NUREG/IA-0024

International

Agreement Report

Application of

RELAP5/MOD3.1 Code

to the LOFT Test L3-6

Prepared by

S. S. Pylev and V. L. Roginskaja

Nuclear Safety Institute

Russian Research Centre

"Kurchatov Institute"

Kurchatov Square, 1

123182, Moscow

Russia

Office of Nuclear Regulatory Research

U.S. Nuclear Regulatory Commission

Washington, DC 20555-0001

February 1998

Prepared as part of

The Agreement on Research Participation and Technical Exchange

under the Code Assessment and Maintenance Program

Published by

U.S. Nuclear Regulatory Commission
AVAILABILITY NOTICE

Availability of Reference Materials Cited In NRC Publications

Most documents cited In NRC publications will be available from one of the following sources:

1. The NRC Public Document Room, 2120 L Street, NW.. Lower Level, Washington, DC 20555-0001

2. The Superintendent of Documents, U.S. Government Printing Office, P. O. Box 37082. Washington, DC

20402-9328

3. The National Technical Information Service. Springfield, VA 22161-0002

Although the listing that follows represents the majority of documents cited in NRC publications, It Is not Intended to be exhaustive.

Referenced documents available for Inspection and copying for a fee from the NRC Public Document Room

Include NRC correspondence and Internal NRC memoranda; NRC bulletins, circulars, information notices, Inspection and Investigation notices; licensee event reports; vendor reports and correspondence: Commission

papers; and applicant and licensee documents and correspondence.

The following documents In the NUREG series are available for purchase from the Government Printing Office:

formal NRC staff and contractor reports, NRC-sponsored conference proceedings. International agreement

reports, grantee reports, and NRC booklets and brochures. Also available are regulatory guides, NRC regulations in the Code of Federal Regulations, and Nuclear R'3gulatory Commission Issuances.

Documents available from the National Technical Information Service Include NUREG-serles reports and technical reports prepared by other Federal agencies and reports prepared by the Atomic Energy Commission,

forerunner agency to the Nuclear Regulatory Commission.

Documents available from public and special technical libraries Include all open literature items, such as books,

Journal articles, and transactions. Federal Register notices, Federal and State legislation, and congressional

reports can usually be obtained from these libraries.

Documents such as theses, dissertations, foreign reports and translations, and non-NRC conference proceedings are available for purchase from the organization sponsoring the publication cited.

Single copies of NRC draft reports are available free, to the extent of supply, upon written request to the Office

of Administration, Distribution and Mail Services Section, U.S. Nuclear Regulatory Commission, Washington,

DC 20555-0001.

Copies of Industry codes and standards used In a substantive manner in the NRC regulatory process are maintained at the NRC Library, Two White Flint North, 11545 Rockville Pike, Rockville, MD 20852-2738. for use by

the public. Codes and standards are usually copyrighted and may be purchased from the originating organization or, If they are American National Standards, from the American National Standards Institute, 1430 Broadway. New York, NY 10018-3308.

DISCLAIMER NOTICE

This report was prepared under an International cooperative agreement for the exchange of technical information. Neither the United States Government nor any agency thereof, nor any of their employees, makes any

warranty, expressed or Implied, or assumes any legal liability or responsibility for any third party's use, or the

results of such use, of any information, apparatus, product, or process disclosed in this report, or represents

that Its use by such third party would not infringe privately owned rights.
NUREG/IA-0024

International

SAgreement Report

Application of

RELAP5/MOD3.1 Code

to the LOFT Test L3-6

Prepared by

S. S. Pylev and V. L Roginskaji

Nuclear Safety Institute

Russian Research Centre

"Kurchatov Institute"

Kurchatov Square, 1

123182, Moscow

Russia

Office of Nuclear Regulatory Research

U.S. Nuclear Regulatory Commission

Washington, DC 20555-0001

February 1998

Prepared as part of

The Agreement on Research Participation and Technical Exchange

under the Code Assessment and Maintenance Program

Published by

U.S. Nuclear Regulatory Commission

ABSTRACT

A calculation of LOFT Experiment L3-6, a small break equivalent to a 4-in. diameter rupture

in the cold leg of a four-loop commercial pressurized water reactor, has been performed to

help validate RELAP5/MOD3.1 for this application.

The version of the code to be used is SCDAP/RELAP5/MOD3.1.8d0.

Three calculations were carried out in order to study the sensitivity to change break nozzle

superheated discharge coefficient.

Conducted comparative analysis of the LOFT L3-6 experiment shows on the whole a

reasonable agreement between calculated and measured data. Some discrepancies in the system

pressure do not distort a picture of the transient.

1
Contents

ABSTRACT 1

1. INTRODUCTION. 3

2. FACILITY AND TEST DESCRIPTION. 4

2.1. The LOFT for the L3-6 Experiment. 4

2.2. The L3-6 Experiment. 5

3. THE CODE. 5

4. INPUT DECK DEVELOPMENT. 5

4.1. Noding. 5

4.2. Initial conditions. 6

5. TRANSIENT ANALYSIS. 7

5.1. The Main Course of Transient. 7

5.2. Transient Results. 7

5.3. Sensitivity Calculations. 8

6. RUN STATISTICS. 9

7. CONCLUSION. 10

8. REFERENCES. 11

Appendix A

Steady-State Input set

Transient Input set

Appendix B

Tables

Appendix C

Figures

2
1. INTRODUCTION.

An International Thermal-Hydraulic Code Assessment and Application Program (ICAP) is at

present being conducted by several countries under the auspices of USNRC. The goal of the

program is to make quantitative statements regarding the prediction capabilities of the current

best-estimate thermal-hydraulic computer codes. Such codes have been used for many years as

state-of-the art instruments to study and verify numerical and correlative computational models

with experimental results. Some of these codes have reached a high degree sophistication. So

far, however, these codes have not achieved status as reactor licensing tools. The present

ICAP aims to quantify uncertainties in the codes so that the codes may be used for licensing

purposes.

The SCDAP/RELAP5/MOD3.1 code has been chosen by RRC KI as tool for performing

Nuclear Reactor Safety Analysis.

Before undertaking the formal plant calculations, the code is being tested in a wide range of

experiments. This exercise is necessary to help identify and quantify any code shortcoming, in

particular for the Russian types of reactors.

The LOFT L3-6 experiment has been chosen as a part of the Russian Thermal-Hydraulic bestestimate codes Verification Program.

The LOFT-experiment series L-3 was designed to provide large-scale blowdown system data

for PWR small break transients. As part of the Russian ICAP contribution one experiment out

of the L3 series was assigned. In the experiment treated in this report, the LOFT L3-6, the

main circulation pumps were allowed to operate at normal speed throughout the test.

This calculation is to form part of assessment matrix for the RELAP5 code. This matrix seeks

to cover the range of conditions likely to be found when calculating full scale plant transients,

and this test, in particular, contains many features that are typical for small break accidents.

3
2. FACILITY AND TEST DESCRIPTION.

2.1. The LOFT for the L3-6 Experiment.

The LOFT (Loss-of-Fluid-Test) facility is a 50-MW(t) PWR with instrumentation to measure

and provide data on the thermal-hydraulic conditions throughout the system. Operation of the

LOFT system is typical of large [- 1000 MW(e)] commercial PWR operations. The LOFT is a

scaled down on a volume and a flow area of components and power representation of a PWR.

The elevations were not preserved with several components. The LOFT facility consists of:

* A reactor vessel with an annular downcomer, a lower plenum, an upper plenum,

and a nuclear core (5.5-ft length) with lower and support structure.

* An active intact loop with a steam generator, a pressurizer, and two parallel

primary coolant pumps.

" A passive broken loop with a simulated steam generator and pump, and two

pipelines (dead-ended or connected to blowdown assemblies for large breaks);

" A blowdown suppresion system consisting of a header, supression tank and a spray

system.

" An emergency core coolant (ECC) injection system consisting of a low head safety

injection pump, a high head safety injection pump, and a accumulator, and the

associated pipework.

The Experiment L3-6 is one of Small Break Experiments Series L3 that was designed to

provide large-scale blowdown system data for a PWR small break transient. In the L3-6 a

small break is an offtake pipe, 34 mm in diameter, connected at right angles to the 14-in. cold

leg of the active loop. This pipe contains a break orifice and leads to a valve and further to a

blowdown suppression tank. The valve is opened to initiate a break. The flow out of the cold

leg is choked at the break orifice that has an area (205.9 mm2) corresponding to the flow area

of a 4-in. diameter break (2.5%) in a commercial PWR.

In the L3-6 the accumulator and Low Pressure Injection System (LPIS) were not actuated, and

the Pressure Injection System (HPIS) flow was directed to the reactor Downcomer.

The broken loop recirculation lines were isolated.

The primary coolant pumps were operated during the experiment. Cooling water was injected

to the bearings of the pumps.

The Experiment L3-6 principal objective was to determine the primary system mass inventory

and distribution as a function of time during the small break depressurization. The specific goal

was to compare with similar Experiment L3-5 to see an influence of the pump run on a core

uncovery.

The LOFT main components and small break configuration are shown in Fig. 1 (Appendix C).

4
2.2. The L3-6 Experiment.

In the Experiment L3-6:

" The Pressurizer heaters were turned off prior to blowdown.

" The reactor with the power level 50 MW was scrammed - 6 s before blowdown

initiation.

* When the control rods were fully inserted, blowdown was initiated from the cold leg.

* In secondary side termination of main feed water and MSCV (Main Steam Control

Valve) closure were started at Scram signal.

" Auxiliary feed water was initiated at 73 s and terminated at 1856 s.

" The HPIS of the ECC injection system was initiated at 3.6 s after break on.

" The primary coolant pumps were automatically tripped at 2371.4 s, when the lowest

indicated primary coolant hot leg pressure reached 2.15 MPa.

The Pump stop indicates the L3-6 finishing and beginning of another Experiment (L8-1).

3. THE CODE.

The code used in calculations is the latest version .8d0 of the SCDAP/RELAP5/MOD3.1. The

version was received from INEL in the May 1994 according to the Agreement between RRC

KI and US NRC. Code has been installed on the IBM PC486/DX2 with reducing of the main

dynamic dimension (lfsize = 450000).

4. INPUT DECK DEVELOPMENT.

4.1. Noding.

As we only started to simulate the LOFT Experiments with the code RELAP5, and there is

collected large experience of modelling and analysing of these transients transferred in many

reports, so we used in this L3-6 calculation the traditional model as a basis of input data set.

Hydrodynamic components and heat structures geometry data were taken from Input Dataset

Reference Document /5/ prepared in Winfrith Centre. Initial conditions cards were added.

Total configuration and numbering of components were preserved as in reference. Our

corrected noding scheme is in Fig. 2.

The main modifications put in the developed input model are as follows:

5
In secondary side the component separatr was replaced with branch. Our experience

shows that similar change permits to receive stable and rather realistic physical

conditions in the Steam generator (accounting energy conservation);

In the Primary side the Downcomer and the Filler gap were divided in parallel flow

channels feeding from the Intact loop and the Broken loop hot legs. Now the

Downcomer is represented as 206 and 216 components, and the Filler gap is 208 and

218. Also, the inlet annulus of the vessel is divided in two parts: 200, 202, 204 and

210, 212, 214;

Cooling water injection to pumps feeds into volume 140;

The break unit is represented as a horizontal volume connecting the cold leg pipe (184

volume) with a crossflow junction and a discharge volume (805) with a valve junction

(183). The break valve 183 has a fully opened area in 205.9 mm2 and a choked flow

flag.

4.2. Initial conditions.

The initial state of system before a scram signal was reached in the usual procedure.

Preliminary distribution of temperatures and pressures were put down in an input deck, and

time dependent volumes were applied as pressure controllers for the Steam Generator and the

Pressurizer. In the Secondary side velocities were used in junction initial conditions cards.

The established conditions are compared to experimental magnitudes in Table 1 (Appendix B).

The coolant temperatures in the Intact loop and the Steam Generator turned out to be a bit

over the upper limit values. This excess was neglected because acceptable heat transfer

through the Steam generator tube walls was achieved. The temperatures in the Broken loop

and the other parameters were agreed with the L3-6 initial conditions measured values, within

experimental uncertainties.

6
5. TRANSIENT ANALYSIS.

5.1. The Main Course of Transient.

When performing of post-test calculations, one has possibility to face to measured data. To run

more successfully an experimental HPIS flow rate set on time was used in the transient. Rates

of closure of the main steam valve (MSCV) and terminating of the main feed supply were

adjusted to reach correct increase of the Steam Generator Dome pressure during the early

stage of the transient (20 to 40 s) through the comparison to experimental pressure. Finally,

main feed is terminated in 4 s after blowdown initiation and MSCV is closed in 10 s after

blowdown. Information of the MSCV partial opening (14% of a full area) occurred on - 88 s

after rupture was used in the steam line operation setting.

Useful references were discovered out from a report on the same Experiment analysis /4/. That

are:

In the Experiment MSCV control logic incorrectly triggered on a noise at 88 s;

Recommendation of using 0.84 value as a two-phase choking multiplier at a break

junction.

Our test runs with a two-phase discharge coefficient (0.82 to 0.88 variety) showed that 0.85 is

rather suitable to the developed model. Thereby, the default value 1.0 was set for a subcooled

coefficient, 0.85 for a two-phase coefficient. Transiting to single vapour flow regime was

occurred in the transient run at -860 s and the exercises with the restart point at the 800 s

were conducted with a superheated coefficient value varied in a wide range: from 0.5 to 1.1.

The run with the superheated multiplier equals to 0.6 presents as a base case. Two other runs

with 0.76 and 1.0 values will be shown later.

The prepared input data set and restart transient files are enclosed in a full form (Appendix A).

Timings of main events are shown in comparison in Table 2.

5.2. Transient Results.

The results of the LOFT L3-6 RELAP5/MOD3.1.8d0 post-test calculations are shown in

Appendix C.

As it was stated above, the substance of the L3-6 is the investigation of the system

depressurization. Special attention is paid to the pressure response during the postulated

transient.

The early stage of the transient is distinctive with emptying of the Pressurizer. As can be seen

from Fig. 3, the liquid level in the Pressurizer was calculated to drop to 0.04 m, which was the

uncertainty limit in the experimental measurement about 4 s later than occurred in the

experiment. The calculated Pressurizer pressure, as shown in Fig. 4 was calculated to decrease

7
a little slower than occurred during the experiment. This difference is not enough to do search

for whys. Then, the primary side pressure is checked out of the hot leg pressure (Fig. 5).

Calculation plot goes close to experimental one until - 860 s. In the secondary pressure plot

(Fig. 6) the occasional opening of MSCV is reflected into drops in pressure and liquid level

(Fig. 7) at 100 s about for all the plots. The calculated value of the Steam Generator collapsed

level is a little underestimated. This can be due to the voidage in the riser region or differences

in geometric details between the input model and the reference being in the cross sectional area

and height. However, divergence between a calculated and measured levels do not oversized

10 cm, that, on our opinion, is not important for the LOFT L3-6 experiment. The liquid level in

the Upper plenum of the Reactor vessel (Fig. 8) is shown only for calculation. The HPIS flow

rate (Fig. 10) was set in the input deck by table (on the measured data), and so it is presented

for calculation only. Calculation temperature plots (Fig. 11 and 12) are not coincident with real

plots exactly, in particular, for the reactor Downcomer temperature (Fig. 12). The cause of this

distortion could be a slightly incorrect initial temperature state (as seen in Table 1).

Obvious discrepancies with the experiment becomes clear in the run when the second third of

the transient starting, concerned to the mass flow rate through break orifice (Fig. 9) and the

hot leg pressure (Fig. 5). At the time about 820 s the calculation shows sharp decrease of the

primary system pressure. Non-realistic behaviour of the pressure can be explained with not

absolutely correct simulation by the RELAP5 code of the critical discharge at transiting from a

two-phase flow to a superheated vapour flow. As seen in Fig. S-8, at the time about 820 s

calculation shows a instantaneous jump in void fraction of the discharge volume (snglvol 184)

from about 0.6 up to 1.0. This leads to a sharp increase of the gas velocity (to 40 mrs) through

break (Fig.' S-7) and further to a primary system pressure fall (Fig. 5, S-2). At the same

moment, the mass rate is perpendicular reduced (Fig. 9, S-1).

After the single vapour discharge began, the code produced a mass error. In Fig. S-5 one may

see that emass parameter is negative and is increasing by magnitude after 860 s.

The coolant in the Primary side is at the saturation, so temperatures of the fluid (Fig. 11, 12, S4) and of the cladding (Fig. 13, 14) have the shape which is similar to the primary pressure.

5.3. Sensitivity Calculations.

A few calculations were carried out in order to study sensitivity to variety of the superheated

discharge coefficient. Three of them are shown in figures S-1 + S-4.

The main goal of this study is an attempt to avoid the non-realistic primary pressure

decreasing, observed after 820 s. The superheated discharge coefficients in sensitivity studies

demonstrated as the most interesting are 0.6, 0.76 and 1.0.

The reduction of superheated discharge coefficient from 1.0 up to 0.6 causes some reducing of

the rate of pressure decreasing, but does not influences on the transient principle picture.

However, for the magnitude of the superheated discharge coefficient in 0.6 some

overestimating of the calculated primary system pressure during the last stage of the transient

(,t > 2000 s) is observed.

8
Varying in superheated coefficients is not depicted in the Secondary pressure (Fig. S-3).

6. RUN STATISTICS.

The input model for RELAP5/MOD3.1 calculation for the LOFT L3-6 encompassed:

S

S

S

0

136

153

144

670

Volumes

Junctions

Heat Structures

Total Mesh Points

The volumes include: 2 pump components, 8 time-dependent volumes of which two were used

for the steady-state initiating. Among the junctions there are 3 valve components and 4 time

dependent junctions.

During the transient calculation the following features were:

" Computer time

" Number of time steps

" Number of volumes

For Transient real time

CPU = 39040.4 sec,

DT = 81532,

C= 136

RT = 2400 sec.

Resulting in the following grind time (the code efficiency factor):

CPU

Grind time = = 0.00352 Cx DT

The computer used was IBM PC486/DX2.

9
7. CONCLUSION.

The LOFT small break experiment L3-6 has been assessed with using the

RELAP5/MOD3.1.8d0 code. Three sensitivity calculations were carried out with changes

concerning the break junction superheated discharge coefficient.

The code predictions compare reasonably well with the experiment concerning to the first-hand

parameters such as the system pressure, fluid temperatures and the Pressurizer and the Steam

generator liquid levels.

In the calculated steady state, the experimental initial data were fairly well reproduced.

The predicted voiding start for the hot leg and for the cold leg of the Intact loop was in close

agreement with the experiment.

Some discrepancies in the primary system pressure after the cold leg dried out took place. This

behaviour of the primary system pressure can be explained as not correct the

RELAP5/MOD3.1 code simulation of the vapour discharge flow at transiting from a twophase flow to a superheated flow.

Two sensitivity calculations with different superheated discharge coefficients showed that

changing of the superheated discharge coefficient from 1.0 up to 0.6 leads to some reduction

of the rate of pressure decreasing. However, for the magnitude of the superheated discharge

coefficient in 0.6 some overestimate of the primary system pressure at the final stage of the

transient (,t>2000 s) is observed.

In general, a whole agreement between the experimental data and the code calculational values

in performed simulation of the LOFT Experiment L3-6 was estimated as good. As many times

noticed, the code RELAP5/MOD3 is really convenient in qualified simulation and estimating of

a wide variety of operational and accident transients.

10
8. REFERENCES.

1. D.L. Reeder.

LOFT System and Test Description (5.5-ft Nuclear Core LOCEs). NUREG/CR0247, TREE-1208.

2. Bayless, J.M. Carpenter.

Experiment Data Report for LOFT Nuclear Small Break Experiment L3-6 and

Severe Core Transient Experiment L8-1. EG&G Idaho. NUREG/CR-1868.

3. J.C. Birchley.

LOFT Input Dataset Reference Document for RELAP5 Validation Studies.

Winfrith Technology Centre. NUREG/IA-0072.

4. A.H. Scriven.

Application of the RELAP5/MOD2 Code to the LOFT Tests L3-5 and L3-6.

Winfrith Technology Centre. NUREG/IA-0060.

5. C.M. Allison et al.

SCDAP/RELAP5/MOD3.1 Code Manual. Volume V: Developmental Assessment

(Draft). EG&G Idaho. NUREG/CR-6150.

6. SCDAP/RELAP5/MOD3.1. Input Requirement. INEL 1993. NUREG/CR-6150.

11

Appendix A

INPUT DATA SET

STEADY-STATE RUN

=LOFT Small Break Experiment L3-6

*crdno vol-no elev liqjtype system-name

120 100010000 0.0 h2o Primary

121 530010000 6.5269 h2o Second

*crdnotime min-dt max_dt ctrl minor major restart

201 30.0 1.0-7 0.01 14003 10000 10000 10000

* Trip Input Data

*

*

*

Assesment of RELAPS/MOD3.1

Against LOFT Small Break Experiment L3-6

*

*

*

401 - Auxiliary trip, always true

402- Auxiliary trip, always false

* Initial Conditions

Power Level

Mass Flow Rate

Hot leg Presssure

50.00+1.00 MW

483.30 : 2.60 kg/s

14.87 ± 0.14 MPa

* 403 - SCRAM Reactivity Table no 609

* Main Steam Valve no 541 Close

* Feed Water Valve no 566 Close

* 404 - Break time

* 405 & 601 - PCP off

* 406 & 602 - IIPIS Start (Set Point P <=13.16 MPa)

* 407 & 603 - Aux. Feed Water Start

* 604 - on while PRZ pressure set to steady-state

* 610 - MSCV Open trip (6.98 < P > 7.12)

* 613 - MSCV Close trip (6.57 < P < 6.50)

Intact Loop

Cold leg Temperature 557.90± 1.1 0 K

Hot leg Temperature 577.10± 1.80 K

Broken Loop

Cold leg Temperature 557.60 + 2.60 K

Hot leg Temperature 561.40 + 2.60 K

Pressurizer

Pressure

Liquid Level

Steam Volume

Liquid Volume

Liquid Temperature

.4.90 ± 0.25 MPa

1.18 ±0.11 m

0.29 ± 0.06 m3

0.64 ± 0.06 m3

614.70 ± 1.40 K

Steam Generator

Pressure 5.57 ± 0.06 MPa

Liquid Level 0.22 ± 0.03 m (the liquid level is defined as 0.0 at 2.95 m

above the top of the tube sheet)

Liquid Temperature 542.80 ± 0.80 K

Mass Flow Rate 27.80 ± 0.10 kg/s

* The Input deck is based on the LOFT facility informations,

* on the Dataset devoloped by INFL for use with RELAP5/MODI

* and LOFT Input Dataset Reference Document for RELAPS

* Validation Studies prepaired by Winfrith Technology Center.

* Modifications to the standard model:

". The Downcomer model was changed to a split (2 - channel)

* downcomer model and was renodalized to allow volume

* boundaries to have the same elevation as core volume

* boundaries.

,

* 2. The Break offtake was modelled with a cross-flow junction

* from the main loop piping feeding into horizontal volume.

* At the end of the horizontal volume a valve was included

* disharging directly into a time dependent volume.

