NUREG-0040 

Vol. 23, No. 4

Licensee Contractor and 

Vendor Inspection 

Status Report 

Quarterly Report 

October - December 1999 

U.S. Nuclear Regulatory Commission 

Office Nuclear Reactor Regulation 

Washington, DC 20555-0001
AVAILABILITY OF REFERENCE MATERIALS 

IN NRC PUBLICATIONS

NRC Reference Material 

As of November 1999, you may electronically 

access NUREG-series publications and other 

NRC records at NRC's Public Electronic Reading 

Room at www.nrc.gov/NRC/ADAMS/index.html. 

Publicly released records include, to name a few, 

NUREG-series publications; Federal Register 

notices; applicant, licensee, and vendor 

documents and correspondence; NRC 

correspondence and internal memoranda; 

bulletins and information notices; inspection and 

investigative reports; licensee event reports; and 

Commission papers and their attachments. 

NRC publications in the NUREG series, NRC 

regulations, and Title 10, Energy, in the Code of 

Federal Regulations may also be purchased from 

one of these two sources. 

1. The Superintendent of Documents 

U.S. Government Printing Office 

P. O. Box 37082 

Washington, DC 20402-9328 

www.access.gpo.gov/sudocs 

202-512-1800 

2. The National Technical Information Service 

Springfield, VA 22161-0002 

www.ntis.gov 

1-800-553-6847 or, locally, 703-605-6000 

A single copy of each NRC draft report for 

comment is available free, to the extent of 

supply, upon written request as follows: 

Address: Office of the Chief Information Officer, 

Reproduction and Distribution 

Services Section 

U.S. Nuclear Regulatory Commission 

Washington, DC 20555-0001 

E-mail: DISTRIBUTION@nrc.gov 

Facsimile: 301-415-2289 

Some publications in the NUREG series that are 

posted at NRC's Web site address 

www.nrc.gov/NRC/NUREGS/indexnum.html 

are updated regularly and may differ from the last 

printed version.

Non-NRC Reference Material 

Documents available from public and special 

technical libraries include all open literature 

items, such as books, journal articles, and 

transactions, Federal Register notices, Federal 

and State legislation, and congressional reports. 

Such documents as theses, dissertations, foreign 

reports and translations, and non-NRC 

conference proceedings may be purchased from 

their sponsoring organization. 

Copies of industry codes and standards used in a 

substantive manner in the NRC regulatory 

process are maintained at

The NRC Technical Library 

Two White Flint North 

11545 Rockville Pike 

Rockville, MD 20852-2738 

These standards are available in the library for 

reference use by the public. Codes and 

standards are usually copyrighted and may be 

purchased from the originating organization or, if 

they are American National Standards, from

American National Standards Institute 

11 West 4 2 0" Street 

New York, NY 10036-8002 

www.ansi.org 

212-642-4900

A year's subscription of this publication consists of four quarterly issues.

Th'e "N-U.REG series comprises .(1) technical 

and administrative reports and tbooks prepared 

by the staff (NUREG-ýX)OO( oiriagency 

contractors (NUREG/CR-XXXX.):, :(2) 

proceedings of conferences 

(NUREG/CP-XXXX), (3) reports resulting from 

international agreements (NUREG/IA-XXXX), 

(4) brochures (NUREG/BR-XXXX), and (5) 

compilations of legal decisions and orders of 

the Commission and Atomic and Safety 

Licensing Boards and of Directors',decisions 

under Section 2.206 of NRC's regulations 

(NUREG-0750).

I Illi
NUREG-0040 

Vol. 23, No. 4 

Licensee Contractor and 

Vendor Inspection 

Status Report 

Quarterly Report 

October - December 1999 

Manuscript Completed: June 2000 

Date Published: June 2000 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation 

U.S. Nuclear Regulatory Commission 

Washington, DC 20555-0001
ABSTRACT

This periodical covers the results of inspections performed between October 1999 and 

December 1999 by the NRC's Quality Assurance, Vendor Inspection, Maintenance and 

Allegations Branch that have been distributed to the inspected organizations.

iii
CONTENTS 

PAGE 

A b stra ct ....................................................................................................................... iii 

In tro d u ctio n ................................................................................................................... v ii 

Inspection R eports ................................................................................................... 1 

ABB Power T&D Company (99901256/1999201) ............................. 2 

Florence, SC 

Anatec International, Incorporated (99901342/1999201) ........................... 30 

San Clemente, CA 

GE Nuclear Energy (99900003/1999202) ........................... 47 

Wilmington, NC 

Tennessee Valley Authority (99901341/1999201) ........................... 61 

Chattanooga, TN 

Select Generic Correspondence on the Adequacy of Vendor ................................ 77 

Audits and the Quality of Vendor Products

V
INTRODUCTION

A fundamental premise of the U. S. Nuclear Regulatory Commission (NRC) licensing and 

inspection program is that licensees are responsible for the proper construction and safe and 

efficient operation of their nuclear power plants. The Federal government and nuclear industry 

have established a system for the inspection of commercial nuclear facilities to provide for 

multiple levels of inspection and verification. Each licensee, contractor, and vendor participates 

in a quality verification process in compliance with requirements prescribed by the NRC's rules 

and regulations (Title 10 of the Code of Federal Regulations). The NRC does inspections to 

oversee the commercial nuclear industry to determine whether its requirements are being met 

by licensees and their contractors, while the major inspection effort is performed by the industry 

within the framework of quality verification programs. 

The licensee is responsible for developing and maintaining a detailed quality assurance (QA) 

plan with implementing procedures pursuant to 10 CFR Part 50. Through a system of planned 

and periodic audits and inspections, the licensee is responsible for ensuring that suppliers, 

contractors and vendors also have suitable and appropriate quality programs that meet NRC 

requirements, guides, codes, and standards. 

The NRC reviews and inspects nuclear steam system suppliers (NSSSs), architect engineering 

(AE) firms, suppliers of products and services, independent testing laboratories performing 

equipment qualification tests, and holders of NRC construction permits and operating licenses in 

vendor-related areas. These inspections are done to ensure that the root causes of reported 

vendor-related problems are determined and appropriate corrective actions are developed. The 

inspections also review vendors to verify conformance with applicable NRC and industry quality 

requirements, to verify oversight of their vendors, and coordination between licensees and 

vendors. 

The NRC does inspections to verify the quality and suitability of vendor products, licensee

vendor interface, environmental qualification of equipment, and review of equipment problems 

found during operation and their corrective action. When nonconformances with NRC 

requirements and regulations are found, the inspected organization is required to take 

appropriate corrective action and to institute preventive measures to preclude recurrence. 

When generic implications are found, NRC ensures that affected licensees are informed through 

vendor reporting or by NRC generic correspondence such as information notices and bulletins.

vii
This quarterly report contains copies of all vendor inspection reports issued during the calendar 

quarter for which it is published. Each vendor inspection report lists the nuclear facilities 

inspected. This information will also alert affected regional offices to any significant problem 

areas that may require special attention. This report lists selected bulletins, generic letters, and 

information notices, and include copies of other pertinent correspondence involving vendor 

issues. 

viii

I II 1
INSPECTION REPORTS

-1-
C**k REc,& 

UNITED STATES 

NUCLEAR REGULATORY COMMISSION 

WASHINGTON, D.C. 20555-0001 

Noverber 8, 1999 

Mr. Jon S. Rennie, Plant Manager 

ABB Power T&D Company 

North America Distribution Switchgear Group 

Circuit Breaker Division 

2300 Mechanicsville Road 

P.O. Box 100524 

Florence, SC 29501-0524 

SUBJECT: NOTICE OF NONCONFORMANCE AND NRC INSPECTION REPORT NO. 

99901256/1999201 

Dear Mr. Rennie: 

On September 27 through 30, 1999, NRC inspectors K. Naidu, S. Alexander, of this office, R. 

Bhatia of NRC Region I, and P. Fillion and N. Merriweather of NRC Region II, conducted an 

inspection at your facility. The inspection was to review ABB T&D's quality assurance program 

(and its implementation) intended to meet Appendix B to Part 50 of Title 10 of the Code of 

Federal Regulations (10 CFR Part 50) in support of your supply of Type 5HK250 and K-Line 

circuit breakers to American Electric Power Company's D.C. Cook Nuclear Generating Plant; 

supply of spare and replacement parts to ABB Service Company, Cleveland, Ohio, and also 

directly to D.C. Cook in support of circuit breaker refurbishment being performed on site by 

personnel from the ABB Service Company shops in Charlotte (Matthews), North Carolina and 

Cleveland, Ohio; and supply of Type VHK(R) modular assemblies to the ABB Service Company 

Product Development Center in Cleveland. The inspectors also reviewed your program and its 

implementation established to meet the requirements of 10 CFR Part 21. 

During this inspection, the NRC inspectors identified instances in which the implementation of 

your quality assurance program failed to meet certain NRC requirements. These instances 

may have contributed to deficiencies identified at D.C. Cook during receipt inspections of Class 

1 E circuit breakers you supplied and also resulted in inadequate corrective action for a 

previously cited violation. The specific nonconformances are cited in the enclosed Notice of 

Nonconformance and the details are discussed in the enclosed report. You are requested to 

provide us within 30 days from the date of this letter a written statement in accordance with the 

instructions in the enclosed Notice of Nonconformance. 

In reviewing ABB's 10 CFR Part 21 program, the inspectors identified that certain records of 

evaluations and correspondence with licensees or affected purchasers required by Part 21 

were not included in the documentation submitted to the inspectors for review and represented 

as being complete for the last five years. Also, not all of the notifications in the files submitted 

for review contained all of the information required by Part 21. These apparent deficiencies 

-2-

IIIii
Mr. Jon S. Rennie

may constitute minor violations of 10 CFR Part 21, pending your ability to produce the missing 

records and more complete correspondence. Therefore they were cited as Unresolved Items in 

the enclosed report. 

In accordance with 10 CFR Part 2.790 of the NRC "Rules of Practice," a copy of this letter and 

its enclosures and your response will be placed in the NRC's Public Document Room (PDR). 

To the extent possible, your response should not include personal, private, proprietary or 

safeguards information so that your response can be placed in the PDR without redaction. 

However, should you find it necessary to include such information, you should clearly identify 

that which you desire not be placed in the PDR and provide the justification for withholding from 

public disclosure as delineated in 10 CFR 2.790. 

The responses requested by this letter and the enclosed Notice of Nonconformance are not 

subject to the clearance procedures of Office of Management and Budget as required by the 

Paperwork Reduction Act of 1980, Public Law No. 96-511. 

Should you have any questions concerning this inspection, please contact Mr. Kamal Naidu at 

301-415-2980/krn@nrc.gov or Mr. Stephen Alexander at 301-415-2995/sda@nrc.gov. 

Sincerely, 

Theodore R. Quay, Chief 

Quality Assurance, Vendor Inspection, 

Maintenance and Allegations Branch 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation 

Enclosures: 1. Notice of Nonconformance 

2. Inspection Report No. 99901256/1999201

-3-

-2-
NOTICE OF NONCONFORMANCE

ABB Power T&D Company, Circuit Breaker Division Docket No. 99901256 

Florence, South Carolina Report No. 1999201 

Based on the results of the Nuclear Regulatory Commission inspection conducted September 

27 through 30, 1999, of activities supporting the manufacture of low and medium-voltage power 

circuit breakers, vacuum modular assemblies, and spare and replacement parts, it appears that 

certain of your activities were not conducted in accordance with NRC requirements. 

A. Criterion Il, "Design Control," of 10 CFR Part 50, Appendix B, states, in part, that design 

control measures shall include verifying the adequacy of design, including design 

reviews and/or a suitable testing program, that the verification must be performed by 

individuals or groups other than those who performed the original design, that design 

control measures shall be applied to delineation of acceptance criteria for inspections 

and tests, and that design changes shall be subject to design control measures 

commensurate with those applied to the original design and be approved by the 

organization that performed the original design. 

Criterion V, "Instructions, Procedures and Drawings," of 10 CFR Part 50, Appendix B, 

states, in part, "Activities affecting quality shall be prescribed by documented 

instructions, procedures or drawings of a type appropriate to the circumstances, and 

shall be accomplished in accordance with these instructions, procedures or drawings. 

Instructions, procedures or drawings shall include appropriate quantitative or qualitative 

acceptance criteria for determining that important activities have been satisfactorily 

accomplished." 

Contrary to the above, ABB circumvented established design control measures by 

instituting a change to the specification for the control device gap for Type 5HK250 

circuit breakers, which gap is defined in ABB Factory Specification TD-6931, without 

benefit of required design reviews, verification and approvals. The change was 

implemented without changing the factory specification in accordance with ABB 

engineering change procedures intended to implement design control measures. 

(99901256/1999201-03) 

B. Criterion XVI, "Corrective Action," of 10 CFR Part 50, Appendix B, states, in part, that 

measures shall be established to assure that conditions adverse to quality such as 

failures, malfunctions, deficiencies, deviations, defective material and equipment, and 

nonconformances are promptly identified and corrected. 

Contrary to the above, ABB failed to ensure that adequate corrective action for a 

violation of 10 CFR Part 21, cited in the previous NRC inspection in that the posting 

required by 10 CFR 21.6 had been incomplete until September 27, 1999, and ABB had 

failed to obtain, or subscribe to, or maintain a subscription to NRC Publication NUREG

0040, that ABB committed to as part of its corrective action for the previous violation 

(99901256/1999201-04). 

Enclosure 1 

-4-

I I~
Please provide a written statement or explanation to the U.S. Nuclear Regulatory Commission, 

ATTN: Document Control Desk, Washington, D.C. 20555, with a copy to the Chief, Quality 

Assurance, Vendor Inspection, Maiptenance and Allegations Branch, Division of Inspection 

Program Management, Office of Nuclear Reactor Regulation, within 30 days of the date of the 

letter transmitting this Notice of Nonconformance. This reply should be clearly marked as a 

"Reply to a Notice of Nonconformance" and should include for each nonconformance: (1) a 

description of steps that have been or will be taken to correct these items; (2) a description of 

steps that have been or will be taken to prevent recurrence; and (3) the dates your corrective 

actions and preventive measures were or will be completed. 

Issued this, the 8thday of November, 1999 

at Rockville, Maryland

2 Enclosure 1

-5-
U. S. NUCLEAR REGULATORY COMMISSION 

OFFICE OF NUCLEAR REACTOR REGULATION

Report No.: 99901256/1999201

ABB Power T&D Company, Inc. 

North America Distribution Switchgear Group 

2300 Mechanicsville Road 

P.O. Box 100524 

Florence, SC 29501-0524

Contact Address:

Telephone:

Jon S. Rennie, Plant Manager

(843) 665-4144

Nuclear Industry 

Activity: 

Dates of Inspection: 

Inspectors: 

Approved by:

Manufacture of medium-voltage Type HK and vacuum circuit 

breakers and 600-V K-Line circuit breakers 

September 27-30, 1999 

Kamalakar R. Naidu, Senior Reactor Engineer, NRR 

Stephen D. Alexander, Reactor Engineer, NRR 

Ram S. Bhatia, Reactor Engineer, RI 

Paul J. Fillion, Reactor Engineer, RII 

Norman Merriweather, Reactor Engineer, RII 

Richard P. Correia, Chief 

Reliability and Maintenance Section, IQMB 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation

Enclosure 2

-6-

I I~
1. INSPECTION SUMMARY

On September 27-30, 1999, the NRC conducted an inspection at Asea Brown Boveri (ABB) 

Power Transmission & Distribution (T&D) Company, Inc., Distribution Systems Division, located 

in Florence, South Carolina, where ABB manufactures medium-voltage Type HK circuit 

breakers and vacuum circuit breakers and 600-volt-rated K-Line (metal-enclosed) circuit 

breakers. The inspection evaluated the ABB quality assurance (QA) program and its 

implementation in the design, qualification, and manufacture of these breakers and its program 

for implementation of 10 CFR Part 21. As part of the NRC circuit breaker task action plan, this 

inspection followed up on issues identified during an inspection at the Donald C. Cook Nuclear 

Generating Station (D.C. Cook) where ABB Service Company was performing breaker 

refurbishment services. Also, the inspection followed up on an inspection of ABB/Combustion 

Engineering, Nuclear Power (CENP), Windsor, Connecticut, which was performed to evaluate 

the actions taken to correct the failure of retrofit ABB vacuum circuit breakers at Baltimore Gas 

& Electric (BG&E) Company's Calvert Cliffs Nuclear Power Plant (Calvert Cliffs). The Calvert 

Cliffs issue will be pursued further in a future inspection at the ABB Service Company's Product 

Development Center (PDC) in Cleveland, Ohio, where the vacuum interrupters and their 

operating mechanisms made by ABB T&D, Florence, were converted for retrofit into existing 

GE Magne-Blast switchgear at Calvert Cliffs. The inspectors observed different circuit breakers 

in various stages of manufacture and testing and identified problems with the implementation of 

the ABB quality assurance program relative to 10 CFR Part 21, and to Criteria III, V and XVI of 

Appendix B to 10 CFR Part 50. 

The inspectors also reviewed the actions taken to correct inspection findings identified in NRC 

Inspection Report 99901256/93-01, reviewed the manufacturing and repair records of two 4.16

kV, HK type circuit breakers that ABB had supplied to American Electric Power Company (AEP) 

for installation at D.C. Cook. 

1.2 Violations and Nonconformances 

1.2.1 Unresolved Item 99901256/1999201-01: Contrary to the requirements of 10 CFR 21.51, 

ABB T&D Co.'s Part 21 evaluation and notification files were determined to be 

incomplete, pending the vendor's location of the missing records (Section 3.1.3) 

1.2.2 Unresolved Item 99901256/1999201-02: Contrary to 10 CFR 21.21(d)(4), not all 

required information was included in all notifications that were made pursuant to 10 CFR 

21.21 (d)(1), pending vendor location of complete correspondence. (Section 3.1.3). 

1.2.2 Nonconformance 99901256/1999201-03: Contrary to the requirements of 10 CFR Part 

50, Appendix B, Criteria III and V, ABB failed to properly change a factory specification. 

Also, the change was implemented without informing users. (Section 3.2.b) 

1.2.3 Nonconformance 99901256/1999201-04: Contrary to the requirements of 10 CFR Part 

50, Appendix B, Criterion XVI, ABB failed to take corrective action committed to for a 

previous violation in that ABB failed to maintain its subscription to NUREG-0040. Also, 

until the first day of the inspection, ABB had not posted its Part 21 procedures per 

§21.6(a) or the alternative notice allowed by §21.6(b). (Sections 2.1 and 3.1.1) 

2

-7-
2.0 STATUS OF PREVIOUS INSPECTION FINDINGS

2.1 Violation 99901256/93-01-01 (Closed) Contrary to the requirements of 10 CFR 21.21(a), 

ABB T&D had failed to update its procedures adopted pursuant to the regulation since 

the substantial revision to Part 21 that became effective on October 29, 1991. Contrary 

to the requirements of 10 CFR 21.6(a), ABB T&D had failed to post the current revision 

of 10 CFR Part 21. During this inspection, the inspectors determined that the Part 21 

procedures had been appropriately updated; although they contained some weaknesses 

as discussed in Section 3.1 below. When observed during this inspection, the current 

revision of Part 21 was posted along with Section 206 of ERA-1974 as required by 

§21.6(a). The ABB T&D procedures adopted pursuant to the regulation were not 

posted, but instead, as permitted by §21.6(b), there was a notice posted that described 

the procedures and stated where the procedures could be viewed as well as the title of 

the person to whom reports were to be made. However, the notice was dated 

September 27, 1999, the date the inspection began, and ABB admitted that neither the 

notice nor their Part 21 procedures had been posted previously; although, when 

inspected, the posting did contain at least the minimum elements required by §21.6; 

therefore the violation was considered corrected. Nevertheless, because neither the 

procedures, nor the notice had been posted prior to the inspection, and because ABB 

apparently had not followed through on all of their commitments for corrective action 

after the previous NRC inspection, the inspectors concluded that this constituted 

inadequate corrective action contrary to the requirements of Criterion XVI, "Corrective 

Action," of 10 CFR Part 50, Appendix B. Accordingly Nonconformance 99901243/ 

1999201-04 was cited. 

2.2 Nonconformance 99901256/93-01-02 (Open): Contrary to the requirements of Criterion 

V, of 10 CFR Part 50, Appendix B, ABB Circuit Breaker Division was not properly 

implementing its quality assurance procedures. The following examples were cited: 

2.2.1 (Closed) Contrary to Paragraph 3.5 of ABB T&D Quality Assurance Procedure (QAP) 

2.5, two nuclear safety-related suppliers had not been audited since 1991. During this 

inspection, the inspectors determined that current ABB procedures addressed supplier 

qualification and no further instances of untimely or missing supplier audits were noted; 

although one audit report reviewed in connection with another issue was of a broad

based programmatic audit and did not document supplier control of the specific 

attributes of interest of the supplied item. (See Section 3.4 of this report.) 

2.2.2 (Closed) Contrary to Paragraph 4.4.9 of ABB's QAP 4.3, "Procurement Documentation 

Control System - General," Revision 1, dated October 29, 1992, ABB had purchased 

items from two vendors which were not listed on the Approved Vendors List and used 

the items in assembling nuclear safety-related circuit breakers. During review of 

material procurements in support of the manufacture of HK and K-Line breakers for D.C. 

Cook, the inspectors found no further instances of use of unauthorized sources. 

Disposition of the material in question and affected breakers was addressed during the 

previous inspection. The inspectors agreed that after this length of time with no 

reported failures attributable to material from the unauthorized vendors, ABB's position 

that final testing and successful service was evidence that the material in question was 

ultimately of acceptable quality was reasonable. 

3 

-8-

I i
2.2.3 (Open) Contrary to Paragraph 3.1 of ABB's QAP 4.3, "Procurement Documentation 

Control System - General," Revision 1, dated October 29, 1992, ABB had not 

documented an evaluation to support the basis for inclusion of all vendors on its 

approved vendors list. This nonconformance was not reviewed during this inspection. 

2.2.4 (Closed) Paragraphs 3.1.2 and 3.2.1 of ABB's QAP 7.1, "Receiving Inspection Components," Revision 1, dated October 29, 1992, referenced "QAP 6.5," and 

paragraph 3.2.4.2 referenced "QAP 16.2." QAP 6.5 and QAP16.2 did not exist and 

therefore could not be followed. The inspectors determined that QAP 6.5 had been 

issued originally on April 12, 1992; therefore, it was in existence at the time of the 

previous inspection. Paragraph 3.2.4.2 of Revision EQ (current) of QAP 7.1 now 

referenced QAP 15.1, "Nonconforming Material." 

