Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data fro

fuel burning power plants and which test methods were used to do so for cases where the test methods are not 

supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in t

if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 se

runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one 

one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet.

yellow are required. All cells that are shaded in green are populated using drop-down lists. You do not need to 

cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. 

resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls 

(example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksh

2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. 

spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission 

results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or c

family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter bot

Hg+2, or if the Ontario-Hydro Method was used, you would need to enter Hg0, HgP, and Hg

Volatile Organic HAP and Speciated Semi-Volatile Organic HAP worksheets allow you to use a drop

Constituent field to define as many records as needed to record each HAP that you have results for. General ins

follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample.

2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop-downs in the Fuel Type Selection 

You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more sa

then enter an input rate of zero. 

2. Please enter the unit of measure using the drop down provided.

3. Please enter the test method used to determine the fuel input rate.

4. Please provide any other information that you feel may be important in the Other Supporting Information fie

Emission Data
1. Some constituents ask for the emission rate results of each run in two different units of measure, while other

If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) 

ppmvd @ 7% O2(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both.

2. Please provide the test method used. This may or may not match the example given in the Test Method Used 

Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010).

3. Please provide any other information that you feel may be important in the Other Supporting Information fie

4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for p

enter these data.
nformation about emission data from fossil 

ses where the test methods are not currently 

nly be used if the method is not in the ERT or 

T. You must complete at least 3 separate 

sheet is intended to be used for one boiler of 

copies of this spreadsheet. Fields shaded in 

down lists. You do not need to populate 

rmation worksheet. Please name each 

nit_[BoilerID]_EmisTestMethods.xls 

ler on the Boiler Information worksheet. 

ent family required for this analysis. On each 

fuel input information, and emission test 

d depending on the constituent or constituent 

Mercury requires that you enter both Hg0 and 

, HgP, and Hg+2. However, both the Speciated 

low you to use a drop-down provided in the 

at you have results for. General instructions 

er Supporting Information field.

downs in the Fuel Type Selection field. 

fuel types entered in one or more samples, 

he Other Supporting Information field.
erent units of measure, while others do not. 

b/MMBtu (Pounds per million BTU) and 

, you are required to provide both.

mple given in the Test Method Used field. 

ethod (ex. U.S. EPA Method 0010).

he Other Supporting Information field.

 method you are entering data for please also 
EIA Facility Code Facility Name Boiler ID

963 Dallman 34
Control Device Configuraton

Listed (by boiler) in the Configuration Order Section of the Facility Unit Configurations Section of the Electronic ICR
lectronic ICR
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/30/2010 13:27 6/30/2010

2 7/1/2010 10:37 7/1/2010

3 7/1/2010 12:12 7/1/2010

CWLP is submitting the ICR data using this excel spreadsheet due to the fact that w

error messages when trying to populate the data into the ERT database. All the requ

is included in this spreadsheet (Acid Gas HAPs and Non-Mercury Metallic HAPs).

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

14:38 <0.24 U.S. EPA Conditional Test Method 033 (CTM-033)

12:50 <0.25 U.S. EPA Conditional Test Method 033 (CTM-033)

13:25 <0.24 U.S. EPA Conditional Test Method 033 (CTM-033)

adsheet due to the fact that we continued to receive 

the ERT database. All the required ICR emissions data 

on-Mercury Metallic HAPs).

Hydrogen Cyanide Emission Test Results

Test End Time
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL <0.000245 1730 15.2 12

BDL <0.000256 1724 15.3 11.7

BDL <0.000233 1723 15.3 11.2

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

6.8 390588 129.4 1443.5 bituminous ton/day Other

7 384963 129.9 1465 bituminous ton/day Other

7.6 386823 129.8 1465 bituminous ton/day Other

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

O2 (%)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

Dallman Unit 34 was only able to achieve ~ 70% of full load. This was discussed with B

Dallman Unit 34 was only able to achieve ~ 70% of full load. This was discussed with B

Dallman Unit 34 was only able to achieve ~ 70% of full load. This was discussed with B

Fuel #4

Other Supporting Information
ad. This was discussed with Bill Maxwell on 6/9/2010.