* Auxiliary Trips:

no var code rel varcode const lin time on

401 time 0 ge null 0 -1.0 1 0.0 ,

no var code rel varcode const lin time on

402 time 0 It null 0 -1.0 I -1.0 *

* SCRAM

* no var code rel var code const lin timeon

403 time 0 It null 0 -1.0 I -1.0

* BREAK

*no var code rel var code const lin timeon

404 time 0 ge timeof 403 6.0 n -1.0

* PCP off

* no var code rel var code .const lin time-on

405 p 100010000 le null 0 2.15+6 n -1.0

* no trip.no rel trip.no lin timeon

601 404 and 405 n -1.0 ,

* ECCS Control Logic

* no var code rel var code const lin time-on

406 p 610010000 le null 0 13.16+6 n -1.0

*no trp.no rel trip.no fin time_on

602 404 and 406 I -1.0

* Auxiliary Feed Water Logic

* no var code rel var code const lin timeon

407 time 0 ge timeof 403 6.0 I -1.0

* no trip-no rel trip-no lin timeon

603 404 and 407 I -1.0 ,

* Pressurizer Stady state controller

* no trip.no rel trip-no lin time-on

604 -403 and -403 n 0.0

* PCP Injection

* no var code rel var code const lin timeon

408 p 100010000 ge null 0 2.15+6 I -1.0

* no trip-no rel trip.no lin timeon

605 -408 and -408 1 0.0

* Main Steam Control Valve

100 new stdy-st

*crdno gas-type

110 nitrogen

*crdno mas .fraction

115 1.0

A-1
*no trip-no rel trip-no lin timepon

606 -403 and -403 n 0.0 t

no trip.no rel trip-no lin time-on

607 -606 and -606 n -1.0

* no var code rtl var code const lin timcon

409 p 530010000 ge null 0 7.12+6 n -1.0

* no var code rel var code const lin timepon

410 p 530010000 ge null 0 6.98+6 n -1.0 ,

no var code rel var code const lin timeon

411 p 530010000 te null 0 6.50+6 n -1.0 ,

ano var code rtl var code const tin time_on

412 p 530010000 le null 0 6.57+6 n -1.0

a no var code rel var code const lin time-on

413 time 0 ge timeof 403 94.0 I -1.0 ,

a no var code rel var code const lin timeon

414vivarea 540 ge null 0 0.15 1 -1.0

a Open trip

*no trip-no rel trip-no lin time-on

608 609 and 410 n -1.0 ,

no trip-no rel trip-no lin time-on

609 409 or 608 n -1.0 a

* no trip-no rel trip-no lin timeon

*610 403 and 609 n -1.0

610 -414 and 413 n -1.0*MSCVtriggeredonthenoise

a Close trip

*no trip-no rel trip-no lin time-on

611 612 and 412 n -1.0

*no trip.no rel trip-no tin timeon

612 411 or 611 n -1.0

* Component no 105

a Intact Loop Ilot leg to Pressurizer Tee ,

*crdno name type

1050000 llIL-2 snglvol *crdno area length volume h-ang v-ang delz

1050101 0.06416 1.0866 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

1050102 4.0e-5 0.0 11000

*crdno ebt pressure temp

1050200 003 14.8742+6 579.368

a Component no 107

* Intact Loop Hot leg Pressurizer Tee

* (V107 = 0.25*FI05+0.25*F11O)

*crdno name type

1070000 IItL-PRZ branch

*crdno no.juns. icc

1070001 3 1

*crdno area length volume h-ang v-ang delz

1070101 0.0 0.5 0.03057 0.0 0.0 0.0

*crdno rough dhy pvbfe

1070102 4.0e-5 0. 11000

*crdno ebt pressure temp

1070200 003 14.8661+6 579.364

*crdno from to area floss doss fvcahs

1071101 105010002 107010001 0.0 0.06 0.06 010000

1072101 107010002 110010001 0.0 0.06 0.06 010000

1073101 107010003 400010001 1.45-3 0.93 0.93 010000

*crdno flowf flowg velj

1071201 482.99 0.0 0.0

1072201 483.16 0.0 0.0

1073201 0.0 0.0 0.0

a Component no 110

a Intact Loop Hot leg from Pressurizer Tee ,

*crdno name type

I I00000 IIIL-3 branch

*crdno no.juns. ice

1100001 1 1

*crdno area length volume h-ang v-ang delz

1100101 0.0 0.8561 0.049782 0.0 0.0 0.0

*crdno rough dhy pvbfe

1100102 4.0e-5 0. 11000

*crdno ebt pressure temp

1100200 003 14.8570+6 579.360

*crdno from to area floss floss fvcahs

1101101 110010002 112010001 0.0 0.15 0.15 010000

*crdno flowf flowg velj

1101201 483.16 0.0 0.0

a Component no 112

a Intact Loop Hot leg elbow and half of Reducer

* no trip-no rel trip.no

*613 403 or 612

613 403 and 414

fin timeon

n -1.0

n -1.0

a

a Intact Loop (Primary Side)

* Component no 100 a Reactor Vessel nozzle Intact Loop Ilot Leg ,

*crdno name type

1000000 IHL-1 branch

*crdno no.juns. ice

1000001 3 1

*crdno area length volume h-ang v-ang delz

1000101 0.0 1.4458 0.09274 0.0 0.0 0.0

*crdno rough dhy pvbfe

1000102 4.0-5 0. 11000

*crdno ebt pressure temp

1000200 003 14.8816+6 579.371

*crdno from to area floss doss fvcahs

1001101 252010003 100010001 0.0634 0.1 0.1 010000

* RPV->IHL

1002101 100010002 105010001 0.0634 0.085 0.085 010000

* IHlL2->AHL2

1003101 100010001 185010002 0.0634 7200.0 7200.0 000000

* IHL->ICL

*crdno flowf flowg velj

1001201 471.00 0.0 0.0

1002201 482.99 0.0 0.0

1003201 -11.998 0.0 0.0

*crdno name type

1120000 IL,-4 pipe

*crdno numbvol

1120001 2

*crdno area vol.

1120101 0.0 2

*crdno length vol.

1120301 1.3889 1

1120302 0.70769 2

*crdno volume vol.

1120401 0.079697 1

1120402 0.057961 2

*crdno v-ang vol.

1120601 0.0 1

1120602 90.0 2

*crdno elev vol.

A-2
1120701 0.0 1

1120702 0.246 2

*crdno rgh dhy vol.

1120801 4.0-5 0.0 2

*crdno floss floss jun

1120901 0.2 0.2 1

*crdno pvbfe vol.

1121001 11000 2

*crdno fvcahs jun.

1121101 000000 1

*crdno ebt pressure temp a4 a5 a6 vol.no

1121201 003 14.8456+6 579.355 0.0 0.0 0.0 1

1121202 003 14.8581+6 579.362 0.0 0.0 0.0 2

*crdno ci

1121300 1

*crdno flowf flowg velj jun

1121301 483.15 0.0 0.0 1

* Component no 114

* Intact Loop SG Inlet Plenum

*(crdno name type

1140000 IHL-SGIn branch

*crdno no.juns. icc

1140001 2 1

*crdno area length volume h-ang v-ang delz

1140101 0.0 0.63 0.3227 0.0 90.0 0.513

*crdno rough dhy pvbfe

1140102 4.0-5 1.022-2 11000

*crdno ebt pressure temp

1140200 003 14.7721+6 579.334

*crdno from to area floss floss fvcahs

1141101 112020002 114010001 0.0512 0.0 0.0 000100

1142101 114010002 115010001 0.0 0.0 0.0 000100

*crdno flowf flowg velj

1141201 483.15 0.0 0.0

1142201 483.12 0.0 0.0

1151001 00000 10

*crdno fvcahs jun.

1151101 000000 9

*crdno ebt pressure temp a4 a5 a6 vol.no

1151201 003 14.7552+6 577.375 0.0 0.0 0.0

1151202 003 14.7470+6 575.605 0.0 0.0 0.0

1151203 003 14.7387+6 572.561 0.0 0.0 0.0

1151204 003 14.7276+6 569.922 0.0 0.0 0.0

1151205 003 14.7179+6 568.018 0.0 0.0 0.0

1151206 003 14.7128+6 566.269 0.0 0.0 0.0

1151207 003 14.7109+6 564.198 0.0 0.0 0.0

1151208 003 14.7087+6 562.288 0.0 0.0 0.0

1151209 003 14.7071+6 561.321 0.0 0.0 0.0

1151210 003 14.7055+6 560.282 0.0 0.0 0.0

1

2

3

4

5

6

7

8

9

10

*crdno ctl

1151300 1

*crdno flowf

1151301 483.11

1151302 483.11

1151303 483.11

1151304 483.10

1151305 483.10

1151306 483.10

1151307 483.10

1151308 483.09

1151309 483.09

flowg

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

velj jun

0.0 1

0.0 2

0.0 3

0.0 4

0.0 5

0.0 6

0.0 7

0.0 8

0.0 9

* Component no 115

* Intact Loop SG Tubes

*crdno name type

1150000 SG-Tubes pipe

*crdno numb.yol

1150001 10

*crdno area vol.

1150101 0.1513 10

*crdno length vol.

1150301 0.5972 1

1150302 0.3048 2

1150303 0.6096 4

1150304 0.4612 6

1150305 0.6096 8

1150306 0.3048 9

1150307 0.5972 10

*crdno volume vol.

1150401 0.0 10

*crdno v-ang vol.

1150601 90.0 5

1150602 -90.0 10

*crdno elev vol.

1150701 0.5972 1

1150702 0.3048 2

1150703 0.6096 4

1150704 0.4612 5

1150705 -0.4612 6

1150706 -0.6096 8

1150707 -0.3048 9

1150708 -0.5972 10

*crdno rgh dhy vol.

1150801 2.50-6 1.022-2 10

*crdno floss rloss jun

1150901 0.0 0.0 9

*crdno pvbfe vol.

* Component no 116 * Intact Loop SG outlet Plenum ,

*crdno name type

1160000 IIIL-SGOu branch

*crdno no.juns. icc

1160001 2 1

*crdno area length volume h-ang v-ang delz

1160101 0.0 0.63 0.335 0.0 -90.0 -0.513

*crdno rough dhy pvbfe

1160102 4.0-5 1.022-2 11000

*crdno ebt pressure temp

1160200 003 14.7087+6 560.281

*crdno from to area floss floss fvcahs

1161101 115100002 116010001 0.0 0.0 0.0 000100

1162101 116010002 118010001 0.0 0.0 0.0 000100

*ctdno flowf flowg velj

1161201 483.09 0.0 0.0

1162201 483.09 0.0 0.0

* Component no 118

* Intact Seal Loop #1

* 52 degree elbow, half of Reducer, 90 degree elbow *t

*crdno name typ

1180000 ISL-I pi

*crdno numb..vol

1180001 3

*crdno area vol.

1180101 0.0 2

1180102 0.0634 3

*crdno length vol.

1180301 0.547 I

1180302 0.689 2

1180303 0.550 3

*crdno volume vol.

1180401 0.0437 1

1180402 0.0462 2

1180403 0.0 3

*crdno v-ang vol.

1180601 -90.0 3

*crdno elev vol.

1180701 -0.498 1

1180702 -0.689 2

1180703 -0.356 3

*crdno rgh dhy v

1180801 4.0-5 0.0

pe

Aol.

3

A-3
*crdno floss floss jun

1180901 0.083 0.083 I

1180902 0.104 0.104 2

*crdno pvbfe vol.

1181001 11000 3

*crdno fvcahs jun.

1181101 000000 2

*crdno ebt pressure temp a4 a5 a6 vol.no

1181201 003 14.6787+6 560.269 0.0 0.0 0.0 1

1181202 003 14.6692+6 560.264 0.0 0.0 0.0 2

1181203 003 14.6640+6 560.261 0.0 0.0 0.0 3

*crdno ctl

1181300 1

*crdno flowf flowg velj jun

1181301 483.09 0.0 0.0 2

* PCP #1

*crdno name type

1350000 PCP-I pump

*crdno area length volume h-ang v-ang delz pvbfe

1350101 0.0366 0.0 0.099 0.0 90.0 0.319 00000

*crdno from area floss floss fvcahs

1350108 130010002 0.0 0.017 0.017 000000

*crdno to area floss floss fvcahs

1350109 140010001 0.0 0.05 0.05 000000

*crdno ebt pressure temp

1350200.003 14.8996+6 560.383

*crdno flag flowf flowg velj

1350201 1 232.15 0.0 0.0

1350202 1 232.15 0.0 0.0

*crdno id 2faz 2fazd torq pvel ptrip rvrs 1350301 0 0 0 -1 -1 601 0

*crdno rpvel initv rflo rhead hiorq momi

1350302 369. 0.889 0.3155 96. 500.6 1.431

*crdno rdens rpmtorq tf2 tf0 tfl tf3

1350303 613.6 0.0 207.433 0.004 19.598 0.0

*crdno rspeed 13 12 I! 10

1350308 0.212465 0.0 -25.0 29.5 6.28

*crdno time-stop max-fvel maxjrvel

1350310 0.0 0.0 0.0

Pump Data

* Single Phase Ilead Curves

* Component no 120

* Intact Seal Loop #2: Pipe, Inlet to pump suction ,

*crdno name type

1200000 ISL-2 branch

*crdno no.juns. icc

1200001 3 1

*crdno area length volume h-ang v-ang delz

1200101 6.34-2 0.76 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

1200102 4.0-5 0.0 11000

*crdno ebt pressure temp

1200200 003 14.6602+6 560.257

*crdno from to area floss floss fvcahs

1201101 118030002 120010001 0.0 0.1 0.1 000000

1202101 120010002 125010001 0.0317 0.4 0.4 000000

*PCP#1

1203101 120010002 155010001 0.0317 0.4 0.4 000000

* PCP #2

*crdno flowf flowg velj

1201201 483.09 0.0 0.0

1202201 232.15 0.0 0.0

1203201 250.94 0.0 0.0

* Component no 125

* Intact Loop : Half of Pump Suction. elbow

*crdno name type

1250000 PCPISuc branch

*crdno no.juns. ice

1250001 I I

*crdno area length volume h-ang v-ang delz

1250101 0.0 1.003 0.0613 0.0 90.0 0.521

*crdno rough dhy pvbfe

1250102 4.0-5 0. 11000

*crdno ebt pressure temp

1250200 003 14.6725+6 560.257

*crdno from to area floss floss fvcahs

1251101 125010002 130010001 0.0 0.13 0.13 000000

*crdno flowf flowg velj

1251201 232.15 0.0 0.0

* Component no 130

* Intact Loop: Half of Reducer, PCP I inlet ,

*crdno name type

1300000 PCPI-In snglvol *crdno area length volume h-ang v-ang delz

1300101 0.0 0.457 0.0189 0.0 90.0 0.457

*crdno rough dhy pvbfe

1300102 4.0e-5 0.0 11000

*crdno ebt pressure temp

1300200 003 14.6543+6 560.249

* Component no 135

* head curve no I

*crdno curve type curve regime

1351100 1 1

* g/gnom h/hnom

1351101 0.00000 1.4036

1351102 0.19061 1.3636

1351103 0.38963 1.3186

1351104 0.59396 1.2328

1351105 0.79020 1.1336

1351106 1.00000 1.0000

* head curve no 2

*crdno curve type curve regime

1351200 1 2

g/gnom b/hnom

1351201 0.00000 -0.67000

1351202 0.20000 -0.50000

1351203 0.40000 -0.25000

1351204 0.57554 0.00000

1351205 0.74432 0.25830

1351206 0.77348 0.37780

1351207 0.86313 0.63260

1351208 1.00000 1.00000

a

a head curve no 3

*crdno curve type curve regime

1351300 1 3

* g/gnom h/hnom

1351301 -1.00000 2.4722

1351302 -0.80574 2.0474

1351303 -0.60690 1.8310

1351304 -0.40683 1.6240

1351305 -0.20017 1.4705

1351306 0.00000 1.4036

a

* head curve no 4

*crdno curvetype curve regime

1351400 1 4 a g/gnom hdhnom

1351401 -1.00000 2.472200

1351402 -0.82297 1.996800

A-4
1351403 -0.63332 1.589700

1351404 -0.45534 1.327900

1351405 -0.27109 1.194900

1351406 -0.17716 1.060500

1351407 -0.090730 1.015600

1351408 0.000000 0.934279

* head curve no 

5

,

*crdno curve type curve regime

1351500 1 5

* g/gnon i/hnom

1351501 0.000000 0.2500

1351502 0.200000 0.2800

1351503 0.400000 0.3400

1351504 0.411800 0.2768

1351505 0.597630 0.4584

1351506 0.793467 0.6992

1351507 0.000000 1.0000

* head curve no 

6

*crdno curve type curve regime

1351600 1 

6

* g/gnom bdhnom

1351601 0.000000 0.934279

1351602 0.091099 0.922900

1351603 0.186509 0.896300

1351604 0.271762 0.875000

1351605 0.455872 0.843300

1351606 0.574406 0.835000

1351607 0.740576 0.846600

1351608 0.766619 0.846900

1351609 0.871471 0.883800

1351610 1.000000 1.000000

* head curve no 

7

,

*crdno curve type curve regime

1351700 1 

7

* g/gnom h/Mnom

1351701 -1.0000 -1.0000

1351702 -0.8000 -0.6300

1351703 -0.6000 -0.3000

1351704 -0.4000 -0.0500

1351705 -0.2000 0.1500

1351706 0.0000 0.2500

* head curve no 8

,

*crdno curve type curve regime

1351800 1 

8

* g/gnom h/hnom

1351801 -1.00000 -1.00000

1351802 -0.80000 -0.97000

1351803 -0.60000 -0.95000

1351804 .0.40000 -0.88000

1351805 -0.20000 -0.80000

1351806 0.00000 -0.67000

*1

*: Single Phase Torque Data *÷ 

+

* torque curve no I

*crdno curve type curve regime

1351900 2 

1

* g/gnom h/hnom

1351901 0.00000 0.60320

1351902 0.19300 0.63250

1351903 0.39300 0.73690

1351904 0.59552 0.83310

1351905 0.79782 0.92290

1351906 1.00000 1.00000

* torque curve no 2

,

*crdno curve type curve regime

1352000 2 

2

* Hggnom Mhnom

1352001 0.00000 -0.670000

1352002 0.40000 -0.250000

"1352003 0.50000 0.150000

1352004 0.73725 0.526586

1352005 0.76804 0.606594

1352006 0.86723 0.743660

1352007 1.00000 1.000000

* torque curve no 

3

*crdno curve type curve regime

1352100 2 

3

* g/gnom h/Mmom

1352101 -1.00000 1.98430

1352102 -0.80096 1.39400

1352103 -0.60638 1.09750

1352104 -0.40686 0.82200

1352105 -0.19928 0.66480

1352106 0.00000 0.60320

,

* torque curve no 4

,

*crdno curve type curve regime

1352200 2 4

* g/gnom hfimom

1352201 -1.000000 1.98430

1352202 -0.822340 1.83080

1352203 -0.633710 1.68240

1352204 -0.458530 1.55700

1352205 -0.267023 1.43620

1352206 -0.176107 1.38790

1352207 -0.089310 1.34810

1352208 0.000000 1.23361

,

* torque curve no 5

,

*crdno curve type curve regime

1352300 2 

5

* g/gnom hhnom

1352301 0.00000 -0.45000

1352302 0.40000 -0.25000

1352303 0.50000 0.00000

1352304 1.00000 0.35690 **

torque curve no 6

*crdno curvetype curve regime

1352400 2 

6

* g/gnom hlhnom

1352401 0.00000 1.23361

1352402 0.090643 1.19650

1352403 0.188569 1.10960

1352404 0.273470 1.04160

1352405 0.458669 0.89580

1352406 0.574480 0.78070

1352407 0.738160 0.61340

1352408 0.768520 0.58490

1352409 0.870057 0.48770

1352410 1.000000 0.35690 **

torque curve no 7

*crdno curve type curve regime

1352500 2 

7

* g/gnom h/hmom

1352501 -1.00000 -1.00000

1352502 -0.30000 -0.90000

1352503 -0.10000 -0.50000

1352504 0.00000 -0.45000

* torque curve no 

8

A-5
*crdno curve type curve regime

1352600 2 8

* g/gnom hMmom

1352601 -1.00000 -1.00000

1352602 -0.25000 -0.90000

1352603 -0.08000 -0.80000

1352604 0.00000 -0.67000

* Two - Phase Multiplier Data

* Head Curve *

*crdno extr.ind

1353000 0

* voidg head..mult

1353001 0.000 0.000000

1353002 0.020 0.020000

1353003 0.060 0.050000

1353004 0.100 0.100000

1353005 0.200 0.460000

1353006 0.240 0.800000

1353007 0.300 0.960000

1353008 0.400 0.980000

1353009 0.600 0.970000

1353010 0.800 0.900000

1353011 0.900 0.800000

1353012 0.960 5.000000

1353013 1.000 0.000000

,

* Torque Curve ,

*crdno extr.ind

1353100 0

* voidg torqjmult

1353101 0.00000 0.00000

1353102 0.12500 0.07000

1353103 0.16500 0.12500

1353104 0.24000 0.56000

1353105 0.80000 0.56000

1353106 0.96000 0.45000

1353107 1.00000 0.00000

,

* Pump 2-Phase Difference Data ,

head curve no I

*

*crdno curve type curve regime

1354100 1 1

* g/gnom Mmom

1354101 0.00000 0.00000

1354102 0.10000 0.83000

1354103 0.20000 1.09000

1354104 0.50000 1.02000

1354105 0.70000 1.01000

1354106 0.90000 0.94000

1354107 1.00000 1.00000 a

1354301 -1.00000 -1.16000

1354302 -0.90000 -1.24000

1354303 -0.80000 -1.77000

1354304 -0.70000 -2.36000

1354305 -0.60000 -2.79000

1354306 -0.50000 -2.91000

1354307 -0.40000 -2.67000

1354308 -0.25000 -1.69000

1354309 -0.10000 -0.50000

1354310 0.00000 0.00000

**

head curve no 4

*crdno curve type curve regime

1354400 1 4

* g/gnom h/hnom

1354401 -1.00000 -1.16000

1354402 -0.90000 -0.78000

1354403 -0.80000 -0.50000

1354404 -0.70000 -0.31000

1354405 -0.60000 -0.17000

1354406 -0.50000 -0.08000

1354407 -0.35000 0.00000

1354408 -0.20000 0.05000

1354409 -0.10000 0.08000

1354410 0.00000 0.11000

***

head curve no 5

*crdno curve type curve regime

1354500 1 5 a glgnom hMhnom

1354501 0.00000 0.00000

1354502 0.20000 -0.34000

1354503 0.40000 -0.65000

1354504 0.60000 -0.93000

1354505 0.80000 -1.19000

1354506 1.00000 -1.47000 aa head curve no 6

aa head curve no 

2

*crdno curve type curve regime

1354600 I 

6 a g/gnom Mhnom

1354601 0.00000 0.110000

1354602 0.10000 0.130000

1354603 0.25000 0.150000

1354604 0.40000 0.130000

1354605 0.50000 0.070000

1354606 0.60000 -0.040000

1354607 0.70000 -0.230000

1354608 0.80000 -0.510000

1354609 0.90000 -0.910000

1354610 1.00000 -1.470000

,

a head curve no 7

*crdno curve type curve regime

1354700 1 

7 a g/gnom hlhnom

1354701 -1.00000 0.0000

1354702 0.00000 0.0000

a head curve no 8

*crdno curve type curve regime

1354800 1 8 a g/gnom h/hnom

1354801 -1.00000 0.0000

1354802 0.00000 0.0000

a Iorque curve no 

I

*crdno curve type curve regime

1354900 2 

1

* g/gnom h/hnom

*crdno curve type curve regime

1354200 1 2

S g/gnom hMnom

1354201 0.00000 0.00000

1354202 0.10000 -0.04000

1354203 0.20000 0.00000

1354204 0.30000 0.10000

1354205 0.40000 0.21000

1354206 0.80000 0.67000

1354207 0.90000 0.80000

1354208 1.00000 1.00000 aa head curve no 3

*crdno curve type curve regime

1354300 1 3 a g/gnom h/hnom

A-6
1354901

1354902

1354903

1354904

1354905

1354906

0.00000

0.19300

0.39300

0.59552

0.79782

1.00000

0.60320

0.63250

0.73690

0.83310

0.92290

1.00000

* g/gnom h/hnom

1355501 -1.00000 -1.00000

1355502 -0.30000 -0.90000

1355503 -0.10000 -0.50000

1355504 0.00000 -0.45000

**

torque curve no 8

** torque curve no 

2

*crdno curve type curve regime

1355000 2 

2

* g/gnom hMhnom

1355001 0.000000 -0.670000

1355002 0.400000 -0.250000

1355003 0.500000 0.150000

1355004 0.737255 0.526586

1355005 0.768049 0.606594

1355006 0.867230 0.743660

1355007 1.000000 1.000000

*crdno curve type curve regime

1355600 2 

8

* g/gnom h/hnom

1355601 -1.00000 -1.00000

1355602 -0.25000 -0.90000

1355603 -0.08000 -0.80000

1355604 0.00000 -0.67000

**

torque curve no 3

*crdno curve type curve regime

1355100 2 

3

* g/gnom Mmom

1355101 -1.00000 1.98430

1355102 -0.80096 1.39400

1355103 -0.60638 1.09750

1355104 -0.40686 0.82200

1355105 -0.19928 0.66480

1355106 0.00000 0.60320

* torque curve no 

4

*crdno curve type curve regime

1355200 2 

4

* g/gnom Mmom

1355201 -1.000000 1.98430

1355202 -0.822340 1.83080

1355203 -0.633710 1.68240

1355204 -0.458530 1.55700

1355205 -0.267023 1.43620

1355206 -0.176107 1.38790

1355207 -0.089310 1.34810

1355208 0.000000 1.23361

**

torque curve no 

5

* Component no 140

* Intact Loop: Pump I outlet pipe. elbow

*crdno name type

1400000 PCPI-dsh snglvol *crdno area length volume h-ang v-ang delz

1400101 0.0366 0.502 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

1400102 4.0-5 0.0 11000

*crdno ebt pressure temp

1400200 003 15.1535+6 560.384

* Component no 145

* Intact Loop: Pipe, Reducer, PCPI outlet

*crdno name type

1450000 PCPI-out branch

*crdno no.juns. icc

1450001 2 

1

*crdno area length volume h-ang v-ang delz

1450101 0.0 1.4084 0.0633 0.0 0.0 0.0

*crdno rough dhy pvbfe

1450102 4.0e-5 0.0102 11000

*crdno cx pressure temp

1450200 003 15.1251+6 560.384

*crdno from to area floss floss fvcahs

1451101 140010002 145010001 0.0 0.0 0.0 000000

1452101 145010002 150010001 0.0 0.1 0.1 000000

*crdno flowf flowg velj

1451201 232.24 0.0 0.0

1452201 232.24 0.0 0.0

*,

* Component no 150

* Intact Loop: PCP outlet tee

*crdno name type

1500000 PCP-out branch

*crdno no.juns. ice

1500001 2 

1

*crdno area length volume h-ang v-ang delz

1500101 0.0634 0.4966 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

1500102 4.0-5 0.0 11000

*crdno ebt pressure temp

1500200 003 15.0673+6 560.403

*crdno from to area floss floss fvcahs

1501101 170010002 150010001 0.0183 0.1 0.1 000000

1502101 150010002 175010001 0.0000 0.0 0.0 000000

*crdno flowf flowg velj

1501201 250.94 0.0 0.0

1502201 483.18 0.0 0.0

* Component no 155

* Intact Loop: Ilulf of PCP2 Suction, elbow

*crdno curve type curve regime

1355300 2 

5

* g/gnom Mhnom

1355301 0.00000 -0.4500

1355302 0.40000 -0.2500

1355303 0.50000 0.0000

1355304 1.00000 0.3569 **

torque curve no 6

*crdno curve type curve regime

1355400 2 

6

* g/gnom Imhnom

1355401 0.000000 1.23361

1355402 0.090643 1.19650

1355403 0.188569 1.10960

1355404 0.273470 1.04160

1355405 0.458669 0.89580

1355406 0.574480 0.78070

1355407 0.738160 0.61340

1355408 0.768520 0.58490

1355409 0.870057 0.48770

1355410 1.000000 0.35690 **

torque curve no 

7

*crdno curve type curve regime

1355500 2 

7

A-7
*crdno name type

1550000 PCPISuc branch

*crdno no.juns. icc

1550001 1 1

*crdno area length volume h-ang v-ang delz

1550101 0.0 1.003 0.0613 0.0 90.0 0.521

*crdno rough dhy pvbfe

1550102 4.0-5 0.0 11000

*crdno ebt pressure temp

1550200 003 14.6685+6 560.261

*crdno from to area floss floss fvcahs

1551101 155010002 160010001 0.0 0.13 0.13 000000

*crdno flowf flowg velj

1551201 250.94 0.0 0.0

* Component no 160

* Intact Loop: Half of Reducer. PCP 2 inlet

*crdno name type

1600000 PCP2-in snglvol *crdno area length volume h-ang v-ang delz

1600101 0.0 0.457 0.0189 0.0 90.0 0.457

*crdno rough dhy pvbfe

1600102 4.0-5 0.0 11000

*crdno ebt pressure temp

1600200 003 14.6478+6 560.252

1750000 ICL-I pipe *crdno numb._vol

1750001 2

*crdno area vol.

