标题：消防增压泵
简介
XBD消防增压泵 ，是消防泵中具有较强增压功能的泵。  XBD消防增压泵产品型号： XBD 
产品详细介绍
产品详细介绍
XBD消防增压泵材质零件名称 材料 
泵 体 HT250
叶 轮 2Cr13 01 
泵体密封环 铸铁HT200 
轴套 球 铁 
XBD消防泵其它要求消防泵的效率要符合GB/T13007的规定，汽蚀余量要按照GB/T 13006的规定执行。
XBD消防增压泵电机与泵配套的电机的设计、制造、检验应符合GB755-2000及相关标准的要求。
防护等级及电压电机及其所有附件的防护等级为IP54，消防泵及冷却水泵的电压等级为380V,稳压泵的电压等级为380V0
消防泵冷却方式电机冷却采用风冷方式。
XBD增压泵运行电压电机应能在电压负序分量不超过正序分量的1%(长期运行)，或不超过1.5%(短班运行)且零序分量不超过正序分举1%的条件下运行。
控制系统说明XBD消防增压泵控制系统控制方式为:就地控制(手动控制、自动控制)、远程(站控室)制，消防联动控制，控制柜山2路电源供电，内部设置双电源自动切换装置。XBD消防增压泵(6张)
技术参数选型表
型 号流量Q扬程
(m)效率
(%)转速
(r/min)功率(Kw)汽蚀
余量
(m)进出
口径
(mm)(L/s)(m 3 /h)轴功率配套功率XBD3.6/0.56-(I)25×320.56363029000.651.11.725XBD4.8/0.56-(I)25×420.56483029000.871.11.725XBD6/0.56-(I)25×520.56603029001.091.51.725XBD7.2/0.56-(I)25×620.56723029001.301.51.725XBD8.4/0.56-(I)25×720.56843029001.522.21.725XBD9.6/0.56-(I)25×820.56963029000.742.21.725XBD10.8/0.56-(I)25×920.561083029001.962.21.725XBD12/0.56-(I)25×1020.561203029002.1731.725XBD13.2/0.56-(I)25×1120.561323029002.3931.725XBD14.4/0.56-(I)25×1220.561443029002.6131.725XBD3.3/1.11-(I)25×341.11334029000.901.11.725XBD4.4/1.11-(I)25×441.11444029001.201.51.725XBD6.6/1.11-(I)25×641.11664029001.802.21.725XBD7.7/1.11-(I)25×741.11774029002.102.21.725XBD8.8/1.11-(I)25×841.11884029002.4031.725XBD9.9/1.11-(I)25×941.11994029002.7031.725XBD11/1.11-(I)25×1041.111104029003.0041.725XBD12.1/1.11-(I)25×1141.111214029003.3041.725XBD13.2/1.11-(I)25×1241.111324029003.6041.725XBD14.3/1.11-(I)25×1341.111434029003.9041.725XBD3.6/1.67-(I)40×361.67365229001.131.51.740XBD4.8/1.67-(I)40×461.67485229001.52.21.740XBD6/1.67-(I)40×561.67605229001.882.21.740XBD7.2/1.67-(I)40×661.67725229002.2631.740XBD8.4/1.67-(I)40×761.67845229002.6431.740XBD9.6/1.67-(I)40×861.67965229003.0141.740XBD10.8/1.67-(I)40×961.671085229003.3941.740XBD12/1.67-(I)40×1061.671205229003.7741.740XBD13.2/1.67-(I)40×1161.671325229004.155.51.740XBD14.4/1.67-(I)40×1261.671445229004.525.51.740XBD3/33.3-(I)50×2123.33305629001.752.21.850XBD4.5/3.33-(I)50×3123.33455629002.6331.850XBD6.0/3.33-(I)50×4123.33605629003.641.850XBD7.5/3.33-(I)50×5123.33755629004.275.51.850XBD9/3.33-(I)50×6123.33905629005.255.51.850XBD10.5/3.33-(I)50×7123.331055629006.27.51.850XBD12/3.33-(I)50×8123.331205629007.07.51.850XBD13.5/3.3-(I)50×9123.331355629007.87111.850XBD15/3.33-(I)50×10123.331505629008.75111.850XBD3/5-(I)50×2185306229002.3731.850XBD4.5/5-(I)50×3185456229003.5641.850XBD6/5-(I)50×4185606229004.755.51.850XBD7.5/5-(I)50×5185756229005.937.51.850XBD9/5-(I)50×6185906229007.127.51.850XBD10.5/5-(I)50×7185105.56229008.30111.850XBD12/5-(I)50×81851206229009.49111.850XBD13.5/5-(I)50×918513562290010.68111.850XBD15/5-(I)50×1018515062290011.87151.850XBD2.4/10-(I)80×23610246829003.464480XBD3.6/10-(I)80×33610366829005.195.5480XBD4.8/10-(I)80×43610486829006.927.5480XBD6/10-(I)80×53610606829008.6711480XBD7.2/10-(I)80×636107268290010.3911480XBD8.4/10-(I)80×736108468290012.1215