2.2.5 (Closed) Contrary to Paragraph 6.2 of ABB's QAP 2.4, "Inspection and Test Personnel 

Qualification," Revision 1, dated October 29,1992, the log book in which job descriptions and certifications of qualifications of personnel were required to be recorded did not 

exist. The inspectors verified that in accordance with current procedures, these records 

are now kept in an electronic database. 

3.0 FINDINGS AND OBSERVATIONS/REPORT DETAILS 

3.1 Implementation 10 CFR Part 21 

a. Inspection Scose: 

The inspectors reviewed ABB's procedures adopted pursuant to 10 CFR 21.21 (a), records required by §21.51, and examined the postings per §21.6. In addition, in order 

to evaluate ABB's identification of potential Part 21 issues under its quality assurance 

program, the inspectors reviewed ABB's procedures relating to nonconforming material 

under Criterion XV of 10 CFR Part 50, Appendix B, including handling customer 

complaints and equipment returned for repair/correction of problems, and procedures for corrective action under Criterion XVI of Appendix B. 

b. Findings and Observations: 

3.1.1 Posting per 10 CFR 21.6 

ABB had properly posted Section 206 of the Energy Reorganization Act of 1974 and the 

latest version of 10 CFR Part 21 (1995) as required by §21.6(a), but had not posted the 

procedures adopted pursuant to §21.21 (a); nor had they ever been posted according to 

the cognizant QA engineer. In addition, as allowed by §21.6(b), in lieu of the 

procedures, ABB had posted a notice that described the procedures and the regulation, stated where the procedures may be viewed (because the regulation was itself posted), and directed that reports be made to the QA manager. However, the notice was dated 

September 27, 1999, the first day of the NRC inspection and the QA engineer admitted 

that no such notice had been posted in lieu of the procedures previously. 

4

-9-
The previous inspection had not identified the lack of posted procedures per §21.6(a) or 

the lack of the alternative notice allowed by §21.6(b), but apparently in posting the latest 

version of Part 21, and in preparation for this inspection, ABB discovered that neither 

the procedures nor an alternate notice was posted. Therefore, as posting each page of 

the procedure in the locked glass case used for the Part 21 posting was impractical, 

ABB prepared and posted the alternate notice as described above. 

In reviewing the posted notice, the inspector noted that the description of the procedures 

was little more than a statement of their purpose. Without explaining the expectations of 

ABB management with regard to reporting by employees of problems identified during 

manufacturing, inspection and testing, or reported from the field, which could adversely 

affect basic components (safety-related equipment) supplied to NRC-licensed facilities, 

the notice was not conducive to meaningful compliance. After discussing this with ABB, 

the inspectors noted that the QA Engineer made the posted notice considerably more 

effective by revising it to state the kinds and sources of information relating to potential 

deficiencies or concerns about Class 1 E and/or "N"-designated (nuclear) items that 

should be reported by employees and that they should be reported to the "Total Quality 

Manager" or the QA Engineer. 

As part of the corrective action for the violation identified in the 1993 NRC inspection 

report in which ABB had not posted the latest version of Part 21 and had not updated its 

procedures to reflect the latest version, ABB had committed to subscribing to the NRC's 

quarterly publication NUREG-0040, "NRC Licensee Vendor and Contractor Inspection 

Status Report," in which revisions to Part 21 were published in addition to their being 

published in the Federal Register. However, the ABB Florence facility did not have 

NUREG-0040, nor were they receiving it, nor were they aware of it. If ABB Florence had 

ever subscribed to NUREG-0040, they had not maintained the subscription. As stated 

in Section 2.1, this was inadequate corrective action contrary to Criterion XVI of 10 CFR 

Part 50, Appendix B, and was cited as Nonconformance 99901256/1999201-04. 

3.1.2 Procedures Adopted Pursuant to 10 CFR 21.21(a) 

ABB's Part 21 procedures were contained in QAP 15.5, "Reporting Product Defects." 

The latest revision, Revision E01, was issued July 30, 1999. The inspectors determined 

that the procedures contained all the provisions required by §21.21(a) to be included in 

procedures adopted pursuant to the regulation. In addition, the inspectors found that 

the procedures were strengthened significantly by inclusion of other provisions to 

implement and explain in terms relevant to ABB Florence other Part 21 requirements 

such as, for example, notifying affected licensees or purchasers in accordance with 

§21.21 (b) of deviations that ABB determines it cannot evaluate in accordance with 

§21.21 (a)(1). However, the procedure also contained some weaknesses such that in 

certain cases, following the procedures verbatim without reference to Part 21 itself could 

lead ABB or allow ABB to fail to meet certain requirements of Part 21 that are not 

explicitly required by the regulation to be included in the procedures adopted to 

implement it. These weaknesses were discussed with the vendor as described in the 

following observations: 

5

-10-
S The Part 21 reporting process was uniquely strengthened by including the 

procedures adopted pursuant to the regulation, QAP 15.5, within the group of 

procedures established pursuant to Criterion XV, "Control of Nonconforming 

Material," of 10 CFR Part 50, Appendix B. However, this advantage was 

diminished because QAP 15.5 did not reference the other relevant Criterion XV 

(and also Criterion XVI, Corrective Action") procedures such as QAP 15.1, 

"Nonconforming Materials" (covers nonconformance reports (NCRs)); QAP 15.2, 

"Production Stop Notice,"QAP 15.4, "Returned Goods Authority"; or QAP 16.1, 

"Corrective and Preventive Action," as prescribing activities in which potential deviations and/or failures to comply in basic components already or previously supplied to NRC-licensed facilities may be identified. QAP 15.5 also did not 

address other external sources of information on potential deviation or failures to 

comply in shipped basic components (e.g., NRC generic communications, 

10 CFR Part 21 notifications or other vendor product bulletins, etc.). 

Weak procedural coordination and interface was not conducive to program 

effectiveness. QAPs 15.1, 15.2 and 15.4 did not provide for screening of 

documentation relating to nonconforming material for potential Part 21 

applicability (or referring to QAP 15.5 to do so), whether information indicating the existence of potential deviation or failures to comply in shipped basic 

components was internal or external. QAP 16.1, governed documentation and 

tracking of corrective action by Corrective Action Requests (CARs). Paragraph 16.1.3.8 stated that the QA manager will determine the impact [of the problem documented in the CAR] on products supplied to nuclear utilities in accordance 

with 10 CFR Part 21. This cross reference was a programmatic strength, but the 

lack of any reference to Part 21 screening on the CAR form or the Corrective 

Action Summary Log form was not conducive to consistent implementation of 

this provision. QAP 16.1 also governed the Internal Complaint Review Process 

(ICRP) and the Customer Complaint Review Process (CCRP), but the guidance for neither process mentioned screening for Part 21 applicability. Sources of 

potential Part 21 issues would include ABB tests, inspections, audits, surveil

lances, commercial-grade surveys or source verifications, which would be 

captured under QAP 15.1 (NCRs) or QAP 16.1 (ICRP), from information 

received from the field (e.g., customer/user problems), captured under QAP 15.4 

(RGA) and QAP 16.1 (CCRP); or other outside sources (e.g., NRC generic com

munications, 10 CFR Part 21 notifications or other vendor product bulletins,). 

* In terms of corrective action incidental to the discovery of deviations and/or 

failures to comply (in addition to reporting requirements), ABB did not cross 

reference the other procedures mentioned above (and also QAP 15.3, "Scrap Procedure") in QAP 15.5 for disposition of the actual material in question, i.e., 

basic components with deviations and/or failures to comply that may have been 

identified initially under the Part 21 program itself, in parallel with the process of 

their being evaluated per 10 CFR 21.21(a)(1), reported to the NRC per 10 CFR 

21.21 (d) or reported to affected licensees or purchasers per 10 CFR 21.21 (b). 

6

-11-
* Specific detailed observations on the content of QAP 15.5 itself were as follows: 

The stated purpose of QAP 15.5 (Paragraph 15.5.1) was to define a system for 

evaluating and reporting deviations and failures to comply with the "Atomic 

Energy Act of 1954, as amended, or the Energy Reorganization Act of 1974 (10 

CFR Part 21)"; whereas the list in 10 CFR Part 21 of those things with which 

something may fail to comply does not include the Energy Reorganization Act of 

1974 or 10 CFR Part 21 itself, but does include "any rule, regulation, order, or 

license of the Commission" which were omitted from the QAP 15.5 statement of 

purpose. 

The scope of QAP 15.5 defined in Paragraph 15.5.2 contained a good working 

definition of basic components in stating that the procedure is applicable to Class 

1 E, i.e., safety-related equipment (which it defined correctly) and services, but 

did not equate them to or even use the term "basic component". However, 

subsequent paragraphs referred to basic components without explaining that 

they are safety-related equipment and services; i.e., without explaining the 

special meaning of this otherwise non-descriptive term within the context of 10 

CFR Part 21. 

Paragraph 15.5.3.1 acknowledged that ABB was a supplier of basic components 

and cited the requirement in 10 CFR 21.21 (a)(1) for evaluation of deviations or 

failures to comply within 60 days of discovery, but the procedure did not explain 

the special meaning and specific elements of this term or refer to its definition in 

§21.3. Paragraph 15.5.3.1 also cited the §21.21 (a)(2) requirement for an interim 

report within 60 days, but did not state that it must be submitted, if required, 

within 60 days of discovery as well. 

Paragraph 15.5.3.2 provided for informing purchasers or affected licensees 

when ABB determined that it could not "perform the evaluation to determine if a 

defect exists," which implemented §21.21 (b). Although §21.21 (a) does not at 

present explicitly include this provision among those things required to be 

included in Part 21 procedures, this provision made the procedure much more 

effective because it addresses the vast majority of cases for any supplier of 

basic components except perhaps the NSSS suppliers of the affected plant 

types, affected architect/engineers or affected licensees themselves, who would 

be expected to be capable of performing such an evaluation. However, the 

added strength was diminished because the language used did not clearly state 

the requirement in §21.21 (b) to inform purchasers or affected licensees of the 

deviation or failure to comply in question, not just that it cannot perform an 

evaluation, which is of secondary importance, being merely the reason why the 

matter is being referred to the affected licensees or purchasers. Although 

explaining a deviation itself was implied by the phrase: "...so that purchasers or 

affected licensees may evaluate the deviation", the paragraph did not include 

failures to comply. 

This observation is not intended in any way to discourage including things in the 

Part 21 procedures that are requirements of Part 21, but not specifically 

required to be in procedures. On the contrary; all applicable Part 21 provisions 

7 

-12-

I I I
must be complied with and some might otherwise be overlooked without direct 

reference to the regulation itself unless included in the procedures. Rather, the 

observation was only intended to convey the caution that in adapting the 

language of Part 21 to more recognizably reflect the specific circumstances and 

common terminology of a particular organization, which may be more conducive 

to meaningful compliance, the procedure must still accurately reflect the intent of 

the Part 21 provisions it is intended to implement, if not restating them verbatim. 

Otherwise, an incorrectly or ambiguously worded procedure, if followed strictly as 

written without reference to Part 21 itself, could allow or even mislead the 

organization into violating or failing to meet certain Part 21 requirements. 

Paragraph 15.5.3.3 apparently was intended to implement §21.21 (a)(3) in a 

manner relevant to the ABB Power T&D Company by designating the "President 

of ABB Power Distribution Company or his designated representative" as the 

director or responsible officer that §21.21 (a)(3) requires be notified of a defect or 

failure to comply associated with a substantial safety hazard within five working 

days of completion of the evaluation. However, the paragraph did not state that 

any so-called designated representative must him or herself also be a director or 

responsible officer as defined in Part 21; nor did it specifically designate an 

alternate who is also a director or responsible officer. Further, it was not clear to 

the inspectors that the title "President of ABB Power Distribution Company" as 

stated in the procedure was exactly consistent with the corporate name or 

organization. Finally, the paragraph failed to mention informing the designated 

director or responsible officer of failures to comply associated with substantial 

safety hazards in addition to defects. 

Paragraph 15.5.3.4 implemented §21.21 (d) and included the provision of 

§21.21 (d)(5) for reporting by a designated representative (not necessarily 

another director or responsible officer). This was a strength, although the 

specific addressees for NRC notification were not given or referenced. 

Section 15.5.4.1 was a significant strength, first, in that the first paragraph recognized the diverse sources of supply (other ABB divisions and outside 

vendors) for manufacturing ABB Power T&D Florence products and took the 

initiative to assign ABB Florence with the responsibility for coordinating the 

evaluation, notification and resolution with the NRC and the customer of 

problems identified in the field with ABB Florence products. However, while 

assuming this responsibility is commendable, the inspectors cautioned ABB that 

some of its suppliers (to the extent that they may supply basic components) as 

well as its customers (to the extent that they may use or also supply basic 

components) continue to be subject to Part 21 requirements. The second 

paragraph prescribed cooperation among the ABB Florence engineering, QA 

and operations departments in performing evaluation, an important concept. The third paragraph acknowledged the same responsibilities as the first, but for 

products from outside vendors. However, it was not made clear that for those 

commercial-grade items that ABB dedicates, assuming Part 21 responsibilities 

as the dedicating entity is required by §21.21 (c) 

8

-13-
Paragraph 15.5.4.5 was a significant strength in that it recognized the need to 

determine when a defect is identified in a product whether any similarly affected 

basic components could have reached purchasers or NRC-licensed facilities; 

although it should have included deviations and failures to comply as well. 

Paragraph 15.5.4.6 provided some clarification of ABB's implementation of 

§21.21 (a)(3) and §21.21(d) that was somewhat ambiguous in Paragraphs 

15.5.3.3 and 15.5.3.4 respectively; although it did not provide for alternate 

directors or responsible officers to whom reports of defects or failures to comply 

related to substantial safety hazards may be reported in order to assure the 

ability to comply with §21.21 (a)(3) should the primary designated officer not be 

available. 

Paragraph 15.5.6.1 under QA responsibilities assigned ABB Florence QA the 

lead in performing evaluations of deviations to identify defects. Germane, but 

not mentioned was the evaluation of failures to comply to determine if they are 

related to substantial safety hazards. 

Paragraph 15.5.6.3 established Part 21 record requirements. It required the QA 

manager to maintain a file "representing the product defect", but records of 

evaluation of and/or notifications sent to purchasers or affected licensees of 

deviations and/or failures to comply, per se, as required by 10 CFR 21.51 were 

not mentioned. In addition, although the QA manager stated that it was ABB's 

practice to maintain such files indefinitely, the §21.51 requirements to maintain 

records relating to evaluation and notification of deviations and failures to comply 

for a minimum of 5 years and to maintain records of the purchasers of basic 

components for a minimum of 10 years after delivery were also not mentioned. 

Section 15.5.8 provided guidance for addressing and documenting during 

performance of §21.21 (a)(1) evaluations (called "potential defect investigations") 

the types of information required by §21.21 (d)(4) to be included as a minimum in 

notifications to the NRC required by §21.21 (d)(1). However, many of the 

subparagraphs in Section 15.5.8 described information related to defects only 

and, except for 15.5.8.6 and 15.5.8.7, did not include failures to comply. 

Because this was the only section in which any specific evaluation guidance was 

provided, the inspector looked for, but did not find in the procedures, an 

explanation or examples of failures to comply relevant to ABB's scope of 

activities (e.g., seismic requirements, license technical specifications, etc.). Also 

absent as evaluation guidance was an explanation of deviations as departures 

from technical requirements in procurement documents that could be considered 

defects due either to their creation of substantial safety hazards or their leading 

to violation of license technical specification safety limits (e.g. exceeding core 

thermal limits due to loss of cooling capability. etc.). 

The procedure also did not explain that for purposes of identifying deviations, 

technical requirements need not be explicitly included or referenced in 

procurement documents, but could be considered to be invoked implicitly. For 

example, specifications in published technical data upon which applications 

engineers rely in specifying equipment by type or model would be presumed to 

9

-14-
be invoked by the procurement documents. Specifications, standards or other 

procurement document requirements certified to in certificates of conformance 

issued by ABB with the supplied equipment or parts could even more clearly be 

presumed to be invoked in the procurement documents. 

In response to the discussion of the forgoing observations by the inspectors, ABB 

committed to revise its Part 21 procedures accordingly and also to improve procedural interfaces by revising its procedures relating to control of nonconforming material, corrective action, and complaints or returns from the field to ensure that problems identified under those procedures are effectively screened for potential Part 21 

applicability. 

3.1.3 Records of Part 21 Evaluations and Notifications 

The inspectors requested the ABB T&D Part 21 evaluation and notification files for the 

previous five years as this is the minimum retention requirement in §21.51. Requested especially were any that may have resulted in no outside notifications. ABB explained that its official Part 21 evaluation and notification files were kept at the Switchgear Division facility in Sanford, Florida, so Sanford faxed copies to Florence for the NRC 

inspectors' review. The group of files produced was represented as complete, i.e., all 

evaluations and notifications, dating back to 1993. However, without a log of all Part 21 

issues, and without screening all potential source documents such as NCRs, CCRPs, RGAs, CARs, etc., the inspectors could not verify that all problems or issues that would 

have required at least a Part 21 applicability screening, if not an actual evaluation and 

possible notification, were captured in the evaluation files presented. Therefore, the 

review was limited to determining whether the evaluations reviewed were technically sound and whether all required notifications were made and included all required 

information. 

The group of Part 21 evaluation and notification files reviewed included 1 file from 1993, 

3 from 1994, 4 from 1995, 2 from 1996, and 1 from 1997. The files are required by §21.51 to include evaluation records and any customer notifications. The inspectors found that some included lists of affected customers and that all the records asserted 

that the NRC and affected customers had been informed; so an assessment of the 

rationale for not making a report was rendered moot. However, in two cases, as 

discussed below, copies of the actual letters that, according to annotations in the 

evaluation record, had been sent to affected customers and the NRC were not present. Therefore, the inspectors could not verify that the notifications were timely or that they contained all the information required by §21.21 (d)(4). In addition, in seven cases, there 

were no records of the evaluations that resulted in the Part 21 notifications. The 1993 

file contained a record of evaluation and a copy of a notification letter to the NRC. The 

NRC notification was typical of most of the others in that it stated that a copy of it was 

being sent to affected customers, so that the NRC notification presumably also 

represented the notification to customers. There were no instances among the files 

reviewed of notifications to purchasers or affected licensees only per §21.21 (b) of 

unevaluated deviations or failures to comply. The lack of records of evaluations in 

seven Part 21 files was an apparent violation of 10 CFR 21.51 (a)(1); so ABB undertook 

to locate the missing records. 

10

-15-
Among the two files with records of evaluation, but no copies of the notifications, the 

record of the evaluation of a report of oversized control wiring lugs found on ABB 

breakers at Southern California Edison's San Onofre Nuclear Generating Station had a 

margin annotation indicating that the issue was reported to the NRC and "distribution 

list", presumably affected customers, on May 10, 1995. As discussed further below, the 

evaluation record itself was not dated (completion date), but it stated that the defect had 

been discovered on March 14, 1995. Therefore, it appeared (but could not be confirmed 

without copies of the notification letters) that the 60-day maximum evaluation period 

requirement of §21.21 (a)(1) had been met. The record was signed by the Vice 

President and General Manager, but his signature was not dated, so it could not be 

verified whether any director or responsible officer (or in particular, the "President of 

ABB Power Distribution"[sic] as required by QAP 15.5 had been notified of the results of 

the evaluation (i.e., existence of a defect in basic components supplied to an NRC

licensed facility, namely San Onofre, at least) within the 5 working days required by 

§21.21 (a)(3). The fact that this file did not include the notifications was a violation of 

10 CFR 21.51(a)(2). In addition, the lack of completion dates on the records of 

evaluation (and the lack of a requirement for this in QAP 15.5) would make it difficult to 

determine precisely within 60 days of the discovery date that was present in one case 

until what date the record must be retained as a minimum. 

In another instance, the file on cracked and broken secondary disconnect strips, 

discovered in June 1995 (no exact date, also at San Onofre) contained a copy of a 

cover letter giving a point of contact and indicating that a Part 21 notification was 

attached. The cover letter, dated September 19, 1995, had an annotation indicating that 

it accompanied "all Part 21 reports" and that they were mailed on September 21, 1995. 

The record of evaluation was again not dated, nor were the review signatures, however, 

if the evaluation took the full 60 days from an assumed discovery date of 30 June, 1995, 

and if the director or responsible officer was notified of the defect five working days 

later, then it appeared, but could not be verified, that the notifications required by 

§21.21(d) had been sent within the time limit specified in §21.21 (d)(3)(ii). However, 

since the actual notification was not on file, this was another example of the violation of 

10 CFR 21.51(a)(2). ABB undertook to locate the missing notifications. 

Finally, not all of the notifications reviewed contained all of the information required by 

§21.21 (d)(4). For example, a notification to the NRC, dated June 28, 1995, did not 

indicate the date the information was obtained [21.21 (d)(4)(v)], nor did it indicate the 

number and location of all affected basic components [21.21 (d)(4)(vi)]. This was the 

case with at least two other notifications as well. 

c. Conclusions 

The inspectors concluded that the ABB Part 21 procedures complied with §21.21 (a). 

The inspectors further concluded that the ABB program for implementation of 10 CFR 

Part 21 was strengthened significantly by locating the procedures among those 

addressing nonconforming material and by including provisions in the procedures to 

implement other Part 21 requirements in terms meaningful to ABB employees. 

However, related procedures were not well cross-referenced and the Part 21 procedures 

themselves contained some weaknesses such that in certain cases, following them 

verbatim without reference to Part 21 itself could lead or allow ABB to violate Part 21. 

11

-16-
On the basis of ABB's failure to have a complete Part 21 posting until the first day of this 

inspection and its apparent failure to have obtained and/or maintained a subscription to 

NUREG-0040 as committed to as part of the corrective action for a previous Part 21 

violation, the inspectors concluded that ABB's corrective action for that previous violation was inadequate and thereby constituted a nonconformance with respect to the 

requirements of Criterion XVI, "Corrective Action," of 10 CFR Part 50, Appendix B. 

Accordingly, Nonconformance 99901256/1999201-04 was cited. 