1750101 0.0634 2

*crdno length vol.

1750301 0.559 1

1750302 0.613 2

*crdno v-ang vol.

1750601 0.0 2

*crdno rgh dhy vol.

1750801 4.0-5 0.0 2

*crdno floss floss jun

1750901 0.0 0.0 1

*crdno pvbfe vol.

1751001 11000 2

*crdno fvcahs jun.

1751101 000000 1

*crdno ebt pressure temp a4 a5 a6 vol.

1751201 003 15.0664+6 560.402 0.0 0.0 0.0 1

1751202 003 15.0654+6 560.400 0.0 0.0 0.0 2

*crdno ctl

1751300 1

*crdno flowf flowg velj jun

1751301 483.18 0.0 0.0 1

* Component no 165

* PCP #2

* Component no 180

* Intact Loop: Pipe to ECC Line

*crdno name type

1650000 PCP-2 pump

*crdn area length volume h-ang v-ang delz pvb

1650101 0.0366 0.0 0.099 0.0 90.0 0.319 00CX

*crdno from area floss floss fvcahs

1650108 160010002 0.0 0.017 0.017 000000

*crdno to area floss floss fvcahs

1650109 170010001 0.0 0.05 0.05 000000

*crdno ebt pressure temp

1650200 003 14.8642+6 560.379

*crdno flag flowf flowg velj

1650201 1 250.94 0.0 0.0

1650202 1 250.94 0.0 0.0

*crdno id 2faz 2fazd torq pvel ptrip rvrs

1650301 135 135 135 -1 -1 601 0

*crdno rpvel initv sflo rhead utorq momi

1650302 369. 0.892 0.3155 96. 500.6 1.431

*crdno rdens rpmtorq tf2 tf0 ff1 tf3

1650303 613.6 0.0 207.433 0.0444 19.5987 0.0

*crdno rspeed 13 12 11 10

1650308 0.212465 0.0 -25.0 29.5 6.28

*crdno time-stopmaxvel maxjvel

1650310 0.0 0.0 0.0

* Component no 170

* Intact Loop: Pump 2 elbow, inlet of PCP outlet

*crdno name type

1700000 PCP2-out branch

*crdno no.juns. icc

1700001 0 1

*crdno area length volume h-ang v-ang delz

17001010.0366 0.514 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

1700102 4.0-5 0.0 11000

*crdno ebt pressure temp

1700200 003 15.0879+6 560.455

* Component no 175

* Intact Loop: 90 degree elbow, Pipe section, elbow

*,

*cdo name type

fe

*crdno name type

1800000 ECC-Tee branch

*crdno no.juns. icc

1800001 2 1

*crdno area length volume h-ang v-ang delz

1800101 0.0 1.01 0.06406 0.0 0.0 0.0

*crdno rough dhy pvbfe

1800102 4.0-5 0.0 11000

*crdno ebt pressure temp

1800200 003 15.0640+6 560.396

*crdno from to area floss floss fvcahs

1801101 175020002 180010001 0.0 0.0 0.0 000000

1802101 180010002 184010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

1801201 483.18 0.0 0.0

1802201 483.18 0.0 0.0

* Component no 182

* Break line ID=0.034m (1.3 in) from Break tee to Break orifice ,

*crdno name type

1820000 BRK-line pipe

*crdno numb.vol

1820001 1

*crdno area vol.

1820101 9.0792-4 1

*crdno length vol.

1820301 0.544 1

*crdno v-ang vol.

1820601 0.0 1

*crdno rgh dhy vol.

1820801 4.0-5 3.4-2 1

*crdno pvbfe vol.

1821001 10000 1

*crdno ebt pressure temp a4 aS a6 vol.

1821201 003 15.0630+6 477.030 0.0 0.0 0.0 1

* Component no 183

* Break orifice - Simulated 4 in break ofPWR (F = 205.6 mm2)

*crdno name type

1830000 brkvlv valve

*crdno from to area floss floss fvcahs

1830101 182010002 805000000 205.6-6 0.4 0.4 000100

A-8
*crdno sub-dsh 2ph-dsh

1830102 1.0 0.85 0.6

*crdno cfl flowf flowg velj

1830201 1 0.0 0.0 0.0

*crdno name

1830300 mtrvlv

*crdno openjtrip close.trip vlv..ch.r. in.pos

1830301 404 402 5.0 0.0

* Component no 805

* Break Disharge volume ,

*crdno name type

8050000 BRK-DSH tmdpvol

*crdno area length volume h-ang v-ang delz

8050101 3.5-3 1.0 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

8050102 0.0 0.0 00000

*crdno ebt

8050200 002

*crdno time pressure quals

8050201 0.0 1.0+5 1.0

9100101 7.-3 1.0 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

9100102 4.0-5 0.0 00000

*crdno ebt

9100200 001

*crdno time temp quals

9100201 0.0 305.0 0.0 'it

* Component no 911

* PCP Injection Pump

*crdno name type

9110000 PCP-INJ trndpjun

*crdno from to area

9110101 910000000 140010001 0.0

*crdno ctl trip

9110200 I 605

*crdno time flowf flowg velj

9110201 -1. 0.0 0.0 0.0

9110202 0.0 0.094 0.0 0.0

* Reactor Vessel

* Component no 184

* Intact Loop: Cold leg break Tee

* Component no 200

* Reactor Vessel: Inlet Annulus, Upper (from intact loop (3/4))

*crdno name type

1840000 ICL-BTee branch

*crdno no.juns. icc

1840001 1 1

*crdno area length volume h-ang v-ang delz

1840101 0.0 0.284 0.01805 0.0 0.0 0.0

*crdno rough dhy pvbfe

1840102 4.0-5 0.0 11000

*crdno ebt pressure temp

1840200 003 15.0630+6 560.395

*crdno from to area floss doss fvcahs

1841101 184010003 182010001 9.0792-4 0.5 0.5 000100

*crdno flowf flowg velj

1841201 0.0 0.0 0.0

Component no 185

*Intact Loop: Pipe from ECC line, nozzle

*crdno name type

1850000 ICL-Vin branch

*crdno no.juns. icc

1850001 3 1

*cydno area length volume h-ang v-ang delz

1850101 0.0 1.152 0.07349 0.0 0.0 0.0

*crdno rough dhy pvbfe

1850102 4.0-5 0.0 11000

*crdno ebt pressure temp

1850200 003 15.0621+6 560.392

*cnrno from to area floss doss fvcahs

1851101 184010002 185010001 0.0 0.0 0.0 000000

1852101 185010002202010003 0.0634 2.8 2.8 000000

1853101 185010002208010001 0.0 52.0 52.0 000000

*crdno flowf flowg veUj

1851201 483.18 0.0 0.0

1852201 426.45 0.0 0.0

1853201 44.736 0.0 0.0

*crdno name type

2000000 RV-In3-1 annulus

*crdno no.vol

2000001 1

*crdno area vol.

2000101 0.00 1

*crdno lcnght vol.

2000301 0.1874 1

*crdno volume vol.

2000401 0.03766 1

*crdno angle vol.

2000601 90.0 1

*crdno rgh dhy vol.

2000801 4.0-5 0.172 1

*crdno pvbfe vol.

2001001 11000 1

*crdno ebt pressure temp a4 a5 a6 vol.

2001201 003 15.0132+6 558.966 0.0 0.0 0.0 1

* Component no 202

* Reactor Vessel: Inlet Annulus, middle (from intact loop (3/4))

*crdno name type

2020000 RV-In3-2 branch

*crdno no.juns. icc

2020001 2 1

*crdno area length volume h-ang v-ang delz

2020101 0.0 0.2852 0.05733 0.0 -90.0 -0.2852

*crdno rough dhy pvbfe

2020102 4.0-5 0.178 11000

*crdno ebt pressure temp

2020200 003 15.0149+6 560.372

*crdno from to area floss dloss fvcahs

2021101 202010001 200010001 0.0 0.0 0.0 000000

2022101 202010002 204010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

2021201 0.13167 0.0 0.0

2022201 319.80 0.0 0.0

* PCP Injection

* Component no 910

* PCP Injection Tank

*crdno name type

9100000 PCP-WAT tnmdpvol

*crdno area length volume h-ang v-ang dclz

* Component no 204

* Reactor Vessel: Inlet Annulus, lower (from intact loop (3/4))

*crdno name type

2040000 RV-In3-3 annulus

*crdno no.vol

A-9
2040001 1

*crdno area vol.

2040101 0.0 1

*crdno lenght vol.

2040301 0.2814 1

*crdno volume vol.

2040401 0.05656 1

*crdno angle vol.

2040601 -90.0 1

*crdno rgh dhy vol.

2040801 4.0-5 0.172 1

*crdno pvbfe vol.

2041001 11000 1

*crdno ebt pressure temp a4 a5 a6 vol.

2041201 003 15.0153+6 560.370 0.0 0.0 0.0 1

* Component no 205

* Reactor Vessel: Inlet Unnulus to Downcomer junction

*crdno name type

2050000 In-Dw sngliun

*crdno from to area floss dloss fvcahs

2050101 204010002 206010001 0.0 0.0 0.0 000000

•crdno cti flowf flowg velj

2050201 1 319.82 0.0 0.0

* Component no 206

Reactor Vessel: Downcomer (from intact loop (3/4))

2080000 FilG-3/4 annulus

*crdno no.vol

2080001 4

*crdno area vol.

2080101 0.02911 4

*crdno lenght vol.

2080301 1.382 1

2080302 1.236 2

2080303 1.118 3

2080304 1.250 4

*crdno volume vol.

2080401 0.0 4

*crdno angle vol.

2080601 -90. 4

*crdno rgh dhy vol.

2080801 4.0-5 0.0 4

*crdno floss floss jun

2080901 0.0 0.0 3

*crdno pvbfe vol.

2081001 11000 4

*crdno fvcahs jun.

2081101 000000 3

*crdno ebt pressure temp a4 a5 a6 vo

2081201 003 15.0216+6 560.215 0.0 0.0 0.0

2081202 003 15.0312+6 560.070 0.0 0.0 0.0

2081203 003 15.0399+6 559.894 0.0 0.0 0.0

2081204 003 15.0486+6 559.758 0.0 0.0 0.0

*crdno ctl

2081300 1

*crdno flowf flowg veUj jun

2081301 42.063 0.0 0.0 1

2081302 38.500 0.0 0.0 2

2081303 43.233 0.0 0.0 3

1

2

3

4

*crdno name type

2060000 DWC-3/4 annulus

*crdno no.vol

2060001 6

*crdno area vol.

2060101 0.1065 6

*crdno lenght vol.

2060301 0.958 1

2060302 0.579 2

2060303 0.657 3

2060304 0.559 5

2060305 0.520 6

*crdno vol vol.

2060401 0.0 6

*crdno angle vol.

2060601 -90. 6

*crdno rgh dhy vol.

2060801 4.0-5 0.102 6

*crdno floss doss jun

2060901 0.0 0.0 5

*crdno pvbfe vol.

2061001 11000 6

*crdno fvcahs jun.

2061101 000000 5

*crdno ebt pressure temp a4 a5 a6 vol.

2061201 003 15.0151+6 560.363 0.0 0.0 0.0

2061202 003 15.0200+6 560.361 0.0 0.0 0.0

2061203 003 15.0240+6 560.359 0.0 0.0 0.0

2061204 003 15.0279+6 560.357 0.0 0.0 0.0

2061205 003 15.0315+6 560.355 0.0 0.0 0.0

2061206 003 15.0349+6 560.354 0.0 0.0 0.0

*crdno ctl

2061300 1

*crdno flowf flowg velj jun

2061301 319.82 0.0 0.0 1

2061302 319.82 0.0 0.0 2

2061303 319.81 0.0 0.0 3

2061304 319.81 0.0 0.0 4

2061305 319.81 0.0 0.0 5

a Component no 210

a Reactor Vessel: Inlet Annulus. Upper (from broken loop (1/4)) a

*crdno name type

2100000 RV-lnI-I annulus

*crdno no.vol

2100001 I

*crdno area vol.

2100101 0.00 1

*crdno lcnght vol.

2100301 0.1874 1

*crdno volume vol.

2100401 0.01255 1

*crdno angle vol.

2100601 90.0 1

*crdno rgh dhy vol.

2100801 4.0-5 0.172 1

*crdno pvbfe vol.

2101001 11000 1

*crdno ebt pressure temp a4 a5 a6 vol.

2101201 003 15.0132+6 558.160 0.0 0.0 0.0 1

a Component no 212

a Reactor Vcssel: Inlet Annulus, middle (from broken loop (1/4))

*crdno name type

2120000 RV-Inl-2 branch

*crdno no.ju=s. icc

2120001 2 1

*crdno area length volume h-ang v-ang delz

2120101 0.0 0.2852 0.01911 0.0 -90.0 -0.2852

*crdno rough dhy pvbfe

2120102 4.0-5 0.178 11000

*crdno ebt pressure lemp

2120200 003 15.0149+6 560.364

*crdno from to area floss doss fvcahs

2121101 212010001 210010001 0.0 0.0 0.0 000000

2122101 212010002 214010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

2121201 -0.12890 0.0 0.0

1

2

3

4

5

6

a Component no 208

a Reactor Vessel: Vessel Filler Cap (from intact loop (3/4))

*crdno name type

A-10
2122201 106.63 0.0 0.0

• Component no 214

• Reactor Vessel: Inlet Annulus, lower (from broken loop (3/4))

*crdno name type

2140000 RV-Inl-3 annulus

*crdno no.vol

2140001 1

*•crdno area vol.

2140101 0.0 1

*crdno lenght vol.

2140301 0.2814 1

*crdno volume vol.

2140401 0.01885 1

*crdno angle vol.

2140601 -90.0 1

*crdno rgh dhy vol.

2140801 4.0-5 0.172 1

*crdno pvbfe vol.

2141001,11000 1

*crdno ebt pressure temp a4 aS a6 vol.

2141201 003 15.0153+6 560.362 0.0 0.0 0.0 1

* Component no 215

• Reactor Vessel: Inlet Unnulus to Downcomerjunction

*crdno name type

2150000 In-Dw sngljun

*crdno from to area floss dloss fvcahs

2150101 214010002 216010001 0.0 0.0 0.0 000000

*crdno ctl flowf flowg velj

2150201 1 106.62 0.0 0.0

a Component no 218

a Reactor Vessel: Vessel Filler Gap (from intact loop (1/4))

*crdno name type

2180000 FSIG-1/4 annulus

*crdno no.vol

2180001 4

*crdoo area vol.

2180101 0.02911 4

*crdno lenght vol.

2180301 1.382 1

2180302 1.236 2

2180303 1.118 3

2180304 1.250 4

*crdno volume vol.

2180401 0.0 4

*crdno angle vol.

2180601 -90. 4

*crdno rgh dhy vol.

2180801 4.0-5 0.0 4

*crdno floss floss jun

2180901 0.0 0.0 3

*crdno pvbfe vol.

2181001 11000 4

*crdno fvcahs jun.

2181101 000000 3

*crdno eh pressure temp a4 a5 a6 vo

2181201 003 15.0216+6 559.742 0.0 0.0 0.0

2181202 003 15.0312+6 559.746 0.0 0.0 0.0

2181203 003 15.0399+6 559.590 0.0 0.0 0.0

2181204 003 15.0486+6 559.685 0.0 0.0 0.0

*crdno cdl

2181300 1

*crdno flowf flowg velj jun

2181301 2.6695 0.0 0.0 1

2181302 6.2288 0.0 0.0 2

2181303 1.4931 0.0 0.0 3 Ak

1

2

3

4

* Component no 216

• Reactor Vessel: Downcomer (from broken loop (1/4))

*crdno name type

2160000 DWC-1/4 annulus

*crdno no.vol

2160001 6

*crdno area vol.

2160101 3.55-2 6

*crdno lenght vol.

2160301 0.958 1

2160302 0.579 2

2160303 0.657 3

2160304 0.559 5

2160305 0.520 6

*crdno vol vol.

2160401 0.0 6

*crdno angle vol.

2160601 -90. 6

*crdno rgh dhy vol.

2160801 4.0-5 0.102 6

*crdno floss dloss jun

2160901 0.0 0.0 5

*crno pvbfe vol.

2161001 11000 6

*crdno fvcahs jun.

2161101 000000 5

*crdno ebt pressure temp a4 aS a6 vol.

2161201 003 15.0151+6 560.356 0.0 0.0 0.0

2161202 003 15.0200+6 560.354 0.0 0.0 0.0

2161203 003 15.0240+6 560.352 0.0 0.0 0.0

2161204 003 15.0279+6 560.351 0.0 0.0 0.0

2161205 003 15.0315+6 560.349 0.0 0.0 0.0

2161206 003 15.0349+6 560.348 0.0 0.0 0.0

*crdno ctl

2161300 1

*crdno flowf flowg velj jun

2161301 106.62 0.0 0.0 5

a Component no 219

* Reactor Vessel: Downcomer cross junction

*crdno name type

2190000 dc-junc mtpljun

*crdno jun.no ctdw

2190001 13 0

*crdno from to area floss doss fvcahs

2190011 200010003 210010003 0.0 0.0 0.0 000000

2190021 202010003 212010003 0.0 0.0 0.0 000000

2190031 204010003 214010003 0.0 0.0 0.0 000000

2190041 206010003 216010003 0.0 0.0 0.0 000000

2190051 208010003 218010003 0.0 0.0 0.0 000000

*crdno subc.d.c. 2ph.d.c. suph.d.c, fromjincr tojncr zero jun.no

2190012 1.0 1.0 1.0 0 0 0 1

2190022 1.0 1.0 1.0 0 0 0 2

2190032 1.0 1.0 1.0 0 0 0 3

2190042 1.0 1.0 1.0 10000 10000 0 9

2190052 1.0 1.0 1.0 10000 10000 0 13

*crdno flowf flowg jun.no

2191011 0.12951 0.0 1

2191021 106.51 0.0 2

2191031 -1.18969-2 0.0 3

2191041 -4.21396-4 0.0 4

2191051 2.6724 0.0 5

2191061 -3.70813-4 0.0 6

2191071 3.5619 0.0 7

2191081 -1.94251-4 0.0 8

2191091 -4.7333 0.0 9

2191101 -6.78366-4 0.0 10

2191111 20.528 0.0 It

2191121 9.98058-4 0.0 12

2191131 -4.27175-3 0.0 13

1

2

3

4

5

6

A-11
* Component no 220

* Reactor Vessel: Lower Plenum lower

*crdno name type

2200000 LWPL-Dw branch

*crdno no.juns. icc

2200001 3 1

*crdno area length volume h-ang v-ang delz

2200101 0.790 0.370 0.0 0.0 90.0 0.370

*crdno rough dhy pvbfe

2200102 4.0-5 0.0 11000

*crdno ebt pressure temp

2200200 003 15.0346+6 559.842

*crdno from to area floss floss fvcahs

2201101 208040002 220010001 0.0 45.0 45.0 00000

2202101 218040002 220010001 0.0 45.0 45.0 000000

2203101 220010002 222010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

2201201 22.702 0.0 0.0

2202201 22.019 0.0 0.0

2203201 44.703 0.0 0.0

* Component no 222

* Reactor Vessel: Lower Plenum upper

*crdno name type

2220000 LWPL-Dw branch

*crdno no.juns. icc

2220001 3 1

*crdno area length volume h-ang v-ang delz

2220101 0.740 0.360 0.0 0.0 90.0 0.360

*crdno rough dhy pvbfe

2220102 4.0-5 0.0 11000

*crdno ebt pressure temp

2220200 003 15.0319+6 560.311

*crdno from to area floss floss fvcahs

2221101 206060002 222010002 0.0 2.0 2.0 000000

2222101 216060002 222010002 0.0 2.0 2.0 000000

2223101 222010002 225010001 0.15 1.5 1.5 000000

*crdno flowf flowg velj

2221201 319.82 0.0 0.0

2222201 106.61 0.0 0.0

2223201 471.12 0.0 0.0

a Component no 225 a Reactor Vessel: Lower Core Support

*crdno name type

2250000 CoreSup branch

*crdao no.juns. icc

2250001 2 1

*crdno area length volume h-ang v-ang delz

2250101 0.250 0.520 0.0 0.0 90.0 0.520

*crdno rough dhy pvbfe

2250102 4.0-5 0.095 11000

*crdno et pressure temp

2250200 003 15.0163+6 560.304

Ocrdno from to area floss doss fvcaIhs

2251101 225010002 230010001 0.0975 1.5 1.5 000000

2252101 225010002 235010001 0.0 21.0 21.0 000000

*crdno flowf flowg velj

2251201 453.46 0.0 0.0

2252201 17.655 0.0 0.0 a

*crdno length vol.

2300301 0.2795 5

2300302 0.3775 6

*crdno volume vol.

2300401 0.0 6

*crdno v-ang vol.

2300601 90.0 6

*crdno rgh dhy vol.

2300801 4.0-5 0.012 6

*crdno floss floss jun

2300901 0.0 0.0 1

2300902 0.66 0.66 2

2300903 0.0 0.0 3

2300904 0.66 0.66 4

23O0905 0.0 0.0 5

*crdno pvbfe vol.

2301001 00100 6

*crdno fvcahs jun.

