Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 1 of 15 Pages



### GENERAL

AIR CONTAMINANT DISC HARGE PERMIT

Department of Environmental Quality Air Quality Division

811 SW Sixth Avenue Portland, OR 97204

- 1390 Telephone: (503) 229

- 5359

This permit is issued on March 1, 2010 in accordance with the provisions of ORS 468A.040

and OAR 340

- 216

- 0060 for the following source category:

Gasoline dispensing facilities subject to the e mission s tandards for gasoline dispensing facilities

in OAR 340

- 244

- 0232 through 0252. NAICS 447110

, 447190.



### TABLE OF CONTENTS

1.0 PERMIT ASSIGNMENT

................................ ................................ ................................ ....... 2

2.0 GENERAL EMISSION STA NDARDS AND LIMITS

................................ ......................... 3

3.0 PLANT SITE EMISSION LIMITS

................................ ................................ ........................ 3

4.0 OPERATION AND MAINTE NANCE REQUIREMENTS

................................ .................. 4

5.0 COMPLIANCE DEMONSTRA TION

................................ ................................ ................... 7

6.0 RECORDKEEPING REQUIR EMENTS

................................ ................................ ............... 9

7.0 REPORTING REQUIREMEN TS

................................ ................................ ........................ 10

8.0 ADMINISTRATIVE REQUI REMENTS

................................ ................................ ............ 12

9.0 FEES

................................ ................................ ................................ ................................ ..... 14

10.0 GENERAL CONDITIONS A ND DISCLAIMERS

................................ ............................. 14

11.0 ABREVIATIONS, ACRONY MS, AND DEFINITIONS

................................ .................... 15Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 2 of 15 Pages



### 1.0 PERMIT ASSIGNMENT

1.1 Qualifications All of the following conditions must be met in order to qualify for assignment to this General Air Contaminant Discharge Permit (ACDP):

a. The permittee is performing gasoline dispensing activit ies listed on the cover page of this permit, including supporting activities.

b. The permittee ha s an underground gasoline storage tank, monthly throughput of 10,000 gallons of gasoline per

month or more

, or sell s gasoline for use in motor vehicles.

c. A Simple or Standard ACDP is not required for the source.

d. The source is not having ongoing, reoccurring or serious compliance problems.

e. The source is not subject to stage II vapor collection system requirements.

f. The source is not an agricultural operation as defined in

ORS 468A.020.

1.2 Assignment DEQ will assign qualifying permittees to this permit that have and maintain a good record of compliance with DEQ ’s Air Qu ality regulations and that DEQ determines would be appropriately regulated by a General ACD P. DEQ may rescind assignment if the permittee no longer meets the requirements of OAR 340

- 216

- 0060 and the conditions of this permit.

1.3 Permitted

Activities This permit allows the permittee to discharge air contaminants

from processes and activities related to the air contaminant source(s) listed on the first page of this permit until this permit expires, is modified, revoked or rescinded. If there are other

e missions activities occurring at the site besides those listed on the cover page of this permit, the permittee may be required to obtain

a Standard or Simple ACDP or a General ACDP Attachment, if applicable.

1.4 Relation to local

land use laws This permit is not valid in Lane County, or at any location where

the operation of the permittee’s processes, activities, and insignificant activities would be in violation of any local land use or zoning laws. It is the permittee’s sole responsibility to obtain

local la nd use approvals as, or where, applicable before operating this facility at any location. For operations within Lane County, contact the Lane Regional Air Pollution Authority for obtaining any necessary permits at (541) 736

- 1056.Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 3 of 15 Pages



### 2.0 GENERAL EMISSION STANDARDS AND LIMITS

2.1 Visible Emissions The permittee must comply with the following visible emission limits, as applicable:

a. In Clackamas, Columbia, Multnomah, or Washington Counties, emissions from any air contaminant source other than fuel burning equipment must not equal or exceed 20% opacity for a period aggregating more than 30 seconds in any one hour.

b. In all other areas of the state, emissions from any air contaminant source must not equal or exceed 20% opacity for a period aggregating more th an 3 minutes in any one

hour.

