Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Information Collection Request Emission Test Program Report

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, November 21, 2011 Page 1 of 35
Information Collection Request Emission Test Program Report

Facility Information:

Cleco Power, LLC

275 Rodemacher Road

Lena LA 71447

Contact: Paul Turregano

Phone: 318 484-7413

Fax:

Email: paul.turregano@clecl.com

Testing Company:

Shaw E & I

4171 Essen Lane

Baton Rouge LA 70809

Contact:Richard Ishikawa

Phone: 225 932-2745

Fax:

Email: richard.ishikawa@shawgrp.com

Air Permit Number: Permitted Source ID/Name:

7446811 Cleco Rodemacher Power Station

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rat

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Boiler 32 216 0 0 0 4.5 12.5 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Boiler 32 Carbon Monoxide Method 10 3 120 0

Boiler 32 2,3,7,8-TCDD Method 23 3 480 0

Boiler 32 1,2,3,7,8-PeCDD Method 23 3 480 0

Boiler 32 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Boiler 32 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Boiler 32 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

EPA's Information Collection Request for electric utility 

steam generating units

0

Monday, November 21, 2011 Page 2 of 35
Information Collection Request Emission Test Program Report

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Boiler 32 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Boiler 32 OCDD Method 23 3 480 0

Boiler 32 2,3,7,8-TCDF Method 23 3 480 0

Boiler 32 1,2,3,7,8-PeCDF Method 23 3 480 0

Boiler 32 2,3,4,7,8-PeCDF Method 23 3 480 0

Boiler 32 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Boiler 32 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Boiler 32 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Boiler 32 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Boiler 32 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Boiler 32 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Boiler 32 OCDF Method 23 3 480 0

Boiler 32 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Boiler 32 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Boiler 32 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Boiler 32 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Boiler 32 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Boiler 32 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Boiler 32 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Boiler 32 Method 23 3 480 0

Boiler 32 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Boiler 32 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Boiler 32 Method 23 3 480 0

Total organic compounds 

(TOC) as Methane

Boiler 32 Method 25A 3 120 0

Boiler 32 Total PM2.5 OTM - 27/28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

Boiler 32 OTM - 27/28 3 240 0

Organic Condensible 

Particulate

Boiler 32 OTM - 27/28 3 240 0

Boiler 32 Filterable PM2.5 OTM - 27/28 3 240 0

Boiler 32 Selenium Method 29 3 240 0

Boiler 32 Arsenic Method 29 3 240 0

Boiler 32 Beryllium Method 29 3 240 0

Boiler 32 Cadmium Method 29 3 240 0

Boiler 32 Chromium Method 29 3 240 0

Boiler 32 Cobalt Method 29 3 240 0

Boiler 32 Lead Method 29 3 240 0

Boiler 32 Manganese Method 29 3 240 0

Boiler 32 Nickel Method 29 3 240 0

Boiler 32 Antimony Method 29 3 240 0

Boiler 32 Co2 Method 3A CO2 3 60 0

Boiler 32 O2 Method 3A O2 3 60 0

Boiler 32 Sulfur Dioxide Method 6C 3 120 0

Boiler 32 Nitrogen oxides (NOx) Method 7E 3 120 0

Monday, November 21, 2011 Page 3 of 35
Information Collection Request Emission Test Program Report

Monday, November 21, 2011 Page 4 of 35
Information Collection Request Emission Test Program Report

Sampling / Stack Data Results Summary

Location Boiler 32 - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Boiler 32 - Method 10 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 5 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 10 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Boiler 32 - Method 10 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 6 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 23

Average

Run Number 1 2 3

Test Date 2/17/2011 2/18/2011 2/19/2011

Run Start Time 4:42:00 AM 8:20:00 

AM

8:25:00 AM

Run Finish Time 8:15:00 AM 4:39:00 PM 4:36:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 253.699 259.440 259.359 257.499

Moisture Content of Stack Gas, % 9.99 9.37 9.47 9.610

Moisture Saturation at Stack Gas Temperature, % 49.98 48.85 51.94 50.257

Carbon Dioxide, % 14.7 14.7 15.1 14.833

Oxygen, % 5 5 4.5 4.833

Average Stack Gas Temperature, °F 178.92 178.00 180.83 179.250

Dry Volumetric Flow Rate, dry scfm 648,138.4 666,629.3 654,834.6 656,534.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 874,559.1 889,979.9 877,612.7 880,717.233

