NUREG/LA-0031

Inteoational

Agreement Report

ICAP Assessment of RELAP5/MOD2,

Cycle 36.05 Against LOFT

Small Break Experiment L3-7

Prepared by

Euy-Joon Lee, Bud-Dong Chung, Hho-Jung Kim

Nuclear Safety Center

Korea Advanced Energy Research Institute

Office of Nuclear Regulatory Research

U.S. Nuclear Regulatory Commission

Washington, DC 20555

April 1990

Prepared as part of

The Agreement on Research Participation and Technical Exchange

under the International Thermal-Hydraulic Code Assessment

and Application Program (ICAP)

Published by

U.S. Nuclear Regulatory Commission
NOTICE

This report was prepared under an international cooperative

agreement for the exchange of technical information: Neither

the United States Government nor any agency thereof, or any of

their employees, makes any warranty, expressed or implied, or

assumes any legal liability or responsibility for any third party's

use, or the results of such use, of any information, apparatus product or process disclosed in this report, or represents that its use

by such third party would not infringe privately owned rights.

Available from

Superintendent of Documents

U.S. Government Printing Office

P.O. Box 37082

Washington, D.C. 20013-7082

and

National Technical Information Service

Springfield, VA 22161
NUREG/IA-0031

International

Agreement Report

ICAP Assessment of RELAP5/MOD2,

Cycle 36.05 Against LOFT

Small Break Experiment L3-7

Prepared by

Euy-Joon Lee, Bud-Dong Chung, Hho--Jung Kim

Nuclear Safety Center

Korea Advanced Energy Research Institute

Office of Nuclear Regulatory Research

U.S. Nuclear Regulatory Commission

Washington, DC 20555

April 1990

Prepared as part of

The Agreement on Research Participation and Technical Exchange

under the International Thermal-Hydraulic Code Assessment

and Application Program (ICAP)

Published by

U.S. Nuclear Regulatory Commission
NOTICE

This report is based on work performed under the sponsorship of The Korea

Advanced Energy Institute of Korea. The information in this report has been

provided to the USNRC under the terms of an information exchange agreement

between the United States and Korea*(Agreement on Thermal-Hydraulic Research

between the United States Nuclear Regulatory Commission and The Korea Advanced

Energy Research Institute, May 1, 1986). Korea has consented to the publication

of this report as a USNRC document in order that it may receive the widest

possible circulation among the reactor safety community. Neither the United

States Government nor Korea or any agency thereof, or any of their employees,

makes any warranty, expressed or implied, or assumes any legal liability of

responsibility for any third party's use, or the results of such use, or any

information, apparatus, product or process disclosed in this report or

represents that its use by such third party would not infringe privately

owned rights.
ICAP

ASSESSMENT OF RELAP5/MODZ, Cycle 36.05

AGAINST LOFT SMALL BREAK EXPERIMENT

L3-7

ABSTRACT

The LOFT small break (1 in-dia) experiment L3-7 has been analyzed using

the reactor thermal hydraulic analysis code RELAP5/MODZ, Cycle 36.05.

The base calculation (Case A) was completed and compared with the

experimental data. Three types of sensitivity studies (Cases B, C, and D)

were carried out to investigate the effects of (1) break discharge

coefficient Cd ,(2) pump two-phase difference multiplier and (3) High

Pressure Injection System (HPIS) capacity on major thermal and hydraulic

(T/H) parameters. A nodalization study (Case E) was conducted to assess the

phenomena with a simplified nodalization.

The results indicate that Cd of 0.9 and 0.1 fit to the single discharge

flow rate of Test L3-7 best among the tried cases. The pump two-phase

multiplier has little effects on the T/H parameters because of the low

discharge flow rate and the early pump coast down in this smaller size

SBLOCA. But HPIS capacity has a very strong influence on parameters such as

pressure, flow and temperature. It is also shown that a simplified

nodalization could accomodate the dominant T/H phenomena with the same degree

of code accuracy and efficiency.
Executive Summary

This report presents the assessment calculations using RELAP5/MOD2

Cycle 36.05, a frozen version of code, to predict the thermal/hydraulic

behavior under the conditions of Loss of Fluid Test (LOFT) SBLOCA Experiment

L3-7. The purpose of this assessment calculation is to determine whether the

code can predict the major phenomena of LOFT L3-7 and to contribute to the

generation of the body of information needed to determine the code

uncertainty. This calculation also represents a part of KAERI's contribution

to the USNRC international Code Assessment and Application Program (ICAP).

The key phenomena of SBLOCA, which depend upon the size and location of

the break, are (1) RCS hydraulics, (2) reactor vessel hydraulics, (3) effect

of RCP operation, (4) core status and heat transfer, and (5) steam generator

(S/G) heat transfer. The LOFT L3-7 [50 Wt] simulated 1 inch diameter cold

leg break of a typical 4-loop 1,000 NWe [3,000 MWt] commercial PWR, which

belongs to a relatively small SBLOCA group and represents the smallest break

experiment conducted in INEL. With respect to the hydraulic aspect in the

experiment, RCP coastdown was completed at 85 s ,and reflux boiling and loop

seal-clearing were not observed experimentally although natural circulation

started at 35 s. The core remained unexposed and not much depressurized.

With respect to the thermal aspect, the core transient decay heat curve was

based on the proposed 79 ANS standard. S/G feed was initiated at 75 s and

terminated at 1,800 s while S/G steam valve was closed at 40 s ,and later a

bleeding was initiated at 3,603 s.

- ii -
The base calculation (Case A) was completed and compared with the

experimental data. The code predicted the dominant phenomena of the L3-7

transient fairly well, except two-phase break flow and depressurization

during the period from 2,000 s to 6,000 s. This period of post-pump coast

-down belongs to the period of two-phase discharge and the transient without

HPIS operation. Thus, it was motivated to investigate the effect of the

following items on the major T/H parameters including the two-phase discharge

flow and the others. Three types of input sensitivity studies (Cases B,C and

D) were carried out to see the effect of (1) break discharge coefficient Cd,

(2) pump two-phase difference multiplier, and (3) HPIS capacities on the

major thermal and hydraulic parameters. A nodalization study (Case E) was

conducted to see if a simplified nodalizationcan catch the phenomena.

Results indicated that single phase Cd of 0.9 and 1.0 fit the test L3-7

best, which also lead to a careful implementation of two-phase critical flow

model. The pump two-phase multiplier has little effects on the T/H

parameters because of the low discharge flow and the early pump coastdown in

this smaller size SBLOCA. But, the primary system pressure, flow and

temperature were very sensitive to HPIS characteristics. For instance, the

changes in primary pressure of 1 HPa and the cladding temperature of about 5

K were resulted by a 0.3 L/s change in HPIS flow. Besides the simpler

nodalization was able to catch the dominant T/H phenomena but did not reduce

the computer time, i.e. same grind time of 1.67. This assessment report

concludes that RELAP5/MOD2 Cycle 36.05 can predict the major phenomena and

T/H parameters of LOFT SBLOCA Test L3-7 failry well.

- iii -
ACKNOWLEDGEMENTS

This report was completed under the sponsorship of the Korean Ministry of

Science and Technology. Dr. Sang Hoon Lee, President of the Korea Nuclear

Safety Center, contributed significantly to the project administration.

Authors expressed a great appreciation to Professors E. C. Lee, C. S.

Kang in Seoul National University and Professors M. H. Chun, S. H. Chang

in Korea Advanced Institute of Science and Technology for their in-depth

technical reviews in Korea.

Another appreciation should be expressed to Mrs. Dick Schultz, Rich

Riemke and Bob Hanson in EG&G, Idaho for their kind friendship and technical

advices when author stayed in INEL. Dr. Aksan of Paul Scherrer Institute in

Switzerland was very helpful for code update work and technical comments

during his visit in Korea.

Final thank goes to Dr. Young Seok Bang for technical discussions and

Mr. Jong Han Park for preparing data plot.

- iv -
LIST OF CONTENTS

ABSTRACT ........ ........................... . i

EXECUTIVE SUMRY ............................ .. ii

ACKNOWLEDGMENT . .. .. .. .. .. .. .. .. .. .. .. . .. iv

TABLE OF CONTENTS . . . . . . . . . . . . . . . . . . ....... V

1 INTRODUCTION . . . . . . . . . .............. 1

2 FACILITY AND TEST .............. .............. 3

2.1 LOFT .............................. 3 2.2 L3-7 . . . . . . . . . . . . . . . . . . . . . . . . . . . . 3

3 CODE AND MODELING ....... ........................ 5

3.1 CODE ........... . . . . ............. 5

3.2 MODELLING ....... .......................... 5

3.2.1 Break .................................. 5

3.2.2 Pump . . . ................... 6

3.2.3 HPIS . ......................... 6

3.2.4 Nodalization .... ..................... 7

4. BASE CALCULATION (Case A) ................. ........ 8

5. SENSITIVITY AND NODALIZATION STUDY . . . . . . ........ 11

5.1 Break Discharge Coefficient, Cd (Case B) ............. 11

5.2 Pump Two-phase Multiplier (Case C) ................ 12

5.3 HPIS Capacity (Case D) ......................... 13

5.4 Nodalization (Case E) .......................... 13

6. RUN STATISTICS ....... ......................... 14

7. CONCLUSION ............................. 15

REFERENCE ........ ............................. 18

TABLE

1. Initial Conditions for Experiment L3-7 and Calculation . . . 20

2. Sequence of Events for Experiment L3-7 and Calculation . . . 21

3. Assessment Data and Measurement Uncertainties. . ...... 22

4. Scope of Sensitivity and Nodalization Study ........... 23

FIGURES

1. LOFT System Configuration ...... .................. 24

2. RELAP5 Nodalization for LOFT Test L3-7 ............... 25

APPENDICES

A. Input Listing (Case A) ...... ................... 26

B. Data Comparison Plots ...... ................... 109
-I
1. INTRODUCTION

The International Code Assessment and Applications Program (ICAP) has

been conducted by fourteen nations and multinational organizations under the

auspices of the USNRC[1]. For the PWR analysis, the USNRC selected two Best

Estimate (BE) codes: RELAP5/MOD2 and TRAC/PF1/MOD1[2]. The goal of the

program is to assess the prediction capabilities of the current BE thermal

hydraulic(T/H) codes utilizing the available facility test and plant data.

At present the ICAP activities in Korea help to quantify uncertainties in the

codes so that the codes may be used for licensing purposes.

Korean contributions to ICAP have been made through the RELAP5/MOD2

calculations against ten experiments and five plant data. Six of the

assessments will be performed with LOFT Integral Effect Test (IET) data and

two with Semiscale IET data. Two Separate Effect Test (SET) data for

critical flow and condensation will also be used to assess the code

RELAP5/MOD2.

The RELAP5/MODZ/cycle 36.04 [3] was implemented in 1986 on KAERI CDC

170-875 computer. The code was updated to cycle 36.05 based on the update

file obtained from Idaho National Engineering Laboratory (INEL) in November

1987. The objective was to assess the RELAP5/MOD2/Cycle 36.05 against the

LOFT small break experiment L3-7. The assessment was performed by comparing

the major calculated parameters with the experimental data as-was done in the

previous developmental assessment [4]. Thus, this study addressed to the

prediction capability of the code for the LOFT SBLOCT. test L3-7. The

capability and user guidelines of the specific code was decided based on the

following steps:

-1-
(1) Base calculation, (2) Sensitivity study (Input and Model), (3)

Nodalization (modelling) study.

A brief description of the LOFT facility and L3-7 test is contained in

Section 2, and Section 3 presents the features of the RELAP5/MODZ to be

assessed. Section 4 discusses the results of the base calculation; and, the

motivation for the sensitivity and nodalization study and results are

included in Section 5. The code efficiency is evaluated in Section 6 through

run statistics. The conclusions drawn from this study are given in Section

7.

- 2-
2. FACILITY AND TEST

2.1 LOFT

The LOFT Integral Effect Test (IET) facility has been designed to

simulate the major components and system responses of a commercial, four-loop

PWR [1000 1We] [5]. The LOFT facility as in Figure 1 consists of:(l) a

reactor vessel with a nuclear core, (2) an intact loop (a steam generator and

two primary pumps parallel),.(3) a broken loop (simulated pump and steam

generator and two quick opening valves), (4) the blow down suppression system

and (5) the emergency core coolant (ECC) system (two LPIS, two HPIS pumps and

two accumulators). To relate LOFT to a PWR, the test facility is designed as

follows:

(1) the same linear heat generation rate of a large reactor is used, (2) LOFT

powers are scaled according to component volumes (1:60), (3) flow areas are

scaled to provide the identical volume ratio to large reactor values, (4)

pipe break areas are set based on the ratio of core volume, and (5) pressure,

temperature, and mass flux are attempted to be identical to large reactor

values.

2.2 L3-7

For Experiment L3-7, the LOFT system was configured to represent a

postulated small break, equivalent to one inch-diameter rupture, in the cold

leg of a commercial PWR. One classifies as SBLOCA if the relevant break

diameter is less than 10 inch and the break belongs to the lower end of the

SBLOCA range when the diameter is less than 1 inch which represents a leakage

from a valve or joint [6].

-3-
The objective of Experiment L3-7 is to investigate how the HPIS and the

primary system behave against such a small break accident(1 in-dia). C.E.

McCreery summarized the test L3-7 in the quick look report[7). Based on this

report, at the time of experiment initiation, the LOFT reactor was operating;

(1) at a maximum linear heat generation rate 52.8 KW/m and a power of 49 NW,

which is about 98% of the LOFT rated power of 50 MW; and (2) at temperatures

in the RCS intact loop of 576 K and 556 K in the hot and cold legs,

respectively, and a pressure of 14.9 MPa in the hot leg. These measurement

initial conditions of the experiment are in Table 1 along with the calculated

values of steady-state calclulation. The sequence of events is summarized in

Table 2, where the measured and calculated times are compared.

-4-
3. CODE AND MODELING

3.1 CODE

The RELAP5/MODZ code [3] has been developed for best-estimate transient

simulation of PWR's and associated systems. The code is based on a

non-homogeneous and non-equilibrium model for one dimensional, two phase

system that is solved by a fast, partially implicit numerical scheme to

permit economical evaluation of system transients. ICAP RELAP5 newsletter

[8], October 1987, summarized the key features of RELAP5/MOD2 Cycle 36.05 and

the changes from the previous Cycles 36.04.

3.2 MODELLING

3.2.1 Break

In the experiment, small break orifice of 4 mn-diameter simulates 25.4

mm (1 in-dia) SBLOCA of a commercial PWR. Critical flow models calculate the

break mass flow rate based on the enthalpy and other necessary information of

the front volume[9]. The break is represented by junction 365 ( quick

opening valve) in the code,which is modelled with a trip valve. The valve is

coded as centrally located (V = 0), abrupt area change (a = 1),

non-homogeneous option(h = 0), and choking option (c = 0) with both singleand two-phase discharge coefficients of 1.0 respectively as the base case.

.- 5 -
3.Z.2 Pump

The pump model of RELAP5 is based on RELAP4/MOD6 model. The pump

related subroutines such as PUMP and PUMPZ basically calculate the head and

torqueof the new time step using the speed and the information of the

previous time step. The pumps are normally degraded in two-phase flow

conditions. The pump performance in two-phase flow conditions are explained

in the following equations:

H = Hi - MH(A)(H1-H2)

T = TI - MT(A)(TI-TZ)

where HI and H2 are single- and two-phase head difference data from

homologous curves ,respectively, MH(A) void dependent two-phase head

multiplier, Ti and T2 are single- and two-phase.torque difference data from

homologous curves, respectively, and MT(A) void dependent two-phase torque

multiplier.

The input required for pump modeling are (1) static geometric data, (2)

initial conditions, (3) two-phase torque and head data and (4) pump dynamic

data. One of the issue here is whether the system relevant to Test L3-7 will

be degraded due to the pump degradation in two-phase.

3.2.3 HPIS

The HPIS in the LOFT is composed of serially connected two pumps. The

HPIS is instated by a low pressure signal and the flow is injected through

the cold leg into the vessel according to the characteristic curve of head

and flow in the combined system. The head and flow diagram is estimated from

the pump data and validated from the experiment. The HPIS is modelled as a

time-dependent junction and instated when primary loop pressure is lower than

the set point, 13.159 MPa. HPIS flow characteristics also affect the primary

loop pressure and the discharge flow.

-6-
3.2.4 Nodalization

The RELAP5/HODZ nodalization diagram of the base case is shown in Figure

2. The nodalization has 130 volumes, 136 junctions, and 137 heat structures.

This includes 1 more control volume and I more flow junction than the one

used for the MOD2 Cycle 7 developmental assessment during 1983 as indicated

in Reference [4]. E. J. Kee initially developed the base LOFT input deck

for RELAP5/MOD2[1O]. He also used RELAP5/MOD1 to predict the L3-7 behavior

as a pre-test simulation[11]. W. H. Grush did post-test calculation in

1981 [12]. The decks L37SS and L37TRAN were provided by the INEL in 1986.

The pump relative speed,-word 1 of case CCC0308, was corrected and the

accumulator was modelled as a component instead of a volume.

-7-
4. THE BASE CASE CALCULATION (Case A)

The input listing for the base calclulation, Case A, is attached in

Appendix A. L37SS of steady state and L37BASE of transient calculation ran

successfully on the KAERI CDC 170-875. The major parameters of concern are

break flow rate, HPIS flow rate, upper plenum pressure, velocity and density

of intact loop hot leg (ILHL), density of broken loop cold leg (BLCL), steam

dome pressure, cladding temperature, and accumulator level. The numerical

performance of the code is evaluated in terms of CPU and DT vs. simulated

time and grind time. The assessment parameters and their measurement

uncertainties are summarized in Table 3.

Figure B.I.1 of Appendix B shows the break mass flow rate. The mass

flow rate at the break orifice was compared with the measured flow at

FR-BL-111 [4]. The code underpredicted the initial peak by 0.5 kg/s. Just

after the initiation of break, the experimental peak was about 1.9 kg/s while

the code still underpredicted as 1.4 kg/s although there was the uncertainty

of measurement ( about 0.2 kg/s ). Single-phase Cd 1.0 and two-phase Cd 1.0

gave higher mean single-phase break flow and lower two-phase discharge flow.

After 350 s, two-phase discharge flow started and the code underpredicted the

flow by 0.2 kg/s. A sensitivity study with Cd has been performed to match

the L3-7 measured discharge flow.

Figure B.I.2 shows the volumetric flow rate of the HPIS. The flow rate

was compared with the measured at FT-P128-104, intact loop cold leg to

vessel. The time dependent flow and pressure provided feedback to the

boundary condition for modeling the HPIS. Figure B.I.2 indicated that the

code closely followed the sequence and data of the experiment. The HPIS was

injected at 70 s and terminated at 1820 s. The HPIS was reinstated at 6000

s. The measured and calculated sequences are summarized in Table 2.

-8-
Figure B.I.3 shows the upper plenum pressure in the reactor vessel. The

upper plenum pressure, affected by the combined action of break and HPIS

flow, was compared with the pressure measured at PE-1UP-OO1A. The code

showed earlier two-phase depressurization than the test and underpredicted

the pressure by 1 !Pa (0.2 MPa measurement uncertainty) at 4000 s. The code

predicted that depressurization occurred faster. A sensitivity study with

higher and lower HPIS flows was performed to see its effect on key T/H

parameters including the primary pressure.

Figure B.I.4 shows the liquid and vapor velocities in the ILHL. The

calculated velocity at volume 112 was compared with the measured at

PE-PC-002A. The result indicated that the two-phase natural circulation

started at 85 s and terminated after repressurized. The code predicted the

velocities little higher but within the acceptable range of the measurement

uncertainty (0.63 m/s). The effect of pump two-phase multiplier changes on

this primary loop velocities was studied.

Figure B.I.5 shows the density in the ILHL, which was compared with the

measured at DE-PC-002B (100 kg/m3 uncertainty). The code followed the

experiment fairly well but underpredicted the density upto 100 kg/m3 when the

HPIS is off. The code again closely followed the experimental data after the

HPIS was reinstated at 6000 s.

Figure B.I.6 shows the density in the BLCL. The code experienced the

low density as in the experiment when the HPIS is not on line. The density

variation surely can affect the break flow strongly after 2000 s; and, thus,

the discharge flow is supposed to be drastically changed. However, no

experimental data of the break flow after 1800 s is available for LOFT Test

L3-7.

-9-
Figure B.I.7 shows the steam dome pressure of the steam generator. The

calculated pressure was compared with the measured at PE-SGS-001 (0.012 MPa

uncertainty). The predicted peak pressure at 35 s was 6.8 MPa. The code

also showed the repressurization phenomena after the secondary coolant system

(SCS) auxiliary feed was terminated at 1800 s and the depressurization when

the SCS steam bleed was initiated at 3600 s.

Figure B.I.8 shows the cladding temperature in the core. The calculated

temperature at fuel assembly 5 row F column 9 at 1.14 m above the bottom of

the fuel rod (TE-5F9-045) and the measured temperature HTIEMP 23003 were

compared. The measurement was made with an uncertainty of 3.0 K. The code

underpredicted the temperature upto 10 K at 4000 s, which was probably caused

by the overestimated flow through the primary loop and the core. It should

be noted that no later core heat-up was shown for this small size (1 in-dia)

SBLOCA since no core uncovery had occurred.

Figure B.I.9 shows the level in the accumulator, which is added as an

additional component in this calculation. The accumulator water level of

control variable 4 was compared with LIT-P120-044. The code predicted that

the accumulator was turned on about 1000 s earlier than measurement because

the code underpredicted the primary system pressure which activated the

accumulator. A code problem was observed when the accumulator became empty.

The problem was resolved by adding a trip to turn the accumulator off when it

became empty.

- 10 -
5. SENSITIVITY AND NODALIZATION STUDY

The base code fairly well predicted the dominant phenomena of the L3-7

transient except for two-phase discharge flow and the system depressurization

during the period from 2OOs to 6000s. This period belongs to post-pump

coast-down, two-phase discharge, and the transient without HPIS operation.

Thus, it was motivated to investigate the effect of the following items on

major T/H parameters including the primary system pressure. The items used

for the sensitivity study are: break discharge coefficients (single- and

two-phase), pump two-phase head and torque multiplier, HPIS flow and head

characteristics, and simpler nodalization. The scope of the sensitivity and

nodalization study is explicitly summarized in Table 4.

5.1 BREAK DISCHARGE COEFFICIENT (Case B)

As in the scope of sensitivity and nodalization study of Table 4, six

different combinations of break discharge coefficients were used to see the

effects of Cd on especially discharge flow. Results from three cases, which

are (1) 1.0 and 1.0, (2) 1.2 and 1.0 and (3) 0.9 and 0.9 in single- and

two-phase break discharge coefficents, are shown in Figure B.11.2 to B.II.9.

Figure B.II.1 shows the effect of Cd on discharge flow. The variation

of single-phase Cd's strongly affects the peak flow rate. Cd M.Z (Case B.1)

gave 1.7Kg/s while Cd 1.0 allowed 1.4Kg/s for the peak value. All Cases B.3

through B.5 with several two-phase Cd's underestimated the flows. Case B.2

gave water property error at 61.2 s because of the artificially high pressure

generated by the code when Cd is 0.8.

- 11 -
Several cases with single-phase and two-phase Cd's were tested. Among

them, Cd of 0.9 (Case B.6) is recommended to fit the mean values of the

single phase flows. The results indicated that tuning of two phase Cd's

(0.8, 1.0, 1.2 and 1.4) was not successful for predicting the two-phase

discharge flow because of the lower flow rate (<0.8 kg/s). The code

underestimated the two-phase discharge flow till 1,800 s. This study shows

that the effect on the single-phase flow propagates into the two-phase

discharge flow. It is suggested that a SET study on two phase discharge flow

be conducted. The effects of Cd's on the other key T/H parameters are

illustrated in Figure B.II series.

5.2 PUMP TWO-PHASE T/H MULTIPLIER (Case C)

Two-phase torque and head multiplier data for the base case (Case A.0)

came from LOFT test L3-6 and a suggestion was made to use a greater

two-phase degradation factor (Case C.0 ) (13]. Figure B.III.1 shows the

input changes in two-phase head multiplier and two-phase torque. Results

from this change were obtained and compared with the base case in Figure

B.III.2 to 9. Figure B.III.1 shows the changes of two phase head multipliers

and the major change occurs at the mid range of void fraction. The head

multiplier of the base case at void fraction 0.5 is 0.6 while the one for

Case C is about 0.95 assuming about 40 % more two-phase degradation.

Results showed that basically no major differences were shown because

the pump coast-down was completed early at 56.2 s ;and, therefore, the

two-phase degradation had little effect on the major T/H parameters.

-12-
5.3 HPIS (Case D)

Figure B.IV.l shows the higher and lower flow cases than the nominal

base case. Figure B.IV.3 shows the calculated and measured HPIS flow rates

as a function of time. A lower HPIS gave less discharge flowrate as shown in

Figure B.IV.2. As in Figure B.I.3, the pressure became below 7 MPa after

1,300 sec and the was activated at 6,000 sec because of the set pressure 4

lPa. As far as HPSI flow sensitivity concerned, a higher and a lower flow

rates of HPSI were assumed as in Figure B.IV.l. It shows that the higher

flow case gives 5.8 kg/s and the lower case does 0.1 kg/s at 7 IPa while the

base case gives 3.8 kg/s.

A higher HPIS flow lead to a more rapid depressurization in steam

generator secondary side (Figure B.IV.8) and cooled fuel rods more quickly

(Figure B.IV.9). From this comparative study, the T/H parameter changes due

to HPIS flow changes could be estimated for LOFT Test L3-7. Figure B.IV.9

shows that, when the HPIS flow is reduced by 0.3 U/s at 1000 sec, the

cladding temperature becomes higher by 5 K at most. Therefore, a lower ECCS

HPIS flow seems to be still acceptable for this L3-7 type SBLOCA.

5.4 NODALIZATION (Case E)

The objective of this nodalization study was to ensure the code

capability to capture the key L3-7 phenomena with a simplified nodalization

as in Table 4. The break flow was predicted well as in the case A.O (Figure

B.V.1). The pressure (Figure B.V.3) and the velocity (Figure B.V.4) of the

primary loop were fairly well predicted. As in Figure B.V.5 and 6, the

densities started to decrease about 1000 s earlier than the base case.

Figure B.V.7, 8 and 9 show that the code with a simplified noding can predict

the key T/H parameters well as the base code. And the same numeric

efficiency was also obtained.

- 13 -
6. RUN STATISTICS

The input models for the base case (Case A) and the simpler nodalization

(Case E) of LOFT L3-7 contained the following number of nodes:

Case A Case E

Volumes 130 123

Junctions 136 132

Heat Structures 137 129

Figure B.VI.1O compares CPU vs Simulated time. Figure B.VI.11 compares DT

vs simulated time. The ratio of CPU vs simulated time came out to be about

5000/10000 (0.5) for both cases A and E. During the transient calculation

the following computing resources were used:

Case A Case E

Computer time CPU (s) 5521 5295

Number of time step DT (s) 25519 25689

Number of Volumes C 130 123

Transient real time RT 10000 9489

The calculated grind time (code efficiency factor) for 9000 s is

CPU * 1000 (5521) x 1000

= 1.64 for case A

C * DT (130) (24801)

(5086) x 1000

= 1.67 for case E

(123) (24833)

CPU benefit as expected with a simpler nodalization was not obtained.

The computer used was a cyber 170-815

- 14 -
7. CONCLUSION

REALP5/MOD2 Cycle 36.05 has been assessed using the LOFT small break

experiment L3-7. Five major calculations were carried out: one base

calculation (Case A) and four sensitivity calculations with changes on break

discharge coefficient (Case B), pump two-phase multiplier (Case C), HPIS

capacities (Case D), and simpler nodalization (Case E).

The key phenomena any assessor must consider in SBLOCA over the duration

of the transient are (1) RCS hydraulics, (2) reactor vessel hydraulics, (3)

effect of RCP operation, (4) core status and heat transfer ,and (5) S/I heat

transfer. The assessor also should consider the size and location of the

break. The type of SBLOCA should be catagorized first based on the principle

in Section 2.2. SBLOCA Test L3-7 belongs to a relatively small size SBLOCA

because the break diameter is just one inch. Thus, the primary pressure

varied very slowly ,and reflux boiling and loop seal/clearing were not

observed although two-phase natural circulation started at 35 s. The core

remained unexposed over the transient. RCP pump coast-down was completed at

early 85 s;therefore, it could not affect the system T/H parameters much in

such a long transient. The core decay heat was digitized from experimental

data. S/G feed was terminated at 1,800 s whereas steam bleeding was

initiated at 3,603 s. A reversed heat transfer to primary side in S/G was

not observed.

In the steady-state calculation, the initial experimental data could be

fairly well reproduced as in Table I. But there exist a relatively large

discrepancies in initial steam dome pressure.

The measured data with uncertainty band were compared with the

calculated values from the base case A. The plots for this case are shown in

- 15 -
plot I's of Appendix B. According to the plot B.I.1, two-phase discharge

flow after 400 s were not properly predicted probably due to poor

imlementation of two-phase critical flow model. The primary system pressure

was underestimated by 1 MPa when HPIS was off, which would not be readily

explained. A earlier study showed that the deficiency was related to

existing four assumptions to calculate two-phase sound speeds [14). R. R.

Schultz found that a big transition in the sound speed occurred between void

fractions of 0.0 and approximately 0.1, which is very relevant to Test L3-7.

The current IOD2 did not include the high sound speed upto 1,830 m/s at the

void close to 0.0. However, the other major T/H parameters were still

predicted fairly well except the mid-range depressurization and the two-phase

discharge flow.

Plot II's in Appendix B include the results for the Case B: break

discharge coefficient sensitivity study. Several break discharge

coefficients (Cd) were tested in the range between 0.8 and 1.2. And 0.9 was

found to be the most suitable for both single- and two-phase discharge flows.

The code consistently tends consistently to underestimate the two-phase

discharge flow, which was actually demonstrated in the test cases with

0.8,1.0,1.2 and 1.4. Thus, it is desirable to conduct a two-phase choked

flow model assessment with a SET to investigate this underestimation.

Plot III's in Appendix B include the results for the Case C: pump twophase multiplier sensitivity study. The change of the pump two-phase torque

and head multiplier did not affect the major T/H parameters because

the complete pump coast down occurred very early in time at 85 s and no other

effects were present afterwards in such a long transient.

- 16 -
Plot IV's in Appendix C include the results 

sensitivity study. 

for the Case D: HPIS curve The flow capacity of the HPIS showed strong influence on certain T/H parameters such as pressures, flowrates and PCT. The higher HPIS flow is, the the higher loop flow rate, and thus, the less obtained, even the PCT is though the discharge flow increases. 

breaks, the designed 

For this size of small HPIS capacity is more than needed.

Plot V's in Appendix D include the results 

sensitivity for the Case E: nodalization study. The simplified nodalization was almost base case in predicting as good as the the major T/H phenomena. The numeric i.e., grind efficiency, time was found to be 1.66, which was the same Additional in both cases. simplification study is recommended to find the minimum volumes and junctions required which simulate the LOFT Test L3-7.

- 17 -
REFERENCE

1. Guidelines and Procedures for the International Code Assessment and

Applications Program, NUREG-1271, April 1987.

2. U.S. Regulatory commission conpendium of ECCS Research for Realistic

LOCA Analysis, NUREG-1230, May 1987.

3. V.H. Ranson et al., RELAP5/MOD2 Code Manual Volumel: Code Structure,

Systems Models, and Solution Methods and Volume 2: Users Guide and Input

Requirements, NUREG/CR-4312, March 1987.

4. V.H. Ranson et al., RELAP5/MOD2 Code Manual Volume 3: Developmental

Assessment Problems, EGG-TFM-7952, December 1987.

5. D.L. Gillas and J.L. Carpenter, Experiment Data Report for LOFT Nuclear

Small Break Experiment L3-7, NUREG/CR-1570, EGG-2049, August 1980.

6. W.E. Burchill, Physical phenomena of a small-Break Loss-of-Coolant

Accident in a PWR, pp525-536, Nuclear Safety, Vol. 23, No.5,

September-October 1982.

7. C.E. McCreery, Quick-Look Report on LOFT Nuclear Experiment L3-7,

EGG-LOFT-5192, June 1980.

8. ICAP RELAP5 Newsletter, NUREG/BR-0103, Vol.3 No4, October 1987.

- 18 -
9. R.A. Dimenna et al., RELAP5/MOD2 Models and Correlations, NUREG/CR-5194,

August 1988.

10. E.J. Kee et al., Base Input for LOFT RELAP5 Calculations,

EGG-LOFT-5199, July 1980.

11. E.J. Kee et al., Best Estimate Prediction for LOFT Nuclear Experiment

L3-7, EGG-LOFT-5172, June 1980.

12. W.H. Grush and G.E. McCreery, Posttest Analysis of Loss-of-Fluid

Tests L3-2 and L3-7, EGG-LOFT-5632, October 1981.

13. John Eriksson, ICAP Assessment of RELAP5/MOD2, Cycle 36.04 Against LOFT

Small Break Experiment L3-5, STUDSVIK/NP-87/63, June 1987.

14. R. R. Schultz, Summary Notes on Sound Speed Used for Two-phase Critical

Flow, December 1988.

