Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_ty pe

legal_address

legal_city legal_state legal_zip 1131 3203 The Municipal Electric Utility of the City

of Cedar Falls, Iowa The Municipal Electric Utiltiy of the City

of Cedar Falls, Iowa legal owner 1 Utility

Parkway

PO Box 769 Cedar Falls IA 50613 Page 1Facility _Information plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip Streeter Station

1 Utility Parkway Cedar Falls IA 50613 PO Box 769 Cedar Falls IA 50613 Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE FALSE TRUE FALSE FALSE TRUE FALSE TRUE Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE 567 24.1(455B) Excess Emission Reporting No Region VII - Kansas City Office, Iowa DNR - W indsor Heights, IA Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 4Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 5Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 6Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 7Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 8Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 9Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 10Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 11Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 12Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 13Facility _Information Design steam pressure and operating steam pressure are boiler pressure.There is no steam reheat cycleSO2 emissions are monitored with CEMS unit. The CEMS is certified annually by RATA testing. CFU is subject to the Acid Rain Program. From 2009 CEMS data we took the SO2 tons * 2000 divided by 2009 MMBTU from the CEMS unit to get the emission rate.Test Report Emission Data - There are no Test Reports for this Facility CEMS data for PM Filterable is opacity .Flue Gas temperature is 348 F for Run1Flue Gas temperature is 367 F for Run 2Flue Gas temperature is 374 F for Run 3Stack Pressure for Run 1 29.65 inches HgStack Pressure for Run 2 29.65 inches HgStack Pressure for Run 3 30.09 inches HgNo testing for mercuryLOI2006 Stack Test our PM emission rate is measured in lb/mmbtu which is not an option in the drop down Meas. Units.Run 1 was .245 lb/mmbtuRun 2 was .203 lb/mmbtuRun 3 was .209 lb/mmbtu Page 14facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 1131 1 Environm ental Coordinator Ed Olthoff 3192685309 3194042013

eolthoff@cfunet.net

TRUE 1131 2 Project Services Manager Dave Rusley

3192685300

3194042111

drusley@cfunet.net

FALSE Page 15facility _coal_utilized facility _id coal_ty pe percentage_mass percentage_btu

sy nfuel_ty pe

coal_note 1131 bitum inous 39 45 1131 subbituminous 61 55 Page 16facility _oil_utilized facility _id oil_ty pe percentage_volume percentage_btu

other_type Page 17facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain Page 18facility _other_materials rcra_explain Page 19boiler_information

facility _id boiler_id boiler_ty pe boiler_other bottom_design

design_fuel heat_input ma x_heat_input MW e_capacity 1131 7 Wa ll firing - front firing Dry Bottom coal 434000 434000 38.4 Page 20boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 35.2 88.1 88.1 1360 1250 950 950 FALSE 0 Page 21boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 0 2600 29.68 N FALSE Page 22boiler_information

NOx_control

SO2_control

combustion_additives No Yes No Page 23boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 1131 7 coal - bituminous 2007 93 94 1131 7 coal - bituminous 2008 86 88 1131 7 coal - bituminous 2009 39 45 1131 7 coal - subbituminous 2007 7 6 1131 7 coal - subbituminous 2008 14 12 1131 7 coal - subbituminous 2009 61 55

Page 24boiler_control_NOx

facility _id boiler_id NOx_ty pe NOx_other NOx_online Page 25boiler_control_SO2

facility _id boiler_id SO2_ty pe SO2_other SO2_online 1131 7 Low Sulfur Coal 6/1/2005 Page 26boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online Page 27facility _units facility _id unit_id 1131 7 Page 28unit_boilers

facility _id unit_id boiler_id 1131 7 7 Page 29facility _controls facility _id control_id control_group control_ty pe