2.2 Fugitive Emissions The permittee must take reasonable precautions for preventing fugitive dust emissions from becoming a nuisance, such as but not

limited to:

a. Treating vehicular traffic areas of the plant site under the control of the permittee.

b. Operating all air contaminant

- generating processes so that fugitive type dust associated with the operation will be adequately controlled at all times.

c. Storing collected materials from air pollution control equipment in a cove red container or other method equally effective in preventing the material from becoming airborne during storage and transfer.

2.3 Particulate Matter

Fallout The permittee must not cause or permit the emission of any

particulate matter larger than 250 microns in size at sufficient duration or quantity as to create an observable deposition upon the real property of anoth er person when notified by DEQ that the deposition exists and must be controlled.

2.4 Nuisance and

Odors The permittee must not cause or allow air contaminants from any

source to cause a nuisance. Nuisance conditions will be verified by DEQ personnel.



### 3.0 PLANT SITE EMISSION LIMITS

3.1 Plant Site

Emission Limits (PSEL) Plant site emissions must not exceed 39 tons of VOC per year.

3.2 Annual Period The annual plant site emissions limits apply to any 12

- consecutive calendar month period.Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 4 of 15 Pages



### 4.0 OPERATION AND MAINTE NANCE REQUIREMENTS

4.1 Compliance Dates a. New or Reconstructed Facility : For any facility where construction or reconstruction began after November 9, 2006, the permittee must be in compliance with the requirements in Conditions 4.2 t hrough 4.10 , as applicable, upon assignment to this permit or upon startup, whichever

is later.

b. Existing Facility : For any facility where construction or reconstruction began on or before November 9, 2006, the permittee must be in compliance with the requirements in

Conditions 4.2 through 4.10 , as applicable, no later than January 10, 2011, except as follows

.

c. For any of the following tanks, the permittee must be in compliance with the stage I vapor balance requirements in

Condition 4.5 upon assignment to this permit.

i. Any tank at a facility located in Clackamas, Multnomah, or Washington County whose annual throughput exceeds 120,000 gallons ; or

ii. A ny tank with a rated capacity between 1,500 and 40,000 gallons and located in the Portland AQMA, Medford AQMA, or Salem S K ATS

. 4.2 Work Pr actices The permittee must not allow gasoline to be handled in a manner that would result in vapor releases to the atmosphere for extended periods of time. Measures to be taken include, but are not limited to, the following:

a. Minimize gasoline spills;

b. Do not top off or overfill vehicle tanks

. If a person can confirm that a vehicle tank is not full after the nozzle

click s off (such as by checking the vehicle’s fuel tank gauge) , the person may continue to dispense fuel using best judgment and caution to prevent a spill ;

c. Post a sign at the GDF instructing a person filling up a motor vehicle to not top off the vehicle tank;

d. Clean up spills as expeditiously as practicable;

e. Cover all open gasoline containers and all gasoline storage

tank fill

- pipes with a gasketed seal when not in use;

f. Minimize gasoline sent to open waste collection systems that collect and transport gasoline to reclamation and recycling devices, such as oil/water separators.Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 5 of 15 Pages

4.3 Submerged Fill The permittee must not transfer or allow the transfer of gasoline into any storage tank with a capacity of 250 gallons or more unless the tank is equipped with a submerged fill pipe:

a. Submerged fill pipes installed af ter November 9, 2006 or on tanks located in the Portland or Medford AQMA or the

Salem S K ATS must be no more than 6 inches from the bottom of the storage tank

. b. Submerged fill pipes installed on or before November 9,

2006 must be no more than 12 inches from the bottom of the storage tank

. 4.4 Applicability of Stage I Vapor Balance System Requirements The permittee must comply with Condition 4.5 for the following

tanks , unless that tank is equipped with a floating roof or equivalent.

