P:\PACIFICORP\370414BART2\TECHNICAL_MEMORANDUM_DELIVERABLES\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 1 

TECHNICAL MEMORANDUM 

Addendum to Naughton Unit 3 BART Report 

PREPARED FOR: Wyoming Division of Air Quality 

PREPARED BY: CH2M HILL 

COPIES: Bill Lawson/PacifiCorp 

DATE: March 26, 2008 

Introduction 

In compliance with the Regional Haze Rule (40 Code of Federal Regulations [CFR] 51), the 

Wyoming Division of Air Quality (WDAQ) required PacifiCorp Energy to conduct a detailed 

Best Available Retrofit Technology (BART) review to analyze the effects to visibility in nearby 

Class I areas from plant emissions, both for baseline and for reasonable control technology 

scenarios. PacifiCorp submitted these evaluations to WDAQ in January 2007. A revised report 

was submitted in October 2007. 

On January 3, 2008, PacifiCorp Energy personnel met with WDAQ staff to discuss the status of 

the BART reviews. At that time, the state requested that additional modeling scenarios for 

several of the PacifiCorp facilities be performed to aid in their BART review. This memorandum 

presents the economics analysis for two scenarios modeled, referred to as Scenario A and 

Scenario B and described as follows: 

• Scenario A: PacifiCorp committed controls at permitted rates—low nitrogen oxide (NOx) 

burners (LNBs) with over-fire air (OFA), wet flue gas desulfurization (FGD), new fabric 

filter baghouse 

• Scenario B: PacifiCorp committed controls and selective catalytic reduction (SCR) at 

permitted rates 

The CALPUFF modeling system (v. 5.711a) was used for this analysis. All technical options and 

model triggers used in CALMET, CALPUFF, and CALPOST are consistent with those used for 

the previous BART analyses and described in the BART report submitted in October 2007. 

Stack Parameters, Emissions Information, and Capital Cost 

Table 1 summarizes the control equipment for Scenarios A and B as well as the current 

equipment installed at the plant. The overall capital cost of installing these options is also shown. 
ADDENDUM TO NAUGHTON UNIT 3 BART REPORT 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 2 

TABLE 1 

Control Scenario Summary 

Naughton Unit 3 

 Equipment Type Capital Cost 

 NOx SO2 PM10 Million dollars 

Baseline LNB Wet sodium FGD ESP — 

Scenario A LNB with OFA Wet sodium FGD Fabric filter $128.0 

Scenario B LNB with OFA and SCR Wet sodium FGD Fabric filter $263.8 

Emissions were modeled for the following pollutants: 

• Sulfur dioxide (SO2) 

• NOx

• Coarse particulate (PM2.5<diameter<PM10) 

• Fine particulate (diameter<PM2.5) 

• Sulfates 

Table 2 shows stack parameters and emission rates that were used for the Naughton Unit 3 

BART modeling and analysis. 

TABLE 2 

Calpuff Model Inputs 

Naughton Unit 3 

 BART Comparison(d)

Model Input Data Baseline 

Scenario 

A (e)

Scenario 

B (f)

Hourly Heat Input (mmBtu/hour) 3,700 3,700 3,700 

Sulfur Dioxide (SO2) Stack Emissions (lb/hr) 1,840 814 814 

Nitrogen Oxide (NOx) Stack Emissions (lb/hr) 1,656 1,369 259 

PM10 Stack Emissions (lb/hr) 348 55.5 55.5 

Coarse Particulate (PM2.5 <diameter< PM10) Stack Emissions (lb/hr)(a) 149 23.9 23.9 

Fine Particulate (diameter<PM2.5) Stack Emissions (lb/hr)(b) 198 31.6 31.6 

Sulfuric Acid (H2SO4) Stack Emissions (lb/hr) 34 34.0 58.5 

Ammonium Sulfate [(NH4)2SO4] Stack Emissions (lb/hr) — — 4.3 

(NH4)HSO4 Stack Emissions (lb/hr) — — 7.4 

H2SO4 as Sulfate (SO4) Stack Emissions (lb/hr) 33.4 33.3 57.3 

(NH4)2SO4 as SO4 Stack Emissions (lb/hr) — — 3.1 

(NH4)HSO4 as SO4 Stack Emissions (lb/hr) — — 6.2 
ADDENDUM TO NAUGHTON UNIT 3 BART REPORT 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 3 

