# FINAL 2013 BIENNIAL LEAK

DETECTION TESTING REPORT

OF BULK FIELD

- CONSTRUCTED

UNDERGROUND STORAGE

TANK 10

JOINT BASE PEARL HARBOR

HICKAM / RED HILL, HAWAII

Prepared for:

Defense Logistics Agency Energy Ft. Belvoir, Virginia

Prepared under:


## NAVFAC Atlantic

Contract N62470

- 10

- D

- 3000

- 00 26

Submitted by: 

## Michael Baker Jr., Inc. Virginia Beach, VA

Date:



## 19 FEBRUARY 2013

Project: 127964

Task: 4.1.033FINAL 2013 BIENNIAL LEAK DETECTION TESTING REPORT

OF BULK FIELD

- CONSTRUCTED UNDERGROUND STORAGE TANK 10

JOINT BASE PEARL HARBOR

- HICKAM / RED HILL, HAWAII

Prepared for:

Defense Logistics Agency Energy

Ft. Belvoir, VA

Prepared under:

NAVFAC Atlantic

Contract N62470

- 10

- D

- 3000

- 0026

Prepared by:

Michael Baker Jr., Inc.

Virginia Beach, Virginia

19 February 2013i TABLE OF CONTENTS

Page No.

LIST OF ABBREVIATIONS AND ACRONYMS

................................ ................................ ........ ii

PROFESSIONAL ENGINEER CERTIFICATION:

................................ ................................ ...... iii

EXECUTIVE SUMMARY

................................ ................................ ................................ ............ iv

1.0 INTRODUCTION

................................ ................................ ................................ .............. 1

1.1 Purpose of Project



### ................................ ................................ ................................ . 1

1.2 Site Background and History



### ................................ ................................ .................. 1

1.3 Historical Leak Detection Results



### ................................ ................................ ........... 2

1.4 Project Scope



### ................................ ................................ ................................ ........ 2

1.5 Project Team



### ................................ ................................ ................................ ......... 5

1.6 Qualifications of Testing Procedures Used



### ................................ .............................. 5

2.0 LEAK DETECTION TESTING AND RESULTS

................................ ............................ 6

3.0 CONCLUSIONS AND RECO MMENDATIONS

................................ ............................. 7

3.1 Conclusions



### ................................ ................................ ................................ .......... 7

3.2 Recommendations



### ................................ ................................ ................................ . 7

4.0 REFERE NCES

................................ ................................ ................................ ................... 8

L ist of Tables

Table 1

- 1 : Items Tested

................................ ................................ ................................ ................... 2

Table 2

- 1 : Test Results

................................ ................................ ................................ .................... 6

List of F igures

Figure 1

- 1: Base Overview Map

................................ ................................ ................................ ..... 3

Figure 1

- 2: Red Hill System Layout

................................ ................................ ............................... 4

List of Appendices

Appendix A Mass Technology Corporation Test Reportii LIST OF A BBREVIATIONS AND ACRONYMS

AFB Air Force Base

Baker Michael Baker Jr., Inc.

BFCUST Bulk field

- constructed underground storage tank

BMP Best Management Practice

CMP Centrally Managed P rogram

DLA Defense Logistics Agency

gph Gallons per hour

JB Joint Base

MDLR Minimum detectable leak rate

MTC Mass Technology Corporation

NW GLDE National Work Group on Leak Detection Evaluationsiii PROFESSIONAL ENGINEER CERTIFICATION :

Final 2013 Biennial Leak Detection Testing Report

O f Bulk Field

- Constructed Underground Storage Tank 10

Joint Base Pearl Harbor

- Hickam / Red Hill, Hawaii

This report has been reviewed by a professional engineer and has been prepared in accordance

with good engineering practices. Laboratory results, field notes

, and supporting data have been

reviewed and referenced correctly.

I hereby certify that I have examined this report and attest that it has been prepared in accordance

with good engineering practices.

Engineer: Christopher D. Caputi, P.E.

Registration Number : 032382

State : Virginia

Date : 19 February 2013iv EXECUTIVE SUMMARY

The scope of this project is to perform biennial leak detection testing of Bulk Field

- Constructed

Unde rground Storage Tank 10 at Naval Supply Systems Command Fleet Logistics Center Pearl

Harbor

– Joint Base Pearl Harbor

- Hickam / Red Hill, Hawaii. There are currently no regulations

that outline test requirements for bulk field

- c onstructed u nde rground storage tanks at Red Hill.

The testing is being conducted un der De fense Logistics Agency Energy’s Leak Detection

Centrally Managed P ro gram as a pollution prevention Best Management P ractice.