a. Each gasoline storage tank with a capacity of 250 gallons or more at a facility with a monthly throughput of 100,000 gallons or more of gasoline;

b. Each gasoline storage tank with a capacity of 250 gallons or more at a facility with an annual throughput of 480,000 gallons or more of gasoline;

c. Each gasoline storage tank with a capacity 1,500 gallons or more at a facility located in the Portland AQMA, Medford AQMA, or Salem S K ATS; or

d. Each gasoline storage tank with a capacity of 250 gallons or more at a facility with an annu al throughput of 120,000 gallons or more of gasoline and located in Clackamas, Multnomah or Washington County

. 4.5 Stage I Vapor Balance System Requirements The permittee must install and operate a stage I vapor balance

system that meet s all of the following management practices:

a. All vapor connections and lines on the storage tank must be equipped with closures that seal upon disconnect.

b. The vapor line from the gasoline storage tank to the cargo tank must be vapor

- tight.

c. The vapor balance system must be designed such that the pressure in the tank truck does not exceed 18 inches water pressure or 5.9 inches water vacuum during product

transfer.

d. The vapor recovery and product adapters, and the method of connection with the delivery elbow, must be designed so as to prevent the over

- tightening or loosening of fittings during normal delivery operations.Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 6 of 15 Pages

e. If a gauge well separate from the fill tube is used, it must be provided with a submerged drop tube that extends the same distance from the bottom of the storage tank as specific in Condition 4.3

. f. Liquid fill connection for all systems must be equipped with vapor

- tight caps.

g. The pressure specifications for pressure

- vacuum vent
valves must be a positive pressure setting of 2.5 to 6.0 inches of water and a negativ e pressure setting of 6.0 to

10.0 inches of water. The total leak rate of all pressure

vacuum vent valves at an affected facility, including connections, must not exceed 0.17 cubic foot per hour at a pressure of 2.0 inches of water and 0.63 cubic foot per

hour at a vacuum of 4 inches of water.

h. The vapor balance system must be capable of meeting the static pressure performance requirement of the following equation:

Pf = 2e - 500.887/v

Where: Pf = Minimum allowable final pressure, inches of water. v = Total ullage affected by the test, gallons. e = Dimensionless constant equal to approximately 2.718. 2 = The initial pressure, inches water.

4.6 Dual

- Point Vapor Balance System Requirement The permittee must install and operate a dual

- point vapor balance

system on any new gasoline storage tank installed after November 9, 2006 at a facility with a monthly throughput of 100,000 gallons of gasoline or more.

4.7 Operation and

Maintenance of Vapor Balance System The permittee must com ply with the following requirements for

any gasoline storage tank equipped with a vapor balance system:

a. Ensure the connection and proper operation of the vapor balance system whenever gasoline is being transferred.

b. All equipment associated with the vapor balance system must be maintained to be vapor tight and in good working

order.

4.8 Management

Practices for Delivery Vessels The permittee must not transfer or allow the transfer of gasoline to

or from the facility by a delivery vessel unless the following

conditions are met:

a. All hoses in the vapor balance system are properly

connected ;

b. The adapters or couplers that attach to the vapor line on the storage tank have closures that seal upon disconnect ;Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 7 of 15 Pages

c. All vapor return hoses, couplers, and adapters used in the gasoline delivery are vapor

- tight ;

d. All tank truck vapor return equipment is compatible in size and forms a vapor

- tight connection with the vapor balance equipment on the facility’s storage tank ;

e. All hatches on the tank truck are closed and securely

fastened ;

f. The filling of storage tanks at the facility shall be limited to unloading by vapor

- tight gasoline cargo tanks ; and

g. Documentation that the cargo tank has met the specifications of EPA Me thod 27 shall be carried on the cargo tank.