TABLE 2 

Calpuff Model Inputs 

Naughton Unit 3 

 BART Comparison(d)

Model Input Data Baseline 

Scenario 

A (e)

Scenario 

B (f)

Total Sulfate (SO4) (lb/hr)(c) 33.2 33.3 66.6 

Stack Conditions 

Stack Height (meters) 145 145 145 

Stack Exit Diameter (meters) 8.08 8.08 8.08 

Stack Exit Temperature (Kelvin) 323 322 322 

Stack Exit Velocity (meters per second) 23.8 20.2 20.2 

NOTES:

(a) Based on AP-42, Table 1.1-6, the coarse particulates are counted as a percentage of PM10. This equates to 43% 

ESP and 57% Baghouse. PM10 and PM2.5 refer to particulate matter less than 10 and 2.5 micrometers, respectively, 

in aerodynamic diameter. 

(b) Based on AP-42, Table 1.1-6, the fine particulates are counted as a percentage of PM10. This equates to 57% 

ESP and 43% Baghouse. 

(c) Total Sulfate (SO4) (lb/hr) = H2SO4 as Sulfate (SO4) Stack Emissions (lb/hr) + (NH4)2SO4 as SO4 Stack Emissions 

(lb/hr) + (NH4)HSO4 as SO4 Stack Emissions (lb/hr) (d) SO2, NOx, and PM rates are expressed in terms of permitted emission rates. Actual emissions will be less than 

the permitted rates. 

(e) PacifiCorp Committed Controls @ permitted rates: LNB with OFA, Wet FGD, New Fabric Filter 

(f) PacifiCorp Committed Controls and SCR @ permitted rates

Economic Analysis 

In completing this additional analysis to supplement the previous BART study, technology 

alternatives were investigated and potential reductions in NOx, SO2, and PM10 emissions rates 

were identified. 

A comparison of Scenarios A and B on the basis of costs, design control efficiencies, and tons of 

pollutant removed is summarized in Tables 3 through 5. Capital costs were provided by 

PacifiCorp. The complete economic analyses for these two scenarios are provided as 

Attachment 1.
ADDENDUM 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 

TABLE 3 Scenario A Control Cost Naughton Unit 3 

 NOx Control SO2 Control PM10 Control 

LNB with OFA Wet FGD Fabric Filter 

Total Installed Capital Costs (million dollars) $1.00 $6.00 $121.0 

Annualized First-Year Capital Costs $0.95 $0.57 $11.51 First Year Fixed & Variable O&M Costs (million dollars) — $0.62 $1.12 Total First Year Annualized Costs (million dollars) (a) $0.95 $1.19 $12.63 

Power Consumption (MW) — 0.33 2.06 

Annual Power Usage (Million kWh/Yr) — 2.60 16.24 

Permitted Emission Rate (lb/mmBtu) 0.37 0.22 0.02 

Additional Tons of Pollutant Removed per Year over Baseline 1,167 4,084 788 First Year Average Control Cost ($/Ton of Pollutant Removed) 82 290 16,037 NOTE:

(a) First year annualized costs include power consumption costs. 
ADDENDUM 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 

TABLE 4 Scenario B Control Cost Naughton Unit 3 

 NOx Control SO2 Control PM10 Control 

LNB with OFA & 

SCR Wet FGD Fabric Filter 

Total Installed Capital Costs (million dollars) $136.8 $6.00 $121.0 

Annualized First-Year Capital Costs $13.01 $0.57 $11.51 First Year Fixed & Variable O&M Costs (million dollars) $2.67 $0.62 $1.12 

Total First Year Annualized Costs (million dollars) (a) $15.68 $1.19 $12.63 

Power Consumption (MW) 1.99 0.33 2.06 

Annual Power Usage (Million kWh/Yr) 15.69 2.60 16.24 

Permitted Emission Rate (lb/mmBtu) 0.07 0.22 0.02 

Additional Tons of Pollutant Removed per Year over Baseline 5,542 4,084 788 First Year Average Control Cost ($/Ton of Pollutant Removed) 2,830 290 16,037 

NOTE:

(a) First year annualized costs include power consumption costs. 
ADDENDUM 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 

TABLE 5 Incremental Control Costs, Scenario B compared to Scenario A Naughton Unit 3 

