,( ­ ... ... ,," ...~Il$·•• .. ~" -.•.

"-. •• &',. - ?";.
 l;/· - \";\ STATE OF UTAH
 

l:i 

~O\ :c:l	 l~~ DEPARTMENT DF HEALTH	 NORMAN H. BANGERTER. Gover _ -,

• ',p.o l~' '\~'\. ,t" t'	 SUZANNE DANDOY. M.D.. M.P.H.. EXECUTIVE DI~EC. ~""--. ,,' 4-,' -_ ".--_ _".. ' ,I

•.... lSI','" "''''''11'# 

FEB? 0 1998 

533-6108 

AliI Larruni
 

United states Air Force
 

Air Force Regional Civil Engineer
 

630 Sansom Street, Room 1316
 

San Francisco, California 94111-2278
 

RE:	 Approval Order for Industrial 

wastewater Treatment Facility 

Davis COlnty CDS A-I 

Dear Mr. Lammi: 

The above referenced project ·has been reviewed by the Executive Secretary, 

utah Air Conservation Committee and found to be consistent with the 

requirements of the Utah Air Conservation Regulations (UACR) and the utah Air 

Conservation Act. A 30 day public comment period \'tas held and all comments 

received were evaluated. The conditions of this approval order reflect any 

changes to the Executive Secretary's original determination which resulted 

from the evaluation of the comments received. This air quality approval 

order authorizes the project with the following conditions: 

1. Hill Air Force Base shall install the proposed industrial wastewater 

treatment plant according to the information submitted to the Executive 

Secretary in the notice of intent dated October 1, 1985. 

2. Total emissions of reactive and non-reactive volatile organic 

compounds shall be reported to the Executive Secretary annually. 

3. All installations and facilities authorized by this approval order 

shall be maintained and operated in proper condition. 

4. The Executive Secretary shall be notified upon start-up of the 

installation, as an initial compliance inspection is required. 

5. Plant through-put of reactive VOC shall not exceed 12 tons/year 

without prior approval of the Executive Secretary in accordance with 

Section 3.1, UACR. 

4.2.4-969 

KENNETH L. ALKEMA. DIRECTOR. DIVISION OF ENVIRONMENTAL HEALTH 

3266 STATE OFFICE BUILDING. P.O. BOX 4550 • SALT LAKE CITY. UTAH 84145·0500 • (801 J 533c6121 

AN EQUAL OPPORTUNITY EMPLOYER 
-.

;.­

Page 2 Unit~ states Air Force 

Approval Order/LRM 

The fee for issuing this approval order is $245.14. The amount (see enclosure 

for breakdown of costs) is payable to the utah Department of Health, sent to 

the Executive Secretary, utah Air Conservation Committee, 2870 Connor Street, 

salt Lake City, Utah 84109 and is due within 30 days after receipt of this 

approval order. 

Sincerely, 

Br61t C. Bradford 

Executive Secretary 

utah Air Conservation Committee 

LRM/jg tl 

0233A 

CC:	 EPA Region VIII (Norm Huey) Davis County Health Department 

Enclosure 

.­

4.2.4-970
 
-


APPROVAL ORDER FEE 

Review Engineer - total hours 

Modeler - total hours 

computer Time - total hours 

Notice To Paper -

Travel - total miles 

Filing Fee -

8 ( $22. 08/hr ) = 

( $17.94/hr ) = 

( $ 5.001hr ) = 

= 

($ 0.23/mile) = 

= 

Total = 

$ 

$ 

$ 

$ 

$ 

$ 

$ 

176.64 

18.50 

50.00 

245.14 

---, 

LRM/jg t\ 

0401Q 

Phil Lammi 

United states Air Force 

Approval Order for Industrial wastewater Treatment Facility 

4.2.4-971
 
---------- ----

-------- ----

------------------

-~"------'-+~---'~---

-!""":--~~-f--'-----

UTAH BUREAU OF AIR QUALITY
 

NEw/MODIFIED SOURCE PLAN REVIEW FOR:
 

Phil Lammi 

United States Air Force 

Air Force Regional Civil Engineer 

630 Sansom Street, Room l316 

san Francisco, California 94111-2278 

RE:	 Industrial Wastewater Treatment 

Facility 

Davis County CDS' A-l 

Engineer: Lynn Menlove
 

Date: December 2, 1985
 

Notice of Intent datea: 10-2-85; Infu. 10-15-85
 

Plant contact: Darrell Hunt, Radian Corp.
 