ad. This was discussed with Bill Maxwell on 6/9/2010.

ad. This was discussed with Bill Maxwell on 6/9/2010.
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/30/2010 12:10 6/30/2010

2 7/1/2010 7:55 7/1/2010

3 7/1/2010 11:15 7/1/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

15:25 [<0.05]

11:02 0.1

14:25 0.08

Test End Time

Hydrogen Chloride Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.000065] 1730 15.1 12

DDL 0.000136 1724 15.4 11.7

DDL 0.0001 1723 14.9 11.2

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

 Test Results

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

6.8 399610 129.3 1443.5 bituminous ton/day Other

7 391001 130.1 1465 bituminous ton/day Other

7.6 384158 128.9 1465 bituminous ton/day Other

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)
Fuel Type Units of 

Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #2 Fuel #3
Fuel Type Units of 

Measure

Measurement 

Method

Method 26A

Method 26A

Method 26A

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/30/2010 12:10 6/30/2010

2 7/1/2010 7:55 7/1/2010

3 7/1/2010 11:15 7/1/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

15:25 [<0.09]

11:02 0.1

14:25 0.09

Hydrogen Flouride Emission Test Results

Test End Time
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.000065] 1730 15.1

DDL 0.000076 1724 15.4

DDL 0.00006 1723 14.9

Test Results

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Calculated 

Emission Rate 

(lb/mmBtu)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12 6.8 399610 129.3 1443.5 bituminous ton/day Other

11.7 7 391001 130.1 1465 bituminous ton/day Other

11.2 7.6 384158 128.9 1465 bituminous ton/day Other

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1 Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 26A

Method 26A

Method 26A

Fuel #4

Other Supporting Information
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 [<0.081]

17:15 [<0.081]

12:10 [<0.079]

Test End Time

Antimony (Sb) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.000000351] 1703 15.6

BDL [<0.000000370] 1717 15.7

BDL [<0.000000360] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppm) Basis (Wet or Dry) Test Method Used 

12:30 [<0.131]

17:15 [<0.132]

12:10 [<0.129]

Test End Time

Arsenic (As) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.000000351] 1703 15.6

BDL [<0.000000371] 1717 15.7

BDL [<0.000000364] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 [<0.272]

17:15 [<0.273]

12:10 [<0.268]

Test End Time

Beryllium (Be) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.0000000877] 1703 15.6

BDL [<0.0000000926] 1717 15.7

BDL [<0.0000000909] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 [<0.022]

17:15 [<0.022]

12:10 [<0.033]

Test End Time

Cadmium (Cd) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.0000000877] 1703 15.6

BDL [<0.0000000926] 1717 15.7

BDL [<0.000000141] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 1.61

17:15 1.512

12:10 0.794

Test End Time

Chromium (Cr) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

DDL 0.00000299 1703 15.6

DDL 0.00000296 1717 15.7

DDL 0.00000155 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 [<0.008]

17:15 [<0.008]

12:10 [<0.008]

Test End Time

Cobalt (Co) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.0000000877] 1703 15.6

BDL [<0.0000000926] 1717 15.7

BDL [<0.0000000909] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 0.038

17:15 0.031

12:10 [<0.021]

Test End Time

Lead (Pb) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

DDL 0.000000281 1703 15.6

DDL 0.000000245 1717 15.7

BDL [<0.000000164] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 0.61

17:15 0.423

12:10 [<0.422]

Test End Time

Manganese (Mn) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

DDL 0.0000012 1703 15.6

DDL 0.000000873 1717 15.7

BDL [<0.000000873] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 1.058

17:15 0.661

12:10 0.658

Test End Time

Nickel (Ni) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

DDL 0.00000222 1703 15.6

DDL 0.00000146 1717 15.7

DDL 0.00000145 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

1 6/29/2010 8:15 6/29/2010

2 6/29/2010 12:55 6/29/2010

3 6/30/2010 7:50 6/30/2010

Run Number Test Start Date Test Start Time Test End Date
Measured Value 

(ppb) Basis (Wet or Dry) Test Method Used 

12:30 [<0.691]

17:15 [<0.472]