2301101 000000 5

*crdno ebt pressure temp a4 a5 a6 vol

2301201 003 14.9878+6 560.859 0.0 0.0 0.0

2301202 003 14.9827+6 563.736 0.0 0.0 0.0

2301203 003 14.9745+6 568.584 0.0 0.0 0.0

2301204 003 14.9693+6 574.042 0.0 0.0 0.0

2301205 003 14.9609+6 578.573 0.0 0.0 0.0

2301206 003 14.9548+6 580.588 0.0 0.0 0.0

*crdno ctl

2301300 1

*crdno flowf flowg velj jun

2301301 453.46 0.0 0.0 5

1

2

3

4

5

6

a Component no 235 a Reactor Vessel: Core Bypass

*crdno name type

2350000 Core.byp pipe *crdno novol

2350001 3

*crdno area vol.

2350101 0.015 3

*crdno length vol.

2350301 0.559 2

2350302 0.657 3

*crdno volume vol.

2350401 0.0 3

*crdno v-ang vol.

2350601 90.0 3

*crdno rgh dhy vol.

2350801 4.-5 0.003 3

*crdno floss doss jun

2350901 0.0 0.0 2

*crdno pvbfe vol.

2351001 00000 3

*crdno fvcahs jun.

2351101 000000 2

*crdno ebt pressure temp a4 a5 a6 vo

2351201 003 14.9906+6 560.305 0.0 0.0 0.0 1

2351202 003 14.9790+6 560.313 0.0 0.0 0.0 2

2351203 003 14.9665+6 560.324 0.0 0.0 0.0 3

*crdno, ctl

2351300 1

*crdno flowf flowg velj jun

2351301 17.654 0.0 0.0 2

a Component no 230

a Reactor Vessel: Active Core

*crdno name type

2300000 Core pipe *crdno no.vol

2300001 6

*crdno area vol.

2300101 0.1705 6

a Component no 240

a Reactor Vessel: Upper end Box center/support

*crdno name type

2400000 corelow branch

*crdno no.juns. ioc

2400001 2 1

*crdno area length volume h-ang v-ang delz

2400101 0.2970.559 0.0 0.0 90.0 0.559

A-12
*crdno rough dhy pvbfe

2400102 4.0-5 0.145 00000

*crdno ebt pressure temp

2400200 003 14.9374+6 579.869

*crdno from to area floss floss fvcahs

2401101 230060002 240010001 0.120 1.5 1.5 000000

2402101 235030002 240010001 0.0 21.0 21.0 000000

*crdno flowf flowg velj

2401201 453.45 0.0 0.0

2402201 17.653 0.0 0.0

* Component no 245

* Reactor Vessel: Upper Support X-flow

*crdno name type

2450000 CoreSUp branch

*crdno no.juns. icc

2450001 2 1

*crdno area length volume h-ang v-ang delz

2450101 0.2970.559 0.0 0.0 90.0 0.559

*crdno rough dhy pvbfe

2450102 4.0-5 0.145 00000

*crdno ebt pressure temp

2450200 003 14.9334+6 579.869

*crdno from to area floss doss fvcahs

2451101 240010002 245010001 0.0 0.0 0.0 000000

2452101 245010002 251010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

2451201 471.09 0.0 0.0

2452201 -1.38548-3 0.0 0.0

* Component no 250

* Reactor Vessel: Upper flow skirt vol

*crdno name type

2500000 Up-Skirt branch

*crdno no.juns. icc

2500001 1 1

*crdno area length volume h-ang v-ang delz

2500101 0.1140.7004 0.0 0.0 90.0 0.7004

*crdno rough dhy pvbfe

2500102 4.0-5 0.131 00000

*crdno ebt pressure temp

2500200 003 14.9182+6 579.859

*crdno from to area floss doss fvcahs

2501101 245010002 250010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

2501201 471.08 0.0 0.0

* Component no 251

* Reactor Vessel: Dead End Fuel Modules

*crdno name type

2510000 DeadEnd snglvol

*crdno area length volume h-ang v-ang delz

2510101 0.183 0.700 0.0 0.0 90.0 0.700

*crdno rough dhy pvbfe

2510102 4.0-50.214 00000

*crdno ebt pressure temp

2510200 003 14.9307+6 577A02

a Component no 252

a Reactor Vessel: Upper Plenum lower a

*crdno name type

2520000 UpPl-low branch

*crdno no.juns. icc

2520001 2 1

*crdno area length volume h-ang v-ang delz

2520101 0.201 0.2852 0.0 0.0 90.0 0.2852

*crdno rough dhy pvbfe

2520102 4.0-5 0.0 11000

*crdno ebN pressure temp

2520200 003 14.9249+6 579.864

*crdno from to area floss doss fvcahs

2521101 252010002 255010001 0.0 0.006 0.006 000000

2522101 250010002 252010001 0.0 0.003 0.003 000000

*crdno flowf flowg velj

2521201 2.85066-2 0.0 0.0

"2522201 471.07 0.0 0.0

* Component no 255 a Reactor Vessel: Upper plenum bottom ,

*crdno name type

2550000 UpPi-bot branch

*crdno no.juns. icc

2550001 1 1

*crdno area length volume h-ang v-ang delz

25501010.288 0.7114 0.0 0.0 90.0 0.7114

*crdno rough dhy pvbfe

2550102 4.0-5 0.0 11000

*crdno ebt pressure temp

2550200 003 14.9227+6 573.761

*crdno from to area floss sloss fvcahs

2551101255010002 260010001 0.0 0.03 0.03 000000

*crdno flowf flowg velj

2551201 1.63408-2 0.0 0.0

a Component no 260

a Reactor Vessel: Upper plenum top

*crdno name type

2600000 UpPI-top snglvol

*crdno area length volume h-ang v-ang delz

26001010.244 0.712 0.0 0.0 90.0 0.712

*crdno rough dhy pvbfe

2600102 4.0-5 0.0 11000

*crdno ebt pressure temp

2600200 003 14.9177+6 572.721

a Broken Loop

a Component no 300

a Broken Loop: Vessel nozzle, Hot leg

*crdno name type

3000000 BIlL-I branch

*crdno no.juns. icc

3000001 2 1

*crdno area length volume h-ang v-ang delz

30001010.0634 0.876 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

3000102 4.0-5 0.0 11000

*crdno ebt pressure temp

3000200 003 14.9249+6 561.738

*crdno from to area floss dloss fvcahs

3001101 252010003 300010001 0.0634 0.0 0.0 000000

3002101 300010002 305010001 0.0 0.1 0.1 000000

*crdno flowf flowg velj

3001201 3.95983-2 0.0 0.0

3002201 3.81269-2 0.0 0.0

* Component no 305

a Broken Loop: BLIlL to RABS Tee ,

*crdno name type

3050000 BIlL-Tee branch

*crdno no.juns. icc

3050001 1 I

*crdno area length volume h-ang v-ang delz

3050101 0.0634 0.698 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

A-13
3050102 4.0-5 0.0 11000

*crdno ebt pressure temp

3050200 003 14.9249+6 561.373

*crdno from to area floss floss fvcahs

3051101 305010002 310010001 0.0 0.1 0.1 000000

*crdno flowf flowg velj

3051201 3.55093-2 0.0 0.0

* Component no 3 10

Broken Loop: BLHL contraction

$

*crdno name type

3100000 BHL-Con branch

*crdno no.juns. icc

3100001 2 0

*crdno area length volume h-ang v-ang delz

3100101 0.0 1.5001 0.06785 0.0 0.0 0.0

*crdno rough dhy pvbfe

3100102 4.0-5 0.0 11000

*crdno ebt pressure temp

3100200 003 14.9249+6 561.158

*crdno from to area floss floss fvcahs

3101101 380030002 310010003 0.0388 0.84 0.84 000000

3102101 310010002 315010001 8.365-30.0 0.0 000100

*crdno flowf flowg velj

3101201 -2.48442-2 0.0 0.0

3102201 5.27375-3 0.0 0.0

* Component no 315

* Broken Loop: Pipe to Isolation Valve *

*crdno name type

3150000 BIIL-end pipe

*crdno numbvol

3150001 2

*crdno area vol.

3150101 0.0 2

*crdno j.area vol.

3150201 0.011086 1

*crdno length vol.

3150301 0.488 1

3150302 1.6085 2

*crdno volume vol.

3150401 0.00541 1

3150402 0.0777 2

*crdno v-ang vol.

3150601 0.0 2

*crdno rgh dhy vol.

3150801 4.0-5 0.0 2

*crdno floss dloss jun

3150901 0.0 0.0 1

*crdno pvbfe vol.

3151001 11000 2

*crdno fvcahs jur.

3151101 000100 1

*crdno ebt pressure temp a4 a5 a6 vol

3151201 003 14.9249+6 559.178 0.0 0.0 0.0 1

3151202 003 14.9249+6 561.476 0.0 0.0 0.0 2

*crdno cfl

3151300 1

*crdno flowf flowg velj jun

3151301 3.87772-3 0.0 0.0 1

3350102 4.0-5 0.0 11000

*crdno eh pressure temp

3350200 003 15.0149+6 555A01

*crdno from to area floss floss fvcahs

3351101 212010003 335010001 0.0634 1.0 1.0 000000

3352101 335010002 340010001 0.0 0.1 0.1 000000

*crdno flowf flowg velj

3351201 9.33549-3 0.0 0.0

3352201 6.78439-3 0.0 0.0

* Component no 340

*Broken Loop: BCL to RABS Tee

*crdno name type

3400000 BCL-Tee branch

*crdtno no.juns. icc

3400001 1 1

*crdno area length volume h-ang v-ang delz

34001010.0634 0.698 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

3400102 4.0-5 0.0 11000

*crdno ebt pressure temp

3400200 003 15.0149+6 556.004

*crdno from to area floss floss fvcahs

3401101 340010002 345010001 0.0 0.1 0.1 000000

*crdno flowf flowg velj

3401201 6.79018-3 0.0 0.0

* Component no 345

* Broken Loop: BCL Contraction

*crdno name type

3450000 BCL-Con branch

*crdno no.juns. icc

3450001 2 1

*crdno area length volume h-ang v-ang delz

3450101 0.0634 0.974 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

3450102 4.0-5 0.0 11000

*crdno elt pressure temp

3450200 003 15.0149+6 556.005

*crdno from to area floss floss fvcahs

3451101345010003 3700100010.0388 0.84 0.84 010000

3452101 345010002 3500100010.0000 0.0 0.0 000000

*crdno flowf flowg velj

3451201 1.89770-3 0.0 0.0

3452201 4.91399-3 0.0 0.0

Component no 350

*Broken Loop: BCL Pipe to Isolation Valve

*crdno name type

3500000 BCL-end pipe

*crdno numb-vol

3500001 2

*crdno area vol.

3500101 0.0 2

*crdno j-area vol.

3500201 0.011086 1

*crdno length vol.

3500301 0.488 1

3500302 1.6085 2

*crdno volume vol.

3500401 0.00541 1

3500402 0.0777 2

*crdno v-ang vol.

3500601 0.0 2

*crdno rgh dhy vol.

3500801 4.0-5 0.0 2

*crdno floss floss jun

3500901 0.0 0.0 1

*crdno pvbfe vol.

3501001 11000 2

A-14

* Component no 335

* Broken Loop: Vessel nozzle, Cold leg

*crdno name type

3350000 BCL-I branch

*chino no.juns. icc

3350001 2 1

*crdno area length volume h-ang v-ang delz

3350101 0.06340.7495 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe
*crdno fvcahs jun.

3501101 000100 1

•crdno ebt pressure temp a4 a5 a6 vol

3501201 003 15.0149+6 553.227 0.0 0.0 0.0 1

3501202 003 15.0149+6 555.479 0.0 0.0 0.0 2

•crdno ctl

3501300 1

*crdno flowf flowg velj jun

3501301 3.61834-3 0.0 0.0 1

• Component no 370

Broken Loop: RABS -BCL side

*crdno name type

3700000 RABS-BCL pipe

*crdno numb..vol

3700001 3

•crdno irea vol.

3700101 0.0388 2

3700103 0.0776 3

*crdno j.area vol.

3700201 0.0388 2

*crdno length vol.

3700301 0.0 3

*crdno volume vol.

3700401 0.0279 1

3700402 0.0700 2

3700403 0.1165 3

*crdno v-ang vol.

3700601 90.0 1

3700602 0.0 3

*crdno elev vol.

3700701 0.64 1

3700702 0.0 3

*crdno rgh dhy vol.

3700801 4.0-5 0.0 3

*crno floss rios jun

3700901 0.28 0.28 1

3700902 0.84 0.84 2

*crdno pvbfe vol.

3701001 11000 3

*crdno fvcahs jun.

3701101 000000 2

*crdno ebt pressure temp a4 a5 a6 vol

3701201 003 15.0126+6 555.2070.0 0.0 0.0 i

3701202 003 15.0102+6 556.0030.0 0.0 0.0 2

3701203 003 15.0102+6 556.004 0.0 0.0 0.0 3

*crdno ctl

3701300 1

*crdno flowf flowg velIj jun

3701301 -6.51096-5 0.0 0.0 1

3701302 -4.06750-5 0.0 0.0 2

• Component no 380 * Broken Loop: RABS - HCL side

3800603 0.0 3

*crdno elev vol.

3800701 0.0 I

3800702 -0.64 2

3800703 0.0 3

*crdno fgh dhy vol.

3800801 4.0-5 0.0 3

*crdno floss riots jun

3800901 0.84 0.84 1

3800902 0.28 0.28 2

*crdno pvbfe vol.

3801001 11000 3

*crdno fvcahs jun.

3801101 000000 2

*crdno ebt pressure temp a4 a5 a6 vol

3801201 003 14.9201+6 552.801 0.0 0.0 0.0

3801202 003 14.9225+6 555.9740.0 0.0 0.0

3801203 003 14.9249+6 556.0520.0 0.0 0.0

*crdno cl

3801300 1

*crdno flowf flowg velj jun

3801301 -2.51837-2 0.0 0.0 2

• Pressurizer

1

2

3

• Component no 400 • Pressurizer. PRZ Surge line - PCS side

*crdno name type

4000000 SURGE-I snglvol

*crdno area length volume h-ang v-ang delz

4000101 0.00145 2.300 0.0 0.0 90.0 0.54

*crdno rough dhy pvbfe

4000102 4.0-5 0.0 01000

*crdno ebm pressure temp

4000200 003 14.8642+6 578.246

• Component no 401

Pressurizer: Surge line pipe junction

*crdno name type

4010000 PRZ-JI sngljun

*crdno from to area floss doss fvcshs

4010101 400010002 405010001 0.0 0.93 0.93 000000

*crdno ctI flowf flowg velj

4010201 I 0.0 0.0 0.0

• Component no 405

• Pressurizer: Surge line

Ocrdno name type

4050000 SRG-Lin pipe

*crdno numbhvol

4050001 2

*crdno area vol.

4050101 0.0145 2

*crdno j-area jun.

4050201 0.00145 1

•crdno length vol.

4050301 2.30 2

*crdno volume vol.

4050401 0.0 2

*crdno v-ang vol.

4050601 90.0 2

*crdno elev vol.

4050701 0.30 2

*crdno rgh dhy vol.

4050801 4.00-5 0.0 2

*crdno floss dloss jun

4050901 0.00 0.00 1

*crdno pvbfe vol.

4051001 11000 2

crdno name type

3800000 RABS-HCL

*crdno numb.vol

3800001 3

*crdno area vol.

3800101 0.0776 1

3800102 0.0388 3

*cnjno jarea jun.

3800201 0.0388 2

*crdno length vol.

3800301 0.0 3

*crdno volume vol.

3800401 0.0915 1

3800402 0.0480 2

3800403 0.0489 3

*crdno v-ang vol.

3800601 0.0 1

3800602 -90.0 2

pipe

A-15
*crdno fvcahs jun.

4051101 000000 1

*crdno ebt pressure temp a4 a5 a6 vol

4051201 003 14.8613+6 578.216 0.0 0.0 0.0 1

4051202 003 14.8592+6 578.320 0.0 0.0 0.0 2

*crdno ctl

4051300 1

*crdno flowf flowg velj jun

4051301 0.0 0.0 0.0 1

* Component no 410

* Pressurizer. Surge line Vessel junction ,

*crdno name type

4100000 SRG-PRZ sngljun

*crdno from to area floss floss fvcahs

4100101 405010000 415000000 0.0 0.93 0.93 000000

*crdno ctl flowf flowg velIj

4100201 1 0.0 0.0 0.0

* Component no 415

Pressurizer Vessel

*crdno name type

4150000 PRZ pipe

*crdno nwnb._vol

4150001 7

*crdno area vol.

4150101 0.0 2

4150102 0.5653 5

4150103 0.0 7

*crdno length vol.

4150301 0.1815 1

4150302 0.1524 2

4150303 0.3967 3

4150304 0.5289 4

4150305 0.3967 5

4150306 0.1943 6

4150307 0.1029 7

*crdno volume vol.

4150401 0.0684 1

4150402 0.0838 2

4150403 0.0 5

4150404 0.0732 6

4150405 0.0142 7

*crdno v-ang vol.

4150601 90.0 7

*crdno rgh dhy vol.

4150801 4.0-5 0.0 7

*crdno floss rloss jun

4150901 0.0 0.0 6

*crdno pvbfe vol.

4151001 00000 7

*crdno fvcahs jun.

4151101 000000 6

*crdno ebt pressure U-liq U-vap voidg a6 vol

4151201 000 14.8575+6 1.35929+6 2.46300+6 0.000000.0

4151202 000 14.8564+6 IA1666+6 2.46303+6 0.000000.0

4151203 000 14.8547+6 1.51541+6 2.46307+6 0.000000.0

4151204 000 14.8521+6 1.56096+6 2.46339+6 0.19875 0.0

4151205 000 14.8506+6 1.58069+6 2.46315+6 0.999760.0

4151206 000 14.8503+6 1.58068+6 2.46316+6 0.99984 0.0

4151207 000 14.8501+6 1.58067+6 2.46316+6 0.99983 0.0

*crdno ctl

4151300 1

*crdno flowf flowg velj jun

4151301 0.0 0.0 0.0 6 a

*crdno no.juns. icc

4200001 1 1

*crdno area length volume h-ang v-ang delz

4200101 0.0 0.1029 0.0142 0.0 90.0 0.1029

*crdno rough dhy pvbfe

4200102 4.5-5 0.0 00000

*crdno ebt pressure quals

4200200 002 14.8500+6 1.0

*crdno from to area floss floss fvcahs

4201101 415070002 420010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

4201201 0.0 0.0 0.0

* Component no 421

* Pressurizer Presure stady state controller

*crdno name type

4210000 PRZ-SS valve

*crdno from to area floss floss fvcahs

4210101 420010002 422000000 0.0 0.0 0.0 000100

*crdnot ct flowf flowg velj

4210201 1 0.0 0.0 0.0

*crdno name

4210300 trpvlv

*crdno trip no

4210301 604

* Component no 422

* Pressurizer Presure stady state controller

*crdno name type

4220000 PRZ-SS tmdpvol

*crdno area length volume h-ang v-ang delz

4220101 0.0 0.1029 0.0142 0.0 0.0 0.0

*crdno rough dhy pvbfe

4220102 0.0 0.0 00000

*crdno ebt

4220200 002

*crdno time pressure quals

4220201 0.0 14.85+6 1.0

* Steam Generator Secondary Side

* Component no 500

* Steam Generator- Separator ,

*crdno name type

5000000 SG-SPR branch

*crdno no.juns. icc

5000001 3 0

*crdno area length volume h-ang v-ang delz

5000101 0.3063 0.4445 0.0 0.0 90.0 0.444

*crdno rough dhy pvbfe

5000102 1.0-5 0.0 00000

*crdno ebt pressure U-liq U-yap voidg

5000200 000 5.58347+6 1.18269+6 2.59302+6 0.94546

*crdno from to area floss floss fvcahs

5001101 500010000 520000000 0.30630 0.000 0.000 001000

5002101 500000000 505000000 0.14024 0.000 0.000 001000

5003101 515010000 500000000 0.29187 2.404 2.404 001000

*crino flowf flowg velj

5001201 -0.26663 3.4015 0.0

5002201 14.446 -9.44287-3 0.0

5003201 0.81508 6.2977 0.0

1

2

3

4

5

6

7

* Component no 420

Pressurizer. PRZ Top

*crdno name type

4200000 PRZ-Top branch

* Component no 502

* Steam Generator Separator Bypass

*crdno name type

5020000 SG-SByp snglvol

*crdno area length volume h-ang v-ang delz

5020101 2.212 0.4445 0.0 0.0 90.0 0.444

A-16
*crdno rough dhy pvbfe

5020102 1.0-5 0.0 11000

*crdno ebt pressure U-liq U-vap voidg

5020200 000 5.58411+6 1.18266+6 2.59323+6 1.00000

* Component no 505

* Steam Generator. Separator Outlet

*crdno name type

5050000 SG-SpOut branch

*crdno no.juns. icc

5050001 2 0

*crdno area length volume h-ang v-ang delz

5050101 0.0 1.2131 1.4850 0.0 -90.0 -1.2131

*crdno rough dhy pvbfe

5050102 1.0-5 1.9048 10000

*crdno elt pressure U-liq U-yap voidg

5050200 000 5.58563+6 1.18200+6 2.59378+6 0.41630

*5050200 000 5.58563+6 1.18200+6 2.59378+6 0.38630

*crdno from to area floss doss fvcahs

5051101 505010002 508010001 0.0 0.0 0.0 000100

5052101 505010001 502010001 0.0 0.0 0.0 000100

*crdno flowf flowg velj

5051201 0.34413 -0.34696 0.0

5052201 -0.19447 2.50132-5 0.0

* Component no 508

* Steam Generator: Feed Water Inlet

*cdwno name type

5080000 SG-FWin branch

*crdno no.juns. icc

5080001 1 0

*crdno area length volume h-ang v-ang delz

5080101 0.0 0.6096 0.22107 0.0 -90.0 -0.6096

*crdno rough dhy pvbfe

5080102 1.0-5 0.163697 10000

*crdno ebt pressure U-liq U-yap voidg

5080200 000 5.59452+6 1.14526+6 2.59311+6 0.0000000

*cydno from to area floss doss fvcahs

5081101 508010002 510010001 0.0 0.0 0.0 000100

*crdno flowf flowg velj

5081201 0.48538 0.61006 0.0

* Component no 510

* Steam Generator. Downcomer

*crdno name type

5100000 SG-DwCom annulus

*crdno no.vol

5100001 3

*crdno area Vol.

5100101 0.297 3

*crdno length vol.

5100301 0.6096 3

*crdno volume vol.

5100401 0.0 3

*crdno v-ang vol.

5100601 -90. 3

*crdno elev. vol.

5100701 -0.6096 3

*crdno rgh dhy vol.

5100801 4.0-5 0.10793 3

*crdno floss rloss jun

5100901 0.0 0.0 2

*crdno pvbfe vol.

5101001 10000 3

*crdno fvcahs jun.

5101101 000000 2

*crdno ebt pressure U-liq U-yap voidg a6 vol

5101201 000 5.59914+6 1.14575+6 2.59308+6 0.00000 0.0 I

5101202 000 5.60379+6 1.14548+6 2.59305+6 0.00000 0.0 2

5101203 000 5.60844+6 1.14518+6 2.59301+6 0.00000 0.0 3

*crdno cil

5101300 0

*crdno flowf flowg velj jun

5101301 0.48549 0.61037 0.0 1

5101302 0.48544 0.61030 0.0 2

Component no 513 • Steam Generator Junction - Downcomer to Boiler

Scrdno name type

5130000 J510-515 sngljun

*crdno from to area floss floss fvcahs

5130101 510030002 515010001 0.258 17.5 17.5 000100

•crdno cil flowf flowg velj

5130201 0 0.51857 0.88711 0.0

* Component no 515

* Steam Generator. Boiler ,

*crdno name type

5150000 SG-Boil pipe *crdno numb_.vol

5150001 6

*crdno area vol.

5150101 0.278 5

5150102 0.306294 6

*crdno jun.area jun.

5150201 0.258 5

*crdno length vol.

5150301 0.9144 2

5150302 1.8288 5

5150303 1.2131 6

*crdno volume vol.

5150401 0.0 6

*crdno v-ang vol.

5150601 60.0 5

5150602 90.0 6

*crdno elcv. vol.

5150701 0.3048 2

5150702 0.6096 5

5150703 1.2131 6

*crdno rgh dhy vol.

5150801 1.0-5 0.0234 5

5150802 1.0-5 0.5962 6

*crdno floss rloss jun

5150901 2.0 2.0 2

5150902 4.05 4.05 5

*crdno pvbfe vul.

5151001 10000 6

*crdno fvcahs jun.