4.9 Fugitive Emissions

Control Plan While operating in the Medford

- Ashland AQMA, the permittee

must prepare and implement site

- specific plans for the control of fugitive emissions in accordance with OAR 340

- 240

- 0180.

4.10 O&M plan While operating in the Medford

- Ashland AQMA or Lakeview UGA, the permittee must prepare and implement an operation and maintenance (O&M) plan in accordance with OAR 340

- 240

- 0190.



### 5.0 COMPLIANCE DEMONSTRA TION

5.1 Testing Requirements The permittee must comply with the following requirements at the

time of installation of a vapor balance system or a new gasoline storage tank if required to install a vapor balance system under

Condition 4.5 or 4.6

, and every 3 years thereafter if the facility has a monthly throughput of 100,000 gallons of gasoline or more.

a. D emonstrate compliance with the leak rate and cracking pressure requirements for pressure

- vacuum vent valves installed on gasoline storage tanks by conducting a test using California Air Resources Board Vapor Recovery

Test Procedure TP

– 201.1E,

— Leak Rate and Cracking Pressure of Pressure/Vacuum Vent Valves, or other

a pproved method , and

b. D emonstrate compliance with the static pressure performance requirement, for your vapor balance system by conducting a static pressure test on gasoline storage tanks using the California Air Resources Board Vapor Recovery Test Procedure TP

– 201.3,

— Determination of 2

- Inch WC Static Pressure Performance of Vapor Recovery Systems of D ispensing Facilities, or other approved

method

.Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 8 of 15 Pages

5.2 Operation and

Maintenance Requirements The per mittee must operate and maintain the facility and

associated air contaminant control devices as follows:

a. In order to ensure that the vapor balance equipment is maintained to be vapor tight and in good working order, have the vapor balance equipment inspected on an annual basis to discover potential or actual equipment failures.

b. Replace, repair or modify any worn or ineffective component or design element within 24 hours to ensure the

vapor

- tight integrity and efficiency of the vapor balance

system. If repair parts must be ordered, either a written or a verbal order for those parts must be initiated within 2 working days of detecting such a leak. Such repair parts must be installed within 5 working days after receipt.

5.3 PSEL Monitoring Compliance with the PSEL is determined for each 12

- consecutive calendar month period based on the gasoline or other material throughput for the reporting period.

a. Facilities will be presumed to be in compliance with the yearly VOC PSEL provided total product throughput does

not exceed 1 3

, 9 00,000 gallons during any 12

- consecutive calendar month period.

b. Facilities that operate and maintain stage II vapor

collection systems will be presumed to be in compliance with the yearly VOC PSEL provided total product throughput does not exceed 2 5

, 1 00,000 gallons during any

12

- consecutive calendar month period.

c. If the permittee exceeds the operational throughput

thresholds sta ted above, as applicable, the permittee must demonstrate compliance with the yearly PSEL on a monthly basis as follows :

E 12

- month = ( T B + T L + L R + L S )/2000

Where:

E 12

- month = Total VOC emissions (in tons) for the 12

- month period

T B = emissions from storage tank breathing and emptying

T L = emissions from storage tank filling

L R = emissions from vehicle refueling

L S = emissions from spillagePermit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 9 of 15 Pages

T B + T L = EF x TP

Where:

EF = emission factor (in lbs/Mgals), use 1. 3 if facility operates and maintains a st age I vapor balance system, otherwise use 6.2

TP = throughput (in 1000 gallons) for the previous

12

- months

L R + L S = EF x TP

Where:

EF = emission factor (in lbs/Mgals ), use 1.8 if facility operates and maintains a stage II vapor collection system, otherwise use 4.3

TP = throughput (in 1000 gallons) for the previous

12

- months



### 6.0 RECORDKEEPING REQUIR EMENTS

6.1 Operation and

Maintenance The permittee must maintain the following records related to the

operation and maintenance of the facility and any vapor balance equipment:

a. Records of all test performed under Condition 5.1

.
b. Records related to the operation and maintenance of vapor balance equipment required under Conditions 4.5 and 4.6