Percent Isokinetic of Sampling Rate, % 104.3 103.7 105.5 104.500

F-Factor, dscfm/MMBtu @ %O2 9968 9854 10036 9,952.667

Fw

Fc

Location Boiler 32 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 7 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Boiler 32 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 8 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Boiler 32 - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 9 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A CO2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Boiler 32 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 10 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Boiler 32 - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, November 21, 2011 Page 11 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A O2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Boiler 32 - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, November 21, 2011 Page 12 of 35
Information Collection Request Emission Test Program Report

Emissions Summary

Location: Boiler 32 - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 2/17-1

Elb/hr 2.97E+01 2.96E+01 2.61E+01 28.467

lb/mmBtuO2 9.97E-02 1.01E-02 8.72E-03 0.040

ppm 1.02E+01 1.05E+01 9.22E+00 9.973

ppm@7%O2 9.21E+00 9.39E+00 8.01E+00 8.870

Location: Boiler 32 - Method 10 3

Compound: Carbon Monoxide

Average

Run 2/17-2 2/17-3 2/18-1

Elb/hr 2.81E+01 3.31E+01 2.49E+01 28.700

lb/mmBtuO2 9.40E-03 1.17E-02 8.03E-03 0.010

ppm 9.93E+00 1.17E+01 8.58E+00 10.070

ppm@7%O2 8.63E+00 1.08E+01 7.45E+00 8.960

Location: Boiler 32 - Method 10 3 6

Compound: Carbon Monoxide

Average

Run 2/18-2 2/18-3 2/19-1

Elb/hr 2.48E+01 2.64E+01 2.50E+01 25.400

lb/mmBtuO2 7.98E-03 8.56E-03 8.14E-03 0.008

ppm 8.53E+00 9.09E+00 8.75E+00 8.790

ppm@7%O2 7.41E+00 7.95E+00 7.42E+00 7.593

Location: Boiler 32 - Method 10 3 6 9

Compound: Carbon Monoxide

Average

Run 2/19-2 2/19-3 3

Elb/hr 2.12E+01 2.19E+01 5.78E+01 33.633

lb/mmBtuO2 6.94E-03 7.23E-03 1.92E-02 0.011

ppm 7.42E+00 7.68E+00 2.01E+01 11.733

ppm@7%O2 6.33E+00 6.59E+00 1.78E+01 10.240

Location: Boiler 32 - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000495 0.0000000181 0.0000000244 0.000

lb/mmBtuO2 5.64E-12 1.99E-12 2.65E-12 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000158 0.00000000766 0.00000000326 0.000

lb/mmBtuO2 1.80E-12 8.43E-13 3.54E-13 0.000

Monday, November 21, 2011 Page 13 of 35
Information Collection Request Emission Test Program Report

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000318 0.00000000398 0.00000000375 0.000

lb/mmBtuO2 3.62E-12 4.38E-13 4.08E-13 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000244 0.00000000626 0.0000000061 0.000

lb/mmBtuO2 2.78E-12 6.89E-13 6.63E-13 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000252 0.00000000503 0.00000000438 0.000

lb/mmBtuO2 2.87E-12 5.54E-13 4.76E-13 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000021 0.0000000054 0.00000000525 0.000

lb/mmBtuO2 2.39E-12 5.94E-13 5.71E-13 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000216 0.00000000432 0.00000000377 0.000

lb/mmBtuO2 2.46E-12 4.75E-13 4.10E-13 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000227 0.00000000583 0.00000000567 0.000

lb/mmBtuO2 2.58E-12 6.42E-13 6.16E-13 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000266 0.00000000531 0.00000000463 0.000

lb/mmBtuO2 3.03E-12 5.84E-13 5.03E-13 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000001181 0.00000000395 0.00000000395 0.000

lb/mmBtuO2 1.34E-12 4.35E-13 4.29E-13 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000161 0.00000000271 0.00000000314 0.000

lb/mmBtuO2 1.83E-12 2.98E-13 3.41E-13 0.000

Monday, November 21, 2011 Page 14 of 35
Information Collection Request Emission Test Program Report