5151101 000100 5

*crdno ebt pressure U-liq U-yap voidg a6 vol

5151201 000 5.60791+6 1.17157+6 2.59302+6 0.23792 0.0 1

5151202 000 5.60575+6 1.18170+6 2.59295+6 0.39791 0.0 2

5151203 000 5.60293+6 1.18368+6 2.59297+6 0.54839 0.0 3

5151204 000 5.59822+6 1.18348+6 2.59294+6 0.53026 0.0 4

5151205 000 5.59291+6 1.18318+6 2.59299+6 0.59106 0.0 5

5151206 000 5.58687+6 1.18285+6 2.59302+6 0.53561 0.0 6

*crdno cdl

5151300 0

*crdno flowf flowg velj jun

5151301 0.67248 1.4019 0.0 1

5151302 0.82720 1.9798 0.0 2

5151303 1.0221 3.2469 0.0 3

5151304 0.90457 5.2295 0.0 4

5151305 0.97083 5.9829 0.0 5

* Component no 520

* Steam Generator. Lower portion of Steam Dome

*crdno name type

5200000 SG-StDlw branch

*crdno no.juns. icc

A-17
5200001 1 0

*crdno area length volume h-ang v-ang delz

5200101 0.27871 0.7180 0.0 0.0 90.0 0.718

*crdno rough dhy pvbfe

5200102 1.0-5 1.0827 10000

*crdno ebt pressure U-Iiq U-yap voidg

5200200 000 5.58361+6 1.18263+6 2.59306+6 0.99997

*crdno from to area floss doss fvcahs

5201101 520010002 525010001 0.0 0.0 0.0 000100

*crdno flowf flowg velj

5201201 3.3231 3.53190.0

* Component no 525

* Steam Generator: Upper portion of Steam Dome

*crdno name type

5250000 SG-StDup branch

*crdno no.juns. icc

5250001 I 0

*crdno area length volume h-ang v-ang delz

5250101 1.5886 0.7620 0.0 0.0 90.0 0.762

*crdno rough dhy pvbfe

5250102 4.0-50.64417 11000

*crdno ebt pressure U-liq U-yap voidg

5250200 000 5.58346+6 1.18262+6 2.59312+6 0.99993

*crdno from to area floss doss fvcahs

5251101 525010002 530010001 0.0 0.0 0.0 000000

*crdno flowf flowg velj

5251201 17.095 21.224 0.0

*crdno flowf flowg velj

5421201 0.0 0.0 0.0

* Component no 544

* Air Cooled Condenser

*crdno name type

5440000 Condens tmdpvol

*crdno area length volume h-ang v-ang delz

5440101 0.21677 17.67 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

5440102 4.0-5 0.02 00000

*crdno ebt

5440200 002

*crdno time pressure quals

5440201 0.0 2.00+6 1.0

* Component no 545

* Steam Line: Main Steam Control Valve ,

*crdno name type

5450000 St-MSCV valve

*crdno from to area floss doss fvcahs

5450101 530010002 546000000 3.50-2 0.0 0.0 000100

*crdno ctl flowf flowg velj

5450201 0 10.753 21.268 0.0

*crdno name

5450300 mtrvlv

*crdno open-trip close..trip vlv..ch.r. init.pos

5450301 606 607 0.10 1.0

* Component no 530

*Steam Line: from SG to Control valve .

*crdno name type

5300000 St-linl snglvol

*crdno area length volume h-ang v-ang delz

5300101 0.04635 25.074 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

5300102 4.0-5 0.0 00000

*crdno ebt pressure U-liq U-yap voidg

5300200 000 5.57198+6 1.18203+6 2.59312+6 0.99988

* Component no 540

* Steam Line: Main Steam Control Valve

* In the L3-6 transient valve opens at 88 sec after SCRAM to 15%

*crdno name type

5400000 St-MSCV valve

*crdno from to area floss rioss fvcahs

5400101 530010002 542000000 3.37-3 0.0 0.0 001100

*crdno cdl flowf flowg velj

5400201 1 0.0 0.0 0.0

*crdno name

5400300 mtrvlv

*crdno, open_trip close.trip vlv.ch.r. init.pos

5400301 610 613 0.023333 0.0

* Component no 542

* Air Cooled Condenser

*crdno name type

5420000 Condens branch

*crdno no.juns. icc

*5420001 2 1

5420001 1 1

*crdno area length volume h-ang v-ang delz

5420101 3.37-3 17.67 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

5420102 4.0e-5 0. 00000

*crdno ebt pressure quals

5420200 002 2.0+6 1.0

*crdno from to area floss floss fvcahs

5421101 542010002 544000000 0.0 0.0 0.0 001000

* Component no 546

* Air Cooled Condenser

*crdno name type

5460000 Condens tmdpvol

*crdno area length volume h-ang v-ang delz

5460101 0.21677 17.67 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

5460102 4.0-5 0.02 00000

*crdno ebt

5460200 002

*crdno time pressure quals

5460201 0.0 5.56+6 1.0

* Simplified Feed Water System

* (Component no 565

* Feed Water Tank

*crdno name type

5650000 FW-Tank tmdpvol

*crdno area length volume h-ang v-ang delz

5650101 29.81 3.048 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

5650102 4.0-5 0.0 00000

*crdno ebt

5650200 003

*crdno time pressure temp

5650201 0.0 7.0+6 510.00

* Component no 566

* Feed Water: Inlet flow

*crdno name type

5660000 FW-PUMP tmdpjun *crdno from to area

5660101 565000000508010001 0.05

*crdno ctl trip

5660200 I 403

A-18
*crdno

5660201

5660202

5660203

time flowf flowg velj

-1. 27.800 0.0 0.0

0.0 27.800 0.0 0.0

4.0 0.000 0.0 0.0

* Component no 568

* Feed Water: Auxiliary Feed Water Storage Tank

*crdno name type

5680000 FW-AUX tmdpvol

*crdno area length volume h-ang v-ang dclz

5680101 29.81 3.048 0.0 0.0 0.0 0.0

*crdno rough dhy pvbfe

5680102 4.0e-5 0.0 00000

*crdno ebt

5680200 003

*crdno time pressure temp

5680201 0.0 8.0+6 315.00

* Component no 569

* Feed Water: Auxiliary Feed Water Inlet Flow

,

*crdno name type

5690000 FW-Auxln tmdpjun

*crdno from to area

5690101 568000000 508010001 0.10

*crdno ctl trip no

5690200 1 603

*crdno time flowf flowg velj

5690201 -1. 0.0 0.0 0.0

5690202 73.0 0.0 0.0 0.0

5690203 73.4 0.50364 0.0 0.0

5690204 1856.0 0.50364 0.0 0.0

5690205 1857.0 0.0 0.0 0.0

5690206 2500.0 0.0 0.0 0.0

* ECC System (ECCS)

* Component no 605

* ECCS: ECC Check Valve

6150201 -1.00

6150202 0.00

6150203 36.40

6150204 54.50

6150205 236.36

6150206 709.09

6150208 712.70

6150209 872.70

6150210 876.36

6150211 1049.17

6150212 1054.00

6150213 1218.00

6150214 1227.00

6150215 1554.00

6150216 1559.00

6150217 1759.00

6150218 1763.00

6150219 2036.00

6150220 2054.54

6150221 2135.80

6150222 2140.00

6150223 2500.00

0.00

0.00

0.26

0.44

0.41

0.41

0.44

0.44

0.47

0.47

0.50

0.50

0.54

0.54

0.575

0.57:

0.60(

0.60(

0.644

0.644

0.674

0.674

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

0.0 0.0

5 0.0 0.0

5 0.0 0.0

) 0.0 0.0

) 0.0 0.0

0 0.0 0.0

0 0.0 0.0

0 0.0 0.0

0 0.0 0.0

*crdno name type

6050000 ECC-CIIKV sngljun

*crdno from to area floss floss fvcahs

6050101 610010002 206010001 5.9896-3 0.935 0.935 001100

*crdno ctl flowf flowg velj

6050201 1 0.0 0.0 0.0

* Component no 610

* ECCS: ECC Hleader to PCS *

*crdno name type

6100000 ECC-Hlead snglvol

*crdno area length volume h-ang v-ang delz

6100101 5.9896--35.0148 0.0 0.0 90.0 3.3071202

*crdno rough dhy pvbfe

6100102 4.0-5 0.0 11000

*crdno ebt pressure temp.

6100200 003 14.870+6 560.

* Component no 615

* HPIS: System A (IIPIS A & B)

*crdno name type

6150000 ttPIS tmdpjun *crdno from to area

6150101 620000000 610010001 0.009099

*crdno ctl trip

6150200 1 602

*crdno time flowf flowg velj

* Component no 620

* IIPIS: Borated Water Storage Tank

,

*crdno name type

6200000 BWST tmdpvol *crdno area length volume h-ang v-ang delz

6200101 20.44 5.0 0.0 0.0 90.0 5.0

*crdno rough dhy pvbfe

6200102 4.0-5 0.0 00000

*crdno ebt

6200200 003

*crdno time pressure temp

6200201 0.0 1.0+5 305.0

* Ieat Structures

* Intact Loop

*

* lHeat Structure no 100-I

* Intact loop Piping

*crdno no.h.s no.m.p geo s.s.flg left

11001000 14 3 2 I 0.142

*crdno mesh fig fmt

11001100 0 1

*crdno intvl rt.cor

11001101 2 0.1780

*crdno comp intvl

11001201 4 2

*crdno source intvl

11001301 0.0 2

*crdno tempflag

11001400 -1

*crdno t(I) t(2) t(3)

11001401 579.09 569.46 560.80

11001402 579.08 569.46 560.80

11001403 579.09 569.47 560.81

11001404 579.10 569.48 560.82

11001405 579.10 569.47 560.81

11001406 559.98 550.90 542.74

11001407 559.99 550.91 542.75

11001408 559.99 550.91 542.75

11001409 560.13 551.05 542.88

11001410 560.13 551.05 542.88

11001411 560.13 551.05 542.88

11001412 560.13 551.05 542.88

11001413 560.12 551.04 542.87

11001414 560.12 551.04 542.87

A-19
*crdno left vol incr b.c sacodc safac h.s.no

11001501 100010000 0 1 1 1.44580 1

11001502 105010000 0 1 1 1.08660 2

11001503 107010000 0 1 I 0.50000 3

11001504 110010000 0 1 1 0.85610 4

11001505 112010000 0 1 1 1.38893 5

11001506 118020000 0 I 1 0.68900 6

11001507 118030000 0 1 1 0.55900 7

11001508 120010000 0 1 1 0.76000 8

11001509 150010000 0 1 1 0.49660 9

11001510 175010000 0 1 1 0.55900 10

11001511 175020000 0 1 1 0.61300 11

11001512 180010000 0 1 1 1.01000 12

11001513 185010000 0 1 1 1.15200 13

11001514 184010000 0 1 1 0.28400 14

*crdno rt vol incr b.c sacode safac h.s.no

11001601 -939 0 3949 1 1.44580 1

11001602 -939 0 3949 1 1.08660 2

11001603 -939 0 3949 1 0.50000 3

11001604 -939 0 3949 1 0.85610 4

11001605 -939 0 3949 1 1.38893 5

11001606 -939 0 3949 1 0.68900 6

11001607 -939 0 3949 1 0.55900 7

11001608 -939 0 3949 1 0.76000 8

11001609 -939 0 3949 1 0.49660 9

11001610 -939 0 3949 1 0.55900 10

11001611 -939 0 3949 1 0.61300 II

11001612 -939 0 3949 1 1.01000 12

11001613 -939 0 3949 1 1.15200 13

11001614 -939 0 3949 1 0.28400 14

*crdno s.type mult dirleft dir.rt h.s.no

11001701 0 0.0 0.0 0.0 14

*crdno dth hl-f hl-r gs-lfgs-Ir floss doss boil-f h.s.no

11001801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 14

*crdno dth hl-f hl-r gs-Ifgs-lr floss floss boil-f h.s.no

11001901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 14

* lleat Structure no 100-2

* Steam Generator Connections

*crdno no.h.s no.m.p geo s.s.flg left

11002000 2 5 2 1 0.1625

*crdno mesh fig fmt

11002100 0 1

*crdno intvl st.cor

11002101 4 0.20300

*crdno comp intvl

11002201 4 4

*crdno source intvl

11002301 0.0 4

*crdno tempflag

11002400 -1

*crdno t(1) t(2) t(3) t(4) t(5)

11002401 579.01 573.51 568.29 563.34 558.62

11002402 559.94 554.75 549.83 545.16 540.71

*crdno left vol incr b.c sacode safac h.s.no

11002501 112020000 0 1 1 0.70769 1

11002502 118010000 0 1 1 0.54700 2

*crdno t vol incr b.c sacode safac h.s.no

11002601 -939 0 3949 1 0.70769 1

11002602 -939 0 3949 1 0.54700 2

*crdno s.type mult dir.Ieft dirat h.s.no

11002701 0 0.0 0.0 0.0 2

*crdno dth hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

11002801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

*crdno dth hl-f hl-r gs-Ifgs-Ir floss floss boil-f h.s.no

11002901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

* Heat Structure no 100-3

* Intact Loop: 0.216 m dia Piping

*crdno no.h.s no.m.p geo s.s.flg left

11003000 7 3 2 1 0.108

*crdno mesh fig fret

11003100 0 I

*crdno intvi rt.cor

11003101 2 0.1365

*crdno comp intvi

11003201 5 2

*crdno source intvl

11003301 0.0 2

*crdno lempflag

11003400 -1

*crdno 1(I) t(2) t(3)

11003401 559.76 557.01 554.57

11003402 559.90 557.15 554.71

11003403 560.07 557.32 554.87

11003404 560.30 557.55 555.10

11003405 560.12 557.37 554.92

11003406 559.92 557.17 554.73

11003407 560.16 557.41 554.96

*crdno left vol incr b.c sacode safac h.s.no

11003501 125010000 0 1 1 1.00000 1

11003502 130010000 0 1 1 0.45700 2

11003503 140010000 0 1 1 0.50200 3

11003504 145010000 0 I 1 1.40840 4

11003505 150010000 0 I 1 1.00300 5

11003506 160010000 0 I 1 0.45700 6

11003507 170010000 0 1 1 0.51400 7

*crdno rt vol incr b.c sacode safac h.s.no

11003601 -939 0 3949 1 1.00000 1

11003602 -939 0 3949 1 0.45700 2

11003603 -939 0 3949 1 0.50200 3

11003604 -939 0 3949 1 1.40840 4

11003605 -939 0 3949 1 1.00300 5

11003606 -939 0 3949 1 0.45700 6

11003607 -939 0 3949 1 0.51400 7

*crdno s.type mult dir.left dir.•t h.s.no

11003701 0 0.0 0.0 0.0 7

*crdno dith hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

11003801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 7

*crdno dth hl-f hl-r gs-If gs-lr floss floss boil-f h.s.no

11003901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 7

* lleat Structure no 100-4

* Steam Generator. Plena

*crdno no.h.s no.m.p geo s.s.flg left

11004000 2 5 3 1 0.6858

*crdno mesh fig frmt

11004100 0 1

*crdno intvl rt.cor

11004101 4 0.7747

*crdno comp intvl

11004201 5 4

*crdno source intvl

11004301 0.0 4

*crdno tcmpflag

11004400 -1

*crdno t(l) t(2) t(3) t(4) t(5)

11004401 578.55 573.96 569.64 565.59 561.76

11004402 559.50 555.23 551.22 547.44 543.88

*crdno left vol incr b.c sacode safac hLs.no

11004501 114010000 0 1 1 0.25 1

11004502 116010000 0 1 1 0.25 2

*crdno it vol incr b.c sacode safac h.s.no

11004601 -939 0 3949 1 0.25 1

11004602 -939 0 3949 1 0.25 2

*crdno s.type mult dir.left dir.at h.s.no

11004701 0 0.0 0.0 0.0 2

*crdno dth hI-f hl-r gs-lf gs-lr floss doss boil-f h.s.no

11004801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

*crdno dth hl-f hl-r gs-If gs-Ir floss floss boil-f hs.no

11004901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

* Ileat Structure no 115-0 * Steam Generator Tubing

A-20
*crdno no.l.s no.m.p geo s.s.flg left

11150000 10 5 2 1 5.1054-3

*crdno mesh fg fmt

11150100 0 1

*crdno intvl rt.cor

11150101 4 6.34898-3

*cTdno comp intvl

11150201 6 4

*crdno source intvl

11150301 0.0. 4

*crdno tempflag

11150400 -1

*crdno t(I) t(2) t(3) 1(4) t(5)

11150401 568.55 563.60 558.89 554.41 550.13

11150402 567.61 563.13 558.87 554.83 550.97

11150403 565.64 561.78 558.12 554.64 551.32

11150404 563.91 560.56 557.39 554.37 551.50

11150405 562.50 559.43 556.52 553.75 551.12

11150406 561.18 558.36 555.68 553.14 550.71

11150407 559.64 557.11 554.71 552.43 550.26

11150408 558.07 555.73 553.52 551.42 549.41

11150409 557.05 554.68 552.44 550.31 548.29

11150410 555.68 553.13 550.71 548.41 546.23

*crdno left vol incr b.c sacode safac h.s~no

11150501 115010000 0 1 1 562.360 I

11150502 115020000 0 1 1 562.360 2

11150503 115030000 0 1 1 1124.710 3

11150504 115040000 0 1 1 1124.710 4

11150505 115050000 0 1 1 849.063 5

11150506 115060000 0 I 1 849.063 6

11150507 115070000 0 1 i 1124.710 7

11150508 115080000 0 1 1 1124.710 8

11150509 115090000 0 1 1 562.360 9

11150510 115100000 0 1 1 562.360 10

*crdno rt vol incr b.c sacode safac h.s.no

11150601 515010000 0 1 1 562.360 1

11150602 515020000 0 1 I 562.360 2

11150603 515030000 0 1 I 1124.710 3

11150604 515040000 0 1 1 1124.710 4

11150605 515050000 0 1 1 849.063 5

11150606 515050000 0 1 1 849.063 6

11150607 515040000 0 1 I 1124.710 7

11150608 515030000 0 1 1 1124.710 8

11150609 515020000 0 1 1 562.360 9

11150610 515010000 0 1 1 562.360 10

*crdno s.type mult dir.Ieft dir.rt h.s.no

11150701 0 0.0 0.0 0.0 10

*crdno dth hl-f hl-r gs-Ifgs-lr floss doss boil-f h.s.no

11150801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 10

*crdno dth hl-f hl-r gs-lf gs-lr floss doss boil-f h.s.no

11150901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 10

* Reactor Vessel

* Heat Structure no 230-0

* Active Core *

*crdno no.h.s no.m.p geo s.s.flg left refl bind ax.int

12300000 6 II 2 1 0.0 2 1 16

*crdno mesh fig fret

12300100 0 I

*crdno intvl rt.cor

12300101 6 4.647-3

12300102 1 4.742-3

12300103 3 5.359-3

*crdno comp intvl

12300201 1 6

12300202 -2 7

12300203 -3 10

*crdno source intvl

12300301 1.0 6

12300302 0.0 10

*crdno tempflag

12300400 -1

*crdno t(I) t(2) t(3) t(4) t(5)

12300401 678.6 676.88 671.74 663.25 651.54

+ 636.75 619.07 569.78 568.18 566.64

+ 565.15

12300402 1281.8 1267.1 1223.6 1153.6 1059.5

+ 949.73 828.33 608.57 600.63 592.95

+ 585.53

12300403 1934.7 1904.1 1812.9 1663.8 1464.9

+ 1232.1 982.62 643.08 630.04 617.40

+ 605.12 ,

12300404 2199.7 2163.9 2056.2 1876.6 1633.3

+ 1344.9 1042.0 659.71 644.75 630.21

+ 616.08

12300405 1907.2 1877.3 1788.7 1643.6 1450.4

+ 1224.4 981.26 650.49 637.84 625.57

+ 613.66 ,

12300406 939.48 933.15 914.35 883.66 841.99

+ 791.15 732.54 604.99 600.60 596.37

+ 592.29

*crdno left vol incr b.c sacode safac h.s.no

12300501 0 0 0 1 363.35 5

12300502 0 0 0 1 490.75 6

*crdno rt vol incr b.c sacode safac h.s.no

12300601 230010000 10000 1 1 363.35 5

12300602 230060000 0 1 1 490.75 6

*crdno s.type mult dir.left dir.rt h.s.no

12300701 1000 0.027100270 0.0 0.0 1

12300702 1000 0.138211380 0.0 0.0 2

12300703 1000 0.233062330 0.0 0.0 3

12300704 1000 0.271002710 0.0 0.0 4

12300705 1000 0.227642280 0.0 0.0 5

12300706 1000 0.102981030 0.0 0.0 6

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

12300901 1.25-2 30.0 30.0 0.0 0.0 0.0 0.0 1. 6

* tleat Structure no 200-0

* Filler Blocks Inlet Annulus Top Volumes

*crdno no.h.s no.m.p geo s.s.flg left

12000000 4 5 2 1 0.508

*crdno mesh fig fmt

12000100 0 1

*crdno intvl rt.cor

12000101 4 0.7264

*crdno comp intvl

12000201 4 4

*crdno source intvl

12000301 0.0 4

*crdno tempflag

12000400 -1

*crdno t(I) t(2) t(3) t(4) t(5)

12000401 553.06 530.53 509.72 490.36 472.23

12000402 552.26 529.79 509.04 489.74 471.66

12000403 559.14 536.12 514.87 495.09 476.56

12000404 559.13 536.12 514.86 495.08 476.56

*crdno left vol incr b.c sacode safac h.Lno

12000501 200010000 0 1 1 0.14055 1

12000502 210010000 0 1 1 0.04685 2

12000503 202010000 0 1 1 0.2139 3

12000504 212010000 0 1 1 0.0713 4

*crdno n vol incr b.c sacode safac h.s.no

12000601 -939 0 3949 1 0.14055 1

12000602 -939 0 3949 1 0.04685 2

12000603 -939 0 3949 1 0.2139 3

12000604 -939 0 3949 1 0.0713 4

*crdno s.type mult dir.Ieft dir.at h.s.no

12000701 0 0.0 0.0 0.0 4

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

12000801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 4

A-21
*crdno dth hl-f hl-r gs-Ifgs-lr foss doss boil-f h.s.no

12000901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 4

Heat Structure no 200-1

* Filler Blocks Inlet Annulus middles Volumes

*crdno no.h.s no.m.p geo s-s.flg left

12001000 18 5 2 1 0.381

*crdno mesh fig fmt

12001100 0 I

*crdno intvl rt.cor

12001101 4 0.419

*crdno comp intvl

12001201 4 4

*crdno source intvl

12001301 0.0 4

*crdno tempflag

12001400 -1

*crdno t(l) t(2) t(3) t(4)

12001401 538.26 542.24 546.12

12001402 537.50 541.47 545.34

12001403 543.68 547.74 551.69

12001404 543.67 547.73 551.68

12001405 544.12 548.19 552.14

12001406 544.11 548.18 552.14

12001407 544.38 548.45 552.41

12001408 544.38 548.45 552.41

12001409 544.38 548.45 552.41

12001410 544.38 548.45 552.41

12001411 544.38 548.45 552.41

12001412 544.37 548.44 552.40

12001413 544.38 548.45 552.41

12001414 544.37 548.44 552.40

12001415 544.38 548.45 552.41

12001416 544.37 548.44 552.40

12001417 544.38 548.45 552.41

12001418 544.37 548.44 552.40

t(5)

549.90

549.10

555.53

555.53

555.99

555.99

556.27

556.26

556.27

556.26

556.27

556.26

556.26

556.26

556.26

556.26

556.26

556.26

553.57

552.77

559.28

559.27

559.75

559.74

560.03

560.02

560.02

560.02

560.02

560.01

560.02

560.01

560.02

560.01

560.02

560.01

*crdno left vol

12001501 -939

12001502 -939

12001503 -939

12001504 -939

12001505 -939

12001506 -939

12001507 -939

12001508 -939

12001509 -939

12001510 -939

12001511 -939

12001512 -939

12001513 -939

12001514 -939

12001515 -939

12001516 -939

12001517 -939

12001518 -939

incr b.c sacode safac h.s.no

*crdno s.type mult dir.left dir.t h.s.no

12001701 0 0.0 0.0 0.0 18

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

12001801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 18

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

12001901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 18

* fleat Structure no 210-0

* Interactive

*crdno no.h.s no.m.p geo s.s.flg left

12100000 16 5 2 1 0.470

*crdno mesh fig fmet

12100100 0 1

*crdno intvl rt.cor

12100101 4 0.7264

*crdno comp intvl

12100201 4 4

*crdno source intvl

12100301 0.0 4

*crdno tempflag

12100400 -1

*crdno t(I) t(2) t(3) t(4) t(5)