On the basis of ABB's Part 21 evaluation records and notifications files presented for 

review not containing some of the required documents, the inspectors concluded that 

ABB T&D's Part 21 records did not meet the requirements of 10 CFR 21.51. The inspectors attributed this in part to the weaknesses in the Part 21 procedure regarding documentation and retention of documentation, as well as inconsistent compliance with 

some of those documentation-related procedural provisions that did exist. However, the 

inspectors further concluded that there were no identified defects or failures to comply associated with substantial safety hazards that did not appear to have been reported either to the NRC or to purchasers and affected licensees; although not all the 

notifications could be verified and not all of them were complete. Finally, the inspectors concluded that with regard to the records reviewed, ABB's technical corrective actions 

appeared to be reasonably appropriate and complete. The lack of complete Part 21 

files contrary to 10 CFR 21:'51 was cited as Unresolved Item 99901256/1999201-01, 

pending the vendor's location of the missing records. The lack of complete information 

in several of the notifications contrary to 10 CFR 21.21 (d)(4) was cited as Unresolved 

Item 99901256/1999201-02, pending vendor location of complete correspondence. 

3.2 Manufacture of Circuit Breakers for D.C. Cook 

3.2.1 Review of Records for Breaker Serial No. CCN 0108001-010897 

a. Inspection Scope: 

In order to evaluate the effectiveness of ABB T&D QA controls over its manufacturing 

process, the inspectors reviewed the procurement, manufacture, testing, shipment and 

repair process for new Type HK circuit breakers. Recent purchases by AEP for D.C. 

Cook of two ABB 4.16-kV Type 5HK 250 breakers were used as a vehicle for this 

review. Areas covered included handling of incoming customer procurement documents, review of original specifications, the material requirements planning (MRP) 

process, preparation of "Job Packs," purchased parts, raw materials and services, 

process controls, and final testing. With regard to purchased materials, the inspectors focused on supplier documentation (certificates of conformance (CoCs), certified 

material test reports, packing lists. etc.) and dedication of commercial-grade Items 

(CGIs). The dedication review focused on receipt inspection and testing and final 

testing, including selection of critical characteristics, verification methods and 

acceptance criteria, supplier audits/surveys, and CoCs to the customer. 

12

-17-
b. Findings and Observations

AEP issued PO No. 66132-040-7x, dated March 31, 1997, to ABB Power T&D 

Company, Columbus, Ohio (local sales office) for one ABB, 4.16-kV, Type 5HK250, 

Model 03, 250 MVA, 2000 amp, circuit breaker. The PO specified that the breakers 

should meet the same specifications as the original breakers supplied in 1971, and 

indicated that it was a nuclear safety-related procurement, imposed a QA program 

based on 10 CFR Part 50, Appendix B, and stated that 10 CFR Part 21 was applicable. 

The ABB Columbus sales office passed the PO to ABB T&D, Sanford where the original 

specifications were researched and verified. This information was then given to the 

ABB T&D Circuit Breaker Division in Florence. ABB Florence prepared job pack No. 

CCN 0108001-010897. The job pack serves as a shop traveler which follows the 

breaker throughout production and testing and contains QA/QC records, bill of material, 

etc. The breaker was completed and successfully tested on August 21, 1997. It was 

shipped to DC. Cook on August 29, 1997 with a CoC of that date. On January 28, 1998, 

AEP notified ABB, Florence of the following problems it found with the breaker: 

1. All three arc chutes had cracks, misaligned bundles and mixed hardware. 

2. The phase 2 primary disconnect finger had bare copper visible in one area. 

3. Cadmium plating was damaged and worn on several bolt heads. 

4. Phase 2 lower lead assembly was marred at pivot point. 

5. Control relay was out of adjustment (improper gap). 

6. Racking mechanism is out of adjustment. 

7. Miscellaneous hardware and other materials found packed with the breaker. 

As a result of these findings, ABB Florence issued returned goods authorization (RGA) 

No. 43803 to AEP to return breaker Serial No. CCN 0108001-010897 for repair. ABB 

performed a receipt inspection and confirmed the AEP findings. ABB's explanations 

and/or corrective actions were as follows: 

1. ABB repaired and replaced the arc chutes as necessary. 

2. ABB replaced the deficient contact finger. The ABB Returned Goods Supervisor 

(RGS) explained that the bare copper area on the Phase 2 primary disconnect 

finger did appear to have been scraped such that the copper was showing 

through the silver plating. Discussions of this condition with ABB staff confirmed 

that the apparent wear pattern was not really consistent with that expected on a 

breaker that had been simply racked in and out many times which would typically 

be less severe, more even (affecting all the fingers) and more of a burnished 

silver rather than scraped appearance. It would also not be consistent with a 

new breaker. Rather, the location, orientation, shape and size of the bare area 

suggested damage when being racked in not exactly straight, without lubrication 

of the primary disconnects or damage by mishandling. ABB also allowed that 

13

-18-
the affected finger might not have been adequately plated, although the wear 

pattern was less consistent with that explanation. The inspectors also explored 

the possibility that an old or used finger might have been installed on the 

breaker, but the way that replaced parts from breakers returned for repair are 

segregated (mostly scrapped and recycled), the way new materials were handled 

and the way the assembly process is organized made this scenario very unlikely. 

3. Some bolt heads did have some distortion of the finish during assembly. The 

RGS said that the chromate finish appeared to be slightly blistered, but the bolts 

still had their zinc coating. ABB did not replace the bolts because their condition 

did not affect the function or reliability of the circuit breaker, particularly in their 

relatively clean and dry nuclear plant environment. 

4. The center phase lower lead assembly was confirmed to have a gouge on it. 

The RGS demonstrated that how during assembly, the movable bridge (moving 

main contact arm) may have accidentally fallen forward, and caused the gouge. 

ABB failed to identify this deficiency during the final inspection. ABB replaced 

this part. 

5. With regard to the insufficient gap between the control device lever and the limit 

switch crank, the inspectors learned that ABB engineers had reduced the 

allowable range of this from 0.060-0.090" to 0.010"-0.090" for manufacturing flexibility and to avoid an excessive gap which might lead to improper operation 

of the control device. However, the inspectors found that the change had been 

effected by the cognizant product engineer simply writing what he called an "errata" for the 5HK instruction book (IB 6.2.1.7D) and instructing the factory 

workers to use the new gap without changing the governing factory specification 

(TD 6931) through the engineering change notice process and without informing 

customers. This issue is also discussed in section 3.2.2 of this report. 

6. ABB had determined that the out-of-adjustment condition of the racking 

mechanism was that the gap between the manual trip bell crank assembly (Part 

#191725K02) and the blocking lever extension (part # 192294B00) was large 

enough to defeat the rack-out interlock which is intended to prevent racking the 

breaker out without tripping it. The necessary adjustments were made. 

7. The records indicated that ABB had successfully retested breaker and shipped it 

back to D.C. Cook. 

On August 26, 1998, DC. Cook notified ABB that it received the recently repaired 

breaker with shipping damage. ABB authorized D.C. Cook to return the breaker again 

using RGA 43942. The reported shipping damage was unique because the outside 

container did not exhibit any obvious signs of damage though one side of its contents 

had indeed suffered some damage. The RGS showed the inspector a similarly 

damaged breaker and explained that during transhipment, a heavy weight had been 

placed on one side of the breaker carton which caused one side of the breaker's 

insulation barrier to buckle without obvious visible damage to its carton. ABB believed 

the same thing had happened to D.C Cook's breaker. ABB repaired breaker, retested it 

and returned it to Cook once again. The damage was as follows: 

14

-19-
1. The fiber-glass insulation barrier assembly directly behind the front cover was 

cracked in the top right hand corner. 

2. The strap which attached two insulating pole structures (called "chair moldings") 

was cracked. Damaged chair moldings were replaced. 

3. The epoxy attaching the flux shield to the inter-phase barriers had separated. 

ABB re-expoxyed and sealed the flux shield. 

4. ABB replaced the bent front panel. 

c. Conclusions 

On the basis of review of the manufacturing and testing records for 5HK250 breaker 

serial number CCN0108001-010897; inspection of the returned goods area, procedures 

and process; inspection of the material receiving, production and testing areas and 

process; review of material procurement, receipt and inspection documentation; 

interviews with ABB personnel and examination of equipment and parts; the inspectors 

concluded that the breaker had been manufactured with some quality deficiencies, but 

that they had been adequately corrected. The inspectors further concluded that when 

the breaker was returned to AEP it suffered damage during shipment which ABB also 

corrected satisfactorily. However, the inspectors were not convinced that ABB had fully 

determined the root causes of some of the deficiencies (where possible) and hence, had 

not yet formulated preventive measures as applicable. The inspectors also concluded 

that ABB could improve its records handling practices in some areas as the documents 

associated with the repairs (as well as some others) were not readily retrievable. 

With regard to the change to the control device gap, the inspectors concluded that it had 

been instituted without properly changing the controlling design and/or manufacturing 

drawing (Factory Specification TD-6931) through the engineering change notice (ECN) 

process prescribed in Standard Practice Procedures 600-070, "Design Control and 

Review" (Revision 3) and 600-050, Engineering Change Notices" (Revision 8); nor had 

ABB notified its customers of the change at the time of the inspection. The manner in 

which the change to the control device gap specification was instituted was contrary to 

Criterion Ill, "Design Control," of 10 CFR Part 50, Appendix B and to the governing ABB 

procedures; hence, also contrary to Appendix B Criterion V, "Instructions, Procedures 

and Drawings" and cited as Nonconformance 99901256/1999201-03. 

3.2.2 Review of Records for Circuit Breaker Serial No. CCN 0547002-010798 

a. Inspection Scope: 

The inspectors reviewed the requirements that AEP imposed in its purchase order (P0) 

66147-062-8x, dated May 13, 1998, to ABB Power T&D Company, Field Marketing 

Office (Columbus, Ohio) for one 4.16-kV Type 5HK250, 2000-ampere-rated circuit 

breaker, and all records associated with manufacturing, testing, and subsequent repair 

of the breaker supplied under that PO. 

15

-20-
b. Findings and Observations:

PO 66147-062-8x specified Model No. 6 35 222-888-03 (00) (16) (34) (64) for the 5HK 

breaker and required ABB to provide a Certificate of Conformance (CoC) with the 

customary identifying information, e.g., PO No., Item No., description, and shop order 

number, attesting to the new circuit breaker's being qualified to the same requirements 

as those supplied under ABB's original D.C. Cook shop order, No. 33-44322, dated 

December 1971. 

After reviewing the original order, Sanford placed an order for the breaker on Florence. 

On June 3, 1998, ABB Florence prepared what it calls a "Job Pack" (No. CCN 547002

010798). According to the manufacturing records, assembly of this breaker 

commenced on June 29, and the breaker was completed on July 02, 1998. A quality

control check list dated June 30, 1998, documented the satisfactory results of the quality 

control inspection of the breakers' eleven subassemblies. A medium-voltage test data 

sheet, dated July 24, 1998, documented successful completion of production testing 

prescribed by the current effective edition of Standard C37.09 of the American National 

Standards Institute (ANSI) and the Institute of Electrical and Electronic Engineers, Inc. 

(IEEE). 

ABB, Florence, issued a CoC, dated July 24, 1998, certifying, that the breaker met the 

AEP PO requirements as well as the applicable industry standards. According to the 

records, an AEP QA inspector was supposed to inspect the breaker and discuss quality 

issues on the previously supplied 5HK250 (No. CCN 010897). On July 31, 1998, the 4

kV HK circuit breaker was released for shipment by the AEP representative. Upon 

receiving the breaker at D.C. Cook, AEP performed a receipt inspection and identified 

the following adverse findings: 

1. The gap between the breaker's control relay lever and the limit switch crank was 

0.010" instead of between 0.060" and 0.090" as specified in IB 6.2.1.7D, 

"Installation/ Maintenance Instructions Medium-Voltage Power Circuit 

Breakers,"(See Section 3.4) 

2. The upper phenolic support between the phase 2 and phase 3 pole structures 

(chair moldings) appeared to be cracked. 

3. The "angle iron" under the breaker frame was held with only one loose bolt and 

appeared to be bent. 

4. The breaker had a locking device installed on it which was not on the original 

breaker. 

5. The breaker appeared to have sustained shipping damage. 

AEP completed the required information on a serialized Returned Goods Authority form 

provided by ABB and returned it along with the breaker to the Florence factory. Upon 

receipt of the breaker, ABB Florence issued Warranty Work Order No. CFR 0779 to 

repair the breaker. The Florence Returned Goods Department inspected the breaker 

and documented the following conditions: 

16

-21-
1. The control device gap was confirmed to be 0.010" instead of 0.060" - 0.090". As 

discussed above regarding the other D.C. Cook breaker, the NRC inspectors 

determined that the factory had set the gap in accordance with the so-called "errata" for IB 6.2.1.7D, dated October 9, 1998. 

2. The upper phenolic spacer between the phase 2 and phase 3 chair moldings 

was confirmed to be cracked, but it was the only one found to be damaged. ABB 

believed that the spacer was cracked during shipment. Once cracked, the 

spacer became loose and no longer maintained pole spacing and alignment. 

The cracked spacer was replaced. 

3. The so-called angle iron under the frame (actually called the interference 

bracket) was confirmed as being held by only one of its two bolts which was 

loose. The bracket is a safety device to prevent a 4-kV rated breaker from being 

inserted into switchgear of a different voltage class. The loss of the other 

mounting bolt allowed the interference bracket to swing to one side making it 

appear to be bent. ABB properly re-fastened the bracket. 

4. The breaker was confirmed to have a locking device installed on it which allows 

for the installation of a pad lock to prevent unauthorized operation of the breaker. 

The provision for a locking device is standard. ABB could only suppose that 

AEP had removed the padlocks and locking devices on the original breakers 

when they were installed in 1970s; so that the present D.C. Cook staff were not 

aware that the breakers normally came with locking devices. 

After completing repairs on the breaker, ABB Florence issued a revised CoC dated 

October 9, 1998, certifying that breaker Serial No. CCN0547002 - 010798 met all the 

applicable requirements. ABB Sanford, Florida issued another CoC dated November 5, 

1998, again certifying that the breaker had been manufactured in accordance with the 

requirements of the original AEP PO. The repaired breaker was returned to D.C. Cook. 

c. Conclusions 

On the basis of the manufacturing and repair records, interviews with factory workers, 

examination of the facilities and review of procedures, the inspectors concluded that the 

new breakers that ABB had manufactured and shipped to D.C. Cook did have some 

deficiencies in quality and workmanship and one had suffered damage, apparently from 

shipping and/or handling. As discussed in Section 3.2.1 above, the inspectors further 

concluded that the improperly instituted change in the control device gap set by the 

factory workers in accordance with the instructions by the cognizant engineer 

constituted a nonconformance with respect to Criterion Ill, "Design Control" of 10 CFR 

Part 50, Appendix B, because, in effect, a design change had been instituted without 

proper (and documented) engineering review and approval and without proper (and 

documented) design verification. The change was also contrary to Criterion V, 

"Instructions, Procedures and Drawings," because the change was made in manner not 

authorized by ABB procedures. Accordingly, Nonconformance 99901256/1999201-03 

was cited. 

17

-22-
With respect to the disposition of non-conforming material, either rejected during production or removed from breakers returned for repair, the inspectors concluded that 

these parts appeared to be consistently dispositioned in accordance with standard 

industry practice. Damaged or substandard production parts were captured (with a few 

exceptions due to sampling) and either reprocessed to meet standards if possible or, 

like damaged, substandard or worn parts from relatively new breakers under warranty returned for repair, deficient parts would be scrapped and the material recycled. 

Finally, the inspectors concluded that breakers that have been in service for some time 

are sent to one of the ABB Service Company or other repair shops for repair or 

refurbishment. The factory did not apparently suffer from lack of timely availability of 

new materials and purchased parts, nor was their any significant time pressure to fill 

orders because of backlog or excessive work load. The factory had suffered some 

degradation of quality, but appeared to be genuinely concerned with improving and 

maintaining high quality as well as with customer perception of quality. 

3.3 Replacement Parts for the D.C. Cook Breaker Refurbishment Project 

a. Inspection Scope: 

Using the D.C. Cook circuit breaker refurbishment project as a vehicle for review, the 

inspection of ABB T&D's spare and replacement parts business included review of 

records and interviews with cognizant personnel and touched on the following areas: 

* Handling of customer orders and translation of customer requirements into job 

packs and procurement documents for purchased parts, materials and services 

* Procurement and dedication of commercial-grade items; including selection of 

critical characteristics, verification methods, acceptance criteria, sampling and 

traceability 

* Subsupplier Audits and Commercial-Grade Surveys 

* Receipt Inspection and testing, handling of nonconforming material 

* Manufacturing, in-process and final inspection and testing 

b. Findings and Observation: 

During the review of receipt inspection records for selected purchased parts, the 

inspectors found the following: 

* On the QC Receipt Inspection Card for gear blanks for closing spring charging ratchet wheels, the concentricity of the hole with the perimeter was not specified 

to be checked during receipt inspection, yet the outside diameter was a finished 

dimension; so if the center hole is not centered, then tooth cuts could be shallow 

on one side, too deep on the other. 

18

-23-
* On the QC Receipt Inspection Card for Arc Chutes which are relatively complex 

parts, there was no requirement to check them against applicable drawings 

* The receipt inspection card for needle bearings had no direction to remove 

lubricant or preservative they come packed in and to repack them with Anderol 

757. 

* On each QC receipt inspection card, critical characteristics, verification methods 

and acceptance criteria needed to be hand written. The inspector was 

concerned that this process was conducive to the omissions noted and not 

conducive to effective, consistent control of purchased material. The vendor 

acknowledged the observed deficiencies, initiated corrective action, and agreed 

to consider developing standard cards (perhaps computer generated) with 

preprinted attributes, acceptance criteria, etc. for each type of part or raw 

material inspected. Then only the actual inspection results, measurements, etc. 

would be handwritten. This would also alleviate the need to have engineering 

verify the pre-positioned information on each new card. 

* Electrical and performance testing of relatively complex subcomponents like the 

control devices, auxiliary switches, and Ryobi closing spring charging motors 

was being done at Florence only when those items were installed in finished 

breakers. For spare and replacement items, ABB had, in effect, been taking 

credit for sampling, i.e., the performance of the parts installed in finished, tested 

breakers. However, even at what amounted to a 60-80% rate, the inspectors 

questioned the appropriateness of sampling with such relatively complex items. 

ABB thought that they could in addition, take credit for verification of certain 

electrical and performance-related critical characteristics. However, the NRC 

inspectors' review of the report of the recent audit (January 15, 1999) of Ryobi, 

for example, ABB's new supplier of the small universal (electric drill) motor and 

geared drive assemblies, found it to be a broad-based programmatic audit that 

did not document that Ryobi controlled the critical characteristics of interest, e.g., 

insulation resistance, winding resistance, current draw, torque, speed, heat, etc. 

For example, some of the components for the D.C. Cook breaker refurbishment project 

were purchased by ABB T&D Florence from ABB T&D, Coral Springs, Florida, on 

Florence PO No. PCO 1716, dated August 13, 1999, as follows: 

* Five Type SS-14 Power Shield® solid-state over-current trip units 

(Part No. 60990 T 010 N) 

* Five SS-14, 600A, trip units, non-safety-related part no. 609902T 01ON 

* Five SS-13, 600A, long-time and instantaneous, "NSR" part No.609902 T012 

ABB Coral Springs then forwarded this PO to ABB, Allentown, Pennsylvania, where the 

components were manufactured. ABB Allentown built the trip units shipped them to 

ABB Florence. ABB Florence receipt inspectors verified that the parts received met the 

PO requirements. ABB Sanford issued a CoC to ABB Florence certifying that the trip 

units meet or exceed the requirements of the relays that were originally manufactured 

and supplied to D.C. Cook in 1971. Based on this information, ABB Florence issued its 

own CoC certifying that the trip units meet DC Cook's PO requirements. 

19

-24-
The review of final breaker testing revealed that the factory test parameters were from 

the production testing section of ANSI/IEEE Standard C37.09-1979 that used values in 

Table 8 from C37.06 for indoor switchgear equipment. Accordingly, for 250 Vdc 

nominal control power equipment, for example, closing spring release coils were at 

tested at 200 Vdc and 280 Vdc, trip coils at 140 Vdc and 280 Vdc. However, in the IBs 

used by customers (usually in Table 4) control component voltage ranges equivalent to 

the outdoor values from the standard were given, i.e., 180-260 Vdc closing, 140-260 

tripping. Similarly, nominal 125-Vdc components were tested at 100 (vice 90) Vdc 

closing. The inspectors were concerned that key personnel in customer organizations, 

particularly those responsible for developing acceptance and maintenance procedures, 

may not know this and believe that the factory test voltages are the same as (or more 

instead of less conservative than) those given in the IBs; even though customers 

presumably have the standards cited by the ABB CoCs as well as the test reports which 

are provided to customers. 

In reviewing manufacturing process controls, the inspectors learned, as discussed 

previously, that the specification for crank arm-to-lever gap on HK control devices had 

been changed from that specified in 5HK Instruction Book IB 6.2.1.7D as 0.060"-0.090" 

to 0.010"-0.090'. However, this gap in Factory Specification TD-6931 for 5HK Model 

"03", dated 3-20-67, Revision 3, dated 3-16-84 was 0.005-0.030" (had been 1/16" to 

1/32" before). The 0.010"-0.090" specification, in use in the factory for some time, was 

documented in a so-called "errata" presumably intended to be published eventually for 

IB 6.2.1.7D. As discussed above, the factory workers had been instructed to use the 

specification in the errata instead of properly changing the factory specification using the 

engineering change notice (ECN) process as required by Standard Practice Procedures 

600-070, "Design Control and Review," Revision 3, (original issue5/21/85) and 600-050, 

"Engineering Change Notices," Revision 8 (original issue 8/13/90). This change had 

been in effect for some months, yet users had not been notified. 

c. Conclusions 

The inspectors concluded that the spare and replacement parts QA controls had 

suffered some degradation and could benefit from some updating of the processes, 

including some automation. The inspectors further concluded that the dedication of the 

more complex spare and replacement parts was weak in that only those components going into completed breakers or breaker mechanisms were subjected to electrical and 

performance testing, that taking credit for sampling for such components was not 

appropriate, and that QA supplier audits or surveys were not sufficiently detailed or 

critical characteristic and item specific to rely on for verification of the critical 

characteristics in question. 

Changing the IB by errata (which would normally be used for correction of an error), 

rather than by a formal revision or interim change was inappropriate because the 

change was intentional. As discussed above, it lacked proper design review and 

verification contrary to Criterion III of 10 CFR Part 50, Appendix B. Being instituted 

contrary to ABB QA and engineering procedures, the change was also a 

nonconformance with respect to Criterion V of Appendix B. 