Phone number: (916) 362-5332
 

Plant location: Hill Air Force Base
 

Filing Fee: = $50.00
 

Review Engineer total hours 8 ($22.08/hr) = $176.64
 

Modeler total hours ($17.94/hr) =
 

Computer time total hours ($5.00) =
 

Notice to paper $18.50
 

Travel total miles -- ($0. 21/mile) = _
 

Total	 $245.14 

Approved by section Manager 

App!'oved by Executive Secretary' 

4.2.4-972
 
Page 2	 -. 

United states Air Force 

Engineering Review/LRM 

I. Description 0 f Proposal 

A.	 History 

Hill Farce Base is planning to construct an industrial wastewater 

treatment facility for their existing and future effluent from the Base. 

B.	 Process 

The facility will be stripping the reactive and non-reacative 

hydrocarbons from the wastewater. The waste HC stripped currently 

enters the atmosphere so this is not a change of HC emissions for 

existing rates of effluent. The increased effluent for Building 220 

expansion will be included in this review. 

75% of the HC stripped from the water is non-reactive as defined by UACR . Section 3.1.7.f. 

The	 wastewater facility follows an existing secondary clarifier. 

The system is closed to the atmosphere except the air stripping tower .­ where the HC is removed by a cOUlter current flow of air contacting 

water in a packed tower. See Figure 1. 

The	 air stripper is expected to remove 99.9% of the Vcr. from the water. 

C.	 Rates of flow
 

water through-put 461 gal/min average
 

vcr. 

Reactive = 5.6 ton/yr
 

Non-reactive =18.4 ton/yr
 

Air Exhaust 7500 acfm
 

Time of Operation
 

24 hrs/day
 365 days/year
 

Construction scheduled 

Late 1986 Completion 

4.2.4-973 
Page 3 r United states Air Force 

Engineering Review/LRM 

II.	 BACT 

Application of VOC control equipment for this source with an emission of 

5.6 tons of reactive VOC per year is not reasonable.
 

I recommend no control equipment with the following limitations:
 

1. Annual reporting of reactive and non-reactive VOC emissions. 

2. Reactive VOC shall not exceed 12 ton/yr. 

III.	 Applicable Regulations 

UACR 3.1.1 Engineering review
 

UACR 3.l.7.f Annual emission report of non-reactive VOC.
 

IV. Recommended Approval Order Conditions 

r 1. Hill Air Force Base shall install the proposed industrial wastewater 

treatment plant according to the information submitted to the Executive 

Secretary in the notice of intent dated October 1, 1985. 

2. Total emissions of reactive and non-reactive volatile organic 

compomds shall be reported to the Executive Secretary annually. 

3. All installations and facilities authorized by this approval order 

shall be maintained and operated in proper condition. 

4. The Executive Secretary shall be notified upon start-up of the 

installation, as an initial compliance inspection is required. 

5. Plant through-put of reactive VOC shall not exceed 12 tons/year without prior approval of the Executive Secretary in accordance with 

Section 3.1, UACR. 

LRM/jg 

0234A 

4.2.4-974
 
----

WASliwAlflll 

'uul·S .... " 

U(O"n.~, 'no~ ~~~]0

C"""'l~ t· 

. 

-~

I p_: 

co,.,e 1'0", 

. "uu" 

."C"w"'It

......".. £ 

DaC"VfASII 

Iv..... 

Radian Corp., lUlU."" _..;::..;;;;~::.I .... 14""If". 1 •••• ••__ 

f>­

tv 

Figure End of Pipe Air Stripping/Cnrbon Adsorption Treatment Process. 1. I 

\0 

-....l 

VI 

OU ,otln••" t;\ 

~A-£\r

----to-! I .~ -~­

... o "li'ftll'rlttO

IU'"'III -,... -~-A-tijt r ••:r:-.....:;.~.

::.:,.:~:.::: .:t.;.... ::,,- ':..; ,... I~£--~ 1 . 1..- ---"'r:--" o Vliasrl flJ---I t?r-:(J_tijl ,uu,·~~~r I ''''

E~ I ttd,nlC)(1Io - i ""flu,. 

-t4- r.. _&_ -~rr­ ••II""lrr, ...... 0

\:J - 1~1

L hr r"'i- 8 

Q 11'111 Sw.fCuw.". 

v:..::;J "'(;'II'U,"" "'"'''' 

O '''C''''',I''''',' lOIC,U"l"At.Oh''''U'k' I" Sift 

M--- I 

\~. (J .- .. 'at "oJ 

. raN 

~~ U) .. ,-.,." 