12100401 560.36 560.32 560.28 560.25 560.22

12100402 560.35 560.19 560.04 559.91 559.79

12100403 560.36 560.28 560.20 560.13 560.07

12100404 560.35 560.18 560.03 559.89 559.77

12100405 560.36 560.27 560.20 560.13 560.07

12100406 560.35 560.18 560.03 559.89 559.77

12100407 560.36 560.22 560.10 559.99 559.90

12100408 560.35 560.13 559.94 559.77 559.62

12100409 560.35 560.22 560.10 559.99 559.90

12100410 560.35 560.13 559.94 559.77 559.62

12100411 560.35 560.18 560.03 559.89 559.76

12100412 560.35 560.16 559.99 559.83 559.70

12100413 560.24 560.10 559.98 559.86 559.76

12100414 560.23 560.07 559.93 559.81 559.69

12100415 559.83 559.81 559.79 559.77 559.76

12100416 559.82 559.78 559.75 559.72 559.69

*crdno left vol incr b.c sacode safac h.s.no

12100501 206010000 0 1 1 0.7185 1

12100502 216010000 0 I 1 0.2395 2

12100503 206020000 0 1 1 0.43425 3

12100504 216020000 0 1 1 0.14475 4

12100505 206030000 0 1 1 0.49275 5

12100506 216030000 0 1 1 0.16425 6

12100507 206040000 0 1 1 0.41925 7

12100508 216040000 0 1 1 0.13975 8

12100509 206050000 0 I 1 0.41925 9

12100510 216050000 0 1 1 0.13975 10

12100511 206060000 0 1 1 0.360 11

12100512 216060000 0 I 1 0.130 12

12100513 222010000 0 1 1 0.270 13

12100514 222010000 0 1 1 0.090 14

12100515 220010000 0 1 1 0.2775 15

12100516 220010000 0 1 1 0.0925 16

*crdno rt vol incr b.c sacode safac h.s.no

12100601 208010000 0 1 1 0.7185 1

12100602 218010000 0 1 1 0.2395 2

12100603 208020000 0 1 1 0.43425 3

12100604 218020000 0 1 1 0.14475 4

12100605 208020000 0 1 1 0.49275 5

12100606 218020000 0 1 1 0.16425 6

12100607 208030000 0 1 1 0.41925 7

12100608 218030000 0 I 1 0.13975 8

12100609 208030000 0 1 1 0.41925 9

12100610 218030000 0 1 1 0.13975 10

12100611 208040000 0 1 1 0.360 I1

12100612 218040000 0 1 1 0.130 12

12100613 208040000 0 1 1 0.270 13

12100614 218040000 0 1 1 0.090 14

12100615 208040000 0 1 1 0.2775 15

12100616 218040000 0 I 1 0.0925 16

*crdno s.type mult dir.left dir.rt h.s.no

12100701 0 0.0 0.0 0.0 16

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

0 3949

1 0.14025 1

1 0.04675 2

1 0.21375 3

1 0.07125 4

1 0.21075 5

1 0.07025 6

1 0.7185 7

1 0.2395 8

1 0.43525 9

1 0.14475 10

1 0.49275 11

1 0.16425 12

1 0.41925 13

1 0.13975 14

1 0.41925 15

1 0.13975 16

1 0.39000 17

1 0.13000 18

*crdno rt vol incr b.c sacode safac h.s.no

12001601 200010000

12001602 210010000

12001603 202010000

12001604 212010000

12001605 204010000

12001606 214010000

12001607 206010000

12001608 216010000

12001609 206020000

12001610 216020000

12001611 206030000

12001612 216030000

12001613 206040000

12001614 216040000

12001615 206050000

12001616 216050000

12001617 206060000

12001618 216060000

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0

0.14025 1

0.04675 2

0.21375 3

0.07125 4

0.21075 5

0.07025 6

0.7185 7

0.2395 8

0.43525 9

0.14475 10

0.49275 11

0.16425 12

0.41925 13

0.13975 14

0.41925 15

0.13975 16

0.39000 17

0.13000 18

A-22
*crdno dth hl-f hl-r gs-Ifgs-lr floss doss boil-f h.s.no

12100801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 16

*crdno dth hl-f hl-r gs-lf gs-lr floss doss boil-f h.s.no

12100901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 16

* HIeat Structure no 204-0

* Interactive

,

*crdno no.h.s no.m.p geo s.s.flg left

12040000 2 5 2 1 0.5010

*crdno mesh fig fmt

12040100 0 1

*crdno intvl rt.cor

120410101 4 0.7264

*crdno comp intvl

12040201 4 4

*crdno source intvl

12040301 0.0 4

*crdno tempflag

12040400 -1

*crdno t(l) t(2) 0() t(4) t(5)

12040401 560.37 560.32 560.29 560.25 560.22

12040402 560.36 560.20 560.05 559.92 559.80

*crdno left vol incr b.c sacode safac h.s.no

12040501 204010000 0 1 1 0.21105 I

120410502 214010000 0 1 1 0.07035 2

*crdno it vol incr b.c sacode safac h.s.no

120410601 208010000 0 1 1 0.21105 I

12010602 218010000 0 1 1 0.07035 2

*crdno s.type mult dir.left dir.rt h.s.no

12040701 0 0.0 0.0 0.0 2

*crdno dth hl-f hl-r gs-ifgs-ir floss doss boil-f h.s.no

120410801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

*crdno dth hl-f hl-r gs-ifgs-lr floss dloss boil-f h.s.no

12040901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 I. 2

* Hleat Structure no 220-0

* Interactive

*crdno no.h.s no.m.p geo s.s.flg left

12200000 I 5 1 1 0.0

*crdno mesh fig fmt

12200100 0 1

*crdno intvl rt.cor

12200101 4 0.092

*crdno comp intvl

12200201 5 4

*crdno source intvl

12200301 0.0 4

*crdno ternpflag

12200400 -1

*crdno t(l) t(2) t(3) t(4) t(5)

12200401 554.03 550.51 546.99 543A7 539.95

*crdno left vol incr b.c sacode safac h.s.no

12200501 220010000 0 1 I 1.68 1

*crdno it vol incr b.c sacode safac h.s.no

12200601 -939 0 3949 1 1.68 1

*crdno s.type mult dir.left dir.rt h.s.no

12200701 0 0.0 0.0 0.0 1

*crdno dth hl-f hl-r gs-lf gs-Ir floss doss boil-f h.s.no

12200801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. I

*crdno dth hl-f hl-r gs-lfgs-lir floss doss boil-fh.s.no

12200901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

12231201 5 4

*crdno source intvl

12231301 0.0 4

*crdno tempflag

12231400 -1

*crdno t(l) t(2) t(3) t(4) t(5)

12231401 559.36 553.24 547.39 541.79 536.42

12231402 553.30 547.33 541.62 536.15 530.91

12231403 559.17 553.05 547.20 541.61 536.24

12231404 554.56 548.54 542.79 537.29 532.02

*crdno left vol incr b.c sacode safac h.s.no

12231501 208010000 0 1 1 1.0365 1

12231502 218010000 0 1 1 0.3455 2

12231503 208020000 0 1 I 0.6015 3

12231504 218020000 0 1 1 0.2005 4

*crdno it vol incr b.c sacode safac h.s.no

12231601 -939 0 3949 1 1.0365 1

12231602 -939 0 3949 1 0.3455 2

12231603 -939 0 3949 1 0.6015 3

12231604 -939 0 3949 1 0.2005 4

*crdno s.type mult dir.left dir.rt h.s.no

12231701 0 0.0 0.0 0.0 4

*crdno dth hl-f hl-r gs-Ifgs-lr floss dloss boil-fh.s.no

12231801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 4

*crdno dth hi-f hl-r gs-ifgs-lir floss dloss boil-f h.s.no

12231901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 4

* tleat Structure no 223-2

* Interactive

*crdno no.h.s no.m.p geo s.s.flg left

12232000 6 5 2 1 0.7328

*crdno mesh fig fret

12232100 0 1

*crdno intvl rt.cor

12232101 4 0.8247

*crdno comp intvi

12232201 5 4

*crdno source intvi

12232301 0.0 4

*crdno tcmpflag

12232400 -I

*crdno t(l) t(2) t(3) t(4) t(5)

12232401 559.19 555.23 551.38 547.65 544.02

12232402 554.67 550.77 546.99 543.32 539.75

12232403 559.02 555.06 551.22 547.49 543.87

12232404 553.95 550.07 546.30 542.65 539.09

12232405 558.72 554.77 550.93 547.21 543.59

12232406 557.34 553.41 549.59 545.89 542.28

*crdno left vol incr b.c sacode safac h.s.no

12232501 208020000 0 1 1 0.3255 1

12232502 218020000 0 1 1 0.1085 2

12232503 208030000 0 1 1 0.8385 3

12232504 218030000 0 1 1 0.2795 4

12232505 208040000 0 1 1 0.9375 5

12232506 218040000 0 1 1 0.3125 6

*crdno it vol incr b.c sacode safac h.s.no

12232601 -939 0 3949 I 0.3255 1

12232602 -939 0 3949 1 0.1085 2

12232603 -939 0 3949 1 0.8385 3

12232604 -939 0 3949 1 0.2795 4

12232605 -939 0 3949 1 0.9375 5

12232606 -939 0 3949 1 0.3125 6

*crdno s.type mult dir.left dir.at h.s.no

12232701 0 0.0 0.0 0.0 6

*crdno dth hi-f hl-r gs-lfgs-ir floss dloss boil-fh.s.no

12232801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 6

*crdno dth hl-f hl-r gs-ifgs-ir floss doss boil-f h.s.no

12232901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 6

* Heat Structure no 223-1

* Interactive

*crdno no.h.s no.m.p geo s.s.fig left

12231000 4 5 2 1 0.7328

*crdno mesh fig fmt

12231100 0 1

*crdno intvl rt.cor

12231101 4 0.8725

*crdno comp intvl

* lIeat Structure no 225-0

* Interactive

*crdno no.h.s no.m.p geo s.s.flg left

A-23
12250000 10 5 2 1 0.300

*crdno mesh fig fmt

12250100 0 1

*crdno intvI rt.cor

12250101 4 0.380

*crdno comp intvl

12250201 4 4

*crdno source intvl

12250301 0.0 4

*crdno tempflag

12250400 -1

*crdno t(1) t(2) t(3) t(4) t(5)

12250401 559.69 550.03 540.88 532.20 523.93

12250402 560.55 550.86 541.69 532.99 524.69

12250403 563.42 553.65 544.39 535.60 527.23

12250404 568.27 558.34 548.94 540.01 531.51

12250405 573.72 563.62 554.06 544.98 536.33

12250406 578.25 568.01 558.32 549.11 540.34

12250407 580.26 569.96 560.21 550.95 542.12

12250408 579.06 568.80 559.08 549.86 541.06

12250409 579.06 568.80 559.08 549.85 541.06

12250410 579.49 569.22 559.49 550.25 541.44

*crdno left vol incr b.c sacode safac h.s.no

12250501 225010000 0 1 1 0.5200 1

12250502 230010000 0 1 1 0.2795 2

12250503 230020000 0 1 1 0.2795 3

12250504 230030000 0 1 1 0.2795 4

12250505 230040000 0 1 1 0.2795 5

12250506 230050000 0 1 1 0.2795 6

12250507 230060000 0 1 1 0.3775 7

12250508 240010000 0 1 1 0.5590 8

12250509 245010000 0 1 1 0.5590 9

12250510 250010000 0 1 1 0.8430 10

*crdno rt vol incr b.c sacode safac h.s.no

12250601 -939 0 3949 1 0.5200 1

12250602 -939 0 3949 1 0.2795 2

12250603 -939 0 3949 1 0.2795 3

12250604 -939 0 3949 1 0.2795 4

12250605 -939 0 3949 1 0.2795 5

12250606 -939 0 3949 1 0.2795 6

12250607 -939 0 3949 1 0.3775 7

12250608 -939 0 3949 1 0.5590 8

12250609 -939 0 3949 1 0.5590 9

12250610 -939 0 3949 1 0.8430 10

*crdno s.type mult dir.left dir.t h.s.no

12250701 0 0.0 0.0 0.0 10

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

122508010.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 10

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

122509010.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 10

*,

Heat Structure no 225-1

* Interactive

*crdno no.hs no.m.p geo ss.flg left

12251000 1 5 2 1 0.282

*crdno mesh flg fmt

12251100 0 1

*crdno intvl stcor

12251101 4 0.300

*crdno comp intvl

12251201 4 4

*crdno source intvl

12251301 0.0 4

*crdno tempflag

12251400 -1

*crdno t(1) t(2) t(3) t(4) t(5)

12251401 559.72 557.62 555.55 553.51 551.49

*crdno left vol incr b.c sacode safac h.s.no

12251501 225010000 0 1 1 0.520 1

*crdno it vol incr b.c sacode safac h.s.no

12251601 -939 0 3949 1 0.520 1

*crdno s.type mult dir.left dir.rt h.s.no

12251701 0 0.0 0.0 0.0 1

*crdno, dth hl-f hl-r gs-lfgs-ir floss doss boil-f h.s.no

12251801 0.0 30.0'30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dht hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

12251901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

* Heat Structure no 240-0

* Interactive

*crdno no.h.s no.m.p geo s.s.flg left

12400000 2 5 2 1 0.282

*crdno mesh fig fret

12400100 0 1

*crdno intvl ti.cor

12400101 4 0.310

*crdno comp intvl

12400201 4 4

*crdno source intvl

12400301 0.0 4

*crdno tempflag

12400400 -1

*crdno t(l) t(2) 1(3) t(4) t(5)

12400401 579.10 575.60 572.17 568.81 565.53

12400402 579.10 575.60 572.17 568.81 565.53

*crdno left vol incr b.c sacode safac h.s.no

12400501 240010000 0 1 1 0.559 1

12400502 245010000 0 1 1 0.559 2

*crdno rt vol incr b.c sacode safac h.s.no

12400601 -939 0 3949 1 0.559 1

12400602 -939 0 3949 1 0.559 2

*crdno s.type mult dir.left dir.t h.s.no

12400701 0 0.0 0.0 0.0 2

*crdno dit hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

12400801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

*crdno dit hl-f hl-r gs-lf gs-Ir floss dloss boil-f h.s.no

12400901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

* Heat Structure no 251-0

* Interactive

*crdno no.h.s no.m.p geo s.s.flg left

12510000 1 5 1 1 0.0

*crdno mesh fig fret

12510100 0 1

*crdno intvl rtcor

12510101 4 0.010

*crdno comp intvi

12510201 4 4

*crdno source intvl

12510301 0.0 4

*crdno tempflag

12510400 -1

*crdno t(l) t(2) t(3) t(4) t(5)

12510401 579.80 579.61 579.41 579.21 579.01

*crdno left vol incr b.c sacode safac h.s.no

12510501 250010000 0 1 1 1.80 1

*crdno it vol incr b.c sacode safac h.s.no

12510601 251010000 0 1 1 1.80 1

*crdno s.type mult dir.left dir.rt h.s~no

12510701 0 0.0 0.0 0.0 1

*crdno dot hl-f hl-r gs-lf gs-Ir floss dloss boil-f hs.no

12510801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dit hl-f hl-r gs-If gs-lr floss doss boil-f h.s.no

12510901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

* Heat Structure no 255-1

* Interactive

*crdno no.h.s no.m.p geo ss.flg left

12551000 3 5 1 1 0.0

*crdno mesh fig fmt

12551100 0 1

*crdno intvl rt.cor

12551101 4 0.005

*crdno comp intvl

A-24
12551201 4 4

*crdno source intvl

12551301 0.0 4

*crd.o temlpfag

12551400 -1

*ctdno t(t) t(2) 1(3) t(4) t(5)

12551401 578.67 578.08 577.48 576.88 576.28

12551402 567.71 567.13 566.55 565.97 565.39

12551403 566.68 566.11 565.53 564.95 564.37

*crdno left vol incr b.c sacode safac h.s.no

12551501 252010000 0 1 1 0.30 1

12551502 255010000 0 1 1 0.70 2

12551503 260010000 0 1 1 1.00 3

crdno it vol incr b.c sacode safac h.s.no

12551601 -939 0 3949 1 0.30 1

12551602 -939 0 3949 1 0.70 2

12551603 -939 0 3949 1 1.00 3

*crdno s.type mull dir.Ieft dirat h.s.no

12551701 0 0.0 0.0 0.0 3

*crdno dth hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

12551801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 3

*crdno dth hl-f hI-r gs-If gs-Ir floss doss boil-f h.s.no

12551901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 3 a

*crdno dth hl-f hI-r gs-f gs-Ir floss floss boil-f h.s.no

12601801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hi-r gs-f gs-ir floss dloss boil-f h.s.no

12601901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

Heat Structure no 255-2

* Interactive

*crdo no.h.s no.m.p geo s.s.flg left

12552000 1 5 2 1 0.381

*crdno mesh fig fmt

12552100 0 1

*crdn inovl rticor

12552101 4 0.474

*crdno comp intvl

12552201 5 4

*crdno source intvl

12552301 0.0 4

*crdno tempflag

12552400 -1

*cydno t(I) t(2) 0(3) 1(4) 1(5)

12552401 566.93 562.44 558.21 554.20 550.39

Ocrdno left vol incr b.c sacode safac h.sno

12552501 255010000 0 1 1 0.854 1

*crdno it vol incr b.c sacode safac h.s.no

12552601 -939 0 3949 1 0.854 1

*crdno s.type mull dir.left dir.rt h.s.no

12552701 0 0.0 0.0 0.0 1

*cydno dth hl-f hl-r gs-If gs-ir floss doss boil-f h.s.no

12552801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hl-r gs-If gs-r floss doss boil-f h.s.no

12552901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

* Heat Structure no 260-i

* Interactive

*crdno no.h.s no.m.p geo s.s.flg left

12601000 1 5 2 1 0.381

*crdno mesh fig fmt

12601100 0 I

*crdno intvl rtcor

12601101 4 0.728

*crdno comp intvl

12601201 5 4

*crdno source intvl

12601301 0.0 4

*crdno tempflag

12601400 -1

*cadno t(l) t(2) t(3) t(4) t(5)

12601401 564.64 545.38 529.38 515.70 503.76

*crdno left vol incr b.c sacode safac h.sno

12601501 260010000 0 1 1 0.712 1

*crdno rt vol incr b.c sacode safac h.s.no

12601601 -939 0 3949 1 0.712 1

*crdno s.type mull dir.left dir.n h.s.no

12601701 0 0.0 0.0 0.0 1

* Heat Structure no 260-2

11 Interactive

*crdno no.h.s no.m.p geo s.s.flg left

12602000 1 5 1 1 0.0

*crdno mesh flg fret

12602100 0 1

*crdno intvl nt.cor

12602101 4 0.474

*crdno comp intvl

12602201 5 4

*crdno source intvl

12602301 0.0 4

*crdno tempflag

12602400 -1

*chdno t(l) t(2) t(3) t(4) t(5)

12602401 567.72 552.22 536.73 521.23 505.74

*crdno left vol incr b.c sacode safac h.s.no

12602501 260010000 0 1 1 0.712 1

*crdno at vol incr b.c sacode safac h.s.no

12602601 -939 0 3949 1 0.712 1

*crdno s.typc mult dir.lcft dir.t h.s.no

12602701 0 0.0 0.0 0.0 1

*crdno dth hi-f hi-r gs-if gs-ir floss floss boil-f h.s.no

12602801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hi-f hl-r gs-If gs-r floss dloss boil-f h.s.no

12602901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

A Broken Loop

A Heat Structure no 300-0

Broken Loop: Hot leg

*crdno no.h.s no.m.p geo s.s.flg left

13000000 3 3 2 1 0.142

*crdno mesh flg fmnt

13000100 0 1

*crdno intvl atcor

13000101 2 0.178

*crdno comp intvl

13000201 4 2

*crdno source intvl

13000301 0.0 2

*crdno tempflag

13000400 -1

*cidno IlM) t(2) 0(3)

13000401 560.57 551.47 543.29

13000402 560.20 551.12 542.95

13000403 560.14 551.06 542.89

*crdno left vol incr b.c sacode safac h.s.no

13000501 300010000 0 1 1 0.876 1

13000502 305010000 0 1 1 0.698 2

13000503 310010000 0 1 1 1.424 3

*crdno vtol incr b.c sacode safac h.s.no

13000601 -939 0 3949 1 0.876 1

13000602 -939 0 3949 1 0.698 2

13000603 -939 0 3949 1 1.424 3

Ocrdno s.type mull dir.left dir.t h.s.no

13000701 0 0.0 0.0 0.0 3

*crdno dth hl-f hl-r gs-if gs-ir floss floss boil-f h.s.no

13000801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 3

*crdno dih hl-f hi-r gs-if gs-Ir floss doss boil-f h.s.no

13000901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 3

A lHeat Structure no 315-1

* Broken Loop: Hot leg

A-25
*crdno, no.h.s no.m.p geo s.s.flg left

13151000 1 3 2 1 0.055

*crdno mesh fig fmt

13151100 0 1

*crdno intvl rt.cor

13151101 2 0.178

*crdno comp intvl

13151201 4 2

*crdno source intvl

13151301 0.0 2

*crdno tempflag

13151400 -1

*crdno t(l) t(2) t(3)

13151401 558.16 515.17 489.43

*crdno left vol incr b.c sacode safac h.s.no

13151501 315010000 0 1 1 0.488 1

*crdno vtol incr b.c sacode safac h.s.no

13151601 -939 0 3949 1 0.488 1

*crdno s.type mult dir.left dir.at h.s.no

13151701 0 0.0 0.0 0.0 1

)crdno dth hl-f hl-r gs-lfgs-lr floss floss boil-f .s.no

13151801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

13151901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

* Heat Structure no 315-2

* Broken Loop: Hot leg

*crdno no.h.s no.m.p geo s.s.flg left

13152000 1 3 2 1 0.0865

*crdno mesh flg fmt

13152100 0 1

*crdno intvl rt.cor

13152101 2 0.1095

*crdno comp intvl

13152201 4 2

*crdno source intvl

13152301 0.0 2

*crdno tempflag

13152400 -1

*crdno t(l) t(2) t(3)

13152401 560.40 554.41 549.07

*crdno left vol incr b.c sacode safac h.s.no

13152501 315020000 0 1 1 1.6085 I

*crdno it Vol incr b.c sacode safac h.s.no

13152601 -939 0 3949 1 1.6085 1

*crdno s.type mult dir.left dir.n h.s.no

13152701 0 0.0 0.0 0.0 1

*crdno dah hl-f hl-r gs4fgs-lr floss doss boil-f h.s.no

13152801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hl-r gs-If gs-Ir floss doss boil-f h.s.no

13152901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

* Heat Structure no 335-0

* Broken Loop: Cold leg

*crdno no.h.s no.m.p geo s.s.flg left

13350000 1 3 2 1 0.142

*crdno mesh fig fret

13350100 0 1

*crdno intvl rt.cor

13350101 2 0.178

*crdno comp intvl

13350201 4 2

*crdno source intvl

13350301 0.0 2

*crdno tempflag

13350400 -1

*crdno t(l) t(2) t(3)

13350401 554.25 545.34 537.32

*crdno left vol incr b.c sacode safac h.sno

13350501 335010000 0 I 1 0.7495 I

*crdno nt vol incr b.c sacode safac h.s.no

13350601 -939 0 3949 I 0.7495 1

*crdno s.type mult dir.left dir.rt h.s.no

13350701 0 0.0 0.0 0.0 1

*crdno dth hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

13350801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hl-r gs-lfgs-lr floss floss boil-f h.s.no

13350901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

* leat Structure no 350-0

* Broken Loop: Cold leg

*crdno no.h.s no.m.p geo s.s.flg left

13500000 I 3 2 1 0.055

*crdno mesh fig fmt

13500100 0 1

*crdno intvl rt.cor

13500101 2 0.178

*crdno comp intvi

13500201 4 2

*crdno source intvl

13500301 0.0 2

*crdno tempflag

13500400 -1 *chino t(I) t(2) 0()

13500401 552.23 510.10 484.89

*crdno left vol incr b.c sacode safac h.s.no

13500501 350010000 0 1 I 0.488 1

*crdno rt vol incr b.c sacode safac h.s.no

13500601 -939 0 3949 1 0.488 1

*crdno s.type mult dir.left dir.rt h.s.no

13500701 0 0.0 0.0 0.0 1

*crdno dth hl-f hl-r gs-lf gs4r floss floss boil-f h.s.no

13500801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

13500901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

Heat Structure no 350-2

* Broken Loop: Cold leg

*crdno no.h.s no.m.p geo s.s.flg left

13502000 1 3 2 I 0.0865

*crdno

13502100 0 1

*crdno intvl rt.cor

13502101 2 0.1095

*crdno comp intvl

13502201 4 2

*crdno source intvl

13502301 0.0 2

*crdno Iempflag

13502400 -1

*crdno t(1) t(2) t(3)