. Any s tage I vapor balance component defect must be logged and tracked by station personnel using forms provided by DEQ or a reasonable facsimile

.

c. Records of total throughput volume of gasoline, in gallons,

for each calendar month.

d. If the permittee exceeds the operational throughput

thresholds stated in Condition 5. 3 a or 5. 3 b, as applicable, records of VOC emissions, in tons, for each calendar

month.

e. Records of permanent changes made at the facility and vapor balance equipment which may affect emissions.Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 10 of 15 Pages

6.2 Complaint Log The permittee must maintain a log of all written complaints and complaints received via telephone that specifically refer to air pollution concerns associated to the permitted facility. The log must include a record of the permittee’s actions to investigate the validity of each complaint and a record of actions taken for complaint resolution.

6.3 Retention of

Records Unless otherwise specified, all records must be maintained on site

for a period of five ( 5 ) years an d made available to DEQ upon request.



### 7.0 REPORTING REQUIREMEN TS

7.1 Initial Notification The permittee must submit an i nitial n otification upon assignment

to this permit. The initial n otification must contain the following

information. The permittee must submit the i nitial n otification to the EPA Region X Office and to DEQ.

a. The name and address of the owner and the operator.

b. The physical address of the facility

.

c. A statement that the notification is being submitted in response to the Gasoline Dispensing Facility NESHAP

.

d. A n identif

ication of the requirements that apply to the facility

.
7.2 Notification of

Performance Test The permittee must submit a Notification of Performance Test in

writing at least 60 calendar days before a performance test, required by Condition 5.1 , is scheduled to begin.

7.3 Notification of Compliance Status The permittee must submit a notification of compliance status to

EPA’s Region 10 Office and DEQ by the compliance date specified in Condition 4.1 . The n otification of c ompliance s tatus must be signed by a responsible official who must certify its accuracy and must indicate whether the facility has complied with the requirements of this permit

.
7.4 Compliance Test Reports If the permittee is subject to the testing requirements in C ondition

5.1 , a test report demonstrating that the v apor recovery systems at
the facility passed the test(s) must be submitted to DEQ within 30 days of the test date.

7.5 Annual Report Th e permittee must submit to DEQ by February 15 of each year this permit is in effect two (2) copies of the following information for the previous calendar year:Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 11 of 15 Pages

a. The total throughput volume of gasoline, in gallons per year, of the facility for the preceding calendar year

.
b. If the permittee exceeds the operational throughput

thresholds stated in Condition 5. 3 a or 5. 3 b, as applicable, VOC emissions, in tons per year, for the preceding calendar year.

c. Summary of complaints relating to air quality received by permittee during the year.

d. List of change s made at the facility and on vapor balance equipment which may affect emissions

.

e. List major maintenance performed on vapor balance equipment

.
7.6 Relocation Notice The permittee must not install or operate the facility or any portion of the facility at any new site without first providing written notice to the Permit Coordinator in the appropriate regional office. The written notice must include the date of the proposed move, approximate dates of operation, a detailed map showing access to the new site, and a description of the air pollution controls and procedures to be installed, operated, and practiced at the new site. The permittee must not operate individual components of the facility at more than one site at a time without obtaining additional permits.

7.7 Notice of Change of Ownership or Company Name The permittee must notify DEQ in writing using a DEQ ―Permit

Application Form‖ within 60 days after the following:

a. Legal change of the name of the company as registered with the Corporations Division of the State of Oregon; or

b. Sale or exchange of the activity or facility.