- 19 -
Table 1. Initial Conditions for Experiment L3-7 and Calculation

Parameter Measured Calculated

Primary Coolant System

Mass flow rate (Kg/s) 481.30 481.26

Hot leg pressure (MPa) 14.90 14.95

Cold leg temperature (K) 556.00 555.81

Hot leg temperature (K) 576.10 574.74

Reactor Vessel

Power level (MW) 49.00 48.91

Pressurizer

Water temperature (K) 615.00 612.33

Pressure (lPa) 14.90 14.89

Liquid level (m) 1.10 1.09

Broken Loop

Cold leg temperature near

reactor vessel (K) 557.70 554.82

Hot leg temperature Near

reactor vessel (K) 561.40 555.63

Steam Generator Secondary Side

Water level (m) 0.25 0.25

Water temperature (K) 544.0 540.1

Pressure (tMPs) 5.576 5.246

Mass flow rate (Kg/s) 28.000 24.982

Accumulator A

Pressure (MPa) 4.31 4.31

Temperature (K) 306.60 300.25

-20-
Table 2. Sequence of Events for Experiment W3-7 and Calculation

Event Time (sec)

Ieasured ICalculated

LOCE initiated 0

Reactor scrammed 36.0

Control rods reached bottom 38.1 33.5

Primary coolant pumps tripped 39.3 33.79

Primary coolant pumps coastdown completed 56.2 70.0

Core natural circulation first indicated 60.8 85.0

HPIS injection initiated 65.6 70.625

SCS auxiliary feed initiated 75 100.0

Pressurizer emptied 264 182.187

Upper plenum reached saturation pressure 382 350

End of subcooled break flow 1037 1550

SCS auxiliary initial feed terminated 1800

HPIS flow terminated 1805.3 1820

SCS steam bleed initiated 3603

HPIS flow reinstated 5974.2 5974.063

Accumulator injection initiated 6028 5581.187

Break isolated 7302.0

Primary system fluid became subcooled 7915

Pressurizer refill initiated 8680

pressurizer refill terminated 19900

Experiment Completed 29500

- 21 -
Table 3. Assessment Data and Measurement Uncertainties

Component Parameter Prediction Measurement Uncertainty EDR (5]

Identifier Figure

BREAK Mass Flow MFLOWJ FR-BL-111 ±10% of 5U-1

Rate 36500 Reading

ECC Volume Flow MFLOWJ FT-P128-104 ±0.02 L/S 511-6

Rate 64000

VESSEL Upper Plenum P25001 PE-IUP-lAI ±0.2 Mpa 5M-43

pressure

Primary

Loop

I.L.H.L Velocity VELFJ11201 FE-PC-002 ±0.63 M/S 5U-5

Density RHO10001 DE-PC-O02 ±100 Kg/m 5U-4

B.L.C.L Density RH034501 DE-BL-001 ±76 Kg/m3 5U-2

Secondary

Loop Pressure P53001 PE-SGS-001 ±0.012 Mpa 5U-16

(steam Dome)

CORE Cladding HTTEMP TE-5E8-34.5 ±3 K 5U-18

Temp 230000310 -5F9-45

ACCUMULATOR Level CNTRLVAR 4 LIT-PI20-044 ±5% 5L-4

RELAP5 CPU

UT

I.L.H.L. Intact Loop Hot Leg

B.L.C.L. Broken Loop Cold Leg

EDR Experiment Data Report [5]

- 22 -
Table 4. Scope of Sensitivity and Nodalization Study

Break Cd Pump APIS Nodalization

1-&Z-Phase 2-phase Factor Flow

Base

(Case A)

Case B.1

2

3

4

5

6

Case C

Case D.1

D.2

Case E

1.0 1.0

1.20

0.80

1.00

1.00

1.00

0.90

1.00

1.00

1.40

1.20

0.80

0.90

L3-6 [12]

Test

'I

it

it

I!

Chen [13]

L3-6

nominal

[12]

it

I,

I?

I,

'I

It

Higher

Lower

Nominal

1.00 1.00

1.00 1.00

1.00 1.00

1.00 1.00

Used in INEL 83

MOD2 Developmental

Assessment [4]

II

it

It

Simpler

Nodalization

Volumes

100&105-IOO(ILHL)

172&175-+172(ILCL)

140&145-445

(Pump Outlet)

240&245-+240

(Upper Core)

300&305-*300(BLHL)

335&340-*335(BLCL)

[ ] Reference number

ILHL Intact loop hot leg ILCL Intact loop cold leg

BLHL Broken loop hot leg

BLCL Broken loop cold leg

-23-
Irntact* loop Broken.- loop

Fig. I LOFr major components.

LOFT System Configuration

-2A4-
420

515 415

3.15

AM TMJ(

srATtJ¶

?g" R-, I P21 ý ,.0

20

(-9-

__INTACT LOCP •dL tO I

PLTW

Nodalization for LOFT L3-7

CV4X

NmowtW

BRýLOOP'

JEN00562
Appendix 'A Input Listings

- Steady-state deck (L37SS)

-. Transient deck (L37BASE)

-26-
/JOB

L37SRI,T2000.

/USER

ATIACH,STH2XT,REL36KX.

PURGE,L3SRPl/NA.

DEFINE, RSTPLT=L3SRPI.

FILE,RSTPLT,SBF=NO.

RFL, CM=350000,EC=200.

REDUCE(-)

REL36KX,,*PL=5O000.

/EOR

=LOFT L3-7 POST TEST ANALYSIS.

* INITIAL CONDITIONS

* CORE POWER = 48.9 1W

* PCS FLOW = 481.3 KG/S

* THOT = 576.1 K

* TCOLD = 556.0 K ,

0000100 NEW STJIY-ST

0000101 RUN

0000105 5.0 10.0

0000110 NITROGEN

* TIME STEP CONTROL CARDS

* END TIME MIN DT MAX DT OPTN MNR MiR RST

0000201 100.0 I.E-6 0.25 11 4 100 100

*CARD ABOVE IS A REPLACEMENT CARD OF THE ONE BELOW

* 0000201 200.0 I.E-6 0.25 2 4 100 100

* MINOR EDIT VARIABLES

* STEADY STATE PLOT REQUESTS

*----------1 P-----1------1------1-- -1- - 1-

0000301 P 250010000

0000302 P 530010000

0000303 TEMPF 250010000

0000304 TEMPF 185010000 0000305 TENPF 515010000

0000306 MFLOWJ 540000000

0000307 MFLOWJ 985000000

0000308 MFLOWJ 995000000

0000309 CNTRLVAR 1

0000310 CNTRLVAR 2

0000311 MFLOWJ 566000000

0000312 CNTRLVVAR 910

0000313 MFLOWJ 100010000

0000314 P 420010000

0000315 VOIDG 500010000

* TEMPERATURES

0000316 SATTEMP 345010000 * TE-BL-lA,lB,1C

0000317 SATTEMP 310010000 * TE-BL-2A,2B,2C

0000318 SAITEMP 100010000 * TE-PC-ZA, 2B, 2C

0000319 SATTEMP 180010000 * TE-PC-1

- 27 -
0000320

0000321

0000322

0000323

0000324

0000325

0000326

0000327

0000328

0000329

0000330

0000331

0000332

0000333

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

SATTEMP

114010000

116010000

510030000

415040000

415030000

205010000

210010000

210050000

210060000

215010000

220010000

250010000

251010000

255010000

*

*

*

*

*

*

*

*

*

*

*

*

*

*

TE-SG-1

TE-SG-2

TE-SG-3

TE-139-19

TE-139-20

TE-IST-1 / TE-2ST-1

TE-1ST-2 / TE-2ST-2

TE-1ST-6 / TE-2ST-6

TE-1ST-7 / TE-2ST-7

TE-iST-O / TE-2ST-10

TE-lST-13 / TE-2ST-13

TE-IuP-6

TE-2UP-4

TE-1UP-3

* DENSITIES

0000334 RHO

0000335 RHO

0000336 RHO

0000337 RHO

0000338 RHO

* VELOCITIES

*----.--------1----.

0000339 VELF

0000340 VELF

0000341 VELF

0000342 VELF

0000343 VELG

0000344 VELG

0000345 VELG

0000346 VELG

*----------- 1----

---- 1------1------..1----1------1---

345010000 * DE-BL-1

310010000 * DE-BL-2

180010000 * DE-PC-I

100010000 * DE-PC-2

118020000 * DE-PC-3

345010000 * FE-BL-1

310010000 * FE-BL-2

180010000 * FE-PC-i

100010000 * FE-PC-2

345010000 * FE-BL-1

310010000 * FE-BL-2

180010000 * FE-PC-i

100010000 * FE-PC-2 --1------1------..1-. ....- 1------1.. --

SMASS FLOW RATES

0000347 ........ 3i5010000 1 1N ,1 BREAK -. .

0000347 MFLOWJ 350010000 * BREAK PLANE BLCL 0000348 NFLOWJ 315110000 * BREAK PLANE BLHL

0000349 MFLOWJ 345020000 * DTT-RA•E BLCL

0000350 MFLOWJ 310020000 * D'T-RAHE BLHL

0000351 MFLOWJ 180010000 * DTT-RAKE ILCL

0000352 MFLOWJ 100020000 * DTT-RAKE ILHL

0000353 MFLOWJ 400010000 * PRES. SURGE LINE FLOW

0000354 MFLOWJ 541010000 * FE-P4-12

0000355 MFLOWJ 566000000 * FE-P4-72-1

* -------------------- --- 1 ------ 1 -------- ---- 1----

* CLADDING TEMPERATURES CONTROL MODULE

0000356 HTrEMP 230000110 *

0000357 HTTEMP 230000210 *

0000358 HTTEMP 230000310 , 0000359 HTIEMP 230000410 *

0000360 HTITEMP 230000510 , 0000361 HTrEMP 230000610 *

* -------- 1-------- 1 ---- ----- ------------ 1 ---- * LIQUID FRACTIONS IN THE PRESSURIZER *

0000362...-1 ---- 415 1------1 -1- -1

0000362 VOIDF 415010000 0000363 V01DF 415020000 '
0000364 VOIDF 415030000

0000365 VOIDF 415040000

0000366 VOIDF 415050000

0000367 VOIDF 415060000

0000368 VOIDF 420010000

0000369 VOIDF 420020000

* TRIPS

*-----------1------1----" -1------1-. ....-1-. ....-1--

* 501-509 GENERAL TRIPS

* ALWAYS TRUE

0000501 TIME 0 GE NULL 0 -1.0 L

* ALWAYS FALSE

0000502 TIME 0 LT NULL 0 -1.0 N

* PRESSURIZER LOW LEVEL ALARM

0000503 CNTRLVAR 002 LE NULL 0 0.3810 L

* ----.---- 1 ----.--- 1 ----- I--1--- ---- 1 ------ 1 ---------- * 510-519 TEST SPECIFIC TRIPS

* -------- 1-------- 1 ------ 1 ------ 1 ------ 1 ------ 1----

* SCRAM

0000510 P 100010000 LE NULL 0 1.4193+7 L

* ---------------- I 1-- ----1 -------- I ---- 1 ------- I---

* LT 677 COLD LEG QOBV CARD 3650301

0000511 TIME 0 LT NULL 0 7302. N

0000512 TIME 0 GE NULL 0 0.0 L

0000677 511 AND 512 N

* ------------ ---- 1------1----

* LT 678 COLD LEG ISOL VALVE CARD 3550301

0000678 501 OR 501 N

* ---------------- 1------ 1 ---- * LT 681 ECC CHECK VALVE CARD 6000301

0000577 IFLOWJ 600000000 GE NULL 0 0.0 N

0000578 P 605010000 GE P 185010000 0.0 N

0000681 577 AND 578 N

* ------------ ---- ---- I ---1----

* LT 682 ACCUMULATOR VALVE CARD 6100301

0000579 TINE 0 GE NULL

0000682 579 OR 579

* ---------------- 1 ------ 1 ---- * LT 683 HPIS JUNCTION CARD

0000513 P 100010000 LE NULL

0000514 TIME 0 LT NULL

0000515 TIME 0 GT NULL

0000610 514 OR 515

0000683 610 AND 513

* -------- 1 ------ 1------ 1----

* LT 684 LPIS JUNCTION CARD

0000684 510 AND 510

*-------- 1 ----- ------ 1 ---- * LT 685-686 STEAM VALVE CARD

* OPEN TRIP

0000589 P 530010000 GT NULL

0000590 P 530010000 LT NULL

0000670 685 OR 589

0000671 -590 AND -686

0000685 671 AND 670

0

L

6400200

0

0

0

N

N

6350200

L

5400301

1.0+9 L

13.159+6

1800.

5974.

L

N

L

0

0

7.1125+6 N

6.9747+6 N

N

N

N

- 29 -
* CLOSE TRIP

0000591 P 530010000 GT NULL 0

0000592 P 530010000 LT NULL 0

0000672 686 OR 592 N

0000673 -591 AND 672 N

0000674 -685 AND 699 N

0000686 673 AND 674 N

* ---- ---- --------------- 1----

* LT 687 STEAM BYPASS VALVE CARD 5450301

0000516 TIME 0 GE NULL 0

0000517 P 530010000 GT P 546010000

0000687 516 AND 517 N

* --------- 1 ---- --- ---1 ---- * IT 688 FEED JUNCTION CARD 5660200

0000688 510 AND 510 L

* -------- 1 ------ 1 ------ 1----

* LT 689 FEED VOLUME CARD 5650200

0000689 510 AND 510 L *-------1----1-- ....-1"-

6.5613+6 N

6.4924+6 N

3574. L

0. N

* LT 690 AUX FEED JUNCTION

0000690 516 AND 516

* -------- 1 ---- ------- 1 ---- * IT 692 PZR SPRAY VALVE

0000583 P 420010000 6T

0000584 P 420010000 IT

0000665 583 OR 692

0000692 -584 AND 665

* -------------------- --- 1----

* LT 695 PCP 1 TRIP

0000695 510 AND 510

* -----------1 ----1 -- ---- 1----

* LT 696 PCP 1 VELOCITY TABLE

0000696 502 AND 502

* -------- 1 ------ 1------ 1----

* LT 697 PCP 2 TRIP

0000697 510 AND 510

* ----.---- 1 ---- 1 ------1----

* LT 698 PCP 2 VELOCITY TABLE

0000698 502 AND 502

CARD 5690200

L

CARD

NULL

NULL

4350301

0

0

N

N

1.533874+7 N

1.516637+7 N

CARD 1350301

N

CARD 1356100

N

CARD 1650301

N

CARD 1656100

N

* ---------------- 1 ------ 1----

* LT 699 SCRAM CARD 20269900 OR 20290000

0000699 510 OR 510 L

* INTACT LOOP *

* REACTOR VESSEL NOZZLE - INTACT LOOP HOT LEG

1000000 "RVN ILHL " BRANCH

1000001 2 0

1000101 0.0 1.58878 0.102752 0.0 0.0 0.0

1000102 4.OE-5 0.0 00

1000200 0 14913500. 1328990.0 2461830.0 0.0

1001101 252010000 100000000 0.0634 0.1 0.1 0002

1002101 100010000 105000000 0.0 0.1 0.1 0000

1001201 10.523000 10.523000 0.0

1002201 10.517000 10.517000 0.0

* -------- 1 ---- 1------ 1 ------ 1 ------ 1------ 1----

-30-
* PRESSURIZER CONNECTION TEE REACTOR VESSEL SIDE

1050000 "PZR T RVS " BRANCH

1050001 1 0

1050101 0.0634444 1.0531192 0.0 0.0 0.0 0.0

1050102 4.OE-5 0.0 00

1050200 0 14905700. 1328990. 2461990. 0.0

1051101 105010000 107000000 0.0 0.12 0.12 0000

1051201 10.757000 10.757000 0.0

* -------- -------- 1 ------ 1 ------ 1 I ..---- -- ---1 .----

* PRESSURIZER CONNECTION TEE

1070000 "PZR T " BRANCH

1070001 1 0

1070101 0.0620253 0.2810215 0.0 0.0 0.0 0.0

1070102 4.OE-5 0.0 00

1070200 0 14897600. 1328990. 2462160. 0.0

1071101 107010000 110000000 0.0 0.135 0.135 0000

1071201 11.009 11.009 0.0

* -------- 1 ------ 1------ 1 ---- 1 ------ 1 ------ 1----

, PRESSURIZER CONNECTION TEE STEAM GENERATOR SIDE

1100000 "PZR T SS " BRANCH

1100001 1 0

1100101 0.0606063 0.9207292 0.0 0.0 0.0 0.0

1100102 4.OE-5 0.0 00

1100200 0 14888500. 1328980. 2462350. 0.0

1101101 110010000 112000000 0.0 0.15 0.15 0000

1101201 11.628000 11.628000 0.0

* --- ---- ----- -----1---- 1------ 1 -----1----------

* HOT LEG PIPING

1120000 "HOT LEG PP" PIPE

1120001 2

1120101 0.0 2

1120201 0.0 1

1120301 1.38893 1

1120302 0.707687 2

1120401 0.0796973 1

1120402 0.0579614 2

1120501 0.0 2

1120601 0.0 1

1120602 90.0 2

1120701 0.0 1

1120702 0.246447 2

1120801 4.OE-5 0.0 2

1120901 0.20 0.20 1

1121001 00 2

1121101 0000 1

1121201 0 14873600. 1328970. 2462670. 0.0 0.0 01

1121202 0 14885900. 1328970. 2462410. 0.0 0.0 02

1121300 0

1121301 11.628000 11.628000 0.0 01

* -------- 1-------- 1 ------ ------ 1 ---------------- * SG INLET PLENUM

1140000 "SG IN PLNM" BRANCH

1140001 2 0

1140101 0.0 0.629795 0.33532 0.0 90.0 0.512756

- 31 -
1140102 4.E-5 0.0102 00

1140200 0 14801000. 1328950. 24642'

1141101 112010000 114000000 0.0512 0.0

1142101 114010000 115000000 0.0 0.0

1141201 8.1466000 8.1466000 0.0

1142201 4.4143000 4.4143000 0.0

*----------- 1--------1 ------ 1--I------- 1----

*SG U-TUBES

1150000 "SG TUBES "PIPE

1150001 8

1150101 0.0 8

1150201 0.151171 7

1150301 0.902 1

1150302 0.6096 3

1150303 0.462908 5

1150304 0.6096 7

1150305 0.902 8

1150401 0.136356 1

115040Z 0.0921538 3

1150403 0.0699783 5

1150404 0.0921538 7

1150405 0.136356 8

1150501 0.0 8

1150601 90.0 4

1150602 -90.0 8

1150701 0.902 1

1150702 0.6096 3

1150703 0.299572 4

1150704 -0.299572 5

1150705 -0.6096 7

1150706 -0.902 8

1150801 1.27-7 0.01022 8

1150901 0.0 0.0 7

1151001 00 8

1151101 000 0 7

1151201 0 14781200. 1308850. 24646

1151202 0 14767100. 1292040. 24649

1151203 0 14755800. 1277830. 24651

1151204 0 14746400. 1267890. 24653

1151205 0 14741200. 1258740. 24654

1151206 0 14738500. 1247990. 24655

1151207 0 14736200. 1237950. 24655

1151208 0 14733400. 1228440. 24656

1151300 0

1151301 4.3678000 4.3678000 0.0 01

1151302 4.3300000 4.3300000 0.0 02

1151303 4.2988000 4.2988000 0.0 03

1151304 4.2777000 4.2777000 0.0 04

1151305 4.2587000 4.2587000 0.0 05

1151306 4.2370000 4.2370000 0.0 06

1151307 4.2166000 4.2166000 0.0 07

*----------- 1------1--I------- 1--------1 ----

SG5 OUTLET PLENUM

1160000 "SG OUT PLN" BRANCH

1160001 2 0

1160101 0.0 0.629795 0.33532 0.0

1160102 43E-5 0.0102 00

00. 0.0

0.0

0.0

0100

0100

----1------1----

----1------1----

20.

10.

50.

50.

60.

20.

70.

30.

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

01

02

03

04

05

06

07

08

-90.0 -0.512756

- 3Z -
1160200 0 14735800. 1228440. 2465580. 0.0

1161101 115010000 116000000 0.0 0.0 0.0 0100

1162101 116010000 118000000 0.0512 0.0 0.0 0100

1161201 4.1997000 4.1997000 0.0

1162201 7.7841000 7.7841000 0.0

* ----.---- 1 ----.--- 1 ------ 1 ------ 1 ----.-- 1 ------ 1 ---- * PUMP SUCTION PIPING

1180000 "PMP SUC PP" PIPE

1180001 3

1180101 0.0 3

1180201 0.0 2

1180301 0.546638 1

1180302 0.688596 2

1180303 0.558577 3

1180401 0.0445625 1

1180402 0.0445137 2

1180403 0.0354278 3

1180501 0.0 3

1180601 -90.0 3

1180701 -0.498052 1

1180702 -0.688596 2

1180703 -0.355604 3

1180801 4.E-5 0.0 3

1180901 0.083 0.083 1

1180902 0.104 0.104 2

1181001 00 3

1181101 0000 2

1181201 0 14659900. 1228430. 2467190. 0.0 0.0 01

1181202 0 14646900. 1228430. 2467470. 0.0 0.0 02

1181203 0 14644400. 1228430. 2467520. 0.0 0.0 03

1181300 0

1181301 9.8172000 9.8172000 0.0 01

1181302 10.006000 10.006000 0.0 02

* -------- ---1- ---- 1 ---- -------- 1 ------ 1 ------ 1 ---- * PUMP SUCTION TEE

1200000 "PMP SCT T " BRANCH

1200001 3 0

1200101 0.0 0.759614 0.0487901 0.0 0.0 0.0

1200102 4.OE-5 0.0 00

1200200 0 14641700. 1228420. 2467580. 0.0

1201101 118010000 120000000 0.0 0.1 0.1 0000

1202101 120010000 125000000 0.0317 0.4 0.4 0100

1203101 120010000 155000000 0.0317 0.4 0.4 0100

1201201 10.006000 10.006000 0.0

1202201 5.2047000 5.2047000 0.0

1203201 4.7736000 4.7736000 0.0

* -------- 1 ---- 1------ 1 -- --------1--- --- 1 ---- * PUMIP SUCTION TEE OUTLET

1250000 "PMP1 SCT T" BRANCH

1250001 1 0

1250101 0.0 1.00308 0.0640548 0.0 90.0 0.520704

1250102 4.OE-5 0.0 00

1250200 0 14619800. 1228410. 2468040. 0.0

1251101 125010000 130000000 0.0 0.13 0.13 0000

1251201 8.5638000 8.5638000 0.0

* ---------------- 1 ------ 1 ---- -------- 1 ------ 1----

-33-
, PUMP 1 INLET

1300000 "PMP1 INLET" SNGLVOL

1300101 0.0 0.457201 0.0177444 0.0 90.0 0.457201

1300102 4.OE-5 0.0 00

1300200 0 14594400. 1228410. 2468590. 0.0

* -------- 1 -- --------1------ 1 ---- 1 ------ 1----

* PRIMARY COOLANT PUMP 1

1350000 "PCPUMPl " PUMP

1350101 0.0 0.4572 0.0991 0.0 90.0 0.317900

1350102 0

1350108 130010000 0.0 0.017 0.017 0000

1350109 140000000 0.0 0.05 0.05 0000

1350200 0 14870800. 1228670. 2462730. 0.0

1350201 0 8.5640000 8.5640000 0.0

1350202 0 9.0771000 9.0771000 0.0

1350301 0 0 0 -1 -1 695 0

1350302 369.00000 .91178862 .31550000 96.000000 500.60000 1.4310000

1350303 613.6 0.0 207.433 0.0444 19.5987 0.0

1350308 78.53982 0.0 -22.86511 27.16043 5.74589

1350310 0.0 0.0 0.0

* ---- ---- --------------- 1 ------ 1 ---- -- ----1----

* PUMP 1 OUTLET PUMP SIDE

1400000 "PMPi OUT P" SNGLVOL

1400101 0.0 0.502185 0.0183849 0.0 0.0 0.0

1400102 4.OE-5 0.0 00

1400200 0 15090400. 1228670. 2457720. 0.0

* ---- -------- ----1 -----1 ---- ------ 1 -- ----1----

* PUMPI OUTLET PIPE TEE SIDE

1450000 "PMP1 OUT T" BRANCH

1450001 2 0

1450101 0.0 1.4084 0.0633 0.0 0.0 0.0

1450102 4.OE-5 0.0 00

1450200 0 15099600. 1228660. 2457500. 0.0

1451101 140010000 145000000 0.0 0.0 0.0 0000

1452101 145010000 150000000 0.0 0.1 0.1 0100

1451201 9.0747000 9.0747000 0.0

1452201 7.3917000 7.3917000 0.0

* -------- 1 ---- -- ------ 1 ---- ------ 1 ------ 1----

* PUMP OUTLET TEE

1500000 "PMP OUT T " BRANCH

1500001 2 0

1500101 0.0636463 0.3542995 0.0 0.0 0.0 0.0

1500102 4.OE-5 0.0 00

1500200 0 15079600. 1228680. 2457980. 0.0

1501101 170010000 150000000 0.0183 0.1 0.1 0100

1502101 150010000 172000000 0.0 0.0 0.0 0000

1501201 8.0488000 8.0488000 0.0

1502201 9.9847000 9.9847000 0.0

* ---- ----------- 1 ------ 1 ---- ------ -1 -- ---- 1----

* PUMP 2 SUCTION TEE OUTLET

* -------- -------- 1 1 ---- --1------ 1 --------------- I1550000 "PMP2 SCT T" BRANCH

1550001 1 0

1550101 0.0 1.00308 0.0640548 0.0 90.0 0.520704

-34-
1550102 4.OE-5 0.0 00

1550200 0 14629600. 1228410. 2467830. 0.0

1551101 155010000 160000000 0.0 0.13 0.13 0000

1551201 7.7885000 7.7885000 0.0

* -------- -------- 1 1 ------ 1 ------ 1 ------ 1 ------ 1----

* PUMP 2 INLET PIPE

1600000 "PMP2 INLET" SNGLVOL

1600101 0.0 0.457201 0.0177444 0.0 90.0 0.457201

1600102 4.OE-5 0.0 00

1600200 0 14608000. 1228410. 2468300. 0.0

* ------------ ---- 1--- --- 1 -- -1--- -- 1-- ----1----

* PRIMARY COOLANT PUMP 2

1650000 "PCPUMP2 " PUMP

1650101 0.0 0.514 0.0991 0.0 90.0 0.317900

1650102 0

1650108 160010000 0.0 0.017 0.017 0000

1650109 170000000 0.0 0.1 0.1 0000

1650200 0 14928600. 1228710. 2461510. 0.0

1650201 0 7.7887000 7.7887000 0.0

1650202 0 8.0515000 8.0515000 0.0

1650301 135 135 135 -1 -1 697 0

1650302 369.00000 .93018970 .31550000 96.000000 500.60000 1.4310000

1650303 613.6 0.0 207.433 0.0444 19.5987 0.0

1650308 78.53982 0.0 -22.86511 27.16403 5.74589

1650310 0.0 0.0 0.0

* -------- 1 ------------ 1 ------ 1 ------ 1 ------ 1----

* PUMP 2 OUTLET

1700000 "PMP2 OUT T" BRANCH

1700001 0 0

1700101 0.0 0.514071 0.0192958 0.0 0.0 0.0

1700102 4.OE-5 0.0 00

1700200 0 15203100. 1228710. 2454990. 0.0

*-------- 1 ------ 1 ------ 1 ------ 1------ 1 ------ 1----

* PRESSURIZER SPRAY TEE

1720000 "PZR SPR T " BRANCH

1720001 1 0

1720101 0.0635359 0.2844229 0.0 0.0 0.0 0.0

1720102 4.OE-5 0.0 00

1720200 0 15078900. 1228680. 2458000. 0.0

1721101 172010000 175000000 0.0 0.0 0.0 0000

1721201 10.002 10.002 0.0

* ----.---- 1 ------ 1------1------1------1------1----

* INTACT LOOP COLD LEG PIPE

* ---- ------- ---- 1 ------ 1 ------------ 1 ---- --- 1----

1750000 "ILCL PIPE " PIPE

1750001 2

1750101 0.0 2

1750201 0.0 1

1750301 0.4163655 1

1750302 0.613244 2

1750401 0.0264082 1

1750402 0.038895 2

1750501 0.0 2

1750601 0.0 2

1750701 0.0 2

- 35 -
1750801 4.0E-5 0.0 2

1750901 0.0 0.0 1

1751001 00 2

1751101 0000 1

1751201 0 15078200. 1228680. 2458020. 0.0 0.0 01

1751202 0 15077300. 1228680. 2458040. 0.0 0.0 02

1751300 0

1751301 10.002000 10.002000 0.0 01

* -------- 1 ---- -- 1 ---- ------ 1 ---- 1 ------1----

* ECC CONNECTION TEE

1800000 "EGG T " BRANCH

1800001 1 0

1800101 0.0 1.15189 0.0730598 0.0 0.0 0.0

1800102 4.OE-5 0.0 00

1800200 0 15075800. 1228670. 2458080. 0.0

1801101 175010000 180000000 0.0 0.0 0.0 0000

1801201 10.002000 10.002000 0.0

* ---------------- 1-------- I ---- 1 ---- -- ------ 1----

* REACTOR VESSEL NOZZLE - INTACT LOOP COLD LEG

1850000 "RVN ILCL " BRANCH

1850001 2 0

1850101 0.0 1.00965 0.0644920 0.0 0.0 0.0

1850102 4.OE-5 0.0 00

1850200 0 15075200. 1228670. 2458090. 0.0

1851101 185010000 202000000 0.0634 2.8 2.8 0101

1852101 180010000 185000000 0.0 0.0 0.0 0100

1851201 8.6438000 8.6438000 0.0

1852201 10.002000 10.002000 0.0

* REACTOR VESSEL

* ---- ---- -------- 1------1------1------1-- ---- 1----

* INLET ANNULUS TOP VOLUME

2000000 "IN AN TOP " BRANCH

2000001 1 0

2000101 0.2617061 0.1876129 0.0 0.0 90.0 0.187

2000102 3.81-6 0.178 00

2000200 0 15030000. 1232640. 2459190. 0.0

2001101 200000000 202000000 0.0 0.0 0.0 0000

2001201 1.59691-7 1.59691-7 0.0

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1 ------ 1----

* INLET ANNULUS

*2020000---1 ---- AN 1 ... 1- --- 1- ---- 1-. .... 2020000 "IN AN " BRANCH

'6129

2020001

2020101

2020102

2020200

2021101

2022101

2021201

2022201

2

0.2617061

3.81-6

0

202010000

202000000

2.2804

6.12444-2

0

0.2851822

0.175

15031700.

205000000

252000000

2.2804

6.12444-2

0.0

00

1228660.

0.0

0.0

0.0

0.0

0.0

2459150.

0.0

4.5+4

-90.0 -0.2851822

0.0

0.0

4.5+4

0000

0003

* -------- --- ----I 1------1------ 1 ------ ---- -- ---- * INLET ANNULUS BOTTOM VOLUME

*-----------1----1----1----1-. ....- 1-----1--

-36-
2050000 "IN AN BOT " BRANCH

2050001 1 0

2050101 0.2296374 0.2525361 0.0

2050102 3.81-6 0.172 00

2050200 0 15031700. 1228660.

2051101 205010000 210000000 0.0

2051201 3.5613000 3.5613000 0.0

* DOWNCOMER

2100000 "DOWNCOMER " ANNULUS

2100001 6

2100101 0.0 6

2100201 0.0 5

2100301 1.0267313 1

2100302 0.4933248 2

2100303 0.7028265 3

2100304 0.5588068 4

2100305 0.6522799 5

2100306 0.4269792 6

2100401 0.1509710 1

2100402 0.0706690 2

2100403 0.1060015 3

2100404 0.0795138 4

2100405 0.0998947 5

2100406 0.06252 6

2100501 0.0 6

2100601 -90.0 6

2100801 3.81-6 0.102 6

2100901 0.0 0.0 5

2101001 00 6

2101101 0000 5

2101201 0 15033300. 1228660.

2101202 0 15038200. 1228660.

2101203 0 15042800. 1228660.

2101204 0 15046500. 1228660.

2101205 0 15051300. 1228660.

2101206 0 15054600. 1228660.

2101300 0

2101301 3.6556000 3.6556000 0.0

2101302 3.6555000 3.6555000 0.0

2101303 3.6801000 3.6801000 0.0

2101304 3.6801000 3.6801000 0.0

2101305 3.5763000 3.5763000 0.0

*LOWER PLEN1UM TP1 VO1-

* LOWER PLENUM TOP VOLUME

*-----------1-. ....-1----1----

0.0

24591

0.0

---1-...-

-90.0 -0.2525361

50. 0.0

0.0 0000

----1------1----

----1------1----

2459110.

2458990.

2458880.

2458790.

2458670.

2458590.

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

01

02

03

04

05

06

01

02

03

04

05 -1----1----1--

*--1-- ---- 1----

2150000

2150001

2150101

2150102

2150200

2151101

2152101

2153101

2151201

2152201

2153201

"LWR PL TOP"

3 0

0.0 0.3533183

3.81-6 0.0

0 15052500.

210010000 215000000

215010000 220000000

215000000 225000000

3.5762000 3.5762000 -. 1243900 -. 1243900

4.0692000 4.0692000

BRANCH

0.24520

00

1228660.

0.0

0.0

0.1499

0.0

0.0

0.0

0.0

2458640.