20

-25-
3.4 Observation of Manufacturing

a. Inspection Scope 

The inspectors observed part manufacturing and breaker assembly for 4-kV Type HK 

breakers, medium-voltage vacuum breakers (e.g., Type VHK(X) for direct retrofit into 

HK switchgear), and low-voltage, metal-enclosed K-Line breakers, including in-process 

production inspections and testing. Also examined were vacuum interrupter element 

and breaker operating mechanism subassemblies called "modular assemblies" (in the 

terminology of ANSI/IEEE Standard C37.59), designated VHK(R) [for retrofit], used for 

building special conversion breakers designed for replacement of other manufacturers' 

air-magnetic type breakers using existing unmodified switchgear. These included the 

type supplied to the ABB Service Company Product Development Group, Cleveland, 

Ohio, which, under the nuclear QA and dedication procedures of ABB/Combustion 

Engineering-Nuclear Power (Windsor, Connecticut), is providing the converted vacuum 

breakers for replacement of GE Type AMH-4.16 (Magne-Blast horizontal drawout) 

breakers at the Calvert Cliffs Nuclear Plant. 

b. Observations and Findings 

The inspectors observed some of the endurance testing that each medium-voltage 

breaker manufactured in the plant undergoes for a minimum of 250 cycles of breaker 

opening and closing operations. However, the inspectors observed that during the 

production testing of a non-nuclear Type 5VHK-R250, 1200A, breaker (JOB NO. 

F131098-001 ), the maximum-voltage closing test was performed at 260 Vdc instead of 

280 Vdc (for 250-Vdc nominal control power), as specified in ANSI/IEEE Standard 

C37.09 and C37.06 and as given in Table 4 of IB 6.2.7.7-4C. The test personnel 

acknowledged this observation, but were unable to provide a satisfactory explanation for 

testing at the lower voltage. ABB initiated efforts to resolve this discrepancy. 

c. Conclusions 

The inspectors concluded that in general, observed manufacturing process were well 

controlled and test records reviewed were found satisfactory except for the test voltage 

issue with a 4-kV VHK-R breaker intended for non-nuclear safety-related service. 

3.5 Review of Medium-Voltage and K-Line Design Changes 

a. Inspection Scope 

During the 1999 meeting of the ABB Circuit Breaker Users Groups sponsored by the 

Nuclear Maintenance Applications Center (NMAC) of the Electric Power Research 

Institute (EPHI), ABB Service Company personnel stated that during the development of 

ABB's medium-voltage vacuum type circuit breakers, certain parts in the K-Line (low

voltage breaker) mechanisms that were being adapted for use in the vacuum breakers 

had failed prematurely due the increased stresses from greater mechanical loads 

caused by the greater operating forces in the vacuum breakers resulting from the 

21

-26-
associated stronger closing and opening springs. The ABB Service Company personnel explained that as a result of these failures, ABB Florence upgraded the design and 

manufacturing of the affected parts (e.g., larger cross sections in parts such as 

mechanism latches, but with the same form, fit and function, i.e., physically 

interchangeable) to give these parts more strength and durability for the more severe 

application. The upgrades were reportedly made to all affected K-Line parts, regardless 

of application, for standardization. 

The implication of this revelation was that the new design parts would be suitable for all 

types of breakers in which they could be used, but that the corresponding parts of the 

old design could fail prematurely if misapplied and used in a K-line mechanism installed 

in a vacuum breaker. The inspectors were concerned that this situation could become 

more probable with the increasing retrofits of conversion vacuum breakers into nuclear 

plant switchgear. For example, conventional medium-voltage air or air-magnetic circuit 

breakers of other manufacturers (particularly GE Magne-Blast) are increasingly being 

replaced with typically higher interrupting capacity and lower maintenance vacuum or 

SF6 gas circuit breakers which have been converted for retrofit into unmodified existing switchgear. The ABB Type VHK(R) unit ("R" for retrofit) being used for the Calvert Cliffs 

Magne-Blast replacement project (horizontal-drawout, Type AMH), has also been 

adapted to replace vertical-lift Magne-Blasts at Fort Calhoun. The VHK(R) is not a 

complete breaker, but rather consists only of the vacuum interrupting elements, the 

mechanism and the basic frame on which they are mounted. This configuration is called 

a modular assembly by ANSI/IEEE Standard C37.59-1991 which is the industry standard that governs the conversion or adaptation of such modular assemblies for use 

as replacements of conventional air or air-magnetic circuit breakers. 

In addition, ABB has developed the Type VKH(X) breaker as a direct vacuum type replacement for its air-magnetic HK models, again using unmodified existing switchgear. 

Therefore, the inspectors (and the users groups as well) were concerned that with wider 

and wider usage of breakers with ABB vacuum interrupters and adapted K-Line 

mechanisms, and because the parts in question have the same part numbers and the 

visual differences are subtle and may not be obvious to the inexperienced eye, it could 

be possible for users who also have K-Line breakers in their plants to inadvertently co

mingle the older and newer designs of the affected parts, or in some other manner allow 

old parts to be used in an unsuitable application. The inspectors had discussed this 

issue with ABB Florence previously and reviewed the issue in detail, including the actual 

design changes and examination of the parts in question during this inspection. 

The inspectors also reviewed ABB's reconciliation of design changes with breaker 

qualification. A principal example was use of closing spring charging motors from the 

Ryobi Company when the previous motors made by Ametek were no longer available. 

b. Findings and Observations 

With regard to the K-Line parts upgrades, using old and new design parts to illustrate, 

ABB stated that these upgrades were not made as a result of failures as implied by 

certain ABB Service Company personnel. Rather, ABB explained that they were 

developed to obviate many of the manufacturing tolerance issues associated with the 

intricate breaker operating mechanism. ABB stated that the changes were also made to 

22

-27-
increase the design margin in the endurance limit of the K-line operating mechanism for 

all applications. ABB Florence denied that there had been any such failures of the type 

described by ABB Service Company during the adaptation of the parts for use in 

vacuum breakers. ABB stated that correctly manufactured older K-line parts should 

work in all applications as specified and design tested by ABB, but recommended that 

the optimized parts be used for all new breakers and refurbishment programs because 

they have superior endurance than the previous ones. ABB stated its intention to 

resolve the apparent misunderstanding of the history of the parts and also to impart this 

information to EPRI/NMAC for dissemination to the users groups. 

c. Conclusions 

The inspectors concluded that the design changes were improvements for more efficient 

manufacturing and for enhanced durability, but that the older designed parts were not 

necessarily to premature failure as long as used as designed. The inspectors further 

concluded that using older design parts in the K-Line type mechanisms of vacuum 

breakers was possible, but unlikely, that experienced technicians would likely recognize 

the differences, and that even if they were used inadvertently, they should function 

satisfactorily, but may not last as quite long as the newer designs. It had not been 

proved (nor should it be expected) that older design parts would last the entire service 

life of a vacuum breaker if misapplied. 

4.0 PARTIAL LIST OF PERSONS CONTACTED 

ABB Power T&D Company, Circuit Breaker Division 

+ Jon S. Rennie, Plant Manager, * Shannon Soupiset, P.E., Director of Engineering 

Robert Behl, Engineer 

Byron Powell, Engineer 

Marty Trivette, Engineer 

+ * Scott Bridges, Quality Assurance Manager (Total Quality Manager) 

+ * Richard Lubin, Senior Quality Assurance Engineer 

+ Daniel Hickman, Manufacturing Manager 

+ * Thomas Woodfin, Manager of Components 

+ * John Southerland, Purchasing Manager 

+ Robert Dietrich, QA Consultant (Former ABB QA Manager) 

* Davis Ringley, Customer Service 

+ * Jill Heiden, Manager of Human Resources 

+ Donald Ruedinger, Plant Accountant 

J. Parrott, Qaulity Control Inspector 

K. Smith, Quality Assurance Inspector 

J. Widdows, Quality Assurance Inspector 

+ Attended entrance meeting * Attended exit meeting 

23

-28-
5.0 LIST OF ITEMS OPENED, CLOSED AND DISCUSSED

Opened:

99901256/1999201-01 

99901256/1999201-02 

99901256/1999201-03 

99901256/1999201-04

URI 

URI 

NON 

NON

Closed:

99901256/93-01-01

99901256/93-02-01 

99901256/93-02-02 

99901256/93-02-04 

99901256/93-02-05

VIO

NON 

NON 

NON 

NON

Not Reviewed:

99901256/93-02-03 NON

Discussed: None

Unresolved Item: 10 FR 21.21(d)(4), incomplete 

information in notifications made pursuant to 10 CFR 

21.21 (d)(1), pending vendor location of missing records 

Unresolved Item: 10 CFR 21.51, incomplete records of 

Part 21 evaluations and notifications, pending vendor 

location of complete correspondence 

Nonconformance: 10 CFR Part 50, Appendix B, Criteria III 

and V, Improperly effected change in specifications 

Nonconformance: 10 CFR Par 50, Appendix B, Criterion 

XVI, Inadequate corrective action for previous violation 

Violation: 10 CFR 21.21 (a), Part 21 procedures not 

updated to reflect major revision in Part 21 in 1991, 

10 CFR 21.6, Latest version of Part 21 not posted 

Nonconformance: 10 CFR Part 50, Appendix B, Criterion 

V, failure to follow QAP 2.5, not all required supplier audits 

performed 

Nonconformance: 10 CFR Part 50, Appendix B, Criterion 

V, failure to follow QAP 4.3, procurement from vendors not 

on approved vendor list 

Nonconformance: 10 CFR Part 50, Appendix B, Criterion 

V, inadequate procedure, QAP 7.1, referenced QAPs 6.5 

and 16.2 which did not exist and therefore could not be 

followed. 

Nonconformance: 10 CFR Part 50, Appendix B, Criterion 

V, failure to follow QAP 2.4, required log book to record 

qualification certifications not established 

Nonconformance: 10 CFR Part 50, Appendix B, Criterion 

V, failure to follow QAP 4.3, lack of required evaluation 

documentation of basis for inclusion of some vendors on 

approved vendors list

24

-29-
UNITED STATES 

o NUCLEAR REGULATORY COMMISSION 

WASHINGTON, D.C. 20555-0001 

October 28, 1999 

Mr. Blaine L. Curtis, President 

Anatec International, Incorporated 

930 F Calle Negocio 

Post Office Box 3758 

San Clemente, California 92673-3758 

SUBJECT: NRC INSPECTION REPORT 999001342/1999201 (NOTICE OF VIOLATION 

AND NOTICE OF NONCONFORMANCE) 

Dear Mr. Curtis: 

On August 30 through September 1, 1999, the United States Nuclear Regulatory Commission 

(NRC) performed an inspection at the Anatec International, Incorporated (Anatec) facility in San 

Clemente, California. The enclosed report presents the findings of that inspection. The 

inspection was conducted to review portions of your program relating to personnel training 

records and certifications for eddy current data analysts, and the safety-related services that are 

provided to commercial nuclear power plant facilities. This inspection focused specifically on 

activities regarding supporting documentation associated with the qualification and certification 

of a selective sample of Level IIA and III eddy current qualified data analyst (QDA) personnel 

records at the Anatec facility in accordance with Appendix G, "Qualification of Nondestructive 

Examination Personnel for Analysis of NDE Data," of the Electrical Power Research Institute 

(EPRI) Document Technical Requirements (TR)-1 07569-Vl R5, "PWR Steam Generator 

Examination Guidelines," and the recommended practice of the American Society for 

Nondestructive Testing, SNT-TC-1A, "Personnel Qualification and Certification in 

Nondestructive Testing." The inspectors assessed Anatec's conformance to their customer's 

procurement requirements and compliance with NRC regulations. 

It was found that certain of your activities appeared to be in violation of NRC requirements. 

Specifically, the review of a potential 10 CFR Part 21 issue regarding suspect training and 

certification records that was received by Anatec in May 1999 was not appropriately 

dispositioned in accordance with 10 CFR Part 21. The issue questioned the accuracy and 

validity of QDA records that were not obtained directly from the previous employer. The 

inspectors found that Anatec neither evaluated the issue in accordance with §21.21 of 10 CFR 

Part 21, nor informed the applicable licensees in order to cause the potential defect to be 

evaluated by the licensee as discussed in §21.21(b) of Part 21. This matter is cited in the 

enclosed Notice of Violation (NOV), and the circumstances surrounding the NOV are described 

in detail in the enclosed report. Please note that you are required to respond to this letter and 

should follow the instructions specified in the enclosed NOV when preparing your response. 

The NRC will use your response, in part, to determine whether further enforcement action is 

necessary to ensure compliance with regulatory requirements.

-30-
Mr. Blaine L. Curtis -2

In addition, the NRC inspectors found that the implementation of your quality assurance 

program failed to meet certain NRC requirements imposed on you by your customers. 

Specifically, the inspectors determined that your certification of certain NDE personnel did not 

conform to the guidance contained in Appendix G of EPRI TR-107569-VIR5 and Anatec's 

certification of NDE personnel procedure in that Anatec certified certain NDE personnel based 

upon outside organization training and certification records that were not received directly from 

those organizations and that were not verified by Anatec. This nonconformance could have 

caused an NRC licensee to be in violation of Criteria VII, "Control of Purchased Material, 

Equipment, and Services," and IX, "Control of Special Processes," of Appendix B to 

10 CFR Part 50, "Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing 

Plants." This nonconformance is cited in the enclosed Notice of Nonconformance (NON), and 

the circumstances surrounding it are described in the enclosed report. You are requested to 

respond to the nonconformance and should follow the instructions specified in the enclosed 

NON when preparing your response. 

In accordance with 10 CFR 2.790 of the NRC's "Rules of Practice," a copy of this letter and its 

enclosures will be placed in the NRC's Public Document Room. 

Sincerely, 

'1 .' • 

Theodore R. Quay, Chief, IQMB 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation 

Docket No. 99901342 

Enclosures: 1. Notice of Violation 

2. Notice of Nonconformance 

3. Inspection Report 99901342/1999201

-31-
NOTICE OF VIOLATION

Anatec International, Incorporated Docket No.: 999001342/1999201 

San Clemente, California 92673-3758 

During an NRC inspection conducted at the Anatec International, Incorporated (Anatec) facility 

at San Clemente, California on August 30 - September 1, 1999, a violation of NRC requirements 

was identified. In accordance with the "General Statement of Policy and Procedure for NRC 

Enforcement Actions," NUREG-1 600, the violation is listed below: 

Section 21.21, "Notification of failure to comply or existence of a defect and its evaluation," of 

10 CFR Part 21, requires, in part, that each individual, corporation, partnership, dedicating 

entity, or other entity subject to the Part 21 regulation adopt appropriate procedures to (1) 

Evaluate deviations and failures to comply to identify defects and failures to comply associated 

with substantial safety hazards as soon as practicable, and, except as provided in 

paragraph (a)(2) of §21.21, in all cases within 60 days of discovery, in order to identify a 

reportable defect or failure to comply that could create a substantial safety hazard, were it to 

remain uncorrected, and (2) Ensure that if an evaluation of an identified deviation or failure to 

comply potentially associated with a substantial safety hazard cannot be completed within 60 

days from discovery of the deviation or failure to comply, an interim report is prepared and 

submitted to the Commission through a director or responsible officer or designated person. 

Section 21.21(b) requires that if the supplier of basic components determines that it does not 

have the capability to perform the evaluation to determine if a defect exists, then the supplier 

must inform the purchasers or affected licensees within five working days of this determination. 

Contrary to the above, Anatec failed to recognize that it was required to perform an evaluation 

of information contained in a letter received approximately May 17, 1999, indicating that the 

validity and accuracy of certain non-destructive examination qualified data analyst testing 

personnel records were suspect. Additionally, Anatec also failed to recognize that it was 

required to inform the applicable utility customers if it determined that it did not have the 

capability to evaluate the issues in accordance with Part 21. (Violation 99901342/1999201-01) 

This is a Severity Level IV violation (Supplement VII). 

Pursuant to the provisions of 10 CFR 2.201, Anatec International, Incorporated is hereby 

required to submit a written statement or explanation to the U.S. Nuclear Regulatory 

Commission, ATTN: Document Control Desk, Washington, D.C. 20555-0001, with a copy to the 

Chief, IQMB, Division of Inspection Program Management, Office of Nuclear Reactor 

Regulation, within 30 days of the date of the letter transmitting this Notice of Violation. This reply 

should be clearly marked as a "Reply to a Notice of Violation" and should include for each 

violation: 

Enclosure 1

-32-
(1) the reason for the violation, or, if contested, the basis for disputing the violation, (2) the 

corrective steps that have been taken and the results achieved, (3) the corrective steps that will 

be taken to avoid further violations, and (4) the date when full compliance will be achieved. Your 

response may reference or include previous docketed correspondence, if the correspondence 

adequately addresses the required response. Where good cause is shown, consideration will 

be given to extending the response time. 

Dated at Rockville, Maryland 

this 28thday of October 1999

-2-

-33-
NOTICE OF NONCONFORMANCE

Anatec International, Incorporated Docket 99901342 

San Clemente, California 

Based on the results of an inspection conducted at the Anatec International, Incorporated 

(Anatec) facility at San Clemente, California on August 30 - September 1, 1999, it appears that 

certain Anatec activities were not conducted in accordance with NRC requirements. 

Criterion V, "Instructions, Procedures, and Drawings," of 10 CFR Part 50, Appendix B requires 

that activities affecting quality be prescribed by documented instructions and procedures and 

shall be accomplished in accordance with those instructions and procedures. 

Section 5.5.4 of Anatec Procedure ANATEC-08, "Certification of NDE Personnel," states, 

"Training programs administered by other companies or organizations prepared in accordance 

with this written practice will be considered adequate." Section 5.9, "Certification," of 

ANATEC-08 states, " If an outside agency is used [for certification], ANATEC executes its 

responsibilities for certification by assuring that training, examination and certification of NDT 

personnel are in accordance with this procedure, as a minimum." 

Contrary to the above, Anatec certified NDE personnel based upon training and certification 

records from other organizations which were not verified to be in accordance with Anatec's 

written practice. Anatec accepted certification records from other organizations (provided by 

incoming Anatec employees) without auditing or otherwise assuring the other organization's 

training, examination and certification of NDE personnel met the requirements of ANATEC-08. 

(Nonconformance 99901342/1999201-02) 

Please provide a written statement or explanation to the U.S. Nuclear Regulatory Commission, 

ATTN: Document Control Desk, Washington, D.C. 20555-0001 with a copy to the Chief, IQMB, 

Division of Inspection Program Management, Office of Nuclear Reactor Regulation, within 30 

days of the date of the letter transmitting this Notice of Nonconformance. This reply should be 

clearly marked as a "Reply to a Notice of Nonconformance" and should include for each 

nonconformance: (1) the reason for the nonconformance, or, if contested, the basis for disputing 

the nonconformance, (2) the corrective steps that have been taken and the results achieved, (3) 

the corrective steps that will be taken to avoid further noncompliances, and (4) the date when 

your corrective action will be completed. Where good cause is shown, consideration will be 

given to extending the response time. 

Dated at Rockville, Maryland 

this 2 8th day of October 1999 

Enclosure 2

-34-
U.S. NUCLEAR REGULATORY COMMISSION 

OFFICE OF NUCLEAR REACTOR REGULATION

Report No.: 

Organization:

Contact:

999001342/1999201

Anatec International, Incorporated 

930 F Calle Negocio 

Post Office Box 3758 

San Clemente, California 92673-3758

Lisa T. Gardner, QA Manager 

(949) 498-3350

Nuclear Activity: 

Date of Inspection: 

Inspectors: 

Approved by:

Anatec International, Incorporated (Anatec) provides 

nondestructive testing and associated activities for the evaluation 

of steam generator, condenser and feedwater heater tubing 

through eddy current testing, data collection and analysis review 

services to the nuclear industry. 

August 30 - September 1, 1999 

Joseph J. Petrosino, Lead Inspector 

Gregory C. Cwalina, Senior Reactor Engineer 

Cheryl D. Beardslee, Materials Engineer 

Daniel H. Dorman, Chief 

Quality Assurance and Safety Assessment Section, IQMB 

Division of Inspection Program Management 

Enclosure 3

-35-
1 INSPECTION SUMMARY

The NRC inspectors examined documentation related to personnel training records and 

certifications for eddy current data analysts, and the safety-related services that are provided to 

commercial nuclear power plant facilities. This inspection specifically focused on activities 

regarding supporting documentation associated with the qualification and certification of a 

selected sample of Level IIA and III eddy current qualified data analyst (QDA) personnel records 

at the Anatec facility in accordance with Appendix G, "Qualification of Nondestructive 

Examination Personnel for Analysis of NDE Data," of the Electrical Power Research Institute 

(EPRI) Document Technical Requirements (TR)-107569-V1R5, "PWR Steam Generator 

Examination Guidelines: Revision 5, Volume 1: Requirements," and the recommended practice 

of the American Society for Nondestructive Testing, Incorporated (SNT) - Technical Council 

(TC) - First Document (1A), "Personnel Qualification and Certification in Nondestructive 

Testing," The inspectors assessed Anatec's conformance to their customer's procurement 

requirements and compliance with NRC regulations. 

The inspection bases were: 

* Appendix B, "Quality Assurance Criteria for Nuclear Power Plants and Fuel 

Reprocessing Plants," to Part 50 of Title 10 of the Code of Federal Regulations (CFR) 

(Appendix B) 

* 10 CFR Part 21, "Reporting of Defects and Noncompliance" 

* SNT-TC-1A, "Personnel Qualification and Certification in Nondestructive Testing," 

* Appendix G of EPRI TR-1 07569-Vl R5, "PWR Steam Generator Examination Guidelines: 

Revision 5, Volume 1: Requirements" 

During this inspection, a violation of NRC requirements was identified and is discussed in 

Section 3.1 of this report. Additionally, one instance was identified where Anatec failed to 

conform to NRC and Electric Power Research Institute requirements contractually imposed 

upon them by NRC licensees. This nonconformance is discussed herein. 

2 STATUS OF PREVIOUS INSPECTION FINDINGS 

This was the first NRC staff inspection conducted at the Anatec facility. 

