Report 

on measurements of flue gas emissions and efficiency 

in combination with a type test of a boiler for solid fuel 

Test laboratory TOV SOD Industrie Service GmbH 

Prufbereich Warmetechnik 

DAkkS Akkreditation no. D-PL-14153-04 

accredited according to DIN EN ISO/IEC 17025 

Subject of test Heating boiler for solid fuel 

Type: BioWIN 600 Premium and BioWIN 600 Exklusiv 

Fuel: Compressed wood 

Fuel fed: automatic stoking 

Combustion air supply: with an induced draught fan 

Customer Windhager Zentralheizung Technik GmbH 

Anton-Windhager-Strasse 20 

5201 SEEKIRCHEN, AUSTRIA 

Manufacturer Windhager Zentralheizung Technik GmbH 

Anton-Windhager-Strasse 20 

5201 SEEKIRCHEN, AUSTRIA 

Scope Evaluation of CO emissions 

Evaluation of emissions of unburnt hydrocarbons 

Evaluation of dust emissions 

Evaluation of efficiency 

Date: 2012-03-28 

Our reference: 

IS-TAF-MUC/sl 

Report no. H-DK51190-00/12 

Order no. 1806552 

Document: 

H-DK51190 0012.doe 

Page 1 

This document includes 

4 pages 

Excerpts from this document 

may only be reproduced and 

used (or adverlising purposes 

with the express written 

approval of TUV SUD 

Industrie Service GmbH. 

The tesl results refer exclusively 

to the units under test. 

Expert 

Period of test 

Basis of test 

Dipl.-Ing. Uwe Schlosser 

March 2012 

DIN EN 303-5:1999-06. clause 4.2 

,,.~'~"'- "

~~~ DAkkS 

Deutsehe 

Akkredltlerungsstelie 

O PL-14153-04-00 

Headquarters: Munich Telefon: +49 89 5190 -1027 Trade Register Munich HRB 96 869 Supervisory Board: Telefax: +49 89 5190 - 3307 VAT ID No. DE129484218 Karsten Xander (Chairman) E-mail feuerung@tuev-sued.de Informagon pursuantto Section 2(1) Board of Management: www.tuevsued.dells DL-InfoV(Germany)at FerdinandNeuwieser(CEO), ® 

www.tuev-sued.comfimprint Dr. Ulrich Klotz, Thomas Kainz T;J~/ 

TUV SUD industrie Service GmbH 

Feuemngs- und Warmetechnik 

Ridlerstrasse 65 

80339 Munich 

Germany 
Page 2 of 4 

Our reference / date: IS-TAF-MUC/sl, 2012-03-28 

Document: H-DK5 1190_0012.doc 

Report no. H-DK51190A0/12 sou, 

industrie Service 

Scope 

The manufacturer orders the evaluation of ineasurements on flue gas emissions and 

efficiency. Basis for the evaluation are the results documented in the test report no. 

H-05 1 1 90-00/11 dated 2011-02-09. 

Basis of test 

DIN EN 303-5:1999-06 Heating boilers for solid fuels, hand and automatically 

stocked, nominal heat output of up to 300 kW, clause 4.2 

3 Test documentation 

Test report no. H-05 1190-00/11 dated 2011-02-09 on the test of performance 

requirements of the heating boiler type BioWIN 600 Premium and BioWIN 600 Exklusiv 

Description 

The boilers were type-tested according to the requirements of DIN EN 303-5:1999-06 by 

the test laboratory for firing and heating technology of TUV SOD Industrie Service GmbH. 

A detailed description of the boilers and the test for boiler performance are documented in 

test report no. H-05 1190-00/11. In the type test a measurement was included for CO, 

unburnt hydrocarbons, dust emission and efficiency. 
Page 3 of 4 

Our reference / date: IS-TAF-MUC/si, 2012-03-28 

Document: H-DK51190_0012.doc 

Report no. H-DK5 1190-00/12 

Industrie Service 

5 Measurement and analysis methods 

5.1 CO2/ CO measurement 

For the CO2/ CO measurement a calibrated device on the principle infrared absorption 

was used. The values are measured continuously during the complete test period. The 

mean values for COZ/ CO are 

13.8 % / 45 ppm (maximum load) 

- 9.3 % / 100 ppm (minimum load) 

5.2 Unburnt Hydrocarbons 

For the measurement of unburnt hydrocarbons a calibrated device on the principle of 

flame ionisation detection (FID) was used. The calibration was performed on the basis of 

propane (C3 H8). The values for unburnt hydrocarbons are measured continuously during 

the complete test period. The mean values for unburnt hydrocarbons are 

1 ppm (maximum load) 

1 ppm (minimum load) 

5.3 Particulate emission (dust) 

For the measurement of the particulate emission (dust) a calibrated filter instrument and a 

calibrated balance were used in a gravimetric procedure according to CEN/TS 15883, 

annex A. The dust emission was measured 4 times in the test period. Each period of 

measurement takes 30 minutes with a constant volume of the sample. The mean values 

for dust emission are 

21 mg/m' (maximum load, related to standard reference conditions) 

15 mg/m3(minimum load, related to standard reference conditions) 

5.4 Efficiency 

The test was performed by TOV SOD Industrie Service GmbH using a test rig according to 

picture A.2 of EN 304:2004-01. The values are measured continuously during the 

complete test period. The mean values for direct efficiency are 

90.1 % (maximum load) 

90.0 % (minimum load) 
Page 4 of 4 

Our reference / date: IS-TAF-MUC/sl, 2012-03-28 

Document: H-DK51190_0012.doc '. ~ 

Report no. H-DK5 1190-00/12 crin . 

Iridustrie Service 

Summary 

The emissions and efficiency as documented in report no. H-05 1190-00/11 are measured 

in line with EN 303-5 regarding the determination of inorganic and organic 

gaseous or particulate air constituents, 

using existing procedures in the quality system of the laboratory for firing and 

heating technology and 

using calibrated measurement devices. 

The calculation of the measured emissions data with reference to 10 % 0 2 and on the 

measured data on efficiency as required by EN 303-5 is documented in the test report 

no. H-05 1190-00/11. 

Feuerungs- und Warmetechnik 

Prufbereich Warmetechnik 

~ ~.~~.v 

Johannes Steig~chner 

The Expert 

A~ 

Uwe Schlosser