2.00

0.005

1.5

-90.0

0.0

2.00

0.005

1.5

-0.3533183

0000

0000

0000

- 37 -
* LOWER PLENUM BOTTOM VOLUME

2200000 "LWR PL BOT" SNGLVOL

2200101 0.0 0.3741720 0.29656 0.0 -90.0 -0.374

2200102 4.OE-5 0.0 00

2200200 0 15055200. 1227510. 2458580. 0.0

* -------- 1-------- 1 ------ 1 ------ 1 ------ 1 ------ 1----

* JUNCTION FROM COLD LEG TO FILLER GAP

2220000 "CL-FLLRGAP" SNGLJUN

2220101 185010000 223000000 0.0 15.000 15.000 0100

2220201 0 1.3659000 1.3659000 0.0

* ....-.... 1 ----.-- 1 ---- ----- ---- ------ 1 ---- * REACTOR VESSEL FILLER GAP

2230000 "FILLER GAP" ANNULUS

2230001 4

2230101 0.0 4

2230201 0.0 3

2230301 1.4218585 1

2230302 1.1961513 2

2230303 1.2110867 3

2230304 0.7802975 4

2230401 0.0899085 1

2230402 0.0722790 2

2230403 0.0334096 3

2230404 0.0309800 4

2230501 0.0 4

2230601 -90.0 4

2230801 3.81-6 0.0 4

2230901 0.0 0.0 3

2231001 00 4

2231101 0000 3

2231201 0 15105600. 1228360. 2457350. 0.0 0.0 01

2231202 0 15115300. 1228100. 2457120. 0.0 0.0 02

2231203 0 15121100. 1227850. 2456970. 0.0 0.0 03

2231204 0 15130300. 1227690. 2456750. 0.0 0.0 04

2231300 0

2231301 1.4291000 1.4291000 0.0 01

2231302 1.3129900 1.3129900 0.0 02

2231303 3.1295000 3.1295000 0.0 03

* JUNCTION FROM FILLER GAP TO LOWER PLENUM

*-------1--- --1----1----1-. ....- 1------..1--

2240000 "FLLRGAP-LP" SNGLJUN

2240101 223010000 220000000 0.0 15. 15. 0000

2240101 223010000 220000000 0.0 45. 45. 0000

2240201 0 2.1743000 2.1743000 0.0

* -------- 1 ------ 1------ 1 ------ I --- -- 1 ----1----

* LOWER CORE SUPPORT STRUCTURE

2250000 "L CORE SUP" BRANCH

2250001 2 0

2250101 0.0 0.4269792 0.12094 0.0 90.0 0.426O

2250102 3.81-6 0.095 00

2250200 0 15038300. 1228490. 2458990. 0.0

2251101 225010000 230000000 0.1134 1.5 1.5 0100

2252101 225010000 235000000 0.0 12. 12. 0100

2251201 3.2020000 3.2020000 0.0

11720

)792
2252201 1.6570000 1.6570000 0.0

* ---- ---- 1----1------1-------- 1----

* ACTIVE CORE ----1------1------1----

* ------------1--------1 ---- -1 ---- ----1------1------1----

2300000 PIPE

2300001

2300101

2300201

2300202

2300203

2300204

2300205

2300301

2300302

2300303

2300401

2300402

2300403

2300404

2300405

2300406

2300501

2300601

2300801

2300901

2300902

2300903

2300904

2300905

2301001

2301101

2301201

2301202

2301203

2301204

2301205

2301206

2301300

2301301

2301302

2301303

2301304

2301305

"CORE

6

0.0 6

0.1705 1

0.144 2

0.1705 3

0.144 4

0.1705 5

0.3728765 1

0.2794034 5

0.4234231 6

0.0683340 1

0.0478582 2

0.0483329 3

0.0479138 4

0.0479052 5

0.0750459 6

0.0 6

90.0 6

1.27-7 0.012

0.0 0.0

0.66 0.66

0.0 0.0

0.66 0.66

0.0 0.0

00 6

0000 5

0 15017600.

0 15012600.

0 15004500.

0 15000500.

0 14992300.

0 14987800.

0

3.4659000 3.4659000

4.1523000 4.1523000

3.5540000 3.5540000

4.2594000 4.2594000

3.6273000 3.6273000

6

1

2

3

4

5

1243280.

1267710.

1294130.

1317510.

1332930.

1337240.

2459490.

2459620.

2459810.

2459910.

2460100.

2460200.

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

01

02

03

04

05

06

0.0

0.0

0.0

0.0

0.0

01

02

03

04

05

* ---- ---- 1----1------1-------- 1----

*CORE BYPASS VOLUME

2350000 "CORE BYPSS" PIPE

2350001 3

2350101 0.0 3

2350201 0.0 2

2350301 0.6522799 1

2350302 0.5588068 2

2350303 0.7028265 3

2350401 0.0091280 1

2350402 0.0072325 2

2350403 0.0088095 3

2350501 0.0 3

2350601 90.0 3

2350801 3.81-6 0.003 3

- 39 -
2350901 0.0 0.0 2

2351001 00 3

2351101 0000 2

2351201 0 15001900. 1228490. 2459460. 0.0 0.0 01

2351202 0 15007600. 1228490. 2459740. 0.0 0.0 02

2351203 0 14994900. 1228500. 2460040. 0.0 0.0 03

2351300 0

2351301 1.7916000 1.7916000 0.0 01

2351302 1.8500000 1.8500000 0.0 02

* -------- -------- 1 1 ------ 1 ------ 1 ------ 1 ------ 1----

* UPPER END BOXES AND SUPPORT STRUCTURE

2400000 "UPR END BXt

' BRANCH

2400001 2 0

2400101 0.0 0.4933248 0.1195494 0.0 90.0 0.4933248

2400102 3.81-6 0.145 00

2400200 0 14969100. 1333110. 2460620. 0.0

2401101 230010000 240000000 0.1118 1.5 1.5 0100

2402101 235010000 240000000 0.0 12. 12. 0100

2401201 3.4977000 3.4977000 0.0

2402201 1.8501000 1.8501000 0.0

* -------- 1 -- --------------- 1 ------ 1------ 1----

* UPPER CORE SUPPORT STRUCTURE - CROSS FLOW REGION

2450000 "UPR CR SUP" BRANCH

2450001 2 0

2450101 0.0 0.4933248 0.1280806 0.0 90.0 0.4933248

2450102 3.81-6 0.145 00

2450200 0 15420100. 1407960. 2449770. 0.0

2451101 240010000 245000000 0.0 0.0 0.0 0000

2452101 245010000 251000000 0.0 0.0 0.0 0100

2451201 2.1756000 2.1756000 0.0

2452201 -. 24832-4 -. 24832-4 0.0

* ---- ------------ 1------ 1 ------ 1 ---- ------1----

* UPPER FLOW SKIRT REGION

2500000 "U FLW SKRT" BRANCH

2500001 1 0

2500101 0.1547532 0.7850547 0.0 0.0 90.0 0.7850547

2500102 3.81-6 0.131 00

2500200 0 14955900. 1333110. 2460920. 0.0

2501101 245010000 250000000 0.0 0.0 0.0 0100

2501201 4.1549000 4.1549000 0.0

* ---- ---- 1 ------ 1 ---- ------ 1 ---- ----------- * DEAD END OF FUEL MODULES

2510000 "DE FL MODS" SNOLVOL

2510101 0.0 0.7844123 0.1154214 0.0 90.0 0.7844123

2510102 3.81-6 0.214 00

2510200 0 14963500. 1329710. 2460750. 0.0

* -------- -------- 1 1 ---- -- 1------1------ 1 ------ 1----

* UPPER HEAD

2520000 "UPR HEAD " BRANCH

2520001 1 0

2520101 0.2622585 0.2869580 0.0 0.0 90.0 0.2869580

2520102 3.81-6 0.0 00

2520200 0 14957200. 1329000. 2460890. 0.0

2521101 250010000 252000000 0.0 0.006 0.006 0000

-40-
2521201 4.1549000 4.1549000 0.0

* ----.------- 1 ---- 1 - - -----.---- I--1 ----- --- --- 1 ---- * UPPER PLENUM BOITOM VOLUME

2550000 "UPR PL BOT" BRANCH

2550001 2 0

2550101 0.2622585 0.6312304 0.0 0.0 90.0 0.6312304

2550102 3.81-6 0.0 00

2550200 0 14954800. 1328590. 2460950. 0.0

2551101 252010000 255000000 0.0 0.006 0.006 0000

2552101 255010000 260000000 0.0 0.03 0.03 0000

2551201 3.56869-6 3.56869-6 0.0

2552201 4.52212-6 4.52212-6 0.0

* --------- 1 ----.-- 1 ------ 1 ------ 1 ------ 1----

* UPPER PLENUM TOP VOLUME

2600000 "UPR PL TOP" SNGLVOL

2600101 0.0 0.7747094 0.1914909 0.0 90.0 0.7747094

2600102 3.81-6 0.0 00

2600200 0 14949800. 1326010. 2461060. 0.0

* BROKEN LOOP

* -------- 1 ------ 1----

* REACTOR VESSEL NOZZLE -

3000000 "RVN BLHL "

---- 1 ------ I----

BROKEN LOOP HOT LEG

---- 1 ------ 1----

BRANCH

----1------1----

----1------1----

3000001

3000101

3000102

3000200

3001101

3002101

3001201

3002201

2

0.0

4. OE-5

0

252010000

300010000

-. 1240600 -. 1311000

0

0.876303

0.0

14957200.

300000000

305000000

-. 1240600 -. 1311000

0.0575410 0.0

00

1221360. 246(

0.0

0.067014

0.063426

0.0

0.0

0.0

0.1

)890. 0.0

0.0

0.1

0.0

0002

0000

* -------- 1 -- ----1 ----------- 1 ----------- * HOT LEG PIPE TO REFLOOD ASSIST BYPASS TEE

3050000 "HLP-RABS T" BRANCH

3050001 1 0

3050101 0.0 0.698336 0.0442927 0.0 0.0

3050102 4.OE-5 0.0 00

3050200 0 14957200. 1221770. 2460890. 0.0

3051101 305010000 310000000 0.0 0.1 0.1

3051201 -. 1838800 -. 1838800 0.0

* ---- ---- ---- ---- 1 ------ ------ 1------1----

* BROKEN LOOP HOT LEG CONTRACTION

3100000 "BLHL CONTR" BRANCH

3100001 2 0

3100101 0.0 1.50013 0.0678467 0.0 0.0

3100102 4.OE-5 0.0 00

3100200 0 14957200. 1222120. 2460890. 0.0

3101101 380010000 310000000 0.0388 0.84 0.84

3102101 310010000 315000000 0.0083647 0.0 0.0

3101201 .21484000 .21484000 0.0

3102201 2.07725-3 2.07725-3 0.0

*-------- 1 ------ 1 ------ 1 ---- ------1----

0.0

0100

0.0

0100

0100

--1 ----

- 41 -
* STEAM GENERATOR AND PUMP SIMULATIOR * - 1 1-.. '1 -...1-.....1 ----.. ..

3150000 "SG+PMP SIM" PIPE

3150001 12

3150101 0.0 12

3150201 0.0083647 

2

3150202 0.032603 

4

3150203 0.105626 

5

3150204 0.032603 

7

3150205 0.0083647 

9

3150206 0.008364 10

3150207 0.0046398 11

3150301 0.367768 

1

3150302 0.552201 

2

3150303 0.993978 

4

3150304 0.849744 

6

3150305 0.993978 

8

3150306 1.371350 

9

3150307 1.365029 10

3150308 1.674812 11

3150309 0.545209 12

3150401 3.0767-3 

1

3150402 4.67621-3 

2

3150403 8.60554-2 

4

3150404 8.97552-2 

6

3150405 8.60554-2 

8

3150406 1.82303-2 

9

3150407 5.46687-2 10

3150408 1.82489-2 11

3150409 2.83241-2 12

3150601 90.0 

5

3150602 -90.0 10

3150603 90.0 11

3150604 0.0 12

3150701 0.127000 

1

3150702 0.552201 

2

3150703 0.993978 

4

3150704 0.457202 

5

3150705 -0.457202 

6

3150706 -0.993978 

8

3150707 -1.371350 

9

3150708 -0.520701 10

3150709 1.212851 11

3150710 0.0 12

3150801 4.OE-5 0.0 

3

3150802 4.OE-5 0.124 

4

3150803 4.OE-5 0.0 

6

3150804 4.OE-5 0.124 

7

3150805 4.OE-5 0.0 12

3150901 0.2 0.2 

1

3150902 0.0 0.0 

2

3150903 93.9 93.9 

4

3150904 0.4 0.4 

5

3150905 93.9 93.9 

7

3150906 0.0 0.0 

8

3150907 0.2 0.2 

9

3150908 4.1 4.1 10

3150909 0.4 0.4 11

3151001 00 12

- 42 

-
3151101 0000 1

3151102 0100 2

3151103 0000 7

3151104 0100 8

3151105 0000 10

3151106 0100 11

3151201 0 14956800. 1204970. 2460900. 0.0 0.0 01

3151202 0 14954200. 1196960. 2460960. 0.0 0.0 02

3151203 0 14948400. 1216750. 2461090. 0.0 0.0 03

3151204 0 14941000. 1217220. 2461250. 0.0 0.0 04

3151205 0 14935500. 1219110. 2461370. 0.0 0.0 05

3151206 0 14935500. 1219140. 2461370. 0.0 0.0 06

3151207 0 14941000. 1217240. 2461250. 0.0 0.0 07

3151208 0 14948400. 1217200. 2461090. 0.0 0.0 08

3151209 0 14957300. 1206410. 2460890. 0.0 0.0 09

3151210 0 14964400. 1209760. 2460730. 0.0 0.0 10

3151211 0 14961800. 1196570. 2460790. 0.0 0.0 11

3151212 0 14957200. 1215100. 2460890. 0.0 0.0 12

3151300 0

3151301 -. 14625-4 -. 14625-4 0.0 01

3151302 -. 35422-4 -. 35422-4 0.0 02

3151303 -. 13114-4 -. 13114-4 0.0 03

3151304 -. 72833-5 -. 72833-5 0.0 04

3151305 -.24333-5 -. 24333-5 0.0 05

3151306 -. 88365-5 -. 88365-5 0.0 06

3151307 -.29947-5 -.29947-5 0.0 07

3151308 -. 19321-4 -. 19321-4 0.0 08

3151309 -. 16785-4 -. 16785-4 0.0 09

3151310 -. 16628-4 -. 16628-4 0.0 10

3151311 -. 12497-4 -. 12497-4 0.0 11

* ---- -------- ---- 1 ------ 1 ---- --- 1 -

* REACTOR VESSEL NOZZLE - BROKEN LOOP COLD LEG

3350000 "RVN BLCL " BRANCH

3350001 2 0

3350101 0.0 0.749305 0.047979 0.0 0.0 0.0

3350102 4.OE-5 0.0 00

3350200 0 15031700. 1228270. 2459150. 0.0

3351101 202000000 335000000 0.064130 1.0 1.0 0002

3352101 335010000 340000000 0.063426 0.1 0.1 0000

3351201 .13028000 .13028000 0.0

3352201 .13170000 .13170000 0.0

* -- ---- 1----1 ---- 1-------- ---- 1 - ---- -- ---- I----

* COLD LEG PIPE TO REFLOOD ASSIST BYPASS TEE

*-------1----1----1-----1------1------..1---

3400000 "CLP-RABS T" BRANCH

3400001 1 0

3400101 0.0 0.698336 0.0443927 0.0 0.0 0.0

3400102 4.OE-5 0.0 00

3400200 0 15031700. 1227890. 2459150. 0.0

3401101 340010000 345000000 0.0 0.1 0.1 0100

3401201 .18613000 .18613000 0.0

* -------- 1 ---- 1------ 1 ------ 1 ------ 1 ------ 1----

* BROKEN LOOP COLD LEG CONTRACTION TO BREAK PLANE

3450000 "BLCL CONTR" BRANCH

3450001 2 0

3450101 0.0 1.50013 0.0673163 0.0 0.0 0.0

3450102 4.OE-5 0.0 00

- 43 -
3450Z00 0 15424700. 1228050. 2449660. 0.0

3451101 345000000 370000000 0.0388 0.84 0.84 0100

3452101 345010000 350000000 0.0046367 0.0 0.0 0100

3451201 .21516000 .21516000 0.0

3452201 6.55835-5 6.55835-5 0.0

* -------- 1 ------ 1 ------ ------ 1 ------ 1---- -- 1----

* SPOOL PIECE AND PIPE TO ISOLATION VALVE

3500000 "BRK SP+PPE" PIPE

3500001 2

3500101 0.0 2

3500201 0.023520 1

3500301 0.453394 1

3500302 1.074803 2

3500401 0.0106640 1

3500402 0.0407801 2

3500601 0.0 2

3500801 4.OE-5 0.0 1

3500802 4.OE-5 0.0 2

3500901 0.0 0.0 1

3501001 00 2

3501101 0100 1

3501201 0 15031700. 1218930. 2459150. 0.0 0.0 01

3501202 0 15031700. 1226360. 2459150. 0.0 0.0 02

3501300 0

3501301 4.59331-5 4.59331-5 0.0 01

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1------ 1----

* COLD LEG ISOLATION VALVE

3550000 "CL ISO VIA" VALVE

3550101 350010000 360000000 0.0 0.0 0.0 0100

3550201 0 -6.7943-7 -6.7943-7 0.0

3550300 TRPVLV

3550301 678

* -------- 1 ------ 1------ 1 ------ 1 ------ 1 ------ 1----

* COLD LEG PIPE BETWEEN ISOLATION VALVE AND QOBV

3600000 "CL IS-QOBV" SNGLVOL

3600101 0.0 0.569219 0.0297722 0.0 0.0 0.0

3600102 4.OE-5 0.0 00

3600200 0 15031700. 1241690. 2459150. 0.0

* ----------- 1 ---- I------- 1 ------ 1 ------ 1 ------ 1----

* COLD LEG QUICK OPENING BLOWDOWN VALVE

3650000 "CL QOBV " VALVE

3650101 360010000 805000000 0.0466 0.0 0.0 0000

3650201 0 .00000000 .00000000 0.0

3650300 TRPVLV

3650301 677 *-----------1----1----1----1-. ....- 1" 1"--

* REFLOOD ASSIST BYPASS PIPING - COLD LEG SIDE

3700000 "RABS C L PIPE

3700001 3

3700101 0.0388 2

3700102 0.0776 3

3700201 0.0388 2

3700301 0.0 3

3700401 0.0279 1

-44-
3700402 0.070 2

3700403 0.1165 3

3700601 90.0 1

3700602 0.0 3

3700701 0.64 1

3700702 0.0 3

3700801 4.0-5 0.0 3

3700901 0.28 0.28 1

3700902 0.84 0.84 2

3701001 00 3

3701101 0000 2

3701201 0 15029300. 1226830. 2459210. 0.0 0.0 01

3701202 0 15026900. 1226050. 2459270. 0.0 0.0 02

3701203 0 15026900. 1224760. 2459270. 0.0 0.0 03

3701300 0

3701301 .21514000 .21514000 0.0 01

3701302 .21508000 .21508000 0.0 02

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1 ---------- * REFLOOD ASSIST BYPASS VALVES

3750000 "RABS VALVS" SNGLJUN

3750101 370010000 380000000 0.0 1.55+4 1.55+4 0000

3750201 0 .10749000 .10749000 0.0

* -------- 1 ------ 1------ 1 ------ 1 -------- ---- 1----

* REFLOOD ASSIST BYPASS PIPING - HOT LEG SIDE

3800000 "RABS H L " PIPE

3800001 3

3800101 0.0776 1

3800102 0.0388 3

3800201 0.0388 2

3800301 0.0 3

3800401 0.0915 1

3800402 0.048 2

3800403 0.0489 3

3800601 0.0 1

3800602 -90.0 2

3800603 0.0 3

3800701 0.0 1

3800702 -0.64 2

3800703 0.0 3

3800801 4.0-5 0.0 3

3800901 0.84 0.84 1

3800902 0.28 0.28 2

3801001 00 3

3801101 0000 2

3801201 0 14952500. 1223750. 2469100. 0.0 0.0 01

3801202 0 14954900. 1223220. 2469090. 0.0 0.0 02

3801203 0 14957200. 1222740. 2460890. 0.0 0.0 03

3801300 0

3801301 .21492000 .21492000 0.0 01

3801302 .21488000 .21488000 0.0 02

* PRESSURIZER

* SURGE LINE PCS SIDE

*-----------1------...1------..1-. ....- 1-.... .-1-. ....- 1"

- 45 -
4000000 "SRG LN PCS" BRANCH

4000001 2 0

4000101 1.44561-3 2.30

4000102 2.3622-5 0.0

4000200 0 14895'

4001101 107000000 40000(

4002101 400010000 40500(

4001201 1.16231-2 1.162

4002201 1.16247-2 1.160

* ----.---- -------- 1 ---- * PRESSURIZER SURGE LINE

4050000 "SRG LN PZR"

4050001 2

4050101 1.44561-3 2

4050201 1.44561-3 1

4050301 2.30 2

4050401 0.0 2

4050601 90.0 2

4050701 0.30 2

4050801 2.3622-5 0.0

4050901 2.85 2.85

4051001 00 2

4051101 1000 1

4051201 0 148921

4051202 0 14890•

71

0

0

3

4

0.0

00

'00. 134568

'000 1.4456

000 1.4456

1-2 0.0

7-2 0.0

PIPE

0.

1-3

1-3

0.0

2462200.

3.9

2.85

90.0

0.0

3.9

2.85

0.54

0002

1000

2

1

300. 138372

300. 143598

0. 2462200. 0.0 0.0 01

0. 2462300. 0.0 0.0 02

4051300 0

4051301 1.16231-2 1.16231-2 0.0 01

* -------- -------- 1 1 ------ I ------- I---

* PRESSURIZER SURGE LINE

4100000 "SRG LINE " SNGLJUN

4100101 405010000 415000000 1.44561-3 0.42

4100201 0 -. 0608789 -. 0608789 0.0

* -------- 1 ------ 1 ------ 1 ------ 1----

* PRESSURIZER VESSEL

4150000 "PZR VESSEL" PIPE

4150001 6

4150101 0.0 2

4150102 0.5653 5

4150103 0.0 6

4150201 0.0 5

4150301 0.1815 1

4150302 0.1524 2

4150303 0.3967 3

4150304 0.5289 4

4150305 0.3967 5

4150306 0.1943 6

4150401 0.0684 1

4150402 0.0838 2

4150403 0.0 5

4150404 0.0732 6

4150501 0.0 6

4150601 90.0 6

4150801 4.OE-5 0.0 6

4151001 00 6

4151101 0000 5

4151201 0 14889200. 1551340. 24623'

----1------1----

----1------1----

1.00 1000

----1------1----

----1------1----

40. 0.0 0.0 01

-46-
4151202 0 14888200. 1576890. 2462360. 0.0 0.0 02

4151203 0 14888600. 1578210. 2462390. 0.0 0.0 03

4151204 0 14884300. 1579040. 2463380. .31381 0.0 04

4151205 0 14882900. 1581860. 2462380. 1.0 0.0 05

4151206 0 14882600. 1581850. 2462350. 1.0 0.0 06

4151300 0

4151301 4.13174-5 4.13174-5 0.0 01

4151302 2.75755-5 2.75755-5 0.0 02

4151303 2.50280-5 .50049 0.0 03

4151304 -. 37026 5.25011-5 0.0 04

4151305 -. 13472 1.81309-5 0.0 05

*-- ---- 1 ---- ------ 1 ------ 1 ------ 1 ------ 1----

* PRESSURIZER VESSEL TO TOP HAT

4170000 "VSSL-TPHAT" SNGLJIUN

4170101 415010000 420000000 0.0 0.0 0.0 0000

4170201 0 -. 19776 3.46367-5 0.0

* -------- 1------ 1 ------ 1 ------ 1 ----1 ------ 1----

* PRESSURIZER TOP HAT AND RELIEF CONNECTION

4200000 "PZR TOPHAT" PIPE

4200001 2

4200101 0.0 2

4200201 0.0 1

4200301 0.1104915 2

4200401 0.0139870 2

4200601 90.0 2

4200801 4.E-5 0.346066 2

4201001 00 2

4201101 0000 1

4201201 0 14882500. 1581850. 2462380. 1.0 0.0 01

4201202 0 14882400. 1581840. 2462380. 1.0 0.0 02

4201300 0

4201301 -. 10996 2.21137-5 0.0 01

* ----.---- 1 ------ 1 ----.-- 1 -----1--- --- 1 ------ 1----

* SPRAY LINE

4300000 "SPRAY " BRANCH

4300001 1 0

4300101 0.0003363 6.322 0.0 0.0 90.0 2.9905

4300102 4.0-5 0.0 00

4300200 0 15067800. 1227770. 2458270. 0.0

4301101 172000000 430000000 0.0 0.0 0.0 0002

4301201 -5.3194-6 -5.3194-6 0.0

* STEAM GENERATOR SECONDARY SIDE

* PRIMARY SEPARATOR

5000000 "SEPARATOR " SEPARATR

5000001 3 0

5000101 0.0 0.4445 0.2425 0.0 90.0 0.4445

5000102 4.E-5 0.2840 00

5000200 0 5222780.0 1161490. 2595710. .89049

5001101 500010000 520000000 0.087745 0.0 0.0 0100

5002101 500000000 505000000 0.087745 0.0 0.0 0100 0.3

5003101 515010000'500000000 0.29187 0.4 0.4 0100

- 47 -
5001201 1.3751 1.4411 0.0

5002201 .53770 .50887 0.0

5003201 2.7804 3.5935 0.0

* -------- 1 -- ---- 1-------- ---- 1 ------ 1------ 1----

* SEPARATOR BYPASS

5030000 "SEPBYPASS " BRANCH

5030001 2 0

5030101 0.0 0.4445 0.4384 0.0 90.0 0.4445

5030102 4.E-5 0.3678 00

5030200 0 5222780.0 1611330. 2595720. .99999

5031101 505000000 503000000 0.98627 0.0 0.0 0100

5032101 503010000 520000000 0.98627 0.8 0.0 0100

5031201 -. 16063 .48006 0.0

5032201 2.38241-2 .17866 0.0

* ---------------- 1 ---- -- 1 ------ 1 ------ 1 ------ 1----

* SEPARATOR OUTLET REGION

5050000 "LWR SEPAR " BRANCH

5050001 1 0

5050101 0.0 1.2131 1.4850 0.0 -90.0 -1.2131

5050102 4.E-5 1.9048 00

5050200 0 5222770.0 1161410. 2595720. .37208

5051101 505010000 508000000 0.0 0.0 0.0 0100

5051201 .47026 -. 47917 0.0

* ----.---- 1 -- ---- ----- ----- ----- ------ 1 ---- * FEED INLET VOLUME

*-----------1-----1----1-----1-. ....-1....

5080000 "UPR DWNCMR" BRANCH

5080001 1 0

5080101 0.0 0.6096 0.22107 0.0 -90.0 -0.6096

5080102 4.E-5 0.163697 00

5080200 0 5228350.0 1094450. 2595690. 0.0

5081101 508010000 510000000 0.0 0.0 0.0 0100

5081201 .58694 .58694 0.0

* ---------------- 1 ---- -- 1 ------ 1 ---- ----------- , STEAM GENERATOR DOWNCOMER

*-----------1-. ....- 1-. ....- 1------..1------1----"

5100000 "DWNCMR " ANNULUS

5100001 3

5100101 0.232 3

5100201 0.0 2

5100301 0.6096 3

5100401 0.0 3

5100601 -90.0 3

5100701 -0.6096 3

5100801 4.E-5 0.10793 3

5100901 0.0 0.0 2

5101001 00 3

5101101 0000 2

5101201 0 5233030.0 1094480. 2595670. 0.0 0.0 01

5101202 0 5237770.0 1095280. 2595640. 0.0 0.0 02

5101203 0 5242510.0 1095650. 2595610. 0.0 0.0 03

5101300 0

5101301 .58704 .58704 0.0 01

5101302 .58714 .58714 0.0 02

* ---------------- 1 ------------ 1 ------ 1 ------ 1----

* JUNCTION FROM DOWNCOMER TO BOILER

*-------1----1------..1------..1----1----1-

-48-
5130000 "DNCNR-BLR " SNGLJUN

5130101 510010000 515000000 0.0 17.5

5130201 0 .58722 .83849 0.0

* ........ 1 ------ 1------ 1 ------ 1----

* STEAM GENERATOR BOILER

*-----------1-----------1------1---

17.5 0100

----1------1----

----1------1----

5150000

5150001

5150101

5150102

5150201

5150301

5150302

5150401

5150601

5150602

5150701

5150702

5150801

5150802

5150901

5151001

5151101

5151201

5151202

5151203

5151204

5151205

5151300

5151301

5151302

5151303

5151304

"BOILER

5

0.2776

0.306294

0.0

1.8288

1.2131

0.0

60.0

90.0

0.6096

1.2131

4.E-5

4. E-5

4.05

00

0100

0

0

0

0

0

0

.94859

1.5589

2.1266

2.6440

it PIPE

4

5

4

4

5

5

4

5

4

5

0.0234

0.5962

4.05

5

4

5241030.0

5237440.0

5233350.0

5232841.0

5237361.0

4

5

4

1154980.

1161810.

1162120.

1161820.

1161540.

2595580.

2595610.

2595650.

2595680.

2595700.

.49316

.71327

.80605

.85407

.87426

0.0

0.0

0.0

0.0

0.0

01

02

03

04

05

1.3289

2.3557

3.3332

4.0529

0.0

0.0

0.0

0.0

01

02

03

04

* LOWER PORTION OF STEAM DOME

5200000 "LWR STM DM" BRANCH

5200001 1 0

5200101 0.0 0.46956 0.705312 0.0

5200102 4.E-5 1.383 00

5200200 0 5219990.0 1161320. 2595680.

5201101 520010000 525000000 0.0 0.0

5201201 .50120 .64094 0.0

* UPPER PORTION OF STEAM DOME

5250000 "UPR STM DM" BRANCH

5250001 1 0

5250101 0.0 0.46956 0.705312 0.0

5250102 4.E-5 1.383 00

5250200 0 5219870.0 1161310. 2595700.

5251101 525010000 530000000 0.0 0.8

5251201 15.687 20.771 0.0

* STEAM PIPE FROM GENERATOR TO CONTROL VALVE

5300000 "STEAM PIPE" SNGLVOL

5300101 0.04635 25.074 0.0 0.0

5300102 4.E-5 0.0 00

--1------1----

--1 1----

90.0

1.0

0.0

0.46956

0100

--1------1----

--1------1----

90.0

1.0

0.8

0.46956

0100

---1------1----

--1------1----

0.0 0.0

- 49 -
5300200 0 5203370.0 1160330. 2595740. .99998

* -----------1 ---- 1 ------ 1 ------ 1 ------ 1 ------ 1----

* STEAM FLOW CONTROL VALVE

5400000 "CV-P4-10 " VALVE

5400101 530010000 541000000 0.0047772 0.0 0.0 1100

5400201 0 16.933 36.097 0.0

5400300 MTRVLV

5400301 685 686 0.05 0.645229 540

20254000 NORMAREA

20254001 0.0 9.25-4

20254002 9.25-4 9.25-4

20254003 1.0 1.0

* -- ---- ----- ----- ----- ------ 1 ---- ------ 1----

* PIPE DOWNSTREAM OF STEAM CONTROL VALVE

5410000 "COND INLET" BRANCH

5410001 1 0

5410101 0.06557 54.44 0.0 0.0 0.0 0.0

5410102 4.E-5 0.0 00

5410200 0 2009650.0 907346. 2597920. .99820

5411101 541010000 542000000 0.0 0.0

5411201 16.933 36.097 0.0

* -------- 1 -- ----1 ----------- 1 ---- * AIR COOLED CONDENSER

*-----------1-. ....- 1----1------1----

5420000 "CONDENSER " TMDPVOL

5420101 0.21677 17.67 0.0 0.0

5420102 4.E-5 0.02 00

5420200 2

5420207 0.0 2.00E6 1.0

*STEAM BYPASS VALVE

5450000 "SM BYPSS " VALVE

5450101 530010000 546000000 3.2-4 0.0

5450201 0 .00000000 .00000000 0.0

5450300 TRPVLV

5450301 687

* ---------------- 1 ------ 1------ 1 ---- * AIR COOLED CONDENSER *-----------1-. ....- 1 .. -- 1

5460000 "CONDENSER " TMDPVOL

5460101 0.21677 17.67 0.0 0.0

5460102 4.E-5 0.02 00

5460200 1 516

5460201 0.0 554.8 0.999

5460202 18000. 332.5 0.999

* ---------------- 1 ----1 ------ 1 ---- * FEED STORAGE TANK

5650000 "FEED TANK " TMDPVOL

5650101 29.81 3.048 0.0 0.0

5650102 4.E-5 0.0 00

5650200 1 689

5650201 -1.0 478.706 0.0

* -------- -------- 1 1 ------ 1 -- ----1----

* FEED WATER

*-------1----1----1----1-

0.0 0100

....- 1----1-

.. ---.-----1-I

0.0 0.0

---- 1----1--

0.0 0100

---- ---- -- 1----

---- 1 ----.--- 1 ----

0.0 0.0

....- 1----1-

....-1----1-

0.0 0.0

....- 1----1-

....- 1----1--

-50-
5660000 "FEED " TtDPJUN

5660101 565000000 508000000 0.05

5660200 1 688

5660201 0.0 25.553 0.0 0.0

5660202 0.7 0.0 0.0 0.0

5660203 59.5 0.0 0.0 0.0.