-2-

-36-
3 INSPECTION FINDINGS AND OTHER COMMENTS

3.1 10 CFR Part 21 

c. Inspection Scope 

The NRC inspectors reviewed Anatec's 10 CFR Part 21 program implementation, conducted discussions with the quality assurance (QA) manager regarding 10 CFR 

Part 21, and reviewed and commented on the procedure that Anatec adopted to 

implement the Part 21 regulation. 

b. Observations and Findings 

b.1 10 CFR Part 21 Evaluation: On May 21, 1999, AJB Technologies (AJB), Greensburg, Pennsylvania transmitted a letter to the NRC identifying a potential 10 CFR Part 21 issue 

regarding suspect NDE personnel records which AJB believed were being used to certify and qualify former AJB personnel without verification of the validity of those records. A 

number of the individuals named in the 10 CFR Part 21 report are currently Anatec 

employees. The contents of this letter were also transmitted to other potentially affected 

NDE personnel vendors and affected licensees, including Anatec. Therefore, during the 

Anatec inspection, the inspectors asked whether Anatec had received the AJB 

information contained in the AJB letter and asked to review a copy of its 10 CFR 

Part 21 evaluation of the issue. 

Anatec stated that they had received a copy of the information contained in the facsimile. 

However, Anatec stated that they had not performed the evaluation required by §21.21, "Notification of failure to comply or existence of a defect and its evaluation," of 10 CFR 

Part 21. The Anatec QA Manager stated that Anatec had not recognized that it was 

required to perform an evaluation of the potentially reportable issue in accordance with 

Part 21. 

The inspectors determined that Anatec had failed to adequately implement the 

requirements of 10 CFR Part 21 and this was identified as a violation of NRC 

requirements. (Violation 99901342/1999201-01) 

The inspectors discussed the 10 CFR Part 21 responsibilities with the QA Manager and 

also explained to Anatec that it was still responsible to evaluate the circumstances of the issue, as it related to Anatec's customers, in order to identify a reportable defect or 

failure to comply that could create a substantial safety hazard, were it to remain 

uncorrected, or to provide the NRC with an interim report if the issue could not be 

evaluated within 60 days. Additionally, the inspectors discussed with Anatec that if they did not have the technical capability to determine if a defect exists, then they were 

required by Part 21 to inform any applicable nuclear power plant customers. 

Anatec's Evaluation of the May 1999 letter: By letter, dated October 11, 1999, Anatec 

provided the NRC a copy of their Part 21 evaluation of the May 1999, AJB letter. The 

inspectors determined that Anatec's evaluation of the issues did not address the 

-3-

-37-
significance of the deviations nor did the evaluation attempt to determine whether a 

particular deviation could create a substantial hazard or determine whether a failure to 

comply is associated with a substantial safety hazard. 

The definition contained in §21.3 of 10 CFR Part 21 of "evaluation" states that it is "the 

process of determining whether a particular deviation could create a substantial hazard 

or determining whether a failure to comply is associated with a substantial safety 

hazard." This aspect was discussed between the Anatec QA manager and the NRC 

inspectors. Nonetheless, Anatec's evaluation did not adequately address the issue of 

verification of previous certifications, records and experience. Additional details 

regarding the qualification and certification of QDAs is discussed in Section 3.2 below. 

For example, ANATEC's response, Page 2, EVALUATION states, "Anatec is stating that 

prior certifications, and/or personnel1 records as described in ANATEC-08, Section 5.12, 

paragraph 5.12.4 are typically used by the hiring company as proof of prior training and 

experience and are normally retained by the individual in the same manner as a Lead 

Auditor or Welder certification would be." 

However, Anatec did not verify the rap2 sheets or certifications. If they had contacted 

AJB, they would have been aware that AJB's policy was to designate and maintain their 

personnel information, including their rap sheets or certifications, as proprietary. It was 

AJB's corporate policy not to provide them to the individuals. Therefore, information that 

was obtained directly from former AJB employees and not from AJB (or any other 

previous employer) should be considered suspect until substantiated with that employer. 

Further, ANATEC-08 states acceptance of certifications (and not personnel records as 

stated in their evaluation) is sufficient. However, in the case of one QDA, no record or 

copy of prior certification was found in his record package; only a copy of a rap sheet 

that was faxed from a funeral home in Pittsburgh, Pennsylvania was found in the 

package. No record as to who faxed the information was noted. Additionally, the 

evaluation states that: "There is no prior history which would lead Anatec to believe the 

QDA records are inaccurate." However, the inspectors noted that there was no objective 

evidence in the reviewed QDA record packages indicating that Anatec took any steps to 

verify the rap sheet information. Instead, Anatec accepted the information provided 

without verification from the previous employers. Lacking any effort to validate 

information provided by the individuals, Anatec would not have been able to identify any 

concern with regard to the employee's prior history. 

1 It was noted during review of the Anatec procedures that Procedure ANATEC-08 does 

not mention personnel records. 

2 The term "rap sheet" describes the data summary sheets that are used by the NDE 

eddy current industry to document results of certification and recertification results for each 

QDA. 

-4-

-38-
The Anatec evaluation also states that, "all records were generated by an authorized organization, either Zetec or AJB as noted below." However, Anatec did not audit AJB and AJB does not appear on Anatec's approved supplier's list. Although, Zetec was on 

Anatec's approved supplier list, the inspectors noted that Zetec information was used to 

certify two QDAs over a month after Anatec had certified them. 

b.2 10 CFR Part 21 Procedure: The inspectors reviewed a copy of the procedure which 

Anatec adopted to implement the provisions of 10 CFR Part 21, Procedure 

ANATEC-G-06, "10 CFR 21 Reporting of Defects and Noncompliance," Revision 2, dated September 26, 1994. 

The inspectors identified several areas within ANATEC-G-06 that did not adequately 

ensure that deviations and failures to comply were dispositioned in accordance with 

Part 21. The procedure also did not ensure that deviations and failures to comply would be appropriately identified and evaluated. Further, the inspectors identified a few areas 

where Anatec's procedure could be confusing to an Anatec employee attempting to determine a course of action for evaluating deviations. Anatec's procedure required employees to notify their supervisor of applicable defects. However, since a defect is determined on the basis of an evaluation, an employee may believe that they were 

required to perform an evaluation prior to informing their supervision. 

For example, the Part 21 procedure used the term defect, as defined in §21.3 of Part 21, throughout its procedure instead of the term deviation. The switching of the two terms 

mandates different Part 21 requirements for the vendor's necessary action. That is, a defect, as determined by a Part 21 evaluation process, must be reported to the NRC; whereas, a deviation is required to be evaluated in accordance with 10 CFR Part 21 to 

determine whether a defect or substantial safety hazard exists. 

The switching of the two terms could have caused inappropriate action or no action to be 

performed. In the case of the violation discussed herein, Anatec did not fully understand 

that the issues identified in the AJB letter could have represented deviations in the Anatec quality assurance (QA) program regarding verification of personnel qualification, certification and educational requirements. Consequently, Anatec did not recognize that 

it was required to perform an evaluation in accordance with Part 21 as cited in 

NOV 99901342/1999201-01. 

The general requirements stated that for those cases where reporting is required by other NRC regulations, duplicate evaluation and reporting under 10 CFR Part 21 is not required. Discussions indicated that Anatec personnel were not aware of other NRC 

regulations concerning reportability nor of the NRC timeliness requirements mentioned in 

the general requirements of ANATEC-G-06. 

The definition section in ANATEC-G-06 did not contain all of the relevant definitions, such as, "discovery," and "evaluation" that would help ensure appropriate and effective 

implementation of the procedure. Evaluation is a significant term because it means that 

-5-

-39-
a decision must be made whether a particular deviation could create a substantial 

hazard or determining whether a failure to comply is associated with a substantial safety 

hazard. 

The inspectors discussed each area of ANATEC-G-06 which contained weaknesses with 

the QA Manager and obtained a commitment from the QA manager that Procedure 

ANATEC-G-06 would be revised as discussed within 120 days to ensure it provided 

appropriate direction to effectively implement the provisions of 10 CFR Part 21. 

c. Conclusions: The inspectors concluded that Anatec failed to recognize its responsibility 

to evaluate deviations or failures to comply in accordance with Part 21, but committed to 

perform an evaluation of the issues and other related deviations and inform the Lead 

Inspector of the results. Anatec's established procedure, ANATEC-G-06, to implement 

the provisions of 10 CFR Part 21 contained numerous weaknesses that contributed to its 

failure to recognize the need to perform an evaluation of the deviation contained in the 

May 1999 information received from AJB. 

Additionally, the inspectors conclude that Anatec's evaluation of the issues contained in 

the May 1999 letter and the evaluation of suspect records for other Anatec QDAs did not 

appropriately address the concerns regarding verification of records, nor address the 

evaluation aspects of §21.3 of Part 21. 

3.2 Qualification/Certification of Qualified Data Analysts 

a. Inspection Scope 

The inspection team reviewed the qualification program and practices for Anatec 

nondestructive testing (NDT) personnel, with particular emphasis on eddy current QDAs. 

The inspectors reviewed the qualifications to assure conformance to licensee purchase 

orders, Anatec internal requirements, the recommended guidance of SNT-TC-1A, and 

Appendix G, of EPRI TR-107569-VIR5, Revision 5. 

The inspectors reviewed the qualification documents for several employees, some of 

whom were qualified directly by Anatec and some of whom were qualified by Anatec 

based upon previous qualifications from another organization. 

b. Observations and Findings 

b.1 General. For each certified eddy current QDA, Anatec kept an up-to-date personnel 

certification summary record. The summary record included the level for which the 

individual was certified, the certification date and expiration date. It also included a 

summary of the technical examinations completed to attain certification, including the 

Method, Level, Date and Examiner (organization responsible for the examination), as 

well as the employee's test scores and copies of the written test. The summary also 

included a listing of the employee's experience, work history, education and training, and 

other documentation appropriate for qualification and certification. 

-6-

-40-
The inspectors noted some inconsistencies or discrepancies in the records reviewed. 

For instance, some records for technical examinations listed the Examiner as the 

organization that actually gave the training and examination while others listed the Examiner as the employer at the time the trainee took the examination. In addition, records for required QDA annual training only consisted of verification that the QDA received the training materials and agreed to read them. There was no evidence that the 

trainee actually read the materials or discussed them with a trainer. The Anatec method 

of annual training seems contrary to the guidance provided in Appendix G of the EPRI 

report. Section G.4.1.3, Annual Training, states, "A record of attendance and topics covered during the training shall be maintained." The inspectors informed Anatec that they felt that wording indicated a more formal method for annual training than that implemented by Anatec. The inspectors identified, through review of older annual 

training records, that Anatec previously implemented a more formal process, which 

required discussion with a trainer. 

b.2 Anatec Trained QDAs. The inspectors did not identify any additional concerns while 

reviewing packages for those employees who were solely trained, qualified and certified 

by Anatec. 

b.3 Previously certified QDAs. SNT-TC-1A states that certification is the responsibility of the 

employer, and an employer's certification is revoked when an employee has been terminated. An employee whose certification has been terminated may be certified to the 

former NDT level by a new employer based upon examination, provided certain conditions are met to the new employer's satisfaction. These conditions are: proof of 

prior certification, employee was working in the capacity to which certified within 6 

months of termination, and the employee is being recertified within 6 months of termination. As detailed below, the inspectors identified several concerns for those 

employees who initially received QDA training, qualification and certification while 

employed at another organization and were recertified by Anatec. 

As stated above, SNT-TC-1A says that an individual can be recertified by a new 

employer based upon examination and written proof of prior certification. In all cases, Anatec administered written examinations for Level IIA or III qualification in accordance 

with Anatec procedures and industry guidance. However, the inspectors identified multiple packages where Anatec relied on certification and qualification test results 

(written and practical) from a previous employer to certify analysts as QDA qualified. [Note: Level IIA written examinations are different than QDA written examinations.] No 

form of practical examination was given (either for the Level IIA/III or QDA certifications). In addition, the inspectors determined that Anatec relied on certifications and QDA "Data 

Summary" Sheets (A.K.A. "rap sheets") that were obtained directly from the employee, not from the employee's former employer. The inspectors concluded this did not adequately meet the intent of "proof of prior certification," because Anatec did not verify the validity of the rap sheet or certification with the previous employer. In addition to the guidance in SNT-TC-1A, Section 5.5.4 of Anatec-08, "Certification of NDT Personnel," 

-7-

-41-
states, "Training programs administered by other companies or organizations prepared 

in accordance with this written practice will be considered adequate." Anatec did not 

verify that the employee's previous training was prepared in accordance with Anatec's 

written practice. 

Specifically, the inspector identified 5 examples (See Table 1, Employees A, B, C, D, and 

E) where Anatec accepted a Level IIA/Ill and QDA certification from another organization 

without verifying that the paperwork supplied by the new employee 

(e.g., certification and/or QDA Data Sheet) was valid. In addition, Table 1 also shows 

that Anatec was inconsistent as to what was acceptable for qualification. In some cases 

Anatec used student supplied rap sheets and certifications (Employees A, and E). In 

others Anatec used only the rap sheet (Employees C, D, and F), or certification 

(Employees B and G). In all the above cases, the rap sheet or certification was a copy of 

the AJB rap sheet or certification. The inspectors contacted AJB and were told that AJB 

considered the rap sheets and certifications as the property of AJB and had not 

authorized their release or use as proof of prior certification. Further, AJB had not been 

audited by Anatec and was not on Anatec's list of approved suppliers. Therefore, there 

was no documented basis for acceptance of AJB rap sheets or certifications, (whether 

provided by AJB or the employee) to fulfill the guidance of SNT-TC-1A or Anatec's 

internal procedure. 

The inspectors noted that, earlier in 1999, Anatec seemed to recognize the weaknesses 

in their certification process. In several cases, Anatec augmented their basis for 

certification by confirming the employee's training and/or experience. In three cases 

(Employees A, B, and G), Anatec contacted Zetec, Incorporated (Zetec), the provider of 

the training. Zetec transmitted a facsimile to Anatec stating that the employees had 

successfully completed their QDA training course. Although Zetec is on Anatec's 

approved supplier list, the training was provided under contract to AJB. Since Anatec 

was not aware of the specific requirements of the AJB training contract, their reliance on 

the Zetec facsimile is unsupported. Anatec did not provide assurance that the Zetec 

training was provided in accordance with the Anatec approved training and QA program. 

Further, the inspectors also noted that, in most cases, verification was done after the 

employee had been certified by Anatec and, in some cases, after the employee had 

performed work at a licensed facility. 

In two other cases (Employees C and D), Anatec's certification was based, in part, upon 

an Anatec interoffice memo stating that the employees had received ET Level IIA Data 

Analysis training while employed at AJB. The memo does not state that the employees 

successfully completed the training, only that it was administered. The memo was 

signed by an Anatec Level III examiner who had also been employed at AJB at the time 

of the testing. There was no documented evidence that Anatec verified the training with 

the former employer. 

The inspectors informed Anatec that the failure to properly verify the validity of rap 

sheets, certifications and other documents relied upon to perform certification, in 

accordance with SNT-TC-1A and Anatec's procedures is identified as 

-8-

-42-
Nonconformance 99901342/1999201-02. The inspectors also informed Anatec that the 

potential improper certifications should be reviewed and dispositioned in accordance with 

10 CFR Part 21. 

The inspectors also identified a weakness in Anatec's documentation process. Through review of the QDA Data Sheets, the inspectors identified two examples (See Table 1, Employee E and F) that appeared to indicate there were errors in the QDA test taking 

process and contrary to the actual outcome, the QDA test should not have been passed. One employee, E, appeared to take the initial qualification test four times in quick succession before passing. Appendix G of EPRI TR-07569-VI R5 and Anatec-08 require additional training and a 30-day waiting period after failing the test the third time. A 

second employee, F, appeared to take the requalification test two times in quick succession before passing. For requalification, EPRI requires a full standard practical examination if the requalification examination is failed the first time. In both cases, 

through discussions with Anatec and documentation from the employee's previous employer, the inspectors determined the third initial qualification test and the first 

requalification test, respectively, were regraded, not retaken. This information should 

have been documented by Anatec when initially identified. 

b.4 Questionable Certification: The inspectors identified a further anomaly with one data 

analyst (See Table 1, Employee D) in addition to the issues described above. The rap sheet indicated the employee failed the practical examination on the third attempt and 

took the examination a fourth time on the following day (October 20, 1998) and passed. Appendix G of the EPRI guidance and Anatec-08 require additional training and a 30-day waiting period after failing the test the third time. There was a handwritten note, dated 

October 20, 1998, on the rap sheet written by the test proctor which stated that an 

administrative error had resulted in the student's test answers being stored in the wrong location [on the third attempt]. That error resulted in the failing grade on the third 

attempt. The proctor's note indicated that the answers had been retrieved and regraded the following day, resulting in the passing grade. In response to inspectors questions on 

the note, Anatec contacted the AJB test proctor (currently employed by Anatec) who 

provided a detailed explanation of the issue. The inspectors visited AJB to verify the 

information provided by the proctor. A review of the employee's qualification file 

revealed that the handwritten note found on the Anatec QDA rap sheet was not on the 

rap sheet in AJB's files. Since the employee had taken the test while employed at AJB, 

the absence of the note on the AJB official records raised a question regarding the 

validity of the note. 

Subsequent discussions conducted with a Westinghouse Level III NDE/ET QDA indicated that the Westinghouse QDA software program used was capable of introducing the anomalies that were stated to have happened. Subsequent discussions with EPRI 

NDE Center representatives indicated that they recalled speaking with the Level III 

subject Proctor regarding the anomalies encountered during the performance of the 

student's QDA exam with the Westinghouse QDA software program. Although neither of 

the two EPRI representatives stated that they had documented the date and time of the 

telephone call with the Level Ill Proctor, they distinctly remember discussing the problem 

with the AJB Level Ill QDA proctor. 

"-9-

-43-
Finally, this matter was discussed again with the Level III Proctor who administered the 

test and wrote the note on the QDA sheet. He indicated to the inspectors that his 

recollection of the matter was that he wrote the note on the original rap sheet and 

provided it to the AJB owners before he left employment with AJB in December 1998. 

The inspectors were unable to determine why the handwritten note found in the Anatec 

qualification file does not also appear in the AJB file. 

The Proctor also indicated that he had provided copies of the AJB rap sheets to each of 

the students that he had trained and conducted the QDA exam. He explained that the 

rap sheets were provided to the students for their own records. 

c. Conclusions 

The Anatec method of annual training does not provide a positive indication of a record 

of attendance and topics covered. The inspectors informed Anatec that more formal 

method for annual training was appropriate. The failure to properly verify the validity of 

rap sheets, certifications and other documents relied upon to perform QDA certification, 

in accordance with Anatec's procedures was identified as a nonconformance. The 

potential improper certifications should be reviewed and dispositioned in accordance with 

10 CFR Part 21. 

3.2 Entrance/Exit Meetings 

In the entrance meeting on August 30, 1999, the NRC inspectors discussed the scope of 

the inspection, outlined the areas to be inspected, and established interfaces with the 

Anatec QA Manager. In the exit meeting on September 1, 1999, the NRC inspectors 

discussed their findings and concerns. 

4. PERSONS CONTACTED 

Lisa Gardner Anatec QA Manger 

Darren Howe Anatec Level III QDA 

Delle Obazenu Anatec Level III QDA 

Craig Smith EPRI NDE Center ** 

Gary Henry EPRI NDE Center ** 

Gary Pierini Westinghouse NDE ** 

** Contacted by Telephone 

-10-

-44-
Table I - QDA Certification Basis

Employee Date of QDA Data (Rap) Sheet Certification Additional Basis for Certification 

ID Anatec 

Cert. 

A 8/20/98 * 8/4/98 fax from employee 8/5/98 fax from employee * 4/16/99 fax from Zetec - name handwritten - AJB cert. of 1/22/98 - successful completion of QDA - no ID of testing organization training and testing 

B 3/4/99 None copy of AJB cert dated 1/22/98 o 4/16/99 fax from Zetec 

- successful completion of QDA training 

C 3/4/99 • 1/18/99 fax from Gaines None * copy of Zetec training certificate 

funeral home (identity of dated 8/2/96 for Level IIA sender unknown) * copy of Zetec Continuing Education - no ID of testing organization Program certificate for Level IIA 

- 3/3/99 Anatec Interoffice Memo from 

Level III stating that Level IIA training 

was given to employee by Level III 

while 

were employee and Level III examiner employed at AJB 

D 3/4/99 * Data sheet indicates test None • 3/3/99 Anatec Interoffice Memo from taken while employed at AJB Level III stating that Level IIA training - handwritten note dated was given to employee by Level III 10/20/98 by Level III while employee and Level III examiner 

explaining basis for regrading were employed at AJB 

after apparent failure on 3rd e 9/99 message from Level III 

attempt examiner documenting basis for - No indication of data sheet 10/20/98 regrading after failure on 3rd origin QDA attempt

-11-

J=
Table I - QDA Certification Basis (cont.)

-12-

91

Employee Date of QDA Data (Rap) Sheet Certification Additional Basis for Certification 

ID Anatec 

Cert. 

E 8/98 • 7/21/98 fax from employee 7/16/98 fax from employee * 4/1/99 fax from previous employer 

- QDA data sheet implied the verifying experience hours 

QDA test was taken 4 times in - 8/31/99 fax from previous employer 

quick succession in conflict documenting basis for regrading after 

with Anatec and industry failure of requalification exam 

practice and guidance 

F 9/98 e 9/18/98 fax from AJB * 9/99 message from previous 

Technologies employer documenting basis for 

- QDA data sheet implied the regrading after failure of requalification 

1997 QDA requalification test exam 

was failed but another 

requalification test was 

immediately taken instead of a 

full standard practical exam 

G 9/21/98 None 9/18/98 fax from AJB ° 8/24/99 fax from Zetec 

- successful completion of QDA 

training
UNITED STATES 

o NUCLEAR REGULATORY COMMISSION 

WASHINGTON, D.C. 20555-0001 

December 1, 1999 

Mr. Craig P. Kipp 

General Manager Nuclear Fuel 

GE Nuclear Energy 

Nuclear Energy Production 

P.O. Box 780 

Wilmington, NC 28402-0780 

SUBJECT: NRC INSPECTION REPORT NO. 99900003/1999202 

AND NOTICE OF NONCONFORMANCE 

Dear Mr. Kipp: 

This letter addresses the inspection of your facility at Wilmington, North Carolina, conducted by Robert Pettis, Jr. and Dr. Shih-Liang Wu, of this office on September 7-10, 1999, and the 

discussions of their findings with Caroline Reda and other members of your staff at the 

conclusion of the inspection. The inspection was conducted to review the implementation of 

selected portions of the General Electric Nuclear Energy (GE-NE) Quality Assurance Program Description (NEDO-11209), including 10 CFR Part 21, as it relates to the activities performed in 

the Chemet laboratory, and to followup on corrective actions performed by GE-NE as a result of 

our previous inspection. 