480XBD9.6/10-(I)80×836109668290013.8515480XBD10.8/10-(I)80×9361010868290015.5918.5480XBD12/10-(I)80×10361012068290017.3118.5480XBD2.8/15-(I)80×25415287029005.887.5480XBD4.2/15-(I)80×35415427029008.8211480XBD5.6/15-(I)80×454155670290011.7615480XBD7/15-(I)80×554157070290014.718.5480XBD8.4/15-(I)80×654158470290017.6418.5480XBD9.8/15-(I)80×754159870290020.5822480XBD11.2/15-(I)80×8541511270290023.5430480XBD12.6/15-(I)80×9541512670290026.4930480XBD14/15-(I)80×10541514070290029.4337480XBD2.8/20-(I)100×27220287329007.53114.5100XBD4.2/20-(I)100×372204273290010.29154.5100XBD5.6/20-(I)100×472205673290015.0518.54.5100XBD7/20-(I)100×572207073290018.81224.5100XBD8.4/20-(I)100×672208473290022.57304.5100XBD9.8/20-(I)100×772209873290026.34304.5100XBD11.2/20-(I)100×8722011273290030.1374.5100XBD12.6/20-(I)100×9722012673290033.9374.5100XBD14/20-(I)100×10722014073290037.6454.5100XBD4.2/25-(I)125×290254273290014.118.54.3125XBD6.3/25-(I)125×390256373290021.2304.3125XBD8.4/25-(I)125×490258473290028.2374.3125XBD10.5/25-(I)125×5902510673290035.3454.3125XBD12.6/25-(I)125×6902512673290040.3554.3125XBD14.7/25-(I)125×7902514773290040.4554.3125XBD16.8/25-(I)125×8902516873290056.4754.3125XBD18.9/25-(I)125×9902518973290063.5754.3125XBD21/25-(I)125×10902521073290070.6904.3125XBD3.8/30-(I)125×2108303874290015.118.54.6125XBD5.7/30-(I)125×3108305774290022.7304.6125XBD7.6/30-(I)125×4108307674290030.2374.6125XBD9.5/30-(I)125×5108309574290037.8454.6125XBD11.4/60-(I)125×61083011474290045.3554.6125XBD13.3/30-(I)125×71083013374290052.9554.6125XBD15.2/30-(I)125×81083015274290060.5754.6125XBD17.1/30-(I)125×91083017174290068.0754.6125XBD19/30-(I)125×101083016074290075.6904.6125XBD4.3/35-(I)150×2126354372290020.5304.4150XBD6.5/35-(I)150×3126356572290030.7374.4150XBD8.7/35-(I)150×4126358772290040.9454.4150XBD10.9/35-(I)150×51263510972290051.2754.4150XBD13.0/35-(I)150×61263513072290061.4754.4150XBD15.2/35-(I)150×71263515272290071.6904.4150XBD17.4/35-(I)150×81263517472290081.9904.4150XBD19.6/35-(I)150×91263519672290092.11104.4150XBD21.8/35-(I)150×1012635218722900102.41324.4150XBD4.1/40-(I)150×2144404176290021.2304.4150XBD6.2/40-(I)150×3144406276290032.0374.4150XBD8.3/40-(I)150×4144408676290042.7554.4150XBD10.4/40-(I)150×51444010476290053.4754.4150XBD12.4/40-(I)150×61444012476290064.0754.4150XBD14.5/40-(I)150×71444014576290074.7904.4150XBD16.6/40-(I)150×81444016676290085.41104.4150XBD18.7/40-(I)150×91444018776290096.01104.4150XBD20.7/40-(I)150×1014440207762900107.11324.4150XBD4/45-(I)150×2162454078290022.6304.5150XBD6/45-(I)150×3162456078290034.0374.5150XBD8/45-(I)150×4162458078290045.3554.5150XBD10/45-(I)150×51624510078290056.6754.5150XBD12/45-(I)150×61624512078290067.9754.5150XBD14/45-(I)150×71624514078290079.2904.5150XBD16/45-(I)150×81624516078290090.61104.5150XBD18/45-(I)150×916245180782900101.91104.5150XBD20/45-(I)150×1016245200782900113.21324.5150