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 1131 HSP PM control Electrostatic precipitator, hot side, w/o flue gas conditioning FALSE 6/1/1973 Page 30facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive Page 31facility _sampling_ports facility _id sampling_port_id 1131 SP1 Page 32facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 1131 EP1 305 8 54.6 Page 33configurations

facility _id configuration_id 1131 7 Page 34configuration_components

facility _id configuration_id

component_id

order component_ty pe port_near 1131 7 7 1 Unit 1131 7 EP1 4 Stack 1131 7 HSP 2 PM control 1131 7 SP1 3 Sam pling Port next Page 35configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_ty pe_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 1131 7 PM (Filterable) Fderal - Title V Operating Permit

0.6 pound per million British Thermal Unit (lb/MMBtu)

Continuous 1131 7 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

6 pound per million British Thermal Unit (lb/MMBtu)

Continuous Page 36configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method Method 17 Page 37configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting 0.22 pound per million British Thermal Unit (lb/MMBtu)

No Opacity CEMS 40 CFR Part 75, Periodic Stack test per permit conditions, Iowa Method 5

Annual Em issions Inventory to the State 567IAC 25.2; 25.1(1); Excess emissions reported following IAC567-24.1(455B) 0.84 pound per million British Thermal Unit (lb/MMBtu)

No CEMS 40 CFR Part 75 Quarterly

and Annual Em issions Inventory to the State (567IAC25.2); Excess emissions reported following 567IAC 24.1(455B) Page 38configuration_pollutants1 Annual Em issions Inventory to the State 567IAC 25.2; 25.1(1); Excess emissions reported following IAC567-24.1(455B) Quarterly

and Annual Em issions Inventory to the State (567IAC25.2); Excess emissions reported following 567IAC 24.1(455B) Page 39control_technologies

facility _id configuration_id

component_id

control_id project_title project_ty pe vendor_name

vndor_contact

vendor_phone Page 40control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive Page 41control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units Page 42control_technologies feed_rate_units Page 43control_coal_ranks

facility _id configuration_id

component_id

control_id coal_ty pe

Page 44control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 45control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year Page 46control_costs

CBI Page 47mi sc_controls

facility _id mi sc_control_id

control_description Page 48mi sc_control_configurations

facility _id mi sc_control_id

configuration_id Page 49fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 1131 1 11/1/2009 14703 short tons (2000 lbs) coal MT MT - Yellowstone 1131 2 12/1/2009 14595 short tons (2000 lbs) coal MT MT - Yellowstone Page 50fuel_shipments

coal_seam shipment_method Mam mo uth Unit Train ma mmo th Unit Train Page 51fuel_shipment_configurations

facility _id shipment_id

configuration_id 1131 1 7 1131 2 7 Page 52fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 1131 2 1 29298 tons 0.56 7.29 12493 Btu/lb Page 53fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_ty pe

supplier_name

supplier_address 0.01 percent (dry) (%) 39 parts per million (dry) (ppm) standard operational procedures Other Cedar Falls Utilities Utility Parkway PO Box 769 Page 54fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies Cedar Falls IA 50613 SGS North America Inc 16130 Van Drunen Road

South Holland

IL 60473 Yes Page 55fuel_shipment_samples analysis_copies Page 56fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 1131 2 1 Arsenic (As) 3 parts per million (dry) (ppm) FALSE 1131 2 1 Cadmium (Cd) 0 parts per million (dry) (ppm) FALSE 1131 2 1 Chromium (Cr) 4 parts per million (dry) (ppm) FALSE 1131 2 1 Lead (Pb) 4 parts per million (dry) (ppm) FALSE 1131 2 1 Mercury (Hg) 0.03 parts per million (dry) (ppm) FALSE 1131 2 1 Selenium (Se) 0 parts per million (dry) (ppm) FALSE 1131 2 1 Vanadium (V) 10 parts per million (dry) (ppm) FALSE Page 57test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 1131 2006 Stack Test

compliance Stack Test for Title V permit compliance 6/1/2006 6/1/2006 No No Page 58test_reports

deviation_reports No Page 59test_report_configurations

facility _id report_id configuration_id 1131 2006 Stack Test

7 Page 60test_report_fuels

facility _id report_id fuel_id 1131 2006 Stack Test

Galatia Coal Page 61test_report_fuel_ty pes

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 1131 2006 Stack Test

Galatia Coal

coal - bituminous 100 100

Page 62cem_data

facility _id tim e_period

cem_period_description 1131 Continuous Page 63cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 1131 Continuous PM (Filterable) 1131 Continuous Nitrogen Oxide (NOx) 1131 Continuous Sulfur Dioxide (SO2) Page 64test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_by pass_percent

testing_by pass_percent 1131 2006 Stack Test

SP1 No No Page 65test_report_sampling

fg_fraction Page 66sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 1131 2006 Stack Test