5660204 60.0 0.50364 0.0 0.0

5660205 1860.0 0.50364 0.0 0.0

5660206 1861.0 0.0 0.0 0.0

* -------- 1-------- 1------ 1 ------ 1 ------ 1 ------ 1----

* AUX FEED STORAGE TANK

5680000 "AUX FD TNK" TMDPVOL

5680101 29.81 3.048 0.0 0.0 0.0 0.0

5680102 4.E-5 0.0 00

5680200 1

5680201 0.0 305.0 0.0

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1 ------ 1----

* AUX FEED WATER

5690000 "AUX FEED " TIiDPJUN

5690101 568000000 508000000 0.05

5690200 1 690

5690201 -1.0 0.00 0.0 0.0

5690202 0.0 0.50364 0.0 0.0

* ECC SYSTEM

*-------1------1------ --- -- 1----1------1-I'

* ECC CHECK VALVE

6000000 "ECC CHKVLV" VALVE

6000101 605010000 185000000 5.9896-3 0.935 0.935 1120

6000201 0 .00000000 .00000000 0.0

6000300 TRPVLV

6000301 681

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1 ------ 1 ---- * ECCS HEADER TO PCS

6050000 "ECGS HEADR" SNGLVOL

6050101 5.9896-3 5.0148 0.0 0.0 90.0 3.3071202

6050102 4.0-5 0.0 01

6050200 0 13595900. 172410. 2489140. 0.0

* ---- ------------------- 1 ------ 1 ------ 1 ------ 1 ----

* ACCUMULATOR VALVE

6100000 "ACCUM VLV " VALVE

6100101 615010000 605000000 5.9896-3 6.278 6.278 1000

6100201 0 0.0 0.0 0.0

6100300 TRPVLV

6100301 682

* -------- ---1- ---- 1 ----------- -1 ------ 1 ------ 1----

* ACCUMULATOR PIPE

6150000 "ACC PIPE " SNGLVOL

6150101 0.0 25.997165 0.4074774 0.0 0.0 0.0

6150102 4.0-5 0.0 01

6150200 0 13580200. 112409. 2489450. 0.0

- 51 -
* . --.--.. 1 -... 1 - 1- 1 . - 1 ---- 1 .......---.---- * ACCUMULATOR VESSEL

*6200000 "ACCUMULATR" ACCUM

*6200101 0.0 1.8103 2.3422 0.0 90.0 1.811

*6200102 4.0-5 0.0 01

*6200200 4.31+6 306.6

*6201101 615000000 8.2132-3 13.3 13.3 0

*6202200 0.0 1.0662 2.4509 1.6927 0.04445 0 0

03

O00

* ----.---- -------- 1 ----.-- 1 ------ 1----

* BWST LPIS

6250000 "BWST LPIS " TMDPVOL

6250101 20.44 5.0 0.0 0.0

6250102 4.OE-5 0.0 00

6250200 3

6250201 0.0 1.0+5 300.0

* ....-.... 1 ---- -------- 1 ------ 1----

* LOW PRESSURE INJECTION SYSTEM

6300000 "LPIS TfDPJUN

6300101 625000000 605000000 5.9896-3

6300200 1 684 P 60501(

6300201 -1.0 0.0 0.0 0.0

6300202 0.0 0.0 0.0 0.0

6300203 8.483+4 7.045 0.0 0.0

6300204 4.297+5 6.091 0.0 0.0

6300205 7.745+5 5.045 0.0 0.0

6300206 9.448+5 4.313 0.0 0.0

6300207 1.119+6 3.454 0.0 0.0

6300208 1.186+6 3.173 0.0 0.0

6300209 1.257+6 2.673 0.0 0.0

6300210 1.326+6 2.159 0.0 0.0

6300211 1.395+6 1.536 0.0 0.0

6300212 1.464+6 0.7182 0.0 0.0

6300213 1.517+6 0.0 0.0 0.0

----1------1----

----1------1----

90.0 5.0

----1------1----

----1------1----

000

* ---- ---- ---- ---- ----- ---- 1------ 1 ------ 1----

* BWST HPIS

6350000 "BWST HPIS " TMDPVOL

6350101 20.44 5.0 0.0 0.0 90.0 5.0

6350102 4.OE-5 0.0 00

6350200 3

6350201 0.0 1.0+5 300.0

* -------- 1 ------ 1 ------ 1 ------ 1------ 1 ------ 1----

* HIGH PRESSURE INJECTION SYSTEM

6400000 "HPIS TMDPJUN

6400101 635000000 185000000 5.9896-3

6400200 1 683 P 185010000

6400201 -1.0 0.0 0.0 0.0

6400202 0.0 .75687272 0.0 0.0

6400203 7.72514+6 .75687272 0.0 0.0

6400204 8.3597+6 .31536281 0.0 0.0

6400205 17.2436+6 .31536281 0.0 0.0

* CONTAINMENT

- 52 -
* --- -- 1 -- -- 1 -- --1 ----- 1 - 1 -- -- 1 -----1---

*CONTAINMENT BROKEN LOOP COLD LEG

8050000 "CONT BLCL "TMDP VOL

8050101 0.0 1.0 0.1 0.0 0.0 0.0

8050102 0.0 0.0 00

8050200 2

8050201 0.0 1.0+5 1.0

RECO*ESLHETSRCUE

*REACTOR VESSEL AL HEAT STRUCTURES

*THE REACTOR VESSEL WALL IS NOT MODELLED ABOVE THE NOZZLES. *THE VESSEL TO FILLER GAP IS ASSUMED TO INSULATE THE VESSEL *FROM THE FILLERS. THE VESSEL TO FILLER GAP IS NOT MODELLED *AT THIS ELEVATION.

*REACTOR VESSEL WALL ABOVE STATION 178 - 5.50 INCHES THICK' *STATION 178 TO 258

12231000

12231100

12231101

12231201

12231301

12231401

12231501

12231502

12231601

12231602

12231701

12231801

12231802

2

0

4

5

0.0

551.0

223010000

223020000

-939

-939

0

0

0

5

1

0.8725

4

4

5

0

0

0

0

0.0

0.0127

0.0127

2 1 0.7328

3949

3949

0.0

0. 1922

0.1922

0.0

1.4218585

0.7621415

1.4218585

0.7621415

1.4218585

0.7621415

2

1

2

1

2

1

2

* ---- ---- 1----1------1-------- 1----

" REACTOR VESSEL WALL BELOW STATION

" STATION 67.7 TO 178

* ---- ---- 1----1------1-------- 1----

---- 1---- ----I--------1 ---- 178 - 3.62 INCHES THICK

---- 1--------1 ---- -- 1-I----

12232000 1 0.7328

12232100

12232101

12232201

12232301

12232401

12232501

12232502

12232503

12232504

12232601

12232602

12232603

12232604

12232701

12232801

12232802

12232803

12232804

4

0

4

5

0.0

553.0

223020000

223030000

223040000

220010000

-939

-939

-939

-939

0

0

0

0

0

5

1

0.8247

4

4

5

0

0

0

0

0

0

0

0

0.0

0. 0127

0.0127

0.0127

0.0127

2

3949

3949

0.0

0.1922

0.1922

0.1922

0.1922

1.

1.309

1.106

0.0712

0.4340098

1.2110867

0.7802975

0.3741720

0.4340098

1.2110867

0.7802975

0.3741720

4

1

2

3

4

1

2

3

4

1

2

3

4

- 53 -
* -1 - 1-1-..--

* REACTOR VESSEL BOTTOM

* STATION 67.7

*-------- 1 ----- ------ 1 ---- 12200000 1 5 1

12200100 0 1

12200101 4 0.092.

12200201 5 4

12200301 0.0 4

12200401 551.0 5

12200501 220010000 0 1

12200601 -939 0 3949

12200701 0 0.0 0.0

12200801 0 0.0 0.0 *-------1----1------1--

* REACTOR VESSEL FILLER BLOCKS HEAT

* INLET ANNULUS TOP VOLUME

* STATION 264 TO 277

12000000 2 5 2

12000100 0 1

12000101 4 0.7264

12000201 4 4

12000301 0.0 4

12000401 556.0 5

12000501 200010000 0 1

12000502 202010000 0 1

12000601 0 0 0

12000602 0 0 0

12000701 0 0.0 0.0

12000801 0 0.1524 0.3247

12000802 0 0.1524 0.3241

* -------- 1 ------ 1 ------ 1----

* INLET ANNULUS LOWER VOLUME

* STATION 247.3 TO 264.0

*-------- 1 ----- ------ 1 ---- 12050000 1 5 2

12050100 0 1

12050101 4 0.7264

12050201 4 4

12050301 0.0 4

12050401 556.0 5

1 0.0

0 1.68 1

0 1.68 1

0.0 1

5.00 1

STRUCTURES

1 0.508

5

5

1 0.1876129 1

1 0.2851823 2

1 0.1876129 1

1 0.2851823 2

0.0 2

0.1876129 1

0.2851823 2 --1------1------1.. --

1 0.501

1 0.2525361 1

1 0.2525361 1

0.0 1

0.2525361 1

0.2525361 1 --1------1-. ....-1--

12050501 205010000 0 1

12050601 223010000 0 1

12050701 0 0.0 0.0

12050801 0 0.1524 0.3245

12050901 0 0.0127 0.0253

*-------- 1 ----- ------ 1 ---- * DOWNCOMER AND LOWER PLENUM

* STATION 67.7 TO 247.3

* -------- -------- 1 1 ------ 1----

12100000 7 5 2

12100100 0 1

12100101 4 0.7264

12100201 4 4

12100301 0.0 4

12100401 556.0 5

12100501 210010000 0 1

---- 1 ------ I----

1 0.47 --1--

1 1.0267313 1

-54-
12100502 210020000 0

12100503 210030000 0

12100504 210040000 0

12100505 210050000 0

12100506 210060000 0

12100507 215010000 0

12100601 223010000 0

12100602 223020000 0

12100603 223020000 0

12100604 223030000 0

12100605 223030000 0

12100606 223040000 0

12100607 223040000 0

12100701 0 0

12100801 0 0

12100802 0 0

12100803 0 0

12100804 0 0

12100805 0 0

12100806 0 0

12100807 0 0

12100901 0 0

12100902 0 0

12100903 0 0

12100904 0 0

12100905 0 0

12100906 0 0

12100907 0 0

*CORE SUPPORT BARREL

*STATION 96.44 TO 27'

12001000 9 5

12001100 0 1

12001101 4 0

12001201 4 4

12001301 0.0 4

12001401 556.0 5

12001501 0 0

12001502 0 0

12001503 0 0

12001504 0 0

12001505 0 0

12001506 0 0

12001507 0 0

12001508 0 0

12001509 0 0

.0

.1016

.1016

.1016

.1016

.1016

.1016

.1016

.0127

.0127

.0127

.0127

.0127

.0127

.0127

0.15

0.15

0.15

0.15

0.15

0.15

0.15

0.025

0.02155

1.

1.271

1.934

1.086

1.586

1.529

1.299

0331 8

0.4299

0.49332483

0.4933248

0.7028265

0. 5588068

0.6522799

0.4269792

0.3533183

1.0267313

0.4933248

0.7028265

0.5588068

0.6522799

0.4269792

0.3533183

7

1

2

3

4

5

6

7

1

2

3

4

5

6

7

2

3

4

5

6

7

1

2

3

4

5

6

7

----- 1 ---- ----I--------1I--------1I----

7

.419

,0

.1016

1016

---- 1--------1 ---- -- 1-I--------1 ---- 2 1 0.381

12001601

12001602

12001603

12001604

12001605

12001606

12001607

12001608

12001609

12001701

12001901

12001902

200010000

202010000

205010000

210010000

210020000

210030000

210040000

210050000

210060000

0

0

0

0

0

0

0

0

0

0

0

0

0.

0.

0.

0

0

0

0

0

0

0

0

0

0.15

0.15

1

1

1

1

1

1

1

1

1

1

1

1

1

1

1

1

1

1

0.0

0.1876129

0.2851823

0.1876129

0.2851823

0.2525361

1.0267313

0.4933248

0.7028265

0.5588068

0.6522799

0.4269792

0.1876129

0.2851823

0.2525361

1.0267313

0.4933248

0.7028265

0.5588068

0.6522799

0.4269792

9

1

2

- 55 -
12001903 0 0.1016 0.2155 0.2525361 3

12001904 0 0.1016 0.2155 1.0267313 4

12001905 0 0.1016 0.2155 0.4933248 5

12001906 0 0.1016 0.2155 0.7028265 6

12001907 0 0.1016 0.2155 0.5588068 7

12001908 0 0.1016 0.2155 0.6522799 8

12001909 0 0.1016 0.2155 0.4369792 9

* ------------ 1--- ---1 I-------1 I-------1 I-------1 I--------1 ----

" FLOW SKIRT - CORE FILLER ASSEMBLY

" STATION 96.44 TO 261.13

* ---- ---- 1----1 ---1------ -- --I----1------1-------- 1-------- 1----

12250000 10 5 2 1 0.3

12250100 0 1

12250101 4 0.38

12250201 4 4

12250301 0.0 4

12250401 575.0 5

12250501 225010000 0 1 1 0.4269792 1

12250502 230010000 0 1 1 0.3728765 2

12250503 230020000 10000 1 1 0.2794034 6

12250504 230060000 0 1 1 0.4234231 7

12250505 240010000 5000000 1 1 0.4933248 9

12250506 250010000 0 1 1 0.7850547 10

12250601 0 0 0 1 0.4269792 1

12250602 0 0 0 1 0.3728765 2

12250603 0 0 0 1 0.2794034 6

12250604 0 0 0 1 0.4234231 7

12250605 0 0 0 1 0.4933248 9

12250606 0 0 0 1 0.7850547 10

12250701 0 0.0 0.0 0.0 10

12250801 0 0.095 0.095 0.4269792 1

12250802 0 0.0124 0.5713 0.3728765 2

12250803 0 0.0124 0.5713 0.2794034 6

12250804 0 0.0124 0.5713 0.4234231 7

12250805 0 0.145 0.5713 0.4933248 9

12250806 0 0.131 0.5713 0.7850547 10

* ---- ---- I----1-- - 11------ ------- -- --1----1------1--------1I----

" LOWER CORE SUPPORT STRUCTURE

" STATION 96.44 TO 116.91

* INCLUDES CORE SUPPORT BARREL LIP ,LOWER CORE SUPPORT

" STRUCTURE , AND FUEL MODULE LOWER END BOXES

* ------------ 1--- --- I-------1 1 I--------1 ---- -- 1-I--------1 ----

12251000 1 5 2 1 0.282

12251100 0 1

12251101 4 0.3

12251201 4 4

12251301 0.0 4

12251401 556.0 5

12251501 225010000 0 1 1 0.4269792 1

12251601 0 0 0 1 0.4269792 1

12251701 0 0.0 0.0 0.0 1

12251801 0 0.095 0.095 0.4269792 1

" ACTIVE CORE

" STAITION 116.91 TO 182.94

*----------- 1--------1-------- 1--------1I------1--I------- 1----

12300000 6 10 2 1 0.0

12300100 0 1

12300101 5 4.647E-3

- 56 -
12300102 1

12300103 3

12300201 1

12300202 -2

12300203 -3

12300301 1.0

12300302 0.0

12300401 575.0

12300501 0

12300601 23001

12300701 900

12300702 900

12300703 900

12300704 900

12300705 900

12300706 900

12300901 0

* ----------- 1----

0

4.742E-3

5.359E-3

5

6

9

5

9

10

0

000 10000

0.13599

0.22454

0.24293

0.2152

0.1419

0.0397

0.01240 --- 1----

0

1

0.0

0.0

0.0

0.0

0.0

0.0

0.0151

--1 ----

1

1

0.0

0.0

0.0

0.0 0.0

0.0

14 1.775 ---- 1----

363.35 6

363.35 6

1 * 100% POWER

2 * 100% POWER

3 * 100% POWER

4 * 100% POWER

5 * 100% POWER

6 * 100% POWER

6 --- 1- -1

* UPPER CORE SUPPORT STRUCTURE

* STATION 190.5 TO 234.5

* -------- 1 ------ 1------

12400000 2 5

12400100 0 1

12400101 4 0.31

12400201 4 4

12400301 0.0 4

12400401 575.0 5

12400501 240010000 5000000

12400601 0 0

12400701 0 0.0

12400801 0 0.56

* ----.-------- 1 ---- 1--- --- * FUEL MODULES

* STATION 187.6 TO 258.4

* -------- 1 ------ 1------

12510000 1 5

12510100 0 1

12510101 4 0.01

12510201 4 4

12510301 0.0 4

12510401 575.0 5

12510501 250010000 0

12510601 251010000 0

12510701 0 0.0

12510801 0 0.0

12510901 0 0.0

* -------- 1 ------ 1 ------ * UPPER PLENUM INTERNALS

12551000 3 5

12551100 0 1

12551101 4 0.005

12551201 4 4

12551301 0.0 4

12551401 575.0 5

12551501 252010000 0

12551502 255010000 0

12551503 250010000 0 3

12551601 0 0 (

1 .... 1 ------ 1 ------ 1----

2 1 0.282

1

0

).0

0.0 I1 --

1

1

0.0

0.9866496 ----1I---- ---

0.4933248

0.4933248

2

2

-1 . .

2

2

-1----

1 ------ 1------ 1 ------ 1----

1 1 0.0

I

0.0

0.0 ).O

....-

1

1

1.8

1.8

1.8

--1 ----

1.8

1.8

1

1

1

1

1

----1----

L------1 ---- ------ 1----

1 1 0.0

I

L

1

1

1

1

1.0

1.0

1.0

1.0

1

2

3

3

- 57 -
12551701 0 0.0 0.0 0.0 3

12551801 0 0.0 0.0 1.0 3

" CORE SUPPORT BARREL - UPPER PLENUM LOWER VOLUME

" STATION 264 TO 297.6

12552000 2 5 2 1 0.381

12552100 0 1

12552101 4 0.474

12552201 5 4

12552301 0.0 4

12552401 575.0 5

12552501 255010000 0 1 1 0.6312304 1

12552502 252010000 0 1 1 0.2869580 2

12552601 0 0 0 1 0.6312304 1

12552602 0 0 0 1 0.2869580 2

12552701 0 0.0 0.0 0.0 2

12552801 0 0.762 0.0 0.6312304 1

12552802 0 0.762 0.0 0.2869580 2

" CORE SUPPORT BARREL - UPPER PLENUM TOP VOLUME

" STATION 297.6 TO 325

12601000 1 5 2 1 0.381

12601100 0 1

12601101 4 0.728

12601201 5 4

12601301 0.0 4

12601401 575.0 5

12601501 260010000 0 1 1 0.7747094 1

12601601 0 0 0 1 0.7747094 1

12601701 0 0.0 0.0 0.0 1

12601801 0 0.762 0.0 0.7747094 1

* UPPER HEAD TOP PLATE

* STATION 325

12602000 1 5 1 1 0.0

12602100 0 1

12602101 4 0.474

12602201 5 4

12602301 0.0 4

12602401 560.0 5

12602501 260010000 0 1 1 0.712 1

12602601 -939 0 3949 1 0.712 1

12602701 0 0.0 0.0 0.0 1

12602801 0 0.0 0.0 0.712 1

* STEAM GENERATOR HEAT STRUCTURES

*TUBING

10060000 8 8 2 1 0.0051054

10060100 0 1

10060101 7 0.006348984

10060201 6 7

10060301 0.0 7

- 58 -
10060401 551.0 8

10060501 115010000 10000 1

10060502 115040000 10000 1

10060503 115060000 10000 1

10060601 515010000 10000 1

10060602 515040000 0 1

10060603 515040000 0 1

10060604 515030000 -10000 1

10060701 0 0 0

10060801 0 0 0

10060901 0 0 0

* ---- ---- 1----1------1--------1I----

*SHROUD -UPPER SECTION

1

1

0

1124.71 3

849.063 5

.1124.71 8

1124.71 3

849.063 4

849.063 5

1124.71 8

8

8

8

--1------

15000000 2 4

15000100 0 1

15000101 3 0.314

15000201 5 3

15000301 0.0 3

15000401 539.0 4

15000501 500010000 0

15000502 515050000 0

15000601 503010000 0

15000602 505010000 0

15000701 0 0.0

15000801 0 0.0

15000901 0 0.0

*----------- 1--------1 ----

*SHROUD - LOWER SECTION

15100000 4 4

15100100 0 1

15100101 3 0.6572

15100201 5 3

15100301 0.0 3

15100401 533.0 4

15100501 515040000 0

15100502 515030000 -10000

15100601 508010000 0

15100602 510010000 10000

15100701 0 0.0

15100801 0 0.0

15100901 0 0.0

*----------- 1---- -- 1-I----

* VESSEL WALL

3

2 ---- 1---- -- 1-I--------1 ---- 1 0.3048

0.0

0.0

--1 ----

0

0

0

0

0.0

0.0

0.0

0.85127 1

2.51199 2

0.87780 1

2.59028 2

2

2

2

I--------

---- 1--------1 -------- 1 -------- 1 ---- 2 1 0.6445

0.0

0.0

1

0

1

0

0.0

0.0

0.0

0.646354 1

2.46858 4

0.646354 1

2.51723 4

4

4

4

--1------

*----------- 1---- --

15250000 8

15250100 0

15250101 4

15250201 5

15250301 0.0

15250401 540.0

15250501 525010000

15250502 520010000

15250503 503010000

15250504 505010000

15250505 508010000

15250506 510010000

15250601 -939

5

1

0. 76397

4

4

5

0

0

0

0

0

10000'

0

--- 1--------1 ---- -- 1-I--------1 ---- 2 1 0.7112

1

1

1

1

1

1

3959

1

1

1

1

1

1

1

0.46956

0.46956

0.4445

1.2131

0.6096

0.6096

0.46956

1

2

3

4

5

8

1

- 59 -
15250602 -939 0 3959 1 0.46956 2

15250603 -939 0 3959 1 0.4445 3

15250604 -939 0 3959 1 1.2131 4

15250605 -939 0 3959 1 0.6096 5

15250606 -939 0 3959 1 0.6096 8

15250701 0 0.0 0.0 0.0 8

15250801 0 0.0 0.0 0.0 8

*PIPING HEAT STRUCTURES

*INTACT LOOP PIPING

*.284 METER DIAMETER PIPING

1100-----1000 -- 1-----5-2

11001100 0 14

11001101 4 0.1780

11001201 4 4

11001301 0.0 4

11001401 560.0 5

11001501 100010000 0 1

11001502 105010000 0 1

11001503 107010000 0 1

11001504 110010000 0 1

11001505 112010000 0 1

11001506 118020000 0 1

11001507 118030000 0 1

11001508 120010000 0 1

11001509 150010000 0 1

11001510 172010000 0 1

11001511 175010000 0 1

11001512 175020000 0 1

11001513 180010000 0 1

11001514 185010000 0 1

11001601 -939 0 3949

11001602 -939 0 3949

11001603 -939 0 3949

11001604 -939 0 3949

11001605 -939 0 3949

11001606 -939 0 3949

11001607 -939 0 3949

11001608 -939 0 3949

11001609 -939 0 3949

11001610 -939 0 3949

11001611 -939 0 3949

11001612 -939 0 3949

11001613 -939 0 3949

11001614 -939 0 3949

11001701 0 0 0

11001801 0 0 0

11001802 0 0 0

11001803 0 0 0

11001804 0 0 0

11001805 0 0 0

11001806 0 0 0

11001807 0 0 0

11001808 0 0 0

1 0.142

1

1.87

1.519

02101

1.279

1.89

1.889

1.587

07914

1.58878

1.0531192

0.2810215

0.9207292

1.38893

0. 688596

0.558577

0. 759614

0.3542995

0.2844229

0.4163655

0.613244

1.15189

1.00965

1.58878

1.0531192

0.2810215

0.9207292

1.38893

0. 688596

0.558577

0.759614

0.3542995

0.2844229

0.4163655

0.613244

1.15189

1.00965

14

1

2

3

4

5

6

7

8

1

2

3

4

5

6

7

8

9

10

11

12

13

14

1

2

3

4

5

6

7

8

9

10

11

12

13

14

- 60 -
11001809 0 0 0

11001810 0 0 0

11001811 0 0 0

11001812 0 0 0

11001813 0 0 0

11001814 0 0 0

*STEAM GENERATOR CONNECTIONS

11002000 2 5 2

11002100 0 1

11002101 4 0.203

11002201 4 4

11002301 0.0 4

11002401 560.0 5

11002501 112020000 0 1

11002502 118010000 0 1

11002601 -939 0 3949

11002602 -939 0 3949

11002701 0 0 0

11002801 0 0 0

11002802 0 0 0

* ---- ---- 1----1------1-------- 1----

*.216 METER DIAMETER PIPING

11003000 7 5 2

11003100 0 1

11003101 4 0.1365

11003201 4 4

11003301 0.0 4

11003401 560.0 5

11003501 125010000 0 1

11003502 130010000 0 1

11003503 140010000 0 1

11003504 145010000 0 1

11003505 155010000 0 1

11003506 160010000 01

11003507 170010000 0 1

11003601 -939 0 3949

11003602 -939 0 3949

11003603 -939 0 3949

11003604 -939 0 3949

11003605 -939 0 3949

11003606 -939 0 3949

11003607 -939 0 3949

11003701 0 0 0

11003801 0 0 0

11003802 0 0 0

11003803 0 0 0

11003804 0 0 0

11003805 0 0 0

11003806 0 0 0

11003807 0 0 0

* ---- ---- 1----1------1-------- 1----

0.3542995 9

0.2844229 10

0.4163655 11

0.613244 12

1.15189 ,13

1.00965 14

1 0.1625

1 0.707687

1 0.546638

1 0.707687

1 0.546638

0 2

0.707687 1

0.546638 2

1

2

1

2

--1----

1 0.108

1

1

1

1

1

1

1

1

1

1

1

1

1

1

0

1.00308

1. 00308

0.457201

0.502185

1.40843

1.00308

0.457201

0.514071

1. 00308

0.457201

0.502185

1.40843

1.00308

0.457201

0.514071

7

1

1

2

3

4

5

6

7

1

2

3

4

5

6

7

0.457201 2

0.502185 3

1.40843 4

1.00308 5

0.457201 6

0.514071 7

*STEAM GENERATOR PLENA

11004000 2 5 3 1 0.6858

11004100 0 1

11004101 4 0.7747

- 61 -
11004201 5 4

11004301 0.0 4

11004401 560.0 5

11004501 114010000 0 1

11004502 116010000 0 1

11004601 -939 0 3949

1100460Z -939 0 3949

11004701 0 0 0

11004801 0 0 0

11004802 0 0 0

11004901 0 0 0

*BROKEN LOOP HOT LEG PIPING

*NOZZLE PIPING

13000000 3 5 2

13000100 0 1

13000101 4 0.1780

13000201 4 4

13000301 0.0 4

13000401 560.0 5

13000501 300010000 0 1

13000502 305010000 0 1

13000503 310010000 0 1

13000601 -939 0 3949

13000602 -939 0 3949

13000603 -939 0 3949

13000701 0 0 0

13000801 0 0 0

13000802 0 0 0

13000803 0 0 0

* ---- ---- 1----1------1-------- 1----

*INLET TO STM GEN SIMULATOR

13151000 3 5 2

13151100 0 1

13151101 4 0.0705

13151201 4 4

13151301 0.0 4

13151401 545.0 5

13151501 310010000 0 1

13151502 315010000 0 1

13151503 315020000 0 1

13151601 -939 0 3949

13151602 -939 0 3949

13151603 -939 0 3949

13151701 0 0 0

13151801 0 0 0

13151802 0 0 0

13151803 0 0 0

* ---- ---- 1----1------1-------- 1----

*STEAM GENERATOR SIMULATOR

13152000 6 5 2

13152100 0 1

13152101 4 0.2285

13152201 4 4

13152301 0.0 4

0

0.630

0.630

0.630

0.25 1

0.25 2

0.25 1

0.25 2

2

1

2

2

- I-------

1 0.1420

1 0.876303 1

1 0.698336 2

1 0.974349 3

1 0.876303 1

1 0.698336 2

1 0.974349 3

0 3

0.876303 1

0.698336 2

0.974349 3

1 0.0515

1 0.525781 1

1 0.367768 2

1 0.552201 3

1 0.525781 1

1 0.367768 2

1 0.552201 3

0 3

0.525781 1

0.36768 2

0.552201 3

1 0.1835

- 6z -
13152401 545.0 5

13152501 315030000 10000

13152502 315050000 10000

13152503 315070000 10000

13152601 -939 0

13152602 -939 0

13152603 -939 0

13152701 0 0

13152801 0 0

13152802 0 0

13152803 0 0

*------ ---- I--1------ 1----

3949

3949

3949

0

0

0

0

1 0.993978

1 0.849744

1 0.993978

1 0.993978

1 0.849744

1 0.993978

0 6

0.993978 2

0.849744 4

0.993978 6

I----1------1-------

2

4

6

2

4

6

*-1----

*STm GEN SIMULATOR OUTLET

13153000 1 5 2 1 0.0550

13153100 0 1

13153101 4 0.0705

13153201 4 4

13153301 0.0 4

13153401 545.0 5

13153501 315090000 0 1 1 1.371350 1

13153601 -939 0 3949 1 1.371350 1

13153701 0 0 0 0 1

13153801 0 0 0 1.371350 1

*----------- 1--------1--------1I---------1-------- 1--------1----

*PUMP SIMULATOR

13154000 1 5 2 1 0.1420

13154100 0 1

13154101 4 0.1780

13154201 4 4

13154301 0.0 4

13154401 545.0 5

13154501 315100000 0 1 1 1.365029 1

13154601 -939 0 3949 1 1.365029 1

13154701 0 0 0 0 1

13154801 0 0 0 1.365029 1

* ---- ---- 1----1-- -11------ ------- -- --1----1------1--------1I----

*PUMP SIM4ULATOR OUTLET

13155000 1 5 2 1 0.0660

13155100 0 1

13155101 4 0.0840

13155201 4 4

13155301 0.0 4

13155401 545.0 5

13155501 315110000 0 1 1 1.674812 1

13155601 -939 0 3949 1 1.674812 1

13155701 0 0 0 0 1

13155801 0 0 0 1.674812 1

* ---- ---- 1----1------1-------- 1-------- 1-------- 1-------- 1---- *PIPING BETWEEN BREAK AND ISOLATION VALVE

13156000 1 5 2 1 0.1285

13156100 0 1

13156101 4 0.1620

13156201 4 4

13156301 0.0 4

13156401 545.0 5

-63 -
13156501 315120000 0 1 1 0.545209 1

13156601 -939 0 3949 1 0.545209 1

13156701 0 0 0 0 1

13156801 0 0 0 0.545209 1

* ---- ---- I----1-- -11------ ------- -- --1----1------1-------- 1----

*BROKEN LOOP COLD LEG PIPING

*NOZZLE PIPING

13350000 3 5 2 1 0.1420

13350100 0 1

13350101 4 0.1780

13350201 4 4

13350301 0.0 4

13350401 550.0 5

13350501 335010000 0 1 1 0.749305 1

13350502 340010000 0 1 1 0.698336 2

13350503 345010000 0 1 1 0.974349 3

13350601 -939 0 3949 1 0.749305 1

13350602 -939 0 3949 1 0.698336 2

13350603 -939 0 3949 1 0.974349 3

13350701 0 0 0 0 3

13350801 0 0 0 0.749305 1

13350802 0 0 0 0.698336 2

13350803 0 0 0 0.974349 3

* ---- ---- 1----1------1-------- 1-------- 1-------- 1-------- 1----

*SMALL PIPING NEAR BREAK

13501000 1 5 2 1 0.0550

13501100 0 1

13501101 4 0.1780

13501201 4 4

13501301 0.0 4

13501401 545.0 5

13501501 345010000 0 1 1 0.5Z5781 1

13501601 -939 0 3949 1 0.525781 1

13501701 0 0 0 0 1

13501801 0 0 0 0.525781 1

* ---- ---- 1----1-- -11------ ------- -- --I----1------1-------- 1----

*PIPING BETWEEN BREAK AND ISOLATION VALVE

13502000 2 5 2 1 0.0865

13502100 0 1

13502101 4 0.1095

13502201 4 4

13502301 0.0 4

13502401 545.0 5

13502501 350010000 0 1 1 0.453394 1

13502502 350020000 0 1 1 1.074803 2

13502601 -939 0 3949 1 0.453394 1

13502602 -939 0 3949 1 1.074803 2

13502701 0 0 0 0 2

13502801 0 0 0 0.453394 1

13502802 0 0 0 1.074803 2

*----------- 1--------1 ---- -- 1-- I-- -- I----1------1--------1----

*REFLOOD ASSIST PIPING AND VALVES

13700000 6 5 2 1 0.111

13700100 0 1

-64 -
13700101 4 0.1365

13700201 4 4

13700301 0.0 4

13700401 550.0 5

13700501 370010000 0 1 1 0.7251 1

13700502 370020000 0 1 1 1.8200 2

13700503 370030000 0 1 1 2.9055 3

13700504 380010000 0 1 1 2.2898 4

13700505 380020000 0 1 1 1.2231 5

13700506 380030000 0 1 1 1.1065 6

13700601 -939 0 3949 10.7251 1

13700602 -939 0 3949 1 1.8200 2

13700603 -939 0 3949 1 2.9055 3

13700604 -939 0 3949 1 2.2898 4

13700605 -939 0 3949 1 1.2231 5

13700606 -939 0 3949 1 1.1065 6

13700701 0 0 0 0 6

13700801 0 0 0 0.7246 1

13700802 0 0 0 1.820 2

13700803 0 0 0 1.7230 3

13700804 0 0 0 1.144 4

13700805 0 0 0 1.181 5

13700806 0 0 0 1.2586 6

*PRESSURIZER HlEAT STRUCTURES

* ---- ---- I----1------1-------- 1----

*VESSEL BOTTOM

14151000---1----1---1--

14151000 1 51

14151101 4 0.0762

14151201 5 4

14151301 0.0 4

14151401 613.0 5

1 0.0

14151501 415010000 0 1 1

14151601 -939 0 3969 1

14151701 0 0 0 0

14151801 0 0.0 0.0 0.0

* ---- ---- 1----1------1-------- 1-------- 1----

*VESSEL SIDES - LARGE DIAMETER SECTION

14152000 6 5 2 1

0.362 1

0.362 1

1

1 ----1---- ----1----

0. 42291

14152100

14152101

14152201

14152301

14152401

14152501

14152502

14152503

14152504

14152505

14152506

14152601

14152602

14152603

14152604

0

4

5

0.0

613.0

415010000

415020000

415030000

415040000

415050000

415060000

_939

-939

-939

-939

1

0.49911

4

4

5

0

0

0

0

0

0

0

0

0

0

196

3969

1

1

1

1

1

1

1

1

1

1

0.1815

0.1524

0.3967

0. 5289

0.3967

0.1943

0. 1815

0.1524

0.3967

0.5289

1

2

3

4

5

6

1

2

3

4

- 65 -
14152605 -939 0 3969 1

14152606 -939 0 3969 1

14152701 0 0 0 0

14152801 0 0.0 0.0 0.0

* -------- 1 ------ 1------ 1------ 1----

* VESSEL SIDES - SMALL DIAMETER SECTION

14153000 2 5 2 1

14153100 0 1

14153101 4 0.3683

14153201 5 4

14153301 0.0 4

14153401 613.0 5

14153501 420010000 10000 1 1

14153601 -939 0 3969 1

14153701 0 0 0 0

14153801 0 0.0 0.0 0.0

* ---- ----.--- ---- 1 ---- ------ 1----

* VESSEL TOP

14201000 1 5 1 1

14201100 0 1

0.3967 5

0.1943 6

6

6

0.2032

0.1029 2

0.1029 2

2

2

--1------

0.0 .... 1....