<,. "nl! • " '_.. I~.:I
 1 I 'h
 

-,.J.. <l P t1 

'\ 6 

--\. 

."")

<;> 

'--~

1) 

'y 

'1--.., 

N 

\: 

1:),0 

-p 

. . . P_. ... · .__--..::.=..z...:..·-I/;." 

~,.-_._-­ }.---- _.--- -­ l: --....... --:---..-,.---···--···r·- '''---'. "'-~' . ..-.--t ·'\1:.·-.-.. ··.4,....,.~WIE"Jt .. ..•. ----._..__.-.-

III 
Industrial Wastewater
 

Treatment Facility - HAFB
 

Page 3
 

1. Annual reporting of reactive 2nd non-reactive VOC emissions. 

2. Reactive VOC shall not exceed 12 ton/yr. 

III. Applicable Regulations 

UACR 3.1.1 Engineering review 

UACR 3.1.7. f Annual emission report of non-reactivex v () C 

IV. Recommended Approval Order Conditions 

1. Hill Air Force Base shall install the proposed industrial 

wastewater treatment plant according to the information 

submitted to the Executive Secretary in the notice of intent 

dated October 1, 1985. 

2. Total emissior~s of reactive ana non-reactive volatile 

organic compounds shall be reported to the Excecutive Secretary 

annually. 

3. All installations and facilities authorized Dy this approval .,- order shall be maintained and operated in proper condition . 

4. The Executive Secretary shall be notifiec ~pon start-up of 

the installation, as an initial compliance inspection is 

required. 

5. Plant through-put of reactive VOC shall not exceed 

12 tons/year without prior approval of the Executive Secretary 

in accordance with Section 3.1, UACR. 

a . construction" shall be _Jbrty~JYlunDJe~1~§~,~19:98S=7~.;----- ... 

0062(;) 

4.2.4-976
 

--

c-(
 

--------------------------------------;--­

/- . 

0' /firl 

il 

r'C'./-/ 

, / ,- c:-"'; 2Cf h v/ ,Ie! 7 r/CXjS /1/'.//", o L.- "~/~ /j I // ./ . v 

87{O ~v//'jl/

Vo c =- t i/Vi:;/ /
 

; j r U- / I J 1/ . 0 3r / I /() / ) 7'/ J. / V ..I ',­ = _--c_.'1--..:..~7!/-.L~~/ _;'v_·i -_-._'_fl_)--,-:.~:....-/_!)_('1_/_(;_'_i_";-;'/'...:.../_?h_iv_._'""'-=J~C n7/:"-"

/OCK"7'/10 . Laaok/Tnv-,
 

:= &, 2 -rov/flr
 . , , / 

I l -7-/ '-il 7iil5 71/~t';'v -, I,' - , ,.. '-, I i --. 'J ,I· I ,': ­

~L"'; k~vS 

4.2.4-978
 
STATE OF UTAH 

DEPARTMENT OF HEALTH ,\JO~MAN H 8ANGE~TER GO\ 

SUZANNE DANOOY. MOM P"i. EXECUTivE OIi=<ECTOi=< 

OCT 7 1985 

533-6108 

Phil Larrmi 

Lhited states Air Force 

Air Force Regional Civil Engineer 

630 Sanson Street, Room 1316 

San Francisco, California 94111-2278 

RE: Receipt of f'btice of Intent 

[ear Mr. Lammi: 

This letter ac~owledges receipt of your applicaticn for an air quality 

appmval 0 rrer for a Ind.Jstrial Waste'fB. te r Treatment Facility. Your notice of 

intent dated October 1, 1985, was recehed October 2, 1985. Evaluation of the 

applicaticn has begLn. If any additional info nmtion is necessary, a detailed 

request will be sent within 30 cays. Please note the utah Air Ccnservation 

Reg.Jlations (UACR) Section 3.1.1, requires an approval order be issued by the 

Executive Secretary prior to initiaticn of construction or modification. 

Since rely, 

~C/'L /Z', /J~( ·L/C~ 'C-­

Lynn R. Menlo ve 

Environmental Health Engineer 

Bureau of Air G;uali ty 

LRv1/jg 

9430Q 

4.2.4-979 

KENNETH L. ALKEMA. OIi=<ECTOi=< • DIVISION OF ENVIi=<ONMENTAL HEAL TH 

3266 ST t. TE OFFICE BUILDING • POBOX 45500 • SALT LAKE CITY. UTAH 8414!'i.n'inr: • :..n,1 ".,.,.;: 1:::.