 NOx Control SO2 Control PM10 Control 

Incremental Installed Capital Costs (million dollars) $135.8 0 0 

Incremental Annualized First-Year Capital Costs $12.92 0 0 

Incremental First Year Fixed & Variable O&M Costs (million dollars) $2.67 0 0 Incremental First Year Annualized Costs (million dollars) (a) $15.59 0 0 

Incremental Power Consumption (MW) 1.99 0 0 

Incremental Annual Power Usage (Million kWh/Yr) 15.69 0 0 

Incremental Improvement in Emission Rate (lb/mmBtu) 0.30 0 0 

Incremental Tons of Pollutant Removed 4,376 0 0 

Incremental First Year Average Control Cost ($/Ton of Pollutant Removed) 

3,562 0 0 

NOTE:

(a)Incremental first year annualized costs include power consumption costs. 
ADDENDUM TO NAUGHTON UNIT 3 BART REPORT 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 7 

Modeling Results and Least-Cost Envelope Analysis 

CH2M HILL modeled Naughton Unit 3 for two post-control scenarios. The results determine 

the change in deciview based on each alternative at the Class I areas specific to the project. 

The Class I areas potentially affected are Bridger Wilderness and Fitzpatrick Wilderness for 

this unit. 

Modeled Scenarios 

Current operations (baseline) and two alternative control scenarios were modeled to cover the 

range of effectiveness for the combination of the individual NOx, SO2, and PM control 

technologies being evaluated. The modeled scenarios include the following: 

• Baseline: Current operations with LNB, wet sodium FGD, and ESP 

• Scenario A: LNB with OFA, Wet sodium FGD, and Fabric filter 

• Scenario B: Scenario A with SCR 

Summary of Visibility Analysis 

Tables 6 and 7 present a summary of the modeling period (2001–2003) results for each 

scenario and Class I area. 

TABLE 6 

Costs and Visibility Modeling Results as Applicable to Bridger Wilderness 

Naughton Unit 3 

Scenario Controls 

Total First Year 

Annualized 

Cost Highest ΔdV 

98th 

Percentile 

ΔdV 

Maximum 

Annual 

Number of 

Days Above 

0.5 dV 

Baseline Current Operations with FGD 

and ESP 

— 5.657 1.971 66 

Scenario A Scenario A: PacifiCorp 

Committed Controls 

$13,912,688 4.943 1.574 52 

Scenario B Scenario B: PacifiCorp 

Committed Controls and SCR 

$29,499,964 2.488 0.800 26 
ADDENDUM TO NAUGHTON UNIT 3 BART REPORT 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 8 

TABLE 7 

Costs and Visibility Modeling Results as Applicable to Fitzpatrick Wilderness 

Naughton Unit 3 

Scenario Controls 

Total First Year 

Annualized 

Cost Highest ΔdV 

98th 

Percentile 

ΔdV 

Maximum 

Annual 

Number of 

Days Above 

0.5 dV 

Baseline Current Operations with FGD 

and ESP 

— 3.862 0.939 24 

Scenario A Scenario A: PacifiCorp 

Committed Controls 

$13,912,688 3.074 0.737 18 

Scenario B Scenario B: PacifiCorp 

Committed Controls and SCR 

$29,499,964 1.529 0.351 4 

Results 

Tables 8 and 9 present a summary of the costs and modeling results for each scenario and 

Class I area. 

TABLE 8 

Incremental Costs and Incremental Visibility Improvements Relative to Bridger Wilderness 

Naughton Unit 3 

Scenario 

Comparison Controls 

Incremental 

Annualized 

Cost 

(Million$) 

Reduction in 

98th 

Percentile 

maximum 

dV 

Reduction in 

Number of 

Days Above 

0.5 dV 

Cost per dV 

Reduction 

(Million$/dV 

Reduced) 

Cost per Day 

to Achieve a 

Reduction in 

the Days 

above 0.5 dV 

(Million$/Day) 

Scenario A 

Compared to 

Baseline 

Scenario A: 

PacifiCorp 

Committed Controls 

$13.91 0.397 14 $35.04 $0.99 

Scenario B 

Compared to 

Baseline 

Scenario B: 

PacifiCorp 

Committed Controls 

and SCR 

$29.50 1.171 40 $25.19 $0.74 

Scenario B 

Compared To 

Scenario A 

Addition of SCR $15.59 0.774 26 $20.14 $0.60 
ADDENDUM TO NAUGHTON UNIT 3 BART REPORT 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 9 