7.8 Construction or

Modification

Notices The permittee must notify DEQ in writing using a DEQ ―Notice

of Construction Form‖ or ―Permit Application Form‖ and obtain approval in accordance with OAR 340

- 210

- 0205 through 340

- 210

- 0250 before:

a. Constructing or installing any new source of air contaminant emissions, including air pollution control equipment;

b. Modifying or altering an existing source that may significantly affect the emission of air contaminants;

c. Making any physical change which increases emissions; or

d. Changing the method of operation, the process, or the fuel use, or increasing the normal hours of operation that result

in increased emissions.Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 12 of 15 Pages

7.9 Where to Send Reports and

Notices The reports, with the permit number and source identification

number prominently displayed, must be sent to the Permit Coordinator for the region where the source is located as

identified in C ondition 8.2

. The mailing address for the EPA Regional Office is as follows:
Air Operating Permits

E PA Region X Mail Stop O AQ

- 108

1200 Sixth Ave

Seattle WA 98101

- 3188



### 8.0 ADMINISTRATIVE REQUI REMENTS

8.1 Reass ignment to

the General ACDP A complete application for reassignment to this permit is due

within 60 days afte r the permit is reissued. DEQ will notify the permittee when the permit is reissued. The application must be sent to the appropriate regional offic e.

a. If DEQ is delinquent in renewing the permit, the existing permit will remain in effect and the permittee must comply with the conditions of the permit until such time that the permit is reissued and the source is reassigned to the permit.

b. The permittee may submit an application for either a Simple or Standard ACDP at any time, but the permittee must continue to comply w ith the General ACDP until DEQ takes final action on the Simple or Standard ACDP application.

c. If a complete application for r eassignment to the General ACDP or Simple or S tandard ACDP is filed with DEQ in a timely manner, the permit will not be deemed to expire until final action has been taken on the application.

8.2 Permit

Coordinator

Addresses All reports, notices, and applicati ons should be directed to the air

quality permit coordinator for the are a where the source is located. The permit coordinator addresses are as follows:

Counties Permit Coordinator Address and Telephone Clackamas, Clatsop, Columbia, Multnomah, Tillamook, and Washington Department of Environmental Quality Northwest Region 2020 SW 4th Avenue, Suite 400 Portland, OR 97201

- 4987 Telephone: (503) 229

- 5582Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 13 of 15 Pages

Benton, Coos, Curry, Douglas, Jackson, Josephine, Lincoln, Linn, Marion, Polk, and

Yamhill Department of Environmental Quality Western Region 750 Front Street NE, Suite 120 Salem, OR 97301

- 1039 Telephone: (503) 378

- 5305
Baker, Crook, Deschutes, Gilliam, Grant, Harney, Hood River, Jefferson, Klamath, Lake, Malheur, Morrow, Sherman, Umatilla, Union, Wallowa, Wasco, Wheeler Department of Environmental Quality Eastern Region 475 NE Bellevue, Suite 110 Bend, OR 9770 1 Telephone: (541) 388

- 6146 ext. 223

8.3 DEQ Contacts Information about air q uality permits and DEQ ’s regulations may be obtained from the DEQ web page at http://www.oregon.gov/DEQ/ . All inquiries about this permit should be directed to the regional office for the area where t he

source is located. DEQ ’s regional offices are as follows:

Counties Office Address and Telephone Clackamas, Clatsop, Columbia, Multnomah, Tillamook, and Washington Department of Environmental Quality

Portland Office 2020 SW 4th Avenue, Suite 400 Portland, OR 97201 Telephone: (503) 229

- 5 263
Benton, Lincoln, Linn, Marion, Polk, and

Yamhill Department of Environmental Quality

Salem Office 750 Front Street NE, Suite 120 Salem, OR 97301

- 1039 Telephone: (503) 378

- 8240 Coos, Curry, and Western Douglas Department of Environmental Quality Coos Bay Office

340 N Front Street Coos Bay, OR 97420 Telephone: (541) 269

- 2721

Eastern Douglas, Jackson, and Josephine Department of Environmental Quality

Medford Office 221 Stewart Avenue, Suite 201 Medford, OR 97501 Telephone: (541) 776