13502401 554.69 548.82 543.57

*crdno left vol incr b.c sacode safac h.s.no

13502501 350020000 0 1 1 1.6085 1

*crdno ft vol incr b.c sacode safac h.s.no

13502601 -939 0 3949 1 1.6085 1

*crdno s.type mult dir.left dir.Tt h.s.no

13502701 0 0.0 0.0 0.0 1

*crdno dth hl-f hl-r gs-If gs-lr floss floss boil-f hs.no

13502801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hl-r gs-If gs-lr floss doss boil-f h.sno

13502901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

* Heat Structure no 370-0

* Broken Loop: Cold leg

*crdno no.h.s no.m.p geo s.s.flg left

13700000 2 3 2 1 0.111

*crdno mesh fig fmt

13700100 0 1

*crdno intvl rt.cor

13700101 2 0.1365

A-26
*crdno comp intvl

13700201 4 2

*crdno source intvl

13700301 0.0 2

*crdno tempflag

13700400 -1

*chino t(l) t(2) t(3)

13700401 548.43 542.20 536.56

13700402 551.56 545.27 539.57

*crdno left vol incr b.c sacode safac h.s.no

13700501 370010000 0 1 1 0.7251 1

13700502 380010000 0 1 1 9.3549 2

*crdno vt vol incr b.c sacode safac h.s.no

13700601 -939 0 3949 1 0.7251 1

13700602 -939 0 3949 1 9.3549 2

*cntno s.type mult dir.left dir.rt h.s.no

13700701 0 0.0 0.0 0.0 2

*crdno dit hi-f hl-r gs-Ifgs-lr floss doss boil-f h.s.no

13700801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

*crdno dth hl-f hl-r gs-If gs-lr floss floss boil-f h.s.no

13700901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 I. 2

* Pressurizer heat structures

0 Heat Structure no 415-2

* Pressurizer. Vessel

*crdno no.h.s no.m.p geo s.s.flg left

14152000 6 3 2 1 0.42291

*crdno mesh fig fret

14152100 0 1

*crdno intvl rt.cor

14152101 2 0.49911

*crdno comp intvl

14152201 5 2

*crdno source intvl

14152301 0.0 2

*crdno tempflag

14152400 -1

Ocrdno t(l) t(2) t(3)

14152401 574.00 566.84 560.26

14152402 583.96 576.54 569.71

14152403 599.59 591.75 584.54

14152404 611.29 602.98 595.48

14152405 613.55 605.34 597.79

14152406 613.67 605A7 597.91

*crdno left vol incr b.c sacode safac h.s.no

14152501 415010000 0 1 1 0.1815 1

14152502 415020000 0 1 1 0.1524 2

14152503 415030000 0 1 1 0.3967 3

14152504 415040000 0 1 1 0.5289 4

14152505 415050000 0 1 1 0.3967 5

14152506 415060000 0 1 1 0.1943 6

*crdo it vol incr b.c sacode safac h.s.no

14152601 -939 0 3949 1 0.1815 1

14152602 -939 0 3949 1 0.1524 2

14152603 -939 0 3949 1 0.3967 3

14152604 -939 0 3949 1 0.5289 4

14152605 -939 0 3949 1 0.3967 5

14152606 -939 0 3949 1 0.1943 6

*crdno s.type mult dir.left dir.t h.s.no

14152701 0 0.0 0.0 0.0 6

*crdno dth hl-f hl-r gs-If gs-Ir floss floss boil-f h.s.no

14152801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 6

*crdno dt hl-f hl-r gs-f gs-Ir floss doss boil-f h.s.no

14152901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 6

*crdno intvl rt~cor

14153101 2 0.3683

*crdno comp intvl

14153201 5 2

*crdno source intvl

14153301 .0.0 2

*crdno tempflag

14153400 -1

*crdno t(l) t(2) t(3)

14153401 613.68 591.80 575A2

14153402 613.68 591.81 575.43

*crdno left vol incr b.c sacode safac Ls.no

14153501 415070000 0 1 1 0.1029 1

14153502 420010000 0 1 1 0.1029 2

*cJnjo at vol incr b.c sacode safac h.s.no

14153601 -939 0 3949 1 0.1029 1

14153602 -939 0 3949 1 0.1029 2

*crdno s.type mult dir.left dir.at h.s.no

14153701 0 0.0 0.0 0.0 2

*crdno dth hl-f hl-r gs-If gs-Ir floss dloss boil-f h.s.no

14153801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

*crdno dih hl-f hl-r gs-Ifgs-Ir floss dloss boil-f h.s.no

14153901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

* Heat Structure no 420-1

Pressurizer Vessel ,

*crdno no.h.s no.m.p'geo ss.flg left

14201000 1 3 1 1 0.0

*crdno meshiflg fret

14201100 0 1

*crdno intvl rt.cor

14201101 2 0.18415

*crdno comp intvl

14201201 5 2

*crdno source intvl

14201301 0.0 2

*crdno tempflag

14201400 -1

*crino t(l) 1(2) 1(3)

14201401 613.89 597.36 580.82

*Ocrno left vol incr b.c sacode sfac h.s.no

14201501 420010000 0 1 1 0.130 1

*crdno t vol incr b.c sacode safac h.s.no

14201601 -939 0 3949 1 0.130 1

*crdno s.type mult dir.left dir.rt h.s.no

14201701 0 0.0 0.0 0.0 1

*crdno dth hl-f hl-r gs-If gs-Ir floss floss boil-f h.s.no

14201801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*crdno dth hl-f hl-r gs-If ga-Ir floss floss boil-f hs.no

14201901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 1

*

* Secondary Side

* leat Structure no 500-0

* Secondary Side: Shroud Upper Plenum

*crdno no.h.s no.m.p geo ss.flg left

15000000 2 5 2 1 0.3048

*crdno mesh fig fret

15000100 0 1

*crdno intvl rt.cor

15000101 4 0.3143

*crdno comp intvl

15000201 5 4

*crdno source intvl

15000301 0.0 4

*crdno tempflag

15000400 -1

*crdno t(I) t(2) t(3) t(4) t(5)

15000401 543.88 543.88 543.88 543.88 543.87

15000402 543.91 543.91 543.91 543.91 543.91

*crdno left vol incr b.c sacode safac h.s.no

* Heat Structure no 415-3

* Pressurizer. Vessel

*crdno no.h.s no.m.p geo ss.flg left

14153000 2 3 2 1 0.2032

*crdno mesh fig fint

14153100 0 1

A-27
15000501 502010000 0 1 0 0.85127 1

15000502 515060000 0 1 0 2.51199 2

*crdno it vol incr b.c sacode safac h.s.no

15000601 500010000 0 1 0 0.87780 1

15000602 505010000 0 1 0 2.59028 2

*crdno s.type mult dir.left dir.at h.s.no

15000701 0 0.0 0.0 0.0 2

*crdno dth hi-f hl-r gs-lfgs-lr floss dloss boil-f h.s.no

15000801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2

*crdno dth hl-f hl-r gs-lfgs-lr floss fdoss boil-f h.s.no

15000901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 2 *

* Heat Structure no 510-0

* Secondary Side: Shroud Lower Section

*crdno no.h.s no.m.p geo s.s.flg left

15100000 5 5 2 1 0.6445

*crdno mesh fig fret

15100100 0 1

*crdno intvl tt.cor . 15100101 4 0.6572

*crdno comp intvl

15100201 5 4

*crdno source intvl

15100301 0.0 4

*crdno tempflag

15100400 -1

*crdno t(l) t(2) t(3) t(4) t(5)

15100401 539.18 535.98 532.79 529.61 526.45

15100402 538.60 535.09 531.59 528.10 524.63

15100403 538.66 535.13 531.63 528.14 524.66

15100404 529.32 526.93 524.55 522.18 519.83

15100405 520.68 519.33 518.00 516.68 515.36

*crdno left vol inc" b.c sacode safac h.s.no

15100501 515050000 0 1 1 0.646354 1

15100502 515040000 0 1 0 2.46858 2

15100503 515030000 0 1 0 2.46858 3

15100504 515020000 0 1 0 1.23429 4

15100505 515010000 0 1 0 1.23429 5

*crdno it vol incr b.c sacode safac h.s.no

15100601 508010000 0 1 1 0.646354 1

15100602 510010000 0 1 0 2.51723 2

15100603 510010000 0 1 0 2.51723 3

15100604 510010000 0 1 0 1.25862 4

15100605 510010000 0 1 0 1.25862 5

*crdno s.type mult dir.left dir.rt h.s.no

15100701 0 0.0 0.0 0.0 5

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f hs.no

15100801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 5

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

15100901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 5

* Heat Structure no 525-0

* Secondary Side: Vessel Wall

*crdno no.h.s no.m.p geo s.s.flg left

15250000 8 3 2 1 0.7112

*crdno mesh fig fmt

15250100 0 1

*crdno intvl rLcor

15250101 2 0.76397

*crdno comp intvl

15250201 5 2

*crtho, source intvl

15250301 0.0 2

*crdno tempflag

15250400 -1

*crdno t(I) t(2) t(3)

15250401 543.26 537.76 532.46

15250402 543.25 537.76 532.45

15250403 543.28 537.79 532.48

15250404 542.75 537.26 531.97

15250405 505.94 501.29 496.82

15250406 507.22 502.55 498.05

15250407 507.21 502.55 498.04

15250408 507.05 502.38 497.88

*crdno left vol incr b.c sacode safac h.s.no

15250501 525010000 0 1 1 0.76238 1

15250502 520010000 0 1 1 0.7520 2

15250503 500010000 0 1 1 0.4445 3

15250504 505010000 0 1 1 1.2131 4

15250505 508010000 0 1 1 0.6096 5

15250506 510010000 0 1 1 0.6096 6

15250507 510020000 0 1 1 0.6096 7

15250508 510030000 0 1 1 0.6096 8

*crdno it vol incr b.c sacode safac h.s.no

15250601 -938 0 3948 1 0.76238 1

15250602 -938 0 3948 1 0.7520 2

15250603 -938 0 3948 1 0.4445 3

15250604 -938 0 3948 1 1.2131 4

15250605 -938 0 3948 1 0.6096 5

15250606 -938 0 3948 1 0.6096 6

15250607 -938 0 3948 1 0.6096 7

15250608 -938 0 3948 1 0.6096 8

*crdno s.type mulr dir.left dir.rt h.s.no

15250701 0 0.0 0.0 0.0 8

*crdno dth hl-f hl-r gs-lfgs-lr floss doss boil-f h.s.no

15250801 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 8

*crdno dth hl-f hl-r gs-lf gs-lr floss doss boil-f h.s.no

15250901 0.0 30.0 30.0 0.0 0.0 0.0 0.0 1. 8

* Enviromental Heat Loss Boundary Conditions

* Table no 939

* Enviromental temperature

*crdno table-type

20293900 temp

*crdno time temp

20293901 0.0 305.0

* Table no 949

* Enviromental Loss Heat XFER Coefficient

*crdno table.type

20294900 hic-t

*crdno time htc

20294901 0.0 30.0

a Table no 938 *Enviromental Heat Loss boundary temperature

*crdno table.type

20293800 temp

*crdno time temp

20293801 0.0 305.0

* Table no 948

*Enviromental Loss Heat XFER Coefficient

*crdno table-type

20294800 htc-t

*crdno time htc

20294801 0.0 40.0

a: Reactor kinetics i

a Point kinetics

A-28
*crdno type ftype

30000000 point separabl

*crdno decay power in.reac, del.n.fract.fis.f. U239

30000001 gamma-ac 50.+6 0. 371.875 1. 1.

* delayed neutron constants

*crdno yield ratio decay const.

30000101 0.0420 3.01

30000102 0.1150 1.14

30000103 0.3950 3.301

30000104 0.1960 0.301

30000105 0.2190 0.305

30000106 0.0330 0.0124 ,

*crdno power time dimens.

30000401 25.+6 9. hr

30000402 50.+6 66. hr ,

*crdno react.curve

30000011 609

* Reactivity curve table

*crdno type trip-no

20260900 reac-t 403 *:

*

*crdno time reactiv.

20260901 -1.0 0.0 *1

20260902 0.1 -2.1 *1

20260903 0.2 -4.3 *

20260904 0.3 -6.8 *

20260905 0.4 -9.2 *

20260906 0.5 -11.1 *i

20260907 0.6 -12.2 *

20260908 0.7 -12.9 *:

20260909 0.8 -13.3 *

20260910 0.9 -13.6 *

20260911 1.0 -13.7 :

20260912 1.1 -13.8 *

20260913 1.2 -13.9 *1

20260914 1.8 -14.0 *

20260915 2500. -14.0 :

*crdno voljno incr

30000701 230010000

30000702 230020000

30000703 230030000

30000704 230040000

30000705 230050000

30000706 230060000

weightj Water_temp..oef

0 0.15746 0.0

0 0.15746 0.0

0 0.15746 0.0

0 0.15746 0.0

0 0. 15746 0.0

0 0.21270 0.0

*crdno heatno incr weight.f fueLtemp_coef

30000801 2300001 0 0.0170 0.0

30000802 2300002 0 0.3639 0.0

30000803 2300003 0 0.2747 0.0

30000804 2300004 0 0.2379 0.0

30000805 2300005 0 0.0976 0.0

30000806 2300006 0 0.0089 0.0

*+

*-

*crdno mater._type

20100100 tbl/fctn

20100200 tbl/fctn

20100300 tbl/fctn

20100400 tbl/fctn

20100500 c-steel

20100600 tbl/fctn

thc-flg cap.flg

1 1 * -.U02

3 1 *2-Gap

I I * 3 - Zircaloy-4

1 I * 4 - S-Steel

* 5 - C-steel

I I * 6- Inconel-600

* )U02 Thermal Conductivity

*crdno

20100101

20100102

20100103

20100104

20100105

20100106

20100107

20100108

20100109

20100110

20100111

20100112

20100113

20100114

20100115

20100116

20100117

20100118

temp. thc

273.150

416.670

533.150

699.817

866.483

1033.150

1088.710

1199.820

1283.150

1366.480

1533.150

1616.480

1699.820

1977.590

2255.370

2533.150

2810.930

3088.710

8.440000

6.450000

5.782385

4.633177

3.880307

3.357625

3.155129

2.983787

2.836674

2.713792

2.521680

2.448990

2.391875

2.289762

2.307069

2.433413

2-661870

2.994171

* Moderator density reactivity table

* stdy-st transnt

*crdno density react, react.

30000501 626.26 0.0 * -4.4769

30000502 663.96 0.0 * -3.2923

30000503 716.17 0.0 * -1.5692

30000504 761.12 0.0 * -0.1692

30000505 768.37 0.0 * 0.04615

30000506 791.57 0.0 * 0.6923

30000507 811.88 0.0 * 1.2398

30000508 862.63 0.0 * 2.2415

30000509 938.04 0.0 * 3.9231

30000510 997.49 0.0 * 5.1077

* Doppler reactivity table

* stdy-st transnt

*crdno temper react, react.

30000601 255.0 0.0 * 1.5

30000602 500.0 0.0 * 0.3

30000603 750.0 0.0 * -0.7

30000604 1000.0 0.0 * -1.6

30000605 1250.0 0.0 * -2.3

30000606 1500.0 0.0 * -3.0

30000607 1750.0 0.0 * -3.7

30000608 2000.0 0.0 * -4.3

30000609 2250.0 0.0 * -4.9

30000610 2500.0 0.0 * -5.4

30000611 2750.0 0.0 * -5.9

30000612 3000.0 0.0 * -6.3

* U02 Volume Heat Capacity

*crdno

20100151

20100152

20100153

20100154

20100155

20100156

20100157

20100158

20100159

20100160

20100161

20100162

20100163

20100164

20100165

temp. vol.hcap

273.15 2.310427+6

323.15 2.571985+6

373.15 2.746357+6

673.15 3.138694+6

1373.15 3.443844+6

1773.15 3.531030+6

1973.15 3.792588+6

2173.15 4.228518+6

2373.15 4.882412+6

2673.15 6.015829+6

2773.15 6.320980+6

2873.15 6.582538+6

2973.15 6.713317+6

3113.15 6.800503+6

4699.82 6.800503+6

A-29
* Gap Thermal Conductivity

*crdno gaz-type mole-frac.

20100201 helium 1.00

*!

Gap Volume Heat Capacity

*!

*crd&o temp. vol.hcap

20100251 273.15 5.4

20100252 5000.00 5.4

* Zhrcoloy-4 Thermal Conductivity

*crdno temp. thc

20100301 380.4 13.6

20100302 469.3 14.6

20100303 577.6 15.8

20100304 685.9 17.3

20100305 774.8 18.4

20100306 872.0 19.8

20100307 973.2 21.8

20100308 1073.2 23.2

20100309 1123.2 25.4

20100310 1152.3 24.2

20100311 1232.2 25.5

20100312 1331.2 26.6

20100313 1404.2 28.2

20100314 1576.2 33.0

20100315 1625.2 36.7

20100316 1755.2 41.2

20100317 2273.2 55.0

* Zisvoloy-4 Volume Heat Capacity

*crdno temp. vol.hcap

20100351 300.00 1.841+6

20100352 400.00 1.978+6

20100353 640.00 2.168+6

20100354 1090.00 2.456+6

20100355 1093.00 3.288+6

20100356 1113.00 3.865+6

20100357 1133.00 4.028+6

20100358 1153.00 4.709+6

20100359 1173.00 5.345+6

20100360 1193.00 5.044+6

20100361 1213.00 4.054+6

20100362 1233.00 3.072+6

20100363 1243.00 2.332+6

20100364 1477.00 2.332+6

20100455

20100456

20100457

20100458

20100459

20100460

699.82 4.504+6

810.93 4.639+6

922.04 4.773+6

1144.26 5.076+6

1366.50 5.376+6

1477.59 5.546+6

* Inconel-600 Thermal Conductivity

*crdno temp. the

20100601 366.5 13.85

20100602 477.6 15.92

20100603 588.7 18.17

20100604 700.0 20.42

20100605 810.9 22.50

20100606 922.0 24.92

20100607 1033.2 26.83

20100608 1144.3 29.42

20100609 1477.6 36.06

* Inconel-600 Volume Heat Capacity

*crdno temp. vol.hcap

20100651 366.5 3.908+6

20100652 477.6 4.084+6

20100653 588.7 4.260+6

20100654 700.0 4.436+6

20100656 810.9 4.665+6

20100657 922.0 4.929+6

20100658 1033.2 5.105+6

20100659 1477.6 5.727+6

*

*

*

ICAP Assessment Parameters

* Levels

* Cntrlvar No I - DowncomerLiquid Level -LE-IST-1

* Cntdvar No 2 - Upper Plenum Liquid Level - LE-3UP-I

* Cntdvar No 3 - SG Liquid Level - LD-P004-008B

* Cntdvar No 4-Pressurizer Liquid Level -LT-P139-007

* Pressure

* S-Steel Thermal Conductivity

*crdno temp. thc

20100401 273.15 12.98

20100402 1199.82 25.10

a S-Steel Volume Heat Capacity

*crdno temp. vol.hcap

20100451 273.15 3.830+6

20100452 366.50 3.830+6

20100453 477.59 4.190+6

20100454 588.59 4.336+6

a P 420010000- PRZ Vapor Space -PE-PC-004

* P 105010000- Intact Loop Hot leg - PE-PC-002

a P 525010000 - SG Dome - PE-SGS-001 a

Mass Flow Rate

* mflowj 183000000 - Break Orifice - FR-PC-SBRK a

a Coolant Temperature

a tempf 105010000- Intact Loop Hot Leg - TE-PC-002A

* tempf206030000- Downcomer I Stalk - TE-IST-005

a Fluid Density

a Fluid Density in Intact Loop Hot leg:

a DE-PC-002A - Beam A (Bottom)

a DE-PC-002C - Beam C (Upper)

a rho 105010000 - Fluid Density in the hot leg

a Luiquid Levels Calculations

Control Variable No 1

A-30
* Downcomer Liquid Level - LE-IST-1 - Computed variable

*crdno name type s.fac, in.v infig l.nt min max

20500100 LE-1ST-1 sum 1.0 5.316 0

*crdno a0 al var code

20500101 0.0 0.1874 voidf 210010000

20500102 0.2852 voidf 212010000

20500103 0.2814 voidf 214010000

20500104 0.9580 voidf 216010000

20500105 0.5790 voidf 216020000

20500106 0.6570 voidf 216030000

20500107 0.5590 voidf 216040000

20500108 0.5590 voidf 216050000

20500109 0.5200 voidf 216060000

20500110 0.3600 voidf 222010000

20500111 0.3700 voidf 220010000

* Control Variable No 2

* Upper Plenum Liquid Level - LE-3UP- I - Computed variable

*crdno name type s.fac. in.v in.fig I.cnt min max

20500200 LE-3UP-1 sum 1. 1.7086 0 4

crdno aO al var code

20500201 0.0 0.2852 voidf 252010000

20500202 0.7114 voidf 255010000

20500203 0.7120 voidf 260010000

* Control Variable No 3

* Steam Generator. Density Compensated

* Liquid Level LD-P004-008B Computed variable

*crdno name type s.fac. in.v in.flg I.ct mrin max

20500300 LD-P004 sum 1. 0.0 1

*crdno a0 &1 var code

20500301-2.95 0.6096 voidf 510010000

20500302 0.6096 voidf 510020000

20500303 0.6096 voidf 510030000

20500304 0.6096 voidf 508010000

20500305 1.2131 voidf 505010000

20500306 0.4440 voidf 502010000

20500307 0.7180 voidf 520010000

* Control Variable no 6

* Fuel average Temperature

*crdno name type s.fac. in.v in.fig I.nt mnn max

20500600 Core-TEM sum 0.5633802 0.0 1

Ocrdno a0 al var code

20500601 0.0 0.2795 htvat 2300001

20500602 0.2795 htvat 2300002

20500603 0.2795 htvat 2300003

20500604 0.2795 htvat 2300004

20500605 0.2795 htvat 2300005

20500606 0.3775 htvat 2300006

* End of input data file

0 Control Variable No 4

0 Pressurizer Liquid Level on the South-West Side LT-P 139-007

*crdno name type s.fac. in.v in.flg I.cnt min max

20500400 LT-P139 sum 1. 0.0 1

*crdno aO at var code

20500401 0.0 0.1815 voidf 415010000

20500402 0.1524 voidf 415020000

20500403 0.3967 voidf 415030000

20500404 0.5289 voidf 415040000

20500405 0.3967 voidf 415050000

20500406 0.1943 voidf 415060000

20500407 0.1029 voidf 415070000

*

* Core Average Coolant Density and Fuel Temperature:

• Control Variable no 5

* Core Coolant average density

*crdno name type s.fac. in.v in.fIg I.cnt min max

20500500 Core-RHO sum 0.5633802 0.0 1

*crdno aO al var code

20500501 0.0 0.2795 rho 230010000

20500502 0.2795 rho 230020000

20500503 0.2795 rho 230030000

20500504 0.2795 rho 230040000

20500505 0.2795 rho 230050000

20500506 0.3775 rho 230060000

A-31
408 p 100010000 ge null 0 2.15+6 1

*no trip-no rel trip..no lin time..on

605 -408 and -408 I 0.0

-1.0

RESTART FILE

TRANSIENT RUN

=LOFT Small Break Experiment L3-6

100

103

restart transnt

934

*crdnotime mindt max_dt ctri minor major restart

201 600.0 1.0-7 0.04 14003 50 15000 15000

202 810.0 1.0-7 0.04 14003 50 5250 5250

203 1500.0 1.0-7 0.04 14003 50 17250 17250

204 2400.0 1.0-7 0.04 14003 75 22500 22500 ,

* Component no 183

Break orifice - Simulated 4 in break of PWR (F = 205.9 mm2)