The team reviewed technical documentation, procedures, representative records, and also 

interviewed GE-NE personnel. At the conclusion of the inspection, the findings were discussed 

with members of your staff. On the basis of this inspection, the team determined that certain of 

your activities appeared to be in violation of NRC requirements, as specified in the enclosed 

Notice of Nonconformance. Specifically, a GE-NE audit of JMS Southeast, Inc. (JMS), did not 

objectively demonstrate that JMS's quality assurance (QA) program complied with the 

requirements of 10 CFR Part 21, which was imposed on JMS by purchase order. A review of 

the audit by the NRC inspection team identified that it did not demonstrate that JMS had 

adequate procedures in-place to identify and evaluate deviations, pursuant to 10 CFR 21.21, and that a recent revision to its QA manual did not address acceptance of Part 21. Over the 

past several years, GE-NE has placed over 10 safety-related purchase orders with JMS for 

thermocouple calibration services which have imposed the reporting requirements of 10 CFR 

Part 21. 

You are required to respond to this letter and should follow the instructions specified in the 

enclosed Notice when preparing your response. In your response, you should document the 

specific actions taken and any additional actions .you plan to prevent recurrence. Your response 

may reference or include previous docketed correspondence, if the correspondence adequately addresses the required response. After reviewing your response to this Notice, including your proposed corrective actions, the NRC will determine whether further NRC enforcement action is 

necessary to ensure compliance with NRC regulatory requirements.

-47-
Mr. Craig P. Kipp -2

In accordance with 10 CFR 2.790 of the NRC's "Rules of Practice," a copy of this letter, its 

enclosures, and your response will be placed in the NRC Public Document Room (PDR). To the 

extent possible, your response should not include any personal privacy, proprietary, or 

safeguards information so that it can be placed in the PDR without redaction. However, if youe 

find it necessary to include such information, you should clearly indicate the specific information 

that you desire not to be placed in the PDR, and provide the legal basis to support your request 

for witholding the information from the public. 

The response requested by this letter and the enclosed Notice of Nonconformance is not subject 

to the clearance procedures of the Office of Management and Budget as required by the 

Paperwork Reduction Act of 1980, Pub. L. No. 96-511. Should you have any questions 

concerning this inspection, we will be pleased to discuss them with you. 

Sincerely, 

Theodore R. Quay, Chief, IQMB 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation 

Enclosures: 

1. Notice of Nonconformance 

2. Inspection Report No. 99900003/1999202

-48-
NOTICE OF NONCONFORMANCE

GE Nuclear Energy (GE-NE) Docket No.: 99900003 

Wilmington, NC 

Based on the results of an NRC inspection conducted on September 7-10, 1999, it appears that 

certain of your activities were not conducted in accordance with NRC requirements. 

Criterion VII of Appendix B to 10 CFR Part 50, "Control of Purchased Material, Equipment, and 

Services," states, in part, "Measures shall be established to assure that purchased material, 

equipment, and services.. .conform to the procurement documents..." 

Contrary to the above, an NRC review of a March 4, 1999, GE-NE audit of JMS Southeast, Inc. 

(JMS), did not adequately demonstrate that JMS's quality assurance (QA) program complied 

with the requirements of 10 CFR Part 21, which was imposed on JMS by purchase order. 

Specifically, the audit did not demonstrate that JMS had adequate procedures in-place to 

identify and evaluate deviations pursuant to 10 CFR 21.21. Section 4.13.3, "Recall Procedure," 

incorporated into the JMS QA manual in Revision 10, dated December 8, 1998, and later 

revised in Revision 11, dated February 26, 1999, was not adequate to allow for the identification 

and evaluation of nonconforming conditions as potential deviations pursuant to 10 CFR 21.21. 

JMS revised its QA manual by adding Section 4.13.3 to address specific findings identified 

during a March 26, 1997, audit by GE-NE which identified several Corrective Action Requests 

(CARs). Specifically, CAR JMS-2 identified that JMS's QA program did not procedurally 

address the reporting of defects to customers pursuant to 10 CFR Part 21. Over the past 

several years GE-NE has placed over 10 safety-related purchase orders with JMS for 

thermocouple calibration services which imposed the requirements of 10 CFR Part 21. Based 

on the March 4, 1997, re-audit of JMS, GE-NE closed CAR JMS-2 and two others which had 

been open for two years without a documented resolution. Since the JMS QA manual revisions 

were not adequate to address compliance to 10 CFR Part 21, the NRC inspection team did not 

agree with GE-NE's closure of CAR JMS-2 (99900003/1999202-01). 

Please provide a written statement or explanation to the U.S. Nuclear Regulatory Commission, 

ATTN: Document Control Desk, Washington, D.C. 20555 with a copy to the Chief, IQMB, 

Division of Inspection Program Management, Office of Nuclear Reactor Regulation, within 30 

days of the date of the letter transmitting this Notice of Nonconformance. This reply should be 

clearly marked as a "Reply to a Notice of Nonconformance" and should include for each 

nonconformance: (1) the reason for the nonconformance, or if contested, the basis for disputing 

the nonconformance, (2) the corrective steps that have been taken and the results achieved, 

(3) the corrective steps that will be taken to avoid further nonconformances, and (4) the date 

when your corrective action will be completed. Where good cause is shown, consideration will 

be given to extending the response time. 

Dated at Rockville, Maryland 

December 1, 1999 

Enclosure 1 

-49-
U.S. NUCLEAR REGULATORY COMMISSION 

OFFICE OF NUCLEAR REACTOR REGULATION

Report No.: 

Organization:

99900003/1999202 

GE Nuclear Energy 

P.O. Box 780 

Wilmington, NC 

Caroline Reda 

Manager, GE-NE Quality

Contact:

Nuclear Activity:

Dates:

Nuclear fuel assemblies and related components for BWRs.

September 7-10, 1999

Inspection Team: 

Approved by:

Robert L. Pettis, Jr., IQMB/DIPM 

Dr. Shih-Liang Wu, SRXB/DSSA 

Daniel Dorman, Chief 

Quality Assurance and afety Assessment Section, IQMB 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation 

Enclosure 2 

-50-
1 INSPECTION SUMMARY

From September 7-10, 1999, representatives of the U.S. Nuclear Regulatory Commission (NRC) conducted a performance-based inspection of the activities at the 

Wilmington, North Carolina, facility of GE Nuclear Energy (GE-NE). In conducting this 

inspection, the team emphasized technically directed observations and evaluations of 

GE-NE activities related to the manufacture and testing of nuclear fuel and related 

components. As the technical bases for the inspection, the team relied upon the 

following: 

Part 21, "Notification of Failure to Comply or Existence of a Defect," as defined in 

Title 10 of the Code of Federal Regulations (10 CFR) 

10 CFR Part 50, Appendix B, "Quality Assurance Criteria for Nuclear Power Plants 

and Fuel Reprocessing Plants" 

* GE-NE Quality Assurance Program Description (NEBO-1 1209). 

1.1 Violations 

No violations were identified during this inspection. 

1.2 Nonconformances 

Nonconformance 99900003/1999202-01 was identified during this inspection and 

is discussed in Section 3.3 of this report. This issue was previously identified as 

Unresolved Item 99900003/1999201-02 during the March 22-25, 1999, NRC inspection. 

1.3 Unresolved Items 

No unresolved items were identified during this inspection. 

2 STATUS OF PREVIOUS INSPECTION FINDINGS 

Violation 99900003/1999201-01 (CLOSED) 

During the previous inspection, the inspection team identified a violation of NRC 

requirements associated with the failure to identify and evaluate a potential deviation 

related to a laboratory analyst who failed to perform over 20 required weekly calibrations 

of the LECO hydrogen analyzer during the period April 1996 through March 1999. The 

analyzer is used to perform hydrogen tests for both zirconium fuel cladding and ceramic 

fuel pellets. Preliminary evaluation results performed by GE-NE during the previous inspection identified several fuel pellets which appeared to exceed the GE-NE 

specification iimit for hydrogen. At the conclusion of that inspection, GE-NE initiated 

Potential Safety Concern (PSC) 9907 and Corrective Action Request (CAR) AI-2170 to 

evaluate the condition under the reportability requirements of 10 CFR Part 21. This 

issue is further discussed in Sections 3.2 and 3.4 of this report. 

2 

-51-
Unresolved Item 99900003/1999201-02 (CLOSED)

During the March 22-25, 1999, NRC inspection, GE-NE could not produce 

documentation to support the resolution of three open CARs identified during GE-NE's 

March 26, 1997, audit of JMS Southeast, Inc. During the September 7-10, 1999, NRC 

inspection, the team further identified this issue as a Nonconformance and 

administratively closed the Unresolved Item. This issue, and the Nonconformance, is 

further discussed in Section 3.3 of this report. 

3 INSPECTION FINDINGS AND OTHER COMMENTS 

3.1 Background 

The NRC inspection team reviewed the activities performed by laboratory analysts in the 

Chemet Laboratory. The Chemet Laboratory is an integral part of the in-process release 

of raw materials, process control, and final release of finished products at the Wilmington 

facility. The Chemet Laboratory consists of a metallurgical and wet laboratory. The 

metallurgical laboratory houses an environmental laboratory while the wet laboratory 

houses a mass spectrometer and standards laboratory. During the inspection, the team 

primarily focused its attention on the activities performed in the wet chemical laboratory. 

The wet chemical laboratory performs a wide variety of chemical and physical analyses 

on uranium dioxide powder and pellets and zirconium fuel cladding. 

3.2 Review of Corrective Actions - Violation 99900003/1999201-01 

a. Inspection Scope 

The inspection team reviewed GE-NE corrective actions associated with Notice of 

Violation 99900003/1999201-01, which was identified during the March 22-25, 1999, 

NRC inspection. 

b. Observations and Findings 

During the March 1999 NRC inspection, the team identified a potential deviation in which 

a laboratory analyst failed to perform over 20 required weekly calibrations over a three 

year period for the LECO hydrogen analyzer. At the conclusion of the inspection on 

March 25, 1999, GE-NE initiated CAR AI-2170 to address the LECO calibration 

deficiencies. Potential Safety Concern (PSC) 9907, "Fuel Pellet/Zircaloy Hydrogen 

Analysis," and CAR AI-2170 were also initiated to evaluate if the deviation could cause a 

substantial safety hazard pursuant to the reportability requirements of 10 CFR Part 21. 

Since certain required weekly calibrations were not performed, the potential exists for 

fuel product to have exceeded either GE-NE or customer fabrication specifications, 

thereby resulting in the shipment of out-of-specification product. 

In a letter to NRC dated May 20, 1999, GE-NE concluded that after completion of the 

evaluation for PSC 9907 and extending the review to all LECO methods, not just 

hydrogen, GE-NE concluded that the issue was not reportable. The LECO methods 

evaluated included pellet and Zircaloy hydrogen, Zircaloy nitrogen and oxygen, powder 

3 

-52-
nitrogen, and powder carbon. During the review, CAR AE-1 104, dated May 3, 1999, was 

initiated to investigate a concern raised by a laboratory analyst regarding the furnace 

blanking method for Pellet Fluoride (PSC 9908) and Powder/Pellet Chloride (PSC 9912) methods and was documented in CAR AI-2212, dated April 16, 1999. This issue is 

further discussed in Section 3.4 of this report. 

PSC 9907 reviewed calibrations performed during the period April 1996 through April 1999 and included a review of the LECO methods previously discussed. For each 

method, the calibration factors reported in the Laboratory Material Control System (LMCS), now replaced by the Laboratory Information Management System (LIMS), were evaluated back to April 1996. The review identified repeat calibration factors for all six LECO methods previously discussed. Eight calibrations enveloping each calibration in question (four before and four after the questioned calibration date) were evaluated for the maximum calibration factor. This factor, in addition to the original calibration factor, 

were used to correct the results using an equation derived by GE-NE. After applying the 

conservatively derived correction factor to all LECO methods, all corrected data was within specification limits except for several Zircaloy oxygen samples which exceeded 

the upper specification limit, which was attributed to an outlier which likely contributed to 

over correction of the data. The data demonstrated that even though a calibration may not have been performed per the required procedure, the calibration factor that was 

utilized was within the process control limits and that product performance during the 

suspect period was as expected and did not exceed specifications. As a result, GE-NE 

concluded that failure to perform weekly calibration did not have a negative impact on the originally reported results and as such, a product nonconformance or inadvertent 

shipment did not occur. 

The inspection team also reviewed a parallel investigation initiated by GE-NE to 

determine if an employee integrity issue existed. GE-NE Integrity Case 99-005, "Falsification of Chemet Laboratory Data - Fluoride and Percent U Titrations," dated March 1999, reviewed three years of calibration constant data associated with the LECO analyzer. As a result, four laboratory analysts were identified as having questionable calibration standard results. Action taken by GE-NE included dismissal of one analyst for falsification of calibration data and written warnings for the others in accordance with 

company policy. When interviewed by GE-NE, none of the analysts could provide an 

explanation for the repeat calibration constants. 

In addition to the CARs and PSC evaluations performed to determine if the falsified 

calibrations created a defect or failure to comply with the reporting requirements of 

10 CFR Part 21, other preventive actions were taken by GE-NE to prevent recurrence. 

These actions included the disciplinary actions previously discussed; suspension of the pellet fluoride and powder/pellet chloride methods at the Wilmington facility pending re

qualification; performance of a "quality standown" for all Chemet Laboratory personnel; and sensitivity training on the requirements of 10 CFR 50, Appendix B, and 10 CFR Part 21. These actions were verified by the NRC inspection team during the inspection. 

c. Conclusions 

The NRC inspection team reviewed all available documentation, including the GE-NE 

Integrity Review, which evaluated the impact of the wet laboratory analyst copying the 

4 

-53-
previous week's calibration constant rather than performing the required weekly 

calibration. The team agreed with GE-NE's 10 CFR Part 21 evaluation which concluded 

that the failure to perform weekly calibrations did not have a negative impact on the 

originally reported results and as such, a product nonconformance or inadvertent 

shipment did not occur. 

3.3 Review of Unresolved Item 99900003/1999201-02 

a. Scole 

Review additional documentation to demonstrate that GE-NE adequately resolved 

several open Corrective Action Requests (CARs) which were identified during a 

March 26, 1997, audit of JMS Southeast, Inc. (JMS). During the March 1999 NRC 

inspection, GE-NE could not provide sufficient documentation to demonstrate adequate 

resolution of the CARs, which have been open for two years. GE-NE has qualified JMS 

as an approved supplier of safety-related thermocouple calibration services in 

accordance with 10 CFR 50, Appendix B, 10 CFR Part 21 and GE-NE supplier quality 

requirements. 

b. Observations and Findings 

On March 26, 1997, GE-NE audited JMS and identified three CARs. CAR JMS-2 was of 

particular concern to the NRC inspection team since it identified that JMS's Quality 

Assurance (QA) program did not procedurally address the reporting of defects to 

customers pursuant to 10 CFR Part 21. Over the past several years GE-NE has placed 

over 10 safety-related purchase orders (POs) with JMS for thermocouple calibration 

services which imposed the requirements of 10 CFR Part 21. The CARs remained open 

through the early part of 1999 when it was determined that a followup audit needs to be 

performed to resolve these two year old open issues. During this time JMS revised its 

QA manual to address the specific findings and on March 4, 1999, GE-NE re-audited 

JMS. As a result of the audit, GE-NE closed all three CARs and certified JMS as an 

approved supplier of safety-related services and equipment. 

The NRC inspection team reviewed the audit report and identified that the audit did not 

adequately demonstrate that JMS's QA program complied with the reporting 

requirements of 10 CFR Part 21, which was imposed on JMS by GE-NE purchase order. 

Specifically, the audit did not objectively demonstrate that JMS had adequate procedures 

in-place to identify and evaluate deviations pursuant to 10 CFR 21.21. Section 4.13.3, 

"Recall Procedure," incorporated into the JMS QA manual in Revision 10, dated 

December 8, 1998, and later revised in Revision 11, dated February 26, 1999, was 

added to address CAR JMS-2. However, the NRC inspection team did not agree since it 

was not of sufficient detail to allow for the identification and evaluation of nonconforming 

conditions as potential deviations pursuant to 10 CFR 21.21. On September 4, 1997, 

GE-NE placed PO No. 33497066632 to JMS for full calibration and recertification of two 

Type "C" thermocouples (GE-NE identification Nos. Z010003 and Z0098534) used to 

determine the thermal profile of the Centorr furnace. The PO required compliance to 

Part 21 and required the vendor to furnish Certificates of Traceability to the National 

Institute of Standards and Technology. The team reviewed preventive actions initiated 

by GE-NE to improve CAR reporting, tracking and closing, including modifications to its 

5 

-54-
Approved Supplier List effective January 1999, which should enhance the visibility of 

unresolved issues on a more timely basis. Nonconformance 99900003/1999202-01 was 

identified during this part of the inspection. 

c. Conclusions 

The NRC inspection team reviewed additional documentation during the inspection to 

support the resolution of three open CARs identified during GE-NE' s March 26, 1997, 

audit of JMS Southeast, Inc. However, the team concluded that the JMS audit was 

inadequate in several areas. Specifically, the audit failed to provide objective evidence 

of JMS's compliance to 21.21 of 10 CFR 21 and as such, does not support closure of 

CAR JMS-2. Based on the inspection team's review, the NRC has concern over JMS's 

ability to identify and evaluate potential deviations in light of their status as an approved supplier of safety-related services and equipment, in accordance with 10 CFR 50, 

Appendix B, and 10 CFR Part 21. 

3.4 Review of CAR AI-2212 - Pellet Fluoride and Chloride Evaluations 

a. Inspection Scope 

The inspection team reviewed GE-NE CAR AI-2212 which was initiated due to a concern 

raised by a laboratory analyst regarding performance of the furnace blanking method for 

pellet fluoride and powder/pellet chloride methods. The concern resulted in initiation of 

PSC 9908 for pellet fluoride and PSC 9912 for powder/pellet chloride. The CAR also 

addressed method qualification and laboratory analyst training. 

b. Observations and Findings 

During performance of GE-NE Integrity Case 99-005, discussed in Section 3.2 of this 

report, one of the wet laboratory analysts raised a concern to management regarding the 

performance of the furnace blanking method for pellet fluoride and powder/pellet chloride 

methods. As a result, GE-NE initiated two additional investigations for reportability 

pursuant to 10 CFR Part 21. PSC 9908 and PSC 9912, closed on April 29, 1999, and 

May 11, 1999, respectively, concluded that no defect or failure to comply, pursuant to 

10 CFR Part 21, existed. GE-NE also initiated CAR AI-2213, dated April 16, 1999, to 

address training and procedural compliance in the Chemet laboratory. 

b.1 Pellet Fluorides Method (PSC 9908) 

In March 1999, an employee raised an issue to management that several of the 

laboratory analysts were not strictly following the procedure of blanking the furnace 

before each fluoride sample run as prescribed in laboratory procedures. The 

pyrohydrolysis method, also called the blanking method, is a method to obtain analytical 

blank values for analysis of fluorine in fuel pellets. An analytical blank value is a fluorine 

concentration level obtained when the method is followed using all standard procedures, 

material, and equipment but without any sample present, and is described in GE-NE 

Calibration and Operation Instruction (COI) 253, "Determination of Fluoride in U02 and 

U02/Gd2O3 Pellets by Pyrohydrolysis and Titration," Revision 1, dated October 14, 

1998. Pending evaluation to determine if a potential safety concern existed, GE-NE 

6 

-55-
suspended performance of the test. PSC 9908 was initiated to investigate the potential 

impact to the product quality. A second evaluation, PSC 9912 (Discussed in 

Section 3.4 (b.2) of this report), was also initiated to evaluate pellet chloride analysis 

because it also utilizes the same blanking method. 

During the wet laboratory quality stand down on April 19, 1999, a laboratory analyst was 

interviewed for alleged falsification of pellet fluoride tests as documented in GE-NE 

Integrity Case 99-005. The analyst was asked to perform a series of blanking methods 

for a few samples in the presence of several laboratory managers. Although the tests 

demonstrated that the analyst did not strictly adhere to the procedures in performing the 

blanking method, GE-NE concluded that no falsification of data existed. The integrity 

review identified that the analyst performed the test "as trained" instead of strictly 

following the procedure. The NRC inspection team reviewed the report, including 

interview notes and laboratory data, and agreed with GE-NE's conclusion that no 

falsification of data existed. 

CAR AI-2212 was issued to assess the fluoride blanking method and address potential 

training issues. GE-NE evaluated the effect of uncertainty in the fluoride concentration in 

fuel pellets in four areas affected by specification requirements: (1) fuel failures during 

normal operations, (2) cladding degradation during power excursions, (3) uranium 

content, and (4) power generation. Fuel failures during normal operation are mainly 

caused by primary hydride in fuel pellets that could attack cladding. However, GE-NE 

indicated that due to recent implementation of the dry conversion process and a strict 

industry requirement regarding hydrogen control, the possibility of increasing fuel failures 

because of the irregularity in the blanking method were very unlikely. 

Cladding degradation during power excursions is affected by stress corrosion cracking of 

Zircaloy cladding due to pellet-clad mechanical interaction (PCMI) in the presence of 

fluorine. Since GE-NE has introduced a new zirconium lined cladding, the PCMI 

problem was basically eliminated and thus the fluorine content had no direct effect in this 

assessment. With respect to uranium content, GE-NE indicated that the amount of 

uranium could be changed by the total impurities including fluorine. They also stated that 

power generation is also affected by the total uranium content and higher impurities may 

reduce power output. GE-NE concluded that no reportable issues existed since the first 

two concerns related to safety were not present and the latter two concerns were 

commercial in nature. The NRC inspection team reviewed the assessment and agreed 

that the likelihood of introducing more fluorine into the fuel pellets was very small and 

would not effect the overall outcome. 

Currently, the procedures to determinate the amount of fluoride in U02 or U02/Gd2O3 

pellets is documented in Quality Notice (QN) F-Q-2302, "Qualification of Pyrohydrolysis 

and IS Detection for Pellet Fluoride Analysis," Revision 0, dated August 12, 1999. The 

QN describes the determination of fluoride in U02 pellets using pyrohydrolysis followed 

by ion selective electrode detection. The pyrohydrolysis method is described in COI 253, 

"Sample Preparation for Fluoride in U02 and (AGATE)02 Pellets by Pyrohydrolysis," 

Revision 2, dated August 12, 1999, which supercedes Revision 1 of the same COI but 

with a different title. The ion selective electrode detection method replaced the titration 

method and is described in CO 252, "Determination of Fluoride in Uranium Oxides 

Using Selective Ion Electrode," Revision 2, dated August 12, 1999. 

