# ,

STATE OF IDAHO DEPARTMENT OF ENVIRONMENTAL QUALITY

1410 North Hilion • Boise, Idaho 83706· (208)**373~J02** C.l. 'ButCh" 01\8•• GoIIe!'Il« Toni Hardesty, IlIn!dor 

### September 7. 2010 Kent Quinney Plant Manager The Amalgamated Sugar Company. LLC

--Nampa Factory 138 West Karcher Avenue Nampa, Idaho 83651 RE: Facility ID No. 027-00010, The Amalgamated SuprCompany, LLC

-- Nampa Factory. Final Tier II Operating PermitLetter Dear Mr. Quinney: The Department ofEnvironmental Quality (DEQ) is issuingTierII Operating Permit No, T2-2009.0105 to The Amalgamated SugarCompany, LLC (T 

### ASCO)

-- Nampa Factory, required to ensure compliance with determined bestavailable retrofit technologies (BART) for the Riley boiler. in accordance with IDAPA 58.01.01.400 through 406, Rules for the

### Control ofAir Pollution in Idaho (Rules). The enclosed TierII operating permit is

### based on the 

### information contained in the BART analyses and on the relevant comments received during the public commentperiod. This permit does not release TASCO from compliance with all other applicable federal. state. 

### orlocal laws, regulations, pennits, orordinances. Please note that this permitexpires five years afterthe 

### issuance date. 

### This Tier II operating permit does not contravene any existing TierIoperating permit conditions. Therefore the process or equipment may be

### operated in accordance with the TierII operating permit before the TierIoperating pennit is revised. Pursuant to IDAPA 58.01.23, you, as well as any otherentity. may have the right to appeal this final agency action within 35 days ofthe date ofthis decision. However, prior to filing a petition for a contested case, Iencourage you to contact MorrieLewis at

### (208) 373-0502 or Morrie.Lewis@deq.idaho.gov to address any questions orconcernsyou may have with the enclosed permit.

Mike Simon Stationary Source Manager Air Quality Division MSIML Permit No. T2·2009.010S Enclosure

# , 

# e PERMITNo.: 1'2-2009.0105 Air Quality FACILITY ID No.: 027-00010 TIERD OPERATING PERMIT AQCR: 64 CLASS: A ZONE: J 1 StateofIdabo SIC: 2063 NAICS: 311313 DepartmentorEnvironmentalQuality UTM COORDINATE (km): 534.5,4828.0 1. PERMITTEE The Amalgamated SugarCompany LLC

- NampaFactory 2. PROJECT Tier II operatingpermit

- required by DEQtoensurecompliance with applicable BARTstandards 3. MAILING ADDRESS CITY STATE ZIP P.O. Box 8787 

### Namjl8 ID 83653-8787 4. FACILITY CONTACT TITLE TELEPHONE Glen Patrick Plant Environmental Manager (208) 468-6883 5. RESPONSIBLE OFFICIAL TITLE TELEPHONE Kent Quinney Plant Manager (208)466-3541 6. EXACTPLANT LOCATION COUNTY J38 W. KarcherAve., Nampa, Idaho Canyon 7. GENERAL NATURE OFBUSINESS & KINDSOFPRODUcrS Beet sugar manufacturing 8. PERMIT AUTHORITY 

### This permit is issued accordingto the Rules forthe Control of

### Air Pollution in Idaho, IDAPA 58.01.01.400 through 410, and pertains only to emissions ofaircontaminants regulated by the state ofIdaho and to the sources specifically allowed to be operated bythis permit.
Changes in design, equipmentoroperations may be considered a modification. Modifications are subject to DEQ review in accordance with IDAPA 58.01.01.200 through 228 ofthe Rules for the Control ofAir Pollution in Idaho.

