### APPENDIX B. ENGINEERING DATA

TABLE OF CONTENTS

B.1 INTRODUCTION

.......................................................................................................... B-2
B.2 BASELINE DESIGN OPTIONS

.................................................................................... B-2
B.3 COST-EFFICIENCY RESULTS

................................................................................... B-2

LIST OF TABLES

Table B.2.1 Baseline Design Options

...................................................................................... B-2 Table B.3.1 Cost-Efficiency Data and Desi gn Options for the Small-Sized Type A Equipment Class

............................................................................................ B-3 Table B.3.2 Cost-Efficiency Data and Design Options for the Medium-Sized Type A .............. Equipment Class

............................................................................................ B-4 Table B.3.3 Cost-Efficiency Data and Desi gn Options for the Large-Sized Type A Equipment Class

............................................................................................ B-5 Table B.3.4 Cost-Efficiency Data and Desi gn Options for the Small-Sized Type B Equipment Class

............................................................................................ B-6 Table B.3.5 Cost-Efficiency Data and Design Options for the Medium-Sized Type B ............... Equipment Class

............................................................................................ B-7 Table B.3.6 Cost-Efficiency Data and Design Opti ons for the Large-Sized Type B Equipment
Class

............................................................................................................... B-8

LIST OF FIGURES

Figure B.3.1 Cost-Efficiency Curve for the Sm all-Sized Type A Equipment Class

................ B-3 Figure B.3.2 Cost-Efficiency Curve for the Medium-Sized Type A Equipment Class

............ B-4 Figure B.3.3 Cost-Efficiency Curve for the La rge-Sized Type A Equipment Class

................ B-5 Figure B.3.4 Cost-Efficiency Curve for the Sm all-Sized Type B Equipment Class

................ B-6 Figure B.3.5 Cost-Efficiency Curve for the Medium-Sized Type B Equipment Class

............ B-7 Figure B.3.6 Cost-Efficiency Curve for the La rge-Sized Type B Equipment Class

................ B-8

B-i BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc

### APPENDIX B. ENGINEERING DATA

B.1 INTRODUCTION

This appendix presents baseline specificati ons and detailed cost-efficiency results for each of the three sizes in the beverage vendi ng machine equipment classes analyzed in the engineering analys is (chapter 5).

B.2 BASELINE DESIGN OPTIONS

Table B.2.1 shows the baseline design options for each size of each equipment class. All changes to cost and efficiency are measured rela tive to this level in the engineering analysis. Refer to chapter 5 of the TSD for de tails about each baseline technology.

Table B.2.1 Baseline Design Options Design Type Type A Type B
Small Medium Large Small Medium Large
Lighting and Ballasts T8 T8 T8 T8 T8 T8
Electronic Electronic Electronic Electronic Electronic Electronic Evaporator Coil High Standard High High High High Design Performance Coil Performance Performance Performance Performance
Coil Coil Coil Coil Coil
Evaporator Fan Motor Permanent Permanent Electrically Permanent Permanent Permanent Split Split Commutated Split Split Split Capacitor Capacitor Capacitor Capacitor Capacitor
Evaporator Fan No Controller No Controller Controller Controller
Control Controller Controller
Insulation Design Standard Standard Standard Standard Standard Standard

Glass Pack Design Enhanced Enhanced Enhanced

- - - - - -

Condenser Coil Standard Standard Standard Standard Standard Standard Design Coil Coil Coil Coil Coil Coil

Condenser Fan Motor Permanent Permanent Permanent Permanent Permanent Permanent Split Split Split Split Split Split Capacitor Capacitor Capacitor Capacitor Capacitor Capacitor
Compressor Standard Standard Standard Enhanced Standard Enhanced Efficiency



### B.3 COST-EFFICIENCY RESULTS

For each size and equipment class analyzed in the engineering analysis, Figure B.3.1 through Figure B.3.6 show cost-efficiency cu rves and Table B.3.1 through Table B.3.6 show detailed cost-efficiency data. Cost-efficiency da ta and technology changes that occur above the
baseline level are included in each table.

Design option changes above the baseline ar e shown in Table B .3.1 through Table B.3.6 as additions to the previous design option level. For example, in the Type A small product class,

B-2 BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc

### “0 + PSC Condenser Motor” would indicate th at the condenser fan motor technology in the baseline level (shaded pole motor, SPM) was replaced with a permanent split capacitor (PSC) motor. Design options are implemented from the lowest to highest payback and only one design option change is made per design option level.

$1,000 $1,500 $2,000 $2,500 $3,000 $3,500

0.0 2.0 4.0 6.0 8.0 10.0
Daily Energy Consumption [kWh/day]Manufacturer Selling Price [$]



### Figure B.3.1 Cost-Efficiency Curve for the Small-Sized Type A Equipment Class

Table B.3.1 Cost-Efficiency Data and Desi gn Options for the Small-Sized Type A Equipment Class Design Option
Level Daily Energy Consumption kWh/day Manufacturer Selling Price $ Design Option Change Above the Baseline

1 6.10
2 5.73
3 5.57
4 5.47
5 5.27

6 3.95
7 3.73
8 3.63
9 3.58
10 3.33
11 3.25 1,856.20 1,868.92 1,876.79 1,881.93 1,893.33

2,003.03 2,027.85 2,043.67 2,055.07 2,204.35 2,971.76 - - 1 + Evaporator Fan Control 2 +Super T8 Lighting 3 + High Efficiency Compressor 4 + ECM (Electronically Commutated Motors) Evaporator Fan Motor 5 + LED (Light Emitting Diode) Lighting 6 + High-Performance Condenser Coil
7 + 1/8" Thicker Insulation
8 + ECM Condenser Motor 9 + Super-Enhanced Doors 10 + Aerogel Insulation

