816 2.4 211 85 833 200 . 2.20 he above ratings are basetl-130%C02 and -00211 wafertlralt 5609 2 55 826 626 2A 295 85 921 221 0.12x20 Oso approvetl with 11e6
.P6 OrA
7. Series1 Forced Orall. Natural Gas 70 6 003 17 270 82 8]1 209 242 8'111 10 10 .1 81

.3 16 8 819 19 0

1629 91

1 453 0° Ve11 670 015 0.4 643 81.9 2008 402 5598'Venl 10 931

II 015 04 1 7 02 764 000 81.9

81 2388

2]]1 ]3 fifi5 6410' Venl

70 10"Vel
1078 1232 13] 02 019 00 129 1 01.9 314'

3529 ]55

847 6 R. Venl

98210'1¢11 171 270 27 674 020 1 1372 Sl S 81.9 IS.

4329 938

1039 117

193 12"Vent
Forced Ora11
. Light 04 2.4 01 827 27 845 011 209 2428'1¢11 445 113 111 521 645 1629 453 e^Vent 55 03. 835 9 - 84.4 2008 482 5% 8'1¢1

I 75 84

I 76 84.4 2388 ]] 5]3

5 68410' Venl

" 05 114

84 84 4 0 8 6 100] 844 2 1 3146 66

755 ]]010 ent

0]10'Venl 14 840 1129 844 3529 041 982 10'Venl 6 16 2 642 8 S 1 

### 250

1372 04.4 844 3908

4329 938

1039 1087 10"Venl

119312'¢11 -b- M- are based an 13.0% COG oil Or 10%C02 gas antl r0

.10 in al vent ell Senest Fometl Orall, Natural Gas R 797 797 22 794 81.9 2483 596 69010'¢11

508

IS 100 130 ]
73 802

7 00.2

7 

### 84 311 819

81 B 2533

3388 42]5 608

1026 J0410'enl

161 tONenl 708 2099 9.6 6 ^fi 5225 1254 1419 12 1 a98 2396

2411} 79.5 02 9.5

802 904 111 812

81.2 82 6154

644 1477

1546 V83

165612'611 113114'¢11 8

' ' 2176 2 0 103 1689 119214'¢11 79 79 0 2.1 -2 8 tt 111 1 1454

]933 1789

904 203141¢11

213214111 1160 08 89 273 811 6813 2115 2369 41em
95 3270 9704 105]9 2329

2539 20914'¢11
14P0 150'. 93 802 GS 3550 3020 143 12358 2]56

2966 308716'¢11

D2216'em 1690'. ]99 1 20]5 ' 396116Vant IS 2 11221 3125 355] 16Nent ]8 780 10 080 71 9] 12 ]9 15 4370 4640 800 800 14138

15000 3393 3602 380018Nen1

403518Nem L19ht OiL F.- Ora11 51IR 6 02.2 82 2 22 79 846 2483 596 69010Nenl
588 7 9.4 27

24 8 2 7 24 17 0 08 844

84.1 2533

3380 608

813 7N PWenf

94310111 688 0 821 2 35 839 42]5 1026 1161 t-1 142 021,

i 021 01 6 190 8

83] 5225

6154 1254

141] 161912Nenf

165612'¢11 9081 1988 17.2 B e 827i

:2.31 827 02 ] 991 176 837

63.0 6442

]030 1546

669 1]3114'¢1

119314'¢11 tOBBR 1008 21 5 8151 02 3 015 2304 242 83.6 ]454 7933 1]69

1904 2003 14'¢11

21114'¢11 88 23.5 1 82.0. 02.8 8 2714 836 0813 2115 236914'enl 12BB 3:: 26 85 12.41

12 024 020 3000 32]0 83.5 Da 05]9 229

2539 260914Nen1

2843 4'¢11 1488 158 31 33 81 01

52]1 02 1 8 17

08 3550

3020 83.5

63.5 1403

12358 2]56

2966 300] 16Venl

3322 16'11:
1 1 365 8241 .24 3900 83.5 128]5 3090 34611fiNen1 8
8 1 35.5 38 52.3

52.

# 11 e 3
21 990 4170 63.45 3229 31]3 355] 16'¢11 he above ratings are based on 12.5%C02 (oil) or 9 5%C02 (Gas) antl r• 0

.10 in of the vent 0: 8 495 813 018 

### 4660 834 15008 3602 403518Nem he above ralinl}s are also approvetl (or boiler with -.. BL RG EGL, AEL, AEG, ARGL, PG

. PL antl PGL and suffix WF aM IF
94 Series3 Natural Gas
. Forcod Or311 798 14 2026 81.2 6563 1575 176314'1"1 2320 81.2 7504 1801 201] 14'1"1
1191 804 09 805 0.9 2612 2.4 813 6450 9396 2028

2255 22116NOn1

25216Nen1 814 0 39 814 10321 247 2774 1-1 

### 14=^. 11 4 11 

### Ina 111 a 1125: 1 1 30261-1 32: 18Nem 

### 19 40]0 81.5 13167 3160 353918--gbl Dil, FOrcetl Drag

vy 0i1. FOfLM Da11 16f'.