TABLE 9 

Incremental Costs and Incremental Visibility Improvements Relative to Fitzpatrick Wilderness 

Naughton Unit 3 

Scenario 

Comparison Controls 

Incremental 

Annualized 

Cost 

(Million$) 

Reduction in 

98th 

Percentile 

maximum 

dV 

Reduction in 

Number of 

Days Above 

0.5 dV 

Cost per dV 

Reduction 

(Million$/dV 

Reduced) 

Cost per Day 

to Achieve a 

Reduction in 

the Days 

above 0.5 dV 

(Million$/Day) 

Scenario A 

Compared to 

Baseline 

Scenario A: 

PacifiCorp 

Committed Controls 

$13.91 0.202 6 $68.87 $2.32 

Scenario B 

Compared to 

Baseline 

Scenario B: 

PacifiCorp 

Committed Controls 

and SCR 

$29.50 0.588 20 $50.17 $1.47 

Scenario B 

Compared To 

Scenario A 

Addition of SCR $15.59 0.386 14 $40.38 $1.11 

Least-Cost Envelope Analysis 

The least-cost envelope graphs for Bridger Wilderness are shown in Figures 1 and 2 and for 

Fitzpatrick Wilderness are shown in Figures 3 and 4. 
ADDENDUM TO NAUGHTON UNIT 3 BART REPORT 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 10 

FIGURE 1 

Least Cost Envelope

 PacifiCorp Naughton Unit 3 - Bridger Wilderness

Baseline

Scenario A

Scenario B

$0.0

$5.0

$10.0

$15.0

$20.0

$25.0

$30.0

$35.0

0 5 10 15 20 25 30 35 40 45

Reduction in Days of Exceeding 0.5 dV (days)

Total Annualized Cost (Mil $)

FIGURE 2 

Least Cost Envelope

 PacifiCorp Naughton Unit 3 - Bridger Wilderness

Scenario B

Scenario A

Baseline

$0.0

$5.0

$10.0

$15.0

$20.0

$25.0

$30.0

$35.0

0.00 0.20 0.40 0.60 0.80 1.00 1.20 1.40

98th Percentile Delta-Deciview Reduction (dV)

Total Annualized Cost (Mil $)
ADDENDUM TO NAUGHTON UNIT 3 BART REPORT 

JMS ES032008003SLC\BART_TMS_NAUGHTONUNIT3_FINAL.DOC 11 

FIGURE 3 

Least Cost Envelope

 PacifiCorp Naughton Unit 3 - Fitzpatrick Wilderness

Scenario B

Scenario A

Baseline

$0.0

$5.0

$10.0

$15.0

$20.0

$25.0

$30.0

$35.0

0 5 10 15 20 25

Reduction in Days of Exceeding 0.5 dV (days)

Total Annualized Cost (Mil $)

FIGURE 4 

Least Cost Envelope

 PacifiCorp Naughton Unit 3 - Fitzpatrick Wilderness

Scenario B

Scenario A

Baseline

$0.0

$5.0

$10.0

$15.0

$20.0

$25.0

$30.0

$35.0

0.00 0.10 0.20 0.30 0.40 0.50 0.60 0.70

98th Percentile Delta-Deciview Reduction (dV)

Total Annualized Cost (Mil $)
ATTACHMENT 1 

Complete Economic Analyses 

for Scenarios A and B 
ECONOMIC ANALYSIS SUMMARY - FIRST YEAR COSTS

Naughton 3 Boiler Design: Tangential-Fired PC

TYPE OF EMISSIONS CONTROLS NOx Control 

Technology Label BASE A B C D E 

Current Operation Low NOx Burners with Overfire Air Rotating Overfire Air

Low NOx Burners with 

Overfire Air and NonSelective Catalytic 

Reduction

Low NOx Burners with 

Overfire Air and 

Selective Catalytic 

Reduction

ESP 

ECONOMIC FACTORS

Interest Rate (%) 7.10% 7.10% 7.10% 7.10% 7.10% 7.Discount Rate (%) 7.10% 7.10% 7.10% 7.10% 7.10% 7.Plant Economic Life (Years) 20 20 20 20 20 

CAPITAL INVESTMENT 

Total Installed Capital Costs ($) $0 $1,000,000 $14,747,608 $15,788,530 $136,800,000  FIRST YEAR DEBT SERVICE ($/Yr) $0 $95,128 $1,402,908 $1,501,929 $13,013,486 