B-3 BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc$1,000 $1,500 $2,000 $2,500 $3,000 $3,500 $4,000

0.0 2.0 4.0 6.0 8.0 10.0
Daily Energy Consumption [kWh/day]Manufacturer Selling Price [$]



### Figure B.3.2 Cost-Efficiency Curve for th e Medium-Sized Type A Equipment Class

Table B.3.2 Cost-Efficiency Data and Design Options for the Medium-Sized Type A Equipment Class Design Option
Level Daily Energy Consumption kWh/day Manufacturer Selling Price $ Design Option Change Above the Baseline

1 6.53
2 5.97
3 5.81
4 5.70
5 5.51
6 4.19
7 3.95
8 3.83
9 3.79
10 3.52
11 3.43 2,222.07 2,243.64 2,251.52 2,257.59 2,268.99 2,378.69 2,408.68 2,427.84 2,439.23 2,602.29 3,456.21 - - 1 + High-Performance Evaporator Coil 2 + Super T8 Lighting 3 + High Efficiency Compressor 4 + ECM Evaporator Fan Motor 5 + LED Lighting 6 + High-Performance Condenser Coil
7 + 1/8" Thicker Insulation
8 + ECM Condenser Motor 9 + Super-Enhanced Doors 10 + Aerogel Insulation

B-4 BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc$1,000 $1,500 $2,000 $2,500 $3,000 $3,500 $4,000

0.0 2.0 4.0 6.0 8.0 10.0 12.0
Daily Energy Consumption [kWh/day]Manufacturer Selling Price [$]



### Figure B.3.3 Cost-Efficiency Curve for th e Large-Sized Type A Equipment Class

Table B.3.3 Cost-Efficiency Data and Desi gn Options for the Large-Sized Type A Equipment Class Design Option
Level Daily Energy Consumption kWh/day Manufacturer Selling Price $ Design Option Change Above the Baseline

1 6.75
2 6.62
3 6.46
4 6.21
5 4.89
6 4.60
7 4.46
8 4.41
9 4.05
10 3.94 2,426.95 2,433.02 2,440.90 2,453.62 2,563.32 2,593.31 2,613.58 2,624.98 2,840.85 3,846.11 - - 1 + High Efficiency Compressor 2 + Super T8 Lighting 3 + Evaporator Fan Controller 4 + LED Lighting 5 + High-Performance Condenser Coil
6 + 1/8" Thicker Insulation
7 + ECM Condenser Motor 8 + Super-Enhanced Door 9 + Aerogel Insulation

B-5 BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc$1,000 $1,500 $2,000 $2,500 $3,000 $3,500

0.0 2.0 4.0 6.0 8.0 10.0 12.0 14.0
Daily Energy Consumption [kWh/day]Manufacturer Selling Price [$]



### Figure B.3.4 Cost-Efficiency Curve for the Small-Sized Type B Equipment Class

Table B.3.4 Cost-Efficiency Data and Desi gn Options for the Small-Sized Type B Equipment Class Design Option
Level Daily Energy Consumption kWh/day Manufacturer Selling Price $ Design Option Change Above the Baseline

1 4.96
2 4.62
3 4.51
4 4.31
5 4.28
6 3.78
7 3.69 1,521.33 1,544.13 1,557.72 1,591.67 1,603.07 2,023.72 2,909.47 - - 1 + ECM Evaporator Fan Motor
2 + 1/8" Thicker Insulation 3 + High-Performance Condenser Coil
4 + ECM Condenser Fan Motor 5 + LED Lighting 6 + Aerogel Insulation

B-6 BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc$1,000 $1,500 $2,000 $2,500 $3,000 $3,500

0.0 2.0 4.0 6.0 8.0 10.0 12.0 14.0
Daily Energy Consumption [kWh/day]Manufacturer Selling Price [$]



### Figure B.3.5 Cost-Efficiency Curve for th e Medium-Sized Type B Equipment Class

Table B.3.5 Cost-Efficiency Data and Desi gn Options for the Medium-Sized Type B Equipment Class Design Option
Level Daily Energy Consumption kWh/day Manufacturer Selling Price $ Design Option Change Above the Baseline

1 5.56
2 5.20
3 5.12
4 4.99
5 4.76
6 4.72
7 4.22
8 4.12 1,716.84 1,739.63 1,744.77 1,760.59 1,796.01 1,807.41 2,228.06 3,247.02 - - 1 + ECM Evaporator Fan Motor 2 + High Efficiency Compressor
3 + 1/8" Thicker Insulation 4 + High-Performance Condenser
5 + ECM Condenser Fan Motor 6 + LED Lighting 7 + Aerogel Insulation

B-7 BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc$1,000 $1,500 $2,000 $2,500 $3,000 $3,500 $4,000

0.0 2.0 4.0 6.0 8.0 10.0 12.0 14.0
Daily Energy Consumption [kWh/day]Manufacturer Selling Price [$]



### Figure B.3.6 Cost-Efficiency Curve for th e Large-Sized Type B Equipment Class

Table B.3.6 Cost-Efficiency Data and Desi gn Options for the Large-Sized Type B Equipment Class Design Option
Level Daily Energy Consumption kWh/day Manufacturer Selling Price $ Design Option Change Above the Baseline

1 5.85
2 5.48
3 5.33
4 5.07
5 5.03
6 4.52
7 4.41 1,779.80 1,802.60 1,819.53 1,854.95 1,866.35 2,287.00 3,439.97 - - 1 + ECM Evaporator Fan Motor
2 + 1/8" Thicker Insulation 3 + High-Performance Condenser Coil
4 + ECM Condenser Fan Motor 5 + LED Lighting 6 + Aerogel Insulation

B-8 BVM_FINAL_FR_TSD_AppendixB_08-14-09.doc