SP1 1 6/1/2006 6/1/2006 36 34 7.8 1131 2006 Stack Test

SP1 2 6/1/2006 6/1/2006 36 34 9.2 1131 2006 Stack Test

SP1 3 6/1/2006 6/1/2006 36 34 8.2 Page 67sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 102760 dscfm 5 13.8 0 101995 dscfm 5.3 13.7 0 104304 dscfm 5.3 13.6 0 Page 68sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 0 0 Method 17 None Galatia Coal 34 7.31 13621 0 0 Method 17 None Galatia Coal 34 7.31 13621 0 0 Method 17 None Galatia Coal 34 7.31 13621 Page 69sampling_runs

fuel_sulfur 1.39 1.39 1.39 Page 70sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 1131 2006 Stack Test

SP1 1 PM (Filterable) FALSE 1131 2006 Stack Test

SP1 2 PM (Filterable) FALSE 1131 2006 Stack Test

SP1 3 PM (Filterable) FALSE Page 71sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 115.87 pound per hour (lb/hr)

FALSE 0.245 pound per million British Thermal Unit (lb/MMBtu) FALSE 94.76 pound per hour (lb/hr)

FALSE 0.203 pound per million British Thermal Unit (lb/MMBtu) FALSE 98.8 pound per hour (lb/hr)

FALSE 0.209 pound per million British Thermal Unit (lb/MMBtu) FALSE Page 72sampling_run_pollutants1 run_pollutant_comment Page 73sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL 1131 2006 Stack Test

SP1 1 Arsenic (As) 14 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 1 Barium (Ba) 15 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 1 Cadmium (Cd) 0 mi crogram per gram (dry) (mg/g) TRUE 1 1131 2006 Stack Test

SP1 1 Chloride (Cl) 1648 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 1 Chromium (Cr) 11 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 1 Fluoride (F) 49 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 1 Lead (Pb) 11 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 1 Mercury (Hg) 0.08 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 1 Selenium (Se) 0 mi crogram per gram (dry) (mg/g) TRUE 1 1131 2006 Stack Test

SP1 1 Vanadium (V) 21 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Arsenic (As) 14 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Barium (Ba) 15 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Cadmium (Cd) 0 mi crogram per gram (dry) (mg/g) TRUE 1 1131 2006 Stack Test

SP1 2 Chloride (Cl) 1648 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Chromium (Cr) 11 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Fluoride (F) 49 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Lead (Pb) 11 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Mercury (Hg) 0.08 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 2 Selenium (Se) 0 mi crogram per gram (dry) (mg/g) TRUE 1 1131 2006 Stack Test

SP1 2 Vanadium (V) 21 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Arsenic (As) 14 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Barium (Ba) 15 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Cadmium (Cd) 0 mi crogram per gram (dry) (mg/g) TRUE 1 1131 2006 Stack Test

SP1 3 Chloride (Cl) 1648 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Chromium (Cr) 11 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Fluoride (F) 49 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Lead (Pb) 11 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Mercury (Hg) 0.08 mi crogram per gram (dry) (mg/g) FALSE 1131 2006 Stack Test

SP1 3 Selenium (Se) 0 mi crogram per gram (dry) (mg/g) TRUE 1 1131 2006 Stack Test

SP1 3 Vanadium (V) 21 mi crogram per gram (dry) (mg/g) FALSE Page 74sampling_run_fuel fuel_conc_MDL Page 75