# JJ~':'>tuJ MORRIE LEWIS, PnMrrWRITER DEPARTMENTOFENVIRONMENTALQVALIT\'

# 1t(Lg~-~~ . .,."r""'" Dateluued: September7,2010 MIKE SIMON, STATIONARY SOURCEPROGRAM MANAGER DateModiftedlRevised: DEPARTMENTOFENVIRONMENTAL QUALITY Date Expires: September7,1015

MSlML

### Table ofContents

ACRONYMS, UNITS, AND CHEMICAL NOMENCLATURE

..........................................................................3 1. TIER II OPERATING PERMIT SCOPE

...................................................................................................4 2. FACILITY-\VlDE CONDITIONS

............................................................................................................ 5 3. RILEY BOILER BART

.............................................................................................................................6 4. SOUTH PULP DRyER

........................................................................................................................... II 5. SUMMARY OF EMISSION RATE LIMITS

......................................................................................... 12 6. TIER 

### HPERMIT TO OPERATE GENERAL PROVISIONS

................................................................ 13

### Acronyms, Units, and Chemical Nomenclature AQCR BART CAA CAM CFR 

### CO 

### DEQ EPA POD fpm gpm lDAPA iwg Ib/hr Ib steam/hr LNB MMBtulhr MMscf/hr 

### NAAQS NAICS N02 NOx 

### NSPS O&M 

### OFA PM PM 10 PSD SIC SIP S02 

### SO" TAP 

### TASCO Tlhr U.S.C. UTM 

### VOC Air Quality Control Region BestAvailable Retrofit Technologies Clean Ail' Act Compliance Assurance Monitoring Code ofFederal Regulations carbon monoxide DepartmentofEnvironmental Quality U.S. Environmental Protection Agency flue gas desulfurization feet per minute gallons perminute anumbering designation for all administrative rules in Idaho promulgated in accordance with the Idaho Administrative Procedures Act inches ofwster gauge pounds per hour pounds ofsteam output per hour low NOx burner system million British thermal units per hour million standard cubic feet per hour National Ambient Air Quality Standards North American Industry Classification System nitrogen dioxide nitrogen oxides New Source Performance Standards operations and maintenance over-fired air particulate matter 

### particulate matter with an aerodynamic diameter less than or 

### equal to anominal 10 micrometers prevention ofsignificant deterioration ofair quality Standard Industrial Classification State Implementation Plan sulfur dioxide sulfur oxides toxic air pollutants The Amalgamated SugarCompany, LLC tons per hour United States Code Universal Transverse Mercator volatile organic compounds

1'2-2009.0105

### 1. TIER II OPERATING PERMIT SCOPE Purpose 1.1 The purpose ofthis Tier II operating permitis to establish Best Available RetrofitTechnology (BART) emission standards and requirements for the Riley Boiler in accordance with 40 CFR 51.308(e) and IDAPA 58.01.01.401.03. 

### RegulatedSources 1.2 The following Regulated Emission Point Sources Table lists all sources ofregulated emissions in this permit: REGULATED EMISSION POINT SOURCES TABLE Permit Section SourceDescription Emissions Controls

2&3**Rile~** Boiler (S-B3) Unitnumber: S-B3 Installation Date: 1969 Rated stenm cllpacity: 250,000 Ib slewn/hr Maximum capacity: 350 MMBtulhr Maximum operation: 8,760 hr/yr Fuel types: coal, natural gas Bughouse (A-B3) Manufactunll': Envirotcch Corp. Control efficiency:**~99.0%** for PM BART for PM Spray dry flue gas desultUrization system Reagent: Lime or limestone Control efficiency: 80·90% for S02 BARTforS02

L,O)!NOx burner**~stem** with over-til'ed air Control efficiency: :2:50%forNOx BARTforNOx 2&4**Pul~** d!)!crs (S-D!, 8-m,lind I:2-D3) Pe!llll'lnent**~llI!tdown**

T2-2009.0 1 05 Page 4

### 2. FACILITY-WIDE CONDITIONS 

### Obligation to Comply 2.1 Receiving aTier 

### n operating permit shall not relieve any owner or operator ofthe responsibility to comply with all applicable local, state, and federal rules and regulations, in accordance with IDAPA 58.01.01.406. 