12:10 [<0.388]

0.000691

Test End Time

Selenium (Se) Emission Test Results
Data Flag (ADL, 

BDL, DDL)

Test Method 

Comments

BDL [<0.00000195] 1703 15.6

BDL [<0.00000140] 1717 15.7

BDL [<0.00000115] 1721 15.4

Calculated 

Emission Rate 

(lb/mmBtu)

Steam Output 

(1000 lb/hr)

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture (%)
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

12.3 6.3 383635 130.2 1478 bituminous ton/day Other

12 6.8 383563 129.9 1478 bituminous ton/day Other

12 6.8 384645 129.1 1444 bituminous ton/day Other

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature 

(F)

Fuel #1
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method Fuel Input Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #2 Fuel #3
Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Method 5/29

Method 5/29

Method 5/29

Other Supporting Information

Fuel #4
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

2 6/29/2010 11:10

3 6/29/2010 13:25

4 6/30/2010 7:50

Run Number Test Start Date Test Start Time
Please note QA/QC documentation starting in Column "AI"

Measured Value 

(μg/dscm) Basis (Wet or Dry)

6/29/2010 13:10 0.83 Dry

6/29/2010 15:25 0.61 Dry

6/30/2010 9:50 0.5 Dry

Test End Date Test End Time

Total Vapor Phase Mercury Em
 starting in Column "AI"

Test Method Used Data Flag (ADL, 

BDL, DLL)

Test Method 

Comments (lb/mmBtu)

U.S. EPA Method 30B ADL 7.20E-07

U.S. EPA Method 30B ADL 5.48E-07

U.S. EPA Method 30B ADL 4.49E-07

Total Vapor Phase Mercury Emission Test Results

Steam Output 

(1000 lb/hr)
Fuel Input Rate

15.6 12.3 6.3 383635 130.2

15.7 12 6.8 383568 129.9

15.6 12 6.8 384645 129.1

Total Heat 

Input 

(mmBtu/hr)

Flue Gas 

Moisture 

(%)

Flue Gas 

CO2 (%)

Flue Gas 

O2 (%)

Flue Gas 

Flow Rate 

(dscfm)

Flue Gas 

Temperature (F)
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel Input 

Rate

Fuel #1 Fuel #2
Fuel Type Units of 

Measure

Measurement 

Method

Fuel Input 

Rate Fuel Type Units of Measure

Measurement 

Method

Fuel #3 Fuel #4
 QA/QC Documentation

Trap ID Section 1 

Mass (ng)

Section 2 

Mass (ng)

Total 

Mass (ng)

Initial 

Spike 

(ng)

Total NonSpike (ng)

Other Supporting Information
Sample 

Volume 

(dscm)

Volume 

Difference (%)

Volume Diff. 

Limit

Breaktrough 

(%)

Breaktrough 

Limit

Concentration 

(μg/dscm) Trap ID

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

#DIV/0! #DIV/0!

Trap #1

≤20% of field 

recovery test

≤ 10% of 

Section 1 Hg 

mass for Hg 

conc. >1 

μg/dscm: or ≤ 

20% of Section 
Section 1 

Mass

Section 2 

Mass

Total 

Mass

Initial 

Spike

Total NonSpikeSample 

Volume

Volume 

Difference (%)

Volume Diff. 

Limit

Trap #2

≤20% of field 

recovery test
Breaktrough (%) Breaktrough 

Limit

Concentration 

(μg/dscm) Abs. diff. RD (%) Limit Crec

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

#DIV/0! #DIV/0! #DIV/0! #DIV/0!

Paired Trap Agreement (RD) Measured Spik

≤ 10% of Section 

1 Hg mass for 

Hg conc. >1 

μg/dscm: or ≤ 

20% of Section 1 

for Hg conc.≤1 

≥10 % RD mass 

for Hg conc. >1 

μg/dscm: or 

≤20% RD or ≤0.2 

μg/dscm abs.diff. 

for Hg conc. ≤1 
R (%) by 

Run Ravg (%) Limit

#DIV/0!

Average 

Recovery, 

between 85 and 

115%

Measured Spike Recovery ( R )