Module
AF3K-THP
AF4K-THP
AF5K-THP
AF6K-THP
PV Input
Max. DC Input Power (kW)
5
6
7.5
9
Max. PV Voltage (V)
1000
Rated DC Input Voltage (V)
620
DC Input Voltage Range (V)
150 - 1000
MPPT Voltage Range (V)
150 - 850
Full MPPT Range(V)
200 - 850
250 - 850
Start-up Voltage (V)
160
Max. DC Input Current (A)
20 x 2
Max. Short Current(A)
30 x 2
No. of MPPT Tracker / Strings
2/2
Battery Port
Battery Nominal Voltage (V)
100
100
100
150
Battery Voltage Range (V)
80 - 600
Max. Charge/Discharge Current (A)
50
Max. Charge/Discharge Power (W)
3K
4K
5K
6K
Charging Curve
3 Stages
Compatible Battery Type
Li-ion battery
AC Grid Output
Nominal AC Output Power (VA)
3000
4000
5000
6000
Max. AC Input Power
4500
6000
7500
9000
Max. AC Output Current (A)
5.3
7
8.5
10.5
Nominal AC Voltage (V)
230 / 400
Nominal AC Frenquency (Hz)
50 / 60
Power Factor
1（- 0.8 - 0.8）
Current THD (%)
< 3 %
AC Load Output (Back-up)
Nominal Output Power (VA)
3000
4000
5000
6000
Nominal Output Voltage (V)
230 / 400
Nominal Output Frequency (Hz)
50 / 60
Nominal Output Current (A)
4.4
5.8
7.3
8.7
Peak Output Power
3300VA, 60s
4400VA, 60s
5500VA, 60s
6600VA, 60s
THDV (with linear load)
< 3 %
Switching Time (ms)
< 10
Eﬃciency
Europe Eﬃciency
97.50 %
Max. Eﬃciency
98.00 %
Battery Charge/Discharge Eﬃciency
98.00 %
Protection
Reverse Polarity Protection
Yes
Over Current / Voltage Protection
Yes
Anti-islanding Protection
Yes
AC Short-ciruit Protection
Yes
Leakage Current Detection
Yes
Ground Fault Monitoring
Yes
Grid Monitoring
Yes
Enclosure Protect Level
IP65
General Data
Dimensions (W x H x D, mm)
558 x 535 x 260 mm
Weight (kg)
29kg
Topology
Transformerless
Cooling Concept
Intelligent Fan
Relatively Humidity
0 - 100 %
Operating Temperature Range (°C)
- 25 to 60 °C
Operating Altitude (m)
< 4000
Noise Emission (dB)
< 30
Standby Consumption (W)
< 5
Display & Communication Interfaces
LCD, LED, RS485, CAN, Wi-Fi, GPRS, 4G
Certiﬁcation & Approvals
NRS097, G98/G99, EN50549-1, C10/C11, AS4777.2, VDE-AR-N4105, VDE0126, IEC62109-1, IEC62109-2
EMC
EN61000-6-2, EN61000-6-3
Module
AF8K-THP
AF10K-THP
AF12K-THP
PV Input
Max. DC Input Power (kW)
12
15
18
Max. PV Voltage (V)
1000
Rated DC Input Voltage (V)
620
DC Input Voltage Range (V)
150 - 1000
MPPT Voltage Range (V)
150 - 850
Full MPPT Range(V)
300 - 850
500 - 850
Start-up Voltage (V)
160
Max. DC Input Current (A)
20 x 2
Max. Short Current(A)
30 x 2
No. of MPPT Tracker / Strings
2/2
Battery Port
Battery Nominal Voltage (V)
200
250
300
Battery Voltage Range (V)
80 - 600
120 - 650
Max. Charge/Discharge Current (A)
50
Max. Charge/Discharge Power (W)
8K
10K
12K
Charging Curve
3 Stages
Compatible Battery Type
Li-ion battery
AC Grid Output
Nominal AC Output Power (VA)
8000
10000
12000
Max. AC Input Power
12000
15000
18000
Max. AC Output Current (A)
13.5
17
21.5
Nominal AC Voltage (V)
230 / 400
Nominal AC Frenquency (Hz)
50 / 60
Power Factor
1（- 0.8 - 0.8）
Current THD (%)
< 3 %
AC Load Output (Back-up)
Nominal Output Power (VA)
8000
10000
12000
Nominal Output Voltage (V)
230 / 400
Nominal Output Frequency (Hz)
50 / 60
Nominal Output Current (A)
11.6
14.5
17.4
Peak Output Power
8800VA, 60s
11000VA, 60s
13200VA, 60s
THDV (with linear load)
< 3 %
Switching Time (ms)
< 10
Eﬃciency
Europe Eﬃciency
97.50 %
Max. Eﬃciency
98.20 %
98.30 %
Battery Charge/Discharge Eﬃciency
98.00 %
Protection
Reverse Polarity Protection
Yes
Over Current / Voltage Protection
Yes
Anti-islanding Protection
Yes
AC Short-ciruit Protection
Yes
Leakage Current Detection
Yes
Ground Fault Monitoring
Yes
Grid Monitoring
Yes
Enclosure Protect Level
IP65
General Data
Dimensions (W x H x D, mm)
558 x 535 x 260 mm
Weight (kg)
29kg
Topology
Transformerless
Cooling Concept
Intelligent Fan
Relatively Humidity
0 - 100 %
Operating Temperature Range (°C)
- 25 to 60 °C
Operating Altitude (m)
< 4000
Noise Emission (dB)
< 30
Standby Consumption (W)
< 5
Display & Communication Interfaces
LCD, LED, RS485, CAN, Wi-Fi, GPRS, 4G
Certiﬁcation & Approvals
NRS097, G98/G99, EN50549-1, C10/C11, AS4777.2, VDE-AR-N4105, VDE0126, IEC62109-1, IEC62109-2
EMC
EN61000-6-2, EN61000-6-3