1830000 brkvlv valve

1830101 182010002 805000000 205.9-6 0.4 0.4 000100

1830102 1.0 0.85 0.60

1830201 1 0.0 0.0 0.0

1830300 mtrvlv

1830301 404 402 5.0 0.0

a

20800001 florgj 183000000

* Auxiliary Trips

*no var code rel var code const tin time on

401 time 0 ge null 0 -1.0 I 0.0

402 time 0 It null 0 -1.0 1 -1.0 a

a SCRAM

403 time 0 gt null 0 0.0 I -1.0

a BREAK

404 time 0 ge timeof 403 6.0 n -1.0

a PCP off

405 p 100010000 Ic null 0 2.15+6 n -1.0

* no trip..no tel trip-no lin time-on

601 404 and 405 n -1.0

a ECCS Control Logic

ano var code tel var code const lin time-on

406 p 610010000 le null 0 13.16+6 n -1.0 a

a no trip-no rel trip-no lin time-on

602 404 and 406 1 -1.0

a Auxiliary Feed Water Logic

no var code rel var code const lin Iimeon

407 time 0 ge timeof 403 6.0 I -1.0

*no trip.no rel trip-no lin time-on

603 404 and 407 I -1.0

a Pressurizer Stady state controller

*no trip-.no tel trip..no lin time-on

604 -403 and -403 n 0.0

a PCP Injection

ano var code rel var code const lin time-on

a Main Steam Control Valve

*no trip..no rel trip-no lin time-on

606 -403 and -403 n 0.0

* no trip-no rel tripjno fin time..on

607 -606 and -606 n -1.0

* no var code rel var code const lin time on

409 p 530010000 ge null 0 7.12+6 n -1.0

* no var code rel var code conot lin timeon

410 p 530010000 ge null 0 6.98+6 n -1.0

* no var code rel var code conot lin timeon

411 p 530010000 le null 0 6.50+6 n -1.0

* no var code rel var code const lin time-on

412 p 530010000 le null 0 6.57+6 n -1.0

* no var code rel var code const lin time_on

413 time 0 ge timeof 403 94.0 1 -1.0

* no var code rel var code const lin timeon

414 vlvarea 540 ge null 0 0.15 I -1.0

a Open trip

ano trip-no rel tripjno lin time..on

608 609 and 410 n -1.0

* no trip-no rel trip-no lin time-on

609 409 or 608 n -1.0

* no trip-no rel trip.no lin time-on

610 -414 and 413 n -1.0

* MSCV triggered on the noise

a Close trip

*no trip-no rel trip.no lin time-on

611 612 and 412 n -1.0

* no trip-no rel trip-no lin time-on

612 411 or 611 n -1.0

* no trip-no rel trip.no lin time-on

613 403 and 414 n -1.0

a Reactor kinetics

* Point kinetics

30000000 point separabl

30000001 gamma-ac 50.+6 0. 371.875 1. 1. a delayed neutron constants

30000101 0.0420 3.01

30000102 0.1150 1.14

30000103 0.3950 3.301

30000104 0.1960 0.301

30000105 0.2190 0.305

30000106 0.0330 0.0124

30000401 25.+6 9. hr

30000402 50.+6 66. hr

30000011 609

a Reactivity curve table

20260900 reac-t 403

20260901 -1.0 0.0

20260902 0.1 -2.1

20260903 0.2 -4.3

20260904 0.3 -6.8

20260905 0.4 -9.2

20260906 0.5 -11.1

20260907 0.6 -12.2

20260908 0.7 -12.9

20260909 0.8 -13.3

20260910 0.9 -13.6

20260911 1.0 -13.7

20260912 1.1 -13.8

20260913 1.2 -13.9

20260914 1.8 -14.0

20260915 2500. -14.0

A-32
* Moderator density reactivity table

30000501 626.26 -4.4769

30000502 663.96 -3.2923

30000503 716.17 -1.5692

30000504 761.12 -0.1692

30000505 768.37 0.04615

30000506 791.57 0.6923

30000507 811.88 1.2398

30000508 862.63 2.2415

30000509 938.04 3.9231

30000510 997.49 5.1077 ,

* Doppler reactivity table

30000601 255.0 1.5

30000602 500.0 0.3

30000603 750.0 -0.7

30000604 1000.0 -1.6

30000605 1250.0 -2.3

30000606 1500.0 -3.0

30000607 1750.0 -3.7

30000608 2000.0 -4.3

30000609 2250.0 -4.9

30000610 2500.0 -5.4

30000611 2750.0 -5.9

30000612 3000.0 -6.3

30000701 230010000 0 0.15746 0.0

30000702 230020000 0 0.15746 0.0

30000703 230030000 0 0.15746 0.0

30000704 230040000 0 0.15746 0.0

30000705 230050000 0 0.15746 0.0

30000706 230060000 0 0.21270 0.0

30000801 2300001 0 0.0170 0.0

30000802 2300002 0 0.3639 0.0

30000803 2300003 0 0.2747 0.0

30000804 2300004 0 0.2379 0.0

30000805 2300005 0 0.0976 0.0

30000806 2300006 0 0.0089 0.0

* End of restart file

A-33

Appendix B

Table 1. Initial conditions of the Experiment L3-6.

Parameters Measured Calculated

I values I values

Primary Coolant System:

Mass flow rate (kg/s)

Hot leg pressure (MPa)

Cold leg temperature (K)

Hot leg temperature (K)

Pressure vessel:

Power level (MW)

Pressurizer:

Liquid temperature (K)

Pressure (MPa)

Liquid Level (m)

Broken Loop:

Cold Leg Temperature near

Reactor Vessel (K)

Hot Leg Temperature near

Reactor Vessel (K)

Primary Coolant Pump

Injection (kg/s)

Steam Generator

Secondary Side:

Liquid Level* (m)

Liquid Temperature (K)

Pressure (MPa)

Mass flow rate (kg/s)

483.3 ± 2.6

14.87 ± 0.14

557.9 ± 1.1

577.1 ± 1.8

50.± 1

614.7 + 1.4

14.90 ± 0.25

1.18 ± 0.11

557.6 ± 2.6

561.4 ± 2.6

0.098 ± 0.016

0.22 ± 0.03

542.8 ± 0.8

5.57 ± 0.06

27.8 ± 0.1

482.42

14.87

560.9

579.7

50.

614.5

14.85

1.17

555.2

561.6

0.094

(to one pump)

0.2

544.1

5.58

27.76

* Level is defined as 0.0 at 2.95 in above the tube sheet.

B-1
Table 2. Sequence of events in the Experiment L3-6.

Events Experiment, RELAP5/MOD3,

S s

Reactor scrammed

Break initiated

HPIS injection initiated

Pressurizer emptied

Upper plenum

reached saturation pressure

Intact loop hot leg

voiding begun

Intact loop cold leg

voiding begun

Subcooled break flow ended

Secondary system Pressure

exceeded

Primary side Pressure

Primary Coolant Pumps

tripped

(End of Transient)

-5.8 ± 0.2

0.0

3.6 + 0.2

20.2 + 0.2

28.5 + 0.2

29.4 ± 5.0

31.4 ± 5.0

44.2 ± 0.2

930.0 ± 30.0

2371.4 ± 0.2

-6.0

0.0

3.6

24.

25.

27.

27.

34.

830.

not tripped

(2400.)

I I

B-2
Appendix C

Stem outlet

to Secondary coolant *yselm

LOFT System--intact loop

,ECC cold leg

Injection

hornogena2er

LOFT smll beak Otrim

Fig.l. LOFT System and the cold leg break configuration.

C-1
420

M1

0

0

CD

r-.

0

-tN

0

line

Pressurizer

Symbols: Volume and Heat structure

Pipe O-Time-dependent

volume

Pump M- Valve 415

,Feed water 310 315

SG Surge line

box/support

Cold leg break

'Downcomer

HPIS

Crossover Intact Loop Reactor

Water Vessel

Storage

Tank

Filler gap Filler gap

218

Lower plenum
LOFT: SBLOCR Experiment L3-6 SCORP/RELRPS/MO03. 1

E

a)

-j

co

L

010)

a)

L

CL_

1

I II I I

I I I I I t I g g I I I I

I • ,I I I

I I I I I I I I

I • I I I .. . . . . .. .• V I .. . . .. . . . . . . .. . . I-. -

I.. Legend -LT-.P139-007

.9 I 9

61. 0. 2b A......... ......... 4b ....... b .......

Time. s Fig. 3. Liquid Level in the Pressurizer.

LOFT: SBLOCR Experiment L3-6 SCORP/RELRP5/MO03.1

-4

CN

UC

r T 1 1 1 I I I I I I I I I I I I I I I I I I I I I I I I I I I I -4--------------------9--------------------I-------------------9-------------------- .4 I I I I .4 I 9 I .1

9.4 I I I I I.4 I I I I I .4 I I I I I I ...L ------ ±--------------4-----------------L----------------L I I I I I

I ~ I I I I 9 .4 I I I I 9 .4 I I I I I .4 I I I I a .4 I I I I I I g 9 I 9 I --------------------------------

I I I I I

I 9 I I I I I I I I I I I I I I I I I I I I I I -9--------------.4 I I I-----------------------------------------.9-----------------------------------------9- .4 I I I I I I C-----------------------------------------I ____________

I I I 1 9-

I I I I I I I I I I I I F----------------T----------------1

I 9 I I I

I I I I I I I I

I I 9 I I I I I I I ------------------------------------------------------------------------------------- 9 I I I I I I I I I I I I I 9 I I I 9 I I I I I I I I I 9 I

Ivb~................4b......sb...... Time. s

Legend

p E-PC-004

xp 420 (atup=0.6)

Time, s

Fig. 4. Pressure in the Pressurizer.

C-3
LOFT: SBLOCR Experiment L3-6 SCORP/RELRP5/1'003. 1

(a

CL

L

CL

(L

a)

L

CL

I I I I

S----------------------------------r----------4T---------- n ------------ r-----------

-- - -- - -- - - - - L - - - - - I -- - - - - - -- - - - - -

-------------- L---------- L---------- J----------- L-----------

I * *

.. .. .. . I T I I

IIIII I

IIIII I

.--------------.--------.. L........ ...... .....

I I I

Legend

PE-PC-002

xp 105 (Gup=0.6)

........ I ......... ! ......... t......... •......... •.........

0 400 800 1200 it

Time, s

Fig. 5. Pressure in the Intact loop hot leg.

LOFT: SBLOCR Experiment L3-6

2000 400

SCORP/RELRPS/MO03. 1

Co

Lf.:

CII lI

I I I II g II II

I I I I

I I£ I II

I I I -• 

I •I•III

I le . II

!" t "I - I

Legend

* PE-SGS-001

p 525 (aup=0.6)

Time, s

Fig. 6. Pressure in the Steam generator dome.

C-4

400
E

CD

-j

('4

0

0

I-P

,-t

C;

CD

C6

0

LOFT: SBLOCR Experiment L3-6

- - - - - - - - - -4 . . . . . . . . . r .. - - . -. -. -. -. . . . ..........- . --.. - - -

-- -- -- -- -- -- - ,---- - -- - -I - - -- -- -- --

- a ar" i i

II I I I' II I I

, . . _ . . I ,. . . . .II

-------- -------- ------------- L --------.- - ----------- ----------- ---- -------- 4------- I--------- ----------- I---------------

Legend

* LO-P004-0088

Xcntri.'La 3 up'0.6

SCORP/RELRP5/M003. 1

I I I I I I i i u vL• w w I , w i i.

C

Time, s

Fig. 7. Liquid level in the Steam generator.

2000 2400

LOFT: SBLOCR Experiment L3-6 SCORP/RELRP5/M003. 1 I S S S I

E

-J

w

a,

-j

c

(J

C

a

C

C

C

I I ,I

- ------- ----------- ----------- 4 ----------- ----------- -----------

"I

II

.1 1

-- ---- ----------- ------ ----------- I ------------...... L -----------

------ .----------- -------------- r----------

-- ---- I-----a-----4 --- --------- ----- 4- -- r- ------ i I

rLIL ' III

...... ....- a - a.. . . . a ..-.

a a a aI

aa a"aIa aaI *- - -4 -- - - - .- - - - - - - a aa -

a a a a

a' aa a a a I- -- - -- - a

a: a ' a•" a a a a a ' a a a a a a a a a

Legen

Xcnrve2 up=0.6

.... i ý. .4 . .... ....... +. . .

. . .. .. . .. 400 .... ... .800 .. .. . 1200 -- ----- I

Time, s

Fig. 8. Liquid level in the Upper plenum.

600 2000

C-5
LOFT: SBLOCR Experiment L3-6 SCORP/1RELRP5/MOO3. 1 * I I --- I

0,

0

-. j

U-

. .. . .. I . . . . .. I. .. . .. . . . . . .J . . . . . .t I . . . . .

*II !

----- -- --------------------- ---------- ------------ ----------- -----------

III I

--- -- --- -- - --- -- -- ---. L - --- -- ----1 - --- -- --- -J - - - - - -L - - - - - -

- L I - J

- I I I -

III I!

-------------------------- r---------- T ---------- n ----------- I -------------

* I *II I.

------------- ---------------- ------- ----------- ------

.. .. .. I .. . . . . r . . . . .T . . . . . e. . . . . .r . . . . .

-- -- ----------. ------ -------

/tI I I I I

4------------L ---------- I---------- -4 4-------------L --

-- ....--- '---- --- - - - - - - - - - I I

*' FR-PC-SBR ----

r .. .. . . . 4M. .. . . . . ........ 1

Time, s

Fig. 9. Break mass flow rate.

LOFT: SBLOCR Experiment L3-6

400

SCORP/RELRP5/M003. 1

0

N.

uUa,

a,

0.

In.

r r I g I

I I I I I I

I I I I I

I I I I

I I I I I I

I I g I I I

I I I I I I

I I I I I I

1~-----------------------------------I-----------------------------------------------------I.----------------

L----------------.J-----------------L----------------.L

I I I I

r

I I I I I I

I * * I

I I I I I I

I I I I

I I I I I

I I I I I

I I I I I I

I I I I

------------------------------------------------------------------------------ I I I I

I I I I I I I I

I I I I I

I I I I I I

I u I I I I I I

I I * I I I * I

Legend

XmfLow)605 OW-0.6

C1'.. 00.. ~. .............. IMo ,

Time, s

Fig. 10. HPIS mass flow rate.

C-6
V) CuLOFT: 5BLOCR Experiment L3-6 SCORP/RELRP5/M003. 1

L,

L

CL

E

I- a

CD

CD:

tn:

V):

In.

*1*.

- - - - - - - - - - - - - - - - - - - - - - -I -- - - - - 1 -- - - - -

- - - - - - T - - - - - - I - - - - - - I - - - - -

I afI

-- - - - - - - - - - - - - - - - - - - - - - - - - - - - - r

----- -4------------------------ ---------- --------------- ----- ------- ----------

Legend

TE-PC-002

tempf 10501000

400 800 1200 1600 2000 O00

Time, s

Fig. 11. Fluid temperature in the Intact loop hot leg.

L, LOFT: SBLOCR Experiment L3-6 SCORP/ReLRP5/M003. 1

Io

L

CD

CL

E

a)

40:

tn:

tn.

InCDI n

-- - - - - -- - - - - I - --I -----------

'Ron'. I

------ 4 1-----4r.-----4-----. ---- ----- --------

0,1

II

I

----- mmI ~iiI+---------

I I I

I I I

Ib 

-

-

- - -

I i * i

I I I I I ' " 6 Im 4 " o "4 4 -------

- - -I -- --- b

"400 1 800 "1200 ."100 '2000 2400

Time. s

Fig. 12. Fluid temperature in the reactor vessel Downcomer.

C-7
,, LOFT: SBLOCR Experiment L3-6 SCDAP/RELRP5/MOD3.1 ID.

to:

L

CL

E

CD

0n.

In.

• 4. 5 I | I * I lli S I 4

S SI I I

I *• ' *DI I

a ,* g I I

I I I I I

I I I

I I I

I I I

taa... I I

Legend

• TE-SH6-032

X httemp 23000311

I

t/n

L• I I I I I

.40 ........ 8b6 1200 ....... 1800 .2bOd . . . 0

Time, s

Fig. 13. Cladding temperature at 0.81 m above the core bottom.

LOFT: SBLOCR Experiment L3-6 SCORP/RELRP5/MO03.1

L

L

CL

E

IID

tn03.

In:

In.

%I.

tn.

I

*

I I I

a I i i i

Legend

--TE-6G14-045

X httemp 23000411

Iný

0* ......... 400 ' ... . 800 . . .. 1200 ....... 1600 ....... 2000

Time, s

Fig. 14. Cladding temperature at 1.14 m above the core bottom.

C-8
0)

0

-a

LLcn

a ILgec

a1 FR-PC-SODR

XMftov 153 euP-0.6

I *fLowjIS3 SupO0.76

a P ill aa

II S __ ___ ___ ___ __;

a °,,I. •

- - - - -- - - - I I A - --- -- - --- - --- ----- - - ---

- - -- i --- - --

(S%,

-b 0 2000

Time, s

Fig. S-1. Break mass flow rate (for 3 values of superheated coef.)

LOFT: SBLOCR Exoeriment L3-6 SCORP/RELRP5/M003. 1

(a

L.

cn

CL

T 7L

* Iaa a, I 

I aI

a a a PE-PCa a a a p 105

a a a 105

------------------- -------- A-----L-----.. ---------- ----

a a

aig a

a a

- a% . . . . . .. a-l . . . . . .

a a•

. .. . . . . . .a a.. •. . .

A.. . . . . . . . . . . . . . . . . . . .

a a

I a "•)o .. .. . . . . a•. . . . .•~ l . . . .2 o . . . .2 o

Tima

Fi.S2.Pesrei h hLlg(fr3vlaso upretdaof)

a a9

agend

.002

sup'.0.6)

(.up-0. 76)

(eupl.0
LOFT: SBLOCR Experiment L3-6 SCORP/RELRP5/MOD3.1

a'-

CL

L.

:3_

Ca

Cc

C0-

-- - - -- - - - - - a-- -- - - - - -a-- - - - - - - - - - -

-- -- - - -- - - - - -- - - - - - - - - -- - - - - - - - -

-- -- -- - - I -- - - - - -a-- - - - - -ý Z z - - - - -- - - - - - -

--- ---- - ---- - - - - - - - - - - - - - - - - - - -

-- -- -- - --- - - - - - -- - - - - - -I- -- - -- - - - - - -

Legend

-. PE-SGS-01 --

xp 525 Cmup-0.6)

p 525 ( up-0.76)

cp 525 (sf -1.0

i00

coef.)

-t

MT

Time, s

Fig. S-3. Pressure in the SG dome (for 3 values of superheated

LOFT: SBLOCP Experiment L3-6 SCDRP/RELRP5/MOD3. ]

CD

CD

CCD

I--

o a o

Ln InI

CV--------------I - I-------------- ini

CIt

'400.. *. .I .............. . L 60 .. . . M2

a I

SS F -I a10

a a

a I

. . .. . . . . . . . . & . . . . . .. a . . . .

in a

ig. a-.Fudtmeauei h eco eslDwemr

o a- a

Legend

Xtempf 206 sup-O.6)

tempf 206 sup-O.76

Otempt 206 sua-1.O)

,00
LOFT: SBLOCR Experiment L3-6 SCORP/RELRP5/M003. 1

0,

.1~

(n

(I,

0.

I-

~1

-4.-

I-

* I

I II I I II I

1 I 

I!II

* I I

I I I I I I Io I

I I I I

Legen

tni104 I....... . ........ s 8e

Fig. S-5. Mass error.

)0 .... 1200 " Time. s"1•tod '2060 "2400

LOFT: SBLOCR Experiment L3-6 SCORP/RELRP5/MO03.1

E

0)

c

a)

--------- 4----------------L--------- --.------- A -------- 4-----J-----------L -----

o----------4------------L-r---------- -----.------ i-------4---- r-----------L

-------- ---- ------ 4----- L-- -- -- -- - - ---------- -------. 44---- -----------

4---------------------------------- I------------ 4---------- 4 ----------- I-----------

----- ----------------------- ------------ --------- 4----------------L -----

C3---------.------------ j ----------- ----------. 4 ---------------.--------------- L.-------------

------------------------------ ----------- --------- ---------- ----------- -----------

* I

- I - -T

-T. ........... .......... AJ I............ d . . . .2t d .. d 

T me, I s

Fig. S-6. Density at the break tee.

Legend

rho 18401000

rhof 18401000

rhog 18401000

•00

C-11
LOFT: SBLOCR Exper Iment L3-6 SCORP/RELRPS1MOO3.1

7T-

+veLgJ 18401000

--= 

n ----------- 4 -- -- -- -- r.......... T ....... . - -- - - -

,

L.. -------. .. .. . LJm Lfl---------------. -----------------------.-------------------- -- --

a a Q3)

a. , 0-----------J---- ------------ L---------.--------- ---- -------- j ----------- L------

II

E I * a

a ar

II -------------------- It----------- ----------- ----------- I------------

I I

Fi.S7 Vlct at th bra tee

- CP------------------.-------- I--------- ---------- j ------- I------ L ----------

4 a- --

LI

II

O......... 46 46 Ih6 AM AM ....... 2400

Time, s

Fig. S-8. Velocity at the break tee.

LOFT: SBLOCRI Exper I ment L3-6 SCORP/RELRPS/MO3.1 r i IT IIaaiJ Legend

. .b ~vol dg 1 Ba01000

w aII EZZI

.3---- ---------- '-i--------------I'•-i- -'----'

oaSI ! I !

o a *----------4------------------4--------.---------I-------- ,-' 0 . . . . . . + . . . . . . . . . . . .,.. . . . . . o a a a a , , W a L! a LLa a a -a-a a a -l*a a -• 0 a a I a a

o a a a a a a a a a a a a a a a a a ' a *: a a a .. . ..j a. . . . a .. . . . . a.. . . . .a.. . . . . . .a . . . . . . *--------.3--------L-------I.--------------- o a a a a a _a a a a a

.----.......----- ..........-- --a------------+-------------. ----........ --..------

Time, s

Fig. S-8. Void fraction upstream the break.

C-12
NRC FORM 335 U.S. NUCLEAR REGULATORY COMMISSION 1. REPORT NUMBER

(2-89) (Assigned by NRC, Add Vol., Supp., Rev., NRCM 1102, and Addendum Numbers, If any.) 3201.3202 BIBLIOGRAPHIC DATA SHEET

(See instructions on the reverse) IA-0024

2. TITLE AND SUBTITLE

Application of RELAP5/MOD3.1 Code to the LOFT Test L3-6

3. DATE REPORT PUBLISHED

MONTH YEAR

February 1998

4. FIN OR GRANT NUMBER

W6238

5. AUTHOR(S) 6. TYPE OF REPORT

S. S. Pylev and V. L. Roginskaja Technical

7. PERIOD COVERED (Inclusive Dates)

8. PERFORMING ORGANIZATION - NAME AND ADDRESS (if NRC, provide Division, Office or Region, U.S. NuclearfRegulatoty Commission, and mailing address; if contractor,

provide name and mailing address.)

Division of Systems Technology

Office of Nuclear Regulatory Research

U. S. Nuclear Regulatory Commission

Washington, D.C. 20555-0001

9. SPONSORING ORGANIZATION - NAME AND ADDRESS (If NRC, type 'Same as above' if contractor, provide NRC Division, Office or Region, U.S. Nuclear Regulatory Commission,

and mailing address.)

Nuclear Safety Institute, Russian Research Center, "Kurchatov Institute,"

Kurchatov Square, 1, 123182, Moscow, RUSSIA

10. SUPPLEMENTARY NOTES

11. ABSTRACT (200 words or less)

A calculation of LOFT Experiment L3-6, a small-break equivalent to a 4-inch diameter rupture in the cold leg of a four-loop commercial pressurized water reactor, has been performed to help validate RELAP5/MOD3.1 for this application. The version

of the code to be used is SCDAP/RELAP5IMOD3.1.8d0. Three calculations were carried out in order to study the sensitivity to

change of the break nozzle superheated discharge coefficient. Conducted comparative analysis of the LOFT L3-6 experiment shows on the whole a reasonable agreement between calculated and measured data. Some discrepancies in the system

pressure do not distort a picture of the transient.

12. KEY WORDSIDESCRIPTORS (List words or phrases that will assist researchers in locating the report.) 13. AVAILABILITY STATEMENT

LOFT Experiment L3-6 unlimited

SCDAP/RELAP5/MOD3.1.8d0 14. SECURITY CLASSIFICATION

pressurized water reactor This Page)

small-break unclassified

cold leg

transient (Tis Report)

unclassified

15. NUMBER OF PAGES

16. PRICE

NRC FORM 335 (2-89)


Federal Recycling Program

NUREG/IA-0024 Ai'1L1CAI1ON Ok' tU~AP~i/MO1J3.1 CODEI '10 'IlE LOk-T ik;S l3W-b IFE~BRUARY 19985

UNITED STATES

NUCLEAR REGULATORY COMMISSION

WASHINGTON, DC 20555-0001

FIRST CLASS MAIL

POSTAGE AND FEES PAID

USNRC

PERMIT NO. G-67

OFFICIAL BUSINESS

PENALTY FOR PRIVATE USE, $300

I IAN1CI1R

4 '

TECHNOLOGY

SsYSTEM4S BR

CC20555