### Incorporation ofFederal Requirements byReference 2.2 Unless expressly provided otherwise, any reference in this penn

### it to any document identified in IDAPA 58.01.01.107.03 shall constitute the full incorporation into this permit ofthatdocument for the purposes ofthe reference, including any notes and appendices therein, in accordance with IDAPA 58.0l.01.1 07. Documents include, but are not limited to:

• Protection ofVisibility, 40 CFR Part SI. Subpal1 P, Section 308

- BestAvailable Retrofit Technology (BART)requirements
• Compliance Assurance Monitoring (CAM), 40CFR Part 64 For permit conditions referencing or cited in accordance with any document incorporated by reference (including permit conditions identified as BART and CAM), shou1d there be any conflictbetween the requirements ofthe pel1nit condition and the requirements ofthe document. the requirements ofthe document shall govern, including any amendments. 

### DEQAddress 2.3 Any reporting required by this permit, including, butnot limited to, records, monitoring data, supporting information, requests for confidential treatment, notifications ofintentto test, testing reports, or compliance certifications, shall contain 

### acertification by a responsible official. The certification shall state that. based on information and beliefformed after reasonable inquiry, the statements and information in the document(s) are true, accurate, and complete. Any reporting required by this permit shall be submitted to the fonowing address: Air Quality Permit Compliance DepartmentofEnvironmental Quality Boise Regional Office 1445 N. Orchard Boise, ID 83706 Phone: (208)373-0550 Fax: (208) 373-0287

1'2·2009.0105 Page S

### 3. RILEY BOILER BART 3.1 Process Description 

### The Riley Boiler is fired by pulverized coal and/or natural gas, and is used to supply steam and generate electricity for processing ofsugar beets into sugar and byproducts, including animal feed at the Nampa facility. 3.2 Emission Control Description 

### The existing baghouse (Unit

### No. A-B3) manufactured by Envirotech Corp. is used for the control of particulate matter (PM) emissions from the Riley Boiler. A spray dry flue gas desulfurizatioll (FGD) 

### system has been required forthe control ofsulfur dioxide (S02) emissions from the Riley Boiler. In a spray dry FGD system, the flue gas is introduced into atower and contacts an atomized spray oflime slurry, which absorbs and neutralizes the S02. A low NOx 

### burner system (LNB) with over-fired air has been required for the control ofnitrogen oxides (NOx) 

### emissions from the Riley Boiler. Low NOx 

### combustion with over-fired air lltiHzes fuel and air mixing optimization and staged combustion techniques to minimize thermaJ NOx 

### formation. 

### Compliance Dates 3.3 BART 40 CFR51.308, SubpartP - BART Installation and Operation Due Date 

### The permittee shall install 

### and operate BART or a 

### DEQ·approved BART alternative on each source subject to 

### BART as expeditiously as practicable, but in no event later

### than five (5) 

### years after approval of the implementation plan, 

### in accordance with lDAPA 58.01.01.668.04 and 40 CFR 51.308(e)(1)(iv). The permittee may submit a

### request to obtain a 

### DEQ-approved BART alternative and to revise this permit in accordance with IDAPA 58.01.01.404.04. DEQ will process the request in accordance with IDAPA 58.01.01.404. The request must be submitted timely such that any revisions to this permit and the corresponding revision to the Regional Haze SIP are approved priorto the BART installation and operation due date (as defined in

### this permit condition). Pursuant to 

### Section 110(k)(2) 

### ofthe Clean Air Act, EPA has 12 

### months to act on 

### arequested SIP revision. 

### Emissions Limits 3.4 BART 40 CFR51.308, SubpartP - BART and BARTAlternativeEmission Limits 

### On and afterthe BART installation and operation due date (as

### defined in Permit Condition 3.3),

### the emissions from the Riley Boiler stack shall not exceed any corresponding emission rate limit listed in the following Riley Boiler BART and BART Alternative Emission Limits 