FIRST YEAR FIXED O&M Costs ($/Yr)

Operating Labor ($/Yr) $0 $0 $0 $0 $0 Maintenance Material ($/Yr) $0 $0 $48,000 $75,000 $156,000 Maintenance Labor ($/Yr) $0 $0 $72,000 $112,500 $234,000 Administrative Labor ($/Yr) $0 $0 $0 $0 $0  TOTAL FIRST YEAR FIXED O&M COST $0 $0 $120,000 $187,500 $390,000 

FIRST YEAR VARIABLE O&M Costs ($/Yr)

Makeup Water Costs ($/Yr) $0 $0 $0 $0 $0 Reagent Costs ($/Yr) $0 $0 $0 $96,490 $993,460 SCR Catalyst / FF Bag Costs ($/Yr) $0 $0 $0 $0 $501,000 Waste Disposal Costs ($/Yr) $0 $0 $0 $0 $0 Electric Power Costs ($/Yr) $0 $0 $1,762,074 $130,086 $784,458 $886 TOTAL FIRST YEAR VARIABLE O&M Costs ($/Yr) $0 $0 $1,762,074 $226,576 $2,278,918 $886

SUMMARY OF FIRST YEAR COSTS ($/Yr)

First Year Debt Service ($/Yr) $0 $95,128 $1,402,908 $1,501,929 $13,013,486 First Year Fixed O&M Costs ($/Yr) $0 $0 $120,000 $187,500 $390,000 First Year Variable O&M Costs ($/Yr) $0 $0 $1,762,074 $226,576 $2,278,918 $886

Total First Year Costs ($/Yr) $0 $95,128 $3,284,982 $1,916,004 $15,682,404 $886

CONTROL COST COMPARISONS

NOx Technology Comparison

Additional NOx Removed From Base Case (Tons/Yr) 0 1,167 2,480 2,188 5,542

First Year Average Control Cost ($/Ton NOx Removed) $0 $82 $1,325 $876 $2,830

Technology Case Comparison A-BASE B-A C-A D-AIncremental NOx Removed (Tons/Yr) 0 1,167 1,313 1,021 4,376

Incremental Control Cost ($/Ton NOx Removed) $0 $82 $2,430 $1,783 $3,562

SO2 Technology Comparison 82.8% 82

Additional SO2 Removed From Base Case (Tons/Yr) 0 

First Year Average Control Cost ($/Ton SO2 Removed) $0 #D

Technology Case Comparison E-BIncremental SO2 Removed (Tons/Yr) 0 

Incremental Control Cost ($/Ton SO2 Removed) $0 #D

PM Technology Comparison 0.0%Additional PM Removed From Base Case (Tons/Yr) 0 

First Year Average Control Cost ($/Ton PM Removed) $0 #DTechnology Case Comparison E-BIncremental PM Removed (Tons/Yr) 0 

Incremental Control Cost ($/Ton PM Removed) $0 #D

SCENARIO A AND B COMPARISONS

Additional NOx, SO2, & PM Removed From Base Case (Tons/Yr) 0 

First Year Average Control Cost Compared to Base Case ($/Ton Removed) $0 

Incremental Tons Removed - Scenario B vs Scenario A (Tons/Yr) 0 

Incremental Control Costs - Scenario B vs Scenario A ($/Ton Removed) $0 

JMS ES032008003SLC\First Yr Summary\Naughton 3 appendix.xls 
INPUT CALCULATIONS

Naughton 3 Boiler Design: Tangential-Fired PC

PARAMETER Current Operation NOx Control Technologies 

Control TechnologiesNOx Emission Control System LNCFS II LNB Tune Exsisting LNB w/OFA ROFA SNCR Tune Exsisting LNB w/OFA & SCR 

SO2 Emission Control System Wet FGD N/A Wet FGD 

liq

PM Emission Control System ESP ESP 

General Plant Design and Operating Data

Type of Unit PC PC PC PC PC PC PAnnual Power Plant Capacity Factor 90% 90% 90% 90% 90% 90% Annual Operation (Hours/Year) 7,884 7,884 7,884 7,884 7,884 7,884 Net Power Output (kW) 330,000 330,000 330,000 330,000 330,000 330,000 Net Plant Heat Rate (Btu/kW-Hr) 11,212 11,212 11,212 11,212 11,212 11,212 Boiler Heat Input, Measured by Fuel Input (MMBtu/Hr) 3,700 3,700 3,700 3,700 3,700 3,700 Annual Heat Input, Measured by Fuel Input (MMBtu/Year) 29,170,485 29,170,485 29,170,485 29,170,485 29,170,485 29,170,485 Boiler Heat Input, Measured by CEM (MMBtu/Hr) 3,700 3,700 3,700 3,700 3,700 3,700 Annual Heat Input, Measured by CEM (MMBtu/Year) 29,170,800 29,170,800 29,170,800 29,170,800 29,170,800 29,170,800 