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.00000153 0.0000000309 0.0000000264 0.000

lb/mmBtuO2 1.74E-10 3.40E-12 2.87E-12 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.0000305 0.000021 0.0000255 0.000

lb/mmBtuO2 3.47E-09 2.31E-09 2.77E-09 0.000

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000123 0.0000182 0.0000251 0.000

lb/mmBtuO2 1.40E-08 2.00E-09 2.73E-09 0.000

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000596 0.0000288 0.0000222 0.000

lb/mmBtuO2 6.79E-09 3.17E-09 2.41E-09 0.000

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.00000449 0.0000039 0.00000304 0.000

lb/mmBtuO2 5.11E-10 4.29E-10 3.30E-10 0.000

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.000194 0.000558 0.0000942 0.000

lb/mmBtuO2 2.21E-08 6.14E-08 1.02E-08 0.000

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000148 0.000101 0.0000575 0.000

lb/mmBtuO2 1.69E-08 1.11E-08 6.25E-09 0.000

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000239 0.00000000478 0.00000000417 0.000

lb/mmBtuO2 2.72E-12 5.26E-13 4.53E-13 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000159 0.00000000268 0.0000000031 0.000

lb/mmBtuO2 1.81E-12 2.95E-13 3.37E-13 0.000

Monday, November 21, 2011 Page 15 of 35
Information Collection Request Emission Test Program Report

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000001127 0.00000000303 0.00000000271 0.000

lb/mmBtuO2 1.28E-12 3.34E-13 2.95E-13 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000101 0.0000000104 0.00000000279 0.000

lb/mmBtuO2 1.15E-12 1.14E-12 3.03E-13 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.000000983 0.000000234 0.0000000976 0.000

lb/mmBtuO2 1.12E-10 2.58E-11 1.06E-11 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.00000107 0.000000533 0.0000000668 0.000

lb/mmBtuO2 1.22E-10 5.87E-11 7.26E-12 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.00000861 0.00000704 0.00000011 0.000

lb/mmBtuO2 9.80E-10 7.75E-10 1.20E-11 0.000

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000231 0.0000151 0.000000121 0.000

lb/mmBtuO2 2.63E-09 1.66E-09 1.32E-11 0.000

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000242 0.000000136 0.000000158 0.000

lb/mmBtuO2 2.76E-12 1.50E-11 1.72E-11 0.000

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000254 0.00000000468 0.00000000526 0.000

lb/mmBtuO2 2.89E-12 5.15E-13 5.72E-13 0.000

Location: Boiler 32 - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

Elb/hr 5.57E-01 9.57E-01 4.49E-01 0.654

Monday, November 21, 2011 Page 16 of 35
Information Collection Request Emission Test Program Report

lb/mmBtuO2 1.88E-04 3.22E-04 1.60E-04 0.000

ppm 3.44E-01 5.91E-01 2.77E-01 0.404

ppm@7%O2 3.01E-01 5.17E-01 2.57E-01 0.358

Location: Boiler 32 - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0011 0.0011 0.0011 0.001

lb/mmBtuO2 2.43E-07 2.43E-07 2.35E-07 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.0013 0.001 0.001 0.001

lb/mmBtuO2 2.87E-07 2.21E-07 2.14E-07 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00002 0.00003 0.00002 0.000

lb/mmBtuO2 4.42E-09 6.63E-09 4.28E-09 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0004 0.0009 0.0002 0.001

lb/mmBtuO2 8.83E-08 1.99E-07 4.28E-08 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0047 0.0024 0.0028 0.003

lb/mmBtuO2 1.04E-06 5.31E-07 5.99E-07 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.002 0.001 0.0019 0.002

lb/mmBtuO2 4.42E-07 2.21E-07 4.06E-07 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0015 0.0022 0.0019 0.002

lb/mmBtuO2 3.31E-07 4.86E-07 4.06E-07 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0098 0.0118 0.0044 0.009

lb/mmBtuO2 2.16E-06 2.61E-06 9.41E-07 0.000

Monday, November 21, 2011 Page 17 of 35
Information Collection Request Emission Test Program Report