- 6010
Baker, Crook, Deschutes, Gilliam, Grant, Harney, Hood River, Jefferson, Klamath, Lake, Malheur, Morrow, Sherman, Umatilla, Union, Wallowa, Wasco, and Wheeler Department of Environmental Quality

Bend Office 475 NE Bellevue, Suite 110 Bend, OR 9770 1 Telephone: (541) 388

- 6146Permit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 14 of 15 Pages



### 9.0 FEES

9.1 Annual Compliance Fee The Annual Fee specified in OAR 340

- 216

- 00 20 , Table 2, Part 2

for a Fee Class Five G eneral ACDP is due on December 1 of each year this permit is in effect. An invoice indicatin g the amount, as determined by DEQ regulations, will be mailed prior to the above

date.

9.2 Change of Ownership or Company Name

Fee The non

- technical permit modification fee specified in OAR 340

-

216

- 00 20 , Table 2, Part 3 is due with an application for changing the ownership or the name of the company of a source assigned to this permit.

9.3 Where to Submit

Fees Fees must be submitted to:
Department of Environmental Quality

Business Office

811 SW Sixth Avenue Portland, Oregon 97204

- 1390



### 10.0 GENERAL CONDITIONS A ND DISCLAIMERS

10.1 Other Regulations In addition to the specific requirements listed in this permit, the permittee must comply with all other legal r equirements enforceable by DEQ

.
10.2 Conflicting

Conditions In any instance in which there is an apparent conflict relative to

conditions in this permit, the most stringent conditions apply.

10.3 Masking of

E missions The permittee must not cause or permit the installation of any

device or use any means designed to mask the emissions of an air contaminant that causes or is likely to cause detriment to health, safety, or welfare of any person or otherwise violat e any other regulation or requirement.

10.4 DEQ Access The permittee must allow DEQ ’s representatives access to the plant site and pertinent records at all reasonable times for the purposes of performing inspections, surveys, collecting samples, obtaining data , reviewing and copying air contaminant emissions discharge records and conducting all necessary functions related to this permit in accordance with ORS 468

- 095.

10.5 Permit Availability The permittee must have a copy of the permit available at the

facility at all times.

10.6 Open Burning The permittee may not conduct any open burning except as allowed by OAR 340 Division 264.

10.7 Asbestos The permittee must comply with the asbestos abatementPermit Number: AQGP

- 022 Expiration Date: 03/01/2020 Page 15 of 15 Pages

requirements in OAR 340, Division 248 when conducting any demolition, renovation, repair, construction, and maintenance activities at the facility.

10.8 Property Rights The issuance of this permit does not convey any property rights in either real or personal property, or any exclusive privileges, nor does it authorize any injury to private property or any invasion of personal rights, nor any infringement of federal, state, or local laws or regulations.

10.9 Termination, Revocation, or

Modification The Commission m ay modify or revoke this permit pursuant to

OAR 340

- 216

- 0060(3) and (4).



### 11.0 ABREVIATIONS, ACRONY MS, AND DEFINITIONS

ACDP Air Contaminant Discharge

Permit

AQMA Air Quality Maintenance Area

calendar

year The 12

- month period

beginning January 1st and ending December 31st

CFR Code of Federal Regulations

date mm/dd/yy

DEQ Oregon Department of

Environmental Quality

EPA US Environmental Protection

Agency

gal gallon(s)

GDF gasoline dispensing facility

HAP Hazardous Air Pollutant as

defined by OAR 340

- 244

- 0040

ID identification number

lb pound(s)

NAICS North American Industry

Classification System

NESHAP National Emissions Standards

for Hazardous Air Pollutants

OAR Oregon Administrative Rules

ORS Oregon Revised Statutes

PSEL Plant Site Emission Limit

scf standard cubic foot

VOC volatile organic compound

year A period consisting of any 12

-

consecutive calendar months

j ce: 2/ 16 / 10 AQGP

- 022 gasoline dispensing stage I.docx gasoline dispensing facilities, stage I