Plant Fuel Source

Boiler Fuel Source Kemmerer Mine Kemmerer Mine Kemmerer Mine Kemmerer Mine Kemmerer Mine Kemmerer Mine KemmeCoal Heating Value (Btu/Lb) 9,950 9,950 9,950 9,950 9,950 9,950 Coal Sulfur Content (wt.%) 1.45% 1.45% 1.45% 1.45% 1.45% 1.45% Coal Ash Content (wt.%) 5.50% 5.50% 5.50% 5.50% 5.50% 5.50% Coal Flow Rate (Lb/Hr) 371,855 371,855 371,855 371,855 371,855 371,855 Coal Consumed (Ton/Yr) 1,465,853 1,465,853 1,465,853 1,465,853 1,465,853 1,465,853 

Nitrogen Oxide Emissions

NOx Emission Rate (Lb/MMBtu) 0.45 0.37 0.28 0.30 0.07 

NOx Emission Rate (Lb/Hr) 1,665 1,369 1,036 1,110 259 

NOx Emission Rate (Lb Moles/Hr) 55.48 45.62 34.52 36.99 8.63 NOx Emission Rate (Ton/Yr) 6,563 5,397 4,084 4,376 1,021 Add'l NOx Removed from Current Operations (Lb/Hr) 0 296 629 555 1,406 

Add'l NOx Removed from Current Operations (Ton/Yr) 0 1,167 2,480 2,188 5,542 

Sulfur Dioxide Emissions

Uncontrolled SO2 (Lb/MMBtu) 2.91 2.91 

Uncontrolled SO2 (Lb/Hr) 10,773 10,773 

Uncontrolled SO2 (Lb Moles/Hr) 168.16 168.16 Uncontrolled SO2 (Tons/Yr) 42,468 42,468 Controlled SO2 Emission Rate (Lb/MMBtu) 0.50 0.50 

SO2 Removal Efficiency (%) 82.8% 82.8% 

Controlled SO2 Emissions (Lb/Hr) 1,850 1,850 

Controlled SO2 Emissions (Ton/Yr) 7,293 7,293 SO2 Removed (Lb/Hr) 8,923 8,923 

SO2 Removed (Ton/Yr) 35,175 35,175 Add'l SO2 Removed from Current Operations (Lb/Hr) 0 0 

Add'l SO2 Removed from Current Operations (Ton/Yr) 0 0 

Particulate Matter Emissions

Uncontrolled Fly Ash (Lb/Hr) 16,362 16,362 Uncontrolled Fly Ash (Lb/MMBtu) 4.422 4.422 Uncontrolled Fly Ash (Tons/Yr) 64,498 64,498 Controlled Fly Ash Emission Rate (Lb/MMBtu) 0.094 0.094 Controlled Fly Ash Removal Efficiency (%) 97.9% 97.9% Controlled Fly Ash Emissions (Lb/Hr) 348 348 Controlled Fly Ash Emissions (Ton/Yr) 1,371 1,371 Fly Ash Removed (Lb/Hr) 16,014 16,014 Fly Ash Removed (Ton/Yr) 63,127 63,127 Add'l Ash Removed from Current Operation (Lb/Hr) 0 0 Add'l Ash Removed from Current Operation (Ton/Yr) 0 0 

Economic Factors

Interest Rate (%) 7.10% 7.10% 7.10% 7.10% 7.10% 7.10% Discount Rate (%) 7.10% 7.10% 7.10% 7.10% 7.10% 7.10% Plant Economic Life (Years) 20 20 20 20 20 20 

SO2 Control T

JMS ES032008003SLC\Tech Calcs\Naughton 3 appendix.xls 
INPUT CALCULATIONS

Naughton 3 Boiler Design: Tangential-Fired PC

PARAMETER Current Operation NOx Control Technologies 

Control TechnologiesNOx Emission Control System LNCFS II LNB Tune Exsisting LNB w/OFA ROFA SNCR Tune Exsisting LNB w/OFA & SCR 