### Table, in accordance with IDAPA 58.01.01.401.03 and 40 CFR 51.308(e): RILEY BOILERBART AND BARTALTERNATIVE EMISSION LIMITS TABLE
Source Description PM SO, NO" Ib/hr(R,b) Ib/hr(··b) Ib/hr**(.~l** Riley Boiler (8-B3) 14 115 186 (a)

(b) (e) Pounds per hour, as detennined by atest method prescribed by (DAPA 58.01.01.157, EPAreference method, or DEQ approved alternative. BART emission rale limit ill accordance wilh 40 CFR 51.308(e). BART alternative emission rate limit in accordance with 40 CFR 51.308(e)(2).

Page

### 3.5 CO Emission Limits On and afterthe BART installation and operation due date (as defined in PermitCondition 3.3), the emissions from the Riley Boiler stack shall not exceed any cOITesponding emission rate limit listed in the following Riley Boiler CO Emission Limits Table, in accordance with IDAPA 58.01.01.401.03 and 40 CFR 51.308(e): RILEY BOILERCO EMISSION LIMITSTABLE CO Source Dcsc\'iption Ib/hr(a) 

## I T/yr(b) Riley Doiler (S·B3) 25.8 

### I 113 (0) Pounds perhour, as determined by atest method prescribed by lDAPA 58.01.01.157, EPA reference method, orDEQ approved alternative. (0) TOllS per any consecutive 12-calendar month period. 

### Operating Requirements 3.6 BART40 CFR51.308, SllbpartP - Bagbouse Control Equipment 

### On and after the BART installation and operation due date (as defined in Permit Condition 3.3), and at all times the Riley Boileris fired with coal, the permittee shall operate a Baghouse (A-B3) to control PM emissions from the Riley Boiler to 

### ensure compliance with the BART PM emission limit (Permit Condition 3.4), in accordance with IDAPA 58.01.01.401.03 and 40 CFR S1.308(e). The baghouse need not be operated during periods when the Riley Boileris being fired exclusively with natural gas. 3.7 BART 40 CFR51.308. SubpartP - Spray Dry Flue GasDesulfurization Control EQuipment 

### On and afterthe BART installation and operation due date (as defined in PermitCondition 3.3), the permittee shall operate at al1 times the Riley Boileris operated, a spray dry flue gas desulfurization (FGD) system to control S02 

### emissions from the Riley Boiler and to ensure compliance with the BART S02 

### emission limit (PermitCondition 3.4), in accordance with IDAPA 58.01.01.401.03 and 40 CFR 51.308(e). 3.8 BART40 CFR51.308, SubpartP - Low NO", Burner Control Equipment 

### On and afterthe BART installation and operation due date (as defined in Permit Condition 3.3), the permittee shail operate at all times the Riley Boiler is operated, a low NOxburner system (LNB) in the Riley Boilerto reduce NOxemissions and to ensure compliance with the BARTNOxemission limit (Permit Condition3.4), in accordance with IDAPA 58.01.01.401.03 and 40 CFR 51.308(e).
• The LNB shall have a maximum rated heat input capacity (highest heating value) ofless than or equal to 350 MMBtulhr, and shall combustonly natural gas and/or coal fuel.
• Ifoperation ofthe LNB with OFA in the Riley Boileris expected to result in an emissions increase, the permittee shall submitthe required preconstruction compliance demonstrations (Permit Condition 3.18). 3.9 BART 40 CFR51.308. SubpartP - Maintenance ofBART EQuipment 

### On and afterthe BART installation and operation due date (as defined in Permit Condition 3.3), the pel'lllittee shall maintain the control equipment required and establish procedures to ensure such equipment is properly operated and maintained, in accordance with IDAPA 58.01.01.668.05 and 40 CFR 51.308(e)(l)(v).

T2-2009.01OS Page 1

### Monitoring andRecordkeeping Requirements 3.10 Baghonse**Prcssun~** Differential Monitoring The permittee shall install, calibrate, and maintain measuring device(s) to continuously 1110nitorthe pressure drop across each ofthe baghouses, in inches watergauge. The pressure drop shall be recorded once perday whilethe boilers are in operation. 