7 

-56-
b.2 Pellet Chloride Method

As mentioned previously, PSC 9912 was initiated to investigate the pellet chloride 

method, due to the same pyrohydrolysis method, and is described in GE-NE CO 256, 

Revision 0, "Determination of Chloride in Uranium Oxide Pellet and Powders with and 

without Guideline," dated September 23, 1998. GE-NE performed a study to assess the 

capability of the analytical method for reliable data in chlorine concentration. They 

concluded that there was no safety concern since the results demonstrated that the 

blanking method for chlorine was adequate and that a product non-conformance did not 

occur. The NRC inspection team reviewed the report and agreed with the conclusion. 

Currently the procedures to determine the amount of chloride in uranium powders is 

documented in QA F-Q-2292, "Qualification of Method for Determination of Chloride in 

Uranium Oxide Powders by Dissolution and Turbidimetry," Revision 1, dated June 16, 

1999. In addition, COI 275, "Determination of Chloride in Uranium Oxide Powders by 

Dissolution and Turbidimetry," Revision 2, dated August 6, 1999, provides further detail 

on the pellet chloride method. 

b.3 Training 

As a result of PSC 9908 and PSC 9912, CAR AI-2213, dated April 16, 1999, was issued 

to address the laboratory training program and to develop an action plan to review 

current training and procedures. After management review of the current organization 

structure, several training courses were conducted for laboratory analysts. The training 

included periodic reviews, communication of procedural changes, and the new LIMS 

software system. On April 19, 1999, a quality standown was conducted with all available 

Chemet Laboratory staff in attendance. As a followup, all Fuel and Chemet Laboratory 

Quality staff were re-qualified into the requirements of 10 CFR Part 21. The NRC 

inspection team reviewed the documentation and concluded that the training program 

was acceptable. 

c. Conclusions 

During GE-NE's evaluation of Integrity Case 99-005, one of the wet laboratory analysts 

raised a concern regarding the performance of the furnace blanking method for pellet 

fluoride and powder/pellet chloride methods. As a result, GE-NE initiated two additional 

investigations for reportability, pursuant to 10 CFR Part 21, and initiated CAR AI-2213 to 

address training and procedural compliance in the Chemet laboratory. At the completion 

of their evaluation, GE-NE concluded that no defect or failure to comply existed. The 

NRC inspection team reviewed the documentation and agreed with their conclusion. 

3.5. Review of Karl Fischer Moisture Analyzer 

a. Scope 

The inspection team reviewed the method employed at GE-NE Wilmington to determine 

the moisture level in uranium powder. The method, known as Karl Fischer titration, is 

documented in GE-NE COI 259.00, Revision 2, dated April 1, 1999, "Determination of 

Moisture in Uranium Powders By Karl Fischer Titration." 

8 

-57-
b. Observations and Findings

In March 1998, an allegation was brought to the attention of GE-NE management from a 

laboratory analyst who alleged 14 separate issues involving various activities performed 

in the wet laboratory. GE-NE initiated Integrity Case 98-006 to evaluate the issues which 

were grouped into the following categories: Falsification of Data; Procedure; Technique; 

Opinion; and Previously Identified Issues. Of these categories, GE-NE identified the 

most significant issues which involved deficiencies in the execution of Fluoride/Chloride 

pellet samples; improper use of test standards; and several discrepancies related to test 

results associated with the performance of Karl Fischer, Chloride, and Nitrogen tests. 

GE-NE concluded from the investigation that although an employee integrity issue did 

not exist, improvements were needed in procedure interpretation and performance of 

laboratory standards and practices. Evidence of implementation of these improvements 

were later initiated through CAR AI-2170 and CAR AI-2212 in March 1999. The team 

reviewed the integrity report, reviewed the CARs, and concluded that GE-NE took 

appropriate action to resolve this allegation. 

In June 1999, the wet laboratory supervisor was made aware of an issue involving a 

laboratory analyst who failed to report an out-of-control indication (OOCI) while 

performing moisture tests using the Karl Fischer analyzer. When twice encountered with 

an OOCI in running the test, the analyst wrote on the bench sheet "unable to stable" for 

the first occurrence and "underqualified" for the second occurrence and did not call 

attention to the supervisor. After review of the issue, the supervisor concluded that there 

was no immediate safety concern because the uncertainty involved in the moisture level 

was well within the nuclear safety specifications established by GE-NE. The analyst 

responsible for the test was reminded of his responsibility to report the OOCI in the future 

and was encouraged to use a more conservative approach while performing tests using 

the Karl Fischer analyzer. The NRC inspection team reviewed the supervisor's 

evaluation and concluded that the action taken was adequate to resolve the issue. 

c. Conclusions 

The NRC inspection team reviewed the evaluations performed by GE-NE in March 1998 

and June 1999 and agreed with the conclusions. 

3.6 Review of Fuel Rod Off-Gas Tests 

a. Scope 

The NRC inspection team reviewed a discontinued practice of performing off-gas tests to 

assure that all uranium dioxide fuel rods and internal metallic components meet the 

specified requirements for total volatiles and rod hydrogen content. 

b. Observations and Findings 

The practice of assuring that all uranium dioxide fuel rods and internal metallic 

components meet the specified requirements for total volatiles and rod hydrogen content 

(fuel rod hydrogen test) was performed by GE-NE in accordance with Product/Process 

9 

-58-
Quality Plan 4.0.4, "Uranium Dioxide Fuel Rod Outgassing," Revision 28, dated April 19, 

1994. The practice of performing fuel rod off-gas tests was used primarily as an 

overcheck in the 1970s through 1990s to address hydrating in nuclear fuel components and to assure that moisture was not introduced into the components prior to final end 

plug welding. The primary test to determine fuel pellet hydrogen content is performed routinely by GE-NE for individual samples using the LECO hydrogen analyzer. 

In 1996, GE-NE eliminated the need for off-gassing based on historical data which 

demonstrated that the fuel rod off-gas operation was stable and reliable and provided a 

great deal of margin for the measured attribute of hydrogenous material in fuel pellets. 

GE-NE QA F-D-1613, Revision 0, "Rationale for Elimination of Bi-Weekly Gumball Test," dated April 14, 1994, discussed the technical rationale for elimination of the test. Factors 

included documented historical data (no failures in the bi-weekly testing in the preceding nine years of running such test), enhanced training, use of administration limits, and GE

NE's conversion from the wet to the dry process. Quarterly qualification of all nine 

uranium dioxide furnaces and both Guideline furnaces will continue to be performed. 

The practice, known as a "Gumball" test, required a test rod, filled with 80 fuel pellets, to 

be assembled and processed through a standard off-gas cycle in each oven on a bi

weekly basis. Fuel pellet samples are selected by Shop Operations from a minimum of 4 

and a maximum of 10 production trays representative of the production run. This test 

rod was outfitted with a dummy rod extension and run through one cycle of the furnace 

qualification run. After the off-gas run is completed, the test rod is sent to the Chemet 

Laboratory for hydrogen analysis. A total of 24 pellets are selected for testing using the 

LECO hydrogen analyzer. Test results were recorded onto a "Fuel Rod Hydrogen Test 

Form" and entered into LMCS. Individual values must not exceed 1 part per million 

(ppm) and the average value for the test rod must not exceed 0.8 ppm hydrogen. 

The NRC inspection team selected for review test rod 2CW0701, dated June 15, 1996, 

which was run through furnace 6Z. The test for pellet hydrogen utilized samples from 

pellets 3, 4 and 5 for all eight zones, a total of 24 samples. The average rod value 

reported on the form was 0.12 ppm with the highest individual pellet value reported as 

0.24 ppm. The test was performed in accordance with QA F-Q-2067, Revision 73, dated 

June 23, 1996. 

c. Conclusions 

In 1996, GE-NE eliminated the need for off-gassing based on historical data which 

demonstrated that the fuel rod off-gas operation was stable and reliable and provided a 

great deal of margin for the measured attribute of hydrogenous material in fuel pellets. The test, known as a Gumball test, was an overcheck to determine if additional moisture 

had been introduced during the rod fabrication and loading process. Pellet hydrogen is 

primarily determined by testing samples of individual fuel pellets, taken from actual 

production runs, and testing them using the LECO hydrogen analyzer. This process differs from the Gumball test since it determines pellet hydrogen during the pellet manufacturing phase (after grinding but prior to fuel rod loading). Based on the 

inspection team's review of the Gumball test, the team concluded that the test, 

performed up through 1996, was adequate as an overcheck to determine additional 

moisture introduced during the off-gas process. 

10 

-59-
4 ENTRANCE AND EXIT MEETINGS

During the entrance meeting on September 7, 1999, the inspection team met with 

members of GE-NE management and staff and discussed the scope of the inspection. 

The team also reviewed its responsibilities for handling proprietary information as well as 

those of GE-NE. In addition, the team established contact persons within the 

management and staff of the applicable GE-NE organizations and discussed the results 

of the inspection with management and staff on September 10, 1999. 

PARTIAL LIST OF PERSONS CONTACTED

Reda 

Moneta 

Fuller 

Mack 

Murray 

Baker 

Ball 

Bianchi 

Hudson

Manager, GE-NE Quality 

Manager, GE-NE E'S 

Manager, Fuel & Chemet Lab Quality 

Manager, PMQC/SCQC 

Manager, Regulatory Compliance 

Nuclear Quality Assurance 

Team Leader/Lead Chemist 

Senior Engineer 

Laboratory Analyst

ITEMS OPENED, CLOSED, AND DISCUSSED

Item Number Typ~e Description

Opened

99900003/1999202-01 NON

Closed

99900003/1999201-01 

99900003/1999201-02

NOV 

URI

GE-NE audit of JMS Southeast, Inc., did not 

adequately demonstrate that their quality assurance 

program complied with the requirements of 10 CFR 

Part 21. This item was previously identified as URI 

99900003/1999201-02. 

Failure to identify and evaluate a potential deviation 

related to the lack of calibration of the LECO 

hydrogen analyzer. 

GE-NE could not produce documentation to support 

the resolution of three open CARs identified during 

GE-NE's March 26, 1997, audit of JMS Southeast, 

Inc. This issue has been identified as 

Nonconformance 99900003/1999202-01. 

11 

-60-

C. 

A. 

B. 

R. 

S. 

W. 

J. 

R. 

R.
0I-•. UNITED STATES 

NUCLEAR REGULATORY COMMISSION 

WASHINGTON, D.C. 20555-0001 

October 4, 1999 

Mr. Richard L. Morley, Manager 

Tennessee Valley Authority 

Central Laboratories & Field Testing Services 

1101 Market Street, PSC 1B-C 

Chattanooga, TN 37402 

SUBJECT: NRC INSPECTION REPORT NO. 99901341/99-201 AND NOTICE OF 

NONCONFORMANCE 

Dear Mr. Morley: 

This refers to the inspection conducted by Richard McIntyre of the Quality Assurance, Vendor 

Inspection, Maintenance, and Allegations Branch (HQMB), Jim Davis of the Materials and 

Chemical ,engineering Branch (ECMB), Hukam Garg of the Electrical and Instrumentation and 

Controls Branch and William Bearden and Gary Claxton of the NRC Region II Office on 

August 16-19 ,1999, at the Tennessee Valley Authority (TVA) Central Laboratories and Field 

Testing Services (CL&FTS) facilities in Chattanooga, Tennessee. The purpose of the inspection 

was to review the implementation of TVA CL&FTS activities for the calibration of measuring and 

test (M&TE) equipment and activities related to metallurgical testing and failure analysis. TVA 

provides these services and testing activities as safety related under their 10 CFR Part 50, 

Appendix B, quality assurance (QA) program to TVA nuclear plants and to other NRC licensees. 

At the conclusion of the inspection, the findings were discussed with you and members of your 

staff identified in the enclosed report. 

Overall, the inspection determined that TVA CL&FTS was adequately implementing their 

10 CFR Part 50, Appendix B, QA program for the areas reviewed. However, during this 

inspection the team found that the implementation of your QA program failed to meet certain 

NRC requirements in one inspection area. Specifically, the inspection identified limited 

examples where Nonconformance Reports (NCRs) initiated in 1998 did not receive timely 

resolution and disposition to completion. Also, certain closed NCRs did not include complete 

documentation packages and no reference was given to the other pertinent documentation 

associated with the particular instrument calibration . 

These issues are cited in the enclosed Notice of Nonconformance (NON), and the 

circumstances surrounding it are described in detail in the enclosed report. Please provide us 

within 30 days from the date of this letter a written statement in accordance with the instructions 

specified in the enclosed Notice of Nonconformance.

-61-
Mr. R. L. Morley

In accordance with 10 CFR Part 2.790 of the NRC's "Rules of Practice," a copy of this letter, its 

enclosures, and your response will be placed in the NRC's Public Document Room. Should you 

have any questions concerning this inspection, we will be pleased to discuss them with you. 

Sincerely,

Theodore R. Quay, Chief, IQMB 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation 

Enclosures: 1. Notice of Nonconformance 

2. Inspection Report No. 99901341/99-201

-62-

-2-

.ez- z e:ýt
NOTICE OF NONCONFORMANCE

TVA Central Laboratories & Field Testing Services Docket No. 99901341 

Chattanooga, TN 

Based on the results of an NRC inspection conducted August 16-19, 1999, it appears that 

certain of your activities were not conducted in accordance with NRC requirements. 

A. 10 CFR 50 Appendix B, Criterion V "Instructions, Procedures, and Drawings," 

requires, in part, that activities affecting quality shall be accomplished in accordance 

with documented instructions, procedures or drawings and shall in include 

appropriate quantitative or qualitative acceptance criteria for determining that 

important activities have been satisfactorily accomplished. 

TVA Central Laboratories & Field Testing Services (CL&FTS) Quality Assurance 

Program (QAP) Manual, QAP 7.2, "Control of Nonconformances," Section 5.2.2 

requires the Manager, QAIQC staff to maintain a log of nonconformances to ensure 

timely resolution and disposition. 

TVA CL&FTS QAP 7.2, Section 6.1.3.11, requires that the QA/QC manager or 

designee, perform a final review and approval signifying the NCR is complete by signature and date and forward the completed paperwork to Document Control for 

processing to the Electronic Document Management System (EDMS) and Records 

and Information Management Systems (RIMS) programs. 

1. Contrary to the above, the inspectors identified the following six open 

Nonconformance Reports (NCRs) which were initiated in 1998 and did not 

include timely resolution and disposition to completion. 

• NCR 98087 - initiated on March 23, 1998 

* NCR 98097 - initiated on April 16, 1998 

* NCR 98133 - initiated on July 9, 1998 

• NCR 98163 - initiated on August 27, 1998 

• NCR 98164 - initiated on August 27, 1998 

* NCR 98165 - initiated on August 27, 1998 

2. Contrary to the above, the inspectors identified the following three 

examples where the NCR package did not include complete 

documentation and no reference was given to the other pertinent 

documentation associated with the particular instrument calibration. 

* NCR 99035 

* NCR 99075 

• NCR 99090 

(Nonconformance 99901341/99-01-01) 

Enclosure 1

-63-
Please provide a written statement or explanation to the U.S. Nuclear Regulatory Commission, 

ATTN: Document Control Desk, Washington, D.C. 20555 with a copy to the Chief, Quality 

Assurance, Vendor Inspection, Maintenance and Allegations Branch, Division of Inspection 

Program Management, Office of Nuclear Reactor Regulation, within 30 days of the date of the 

letter transmitting this Notice of Nonconformance. This reply should be clearly marked as a 

"Reply to a Notice of Nonconformance" and should include for each nonconformance: (1) the 

reason for the nonconformance, or, if contested, the basis for disputing the nonconformance, (2) 

the corrective steps that have been taken and the results achieved, (3) the corrective steps that 

will be taken to avoid further noncompliances, and (4) the date when your corrective action will 

be completed. Where good cause is shown, consideration will be given to extending the 

response time. 

Dated at Rockville, Maryland 

this 4 th day of October 1999 

-2-

-64-
U.S. NUCLEAR REGULATORY COMMISSION 

OFFICE OF NUCLEAR REACTOR REGULATION

Report no: 

Organization:

99901341/1999201

"TVA Central Laboratories & Field Testing Services (CL&FTS)

Contact: Sammy Walker, Manager QA/QStaff 

(408) 925-6587

Nuclear Activity: CL&FTS provides services to TVA plants (nuclear and fossil) and 

to the nuclear industry for the calibration and repair of measuring 

and test equipment (M&TE) and also provides a wide range of 

metallurgical analysis and material testing services.

August 16-20, 1999

Richard McIntyre, Team Leader, IQMB 

Jim Davis, EMCB 

Hukam Garg, HICB 

Bill Beardon, Region II 

Gary Claxton, Region II, 01

Approved by: Daniel H. Dorman, Chief , .A'k 

Quality Assurance and Safety Assessment Section 

IQMB 

Division of Inspection Program Management

Enclosure 2

-65-

Date:

Inspectors:
I INSPECTION SUMMARY

The purpose of the inspection was to review the implementation of TVA Central 

Laboratories and Field Testing Services (CL&FTS) activities for the calibration of 

measuring and test equipment (M&TE) and activities related to metallurgical testing and 

material failure analysis. TVA CL&FTS provides these services and testing activities as 

safety related under their 10 CFR Part 50, Appendix B, quality assurance (QA) program 

to TVA power plants (nuclear and fossil) as well as to other nuclear licensees. 

During this inspection, one nonconformance was identified and is discussed in 

Section 3.3 of this report. 

2 STATUS OF PREVIOUS INSPECTION FINDINGS 

No previous inspection findings were examined during this inspection. 

3 INSPECTION FINDINGS AND OTHER COMMENTS 

3.1 Background 

TVA CL&FTS is a diverse engineering and technical service facility that has the 

capability to perform precision instrument calibration and repair; chemical and 

metallurgical analysis; nuclear qualification of commercial grade electrical equipment and 

other materials; specialized engineering services such as environmental qualification; 

and shop services such as the repair of electronic equipment. 

The CL&FTS organization structure includes Instrumentation Services, Analysis and 

Evaluation Services, Field Testing Services Departments, and the QA/C Staff. The 

organization also includes the Business Development/Support Services department. All 

of the calibration of precision M&TE is performed by the Instrumentation Services 

Department. Instrumentation Services is comprised of the following five groups: 

Physical I; Physical II; Electrical I; Electrical II; and Laboratory Standards. The Analysis 

and Evaluation Services department perform a variety of technical support services, 

including metallurgical and material failure analysis by the Metallurgical Services Group. 

The Analytical Chemistry, Oil Analysis, and Environmental qualification Groups are also 

part of the Analysis and Evaluation Services department. 

This inspection was conducted to review the implementation of the TVA CL&FTS 

10 CFR Part 50, Appendix B, QA program as it relates to calibration of M&TE and as it 

relates to metallurgical analysis and material testing. 

3.2 Metallurgical Services 

a. Inspection Scope 

The NRC inspectors reviewed the applicable portions of the CL&FTS QA program 

related to metallurgical analysis and failure analysis. QAP No. 4.10, "Analysis and 

2

-66-
Evaluation Analysis," describes the requirements and delineates the responsibilities for 

management of the CL&FTS Analysis and Evaluation Analysis Department. The 

purpose is to ensure that all analyses/tests performed for the nuclear power industry are 

properly controlled and accomplished in accordance with approved methods and are 

within QA program requirements. Metallurgical Services is a group within the Analysis 

and Evaluation Analysis Department. The inspectors also reviewed selected 

metallurgical Quality Program Instructions (QPIs) and observed implementation of 

several procedures (QPIs) during actual test activities. Emphasis was placed on the use 

of standards traceable to National Institute of Standards and Technology (NIST) 

standards. 

b. Observations and Findings

The following metallurgical QPIs were reviewed by the inspectors:

Instruction No. 

101.02-28 

201.03-001 

202.01-001 

202.01-002 

202.01-003 

202.01-004 

202.01-007 

202.01-008 

202.01-009 

203.02-002 

203.02-003 

206.01-001 

327.03-002 

327.03-003

Title

Metal Analysis using Varian Spectroscopy Atomic 

Absorption-600; 

Determination of Total Carbon and Sulfur in Metals using 

Infrared Spectroscopy; 

Determination of Hardness using a Rockwell Tester; 

Determination of Hardness using a Portable Tester; 

Microhardness Testing of Material; 

Brinell Hardness of Metallic Materials; 

Determination of Hardness using a Rockwell 556T Tester; 

Microindentation Hardness Testing; 

Notched Bar Impact Testing of Metallic Material; 

Recommended Metallographic Techniques; 

Dimensional Measurements for Metal Samples; 

Chemical Analysis by X-Ray Flouresence Spectroscopy of 

Solid Metals; 

Tinius Olsen Super "L" Universal Test Machine; and 

Tinius Olsen 1000 Series Universal Test Machine.

During review of the QPIs the inspectors noted that revisions to the QPIs did not include 

the initials or the signature of the preparer as required by QAP 2.1 Section 6.2.2.2.11. 

QAP 2.1 provided a step-by-step procedure for preparing and approving QPIs. CL&FTS 

demonstrated that for newer QPI sections, the preparer's signature is electronic and the 

presence of the preparer's initials in the document indicates that the preparer has 

electronically signed the document. 

There was no discussion in the QPIs on how the proving rings used to calibrate the 

tensile machines are calibrated and maintained traceable to NIST. CL&FTS staff 

demonstrated that the proving rings are sent to a CL&FTS approved supplier, 

Morehouse, where they are calibrated using standards traceable to NIST. 

3

-67-
Observations Specific to the QPIs Reviewed:

QPIs 202.01-001, 202.01-002, 202.01-003, and 202.01-004, which described various 

methods for determining the hardness of a metallic material, interchanged the 

referencing of National Bureau of Standards (NBS) and National Institute of Standards 

and Technology (NIST) when describing the calibration blocks for these instructions. 

NBS officially changed its name to NIST in the mid 1980's. The TVA staff demonstrated 

to the inspectors that the current Wilson calibration blocks are traceable to NIST. 