SO2 Emission Control System Wet FGD N/A Wet FGD 

liq

PM Emission Control System ESP ESP 

SO2 Control T

Installed Capital Costs

NOx Emission Control System ($2006) $1,000,000 $14,747,608 $15,788,530 $136,800,000 

SO2 Emission Control System ($2006) $0 

PM Emission Control System ($2006) $0 Total Emission Control System Capital Costs ($2006) $1,000,000 $14,747,608 $15,788,530 $136,800,000 $0 NOx Emission Control System ($/kW) $3 $45 $48 $415 

SO2 Emission Control System ($/kW) 

PM Emission Control System ($/kW) Total Emission Control Capital Costs ($/kW) $3 $45 $48 $415 

Fixed Operating & Maintenance Costs

Operating Labor ($) $0 $0 $0 $0 $0 Maintenance Material ($) $0 $48,000 $75,000 $156,000 $0 Maintenance Labor ($) $0 $72,000 $112,500 $234,000 $0 Administrative Labor ($) $0 $0 $0 $0 $0 Total 1st Fixed Year O&M Cost ($) $0 $120,000 $187,500 $390,000 $0 Annual Fixed O&M Cost Escalation Rate (%) 2.00% 2.00% 2.00% 2.00% 2.00% Levelized Fixed O&M Cost ($/Yr) $0 $142,260 $222,282 $462,346 $0 

Variable Operating & Maintenance Costs

Water CostMakeup Water Usage (gpm) 0 0 0 0 0 Unit Price ($/1000 gallons) $1.22 $1.22 $1.22 $1.22 $1.22 First Year Water Cost ($) $0 $0 $0 $0 $0 Annual Water Cost Escalation Rate (%) 2.00% 2.00% 2.00% 2.00% 2.00% Levelized Water Costs ($/Yr) $0 $0 $0 $0 $0 Reagent CostType of Reagent None None Urea Anhydrous NH3 Waste Unit Cost ($/Ton) $0.00 $370.00 $400.00 $91.25 Unit Cost ($/Lb) $0.000 $0.185 $0.200 $0.046 Molar Stoichiometry 0.00 0.45 1.00 1.40 Reagent Purity (Wt.%) 100% 100% 100% 90% Reagent Usage (Lb/Hr) 66 630 0 First Year Reagent Cost ($) $0 $96,490 $993,460 $0 Annual Reagent Cost Escalation Rate (%) 2.00% 2.00% 2.00% 2.00% Levelized Reagent Costs ($/Yr) $114,389 $1,177,749 $0 SCR Catalyst / Fabric Filter Bag Replacement CostMaterial Replaced SCR Catalyst BaAnnual SCR Catalyst (m3) / No. FF Bags 167 SCR Catalyst ($/m3) / Bag Cost ($/ea.) $3,000 First Year SCR Catalyst / Bag Replacement Cost ($) $501,000 Annual SCR Catalyst / Bag Cost Escalation Rate (%) 2.00% Levelized Catalyst/Fabric Fitler Bag Costs ($/Yr) $593,937 FGD Waste Disposal CostFGD Solid Waste Disposal Rate, Dry (Lb/Hr) 0 FGD Waste Disposal Unit Cost ($/Dry Ton) $24.33 First Year FGD Waste Disposal Cost ($) $0 Annual Waste Disposal Cost Esc. Rate (%) 2.00% Levelized Waste Disposal Costs ($/Yr) $0 Auxiliary Power CostAuxiliary Power Requirement (MW) 0.00 4.47 0.33 1.99 2.25 Auxiliary Power Requirement (% of Plant Output) 0.00% 1.35% 0.10% 0.60% 0.68% Auxilliary Power Useage (MWh) 0 35,241 2,602 15,689 17,739 Unit Cost ($2006/MW-Hr) $50.00 $50.00 $50.00 $50.00 $50.00 First Year Auxiliary Power Cost ($) $0 $1,762,074 $130,086 $784,458 $886,950 Annual Power Cost Escalation Rate (%) 2.00% 2.00% 2.00% 2.00% 2.00% Levelized Auxilliary Power Costs ($/Yr) $0 $2,088,944 $154,217 $929,977 $1,051,482 

JMS ES032008003SLC\Tech Calcs\Naughton 3 appendix.xls