### In the event

### a measuringdevice becomes inoperable, it shall be repaired or replaced as soon as practicable. The records shall be maintained in accm'dance with General Provision 7. 3.11 Spray Dry FGDAdiabatic Apprgach Temperature Monitoring The permittee shalt install, calibrate, and maintain measuring device(s) to continuously monitor the adiabatic approach temperature for the spray dry FGD spray tower in degrees Fahrenheit. The temperature differential shall be recorded once perday while the Riley Boiler is in operation. In the event a measuring device becomes inoperable, it shall be repaired orreplaced as soon as practicable. The records shall be maintained in accordance with General Provision 7. 3.12 Primaryand Over-FiredAil' Flow Monitol'ing The permittee shall install, calibrate, and maintain measuring devices to continuously monitor the primary and over-fired air flow rates into the Riley Boiler, in feet per minute. The flow rate shall be recorded once perday whi1e the Riley Boiler is in operation. In the event a measuring device becomes inoperable, it shall be repaired orreplaced as soon as practicable. The records shall be maintained in accordance with General Provision 7. 3.13 Operation and Maintenance Mannals Within 

### 60 days afterthe BART installation and operation due date (as defined in Permit Condition 3.3), the permittee shall develop and submit to DEQ an Operation and Maintenance (O&M) manual for review and comment at the address provided (Permit Condition 2.3). Any changes to the O&M manual shall be submitted to DEQ for review and commentwithin IS days ofthe change.
• The O&M manual shall describe for each ofthe control equipment described in the Regulated Emission PointSources Table (Permit Condition 1.2) procedures that will be followed to ensure compliance with BART emission limits (PermitCondition 3.4), CO emission limits (Permit Condition 3.5), the maintenance ofBART equipment requirement (Permit Condition 3.9), the control equipment maintenance and operation general provision (General Provision 2), and the manufacturer's specifications. The O&M manual shall be apermittee developed document based upon, but independentfrom, the manufacturer supplied operating manual(s).
• The permittee shall operate the control equipment in accordance with the O&M manual. The procedures specified in the O&M manual are incorporated 

### by reference into this permit and are enforceable permitconditions_ The O&M manual and copies ofany manufacturer's manual(s) and recommendations shall remain on site at all times and shall be made available to DEQ representatives upon request.
• At a minimum, the manufacturer's recommended values that shall be maintained for each ofthe following operating parameters shall be included inthe manual:
• Baghouse minimum and maximum pressure drop, in inches ofwater (iwg); • Spray dry FOD minimum slurry flow rate, in gallons per minute (gpm); • Spray dry FOD adiabatic approach temperature, in degrees Fahrenheit (OF) above the adiabatic saturation temperature;

12-2009.0105 Page 8

### • LNB minimum 

### and maximum flow rates for both primalY 

### and over-fired airflow, in feet 

### per minute (fpm); and • Requirements to monitor and 

### record the parameters listed above accordance with the frequency recommended by the manufacturer, and at 

### aminimum each day thatthe Riley Boiler is operated. 

### Performance Testing Requirements 3.14 

### InitialPel'formanccTests


### • No later than 90 

### days after the BART installation and operation due date (as defined in Permit Condition 3.3), 

### performance tests shall be conducted on the RiJey Boiler stackto demonstrate compliance with the following emission Jimits, in accordance with IDAPA 58.01.01.405 

### and IDAPA 58.01.01.157: 

### • The BARTPM emission limit in pounds perhour (Permit Condition 3.4); 

### • The BART S02 emission limit in pounds per hour (Permit Condition 3.4); 

### • The BARTNOx

### emission limit in pounds perhour (Permit Condition 3.4); 

### and • The CO emission limit in pounds perhour (Permit Condition 3.5). 

### • Each performance test shall be conducted underthe following conditions, unless otherwise approved by DEQ, 

### in accordance with IDAPA 58.01.01.405, 

### IDAPA 58.01.01.157, 

### and General Provision 6: 

### • Emissions shall be 

### measured while combusting coal fuel in the

### Riley Boiler. • Three separate test runs 

### shall be conducted for each performance test. • Parameters shall be monitored and recorded as specified in the performance testmonitoring and recordkeeping requirement (Permit Condition 3.16). 3.15 