B^ 219-+

- 2e ^^
+

996 994 094 14 1296 1394 494

694 1]9 109 1994 2094 2194 2294 2394 2494 2596

994 11

1294 1394 144 15 4

1994 2.4 ,41:' ^f13

- 7. 1, 711

3651 00

b0. 80

- ell

1>fi 823 20 829 22 5 82.9 23 830 21 029 30 02. 2.5 02 31 13 Sl 37. 5 40 83. 62.5 'S 45 4)5 83. 50 03. 53 822 55 83. 8 60 03.

014 014

001

01.1 1) 619

013 02. ..: 006 09 00-5 1 .0 005 0 00.5 1.0 805 1.0 005

80-5 1 .0 798 2 805 to

82 14 029 829 09 830 09 82 10 82 020 03.1 09 030 1 0 030 0 1130 1.0

83 0 f S 830 0 822

823 18 83.0

Bi4 23 81 .6 2.2 810 2,6 00] 29 et8 tB 2,2 811 25 82.2 Bi .9 11 81 20 13 23 .2 0 1 01.8 465p 4940 5230 5520 5810 6100 639p

6910

2020 320 2612 2904 3190

310 40]0 4360 4650 4940 5230 520 5810 610 6390 6690 9]0

2028 2320 2612 2p4 3190 348D

3" 60]0
465p 494 5230 5520 81.5

1.5 81.5

552 810.5
B3] 83.0 838 83.9 03.9

839 04 86 84 04 04 84 84 84

841 04.1

83,6

036 836

' 836

836 836 036 036 15042

159]9
1]058 18]96 19]33 20]1 1608 22566

6563 504 &50

10321 11250 12196 1316] 14104 15042 159]9 1691 1 " 11 1.7 19]33 206]1 21608 22546

563 ]504 0450

10321 11258 12195 1316]

15042

8 1' 7N8 3305

%t0 3835

511 4]36

S80fi .11

1805 2028 2255 24]] 2]02 29 ] 3180 3385 3610 3835 6061

455 4]36 4961

5488

1515 1001 2028

2477 2]02 2921

3385 3610 3835 4061 4206 3]91 10V80I

40432- 429620Nen1 454820Ven1 480020Ven1 505220Nenl 530422- SSSt 22Nenl 500922-1 806122-1

1113141-I 21] t4Ven1 22]116Venl 25251fiNen 2]]416-Z: .. III_ 3- 111- 3539 lZI

319' 1" 4432-Z 42. 20Nee1 454020Ne01 41' 21-1: 505220Ve 530422- 155]2-1

606/22/2
1)511-1 .1714-1

25254fiNen1 277 16- 302:=- 3278 iBVenl

319110Venl

I'll 4043 41N10Ven1 4"a 20Venl 48002-1

AVERAGE- 7997 144 82.32 2.17 0341 Toe above slings are based on 12 25%C02 (oil) or 9 5%C02 (ga)s a The above ralings are - approved for boilers wilt pie61 AeG, AeGI,-1 , .1,'8.1, 9G, 11 , --1.1 aatl so1TU-aetl 0F.1=B=R Commercial Boiler EffiicieneySnmmer^

TM1ermal EIRc. X Comb.

EIRC. ENC.
e OR OIt 11harmal cmb. ERIC.

ENC. OlHVrence ALL BOILERS M1vrmal EHic. NC. X 5 DlHVrvnce X
AvemOV for Bailers arAllSrses 

### m.6] 6r 9p 194 49 2.1; a2 z 

### ata4 296 Maximum 84 50 56 8020 

### ez1B 6620
SlaMartl OenaLo ]6.03 79 80.50 0120 ]1.71 102 ]5.03 212 80.50

1.63
x300 kSt- 852,500 'BI ]9.98 82.14 2.18 82.32 84.49 2.11 81.73 63
.90 2.17

Maximum Minimum 84 50 ]B 3 560

00.50 8].10 88.20 71 SS ^II

0 86 44 > 93 8155

8l 02 StnMartl 9evialio B2 , 11 SS 1 02 ; e 94

k l >2,5 19.95 81 ]0 t.>4 ]9.95 81.]0 1.74

B ^ 1411 1

6B3 SSAS 683 060 St._ Oona80 175 085 1J5 OBS

Casl Iro ]99] 01

.91 1.94 6236 80

.51 2.15 61.13 83.40 221 C Spe ]98] 0181 1.90 0169 60

. 17 26] 81.12 8352 2.50 8^ainlass Sieeel ]02

1. Motlel series slanin9 mfM1 # are nal ircla0etl. 2 For IigM1100 mo6els, a raminal Fcalin0 value of 140800 Btu per9allon is usetl. For M1eavy ail motlels, a mminal Foaling value of 150.000 Blu per gallon is usvtl.