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0145 0.0234 0.0117 0.017

lb/mmBtuO2 3.20E-06 5.17E-06 2.50E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0038 0.001 0.0022 0.002

lb/mmBtuO2 8.39E-07 2.21E-07 4.71E-07 0.000

Location: Boiler 32 - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 0.7 0.3 1.3 0.767

lb/mmBtuO2 1.69E-04 7.06E-05 3.07E-04 0.000

Compound: Inorganic (Aqueous) Condensible P

Average

RunNumber 1 2 3

Mass_mg 0.8 13.7 34.2 16.233

lb/mmBtuO2 1.94E-04 3.22E-03 8.07E-03 0.004

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 18.2 2.4 1.6 7.400

lb/mmBtuO2 4.41E-03 5.65E-04 3.78E-04 0.002

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 19.7 16.4 37.1 24.400

lb/mmBtuO2 4.77E-03 3.86E-03 8.76E-03 0.006

Monday, November 21, 2011 Page 18 of 35
Information Collection Request Emission Test Program Report

Process Run Data

APCD Run Data

Process Lab Run Data

Monday, November 21, 2011 Page 19 of 35
Information Collection Request Emission Test Program Report

Sampling / Stack Data Results Detail

Location Boiler 32 - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 20 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 10 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 21 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 10 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 22 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 10 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 23 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 23

Average

Run Number 1 2 3

Test Date 2/17/2011 2/18/2011 2/19/2011

Run Start Time 4:42:00 AM 8:20:00 AM 8:25:00 AM

Run Finish Time 8:15:00 AM 4:39:00 PM 4:36:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.191 0.191 0.191 0.191

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.999 0.999 0.999 0.999

Barometric Pressure, inches of Mercury 29.88 29.95 30 29.943

Average Orifice Meter Differential, inches H2O 1.02 1.07 1.04 1.043

Dry Gas Meter Volume Sampled, cubic feet 258.619 266.150 264.710 263.160

Average Dry Gas Meter Temperature, °F 78.33 83.08 81.17 80.860

Dry Gas Meter Volume Sampled, dscf 253.699 259.440 259.359 257.499

Total Moisture Liquid collected, g 598.5 569.8 576.6 581.633

Volume of Water Vapor, standard cubic feet 28.17 26.82 27.14 27.377

Moisture Content of Stack Gas, % 9.99 9.37 9.47 9.610

Moisture Saturation at Stack Gas Temperature, % 49.98 48.85 51.94 50.257

Dry Mole Fraction 0.9001 0.9063 0.9053 0.904

Carbon Dioxide, % 14.7 14.7 15.1 14.833

Oxygen, % 5 5 4.5 4.833

Carbon Monoxide & Nitrogen, % 80.3 80.3 80.4 80.333

Fuel Factor 1.08 1.08 1.09

Dry Molecular Weight, lb/lb-Mole 30.55 30.55 30.60 30.567

Wet Molecular weight, lb/lb-Mole 29.30 29.37 29.41 29.360

Flue Gas Static Pressure, inches of H2O -1 -1 -1 -1.000

Absolute Flue Gas Pressure, inches of Mercury 29.81 29.88 29.93 29.873

Average Stack Gas Temperature, °F 178.92 178.00 180.83 179.250

Average Velocity Head, inches of H2O 0.8698851956

87598

0.906253941

756931

0.8800649097

9658

0.885

Average Stack Gas Velocity, feet/second 57.28 58.29 57.48 57.683

Stack Cross-Sectional Area, square feet 254.469 254.469 254.469 254.469

Dry Volumetric Flow Rate, dry scfm 648,138.4 666,629.3 654,834.6 656,534.100

Actual Wet Volumetric Flue Gas Flow Rate, acfm 874,559.1 889,979.9 877,612.7 880,717.233

Percent Isokinetic of Sampling Rate, % 104.3 103.7 105.5 104.500

Percent Excess Air, % 30.9 26.9

F-Factor, dscfm/MMBtu @ %O2 9968 9854 10036 9,952.667

Round Duct Diameter, inches 216 216 216

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Monday, November 21, 2011 Page 24 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 25 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, November 21, 2011 Page 26 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 27 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 28 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 29 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A CO2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 30 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 31 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 32 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 33 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - Method 3A O2 3 6 9

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, November 21, 2011 Page 34 of 35
Information Collection Request Emission Test Program Report

Location Boiler 32 - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, November 21, 2011 Page 35 of 35