### PeriodicPerformanceTesting 

### Performancetests to determine PM, S02, 

### NOx, 

### and CO emissions in pounds perhourfrom the Riley Boiler stack shall be 

### conducted no less frequently than annuaJIy following the date ofeach required initial performancetest, in accordance with IDAPA 58.01.0lAOS 

### and under the conditions required for the initial performance tests (Permit Condition 3.14), 

### unless anothertesting frequency has been approved by DEQ. 3.16 

### PerfOl'manceTest Monitoring andRetordkeeping 

### The permittee shall monitor and record the following during each performance test, unless otherwise approved by DEQ:


### • Steamproduction rate ofthe Riley

### Boiler, in 

### pounds perhour (lb steam/hr), once every 15 

### minutes;
• CoaJ feed rate to the Riley Boiler, in tons perhour(Tlhr), once every 15 minutes (the coal feed rate may be determined nsing alternate relevantoperational parameter(s) and acalculation method which has been approved by DEQ);


### • Natural gas firing rate, in million standard cubic feet perhour (MMscf/hr), once every 15 minutes;
• Highest heating value and analysis results, including ash content, ofthecoal fired;
• Pressure drop across the baghouse during each test, in inches water gauge (iwg), once every 15 

### minutes;
• Spray dry FGD 

### minimum slurry flow rate, in gallons per minute (gpm); • Spray dry FGD 

### adiabatic approach temperature, in degrees Fahrenheit (OF), 

### once every 15 

### minutes; and
T2-2009.0105 Page 9

### • LNB primary and over-fired air flow 

### rates, in feet per minute (fpm), once every 15 minutes.
3.17 

### PerformanceTest**Reportin~** 

### The permittee shall submit performance test reports to DEQ which include records ofthe monitoring required (PermitCondition 3.16) and in accordance with the performance testing general provision (Gcneral Provision 6), 

### Performance test repOlts shall be 

### submitted by the

### permitteeto the DEQ address provided (Permit Condition 2.3). 

### Compliance Submittals andNotifications 3.18 Preconstruction Compliance Demonstrations 

### No later than 180 

### days prior to the BART installation and operation due date (as defined in Penn

### it Condition 3.3),

### the permittee shall submit information and 

### modeling analyses demonstrating that instal1ation and operation ofBART will notcause or significantly contribute to a violation ofany ambient airquality standards, 

### in accordance with the procedures provided 

### in IDAPA 58.0] .01.200-228. This shall 

### includethe following, unless otherwise approved by DEQ:
• Demonstmtion ofPreconstruction Compliance with Toxic Standards
• Demonstmtion ofPreconstruction Compliance with National AmbientAir Quality Standards
3.19 CAM40 CFR 64 and IDAP A 58.01.01.668.06.c

- Documentation ofNeed forImproved Monitoring 

### No laterthan 90

### days after

### the BART 

### installation and operation due date (as 

### defined in Permit Condition 3.3) and unless otherwise approved by 

### DEQ, the pemlittee shall submit infonnation to address monitoring changes in accordance with IDAPA 58.01.01.668.06.c. and in a Compliance Assurance Monitoring (CAM) plan relevant to the installation and operation ofBART in accordance with the procedures 

### in 40 

### CFRPart 64. 

### 3.20 Submittal and Notification 

### Reguh'ements Required compliance submittals and notifications (Pelroit Conditions 3.18 and 3.19) shaU be submittedto the DEQ address provided (Pennit Condition 2.3).

f2..2009.0105 Page 10

### 4. SOUTH PULP DRYER 

### Operating Requirements 4.1 BART40 CFR51.308, SubpartP - Shutdown ofSouth Pulo Dryor The permittee shall permanently shut down the South pulp dryer (8-D1). 