14201101 4 0.18415

14201201 5 4

14201301 0.0 4

14201401 613.0 5

14201501 420020000 0 1 1 0.13 1

14201601 -939 0 3969 1 0.13 1

14201701 0 0 0 0 1

14201801 0 0.0 0.0 0.0 1

* HEAT STRUCTURE THIERMAL PROPERTY DATA

* -------------- 1 ------ 1 ---- 20100100 TBL/FCTN 1 1

20100200 TBL/FCTN 1 1

20100300 TBL/FCTN 1 1

20100400 TBL/FCTN 1 1

20100500 C-STEEL

20100600 TBL/FCTN 1 1

* ----.---- 1 ---- 1------ 1----

* U02 - THERMAL CONDUCTIVITY

20100101 2.7315E2 8.44

20100102 4.1667E2 6.46

20100103 5.3315E2 5.782385

20100104 6.99817E2 4.633177

20100105 8.66483E2 3.880307

20100106 1.03315E3 3.357625

20100107 1.08871E3 3.155129

20100108 1.19982E3 2.983787

20100109 1.28315E3 2.836674

20100110 1.36648E3 2.713792

20100111 1.53315E3 2.521680

20100112 1.61648E3 2.448990

20100113 1.69982E3 2.391875

20100114 1.97759E3 2.289762

20100115 2.25537E3 2.307069

* U02

* GAP

* ZR

* S-STEEL

* INCONEL 600 ....-1------1------..1"-

---. 1---- 1-. ....-1"-

-66-
20100116 2.53315E3 2.433413

20100117 2.81093E3 2.661870

20100118 3.08871E3 2.994171

* U02 - VOLUMETRIC HEAT CAPACITY

20100151 2.73150E2 2.310427E6

20100152 3.23150E2 2.571985E6

20100153 3.73150E2 2.746357E6

20100154 6.7315E2 3.138694E6

20100155 1.37315E3 3.443844E6

20100156 1.77315E3 3.531030E6

20100157 1.97315E3 3.792588E6

20100158 2.17315E3 4.228518E6

20100159 2.37315E3 4.882412E6

20100160 2.67315E3 6.015829E6

20100161 2.77315E3 6.320980E6

20100162 2.87315E3 6.582538E6

20100163 2.97315E3 6.713317E6

20100164 3.11315E3 6.800503E6

20100165 4.69982E3 6.800503E6

* GAP - THERMAL CONDUCTIVITY

20100201 273.15 0.14

20100202 590.0 0.24

20100203 810.0 0.29

20100204 1090.0 0.36

20100205 1370.0 0.42

20100206 3260.0 0.75

* GAP - VOLUMETRIC HEAT CAPACITY

20100251 273.15 5.4

20100252 3260.0 5.4

* ZIRCALOY-4 - THERMAL CONDUCTIVITY FROM IIATPRO

*----------1----1 ----------- 1----1------1--

20100301 380.4 13.6

20100302 469.3 14.6

20100303 577.6 15.8

20100304 685.9 17.3

20100305 774.8 18.4

20100306 872.0 19.8

20100307 973.2' 21.8

20100308 1073.2 23.2

20100309 1123.2 25.4

20100310 1152.3 24.2

20100311 1232.2 25.5

20100312 1331.2 26.6

20100313 1404.2 28.2

20100314 1576.2 33.0

20100315 1625.2 36.7

20100316 1755.2 41.2

20100317 2273.2 55.0

* ZIRCRLOY-4 - VOLUMETRIC HEAT CAPACITY FROM KATPRO

*-2010035 1 300. .1-.----1E1 1 ---- 20100351 300.0 1.841E6

- 67 -
20100352 400.0 1.978E6

20100353 640.0 2.168E6

20100354 1090.0 2.456E6

20100355 1093.0 3.288E6

20100356 1113.0 3.865E6

20100357 1133.0 4.028E6

20100358 1153.0 4.709E6

20100359 1173.0 5.345E6

20100360 1193.0 5.044E6

20100361 1213.0 4.054E6

20100362 1233.0 3.072E6

20100363 1243.0 2.332E6

20100364 1477.0 2.332E6

* S-STEEL - THERMAL CONDUCTIVITY

20100401 273.15 12.98

20100402 1199.82 25.1

* S-STEEL - VOLUMETRIC HEAT CAPACITY

20100451 273.15 3.83E6

20100452 366.5 3.83E6

20100453 477.59 4.190E6

20100454 588.59 4.336E6

20100455 699.82 4.504E6

20100456 810.93 4.639E6

20100457 922.04 4.773E6

20100458 1144.26 5.076E6

20100459 1366.5 5.376E6

20100460 1477.59 5.546E6

* INCONEL-600 - THERMAL CONDUCTIVITY

20100601 366.5 13.85

20100602 477.6 15.92

20100603 588.7 18.17

20100604 700.0 20.42

20100605 810.9 22.50

20100606 922.0 24.92

20100607 1033.2 26.83

20100608 1144.3 29.42

20100609 1477.6 36.06

* INCONEL-600 - VOLUMETRIC HEAT CAPACITY

20100651 366M5 3.908+6

20100652 477.6 4.084+6

20100653 588.7 4.260+6

20100654 700.0 4.436+6

20100656 810.9 4.665+6

20100657 922.0 4.929+6

20100658 1033.2 5.105+6

20100659 1477.6 5.727+6

* CONTROL VARIABLES

-68-
* 001-006 LEVEL CALCULATORS

* 001 STEAM GENERATOR LEVEL

20500100 SGLVL SUM 1.0 0.0 1

20500101 0.0 0.4445 VOIDF 503010000

20500102 1.2131 VOIDF 505010000

20500103 0.6096 VOIDF 508010000

20500104 0.6096 VOIDF 510010000

20500105 0.6096 VOIDF 510020000

20500106 0.6096 VOIDF 510030000

* 002 PRESSURIZER LEVEL

20500200 PZRLVL SUM 1.0 0.0 1

20500201 0.0 0.1815 VOIDF 415010000

20500202 0.1524 VOIDF 415020000

20500203 0.3967 VOIDF 415030000

20500204 0.5289 VOIDF 415040000

20500205 0.3967 VOIDF 415050000

20500206 0.1943 VOIDF 415060000

20500207 0.1029 VOIDF 420010000

20500208 0.1029 VOIDF 420020000

* 004 ACCUM4ULATOR LEVEL

*20500400 ACCMLVL INTEGRAL -6.3480-3 2.0447 0

*20500401 VELFJ 620010000

* 061-072 PRIMARY SYSTEM MASS CALCULATOR

* 061 INTACT LOOP HOT LEG MASS

20506100 ILHLMASS SUM 1.0 0.0 1

20506101 0.0 0.102752 RHO 100010000

20506102 7.57291-2 RHO 105010000

20506103 6.43178-2 RHO 110010000

20506104 7.96973-2 RHO 112010000

20506105 5.79614-2 RHO 112020000

* 062 STEAM GENERATOR PRIMARY MASS

20506200 SGPRIM/SS SUM 1.0 0.0

20506201 0.0 0.335320 RHO 114010000

20506202 0.136356 RHO 115010000

20506203 9.21538-2 RHO 115020000

20506204 9.21538-2 RHO 115030000

20506205 6.99783-2 RHO 115040000

20506206 6.99783-2 RHO 115050000

20506207 9.21538-2 RHO 115060000

20506208 9.21538-2 RHO 115070000

20506209 0.136356 RHO 115080000

20506210 0.335320 RHO 116010000

* 063 PUMP SUCTION PIPING MASS

20506300 PMPSUMASS SUM 1.0 0.0

20506301 0.0 4.45625-2 RHO 118010000

20506302 4.45137-2 RHO 118020000

20506303 3.54278-2 RHO 118030000

20506304 4.87901-2 RHO 120010000

20506305 6.40548-2 RHO 125010000

20506306 1.77444-2 RHO 130010000

20506307 6.40548-2 RHO 155010000

20506308 1.77444-2 RHO 160010000

* 064 INTACT LOOP COLD LEG MASS

20506400 ILCLMASS SUM 1.0 0.0 1

20506401 0.0 9.91000-2 RHO 135010000

20506402 1.83849-2 RHO 140010000

- 69 -
20506403 6.33861-2 RHO 145010000 20506404 3.16011-2 RHO 150010000 20506405 9.91000-2 RHO 165010000 20506406 1.92958-2 RHO 170010000 20506407 3.54280-2 RHO 175010000 20506408 3.88950-2 RHO 175020000 20506409 7.30598-2 RHO 180010000 20506410 6.44920-2 RHO 185010000 * 065 DOWNCOMER/LOWER PLENUM MASS

20506500 DCLPMASS SUM 1.0 0.0 20506501 0.0 0.0864164 RHO 200010000 20506502 0.0907360 RHO 205010000 20506503 0.1509710 RHO 210010000 20506504 0.0706690 RHO 210020000 20506505 0.1060015 RHO 210030000 20506506 0.0795138 RHO 210040000 20506507 0.0998947 RHO 210050000 20506508 0.06252 RHO 210060000 20506509 0.24520 RHO 215010000 20506510 0.29656 RHO 220010000 * 066 REACTOR VESSEL FILLER GAP MASS

20506600 FOAPMASS SUM 1.0 0.0 20506601 0.0 0.0899085 RHO 223010000 20506602 0.0722790 RHO 223020000 20506603 0.0334096 RHO 223030000 20506604 0.03098 RHO 223040000 * 067 CORE/UPPER PLENUM MASS

20506700 CRUPMASS SUM 1.0 0.0 20506701 0.0 0.12094 RHO 225010000 20506702 0.0683340 RHO 230010000 20506703 0.0478582 RHO 230020000 20506704 0.0483329 RHO 230030000 20506705 0.0479138 RHO 230040000 20506706 0.0479052 RHO 230050000 20506707 0.0750459 RHO 230060000

20506708 0.0091280 RHO 235010000 20506709 0.0072325 RHO 235020000 20506710 0.0088095 RHO 235030000 20506711 0.1195494 RHO 240010000 20506712 0.1280806 RHO 245010000 20506713 0.1436936 RHO 250010000 20506714 0.1154214 RHO 251010000 20506715 0.2031741 RHO 255010000 20506716 0.1914909 RHO 260010000 * 068 BROKEN LOOP HOT LEG MASS

20506800 BLHLMASS SUM 1.0 0.0 20506801 0.0 5.75410-2 RHO 300010000 20506802 4.42927-2 RHO 305010000 20506803 6.78467-2 RHO 310010000 20506804 3.07670-3 RHO 315010000 20506805 4.67621-3 RHO 315020000 20506806 8.60554-2 RHO 315030000 20506807 8.60554-2 RHO 315040000 20506808 8.97552-2 RHO 315050000 20506809 8.97552-2 RHO 315060000 20506810 8.60554-2 RHO 315070000 20506811 8.60554-2 RHO 315080000 20506812 1.82303-2 RHO 315090000 20506813 5.46687-2 RHO 315100000

- 70 -
20506814 1.82489-2 RHO 31511'

20506815 2.83241-2 RHO 31512'

20506816 9.15000-2 RHO 380011

20506817 4.80000-2 RHO 380021

20506818 4.89000-2 RHO 380034

* 069 BROKEN LOOP COLD LEG MASS

20506900 BLCLMASS SUM 1.0 0.0

20506901 0.0 4.79790-2 RHO 335011

20506902 4.43927-2 RHO 340011

20506903 6.73163-2 RHO 345011

20506904 1.06640-2 RHO 350011

20506905 4.07801-2 RHO 350021

20506906 2.97722-2 RHO 360011

20506907 2.79000-2 RHO 370011

20506908 7.00000-2 RHO 370024

20506909 1.16500-1 RHO 370031

* 070 PRESSURIZER MASS

20507000 PZRMASS SUM 1.0 0.0

20507001 0.0 3.33500-3 RHO 400014

20507002 3.33500-3 RHO 405011

20507003 3.33500-3 RHO 405024

20507004 6.84000-2 RHO 415014

20507005 8.38000-2 RHO 415024

20507006 2.24255-1 RHO 415034

20507007 2.98987-1 RHO 415044

20507008 2.24255-1 RHO 415054

20507009 7.32000-2 RHO 415064

20507010 1.42000-2 RHO 42001

20507011 1.42000-2 RHO 42002(

20507012 2.12609-3 RHO 430014

* 071 REACTOR VESSEL TOTAL MASS

20507100 RVMASS SUM 1.0 0.0

20507101 0.0 1.0 CNTRLVAR 65

20507102 1.0 CNTRLVAR 66

20507103 1.0 CNTRLVAR 67

* 072 PCS TOTAL MASS

20507200 PCSMASS SUM 1.0 0.0

20507201 0.0 1.0 CNTRLVAR 61

20507202 1.0 CNTRLVAR 62

20507203 1.0 CNTRLVAR 63

20507204 1.0 CNTRLVAR 64

20507205 1.0 CNTRLVAR 68

20507206 1.0 CNTRLVAR 69

20507207 1.0 CNTRLVAR 70

20507208 1.0 CNTRLVAR 71

* -------- 1 ------ 1 ------ 1 ------ 1 ----

* 073-076 STEAM GENERATOR MASS CALCULATOR

* 073 STEAM GENERATOR DOWNCOMER MASS

20507300 SGDCMASS SUM 1.0 0.0

20507301 0.0 0.4384 RHO 50301(

20507302 1.4850 RHO 50501(

20507303 2.21070-1 RHO 50801(

20507304 1.41427-1 RHO 51001(

20507305 1.41427-1 RHO 51002(

20507306 1.41427-1 RHO 51003(

* 074 STEAM GENERATOR BOILER MASS

20507400 SGBLRMASS SUM 1.0 0.0

20507401 0.0 5.07675-1 RHO 515010

0000

0000

0000

0000

0000

0

0

0

0

0

0

0

0

0

0

C

C

C

(]

0

0

(]

0

0

0

0

4000

4000

O000

)000

)000

4000

4000

4000

4000

3000

3000

3000

3000

)000

)000 4000

4000

4000

4000

4000

00

400

...000. . . .

0O00

000

)O00

000

0O00

4000

4000

1

1

- 71 -
20507402 5.07675-1 RHO 515020000

20507403 5.07675-1 RHO 515030000

20507404 5.07675-1 RHO 515040000

20507405 3.71565-1 RHO 515050000

20507406 0.2425 RHO 500010000

* 075 STEAM GENERATOR DOME AND PIPE MASS

20507500 SGDNMASS SUM 1.0 0.0

20507501 0.0 0.705312 RHO 520010000

20507502 0.705312 RHO 525010000

20507503 1.162180 RHO 530010000

* 076 STEAM GENERATOR TOTAL MASS

20507600 SGMASS SUM 1.0 0.0

20507601 0.0 1.0 CNTRLVAR 73

20507602 1.0 CNTRLVAR 74

20507603 1.0 CNTRLVAR 75

* GENERAL TABLE DATA

*

*

*

*

*

*

*

*

*

*

*

TABLE

NUMBER DESCRIPTION

900

939

949

959

969

* ----.---- 1----

20290000 POWER

20290001 0.0

20290002 0.15

20290003 0.3

20290004 0.6

20290005 0.85

20290006 1.0

20290007 1.3

20290008 2.0

20290009 4.0

20290010 7.0

20290011 10.

20290012 25.

20290013 65.

20290014 100.

20290015 250.

20290016 650.

20290017 1000.

20290018 1500.

20290019 3000.

20290020 5000.

20290021 1.+5

* ENVIRONMENTAL

20293900 TEMP

20293901 0.0

REACTOR POWER VS TINE AFTER SCRAM

ENVIRONMENTAL HEAT LOSS BOUNDARY TEMPERATURE

PRIMARY SYSTEM ENVR LOSS HEAT XFER COEFFICIENT

STEAM GENERATOR ENVR LOSS HEAT XFER COEFFICIENT

PRESSURIZER ENVR LOSS HEAT XFER COEFFICIENT

699 1.0 48.9+6

1.0 * FROM RELAP4 L3-1 POSTIEST

0.88

0.76

0.58

0.176

0.122605

0.1

0.087420

0.075788

0.064

0.060012

0.046738

0.035

0.031546

0.025210

0.0188

0.0164

0.0140

0.0110

0.0092

0.001460 * FROM LTR LO-08-81-173

HEAT LOSS BOUNDARY TEMPERATURE

1I----- ----- -- ----- 1---- ------- 1----

311.0

- 72 -
* PRIMARY SYSTEM ENVIRONMENTAL LOSS HEAT XFER COEFFICIENT

20294900 HTC-T

20294901 0.0 10.76 * 174 KW FROM PCS (EXCEPT PZR) *-----------1---- -1----1------1---- -1--- -- 1--

* STEAM GENERATOR ENVIRONMENTAL LOSS HEAT XFER COEFFICIENT

20295900 NTC-T

20295901 0.0 3.385 * 20 KW FROM STEAM GENERATOR *-----------1-. ....- 1----1-. ....- 1----1--- -- 1-'-

* PRESSURIZER ENVIRONMENTAL LOSS HEAT XFER COEFFICIENT

20296900 HTC-T

20296901 0.0 3.019 * 6 KW FROM PRESSURIZER

* PUMP DATA

* ----.---- 1 ----.-- 1 ------ 1 ------ 1 ---- * SINGLE PHASE HEAD CURVES

* HEAD CURVE NO. 1

1351100 1 1

1351101 O.O00000E+O0 1.403600E+00

1351102 1.906100E-01 1.363600E+00

1351103. 3.896300E-01 1.318600E+00

1351104 5.939600E-01 1.232800E+00

1351105 7.902000E-01 1.133600E+00

1351106 1.OOOOOOE+00 1.OOOOOOE+O0

* ----.---- 1 ------ 1------1------1----

* HEAD CURVE NO. 2

*-----------1--- --1----1----1--

1351200 1 2

1351201 O.OOOOOOE+O0 -6.700000E-01

1351202 2.OOOOOOE-O1 -5.OOOOOOE-01

1351203 4.OOOOOOE-O1 -2.500000E-01

1351204 5.755400E-01 O.OOOOOOE+O0

1351205 7.443200E-O1 2.583000E-01

1351206 7.734800E-01 3.778000E-01

1351207 8.631300E-01 6.326000E-01

1351208 1.OOOOOOE+O0 1.OOOOOOE+O0

* ---- ---- .------ --------.-1-- ---- 1----

* HEAD CURVE NO. 3

1351300 1 3

1351301 -1.OOOOOOE+O0 2.472200E+00

1351302 -8.057400E-01 2.047400E+00

1351303 -6.069000E-01 1.831000E+00

1351304 -4.068300E-01 1.624000E+O0

1351305 -2.001710E-01 1.470500E+00

1351306 O.O00000E+00 1.403600E+00

* ----.---- 1 -- ---- ---- -- ----1----

* HEAD CURVE NO. 4

1351400 1 4

1351401 -1.OOOOOOE+O0 2.472200E+00

1351402 -8.229700E-01 1.996800E+00

..-.- 1------1--"

....1------1---

.... 1-- ....- 1--...

....--1...----1--

---- 1-----1.-,

....-1-- -- 1.--

- 73 -
1351403 -6.333200E-01

1351404 -4.553400E-01

1351405 -2.710900E-01

1351406 -1.771600E-01

1351407 -9.073000E-02

1351408 O.O00000E+00 * ----- -- .--------- 1--- * HEAD CURVE NO. 5

1351500 1

1351501 O.OOOOOOE+00

1351502 2.OOOOOOE-01

1351503 4.OOOOOOE-01

1351504 4.118000E-01

1351505 5.976300E-01

1351506 7.934670E-01

1351507 1.000000E+00

* ---- --------- ----1----

* HEAD CURVE NO. 6

1351600 1

1351601 0.OOOOOOE+00

1351602 9.109900E-02

1351603 1.865090E-01

1351604 2.717620E-01

1351605 4.558720E-01

1351606 5.744060E-01

1351607 7.405760E-01

1351608 7.666190E-01

1351609 8.714710E-01

1351610 1.000000E+00

* ---- ---- ------------ 1 

* HEAD CURVE NO. 7

1351700 1

1351701 -1.OOOOOOE+00

1351702 -8.OOOOOOE-01

1351703 -6.OOOOOOE-01

1351704 -4.OOOOOOE-O1

1351705 -2.OOOOOOE-01

1351706 .OOOOOOE+O0

* ----.---- 1 ------ 1----

* HEAD CURVE NO. 8

1351800 . 1

1351801 -1.O00000E+O0

1351802 -8.OOOOOOE-01

1351803 -6.OOOOOOE-01

1351804 -4.OOOOOOE-01

1351805 -2.OOOOOOE-01

1351806 .OOOOOOE+00

* -------- -------- 1 1----

1.589700E+00

1.327900E+00

1.194900E+00

1.060500E+00

1.015600E+00

9.342790E-01 ----1------1---

5

2.500000E-01

2.800000E-01

3.400000E-01

2.768000E-01

4.584000E-01

6.992000E-01

1.000000E+00 --1----1---

.... 1-- ....-1---

6

9.342790E-01

9.229000E-01

8.963000E-01

8.750000E-01

8.433000E-01

8.355000E-01

8.466000E-01

8.469000E-01

8.838000E-01

1.OOOOOOE+00

7

-1.OOOOOOE+00

-6.300000E-01

-3.OOOOOOE-01

-5OOOOOOE-02

1.500000E-01

2.500000E-01

8

-1.OOOOOOE+00

-9.700000E-01

-9.500000E-01

-8.800000E-01

-8.OOOOOOE-01

-6.700000E-01 . -------- 1 1----

---1----1--

....- 1--.... 1.. --

---1--------

---1- ---1-

-...- 1--.... 1.. --

...1.-------

....- 1-----1.--

....- 1------1--

....- 1-- -- 1.-

--1------1--.

--1----1.--

* SINGLE PHASE TORQUE DATA

* TORQUE CURVE NO. 1

1351900 2 1

1351901 O.OOOOOOE+0O 6.032000E-01

1351902 1.930000E-01 6.325000E-01

- 74 -
1351903 3.930000E-0l

1351904 5.955200E-01

1351905 7.978200E-01

1351906 1.OOOOOE+00

* ----.---- 1 ------ 1----

* TORQUE CURVE NO. 2

1352000 2

1352001 0.000000E+00

1352002 4.OOOOOOE-01

1352003 5.OOOOOOE-01

1352004 7.372550E-01

1352005 7.680490E-01

1352006 8.672300E-01

1352007 1.OOOOOOE+OO

* -------- -------- 1 1 ---- * TORQUE CURVE NO. 3

1352100 2

1352101 -1.OOOOOOE+00

1352102 -8.009600E-01

1352103 -6.063800E-01

1352104 -4.068600E-01

1352105 -1.992800E-01

1352106 0.000000E+00

* -------- 1 ------ 1 --.- * TORQUE CURVE NO. 4

1352200 2

1352201 -1.OOOOOOE+0O

1352202 -8.223400E-01

1352203 -6.337100E-01

1352204 -4.585300E-01

1352205 -2.670230E-01

1352206 -1.761070E-01

1352207 -8.931000E-02

1352208 0.OOOOOOE+00

* ---- "------------ 1--

'* TORQUE CURVE NO. 5

1352300 2

1352301 0.OOOOOOE+00

1352302 4.OOOOOOE-01

1352303 5.OOOOOOE-01

1352304 1.OOOOOOE+00

* ----- ------------1----

* TORQUE CURVE NO. 6

1352400 2

1352401 0.OOOOOOE+00

1352402 9.064300E-02

1352403 1.885690E-01

1352404 2.734700E-01

1352405 4.586690E-01

1352406 5.744800E-01

1352407 7.381600E-01

1352408 7.685200E-01

1352409 8.700570E-01

1352410 1.OOOOOOE+00

7.369000E-01

8.331000E-01

9.229000E-01

1.OOOOOOE+O0

2

-6.700000E-01

-2.500000E-01

1.500000E-01

5.265860E-01

6.065940E-01

7.436600E-01

1.O00000E+00

3

1.984300E+00

1.394000E+00

1.097500E+00

8.220000E-01

6.648000E-01

6.032000E-01

--1------ 1 1 ----

,--1------1-.. --

-...-1------..1--.

.... 1.- ....- 1....

-...-1------..1------..1-.....-1-

4

1.984300E+00

1.830800E+00

1.682400E+00

1.557000E+00

1.436200E+00

1.387900E+00

1.348100E+00

1.233610E+00

----1----1---

5

-4.500000E-01

-2.5000OOE-01

O.O00000E+00

3.569000E-01

6

1.233610E+00

1.196500E+00

1.109600E+00

1.041600E+00

8.958000E-01

7.807000E-01

6.134000E-01

5.849000E-01

4.877000E-01

3.569000E-01

--1---'---1-

--- 1----1-... ..- I

- 75 -
* ----. -.-- 1 ---- 1---- I- - * TORQUE CURVE NO. 7

1352500 2

1352501 -1.OOOOOOE+O0

1352502 -3.OOOOOOE-01

1352503 -1.OOOOOOE-01

1352504 O.OOOOOOE+O0

* -------- 1 ------- I---

* TORQUE CURVE NO. 8

1352600 2

1352601 -1.OOOOOOE+OO

1352602 -2.500000E-01

1352603 -8.OOOOOOE-OZ

1352604 O.OOOOOOE+O0

* -------- ---- 1 ---- 1----

----1------.1-. ....-1----1--"

7

-1.OOOOOOE+00

-9.OOOOOOE-01

-5.OOOOOOE-O1

-4.500000E-01 --1----1--

8

-1.000000E+00

-9.OOOOOOE-01

-8.OO0000E-01

-6.700000E-01

1 ---- ---- 1----

....-1--....-1-"-

-... 1-- ....-1--

--1----..-1--

....-1-- ....-1--

* TWO - PHASE MULTIPLIER DATA FROM L3-6 TEST DATA

* ---- ------------- 1----

* HEAD CURVE

1353000 0

1353001 O.OOOOOOE+00

1353002 1.OOOOOOE-O1

1353003 2.OOOOOOE-01

1353004 3.OOOOOOE-01

1353005 3.500000E-01

1353006 4.OOOOOOE-01

1353007 5.OOOOOOE-01

1353008 6.OOOOOOE-01

1353009 7.OOOOOOE-01

1353010 8.OOOOOOE-01

1353011 9.OOOOOOE-01

1353012 1.OOOOOOE+00

* -------- 1-------- 1----

* TORQUE CURVE

1353100 0

1353101 O.OOOOOOE+00

1353102 1.OOOOOOE-O1

1353103 2.OOOOOOE-01

1353104 3.OOOOOOE-01

1353105 3.500000E-01

1353106 4.OOOOOOE-01

1353107 5.OOOOOOE-01

1353108 6.OOOOOOE-01

1353109 7.OOOOOOE-01

1353110 8.OOOOOOE-01

1353111 9.OOOOOOE-01

1353112 1.000000E+00 *-------1----1"--

* PUMP 2-PHASE DIFFERENCE

* HEAD CURVE NO. 1

1354100 1

1354101 O.OOOOOOE+00

1354102 1.000000E+O0

* -------- 1-------- I----

--1------1------1-.....-1---

---- 1----1------1------

O.OOOOOOE+00

O.OOOOOOE+O0

1.O0O000E-Ol

2.OOOOOOE-O1

3.OOOOOOE-01

6.OOOOOOE-01

6.OOOOOOE-01

6.OOOOOOE-01

6.OOOOOOE-01

5.OOOOOOE-O1

3.OOOOOOE-01

0.OOOOOOE+00 .---- 1 ----1---- ----1------1----

..-- 1-- -- 1-. ....-1-. ....- 1.--

O.OOOOOOE+O0

O.OOOOOOE+00

1.OOOOOOE-O1

3.OOOOOOE-01

5.OOOOOOE-01

7.500000E-01

7.500000E-01

7.500000E-01

7.500000E-01

7.500000E-01

5.OOOOOOE-O1

O.OOOOOOE+00

DATA

---- 1------1--

1

1.O00000E+00

1.OOOOOOE+00

--------- 1 1----

--1---...-1.--

---1---...-1-..-.

---- 1-- ....-1..--

---1---...-1...-

- 76 -
* HEAD CURVE NO. 2

1354200 1

1354201 O.OOOOOOE+00

1354202 1.OOOOOOE+00

* ------------ ---- I ---- * HEAD CURVE NO. 3

1354300 1

1354301 -1.000000E+00

1354302 -9.OOOOOOE-01

1354303 -8.000000E-01

1354304 -7.OOOOOOE-01

1354305 -6.OOOOOOE-01

1354306 -5.OOOOOOE-01

1354307 -4.OOOOOOE-01

1354308 -2.500000E-01

1354309 -1.OOOOOOE-01

1354310 O.OOOOOOE+00

* ----.---- -------- 1 ---- * HEAD CURVE NO. 4

1354400 1

1354401 -1.OOOOOOE+00

1354402 -9.OOOOOOE-01

1354403 -8.OOOOOOE-01

1354404 -7.OOOOOOE-01

1354405 -6.OOOOOOE-01

1354406 -5.OOOOOOE-01

1354407 -3.500000E-01

1354408 -2.OOOOOOE-01

1354409 -1.OOOOOOE-O1

1354410 0.OOOOOOE+00

* -------- -------- I 1----

* HEAD CURVE NO. 5

1354500 1

1354501 O.OOOOOOE+00

1354502 2.OOOOOOE-01

1354503 4.OOOOOOE-01

1354504 6.OOOOOOE-01

1354505 8.OOOOOOE-01

1354506 1.OOOOOOE+00

* -------- -------- 1 1----

* HEAD CURVE NO. 6

*-------1-----1--

1354600 1

1354601 O.OOOOOOE+00

1354602 1.OOOOOOE-01

1354603 2.500000E-01

1354604 4.OOOOOOE-01

1354605 5.OOOOOOE-01

1354606 6.OOOOOOE-01

1354607 7.OOOOOOE-01

1354608 8.OOOOOOE-01

1354609 9.OOOOOOE-01

1354610 1.OOOOOOE+00

* ----.---- 1 ------ 1----

* HEAD CURVE NO. 7

2

1.O00000E+00

1.OOO000E+00 ....- 1------1--

3

-1.160000E+00

-1.24O000E+00

-1.770000E+00

-2.360000E+00

-2.790000E+00

-2.910000E+O0

-2.670000E+00

-1.690000E+00

-5.OOOOOOE-01

O.OOOOOOE+00 --1----1---

4

-1.160000E+00

-7.800000E-01

-5.OOOOOOE-01

-3.100000E-O1

-1.700000E-01

-8.OOOOOOE-02

O.OOOOOOE+00

5.OOOOOOE-02

8.OOOOOOE-02

1.100000E-01

5

O.OOOOOOE+00

-3.400000E-01

-6.500000E-01

-9.300000E-01

-1.190000E+00

-1.470000E+00

6

1.100000E-01

1.300000E-01

1.500000E-01

1.300000E-01

7.OOOOOOE-02

-4.OOOOOOE-02

-2.300000E-01

-5.100000E-01

-9.100000E-O1

-1.470000E+00

--1 1------ I ----

....- 1----1---

--1------1-....

...1.------I

....- 1----1-

--1------1--

I--1--------

....- 1------1.--1

I--1---1--

I--1---1--

....- 1---- 1-

- 77 -
* . --.--. 1 - .----

1354700 1

1354701 -1.OOOOOOE+0O

1354702 O.OOOOOOE+O0

* . --.--.. 1 - ... ---- 1 

* HEAD CURVE NO. 8

1354800 1

1354801 -1.OOOOOE+O0

1354802 O.OOOOOOE+O0

* -------- ---- 1 ---- 1----

* TORQUE CURVE NO. 1

1354900 2

1354901 O.OOOOOOE+O0

1354906 1.000000E+O0

* -------- 1 ------ 1 ---- * TORQUE CURVE NO. 2

1355000 2

1355001 O.O00000E+O0

1355007 1.OOOOOOE+O0

* ---- 1------------ 1----

* TORQUE CURVE NO. 3

1355100 2

1355101 -1.OOOOOOE+OO

1355102 -8.009600E-01

1355103 -6.063800E-01

1355104 -4.068600E-O1

1355105 -1.992800E-01

1355106 O.OOOOOOE+0O

* ----.---- 1 ------ 1----

* TORQUE CURVE NO. 4

1355200 2

1355201 -1.OOOOOOE+00

1355202 -8.223400E-01

1355203 -6.337100E-01

1355204 -4.585300E-01

1355205 -2.670230E-01

1355206 -1.761070E-01

1355207 -8.931000E-02

1355208 O.OOOOOOE+00

* -------- -------- 1 1----

* TORQUE CURVE NO. 5

1355300 2

1355301 O.OOOOOOE+O0

1355302 4.OOOOOOE-01

1355303 5.OOOOOOE-01

1355304 1.OO0OOOE+O0

* -------- 1 ------ 1----

* TORQUE CURVE NO. 6

1355400 2

1355401 O.OOOOOOE+O0

1355402 9.064300E-02

1355403 1.885690E-O1

-- 1-----1--

7

0. OOOOOOE+0O

O.OOOOOOE+O0

8

O.OOOOOOE+O0 O.O00000E+O0

0. OOOOOOE+OO

1. OOOOOOE+00

1. OOOOOOE+0O

1.O400E000E0

1.3O9400E+O0

1.0975300E+00

1.O004000E+O0

1.O000500E+O0

8.2200OOE-O1

6.648000E-01

6.032000E-01 ---1----1--

....-1---'---1.