Instructions 202.01-001, 202.01-003, and 202.01-004 required that the calibration 

standard serial number be identified and that the test results from the calibration 

standard be included in the final report. Instruction 202.1-02 did not require that the 

calibration standard serial number be identified and referenced and that the test results 

from the calibration standard be reported. TVA staff noted that even though the QPI did 

not include this requirement, Section 4.10 of the QAP Manual requires that the 

calibration standard serial number be identified and referenced and that the test results 

from calibration standard be reported. 

The QPIs 202.01-001, 202.01-002, 202.01-003, and 202.01-004 reference ASTM 

standards that are no longer valid standards since they are more than 5 years old. 

However, the inspectors noted that the ASTM standards referenced in the QPIs do have 

the year of issue specified. This ensures that if an ASTM standard undergoes a 

significant revision, the revised standard does not become the referenced standard, 

possibly without review by the TVA staff. The inspectors verified that CL&FTS has 

recently implemented a new requirement that all quality program instructions are revised 

every 4 years. 

The inspectors pointed out that QPI 202.01-008 references ASTM E-384 with no year 

indicated. CL&FTS staff stated that the 1989 edition of the standard is being used and 

that no modifications to this standard have been made in later editions. CL&FTS staff 

also stated that when the QPI is revised, the appropriate edition of the standard will be in 

the revised standard. 

QPI 202.01-009, on notched bar impact testing of metallic materials, states in the 

General Instructions that this method is used to find brittle materials. The inspectors 

suggested that the General Instructions be modified to state that this method can be 

used to determine ductile-to-brittle transition temperature,. nul-ductility temperature, 

upper shelf energy, and toughness at any temperature. 

Laboratory Environmental Monitoring 

During the tour of the laboratory facilities the inspectors inquired what was the basis for 

the different (680F+/- 1 OF and the 720F +/- 20F) laboratory temperatures that are 

monitored in the various laboratory areas using temperature/humidity chart recorders? 

CL&FTS stated that QAP No. 4.1, "M&TE Calibration Program," Section 7.1, "Facilities 

and Environment," provided references that stated that the 680F+/- 1F or 20 0C room is 

for dimensional measurements conducted in the Standard Laboratory room while the 

4

-68-
72 0F +/- 20F is for other disciplines of metrology such as electrical standards. In addition, 

the relative humidity is maintained below 50 percent. 

The inspectors determined that NCR 99061 was written in December 21, 1998 

identifying inconsistencies between program requirements and laboratory environmental 

monitoring equipment performance. This issue was also identified as audit finding 

(Deviation Report) in the TVA Nuclear (WVAN) Supplier Audit 99V-17, dated June 4, 

1999. This was an external audit of the WVA CL&FTS QA program by WVA Corporate 

Quality Assurance. 

NCR 99061 was closed on March 22, 1999, and the remaining issues were rolled into 

NCR 99125. NCR 99125 was written on August 15, 1999, to address ineffective 

implementation of environmental monitoring described in the above Deviation Report. 

CL&FTS stated that a complete upgrade of laboratory environmental monitoring was 

ongoing as part of the corrective actions described by CL&FTS to the TVAN deviation 

Report 99V-17-1. These corrective action activities, if adequately implemented and 

completed, appear to address the TVA CL&FTS internal and TVAN Corporate external 

audit finding concerns with CL&FTS laboratory environmental monitoring. 

Review of Implementation of CL&FTS Testing Activities 

The inspectors observed a demonstration of the preparation of material samples and the 

testing of samples using X-Ray Fluorescence Spectroscopy to determine the chemical 

composition of the metal sample using QPI 206.01-001. The inspectors were also 

provided a demonstration of the preparation of samples and the Infrared testing of metal 

samples to determine carbon and sulfur. The use of calibration standards for each 

method was also demonstrated. The technician conducting these procedures knew the 

procedures in detail and had no difficulty in preforming the tests. The technician was 

asked what metallurgical procedures he conducted. He stated that it is CL&FTS policy 

that all laboratory technicians are trained to conduct all of the procedures in the 

Metallurgical Laboratory. The inspectors stated that this was somewhat unusual to have 

a technician trained on more than one or two pieces of equipment. However, the 

inspectors did not identify any problems with the conduct of the tests and did find that the 

cross-training on the various QPIs was desirable. 

c. Conclusion 

During the review of the QPIs the inspectors identified a number of observations and 

identified areas that required clarification by CL&FTS. CL&FTS was able to answer all 

questions and clarify the inspectors issues related to the observations. Based on this, no 

nonconformances were identified during this portion of the inspection. The NRC 

inspectors were given demonstrations of the X-Ray Fluorescence Spectroscopy test to 

determine chemical composition and the Infrared analysis test to determine carbon and 

sulfur concentration. The technician conducting the tests was well trained and was very 

knowledgeable in performing all the steps and procedural requirements. Finally, 

5

-69-
the recent and ongoing long term upgrades to hardware and software for environmental 

monitoring of temperature and humidity should provide adequate coverage to satisfy the 

accuracy requirements of the QAP. 

3.2 Training and Qualifications of TVA CL&FTS Personnel 

a. Inspection Scooe 

The team reviewed training and personnel records for selected managers, laboratory 

technicians and calibration personnel in both the Instrumentation Services and Analysis 

and Evaluation Services groups to verify that those personnel were adequately trained 

and qualified as per TVA CL&FTS QAP requirements to perform safety-related work 

activities. 

b. Observations and Findings 

The team reviewed training and personnel history records (PHRs) for the Quality 

Assurance/Quality Control Manager, Instrumentation Services Manager, five 

instrumentation department program administrators, and the Lead Metallurgical 

Engineer. Additionally, training records and PHRs for one quality specialist and 

10 technical personnel were reviewed. At least one supervisor and one technician from 

the Metallurgical Laboratory and each of the fivegroups in the Instrumentation Services 

Department were included in this review. Each individual's academic training and 

experience was evaluated and compared to the specific requirements stated in the 

associated job description to verify that these personnel were qualified to perform work 

activities commensurate with their responsibilities. 

The team determined that, for those training records and PHRs reviewed, selection of 

management and technical personnel met the academic training and experience 

requirements contained in the associated WVA job descriptions. Each individual's level 

of training and previous work experience satisfied the minimum stated requirements prior 

to that individual being placed in the respective position. In most cases the individual's 

actual experience level was well above the minimum required years of on-the-job 

experience. 

CL&FTS QAP No. 11.1, Rev. 8, "Quality Assurance Indoctrination and Technical 

Training", requires CL&FTS personnel to receive initial indoctrination training including 

training on quality assurance requirements. Additionally, each individual was required to 

receive an initial evaluation of on-the-job performance prior to independent performance 

of assigned duties. In most cases individuals had received the required level of initial 

indoctrination training and qualification was properly documented prior to that individual 

performing safety-related work activities. However, the team identified one example of a 

manager that had performed safety-related work activities prior to completion of initial 

indoctrination training. 

The Instrumentation Services Manager, who had newly reported to the CL&FTS facility 

on August 15, 1998, had not completed initial indoctrination training until October 1, 

6

-70-
1998. In this case, the individual had considerable experience as an instrumentation 

engineer and instrumentation supervisor at TVA's Sequoyah Nuclear Plant, was fully 

qualified in the new position. This issue had been considered after the newly assigned 

manager had been placed directly in the position. CL&FTS management had decided 

that a problem had not existed since all quality related work activities would receive 

additional review and signature from the Quality Manager or another qualified manager 

until such time that indoctrination training was completed. However, a small number of 

work related documents were processed without this additional level of review prior to 

October 1, 1998. The failure to satisfy indoctrination training requirements had occurred 

due to a lack of sensitivity by CL&FTS management and Quality Assurance personnel. 

The team noted that this had been an isolated case and that only a small number of work 

activities had been affected. 

The inspectors determined that this problem had previously been self-identified by 

CL&FTS personnel and documented in NCRs 99032 and 99033 on November 6, 1998. 

Corrective actions included verification of completed indoctrination training and review of 

all potentially affected documents to determine impact on quality related work activities. 

CL&FTS quality assurance personnel verified that only 4 out of 183 potentially affected 

records had included the new manager's signature as the sole authorizing signature. Additionally, no problems were identified during the subsequent review of those records. 

The inspectors emphasized that the process used to qualify the newly hired manager 

was contrary to requirements of QAP 11.1, Section 6.1.1, but no nonconformance would 

be written based on the fact that it had been self-identified and corrective actions had 

been comlpeted. 

The team determined that periodic training on revisions to CL&FTS QAP manual, 

procedures and quality assurance requirements was adequate. In each case, for those 

training records reviewed, documentation was available to show that personnel had 

received additional training associated with significant program or procedure changes. 

Additionally, each individual was required to receive an annual evaluation of on-the-job 

performance in order to continue to independently perform assigned duties. 

c. Conclusions 

Based on the information reviewed the inspectors concluded that CL&FTS personnel 

were adequately qualified to perform assigned duties. The team did identify one 

example of a manager that had performed safety-related work activities prior to 

completion of initial indoctrination and training. However, the one example described 

above was an isolated case and had been previously self-identified and included and 

addressed by the TVA CL&FTS NCR process. 

3.3 Instrumentation Services 

a. Inspection Scope 

During this inspection, the NRC inspectors reviewed selected calibration reports, Quality 

Program calibration instructions, nonconformance reports (NCRs), and observed a 

7

-71-
demonstration of the computerized Labmate calibration report process and the Electronic 

Document Management System (EDMS) and Records and Information Management 

Systems (RIMS) programs. 

QAP No. 4.1, "M&TE Calibration Program," describes the requirements and delineates 

the responsibilities for management of the CL&FTS calibration program. The purpose is 

to ensure that M&TE calibrated for use in the nuclear power industry is properly 

controlled and calibrated at specific intervals. 

b. Observations and Findings 

Calibration Instructions 

During this inspection the following two QPIs were reviewed by the inspector: 

Instruction No. Title Rev. Date Rev. level 

308.01-009 Resistance Test Boxes 8/23/90 01 

416.01-009 Scientific Columbus Transducer Calibrator 1/6/97 09 

The first instruction was very simple and the second was complex. During the review, 

the inspector noted that the originator had not signed the instruction. The TVA CL&FTS 

personnel explained that when the original instruction is written the originator also signs 

the instruction, however, once the instructions are written by the computer, the originator 

is not required to sign the instruction. TVA showed the signature of the originator on the 

original instruction which resolved the instructor's concern. The inspector also requested 

the originator (J. Moore) for the second instruction to demonstrate how the instruction is 

used during actual calibrations. Mr. Moore demonstrated one portion of the instruction, 

"Voltage Calibration," to the inspector in a step by step manner. Other portions of the 

instruction for "Current Calibration," "Power Calibration," and "Error Meter Calibration" 

were also explained by the originator. Based on this demonstration, the inspector was 

able to determine that the instructions are adequate for these calibrations. 

The inspector also noted that the format for the instructions included many sections such 

as, Maintenance, Data Evaluation, Final Check, and Process, but most of the instruction 

does not include any instruction for performing these sections. CL&FTS explained that 

the format is standard format and provide flexibility to add additional information when 

required. The inspector was satisfied with the CL&FTS's explanation. 

Calibration Reports 

The inspector requested CL& FTS to provide a list of calibration work which was 

performed for external contracts (non TVA plants) during last two years. CL&FTS 

provided the list and the inspector selected the following reports for two clients, Cooper 

Nuclear Station and Crane Movats for review. 

8

-72-
Report No. Date

1000019567 10/21/98 Cooper Nuclear Station Deadweight Tester- Pneumatic 

1000018563 9/11/98 Cooper Nuclear Station Deadweight Tester- Hydraulic 

E28473 5/18/99 Cooper Nuclear Station Digital Multimeter 

1000027403 6/10/99 Cooper Nuclear Station Electrostatic Voltmeter 

1000028453 5/13/99 Cooper Nuclear Station Resistance Meter 

1000028897 6/03/99 Crane Movats Deadweight Tester- Hydraulic 1000028971 5/26/99 Crane Movats Megohmmeter 

During the review of the reports the inspectors noticed that some reports were signed by 

the originator and others were not signed by the originator. The inspector was 

concerned that the reports could be changed without the knowledge of the originator. The inspector requested CL&FTS to provide some calibration reports which have been 

revised at a later date. The inspector reviewed the following revised calibration reports: 

Report No. Date Client Item 

1000029120 6/3/99 Peco Energy Co. Torque Wrench (Indicating) 1000027927 4/28/99 Browns Ferry NP Impulse Rotary Transducer 

1000029741 6/21/99 Browns Ferry NP Digital Pressure Gauge 

1000027097 5/4/99 Watts Bar NP Conductivity/ph Meter 

1000024946 3/1/99 Browns Ferry NP Sling Psychrometer 

The inspector noticed the same pattern on these reports also. The inspector questioned 

CL&FTS to explain how the originator becomes aware of the changes made to the 

calibration report by the approving personnel, as it seems the originator never signs the 

report. CL&FTS explained that the organization is small and all personnel work in the 

close proximity. Therefore, if any questions or problems are identified by the approving 

person, he will first talk to the originator before making any changes to the calibration 

report. CL&FTS also explained that only the Physical I Group requires the originator to 

sign the calibration report. This is a requirement only in the Physical I Group and is in 

addition to the requirements of section 6.6.2.18.1 of QAP No. 4.1, Rev. 10, "M&TE 

Calibration Program," dated 1/15/99. 

CL&FTS also explained that all the calibration reports are contained in EDMS/RIMS and 

is accessible to all personnel. CL&FTS also explained that the Labmate program which 

is used to generate the calibration report is also available to all technicians and 

managers. The inspector also observed the demonstration of the Labmate and 

confirmed the accessibility of the calibration report from the Labmate. However, once 

the technician or the originator of the calibration report signs the report he will no longer 

be able to access and make any changes to the report. But, if he does have any problem with the calibration report, he can raise and hopefully resolve the issue with the 

reviewer. During interactions with technicians, the inspectors also determined that 

technicians are not trained on the accessibility of the document from the EDMS. 

CL&FTS explained that all the management personnel were trained on the system and 

9

-73-

Client Item
were then asked to train personnel working for them. However, this may not have 

occurred because of time, priorities or some other reasons. The team recommended 

and CL&FTS management committed to conduct formal training for technicians on the 

EDMS. The team considered this to satisfactorily resolve the concern. 

Nonconformance Reports 

CL&FTS QAP No. 7.2, "Control of Nonconformances," establishes the requirements and 

assigns the responsibilities to ensure the identification, documentation, control, and 

disposition of items and activities that do not conform to the CL&FTS QA requirements. 

The inspector requested CL&FTS to provide a list of all Nonconformance Reports 

(NCRs) that had been issued during the last two years. CL&FTS provided the NCR 

logbooks for fiscal years (FY) 98 and 99. The inspector selected the following NCRs for 

review:

NCR No. Date Item Description NCR Description

2/27/98 Pressure Controller 

4/29/98 Load Cell with Indicator 

8/27/98 Standard Resistor 

9/8/98 Instruction 307.04-004 R2 

Instruction 406.02.018 RO 

11/9/98 Teraohmmeter 

1/25/99 Deadweight Tester 

1/28/99 Spreadsheet 

3/24/99 DC Reference Standard 

4/21/99 Proving Ring 

7/19/99 AC Voltmeter 

7/20/99 Spreadsheet

Calc Error in spreadsheet 

Incorrect Standard No. 

Out of Tolerance 

Instructions not dated 

Failed in Service 

Out of Tolerance 

Error on Page 5 

Instr Cal light not lit 

Uncertainty CaIc. does not 

Conform to ASTM E74-95 

Metcal Proc. SCR990075 RO 

uses wrong voltage at Test 

Point No. 27.004 

Out of tolerance condition

3/3/98 

7/23/98 

Open 

11/12/98 

11/23/98 

2/2/99 

2/22/99 

6/18/99 

Open 

CAR99-02 

Open 

Open

The inspectors noted that the threshold used for identifying and documenting NCRs at 

CL&FTS was very low and consider this as an apparent strength in the NCR process. 

This was evident since the number of NCRs issued in FY 98 was 179 and 203 so far for 

FY 99. Also, QAP No. 7.2, Section 5.4.1 states that any employee can issue an NCR for 

any suspect deficiency in characteristic, documentation, procedure, process or method 

which renders the quality of an item or report data unacceptable or indeterminate and 

notifies the immediate supervisor and/or department manager. 

10

-74-

Completed

98079 

98102 

98163 

98168 

99035 

99075 

99077 

99106 

99123 

99182 

99185
NCR Disposition and Closure

CL&FTS QAP No. 7.2, Section 5.2.2 requires the Manager, QA/QC staff to maintain a 

log of nonconformances to ensure timely resolution and disposition. The inspector 

determined that QA/QC manager issues the list of all open NCRs weekly to all 

supervisors. The inspector requested the latest list documenting the open NCRs. Upon reviewing the list dated 8/19/99, the inspector noted that there were six NCRs which 

were initiated in 1998 but were still open. During the review of NCR 98163, the inspector noted that the corrective actions were identified for the closure of the NCR. However, 

corrective actions had not been implemented and the NCR was still open. CL&FTS 

explained that this NCR is applicable to Standards Laboratory and just one technician 

and his supervisor are assigned to work in the Standards Lab. The technician was the 

initiator of the NCR and the supervisor was the reviewer of the NCR. Therefore, both are 

quite familiar with and are following the requirements of the corrective actions. CL&FTS 

agreed that this NCR should have been closed in a timely manner but somehow had 

fallen through the cracks. The failure to ensure timely resolution and disposition of six 

NCRs issued during FY 98 per the above QAP requirement was identified as the first 

example of Nonconformance 9990134/99-01-01. 

CL&FTS QAP No. 7.2, Step 6.1.3.11, requires that the QA/QC manager or designee, perform a final review and approval signifying the NCR is complete by signature and 

date and forwards the completed paperwork to Document Control for processing to 

EDMS/RIMS. However, during the review of the NCRs, the inspector identified that 

NCR packages, NCRs 99035, 99075 and 99090, did not include complete 

documentation and no reference was given to the other documentation. 

CL&FTS explained that EDMS will identify all the documentation associated with the 

particular instrument in calibration and they produced the documentation when 

requested. However, the inspector concluded that the procedure requires a complete NCR package be sent to EDMS, hence, either all the document should be referenced in 

the NCR or should be attached to the NCR. The inspector was also concerned that the 

once the NCR is closed, the initiator of the NCR does not get the copy of the completed NCR package. The failure to include the complete NCR documentation package or a 

reference to all the documentation associated with the particular instrument calibration 

per the above QAP requirement was identified as the second example of 

Nonconformance 9990134/99-01-01. 

CL&FTS explained that to the inspectors that all the NCRs are available on the EDMS 

and could be retrieved by anyone. The inspector observed the demonstration of EDMS 

and determined that the document could be easily retrieved from the EDMS but all the 

personnel should be trained to use it effectively. As discussed previously, the team 

recommended and CL&FTS management committed to conduct formal training for 

technicians on the EDMS. 

11

-75-
C. Conclusions

Based on the information reviewed the inspectors concluded that CL&FTS personnel 

were adequately implementing the QA program requirements for the calibration of M&TE 

with the exception of the two NCR examples identified above in Nonconformance 

9990134/99-01-01. 

4.0 LIST OF PERSONS CONTACTED 

Richard L Morley, Manager, Central Laboratories & Field Testing Services 

Sammy R. Walker, Manager, QA/QC Staff 

Douglas Snyder, QA/QC Specialist 

Scott Long, Manager, Instrumentation Services, 

Rick Grau, Manager, Analysis & Evaluation Services 

Joe Saxon, Program Administrator, Physical I 

Lynn Crawford, Program Administrator, Physical II 

Roger Phillips, Program Administrator, Electrical I 

Vince Kmet, Program Administrator, Electrical II 

Jerry Moore, Supervisor, Laboratory Standards 

12

-76-
Selected Generic Correspondence on the Adequacy of 

Vendor Audits and the Quality of Vendor Products 

Identifier Title

Information Notice 99-34 Potential Fire Hazard in the Use of Polyalphaolefin in Testing of 

Air Filters

-77 -
NRC FORM 335 U.S. NUCLEAR REGULATORY COMMISSION 1. REPORT NUMBER 

(2-49) (AssIgned by NRC, Add Vol., Supp., Rev., 

NRCM 110Z and Addendum Numbers, If any.) 

3ol, 3o2 BIBUOGRAPHIC DATA SHEET 

(See ushatco. on & ree, NUREG-0040 

2. TITLE AND SUBTITLE Vol. 23, No. 4 

Ucensee Contractor and Vendor Inspection 3. DATE REPORT PUBLISHED 

Status Report 

Quarterly Report MONTH j YEAR 

October- December 1999 June 2000 

4. FIN OR GRANT NUMBER 

5. AUTHOR(S) 6. TYPE OF REPORT 

Quarterly 

7. PERIOD COVERED (inclusive Dawes) 

October - December 1999 

8. PERFORMING ORGANIZATION - NAME AND ADDRESS (f NRC, provide Diviswor Ofl'ce cr Region, U.S. Nucler Regulalory Commniss•on, and mailing address; if contractor, 

prov- nww and mnag addh.asj 

Division of Inspection Program Management 

Office of Nuclear Reactor Regulation 

U.S. Nuclear Regulatory Commission 

Washington, DC 20555-0001

9. SPONSORING ORGANIZATION - NAME AND ADDRESS (If NRC, l,pe "Same as above', if contracto, provide NRC Division, Oi0ce arRegion, U.S. NuclawRegulatory Commission, 

and mailing address.)

Same as above.

10. SUPPLEMENTARY NOTES

11. ABSTRACT (200 wads cres) 

This periodical covers the results of inspections performed by the NRC's Quality Assurance, Vendor Inspection and Maintenance 

Branch, that have been distributed to the inspected organizations during the period October through December 1999.

12. KEY WORDS/DESCRIPTORS (List words arpphrases Wat wifassist erers in kw.abwng repor.) 13. AVAILABILITY STATEMENT 

Vendor Inspection unlimited 

14. SECURITY CLASSIFICATION 

(This Page) 

unclassified 

(This Repot) 

unclassified 

15. NUMBER OF PAGES 

16. PRICE

NRC FORM 335 (2-89)
Federal Recycling Program
NUREG-0040, Vol. 23, No. 4 LICENSEE CONTRACTOR AND VENDOR INSPECTION STATUS REPORT 

OCTOBER- DECEMBER 1999

UNITED STATES 

NUCLEAR REGULATORY COMMISSION 

WASHINGTON, D.C. 20555-0001

years

JUNE 2000