### Notification andReporting Requirements 4.2 PulpDryer Shutdown Notificatioq Within 30 days after completing permanent shut down ofthe South pulp dryer (as required by Permit Condition 4.1), the permittee 

### shall provide written notification to DEQ ofthe decision to permanently shutdown the South pulp dryer. The notification shall include a description ofthe method used to ensure permanent shut down ofthe South pulp dryer.

1'2·2009.0105 Page It

### 5. SUMMARY OF EMISSION RATE LIMITS The following lable provides a summary ofall emission rate limits required by this permit; SUMMARY OF EMISSIONRATELIMITS
Source Description PM 

## I SO. NOx 

### CO Ib/hr(lI,<) 

## I Iblhr(>'<) Ib/b

.. (a,.) Iblllr(o) T/Yr(b) Riley Boiler (8·B3) with BART 14 

## I liS 186 25.8 113 (,' Pounds per hour, as determined by atest method prescribed by IDAPA 58.01.01.157, EPA reference method, or DEQ approved alternative. (0) Tons per nny consecutive 12-calendurmonth period. (c) BART emissions rate in accordance with 40 CPR 5UOS(c),

12·2009.0105 Page 12

### 6. TIER II PERMIT TO OPERATE GENERAL PROVISIONS 

### General Compliance 1. The permittee has a continuing duty to comply with all terms and conditions ofthis permit. All emissions authorized herein shall be consistent with the terms and conditions ofthis permit and the Rules for the Control ofAir Pollution in Idaho. The emissions ofany pollutant in excess ofthe limitations specified herein, or noncompliance with any other condition or limitation contained in this permit, shall constitute a violation ofthis petruit and the Rules for the Control ofAir Pollution in Idaho, and the Environmental Protection and Health Act, Idaho Code §39w lOl, ct seq. IIdaho Code §39-10l, et seq.

### I 2. The permittee shall at all times (except as provided in the Rules for the Control ofAir Pollution in Idaho) maintain in good working order and operate as efficiently as practicable, all treatment or control facilities or systems installed or used to achieve compliance with the terms and conditions ofthis permit and other applicable Idaho laws for the control of

### airpollution. [JDAPA 58.01.01.405, 5111941 3. Nothing 

### in this permit is intended to relieve or exempt the permittee fi'om the responsibility to comply with all applicable local, state, orfederal statutes, rules and regulations. [JDAPA 58.01.01.406, 5/1194) 

### Inspection andEntry 4. Upon presentation ofcredentials, the permittee shall allow DEQ or an authorized representative ofDEQ to do the following:
a. Enterupon thepermittee's premises where an emissions source is located or emissions related activity is conducted, or where records arekept under conditions ofthis permit; b. Have access to and copy, at reasonable times, any records that are kept under the conditions ofthis permit; c, Inspectat reasonable times any facilities. equipment (including monitoring and air pollution control equipment), practices, oroperations regulated orrequired underthis permit; and d. As authorized by the Idaho Environmental Protection and Health Act, sample ormonitor, at reasonable times, substances or parameters for the purpose ofdetermining orensuring compliance with this pennit or applicable requirements. [Idaho Code §39-108) 

### Construction and Operation Notification S. The permittee shall furnish DEQ written notifications as follows:
a. Anotification ofthe date ofinitiation ofconstruction, within five working days afteroccurrence; b. A notification ofthe date ofany suspensionofconstruction, ifsuch suspension lasts for one year 01' more; c. A notification ofthe anticipated date ofinitial start-up ofthe stationary source orfacility not more than sixty days or less than thirty days priorto such date; d. Anotification ofthe actual date ofinitial start-up ofthe stationary source or facility within fifteen days after such date; and