---- 1------1--

---- 1----1--

---- 1----1-

----1--....-1--

---- 1------1--

--1----1--

---- 1------1--

---1-----..-

.... 1-- ....- 1------..1------

4

1.984300E+00

1.830800E+00

1.682400E+00

1.557000E+00

1.436200E+00

1.387900E+00

1.348100E+00

1.233610E+00

5

-4.500000E-01

-2.500000E-01

O.OOOOOOE+00O

3;569000E-01

6

1.233610E+00

1.196500E+00

1.109600E+00

-78-
1355404 2.734700E-01 1.041600E+00

1355405 4.586690E-01 8.958000E-01

1355406 5.744800E-01 7.807000E-01

1355407 7.381600E-01 6.134000E-01

1355408 7.685200E-01 5.849000E-01

1355409 8.700570E-01 4.877000E-01

1355410 LOO0000E+0O 3.569000E-01

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1 ------ 1----

* TORQUE CURVE NO. 7

1355500 2 7

1355501 -1.OOOOOOE+OO -1.OOOOOOE+00

1355502 -3.OOOOOOE-01 -9.OOOOOOE-01

1355503 -1.OOOOOOE-01 -5.OOOOOOE-01

1355504 O.OOOOOOE+00 -4.500000E-01

* ----.---- -------- 1 -------- ---- 1- ----------- 1 ----

* TORQUE CURVE NO. 8

1355600 2 8

1355601 -1.OOOOOOE+O0 -1.OOOOOOE+O0

1355602 -2.500000E-01 -9.OOOOOOE-01

1355603 -8.OOOOOOE-02 -8.OOOOOOE-01

1355604 O.OOOOOOE+00 -6.700000E-01

* $$$ REMOVE ALL REMAINING DATA CARDS AFTER ACHIEVING STEADY STATE

* PUMP DATA

* -------- 1------ 1 ------ 1 ------ 1----

* SINGLE PHASE HEAD CURVES

*-----------1-. ....- 1----1-----1'-

* HEAD CURVE NO. 1

*-----------1-. ....- 1----1-----1I'

1651100 1 1

1651101 O.OOOOO0E+O0 1.403600E+00

1651102 1.906100E-01 1.363600E+00

1651103 3.896300E-01 1.318600E+O0

1651104 5.939600E-01 1.232800E+00

1651105 7.902000E-01 1.133600E+00

1651106 1.000000E+00 1.OOOOOOE+0O

* ---------------- 1 ---- ----I ----1----

* HEAD CURVE NO. 2

1651200 1 2

1651201 O.OOOOOOE+O0 -6.700000E-01

1651202 2.OOOOOOE-01 -5.OOOOOOE-01

1651203 4.OOOOOE-O1 -2.500000E-01

1651204 5.755400E-01 O.OOOOOOE+0O

1651205 7.443200E-01 2.583000E-01

1651206 7.734800E-01 3.778000E-01

1651207 8.631300E-01 6.326000E-01

1651208 1.OOOOOOE+O0 1.OOOOOOE+0O

* -- ---- ------ ---- -------- ----1----

* HEAD CURVE NO. 3

1651300 1 3

1651301 -1.000000E+00 2.472200E+00

1651302 -8.057400E-01 2.047400E+00

1651303 -6.069000E-01 1.831000E+00

-.1-----1"-

....- 1------1..--

.... 1----1--

.... 1-- ....- 1---

- 79 -
1651304 -4.068300E-01

1651305 -2.001710E-01

1651306 O.O00000E+00

* -------- 1 ------ 1 ---- * HEAD CURVE NO. 4

*------------1-----1---

1651400 1

1651401 -1.O00000E+O0

1651402 -8.229700E-01

1651403 -6.333200E-01

1651404 -4.553400E-01

1651405 -2.710900E-01

1651406 -1.771600E-01

1651407 -9.073000E-02

1651408 O.OOOOOOE+00

* -------- 1 ------ 1----

* HEAD CURVE NO. 5

*-----------1------1---

1651500 1

1651501 O.OOOOOOE+00

1651502 2.OOOOOOE-01

1651503 4.OOOOOOE-01

1651504 4.118000E-01

1651505 5.976300E-01

1651506 7.934670E-01

1651507 1.000000E+00

* -------- 1 -- ----1----

* HEAD CURVE NO. 6

1651600 1

1651601 O.OOOOOOE+00

1651602 9.109900E-02

1651603 1.865090E-01

1651604 2.717620E-01

1651605 4.558720E-01

1651606 5.744060E-01

1651607 7.405760E-01

1651608 7.666190E-01

1651609 8.714710E-01

1651610 1. 0O0000E+0

* -------- 1 -- ----1 ---- * HEAD CURVE NO. 7

1651700 1

1651701 -1.OOOOOOE+00

1651702 -8.OOOOOOE-01

1651703 -6.OOOOOOE-01

1651704 -4.OOOOOOE-01

1651705 -2.OOOOOOE-01

1651706 O.OOOOOOE+00

* ----.------------- 1....

* HEAD CURVE NO. 8

1651800 1

1651801 -1.OOOOOOE+00

1651802 -8.OOOOOOE-01

1651803 -6.OOOOOOE-01

1651804 -4.OOOOOOE-01

1651805 -2.OOOOOOE-01

1.624OOOE+00

1.470500E+00

1.403600E+00

S---1--- 1 ----....-1------..1....

....----- 1------1------1.--

4

2.472200E+00

1.996800E+00

1.589700E+00

1.327900E+00

1.194900E+00

1.060500E+00

1.015600E+00

9.342790E-01

5

Z.5000OOE-01

2.800000E-01

3.400000E-01

2.768000E-01

4.584000E-01

6.992000E-01

1.00000+OO

6

9.342790E-01

9.229000E-01

8.963000E-01

8.750000E-01

8.433000E-01

8.355000E-01

8.466000E-01

8.469000E-01

8.838000E-01

1.OOOOOOE+O0

7

-1.O00000E+00

-6.300000E-01

-3.OOOOOOE-01

-5.OOOOOOE-02

1.500000E-01

2.5000OOE-01 --1----1--

8

-1.OOOOOOE+00

-9.700000E-01

-9.5000OOE-01

-8.800000E-01

-8.OOOOOOE-OI

....- 1------1---..

--1------

....1------..1-.-

....- 1------..1,--

.... 1-- -- 1.-

-80-
1651806 O.OOOOOOE+00 -6.700000E-01 * ----. -.-- 1 ---- --- 1 - - - --1 ---- --- 1'- -

* SINGLE PHASE TORQUE DATA

* TORQUE CURVE NO. 1

1651900 2 1

1651901 O.OOOOOOE+O0 6.032000E-01

1651902 1.930000E-01 6.325000E-01

1651903 3.930000E-01 7.369000E-01

1651904 5.955200E-01 8.331000E-01

1651905 7.978200E-01 9.229000E-01

1651906 1.OOOOOOE+00 1.OOOOOOE+00

* -------- 1-------- 1 ------ 1 ------ 1----

* TORQUE CURVE NO. 2

1652000 2 2

1652001 O.O00000E+O0 -6.700000E-01

1652002 4.OOOOOOE-01 -2.500000E-01

1652003 5.OOOOOOE-01 1.500000E-01

1652004 7.372550E-01 5.265860E-01

1652005 7.680490E-01 6.065940E-01

1652006 8.672300E-01 7.436600E-01

1652007 1.OOOOOOE+0 1.OOOOOOE+0O

* -------- 1 ------ 1 ------ 1 ------ 1----

* TORQUE CURVE NO. 3

1652100 2 3

1652101 -1.OOOOOOE+O0 1.984300E+00

1652102 -8.009600E-01 1.394000E+00

1652103 -6.063800E-01 1.097500E+00

1652104 -4.068600E-01 8.220000E-01

1652105 -1.992800E-01 6.648000E-01

1652106 O.O00000E+O0 6.032000E-01

* ------------ ----1----1 - - ---- 1----

* TORQUE CURVE NO. 4

1652200 2 4

1652201 -1.OOOOOOE+00 1.984300E+00

1652202 -8.223400E-01 1.830800E+00

1652203 -6.337100E-01 1.682400E+00

1652204 -4.585300E-01 1.557000E+0O

1652205 -2.670230E-01 1.436200E+00

1652206 -1.761070E-01 1.387900E+00

1652207 -8.931000E-02 1.348100E+00

1652208 O.OOOOOOE+00 1.233610E+00

* -------- -------- 1 ---- ------ 1----

* TORQUE CURVE NO. 5

*-----------1----1----1--- -- 1-....

1652300 2 5

1652301 O.O00000E+00 -4.5000OOE-01

1652302 4.OOOOOOE-01 -2.500000E-01

1652303 5.OOOOOOE-01 O.OOOOOOE+00

1652304 1.000000E+00 3.569000E-01

* -------- 1 ---- 1 ------ 1 ------ 1----

* TORQUE CURVE NO. 6

1652400 2 6

1652401 O.O00000E+00 1.233610E+00

....- 1---- 1,-

....- 1------..1,-

....- 1------..1.-

-...- 1------1..-.

....- 1------..1--

--1------1---

-...- 1------1--

--1------1.--

....- 1------1-.

--1----1,--

....- 1-----1-

---1---...-1.-

---1---...-1.-

- 81 -
1652402 9.064300E-02 1.196500E+00

1652403 1.885690E-01 1.109600E+00

1652404 2.734700E-01 1.041600E+00

1652405 4.586690E-01 8.958000E-01

1652406 5.744800E-01 7.807000E-01

1652407 7.381600E-01 6.134000E-01

1652408 7.685200E-01 5.849000E-01

1652409 8.700570E-01 4.877000E-01

1652410 1.OOOOOOE+00 3.569000E-01

* TORQUE CURVE NO. 7

1652500 2 7

1652501 -1.OOOOOOE+O0 -1.OOOOOOE+O0

1652502 -3.OOOOOE-01 -9.OOOOOOE-01

1652503 -1.OOOOOOE-01 -5.OOOOOOE-01

1652504 O.OOOOOOE+00 -4.500000E-01

* TORQUE CURVE NO. 8

1652600 2 8

1652601 -1.OOOOOOE+00 -1.OOOOOOE+00

1652602 -2.5000OOE-01 -9.OOOOOOE-01

1652603 -8.OOOOOOE-02 -8.000000E-01

1652604 O.OOOOOOE+O0 -6.700000E-01

*TWO -..... 1 ----- MULTIPLIE1R 1 FO1- . L- .1-- TT1D

* TWO - PHASE MqULTIPLIER DATA FROM L3-6 TEST DATA

*-----------1------..1------1-. ....- 1-. ....- 1------1..1

* HEAD CURVE

1653000 0

1653001 O.OOOOOOE+O0

1653002 1.OOOOOOE-01

1653003 2.OOOOOOE-01

1653004 3.OOOOOOE-01

1653005 3.500000E-01

1653006 4.OOOOOOE-01

1653007 5.OOOOOOE-01

1653008 6.OOOOOOE-01

1653009 7.OOOOOOE-01

1653010 8.OOOOOOE-O1

1653011 9.OOOOOOE-01

1653012 1.OOOOOOE+O0

* ----.---- 1 ------ 1----

* TORQUE CURVE

1653100 0

1653101 O.OOOOOOE+O0

1653102 1.OOOOOOE-01

1653103 2.OOOOOOE-01

1653104 3.OOOOOOE-01

1653105 3.500000E-01

1653106 4.OOOOOOE-01

1653107 5.OOOOOOE-01

1653108 6.OOOOOOE-01

1653109 7.OOOOOOE-01

1653110 8.OOOOOOE-01

1653111 9.OOOOOOE-01

1653112 1.OOOOOOE+O0

.... 1-- -- 1-. ....- 1------..1....

O.OOOOOOE+O0

O.OOOOOOE+0O

1.000000E-01

2.OOOOOOE-01

3.OOOOOOE-01

6.000000E-01

6.OOOOOOE-01

6.OOOOOOE-01

6.OOOOOOE-01

5.OOOOOOE-01

3.OOOOOOE-01

O.OOOOOOE+O0 ....- 1------1.. --

O.OOOOOOE+O0

O.OOOOOOE+O0

1.OOOOOOE-01

3.OOOOOOE-01

5.000O0E-O1

7.500000E-01

7.500000E-01

7.500000E-01

7.500000E-01 7. 500000E-01

5.OOOOOOE-O1

O.OOOOOOE+00

- 82 -
* -1-1--

* PUMP 2-PHASE DIFFERENCE

* -.... 1-.....1....

* HEAD CURVE NO. 1

1654100 1

1654101 O.OOOOOOE+00

1654102 1.O00000E+00

* ----.---- 1 ------ 1----

* HEAD CURVE NO. 2

*-----------1----1---

1654200 1

1654201 O.OOOOOOE+00

1654202 1.OOOOOOE+00

* -------- 1 ------ 1 ---- * HEAD CURVE NO. 3

1654300 1

1654301 -1.OOOOOOE+O0

1654302 -9.OOOOOOE-01

1654303 -8.OOOOOOE-01

1654304 -7. OOOOOOE-01

1654305 -6. OOOOOOE-01

1654306 -5.OOOOOOE-01

1654307 -4. OOOOOOE-O1

1654308 -2. 5000OE-01

1654309 -1. 000000E-01

1654310 0.OOOOOOE+00

* ---- 1------------ 1----

* HEAD CURVE NO. 4

*-----------1-.....-1---

1654400 1

1654401 -1.OOOOOOE+00

1654402 -9.000000E-01

1654403 -8.OOOOOOE-01

1654404 -7.000000E-01

1654405 -6.OOOOOOE-01

1654406 -5.OOOOOOE-01

1654407 -3.500000E-01

1654408 -2.OOOOOOE-01

1654409 -1.OOOOOOE-O0

1654410 O.OOOOOOE+00

* ------------ ---- ---- * HEAD CURVE NO. 5

1654500 1

1654501 O.OOOOOOE+00

1654502 2.OOOOOOE-01

1654503 4.OOOOOOE-01

1654504 6.OOOOOOE-01

1654505 8.OOOOOOE-01

1654506 1.OOOOOOE+00

* -------- 1 ------ 1----

* HEAD CURVE NO. 6

1654600 1

1654601 O.OOOOOOE+0O

1654602 1.000000E-01

1654603 2.500000E-01

DATA

1

1.OOOOOOE+00

1.000000E+00

2

1.OOOOOOE+0O

1.000000E+O0

3

-1.160000E+00

-1.240000E+00

-1.770000E+00

-2.360000E+00

-2.790000E+00

-2.910000E+00

-2.670000E+00

-1.690000E+00

-5.OOOOOOE-01

O.OOOOOOE+00

4

-1.160000E+00

-7.800000E-01

-5.OOOOOOE-01

-3.100000E-01

-1.700000E-01

-8.OOOOOOE-02

O.OOOOOOE+O0

5.OOOOOOE-OZ

8.OOOOOOE-02

1.100000E-01

5

O.OOOOOOE+O0

-3.400000E-01

-6.500000E-01

-9.300000E-01

-1.190000E+00

-1.470000E+00

6

1.100000E-01

1.300000E-01

1.500000E-01

- 83 -
1654604 4.000000E-01

1654605 5.000000E-O1

1654606 6.OOOOOOE-O1

1654607 7.OOOOOOE-01

1654608 8.000000E-01

1654609 9.000000E-01

1654610 1.000000E+O0

* -------- 1 ---- -- ---- * HEAD CURVE NO. 7

1654700 1

1654701 -1.OOOOOOE+O0

1654702 O.OOOOOOE+0O

* ----.----- 1---- --1----

* HEAD CURVE NO. 8

1654800 1

1654801 -1.000000E+00

1654802 O.OOOOOOE+00

* -------- 1 ------ 1 ---- * TORQUE CURVE NO. 1

1654900 2

1654901 0.OOOOOOE+00

1654906 1.OOOOOOE+00

* ----.---- 1 ------ 1----

* TORQUE CURVE NO. 2

*-----------1----1---

1655000 2

1655001 O.OOOOOOE+0O

1655007 1.OOOOOOE+O0

* ---- ----I--------1----

* TORQUE CURVE NO. 3

*-------1-----1I1655100 2

1655101 -1.OOOOOOE+O0

1655102 -8.009600E-01

1655103 -6.063800E-01

1655104 -4.068600E-01

1655105 -1.992800E-01

1655106 O.OOOOOOE+0O

* ----.---- 1------ 1----

* TORQUE CURVE NO. 4

1655200 2

1655201 -1.OOOOOOE+O0

1655202 -8.223400E-01

1655203 -6.337100E-01

1655204 -4.585300E-01

1655205 -2.670230E-01

1655206 -1.761070E-01

1655207 -8.931000E-02

1655208 O.OOOOOOE+00

* -------- 1 ------ 1----

* TORQUE CURVE NO. 5

1655300 2

1655301 O.OOOOOOE+00O

1655302 4.OOOOOOE-01

1.300000E-OI

7.OOOOOOE-02

-4.OOOOOOE-02

-2.300000E-01

-5.100000E-01

-9.100000E-01

-1.470000E+0O ---- 1----1-

7

O.OOOOOOE+O0

O.OOOOOOE+0O ---- 1----1,-

8

O.OOOOOOE+O0

O.OOOOOOE+0O

1

1.OOOOOOE+O0

1.OOOOOOE+00 ----1----1--

---- 1----1-

2

1.OOOOOOE+0O

1.OOOOOOE+0O

3

1.984300E+00

1.394000E+0O

1.097500E+00

8.220000E-01

6.648000E-01

6.032000E-01 . -------- 1 1----

--1--- ...-1.--

--1----..-1.-

....- 1----1.-

....- 1------..1.-

....- 1------..1....

....- 1------..1.-

....- 1----1.-

....- 1------..1.-

....- 1------1.. --

---1--- ...-1'-

....- 1----1.-

....1----1-. ...-------- 1'-

4

1.984300E+00

1.830800E+00

1.682400E+00

1.557000E+00

1.436200E+00

1.387900E+00

1.348100E+00

1.233610E+00 --1----1--

---- 1----1--

5

-4.500000E-01

-2.500000E-01

.-1-- ...-1---

--1----1.-

-84 -
1655303 5.OOOOOOE-O1 O.OOOOOOE+O0

1655304 1.OOOOOOE+00 3.569000E-01

* TORQUE CURVE NO. 6

1655400 2 6

1655401 O.OOOOOOE+00 1.233610E+00

1655402 9.064300E-02 1.196500E+00

1655403 1.885690E-01 1.109600E+00

1655404 2.734700E-01 1.041600E+00

1655405 4.586690E-01 8.958000E-01

1655406 5.744800E-01 7.807000E-01

1655407 7.381600E-01 6.134000E-01

1655408 7.685200E-01 5.849000E-01

1655409 8.700570E-01 4.877000E-01

1655410 1.OOOOOOE+00 3.569000E-01

* TORQUE CURVE NO. 7

1655500 2 7

1655501 -1.OOOOOOE+OO -1.000000E+00

1655502 -3.OOOOOOE-01 -9.OOOOOOE-01

1655503 -1.OOOOOOE-01 -5.OOOOOOE-01

1655504 O.OOOOOOE+00 -4.500000E-01

* TORQUE CURVE NO. 8

1655600 2 8

1655601 -1.OOOOOOE+O0 -1.O00000E+00

1655602 -2.500000E-01 -9.OOOOOOE-01

1655603 -8.OOOOOOE-02 -8.OOOOOOE-01

1655604 O.OOOOOOE+O0 -6.700000E-01

* STEADY STATE CONTROL SYSTEM

* PRIMARY COOLANT PUMP SPEED CONTROLLERS

* CALCULATE MASS FLOW ERROR

20590100 NSSERR SUN 1.0 0.0 1

20590101 481.30 -1.0 MFLOWJ 100010000

" SP XXXxxx

* SP - HOT LEO MASS FLOW SETPOINT

* -------- 1 ------ 1 ------ 1----

* PUMP 1 SPEED

20590200 PCP1SPD INTEGRAL 0.34482 321.95 1

20590201 CNTRLVAR 901

* -------- 1 ------ 1 ------ 1----

* PCP1 PUMP VELOCITY TABLE

1356100 501 CNTRLVAR 902

1356101 0.0 0.0

1356102 369.0 369.0

* -------- -------- 1 1 ------ 1----

* MODIFY PCPI PUMP DATA

*-------------1----1I-

- 85 -
1350301 0 0 0 -1 0 695 0

* . -. 1 -- -1 ----

* PUMP 2 SPEED

20590300 PCP2SPD INTEGRAL 0.34482 328.74 1

20590301 CNTRLVAR 901

* -------- 1------- ------ 1 ---- * PCP2 PUMP VELOCITY TABLE

*-----------1----1------1----

1656100 501 CNTRLVAR 903

1656101 0.0 0.0

1656102 369.0 369.0 *-----------1--- -- 1-- ....- 1--

* MODIFY PCP2 PUMP DATA

1650301 0 0 0 -1 0 697 0 *-----------1-...-:---1------..1----1----1------1--

* PRESSURIZER SPRAY VALVE CONTROLLER

* SPRAY VALVE

4350000 "SPRVLV " VALVE

4350101 430010000 415010000 3.3451E-4 1.5432E01 1.5432E01 0100

4350201 0 .00000000 .00000000 0.0

4350300 SRVVLV

4350301 904 999

* --------- 1 ---- 1 ------1----

* SPRAY VALVE POSITION CALCULATOR

20590400 SPRAY SUm -1.0 0.0 1 * CONTIN

+ 3 0.0 1.0

20590401 14.90+6 -1.0 P 4ZOO10000

* SP XXXXXXX

* SP - TOP END OF PRESSURE CONTROL BAND ; SPRAY TURNS ON

* ---------------- 1 ---- -- 1----

* POSITION VS AREA TABLE

20299900 NORMAREA

20299901 0.0 0.0

20299902 0.0001 0.0

20299903 1.0 1.0 *-----------1' 1-------.11. .. 1 1

* PRESSURIZER HEATERS IN INITIALIZATION

* TRIP SETPOINTS

*-----------1-. ....- 1"----,-1--

* LT 693 CYLCING HEATERS CARD 20241700

0000585 P 100010000 GT NULL 0 14.85+6 N

* SP XXXXXXX

* SP - BOTTOM END OF PRESSURE CONTROL BAND ; HEATERS TURN OFF

0000586 P 100010000 LT NULL 0 14.8499+6 N

* SP XXXXOOXXC

* SP - (BOTTOM END . . .) - DELTA ; HEATERS TURN ON

0000666 586 OR 693 N

0000667 -585 AND 666 N

0000693 -503 AND 667 N

* -------- -------- 1 1 ------ 1----

* LT 694 BACKUP HEATERS CARD 20241800

0000587 P 420010000 OT NULL 0 14.85+6 N

- 86-
* SP xxxxxxx

* SP - BACKUP HEATERS TURN OFF

0000588 P 420010000 LT NULL 0 14.84+6 N

* SP XXxXXXX

* SP - BACKUP HEATERS TURN ON

0000668 588 OR 694 N

0000669 -587 AND 668 N

0000694 -503 AND 669 N

* PRESSURIZER HEATERS

14172000 2 9 2 1 0.0

14172100 0 1

14172101 8 8.3820E-3

14172201 4 8

14172301 1.0 8

14172401 615. 9

14172501 0 0 0 1 5.4864 1

14172502 0 0 0 1 1.8288 2

14172601 415040000 0 1 1 5.4864 1

14172602 415040000 0 1 1 1.8288 2

14172701 417 1.0 0.0 0.0 1 * CYCLING

14172702 418 1.0 0.0 0.0 2 * BACKUP

14172901 0 1.6764E-2 1.6764E-2 5.4864 1

14172902 0 1.6764E-2 1.6764E-2 1.8288 2

* ------------1 ---- --- --- 1----

* PRESSURIZER CYCLING HEATERS

20241700 POWER 693

20241701 -1.0 0.0

20241702 0.0 0.0

20241703 1.0 3.6+4

* ------------1 ---- --- ---1----

• PRESSURIZER BACKUP HEATERS

20241800 POWER 694

20241801 -1.0 0.0

20241802 0.0 0.0

20241803 1.0 3.6+4

* ---- ------------------- 1 ---- --- -----------1----

* PRESSURIZER LEVEL CONTROL USING CHARGING AND LETDOWN COMPONENTS

* -------- 1 ------ 1 ------ 1-------- ---- 1 ------ ---- * MODIFY PZR LEVEL CONTROL VARIABLE

20500206 0.1249 VOIDF 415060000

20500207 0.02477 VOIDF 420010000

20500208 0.02447 VOIDF 420020000

• CHARGING RESERVIOR

9800000 "CHRG RESRV" ThDPVOL

9800101 1.0 1.0 0.0 0.0 0.0 0.0

9800102 4.0-5 0.0 00

9800200 3

9800201 0.0 2.07+07 559.2

* CHARGING VALVE

9850000 "CHRG VALVE" VALVE

- 87 -
9850101 980000000 185000000 3.8E-05 0.0 0.0 0100

9850201 0 .00000000 .00000000 0.0

9850300 SRVVLV

9850301 905 999

* -------- 1 ----1 ------ 1----

* CHARGING VALVE POSITION CALCULATOR

*-------1----1------1---

20590500 CHARGE SUM 7.7 0.0 1 *CONTIN

+ 3 0.0 1.0

20590501 1.09 -1.0 CNTRLVAR 2

* SP xxxxx

* SP - BOTTOM END OF LEVEL CONTROL BAND ; CHARGING TURNS ON

* ----.---- 1 ------ 1 ---------- * LETDOWN SINK

*-------1----1---...-1---

9900000 "LTDWN SINK" ThDPVOL

9900101 1.0 1.0 0.0 0.0 0.0 0.0

9900102 4.0-5 0.0 00

9900200 3

9900201 0.0 1.4+7 559.2

* -------- -------- 1 1 -- ---- 1----

* LETDOWN VALVE

9950000 "LTDWN VLV " VALVE

9950101 185000000 990000000 2.5-5 0.0 0.0 0100

9950201 0 .00000000 .00000000 0.0

9950300 SRVVLV

9950301 906 999

* ----.---- 1 ---- 1------ 1----

* LETDOWN VALVE POSITION CALCULATOR

20590600 LETDOWN SUM -7.7 0.0 1 *CONTIN

+ 3 0.0 1.0

20590601 1.11 -1.0 CNTRLVAR 2

* SP xxxxx

* SP - TOP END OF LEVEL CONTROL BAND ; LETDOWN TURNS ON

* ---- ------------------- 1 ------ 1 ------ 1------1----

* STEAM VALVE CONTROLLER

* CHANGES TO STEAM VALVE

5400201 0 16.946000 20.832000 0.0

5400300 SRVVLV

5400301 910 540

20254000 NORMAREA

20254001 0.0 0.0

20254002 0.0001 0.0

20254003 1.0 1.0

* COMPUTE DELTA T ERROR

20590700 "DELTA T" SUM 1.0 0.0

20590701 556.00 -1. TEMPF 185010000

* SP XXXXXX

* SP - COLD LEG TEMPERATURE SETPOINT

* -------- 1 ------ 1 ------ 1----

* FILTER DELTA T THRU DEADBAND

20590800 DEADBAND FUNCTION 1.0 0.0

-88-
20590801 CNTRLVAR 907 908

20290800 REAC-T

20290801 -100. -100.

20290802 -0.25 -0.25

20290803 -0.25 0.0

20290804 0.25 0.0

20290805 0.25 0.25

20290806 100. 100.

* ----.---- 1 ------ 1 ------ 1 ---- * INTEGRATE DELTA T ERROR

20590900 "INT D T" INTEGRAL 1.0 0.0

20590901 CNTRLVAR 908

* -------- 1 ------ 1 ----.---- 1 ---- * STEAM VALVE POSITION CALCULATOR

20591000 TCONTROL SUM 1.0 0.64502

+ 3 0.6 0.90

* SP xxxxxxx

* SP - STEAM VALVE INITIAL POSTION

20591001 0.645229 -0.07126 CNTRLVAR 908

* SP xxxxxxx

* SP - STEAM VALVE INITIAL POSITION

20591002 -0.01492 CNTRLVAR 909

* SIMPLIFIED FEED SYSTEM CONTROLLER

*-----------1------1-. ....- 1----1- -

20591100 SGLVLERR SUM 1.0 0.0

20591101 3.20 -1.0 CNTRLVAR 001

* SP xxxxxx

* SP - STEAM GENERATOR LEVEL SETPOINT

20591200 FEEDFLOW SUM 1.0 0.0

20591201 0.0 1.0 MFLOWJ 54000000

20591202 48.4 CNTRLVAR 911

* -------- 1 ------ 1------ 1 ---- * REPLACE FEED JUNCTION TABLE

5660200 1 0 CNTRIVAR 912

5660201 -100.0 25.553 0.0 0.0

* sP xxxxxx

* SP - INITIAL FEED FLOW RATE

5660202 -1.0 0.0 0.0 0.0

5660203 0.0 0.0 0.0 0.0

5660204 50.0 50.0 0.0 0.0

5660205

5660206

5660207

5660208

5660209 *-----------1----1------1----1---

* CONSTANT REACTOR POWER TABLE

*-----------1------..1------..1----1"----

20290000 POWER

20290001 0.0 48.9+6

20290002 100. 48.9+6

20290003 200. 48.9+6

20290004 1.E+3 48.9+6

20290005

20290006

1

0 *CONTI

1

J0

1

*--1------1----

- 89 -
20290007

20290008

20290009

20290010

20290011

20290012

20290013

20290014

20290015

20290016

20290017

20290018

20290019

20290020

* REPLACE TRIPS FOR STEADY STATE

* SCRAM

0000510 TIME 0 GE NULL 0 1.+9 L

* BREAK OPENS

0000511 TIME 0 GE NULL 0 1.+9 L

* HPIS ON

0000513 TIME 0 GE NULL 0 1.+9 L

..... RELAP5 END CARD

-90-
/JOB

L37BASE,T6000.

/USER

AITACH,REL36KX.

ATTACH,STH2XT=STEAM/UN=KA41202.

*PURGE,L37PRPl/NA.

*DEFINE,RSTPLT=L37PRP1.

PURGE,L37PFB1/NA.

DEFINE,PLOTFL=L37PFB1.

ATTACH,RSTIN=L3SRP1.

FLE,RSTIN,SBF=NO.

FILE,RSTPLT,SBF=NO.

RFL,CM=350000,EC=20O.

REDUCE(-)

REL36KX,,*PL=50000.

/EOR

= LOFT L3-7 POST TEST ANALYSIS

0000100 RESTART TRANSNT

0000101 RUN

0000103 408

0000105 5.0 10.0

0000201 10000.0 1.0-6 5.0 3 2 200 400

* REMOVE PUMP SPEED CONTROLLERS

*2059 100 . ... 1------..1-.. 0 .10 .0-..10 0 .0-.1-

20590100 KSSERR DELETE 0.0 0.0 0.0 0.0 0.0 0.0

20590200 PCP1SPD DELETE 0.0 0.0 0.0 0.0 0.0 0.0 20590300 PCP2SPD DELETE 0.0 0.0 0.0 0.0 0.0 0.0

* ----.---- 1 ----------- 1----- ----- I 1------1----

* RENODALIZE PUMPI

1350000 "PCPUMP1 PUMP

1350101 0.0 0.4572 0.0991 0.0 90.0 0.317900

1350102 0

1350108 130010000 0.0 0.017 0.017 0000

1350109 140000000 0.0 0.05 0.05 0000

1350200 0 1.48280+7 1.22765+6 2.46363+6 0.

1350201 0 8.5604 8.5604 0.0

1350202 0 9.0732 9.0732 0.0

1350301 0 0 0 -1 -1 595 0

1350302 369.00000 .91140921 .31550000 96.000000 500.60000 1.4310000

1350303 613.6 0.0 207.433 .0444 19.5987 0.0

1350308 0.212845 0.0 -22.86511 27.16043 5.74589

1350310 0.0 0.0 0.0

* PUMP DATA ,

* SINGLE PHASE HEAD CURVES

* HEAD CURVE NO. I

1351100 1 1

1351101 O.OOOOOOE+00 1.403600E+O0

1351102 1.906100E-01 1.363600E+00

1351103 3.896300E-01 1.318600E+00

1351104 5.939600E-01 1.232800E+00

1351105 7.902000E-01 1.133600E+00

- 91 -
1351106 1.OOOOOOE+OO

* . --.--.. 1 --- ----... 1 

* HEAD CURVE NO. 2

1351200 1

1351201 O.000000E+O0

1351202 2.O00000E-01

1351203 4.000000E-01

1351204 5.755400E-01

1351205 7.443200E-01

1351206 7.734800E-01

1351207 8.631300E-01

1351208 1.OOOOOOE+0O

* ----.---- 1 ----.-- 1 ---- * HEAD CURVE NO. 3

1351300 1

1351301 -1.OOOOOE+O0

1351302 -8.057400E-01

1351303 -6.069000E-01

1351304 -4.068300E-01

1351305 -2.001710E-01

1351306 O.OOOOOOE+00

* ----.---- 1 ----.-- 1 ---- * HEAD CURVE NO. 4

1351400 1

1351401 -1.OOOOOOE+O0

1351402 -8.229700E-01

1351403 -6.333200E-01

1351404 -4.553400E-01

1351405 -2.710900E-01

1351406 -1.771600E-01

1351407 -9.073000E-02

1351408 O.OOOOOOE+00

* -------- -------- 1 1----

* HEAD CURVE NO. 5

1351500 1

1351501 O.OOOOOOE+00

1351502 2.OOOOOOE-01

1351503 4.OOOOOOE-01

1351504 4.118000E-01

1351505 5.976300E-01

1351506 7.934670E-01

1351507 1.OOOOOOE+O0

* -------- -------- 1 1----

* HEAD CURVE NO. 6

*----------------- 1 ---- 1351600 1

1351601 O.OOOOOOE+00

1351602 9.109900E-02

1351603 1.865090E-01

1351604 2.717620E-01

1351605 4.558720E-01

1351606 5.744060E-01

1351607 7.405760E-01

1351608 7.666190E-01

1351609 8.714710E-01

1.OOOOOE+O0

2

-6.700000E-01

-5.OOOOOOE-01

-2.500000E-01

O.OOOOOOE+00

2.583000E-01

3.778000E-01

6.326000E-01

1.OOOOOOE+00

3

2.472200E+00

2.047400E+00

1.831000E+00

1.624000E+00

1.470500E+00

1.403600E+00 ....-1----1--

4

2.472200E+00

1.996800E+00

1.589700E+00

1.327900E+00

1.194900E+00

1.060500E+00

1.015600E+00

9.342790E-01

5

2.500000E-01

2.800000E-01

3.400000E-01

2.768000E-01

4.584000E-01

6.992000E-01

1.OOOOOOE+00

6

9.342790E-01

9.229000E-01

8.963000E-01

8.750000E-01

8.433000E-01

8.355000E-01

8.466000E-01

8.469000E-01

8.838000E-01

- 92 -

....-1------.1--

---------

--. 1---1--

....-1------1--

....-1------1..--

--..1--------

....-1----1-

....-1------1..-1

-I-1---i--
1351610 1.000000E+O0 * - - -- -1 ---- --- 1 - -

* HEAD CURVE NO. 7

1351700 1

1351701 -1.OOOOOOE+00

1351702 -8.OOOOOOE-01

1351703 -6.OOOOOOE-01

1351704 -4.OOOOOOE-01

1351705 -2.OOOOOOE-O1

1351706 O.OOOOOOE+0O

* --------.--- 1 ---- 1----

* HEAD CURVE NO. 8

1351800 1

1351801 -1.000000E+O0

1351802 -8.OOOOOOE-01

1351803 -6.000000E-01

1351804 -4.OOOOOOE-01

1351805 -2.000000E-01

1351806 O.OOOOOOE+0O

* SINGLE PHASE TORQUE DATA

* TORQUE CURVE NO. 1

1351900 2

1351901 O.O00000E+00

1351902 1.930000E-01

1351903 3.930000E-01

1351904 5.955200E-01

1351905 7.978200E-01

1351906 1.000000E+O0

* -------- 1 ------ 1---- -

* TORQUE CURVE NO. 2

1352000 2

1352001 O.O00000E+00

1352002 4.OOOOOOE-01

1352003 5.000000E-01

1352004 7.372550E-01

1352005 7.680490E-01

1352006 8.672300E-01

1352007 1.OOOOOOE+00

* ----.------------- 1---- -

* TORQUE CURVE NO. 3

1352100 2

1352101 -1.OOOOOOE+00

1352102 -8.009600E-01

1352103 -6.063800E-01

1352104 -4.068600E-01

1352105 -1.992800E-01

1352106 .OOOOOOE+00

* -------- 1 ------ 1---- -

* TORQUE CURVE NO. 4

135220G 2

1352201 -1.OOOOOOE+00

1.0OOO0E+00

7

-1.OOOOOOE+00

-6.300000E-01

-3.OOOOOOE-01

-5.OOOOOOE-02

1.500000E-01

2.500000E-01 --1------1-....

