CCTP Typ: LOGISTICS PLATEFORM – GTB-Solution “DALI 2”

## LIGHTING CONTROLS

Generally, lighting management will be carried out by presence and brightness detectors. The nature of the detectors, the number, the brightness, and time delay adjustment values will be adapted to the premises and to the controlled lighting sources. Circuits will be properly subdivided so that only dark areas are lit during the day. All detectors must be adjustable by remote control.

## Principles of operation and material requirements

### 1- Small Rooms Management:

Automatic operation by presence and light sensor

Typical detector PD3N-1C for ceiling mounting (recessed or surface-mounted depending on the nature of the ceiling) of the BEG LUXOMAT brand or technically equivalent and will have the following characteristics:

Degree / protection class: IP44, FC: IP54/Class II/CE Detection area: h=2,50 m: Ø 10 m across, 6 m towards, 4 m activity seat Switching power: 2300W cos φ 1/1150VA cos φ 0.5, LED 300W maxi Follow-up time: 30 s to 30 min or pulse / Brightness: 10 to 2500 Lux Applications: Toilets / Lockers rooms / Equipment rooms / Airlocks…

Detector type PD9-M-1C-IP65-FC for flush ceiling mounting, brand BEG LUXOMAT or technically equivalent, with the following characteristics

Protection class: Detection head: IP65/Class III/CE, Power supply IP20/Class II/CE Detection area h=2.50 m: Ø 10 m across, Ø6 m towards, Ø4 m seated Switching power: 2300W cos φ 1/1150VA cos φ 0.5, LED 300W max Follow-up time: 15 s to 30 min or pulse / Brightness: 10 to 2000 Lux Application: Showers

2- Management of the administrative building and storages: The lighting management will be based on DALI2 technology, according to IEC 62386 standard. The DALI bus will be used to connect luminaires and presence detectors via controllers or bus interfaces connected to the BMS. The management system will automatically dim the lighting to consider the natural light inflow and will allow the light sources to be completely switched off when unoccupied. This solution will offer the possibility of easily modifying the partitions, without intervention on the luminaires or the wiring, and will have to be evolutionary allowing to anticipate a possible extension to new installations. Each luminaire will be addressed individually, to report the status and defects of each device to the supervision system.

Through the components connected to the BUS, this solution will provide the following characteristics:

2.1- Management of Offices and Meeting Rooms

- - management by presence or absence detection / Lighting variation, constant lighting threshold - management by presence or absence detection / Lighting variation, constant lighting threshold
- - overrides by local PB or by "wireless" interface - overrides by local PB or by "wireless" interface
- - of lighting scenarios and/or atmospheres in the meeting rooms for projection or videoconferencing - of lighting scenarios and/or atmospheres in the meeting rooms for projection or videoconferencing
- - of air renewal by information from presence sensors to the HVAC package - of air renewal by information from presence sensors to the HVAC package

2.2- Management of Circulation and Stairwells

- - management by presence and luminosity detection - management by presence and luminosity detection
- - lighting management system will offer the possibility of creating an intelligent operation of the corridors, thus allowing energy - lighting management system will offer the possibility of creating an intelligent operation of the corridors, thus allowing energy savings. Only the occupied zone will be switched on at the regulatory value, and in anticipation, the upstream zone will be switched on at reduced power (10 / 20%)
- - the stairwells, this solution will ensure level by level operation - the stairwells, this solution will ensure level by level operation
- 2.3- Dock management
- - management by presence and luminosity detection - management by presence and luminosity detection
- - to 10% of the set point if the platform is unoccupied for a predefined time or permanently during operating hours - to 10% of the set point if the platform is unoccupied for a predefined time or permanently during operating hours
- 2.4- Management of loading zones, storage aisles and rack access routes
- - management by presence detection High Bay - management by presence detection High Bay
- - lighting management system will offer the possibility of creating an intelligent operation of the access aisles to the racks and - lighting management system will offer the possibility of creating an intelligent operation of the access aisles to the racks and in the racks, thus allowing energy savings. Only the occupied zone will be switched on at the regulatory value, and in anticipation, the upstream zone will be switched on at reduced power (10 / 20%). In the event of prolonged activity in a rack, the traffic light will remain switched on to indicate the presence of a person in the rack.

The selected sensors will be " Multi-Master " on DALI 2 protocol of BEG LUXOMAT brand or technically equivalent and will have the following technical characteristics:

- - DALI type PDx-BMS-DALI2 - DALI type PDx-BMS-DALI2
- DALI Multi-Master technology according to IEC 62386, part 103
- Compatible with DALI 2 controllers according to IEC 62386 part 101/103/304. Section 0 provides information on room assignment and motion detection on the DALI bus according to IEC 62386 part 303. Section 1 provides the LUX values on the DALI bus