1'2-2009.0105 Page 13

## •

e. A notification ofthe initial date ofachieving the maximum production rate, within five working days after occurrence - production rate and date. IIDAPA 58.01.01.405, 5/1194) Performance Testing 6. Ifperformance testing (air emissions source test) is required by this permit, the permittee shall provide notice ofintentto testto DEQ at least 15 days prior to the scheduled test date orshorter time period as approved by DEQ. DEQ may, at its option. have an observer present at any emissions tests conducted on a source. DEQ requests that such testing not be performed on weekends or state holidays. All performance testing shall be conducted in accordance with the procedures in lDAPA 58.01.01.157. Without prior DEQ approval. any alternative testing is conducted solely at the permittee's risk. Ifthe permittee fails to obtain prior written approval by DEQ for any testing deviations, DEQ may determine that the testing does not satisfy the testingrequirements. Therefore, at least 30 days prior to conducting any performance test, the permittee is encouraged to submit a performance test protocol to DEQ for approval. The written protocol shall include a description ofthe test methodes) to be used, an explanation ofany or unusual circumstances regarding the proposed test, and the proposed test schedule for conducting and reporting the test. Within 30 days following the date in which apertormance test required by this permit is concluded, the permittee shall submitto DEQ aperformance test report. The written report shall include a description of the process, identification ofthe test methodes) used, equipment used, all process operating data coJlected during the test period, and testresults, as well as raw test dataand associated documentation, including any approved test protocol. (IDAPA 58.01.01.157, 4/5/001 Monitoring and Recordkeeping 7. The permittee shall maintain sufficient records to ensure compliance with all ofthe terms and conditions ofthis permit. Records ofmonitoring information shall include, butnot be limited to the following: (a) the date, place, and times ofsampling ormeasurements; (b) the date analyses were performed; (c) the company or entity that performed the analyses; (d) the analytical techniques ormethods used; (e) the results ofsuch analyses; and (f) the operating conditions existing at the time ofsampling or measurement. All monitoring records and support information shall be retained for aperiod ofat least five years from the date ofthemonitoring sample, measurement, report, or application. Supporting information includes, but is not limited to, all calibration and maintenance records and all original strip-chart recordings for continuous monitoring instrumentation and copies ofall reports required by this permit. All records required to be maintained by this permit shall be made available in either hard copy or electronicformat to DEQ representatives upon request. [IDAPA 58.01.01.405, 5/11941

1'2-2009.0105 Page

# ..

Excess Emissions 8. Thepermittee shall comply with the procedures and requirements ofIDAPA 58.01.01.130-136 for exees:; emissions due to startup, shutdown, scheduled maintenance, safety measures, upsets and breakdowns. [IDAPA 58.01.01.130-136,4/5/001 

### Certification 9. All documents submitted to DEQ, including, butnot limited to, records, monitoring data, supporting information, requests for confidential treatment, testing reports, or compliance certification shall contain a certification by a responsible official. The certification shall state that, based on information and belief formed after reasonable inquiry, the statements and information in the document(s) are true, accurate, and complete. [IDAPA 58.01.01.123.5/11941 

### False Statements 10. No person shall knowingly make any false statement, representation, orcertification in any form, notice, orreportrequired under this permit, orany applicable rule or order in force pursuant thereto. [JDAPA 58.01.01.125, 3123/98) 

### Tampering 11. No person shall knowingly render inaccurate 

### any monitoring device or method required under this permit or any applicable rule ororder in force pursuant thereto. [JDAPA 58.01.01.126,3123/981 

### Expiration andRenewal 12. This permit shall be renewable on the expiration date, provided the pcnnittee submits anapplication for renewal to the Department and continues to meet all terms and conditions contained in the permit. The expirationofthis permit will not affect the operationofthe stationary source offacility during the administrative procedure period associated with the permit renewal process. [IDAPA 58.01.01.404.04, 7fl/02) 

### Transferability 13. This pennitis transferable in accordance with procedures listed in IDAPA 58.01.01.404.05. (IDAPA 58.01.01.404.05, 4/11/06]

1'2·2009.0lOS Page 15