8

-1.OOOOOOE+00

-9.700000E-01

-9.5000OOE-01

-8.800000E-01

-8.OOOOOOE-01

-6.700000E-01

1

6.0320OOE-01

6.325000E-01

7.369000E-01

8.331000E-01

9.229000E-01

1.OOOOOOE+O0

2

-6.700000E-01

-2.500000E-01

1.5000OOE-01

5.265860E-O1

6.065940E-01

7.436600E-01

1.OOOOOOE+0O

3

1.984300E+00

1.394000E+00

1.097500E+00

8.220000E-01

6.648000E-01

6.03ZOOOE-01 . .1-.... -

--..-1------1..--

---- 1------..1.-

----1-- .... ... 1-....

---- 1----1--

--1------1-....

---- 1------1..--

..---1------1..--

---- 1------1..--

--1------1--

----1----

---- 1------1..--

..---1-- ....-1....

...1.....1------..1-. ....-1..-.

4

1.984300E+00

- 93 -
1352202 -8.223400E-01

1352203 -6.337100E-01

1352204 -4.585300E-01

1352205 -2.670230E-01

1352206 -1.761070E-01

1352207 -8.931000E-02

1352208 O.OOOOOOE+O0

* -------- -------- 1 1----

* TORQUE CURVE NO. 5

1352300 2

1352301 0.OOOOOOE+00

1352302 4.OOOOOOE-01

1352303 5.OOOOOOE-O1

1352304 1.000000E+00

*----------------- 1 ---- * TORQUE CURVE NO. 6

1352400 2

1352401 O.OOOOOOE+O0

1352402 9.064300E-02

1352403 1.885690E-01

1352404 2.734700E-01

1352405 4.586690E-01

1352406 5.744800E-01

1352407 7.381600E-01

1352408 7.685200E-01

1352409 8.700570E-01

1352410 1.OOOOOOE+00

* ---- 1------------ 1----

* TORQUE CURVE NO. 7

*-------1----1"--

1352500 2

1352501 -1.OOOOOOE+O0

1352502 -3.000000E-01

1352503 -I.OOOOOOE-O1

1352504 O.OOOOOOE+00

* ---- '------------ 1----

* TORQUE CURVE NO. 8

*-----------1-. ....-1--

1352600 2

1352601 -1.OOOOOOE+00

1352602 -2.5000OOE-01

1352603 -8.OOOOOOE-02

1352604 O.OOOOOOE+O0

* ----.---- 1 ------1----

1.830800E+00

1.682400E+00

1.557000E+00

1.436200E+00

1.387900E+00

1.348100E+00

1.233610E+00

5

-4.500000E-01

-2.5000OOE-01

O.OOOOOOE+O0

3.569000E-01

6

1.233610E+00

1.196500E+00

1.109600E+00

1.041600E+00

8.958000E-01

7.807000E-01

6.134000E-01

5.849000E-01

4.877000E-01

3.569000E-01

7

-1.OOOOOOE+O0

-9.OOOOOOE-01

-5.OOOOOOE-01

-4.500000E-01

8

-1.OOOOOOE+O0

-9.OOOOOOE-01

-8.OOOOOOE-O1

-6.700000E-01 - -------- 1 1----

....- 1----1---

....-1-----1.-

---1----1---

...-- 1------..1.-

....- 1------..1.-

---1--- ...-1.-

* TWO - PHASE MULTIPLIER DATA FROM L3-6 TEST DATA

* HEAD CURVE

*-------1----1----1----1----1-. ....- 1"

1353000

1353001

1353002

1353003

1353004

1353005

1353006

1353007

1353008

0

O.OOOOOOE+O0

1.000000E-01

2.OOOOOOE-01

3.OOOOOOE-01

3.500000E-01

4.OOOOOOE-O1

5.OOOOOOE-O1

6.OOOOOOE-O1

O.000000E+0O

0.OOOOOOE+00

1.O0000E-01

2.OOOOOOE-O1

3.OOOOOOE-O1

6.000000E-O1

6.000000E-O1

6.000000E-O1

-94-
1353009 7.000000E-01

1353010 8.000000E-01

1353011 9.000000E-01

1353012 1.OOOOOOE+00

* -------- 1 ------ 1 ---- * TORQUE CURVE

1353100 0

1353101 O.OOOOOOE+0O

1353102 1.OOOOOOE-01

1353103 2.OOOOOOE-01

1353104 3.000000E-01

1353105 3.500000E-01

1353106 4.000000E-01

1353107 5.OOOOOOE-01

1353108 6.OOOOOOE-01

1353109 7.OOOOOOE-01

1353110 8.OOOOOOE-01

1353111 9.OOOOOOE-01

1353112 1.000000E+00 *-----------1----1--

* PUM1 2-PHASE DIFFERENCE

* HEAD CURVE NO. 1

1354100 1

1354101 0.OOOOOOE+00

1354102 1.OOOOOOE+00

* ----.---- 1 ----.-- 1--- * HEAD CURVE NO. 2

1354200 1

1354201 0.OOOOOOE+00

1354202 1.OOOOOOE+00

* ----------- 1 ---- 1----

* HEAD CURVE NO. 3

*-----------1-.....-1---

1354300 1

1354301 -1.OOOOOOE+00

1354302 -9.OOOOOOE-01

1354303 -8.OOOOOOE-01

1354304 -7.OOOOOOE-01

1354305 -6.OOOOOOE-01

1354306 -5.OOOOOOE-01

1354307 -4.OOOOOOE-01

1354308 -2.500000E-01

1354309 -1.OOOOOOE-O1

1354310 O.OOOOOOE+0O

* -------- -------- 1 1----

* HEAD CURVE NO. 4

1354400 1

1354401 -1.OOOOOOE+00

1354402 -9.000000E-01

1354403 -8.000000E-01

1354404 -7.OOOOOOE-01

1354405 -6.OOOOOOE-01

1354406 -5.OOOOOOE-01

1354407 -3.5000OOE-01

6.OOOOOOE-01

5.OOOOOOE-01

3.OOOOOOE-01

0.OOOOOOE+00 ....-1------..1.... ....- 1----1--

------ 1 ------. 1-. ....-1-

0.OOOOOOE+00

O.OOOOOOE+00

1.OOOOOOE-01

3.OOOOOOE-01

5.OOOOOOE-01

7.500000E-01

7.500000E-01

7.500000E-01

7.500000E-01

7.500000E-01

5.OOOOOOE-01

0.OOOOOOE+00

DATA

1

1.OOOOOOE+00

1.OOOOOOE+00 ---- 1----1--

---- 1----1--

2

1.OOOOOOE+00

1.OOOOOOE+00

3

-1.160000E+00

-1.240000E+O0

-1.770000E+00

-2.360000E+00

-2.790000E+00

-2.910000E+00

-2. 670000E+O0

-1.690000E+00

-5.OOOOOOE-01

O.OOOOOOE+00

4

-1.160000E+00

-7.800000E-01

-5.OOOOOOE-01

-3.100000E-01

-1.700000E-01

-8.OOOOOOE-02

0.OOOOOOE+00

-- 1----1---

--1----..-1--

--1----..-1--

---- 1-- ....- 1-.

---- 1----1-.

---- 1-- ....- 1..-.

--1-----1--

---- 1------1----

--1----1--

- 95 -
1354408 -2.O00000E-Ol

1354409 -1.000000E-01

1354410 0.000000E+00 * ---- --- .. I. ....-- 1 ----

* HEAD CURVE NO. 5 ,------------1-----1----.

1354500 1

1354501 O.OOOOOOE+00

1354502 2.OOOOOOE-01

1354503 4.0OOOOOE-01

1354504 6.OOOOOOE-01

1354505 8.000000E-01

1354506 1.OOOOOOE+0O

* -------- 1 ------ 1 ---- * HEAD CURVE NO. 6

1354600 1

1354601 O.OOOOOOE+00

1354602 1.OOOOOOE-01

1354603 2.500000E-01

1354604 4.000000E-01

1354605 5.OOOOOOE-01

1354606 6.OOOOOOE-01

1354607 7.OOOOOOE-01

1354608 8.OOOOOOE-01

1354609 9.OOOOOOE-01

1354610 1.OOOOOOE+OO

* -------- 1 ------ 1 ---- * HEAD CURVE NO. 7

1354700 1

1354701 -1.0OOOOOE+00

1354702 0.OOOOOOE+00

* ----.---- 1 ------ 1----

* HEAD CURVE NO. 8

1354800 1

1354801 -1.OOOOOOE+O0

1354802 0.OOOOOOE+00

* ---- 1------------ 1----

* TORQUE CURVE NO. 1

*----------------1--

1354900 2

1354901 O.OOOOOOE+00

1354906 1.OOOOOOE+00

* -------- -------- 1 1----

* TORQUE CURVE NO. 2

1355000 2

1355001 O.OOOOOOE+00

1355007 1.000000E+00

* ---- "------------ 1--

* TORQUE CURVE NO. 3

1355100 2

1355101 -1.000000E+00

1355102 -8.009600E-01

1355103 -6.063800E-01

1355104 -4.068600E-01

5.000000E-02

8.OOOOOOE-02

1.100000E-01

5

O.OOOOOOE+00

-3.400000E-01

-6.500000E-01

-9.300000E-01

-1.190000E+00

-1.470000E+00

6

1.100000E-01

1.300000E-01

1.500000E-01

1.300000E-01

7.OOOOOOE-02

-4.OOOOOOE-02

-2.300000E-01

-5.100000E-01

-9.100000E-01

-1.470000E+00

7

O.OOOOOOE+00

O.OOOOOOE+00O ---- 1------1.-.

8

O.OOOOOOE+00

0.000000E+00 ----1------1..-

----1------1...

1

1.000000E+00

1.984300E+O0

2

1.394000E+0O 1. O00000E+00

--1------1--...

3

1. 984300E+00

1. 394000E+00

1.097500E+00

8.220000E-01

....-1------..1-,

....-1------1--

--1------1--

..---1------..1....

---1---1--

..---1-- ....- 1-..--

..---1----1---

--1------1-....

---- 1------..1....

---- 1----1--

---- 1------..1....

-96-
1355105 -1.992800E-01

1355106 O.OOOOOOE+O0

* -------- 1 ------ 1----

* TORQUE CURVE NO. 4

1355200 2

1355201 -1.OOOOOOE+O0

1355202 -8.223400E-01

1355203 -6.337100E-01

1355204 -4.585300E-01

1355205 -2.670230E-01

1355206 -1.761070E-01

1355207 -8.931000E-02

1355208 O.OOOOOOE+0O

* -------- ---1- ---- 1----

* TORQUE CURVE NO. 5

1355300 2

1355301 O.OOOOOOE+0O

1355302 4.OOOOOOE-01

1355303 5.OOOOOOE-01

1355304 1.OOOOOOE+00

* ----.---- 1 ----.-- 1 ---- * TORQUE CURVE NO. 6

1355400 2

1355401 O.OOOOOOE+00O

1355402 9.064300E-02

1355403 1.885690E-01

1355404 2.734700E-01

1355405 4.586690E-01

1355406 5.744800E-01

1355407 7.381600E-01

1355408 7.685200E-01

1355409 8.700570E-01

1355410 1.OOOOOOE+O0

* ----.---- 1 ------1----

* TORQUE CURVE NO. 7

1355500 2

1355501 -1.OOOOOOE+OO

1355502 -3.OOOOOOE-01

1355503 -1.OOOOOOE-O1

1355504 O.000000E+O0

* -------- 1 -- ----1 ---- * TORQUE CURVE NO. 8

*-----------1-. ....- 1"-

1355600 2

1355601 -1.000000E+00

1355602 -2.500000E-01

1355603 -8.OOOOOOE-02

1355604 O.OOOOOOE+O0

* -------- 1 ------ 1 ---- * RENODALIZE PUMP 2

1650000 "PCPUMP2 "

1650101 0.0 0.514

1650102 0

1650108 160010000 0.0

6.648000E-01

6.032000E-01 ---- 1----1-. ....- 1------..1-

------ 1 ---- 1---1--

4

1.984300E+00

1.830800E+00

1.682400E+00

1.557000E+00

1.436200E+00

1.387900E+00

1.348100E+00

1.233610E+00

5

-4.500000E-01

-2.500000E-01

O.O00000E+00

3.569000E-01 ---- 1----1--

6

1.233610E+00

1.196500E+00

1.109600E+00

1.041600E+00

8.958000E-01

7.807000E-01

6.1340OOE-01

5.849000E-01

4.877000E-01

3.569000E-01 ----1-----1--

7

-1.OOOOOOE+OO

-9.OOOOOOE-01

-5.000000E-01

-4.500000E-01

8

-1.000000E+00

-9.OOOOOOE-01

-8.OOOOOOE-01

-6.700000E-01

PUMP

0.0991 0.0

....- 1------1--

--1------1,--

...-- 1------1.-

....- 1------1--

....- 1------1-.-.

....- 1----1--

---1--- ...- 1--

-...- 1------..1.-

-...1------1--

....-1------..1....

90.0 0.317900

0.017 0.017 0000

- 97 -
1650109 170000000 0.0 0.1 0.1 0000

1650200 0 1.48858+7 1.22768+6 2.46241+6 0.

1650201 0 7.7855 7.7855 0.0

1650202 0 8.0481 8.0481 0.0

1650301 135 135 135 -1 -1 597 0

1650302 369.00000 .92981030 .31550000 96.000000 500.60000 1.4310000

1650303 613.60000 .00000000 207.43300 .04440000 19.598700 .00000000

1650308 0.212845 0.0 -22.86511 27.16043 5.74589

1650310 0.0 0.0 0.0

* ---- 1 "---- ----- ------ ------ .---- 1--- 1----

* REMOVE SPRAY VALVE AND CALCULATOR

*-------1----1------..1------1----1---1 1----.

4350000 SPRVLV DELETE

20590400 SPRAY DELETE 0.0 0.0 0.0 0.0 0.0 0.0

* ---- 1 -- "---- --------1------ 1 ---- 1 ------ 1----

* REMOVE PRESSURIZER TRIPS AND HEATERS

*00 5 D1IA 1 - 1 -11

0000585 DISCARD

0000586 DISCARD

0000666 510 DISCARD

0000667 510 DISCARD

0000693 510 DISCARD

0000587 DISCARD

0000588 DISCARD

0000668 510 DISCARD

0000669 510 DISCARD

0000694 510 DISCARD

14172000 DELETE

20241700 DELETE 20241800 DELETE

* --------- 1 ------ ------ 1---------- -1 -- ---- 1----

* REMOVE PRESSURIZER LEVEL CONTROLLERS, CHARGING COMPONENT, AND

* LETDOWN COMPONENT

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1 ------I----

20500200 PZRLVL SUM 1.0 0.0 1

20500201 0.0 0.1815 VOIDF 415010000

20500202 0.1524 VOIDF 415020000

20500203 0.3967 VOIDF 415030000

20500204 0.5289 VOIDF 415040000

20500205 0.3967 VOIDF 415050000

20500206 0.1943 VOIDF 415060000

20500207 0.1029 VOIDF 420010000

20500208 0.1029 VOIDF 420020000

9800000 "CHRG R" DELETE

9850000 "CHRG V" DELETE

20590500 CHARGE DELETE 0.0 0.0 0.0 0.0 0.0 0.0

9900000 "LTDWN S" DELETE

9950000 "LTDWN V" DELETE

20590600 LETDOWN DELETE 0.0 0.0 0.0 0.0 0.0 0.0

* -------- 1 ---- --- --- 1 -- --------------- 1----

* REMOVE STEAM VALVE CONTROLLER

5400000 "CV-P4-10 " VALVE

5400101 530010000 541000000 0.0047772 0.0 0.0 1100

5400201 0 16.963 20.945 0.0

5400300 MTRVLV

5400301 685 686 0.05 .649345 540

20254000 NORMAREA

20254001 0.0 7.066-3

-98-
20254002 7.066-3 7.066-3

20254003 1.0 1.0

20590700 "DELTA T"'DELETE 0.0 0.0 0.0 0.0 0.0 0.0

20590800 DEADBAND DELETE 0.0 0.0 0.0 0.0 0.0 0.0

20590900 "INT D T" DELETE 0.0 0.0 0.0 0.0 0.0 0.0

20591000 TCONTROL DELETE 0.0 0.0 0.0 0.0 0.0 0.0

20290800 DELETE

* ---------- 1 ----- ------------ 1 ---- ---- ---- 1 ---- * REMOVE FEED SYSTEM CONTROLLER

*----------1-- --- 1-. DEE1-- ....-1-- -- .01 1- 0- --.

20591100 SOLVLERR DELETE 0.0 0.0 0.0 0.0 0.0 0.0 20591200 FEEDFJJOW DELETE 0.0 0.0 0.0 0.0 0.0 0.0

5660000 "FEED " TMDPJUN

5660101 565000000 508000000 0.05

5660200 1 688

5660201 0.0 25.593 0.0 0.0

5660202 0.7 0.0 0.0 0.0

5660203 59.5 0.0 0.0 0.0

5660204 60.0 0.50364 0.0 0.0

5660205 1860.0 0.50364 0.0 0.0

5660206 1861.0 0.0 0.0 0.0

* -------- 1 -- ---------1--- --- 1 -------- ----1----

* REPLACE REACTOR POWER TABLE

20290000 POWER 699 1.0 48.9+6

20290001 0.0 1.0 * FROM RELAP4 L3-1 POSTEST

20290002 0.15 0.88

20290003 0.3 0.76

20290004 0.6 0.58

20290005 0.85 0.176

20290006 1.0 0.122605

20290007 1.3 0.1

20290008 2.0 0.087420

20290009 4.0 0.075788

20290010 7.0 0.064

20290011 10. 0.060012

20290012 25. 0.046738

20290013 65. 0.035

20290014 100. 0.031546

20290015 250. 0.025210

20290016 650. 0.0188

20290017 1000. 0.0164

20290018 1500. 0.0140

20290019 3000. 0.0110

20290020 5000. 0.0092

20290022 1.+5 0.001460 * FROM LTR L0-08-81-173

* REPLACE TRIPS 510,511,513

* SCRAM

0000510 P 100010000 LT NULL 0 1.4193+7 L

* BREAK OPENS

0000511 TIME 0 LT NULL 0 7302. N

* HPIS ON

0000513 P 100010000 LE NULL 0 13.159+6 L

0000595 TIME 0 GE NULL 0 39.3 L

0000597 TIME 0 GE NULL 0 39.3 L *-----------1----1----1----1-----1----1-...-

-99-
, RENODALIZE DEAD END OF FUEL MODULES AND BROKEN LOOP

* DEAD END OF FUEL MODULES

*--------1----1-. ....- 1----1------1------..1---

2510000 "DE FL NODS" SNGLVOL

2510101 0.0 0.7844123 0.1154214 0.0 90.0 0.7844123

2510102 3.81-6 0.214 00

2510200 0 1.49207+7 1.33213+6 2.46168+6 0.0

* -------- 1 ------ 1 ------ 1 ------ 1 ------ 1 ------ 1----

* REACTOR VESSEL NOZZLE - BROKEN LOOP HOT LEG

3000000 "RVN BLHL " BRANCH

3000001

3000101

3000102

3000200

3001101

3002101

3001201

3002201

2

0.0

4. OE-5

0

252010000

300010000

0.0

0.0

0

0.876303

0.0

1.49144+7

300000000

305000000

0.0

0.0

0.0575410 0.0

00

1.25750+6 2.46181+6

0.067014 0.0

0.063426 0.1

0.0

0.0

0.0

0.0

0.0

0.1

0.0

0002

0000

* ----.---- 1 ------ 1 ----- 1--- --- 1----

* HOT LEG PIPE TO REFLOOD ASSIST BYPASS TEE

3050000 "HLP-RABS T" BRANCH

3050001 1 0

3050101 0.0 0.698336 0.0442927 0.0

3050102 4.OE-5 0.0 00

3050200 0 1.49144+7 1.25750+6 2.461f

3051101 305010000 310000000 0.0 0.1

3051201 0.0 0.0 0.0

* --- ---- ---- ----- ----- ------ 1----

* BROKEN LOOP HOT LEG CONTRACTION

3100000 "BLHL CONTR" BRANCH

3100001 2 0

3100101 0.0 1.50013 0.0678467 0.0

3100102 4.OE-5 0.0 00

3100200 0 1.49144+7 1.25750+6 2.461•

3101101 380010000 310000000 0.0388 0.84

3102101 310010000 315000000 0.0083647 0.0

3101201 0.0 0.0 0.0

3102201 0.0 0.0 0.0

* ---------------- 1 ------ 1 -- ---- 1----

* STEAM GENERATOR AND PUMP SIMULATIOR

3150000 "SG+PMP SIM" PIPE

3150001 12

3150101 0.0 12

3150201 0.0083647 2

3150202 0.032603 4

3150203 0.105626 5

3150204 0.032603 7

3150205 0.0083647 9

3150206 0.008364 10

3150207 0.0046398 11

3150301 0.367768 1

3150302 0.552201 2

3150303 0.993978 4

----1------1----

----1------1----

0.0 0.0

0100

31+6 0.0

0.1

----1------1----

----1------1----

0.0 0.0

31+6 0.0

0.84

0.0

0100

0100

----1------1----

----1------1----

- 100 -
3150304

3150305

3150306

3150307

3150308

3150309

3150401

3150402

3150403

3150404

3150405

3150406

3150407

3150408

3150409

3150601

3150602

3150603

3150604

3150701

3150702

3150703

3150704

3150705

3150706

3150707

3150708

3150709

3150710

3150801

3150802

3150803

3150804

3150805

3150901

3150902

3150903

3150904

3150905

3150906

3150907

3150908

3150909

3151001

3151101

3151102

3151103

3151104

3151105

3151106

3151201

3151202

3151203

3151204

3151205

3151206

3151207

3151208

3151209

0.849744

0.993978

1.371350

1.365029

1.674812

0.545209

3.0767-3

4.67621-3

8.60554-2

8.97552-2

8.60554-2

1.82303-2

5.46687-2

1.82489-2

2.83241-2

90.0

-90.0

90.0

0.0

0.127000

0.552201

0.993978

0.457202

-0.457202

-0.993978

-1.371350

-0.520701

1.212851

0.0

4.OE-5

4.OE-5

4.OE-5

4. OE-5

4.OE-5

0.2

0.0

93.9

0.4

93.9

0.0

0.2

4.1

0.4

00

0000

0100

0000

0100

0000

0100

0

0

0

0

0

0

0

0

0

6

8

9

10

11

12

1

2

4

6

8

9

10

11

12

5

10

11

12

1

2

4

5

6

8

9

10

11

12

0.0

0.124

0.0

0.124

0.0

0.2

0.0

93.9

0.4

93.9

0.0

0.2

4.1

0.4

12

1

2

7

8

10

11

14914000.

14911400.

14905500.

14998100.

14992600.

14992600.

14998100.

14905500.

14914500.

3

4

6

7

12

1

2

4

5

7

8

9

10

11

1257500.

1257500.

1257500.

1257500.

1257500.

1257500.

1257500.

1257500.

1257500.

2461820.

2461870.

2461990.

2462150.

2462270.

2462270.

2462150.

2461990.

2461810.

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

0.0

01

02

03

04

05

06

07

08

09

- 101 -
3151210 0 14921(

3151211 0 14919(

3151212 0 14914:

3151300 0

3151301 0.0 0.0

*--------- 1 ------ 1----

, REACTOR VESSEL NOZZLE -

3350000 "RVN BLCL "

600. 1257500.

000. 1257500.

300. 1257500.

2461660.

2461710.

2461810.

0.0

0.0

0.0

0.0

0.0

0.0

10

11

12

0.0 11 ---- 1 ---- -- 1------ 1 ------ 1----

BROKEN LOOP COLD LEG

BRANCH

3350001

3350101

3350102

3350200

3351101

3352101

3351201

3352201

2

0.0

4.OE-5

0

202000000

335010000

0.0

0.0

0

0.749305

0.0

1.49889+7

335000000

340000000

0.0

0.0

0.047979 0.0

00

1.23500+6 2.46018+6

0.064130 1.0

0.0 0.1

0.0

0.0

0.0

0.0

1.0

0.1

0.0

0002

0000

* ---------------- 1 ------ I ------- I ---- I -- 1----

* COLD LEG PIPE TO REFLOOD ASSIST BYPASS TEE

3400000 "CLP-RABS T" BRANCH

3400001 1 0

3400101 0.0 0.698336 0.0443927 0.0 0.0 0.0

3400102 4.OE-5 0.0 00

340O200 0 1.49889+7 1.23500+6 2.46018+6 0.0

3401101 340010000 345000000 0.0 0,1 0.1 0100

3401201 0.0 0.0 0.0

* BROKEN LOOP COLD LEG CONTRACTION TO BREAK PLANE

3450000 "BLCL CONTR" BRANCH

3450001 2 0

3450101 0.0634 0.974 0.0 0.0 0.0 .0.0

3450102 4.OE-5 0.0 00

3450200 0 1.49889+7 1.23500+6 2.46018+6 0.0

3451101 345000000 370000000 0.0388 0.84 0.84 0100

3452101 345010000 350000000 0.0 0.0 0.0 0100

3451201 0.0 0.0 0.0

3452201 0.0 0.0 0.0

* -------- ---- I ---- I----

* SPOOL PIECE AND PIPE TO

3500000 "BRK SP+PPE"

3500101 0.0525 0.823

3500102 4.OE-5 0.0

ISOLATION VALVE

SNGLVOL

0.0 0.0

00

----1------1----

----1------1----

0.0 0.0

3500200 0 1.49889+7 1.23500+6 2.46018+6 0.0

*-------- 1 ------ 1------ 1 ------ 1 ------ 1 ------ 1----

" REMOVE COLD LEG ISOLATION VALVE AND COLD LEG PIPE BETWEEN

* ISOLATION VALVE AND QOBV

* ---- ----.--- ---- 1------- I -------- 3550000 "CL ISO VLV" DELETE

3600000 "CL IS-QOBV" DELETE

* ---------------- --- --- 1 -- ---- 1----

* COLD LEG QUICK OPENING BLOWDOWN VALVE

3650000 "CO QOBV " VALVE

3650101 350010000 805000000 1.27778-5 0.0

3650201 0 0.0 0.0 0.0

3650300 TRPVLV

----1------1----

----1------1----

----1------1----

0.0 0100 1.0 1.0

- 102 -
3650301 677

* - 1--- ------- 1 ---- -- ------I---- I ---- ----* REFLOOD ASSIST BYPASS PIPING - COLD LEG SIDE

3700000 "RABS C L " PIPE

3700001 3

3700101 0.0388 2

3700102 0.0776 3

3700201 0.0388 2

3700301 0.0 3

3700401 0.0279 1

3700402 0.070 2

3700403 0.1165 3

3700601 90.0 1

3700602 0.0 3

3700701 0.64 1

3700702 0.0 3

3700801 4.0-5 0.0 3

3700901 0.28 0.28 1

3700902 0.84 0.84 2

3701001 00 3

3701101 0000 2

3701201 0 1.49865+7 1.23500+6 2.46023+6 0.0 0.0 01

3701202 0 1.49841+7 1.23500+6 2.46028+6 0.0 0.0 02

3701203 0 1.49841+7 1.23500+6 2.46028+6 0.0 0.0 03

3701300 0

3701301 0.0 0.0 0.0 01

3701302 0.0 0.0 0.0 02

* -------- ------- 1 ------ 1 ---- -------- 1 ----------

* REFLOOD ASSIST BYPASS VALVES

3750000 "RABS VALVS" SNGLJUN

3750101 370010000 380000000 0.0 1.55+2

3750201 0 0.0 0.0 0.0 *-----------1-. ....- 1----1------1-----.

* REFLOOD ASSIST BYPASS PIPING - HOT LEG SIDE

3800000 "RABS H L " PIPE

3800001 3

3800101 0.0776 1

3800102 0.0388 3

3800201 0.0388 2

3800301 0.0 3

3800401 0.0915 1

3800402 0.048 2

3800403 0.0489 3

3800601 0.0 1

3800602 -90.0 2

3800603 0.0 3

3800701 0.0 1

3800702 -0.64 2

3800703 0.0 3

3800801 4.0-5 0.0 3

3800901 0.84 0.84 1

3800902 0.28 0.28 2

3801001 00 3

3801101 0000 2

3801201 0 1.49097+7 1.25750+6 2.46191

3801202 0 1.49121+7 1.25750+6 2.46186

1.55+2 0000

------------------------ 1--

---------------------------

+6 0.0 0.0 01

+6 0.0 0.0 02

- 103 -
3801203 0 1.49144+7 1.25750+6 2.46181+6 0.0 0.0 03

3801300 0

3801301 0.0 0.0 0.0 01

3801302 0.0 0.0 0.0 02

* MINOR EDIT VARIABLES

* STEADY STATE AND TRANSIENT PLOT REQUESTS

*----- 1 1001------1----1------1------1- P ..