Bulk Field

- Constructed Unde rground Storage Tank 10 was Mass Technology Corporation leak

detection tested from 30 January through 6 February 2013 with no detectable leak above the test

method’s minimum detectable leak rate of 0.7 gallons per hour resulting in a passed test.

Biennial leak detection testing of Bulk Field

- Constructed Unde rground Storage Tank 10 should

be comple ted on or before the anniversary date of 6 February 201 5 under Defense Logistics

Agency Energy’s Leak Detection Centrally Managed P ro gram as a pollution prevention Best

Management P ractice.1

1.0 INTRODUCTION

1.1 Purpose of Project

The Defense Logistics Agency (DLA) Energy contracted Michael B aker Jr., Inc. (Baker) through

Naval Facilities Engineering Command (NAVFAC) Atlanti c Contract N62470

- 10

- D

- 3000

- 0026

to perform biennial leak detection testing of Bulk Field

- Constructed Unde rground Storage Tank

(BFCUST) 10 at Naval Supply Systems Command Fleet Logistics Center Pearl Harbor

– Joint

Base (JB) Pearl Harbor

- Hickam / Red Hill, Hawaii. There are currently no regulations that

outline test requirements for BFCUSTs at Red Hill. The testing is being conducted under DLA

Energy’s Leak Detection Centrally Managed P rogram (CMP) as a pollution prevention Best

Management P ractice (BMP)

.

1.2 Site Background and History

In 2010, Naval Station Pearl Harbor and Hickam Air Force Base (AFB) were me rged into JB

Pearl Harbor

- Hickam combining the two historic bases into a single joint installation to support

both Air Force and Navy missions, along with the tenant commands, and all the service members

and their families. Pearl Harbor was established as a United States naval base in 1908. In 1934,

the Army Air Corps began construction of the base that, on May 31, 1935, was dedicated as

Hickam AFB. Together, the two bases play a central role in the Pacific theater and constitute a

vital part of the Unit ed States defense establishment today.

The Red Hill underground fuel storage facility consists of 20 BFCUSTs located hundreds of feet

below ground and was constructed between 1940 and 1943 to replace vulnerable aboveground

fuel storage tanks that were loc ated around Pearl Harbor. The BFCUSTs at Red Hill are

accessible through a tunnel system. The top tunnel runs approximately 60 feet below the top

section of the tanks and the bottom tunnel runs equal to the bottom level of the tanks. The

issue/receipt a nd water drain pipelines are accessible immediately adjacent to each tank within

the lower tunnel. All lines are equipped with D ouble B lock and B leed Valves for isolation.

BFCUST 10 is 100 feet in diameter, 250 feet in height, and has a capacity of 12,600,000 gallons

of JP

- 5.2

1.3 Historical Leak Detection Results

The last biennial test event of BFCUST 10, a Mass Technology Corporation (MTC) leak

detection test conducted from 5 January to 13 January 2011, showed passing results with no

detectable leak above the test method’s minimum detectable leak rate (MDLR) (Baker, 2011).

1.4 Project Scope

A MTC leak detection test on BFCUST 10 was performed from 30 January through 6 February

2013 . Table 1

- 1 provides a description of the systems tested. Figure 1

- 1 provides a base

overview map

. Figure 1

- 2 provides a layout of the Red Hill system.

Table 1

- 1 : Items Tested

Designation Diameter Height or Length

(Feet) Volume

(Gallons) Product Comments

BFCUST 10 100 feet 250 12,600,000 JP

- 5 Product Level at Test: 211.38

feet3 Figure 1

- 1 : Base Overview Map

(Source: Google Maps, 2013 )4 Figure 1

- 2 : Red Hill System Layout

(Source: Baker, 2009 )5

1.5 Project Team

Baker subcontracted MTC to perform the leak detection testing. Field

- testing oversight,

coordination with facility fuels representat ives, quality assurance/quality controls

, and final report

preparation and submission was provided by Baker personnel.

1.6 Qualifications of Testing Procedures Used

The testing procedures used were those defined as the MTC

- Precision Mass Measurement

Systems SIM

- 1000 / CBU

- 1000 ( 

### 72 hour test) leak detection method. Determination of leakage

is based on the criteria established in the Ken Wilcox Associates third party evaluation (National

Work Group on Leak Det ection Evaluations [NWGLDE, 2012])

. The MTC Precision Mass

Measurement System ( 

### 72 hour test) is certified with a capability to detect leaks on a tank

proportional to the product surface area with a probability of detection of 95 percent and

probability of a false alarm of 5 percent. Due to the extreme height of the tank, a total of 168

hours of testing was performed.

By performing a number of non

- overlapping tests in sequence and averaging the resultant leak

rates, a modif

ied threshold can be established for declaring a leak. Through standard statistical

analysis, the larger the number of tests used in the averaging will result in a lower threshold and,

therefore, a smaller size leak can be detected with a 95 percent proba bility of detection.6

2.0 LEAK DETECTION TESTING AND RESULTS

MTC ’s test report is provided in Appendix A. BFCUST 10 was leak detection tested with no

detectable leak above the test method’s minimum detectable leak rate (MDLR) of 0.7 gallons per

hour ( gph )

. Test results are listed in Table 2

- 1

.

Table 2

- 1 : Test Results

Designation Volume

(Gal lon s) Height

or Length
(Feet) Product Certified

MDL R
( gph ) Test

Date Result

BFCUST 10 12,600,000 250 JP

- 5 0.7 30 Jan 2013

– 6 Feb 2013 Passed7

3.0 CONCLUSIONS AND RECO MMENDATIONS

3.1 Conclusions

BFCUST 10 passed the 2013 biennial leak detection testing.

3.2 Recommendations

Biennial leak detection testing of BFCUST 10 should be completed on or before the anniversary

date of 6 February 2015 under DLA Energy’s Leak Detection CMP as a pollution prevention

BMP

.8

4.0 REFERENCES

Baker, 2011 Final 2011 Biennial Integrity Testing Report Of Bulk Field Construc ted

Underground Storage Tank 10

- Naval Station Pearl Harbor / Red Hill,

Hawaii

. Prepared for Defense Logistics Agency Energy, Ft. Belvoir,

VA. Prepared under NAVFAC Atlantic Contract N62470

- 10

- D

- 3000

-

0004. Dated 10 March 2011.

NWGLDE, 2012 Listing by the NWGLDE (Nineteenth Edition): Precision Mass

Measurement Systems SIM

- 1000 an d CBU

- 1000 (72 hour test)

– BULK

UNDERGROUND STORAGE TANK LEAK DETECTION METHOD

(50,000 gallons or greater).

Issue Date: 23 August 1999

Revision Date: 28 May 2008

http://nwglde.org/evals/mas s_technology_c.html

.

### Michael Baker Jr., Inc.



## TEST REPORT

JB PEARL HARBOR

- HICKAM / RED HILL, HAWAII

APPENDIX A

–

MASS TECHNOLOGY CORP ORATION TEST REPORT 1



### 176

FISC Red Hill Project Manager

– Mr. Mark Caldon

Pearl Harbor

, HI

Site Supervisor

– T ravis Ricketson

Scope of Work: Furnish all required management, labor, services, materials and equipment

to perform the required annual tightness testing of Tank # 10 a n underground fuel storage tank located at FISC Red Hill, Pearl Harbor, HI.

Report compiled by: Date: 02

- 1 3

- 20 1 3

Ricky S laughte r

Summary

Testing of Tank # 10 a 12,600,000 gal underground storage tank located at FISC Red Hill, Pearl

Harbor, Hawaii commenced January 3 0

, 2013 and was completed February 6 , 2013 . The tank

c ontained JP

- 5 and a precision leak test was conducted. The result of that testing is that the tank

system is determined to be tight to isolation. All tank valves were adequately secured such th at no
unusual readings were noted. Testing was performed using the Mass Technology Corporation

protocols set out in the third party evaluations. All tank valves were adequately secured such that

any fluid loss was isolated to leakage. Therefore, the c ontainment integrity of the tank was not

compromised and the test is considered conclusive.

Tank # 10 : After 1 68 hours of testing the tank is certified to be tight

. 

### Precision Leak Measurement Report

P.O. Box 1578 Kilgore, Texas 75662 2



### Tank Data Tank # 10

Diameter: 1 00 ft. Height: 2 50 ft.

Tank Type: Vertical UST Contents: JP

- 5
Specific Gravity : 0. 8 2 Product Level: 2 11

. 3 8 ft.

Start Date: 01/ 3 0 /2013 Completion Date: 0 2 / 0 6 /2013

Unit Operator: T ravis Ricketson Test Results : Certified Tight

All dimensions, line locations, sizes and

valve descriptions have been furnished
by the facility operator. 3



### Results

The fluid mass data was recorded over a 1 68

- hour period. A linear regression of the recorded fluid

mass data resulted in a leak rate detected below the minimum detection level of 0. 7 gallon s per

hour. All tank valves were adequately secured such that any fluid loss was isolated to leakage.

Therefore, the containment integrity of the tank was not compromised and the test is considered

conclusive.

Tank # 10 is certified to be tight

.