0000301 P 250010000

0000303 P 530010000

0000303 TEMPF 250010000 0000304 TEMF 185010000

0000305 TEMPF 515010000

0000306 MFLOWJ 540000000

0000309 CNTRLVAR 1

0000310 CNTRLVAR 2

0000311 MFLOWJ 566000000

0000313 MFLOWJ 100010000

0000314 P 420010000

0000315 VOIDG 500010000

0000316 VELFJ 112010000

0000317 VELGJ 112010000

0000318 TEIPF 215010000

0000319 MFLOWJ 365000000

0000320 RHO 100010000

* -------- 1 ---- ------ 1 ------ 1 ---- 1 ------ 1----

* TEMPERATURES

0000321 SATEMP 345010000 * TE-BL-1A,1B,IC

0000322 SATTEMP 310010000 * TE-BL-2A,2B,2C

0000323 SATTEMP 100010000 * TE-PC-2A,2B,2C

0000324 SATTEMP 180010000 * TE-PC-1

0000325 SATITEP 114010000 * TE-SG-1

0000326 SATTEMP 116010000 * TE-SG-2

0000327 SATTEMP 510030000 * TE-SG-3

0000328 SATTEMP 415040000 * TE-139-19

0000329 SATTEMP 415030000 * TE-139-20

0000330 SATTEMP 205010000 * TE-1ST-1 /TE-2ST-1

0000331 SATTEMP 210010000 * TE-1ST-2 / TE-2ST-2

0000332 SATTEMP 210050000 * TE-1ST-6 / TE-2ST-6

0000333 SATTEMP 210060000 * TE-1ST-7 / TE-28T-7

0000334 SATTEMP 215010000 * TE-IST-O/ TE-2ST-10

0000335 SATTEMP 220010000 * TE-IST-13 / TE-2ST-13

0000336 SATTEMP 250010000 * TE-1UP-6

0000337 SATTEMP 251010000 * TE-2UP-4

0000338 SATTEMP 255010000 * TE-1UP-3

* -------- I-------- 1------ 1 ------------ 1 ------ 1----

* DENSITIES

*----------1------1- 1RHO .. 1----- *.. -1-1

0000341 RHO 345010000 * DE-BL-1

0000343 RHO 310010000 * DE-BL-2

0000343 RHO 180010000 * DE-PC-1

0000344 RHO 100010000 * DE-PC-3 0000345 RHO 118020000 * DE-PC-3

* -------- --- I ---- ---- ---- ------ 1---- ---- I - ---- * VELOCITIES

- 104 -
0000351 VELF 345010000 * FE-BL-1

0000352 VELF 310010000 * FE-BL-2

0000353 VELF 180010000 * FE-PC-1

0000354 VELF 100010000 * FE-PG-2

0000355 VELG 345010000 * FE-BL-1

0000356 VELG 310010000 * FE-BL-2

0000357 VELG 180010000 * FE-PC-i

0000358 VELG 100010000 * FE-PC-2

* ---------------- 1 ------ 1 ---- -- 1 ------ 1------ 1 ---- * MASS FLOW RATES

• ........ 34.....-1------1 *-1 - - - 1- - -1-

0000361 MFLOWJ 345020000 * BREAK PLANE BLUL 0000362 IILOWJ 315110000 * BREAK PLANE BILHL

0000363 MFLOWJ 345020000 * DfT-RAEE BLCL

0000364 IFLOWJ 310020000 * DIT-RAKE BLHL

0000365 MFLOWJ 180010000 * DTI-RAKE ILCL

0000366 IFLOWJ 100020000 * DTT-RAKE ILHL

0000367 MFLOWJ 400010000 * PRES. SURGE LINE FLOW

0000369 MFLOWJ 541010000 * FE-P4-12

0000370 IIFLOWJ 566000000 * FE-P4-72-1

*-------- 1 ------------ 1 ------------ 1 ------ 1 ---- C CLADDING TEMPERATURES CONTROL MODULE

0000381 HTTEMP 230000110 ,

0000382 HTTEMP 230000210 , 0000383 HITEMP 230000310 *

0000384 HTTEMP 230000410 *

0000385 HTEMP 230000510 *

0000386 HTTEMP 230000610 *

* ----------- ---- 1 ---- I-------- 1 ------ 1 ------ 1----

* LIQUID FRACTIONS IN THE PRESSURIZER *

000039....-1 ----- 1"50 1-----1- -1- -1-

0000391 VOIDF 415010000

0000392 VOIDF 415020000

0000393 VOIDF 415030000

0000394 VOIDF 415040000

0000395 VOIDF 415050000

0000396 VOIDF 415060000

0000397 VOIDF 420010000 0000398 VOIDF 420020000

* -------- 1-------- I ---- -- I---- 1---- ---- I ---- -- I--

* EGGS HEADER TO PCS

6050000 "ECGS HEADR" SNGLVOL

6050101 5.9896-3 5.0148 0.0 0.0 90.0 3.3071202

6050102 4.0-5 0.0 00

6050200 0 13595900. 172410. 2489140. 0.0

* -------- -------- I -------- I I ----1------------ I -- -- * ACCUMULATOR PIPE

6150000 "ACC PIPE " SNGLVOL

6150101 0.0 25.997165 0.4074774 0.0 0.0 0.0

6150102 4.0-5 0.0 00

6150200 0 13580200. 112409. 2489450. 0.0

*-------- 1 ------ 1 ------1 -------- -- -1 -- ---- 1 ---- * PIPING BETWEEN BREAK AND VALVE

13502000 1 5 2 1 0.0865

- 105 -
13502100 0 1

13502101 4 0.1095

13502201 4 4

13502301 0.0 4

13502401 551.0 5

13502501 350010000 0 1

13502601 -939 0 3949

13502701 0 0 0

13502801 0 0 0

* -------- 1 ------ 1 ------ 1----

* 069 BROKEN LOOP COLD LEG MASS

20506900 BLCLMASS SUM 1.0

20506901 0.0 4.79790-2 RHO

20506902 4.43927-2 RHO

20506903 6.73163-2 RHO

20506904 4.32075-2 RHO

20506905 2.79000-2 RHO

20506906 7.00000-2 RHO

20506907 1.16500-1 RHO

1

1

0

0.823

0.823

0.823 1

1 ---1--

1

1

----1----

..-.-1----1-. ....-1.--

0.0 1

335010000

340010000

345010000

350010000

370010000

370020000

370030000

REACTOR VESSEL LIQUID LEVEL CONTROL VARIABLE

20501000

20501001

20501002

20501003

20501004

20501005

20501006

* REPLAC

6400000

6400101

6400200

6400201

6400202

6400203

6400204

6400205

RVLVL SUM

0.0 1.0

1.0

1.0

1.0

1.0

1.0

HPIS 89.2.13

0.2794034 0.0

VOIDF 230010000

VOIDF 230020000

VOIDF 230030000

VOIDF 230040000

VOIDF 230050000

VOIDF 230060000

1

"HPIS",

635000000

1

-1.0

0.0

3.5+6

6.6+6

17.0+6

TMDPJUN

185000000

683

0.0

0.700

0.575

0.460

0.100

5.9896-3

P

0.0

0.0

0.0

0.0

0.0

185010000

0.0

0.0

0.0

0.0

0.0

* IMPROVE ACCUMULATOR (E J LEE 89.2.28)

* ACCUMULATOR VALVE TRIPS

*------ ---- 1--------1------1----1---- -1'--

0000579 MFLOWJ 610000000 GE NULL 0 0.0 N

0000580 CNTRLVAR 4 LT NULL 0 1.520 L

* MODIFIED THE LIMIT OF ACCUM EMPTY CASE INTO 1.52 FROM 0.939 (P160 EDR, 89.5.15) EJL

0000682 579 AND -580 N

* -------- 1 ---- 1------ 1------ 1 ------ 1 ------1----

* ACCUMULATOR LEVEL CONTROL VARIABLE

20500400 ACCMLVL INTEGRAL -6.549E-3 1.85 0

20500401 VELFJ 620010000

* -------- 1 ---- 1 ------ 1 ---- -- 1 -------- ---- ---- * ECC CHECK VALVE

*-------1------1-----1-. ....-1------..1-. ....- 1-

- 106 -
6000000 "ECC CHKVLV" VALVE

6000101 605010000 185000000 0.0 1.3869 1.3869 0100

6000201 0 0.0 0.0 0.0

6000300 TRPVLV

6000301 681

* ----.---- 1 --- ---- ---- ---- 1 ----- ------ 1----

* ECCS HEADER TO PCS

6050000 "ECCS HEADR" SNGLVOL

6050101 5.989E-3 4.8247 0.0 0.0 90.0 2.2061

6050102 1.0165-5 0.0 10

6050200 0 4.31E+6 125472. 2600290. 0.0

* ----.---- 1 ------ 1 ------ 1 ------ 1 ------ 1 ------ 1 ---- * ACCUMULATOR VALVE *-------1------1 '-----1 .... .. 1. .. 1..

6100000 "ACCUM VLV " VALVE

6100101 615010000 605000000 0.0 8.1009 8.1009 0000

6100201 0 0.0 0.0 0.0

6100300 TRPVLV

6100301 682

* ----.---- 1 ---- - 1 ---.--- 1 ------ 1 ---- -------- 1 ---- * ACCUMULATOR PIPE

6150000 "ACC PIPE " SNGLVOL

6150101 0.01608 24.5486 0.0 0.0 0.0 0.0

6150102 1.0165-5 0.0 10

6150200 3 4.31E+6 306.6

* -------- 1 ------ 1 ---- -------- 1 ------ 1 ------ 1----

* ACCUMULATOR VESSEL

* ----------- 1 - - - - - 1 - - - - - 1 - - - - - 1 - - - - - - - - - -1.--

* DO'NT ADD ACCUII COMPONENT WITH REFLOOD OPTION IN RESTART CASE

* MOVE TO S/S COMPONENT BY B. D. CHUNG

6200000 "ACCUMULATR" ACCUM

6200101 1.254 1.8261563 0.0 0.0 -90.0 -1.8261563

6200102 2.286-5 0.0 10

6200200 4.31E+6 306.6

6201101 615000000 8.213E-3 6.7582 8.3202 0

6202200 1.10 0.0 4.0251 0.67056 0.04445 0 0 0 0

*00 PLOT REQUEST VARIALES *

20300100

20300200

20301600

20301700

20301800

20301900

20302000

20302100

20302200

20302300

*20302400

20302500

20302600

P

P

VELFJ

VELGJ

RHO 10(

RHO 34,

MFLOWJ

MFLOWJ

HTTEMP

CPUTIME

ACVLIQ

MFLOWJ

MFLOWJ

X0

250010000 * UPPLENUM PRESSURE(PE-1UP-IA1)

530010000 * STEANDOME PRESSURE(PE-SGS-1)

112010000 * IL HL LIQUID VEL

112010000 * IL HL VAPOR VEL

10000 * IL HL DENSITY(DE-PC-2)

10000 * BL CL DENSITY(DE-BL-1)

365000000 *BREAK FLOW(FR-BL-111)

40O000000 *HPIS FLOW

230000310 *HOTEST CLAD TEMP(TE-5E8-34.5)

0 *CPU TIME

62000000 *ACCUMU VOL

545000000 * STEAM MASS OUT

540000000 * STAEM MASS OUT

- 107 -
20302700 MFLOWJ 569000000 * STEAM MASS IN

20302800 MFLOWJ 566000000 * STAEM MASS IN (AUX)

20302900 VOIDF 515010000 * SG2

20303000 VOIDF 515020000 *

20303100 VOIDF 515030000

20303200 VOIDF 515040000

20303300 VOIDF 515050000

20303400 VOIDG 250010000 • UPPER PLENUM

20303500 VOIDF 250010000

20303600 VOIDF 245010000

20303700 VOIDF 240010000

20303800 VOIDF 230060000

20303900 VOIDF 230050000

20304000 VOIDF 230040000

20304100 VOIDF 230030000

20304200 VOIDF 230020000

20304300 VOIDF 230010000

20304400 VOIDF 225010000

20304500 VOIDF 215010000

20304600 MFLOWJ 610000000

20304700 MFLOWJ 630000000 *LPIS

*20304800 RHO 350010000 *DENSITY BEFORE BREAK

*20304900 VOIDG 350010000

*20305000 TEMPF 35001000

20305100 CNTRLVAR 1

20305200 CNTRLVAR 2

20305300 CNTRLVAR 4

20305400 CNTRL VAR 10

20305500 CNTRLVAR 69

20305600 DT 0

20305700 MFLOWJ 100010000

* END OF INPUT DATA

- 108 -
Appendix B Data Comparison Plots

- 109 -
Data Comparison Plots

Case A:

Figure B.I.1

Figure B.I.2

Figure B.I.3

Figure B.I.4

Figure B.I.5

Figure B.I.6

Figure B.I.7

Figure B.I.8

Figure B.I.9

Case B:

Figure B.II.l

Figure B.II.2

Figure B.II.3

Figure B.II.4

Figure B.II.5

Figure B.II.6

Figure B.II.7

Figure B.II.8

Figure B.II.9

Break mass flow rate (Case A.O [Base] vs. Experiment L3-7)

HPIS volume flow rate (Case A.O [Base] vs. Experiment L3-7)

Upper plenum pressure (Case A.O [Base] vs. Experiment L3-7)

Liquid velocity of ILHL (Case A.O [Base] vs. Experiment L3-7)

Density of ILHL (Case A.O [Base] vs. Experiment L3-7)

Density of BLCL.(Case A.O [Base] vs. Experiment L3-7)

Steam doem pressure (Case A.O [Base] vs. Experiment L3-7)

Peak cladding-temperature (Case A.O [Base] vs. Experiment L3-7)

Accumulator level (Case A.O [Base] vs. Experiment L3-7)

The

The

The

The

The

The

The

The

The

effect of break discharge

effect of break discharge

effect of break discharge

effect of break discharge

effect of break discharge

effect of break discharge

effect of break discharge

effect of break discharge

effect of break-discharge

coefficient

coefficient

coefficient

coefficient

coefficient

coefficient

coefficient

coefficient

coefficient

on

on

on

on

on

on

on

on

on

break flow

HPIS flow

upper plenum pressure

ILHL liquid velocity

ILHL density

BLCL density

steam dome pressure

peak cladding temperature

accumulator level

Case C:

Figure B.III.1

Figure B.1II.Z

Figure B.III.3

Figure B.III.4

Figure B.III.5

Figure B.III.6

Figure B.111.7

Figure B.III.8

Figure B.III.9

Figure B.III.lO

The changes of pump two-phase multipliers

The effect of pump Z-phase factor on break flow

The effect of pump 2-phase factor on HPIS flow

The effect of pump 2-phase factor on upper plenum pressure

The effect of pump 2-phase factor on ILHL liquid velocity

The effect of pump 2-phase factor on ILHL density

The effect of pump 2-phase factor on BLCL density

The effect of pump 2-phase factor on steam dome pressure

The effect of pump 2-phase factor on peak cladding temperature

The effect of pump 2-phase factor on accumulator level

Case D:

Figure B.IV.l The

Figure B.IV.2 The

Figure B.IV.3 The

Figure B.IV.4 The

Figure B.IV.5 The

Figure B.IV.6 The

Figure B.IV.7 The

Figure B.IV.8 The

Figure B.IV.9 The

Figure B.IV.1O The

changes of HPIS characteristics

effect of HPIS characteristic on

effect of HPIS characteristic on

effect of HPIS characteristic on

effect of HPIS characteristic on

effect of HPIS characteristic on

effect of HPIS characteristic on

effect of HPIS characteristic on

effect of HPIS characteristic on

effect of HPIS characteristic on

break flow

HPIS flow

upper plenum pressure

ILHL liquid velocity

ILHL density

BLCL density

steam dome pressure

peak cladding temeprature

accumulator level

Case E:

Figure B.V.1

Figure B.V.2

Figure B.V.3

Figure B.V.4

Figure B.V.5

Figure B.V.6

Figure B.V.7

Figure B.V.8

Figure B.V.9

Figure B.V.IO

Figure B.V.11

The

The

The

The

The

The

The

The

The

effect

effect

effect

effect

effect

effect

effect

effect

effect

of

of

of

of

of

of

of

of

of

simpler nodalization

simpler nodalization

simpler nodalization

simpler nodalization

simpler nodalization

simpler nodalization

simpler nodalization

simpler nodalization

simpler nodalization

0

0

0

0

0

0

0

0

0

in break flow

in HPIS flow

in upper plenum pressure

in ILHL liquid velocity

in ILHL density

n BLCL density

n steam dome pressure

in peak cladding temperature

in accumulator level

on CPU vs. simulated time

on DT vs. simulated time

The effect of simpler nodalization

The effect of simpler nodalization

- 110 -
L3-7 (CASE A.O)

MASS FLOW RATE (BREAK)

I

0

0ý

2.4

2.2

2

1.8

1.6

1.4

1.2

1

0.8

0.6

0.4

0.2

0

0 0.2 0.4 0.6 0.8 1 1.2 1.4 1.6 1.8

(Thousands)

TIME (SEC)

Break mass flow rate (Case A.O [Base] vs. Experiment L3-7) Figure B.I.1
L3-7 (CASE A.O)

VOLUME FLOW (HPIS)

I-A

0

1.2

1.1

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

0.1

0

-0.1

-0.2

0 2 4 8 8

(Thousands)

TIME (SEC)

10

Figure B.I.2 HPIS volume flow rate (Case A.O [Base) vs. Experiment L3-7)
L3-7 (CASE A.O)

UPPER PLENUM PRESSURE

I--A

IL

0c

.2

15

14.

13

12

11

10

9

8

7

6

5

4

3

2

1

0

0 2 4 6 8

(Thousands)

TIME (Sec)

Figure B.I.3 Upper plenum pressure (Case A.0 [Base] vs. Experiment W3-7)

10
L3-7 (CASE A.O)

UQUID VELOCITY (I.L H.L)

12

11 -

10 -

9-

8-

7-

6-

5-

4-

3-

13 Exp. FE-PC-002

Col. VELFJ-11201

I

0

I

2

1

0

-1

-2

I

I-I

0 2

I 4

4- I I

6

(Thousands)

TIME (SEC)

8

i

10

Figure B.I.4 Liquid velocity of ILHL (Case A.O [Base] vs. Experiment L3-7)
L3-7 (CASE A.O)

INTACT LOOP HOT LEG

1

0.9

I-A

p-A

0

0.8

0.7

0.6

0.5

02 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.I.5 Density of ILHL (Case A.O [Base] vs. Experiment L3-7)
L3-7 (CASE A.O)

BROKEN LOOP COLD LEG

0)

Esz 9

w

a

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

lME (sEc)

Figure B.I.6 Density of BLC, (Case A.O [Base] vs. Experiment I,3-7)

10
L3-7 (CASE A.O)

STEAM DOME PRESSURE

C0

W c

8

7

6

5

4

3

2

1

I

0 2 4 6 8

(Thousands)

WIME (SEC)

10

Figure B.I.7 Steam doem pressure (Case A.O [Base] vs. Experiment W3-7)
L3-7 (CASE A.O)

CLADDING TEMPERATURE

00

Iii

a:

a.

700

680

660

640

620

600

580

560

540

520

500

480

460

440

420

400

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.I.8 Peak cladding temperature (Case A.O [Base] vs. Experiment L3-7)
L3-7 (CASE A.O)

ACCUMULATOR LEVEL

e1%

Ei

'aw

1.9

1.85

1.8

1.75

1.7

1.65

1.6

1.55

1.5

0 2 4 6 8

(Thousands)

11ME (SEC)

Figure B.I.9 Accumulator level (Case A.O [Base] vs. Experiment W3-7)

10
L3-7 ( CASE A.O , B.1&B.6 )

MASS FLOW RATE (BREAK)

2.4

2.2

2

1.8

1.6

1.4

1.2

0,

0

I

1

I

0.8

0.6

0.4

0.2

0

0 0.2 0.4 0.6 0.8 1

(Thousands)

TIME (SEC)

1.2 1.4 1.6 1.8

Figure B.II.1 The effect of break discharge coefficient on break flow
L3-7 ( CASE A.O, B.1&B.6 )

VOLUME FLOW (HPIS)

1.2

1.1

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0

I

I

0.2

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.II.2 The effect of break discharge coefficient on HPIS flow
L3-7 ( CASE-A.O , B.1&B.6)

UPPER PLENUM PRESSURE

15

14

13

12

1.1

10

a. I

9

8

7

6

5

3

2

1

0

0 2 4 6 8

(Thousands)

TIME (Sec)

10

Figure B.II.3 The effect of break discharge coefficient on upper plenum pressure
L3-7 ( CASE A.0, B.1&B.6 )

UQUID VELOCrlY (I.L H.L),"

.12*

10-V

o EXp. FE-PC-002

CASE A.0 (Cd 1.0&1.0)

A CASE 9.1 (Cd 1.2&1.0)

9- V CASE B.6 (Cd 0.9&0.9)

8-

'NE

0

-,

7

6

:5.

4

3

2

-

.0

-1

-2

I ~bJ~ ~L

I I ~ I -I I I . I

0 2 4 6 8 10

(Thousands)

TIME (SEC)

Figure B.II.4 The effect of break discharge coefficient on ILII liquid velocity
L3-7 ( CASE A.O , B.1&B.6 )

INTACT LOOP HOT LEG

1

0.9

E,

a

0.8

I

I-J

I 0.7

0.6

0.5

0 2 4 8 5

(Thousands)

TIME (SEC)

10

Figure B.II.5 The effect of break discharge coefficient on ILHL density
L3-7 ( CASE A;O , B.I&B.6 )

BROKEN LOOP COLD LEG

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

CDz

Y C

0

1-

z

Id

a

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.II.6 The effect of break discharge coefficient on BLCL density
L3-7 ( CASE A.O , B.1&B.6 )

STEAM DOME PRESSURE

8

7-

6

I

a.

a.2

Cr

a.

5

4

3

2

1

0 2 ( ud 6 8

(ThousaEdC) •.. : TIME (SEC)"

10

Figure B.II.7 The effect of break discharge coefficient on steamddome pressure
L3-7 ( CASE A.0 , B.1&EB.6 )

CLADDING TEMPERATURE

700

680 0 Exp. TE-5E8-34.5

660 - CASE A.0 (Cd 1.0&1.0)

A CASE B.1 (Cd 1.2&1.0)

640 - V CASE B.6 (Cd 0.9&0.9 )

620 -

600'

580

II 560

* g 540

520

500,

480:

4 6 0 ....

440

420

400

0 2 4 6 8 10

(Thousands)

TiME (SEC)

Figure B.II.8 The effect of break discharge coefficient on peak cladding temperature
L3-7 ( CASE A.O., B.1&B.6 )

ACCUMULATOR LEVEL

1.9

1.85

1.8

1.75

I

1.7

I

1.65

1.6

1.55

1.5

0 2 4 6 8

(Thousands)

TiME (sEc)

10

Figure B.II.9 The effect of break discharge coefficient on accumulator level
LOFT PUMP TWO PHASE MULTIPLIER

Head Curves

1.2

1.1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

0.1

0

0 0.2 0.4 0.6 0.8

Void FracUon

Figure B.III.1 The changes of pump two-phase multipliers

- 129 -
LOFT PUMP TWO PHASE MULTIPLIER

Torque Curves

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

0.1

0

0 0.2 0.4 0.6 0.8

Void Fradion

Figure B.III.1 The changes of pump two-phase multipliers

- 130 -
L3-7 ( CASE A.O & CASE C.O )

MASS FLOW RATE (BREAK)

CA3

I."

I

0'

2.4

2.2

2

1.8

1.6

1.4

1.2

1

0.8

0.6

0.4

0.2

0

0 0.2 0.4 0.6 0.8 1

(Thousands)

TIME (SEC)

1.2 1.4 1.6 1.8

Figure B.III.2 The effect of pump 2-phase factor on break flow
L3-7 ( CASE A.0 & CASE C.0 )

VOLUME FLOW (HPIS)

CA

0

1.2

1.1

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

TIME (SEC)

Figure B.III.3 The effect of pump 2-phase factor on HPIS flow

10
L3-7 ( CASE A.O & CASE C.O )

UPPER PLENUM PRESSURE

I

a

0~

wc

w

0.

15

14

13

12

11

10

9

8

7

6

5

4

3

2

1

0

0 2 4 6 8

(Thousands)

TIME (Sec)

10

Figure B.III.4 The effect of pump 2-phase factor on upper plenum pressure
L3-7 ( CASE A.O & CASE C.0 )

UQUID VELOCrlY (I.L H.L)

12

11

10 -

9-

8-

k

I

o3 Exp. FE-PC-002

CASE A.0 (Cd 1.0&1.0) [L3-6]

A CASE C.0 (Cd 1.0&1.0) [Chen]

7-

0

'N

0

0

-J

tLi

I

6-

5-

4

3-

2-

1 -

0 -4

-1 -

-2 -

I

4$

4 I

2 0 4

I I

6

(Thousands)

TIME (SEC)

8

I

10

Figure B.III.5 The effect of pump 2-phase factor on ILHL liquid velocity
L3-7 ( CASE.A.0 & CASE C.0 )

INTACT LOOP HOT LEG

1

0.9

!.1

03

0

0

wi

0

0.8

0.7

0.6

0.5

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.III.6 The effect of pump 2-phase factor on ILHL density
L3-7 (CASE A.0. & CASE C.0)

BROKEN LOOP COLD LEG

1-

0.9 -

0.8 -

0.7

0.6

0.5

0) 0.4

0.3 -

* CASE C.0 (Cd 1.0&1.0) [Chen]

-0.2

0 2 4 6 8 10

(Thousands)

11ME (SEC)

Figure B.III.7 The effect of pump .-phase factor on BLCI density
L3-7 ( CASE A.0 & CASE C.0 )

STEAM DOME PRESSURE

C-.,

a.

Lld

M.2

8

7

6

5

4

3

2

0 2 4 6 8

(Thousands)

TiME (SEC)

10

Figure B.III.8 The effect of pump 2-phase factor on steam dome pressure
(3c

Lii [2<

UI) LIi t/

C4-4

cC/) toV2

C.D Cý

0 

4-4

Q-4

Cq,

-X4

0 0 000 0o0 00 0 00 0 0 00' 0~c cw w -N a ccc N 0 wc cc -.4 N 0

r- ~ ~ ~ ~ N cc c c c N n ivn i n - -l4

- 138 -
L3-7 ( CASE A.0 & CASE C.0 )

ACCUMULATOR LEVEL

1.9

1.85

1.8

1.75

E

-J

w~ 1.7

1.65

1.6

1.55

1.5

0 2 4 6 8

(Thousands)

TIME (SEC)

Figure B.III.1O The effect of pump Z-phase factor on accumulator level

10
HPIS CHARACTERISTIC CURVES

HIGHER AND LOWER CAPACIES

O~c

'.- 0

I

20

19

18

17

16

15

14

13

12

11

10

9

8

7

6

5

4

3

2

1

0

0 0.2 0.4 0.6 0.8 1

VOLUM FLOW (L/s)

Figure B.IV.1 The changes of HPIS characteristics
L3-7 ( CASE A.O , CASE D.1&D.2 )

MASS FLOW RATE (BREAK)

2.4

2.2

2

1.8

1.6

1.4

1.2

0

N,

1,.-A

1.-

0

1

0.8

0.6

0.4

0.2

0

0 0.2 0.4 0.6 0.8 1

(Thousands)

TIME (SEC)

1.2 1.4 1.6 1.8

Figure B.IV.2 The effect of HPIS characteristic on break flow
L3-7 ( CASE A.O , CASE D.1&D.2 )

VOLUME FLOW (HPIS)

1.2

1.1

1

0.9

0.8

0.7

0.6

'-I

0

N

-J

0

ii:~

0.5

0.4

0.3

0.2

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

liME (SEC)

Figure B.IV.3 The effect of HPIS characteristic on HPIS flow

10
L3-7 ( CASE A.O , CASE D.1&D.2 )

UPPER PLENUM PRESSURE

15

14-

13

12

11

10

IL

C,-. (dc

9

8

7

6

4

3

2

1

0

0 2 4 6 a

(Thousands)

TIME (Sec)

10

Figure B.IV.4 The effect of HPIS characteristic on upper plenum pressure
L3-7 ( CASE A.O , CASE D.I&D.2 )

UQUID VELOCITY (I.L H.L)

12 •

11

10

9-

'.•=8 -

1~~

I

* Exp. FE-PC-002

CASE A.0 (Cd 1.0&1.0) [Nominal]

* CASE D.1 (Cd 1.0&1.0) [Higher]

V CASE D.2 (Cd 1.0&1.0) [Lower]

7

I

0

-J

Id I

6

5-

4-

3-

2 -

1 -

I

0 t-

-'I.

-1

-2 -I

0

I I I I I I I

2 4 8 8

(Thousands)

1IME (SEC)

10

Figure B.IV.5 The effect of HPIS characteristic on ILHL liquid velocity
L3-7 ( CASE A.O ,-CASE D.1&D.2 )

INTACT LOOP HOT LEG

I

0.9

Ica,t

U,E.-.

U.-., 0

02

0.8

0.7

0.6'

0.5

0 2 4 6 8

(Thousands)

ME (SEC)

10

Figure B.IV.6 The effect of HPIS characteristic on ILHL density
L3-7 ( CASE A.O , CASE D.1&D.2 )

BROKEN LOOP COLD LEG

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

I

E,

U',m

I 0

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.IV.7 The effect of HPIS characteristic on BLCL density
L3-7 ( CASE A.O , CASE D.1&D.2 )

STEAM DOME PRESSURE

(La

W C

8

7

6

5

4

3

- I

I

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.IV.8 The effect of HPIS characteristic on steam dome pressure
L3-7 ( CASE A.O , CASE D.1&D.2 )

CLADDING TEMPERATURE

I

700

680

660

640

620

600

580

560

540

520

500

480

460

440

420

400

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.IV.9 The effect of HPIS characteristic on peak cladding temeprature
L3-7 ( CASE A.0 , CASE D.I&D.2 )

ACCUMULATOR LEVEL

1.9

1.85

1.8

1.75

1.7

1.65

1.6

1.55

1.5

0 2 4 6 8

(Thousands)

TME (sEc)

Figure B.IV.1O The effect of HPIS characteristic on accumulator level

10
L3-7 ( CASE A.O & CASE E.O )

MASS FLOW RATE (BREAK)

2.4

2;2

2

1.8

1.6

1.4

1.2

I

0

1N

I

1

0.8

0.6

0.4

0.2

0

0 0.2 0.4 0.6 0.8 1

(Thousands)

TIME (SEC)

1.2 1.4 1.6 1.8

Figure B.V.1 The effect of simpler nodalization on break flow
L3-7 ( CASE A.O & CASE E.O )

VOLUME FLOW (HPIS)

1.2

1.1

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

-I-

-C..,

'-

0

0.2

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.V.2 The effect of simpler nodalization on HPIS flow
L3-7 ( CASE A.O & CASE E.O )

UPPER PLENUM PRESSURE

15

14 0 Exp. PE-1UP-1A1

CASE A.0 (Cd 1.0&1.0) [Base Nodalizatlon]

13 -~ CASE E.0 (Cd 1.0&1.0) [Simpler NodalizatlIon]

12

11

10

CL 9

C" 8 n,2

noLI)j 7

6

5

4

3

2

1

0- I I I I I

0 2 4 6 8 1

(Thousands)

TIME (Sec)

Figure B.V.3 The effect of simpler nodalization on upper plenum pressure
L3-7 ( CASE A.O & CASE E.O )

UQUID VELOCITY (t.L H.L)

12

11 ,

10 -

9-

8-

I

El Exp. FE-PC-002

CASE A.0 (Cd 1.0&1.0) (Base Nodalizatton]

A CASE E.0 (Cd 1.0&1.0) (Simpler Nodalization] I

I-A

C-"

0,

E

0

-J

w

7-

6-

5-

4-

3-

2

1

0

-1

-2

I

.~. -~ -~2¶-~----(7 YT ~~r' A

1'

..1

0

I I I I I I I

2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.V.4 The effect of simpler nodalization on ILHL liquid velocity
L3.-7 ( CASE A.O & CASE E.O )

INTACT LOOP HOT LEG

0.9

M'-

0

0.8

I-A

0.7

0.6

0.5

0 2 4 6 8

(Thousands)

"riME (sEc)

Figure B.V.5 The effect of simpler nodalization on ILHL density

10
L3-7 ( CASE A.O & CASE E.O )

BROKEN LOOP COLD LEG

1

0.9

0.8

0.7

0.6

0.5

0.4

0.3

0.2

9~

%-, a

U,

I~J

C

'-ACM' C.U

I,

0.1

0

-0.1

-0.2

0 2 4 6 8

(Thousands)

TIME (SEC)

Figure B.V.6 The effect of simpler nodalization on BLCL density

10
L3-7 ( CASE A.O & CASE E.O )

STEAM DOME PRESSURE

I

0

t.

X.2

8

7

6

5

4

3

2

1

I

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.V.7 The effect of simpler nodalization on steam dome pressure
L3-7 ( CASE A.O & CASE E.O )

CLADDING TEMPERATURE

I

Li]

0.

w

I700

680

660

640

620

600

580

560

540

520

500

480

460

440

420

400

0 2 4 6 8

(Thousands)

TIME (SEC)

10

Figure B.V.8 The effect of simpler nodalization on peak cladding temperature
L3-7 ( CASE A.O & CASE E.O )

ACCUMULATOR LEVEL

1.9

1.85

1.8

1.75

I

Id 1.7

I

1.65

1.6

1.55

1.5

0 2 4 6 8

(Thousands)

flME (SEC)

Figure B.V.9 The effect of simpler nodalization on accumulator level

10
L3-7 ( CASE A.O & CASE E.O )

CPU vs SIMULATED TIME

40

35 -

30 -

25 -

20 -

15 -

CSAE A.0 (Cd 1.0&1.0) (Base Nodalization]

A CASE E.0 (Cd 1.0&1.0) (Simpler Nodalization]

I-A

1;)

C

a.,

10

5

0

0

I I I I I I I I

2 4 6 8 10

(Thousands)

TIME (SEC)

- Figure B.V.1O The effect of simpler nodalization on CPU vs. simulated time
L3-7 ( CASE A.O & CASE E.O )

D.T (Max Time Step)

CSAE A.0 (Cd 1.0&1.0) [Base Nodaliz

0.9 - A CASE E.0 (Cd 1.0&1.0) [Simpler Nod4

0.8 -

0.7 -

0.6 -

0.5 -

P 0.4 -

0.3

0.2 1

0.1

0 '

ation)

alization]

0 2 4 6

(Thousands)

TiME (SEC)

- Figure B.V.11 The effect of simpler nodalization on DT vs. simulated time
NRC FORM 335 U.S. NUCLEAR REGULATORY COMMISSION 1. REPORT NUMBER

12.Bg) IANbwd bV NRC. Add Vol.. Sop.. A..., NRCM 1102. emd Addell~tstm Nwntsr, it onv*.),

,.3202 32 BIBLIOGRAPHIC DATA SHEET

fS, insrruc,,ons on th, nversel NUREG/IA-0031

2 TITLE ANC SUBTITLE

13 DA•TE REPORT PUBLISWED

ICAP Assessment of RE1APS/MOD2, Cycle 36.05 Against ,. P US

LOFT Small Break Experiment L3-7 Aprti 19§06

4. FIN OR GRANT NUMBEP

5. AUTHOR(S) 6. TYPE OF REPORT

Euy-Joon Lee Technical

Bub-Dong Chung 7. PER,!1 D COVERED

Hho-Jung Kim

8. PEA FORMING ORGANI I ION -- NAME ANU A •U, imcoft • NRC.O D 'ro8Vls lW~o R.O Ce Of R0900. U.S. Nuc•ler Reularorv COm-sin$1 . and ma~hnig l•rets 0 conttr~rjr vwe• ns,,, a.nd maling add•lessl

Korea Nuclear Safety Center (KNSC)

Korea Advanced Energy Research Institute (KAERI)

P.O. Box 7, Daeduk-Danji

Daejon - Korea

9. SPONSOR ING ORGAN IZATION - NAME AND ADO R ESS fit NRC. rI.De **Same *s *bO~e~ S COIIt'JCO'. pO~,d# NRC ..,gon. Of he. o~ A.g~on. Id £ N.,cl.., A.guLaror,' Con,,.,,..on. 9. SPO NSORA I NG 0ORG AN I ZA TI10N - N AM E A ND A DO A E SS fit NR¢. wve "San as obov -. ,d coi•c,. provide NRC Dson. Office or Regin. U.1 Nuclear Rogulrory Comrnowo.

anoTVM9d" add'lesid

Office of Nuclear Regulatory Research

U.S. Nuclear Regulatory Commission

Washington, DC 20555

10. SUPPLEMENTARY NOTES

11. ABSTRACT f200.ros of leThe LOFT small break (I in-dia) experiment L3-7 has been analyzed using

the reactor thermal hydraulic analysis code RELAP5/MOD2, Cycle 36.05.

The base calculation (Case A) was completed and compared with the

experimental data. Three types of sensitivity studies (Cases B, C

and D) were carried out to investigate the effects of (1) break discharge

coefficient Cd, (2) pump two-phase difference multiplier and (3) High

Pressure Injection System (HPIS) capacity on major thermal and hydraulic

(T/H) parameters. A nodalization study (Case E) was conducted to assess the

Phenomena with a simplified nodalization.

12. KEY WORDS/DESCR!PTORS ,L,s, 10,o'U0o11 O .h,'4s that dt,l assiltrelaerciers in loCatfingMe WOrt.J 13 AVAILABILITV STATEMENT

Unlimited

LOFT, Small Break ,SCURITY CLASSIFICATION

I riji Pjaei

Unclassified

(tils RAwool

Unclassified

15. NUMBER OF PAGES

16. PRICE

NRC FORM 335 1249'




UNITED STATES

NUCLEAR REGULATORY COMMISSION

WASHINGTON, D.C. 20555

OFFICIAL BUSINESS

PENALTY FOR PRIVATE USE. $300

SPECIAL FOURTH-CLASS RATEI APOSTAGE & FEES PAID

U USNRC 

1

PERMIT No. G-67