标题：acwu90
产品介绍
ACWU90（-40）是一种高柔性的自锁型铝铠装、pvc外护套、90度交联聚乙烯防水型绝缘单芯或多芯阻燃B级电缆。因为具有FT4级的PVC外护套，ACWU90（-40）可直接埋地敷设，并使用于腐蚀环境和非燃性建筑中。ACWU90(-40) 别称为YJHLV82，用来替代铜缆ZR-YJV22、WDZ-YJV22、ZR-VV22等系列电力电缆产品。ACWU90（-40）减少了管道布线所带来的施工难度和人力成本。电缆已在工厂用高柔韧性的自锁型铝铠装和密封PVC外护套组装完毕，不需要管道及其附件和人工密集的拉线、扣纹和成管等工序。ZB-ACWU90（-40）完全符合GB3956，也符合GB/T 12706.1及IEC60502最新版的各项标准。
综合性能
价格：实现同等电气性能的前提下，ACWU90（-40）铝合金电缆比铜芯电缆的价格大约低30%~50%
导体：抗蠕变、高柔韧、强延展、低反弹、连接稳定
绝缘：耐高温、防燃烧、抗老化、强耐用、低碳环保。
铠装层：经济性能优越，特殊的自锁形式，坚固强韧。
外护套：采用无铅无镉的PVC，可在潮湿场所安装，亦可直埋或敷设在水泥中使用。
使用：ACWU90（-40）铝合金电力电缆在美、加等发达国家已得到广泛应用。
使用范围
适用于600V~35kV电压等级；适用于90℃下干燥或潮湿场所；可室内、室外安装，可垂直安装，也可托架或沿墙敷设，也可地下直埋安装；弯曲半径最小为7倍外径，也可360°弯曲；适用于民用、商业、工业、大型场馆、娱乐场所、矿井、地铁以及各类级别危险地区等场所。
电缆结构：
  ACWU90铝合金电缆结构图[1]
重要参数
ACWU90铝合金电缆重要参数
电压：0.6/1KV 产品名称：外护套铠装型铝合金电缆 产品型号：YJHLV82(ACWU90)
3芯、XLPE绝缘铝合金钢带连锁铠装PVC外护套低压铝合金电力电缆
导体
标称截面导体
直径绝缘
厚度护套
厚度电缆
近似外径电缆
近似重量绝缘电阻20℃时导体
直流电阻电缆载流量在空气中直埋土壤中mm2mmmmmmmmkg/km≥MΩ/km≤Ω/kmAA3×103.800.71.523.24840.5233.0859683×164.800.72.024.35500.4311.9177803×256.000.92.025.76010.4441.20961013×357.000.92.027.36910.3790.8681201313×508.401.02.031.89630.3550.6411571663×7010.001.12.534.711630.3350.4431861923×9511.601.12.542.217080.2900.3202432243×12013.001.22.545.419710.2820.2532632563×15014.601.43.049.323090.2940.2063022893×18516.201.63.053.126480.3030.1643403213×24018.401.73.060.835840.2830.1253783553×30020.601.83.566.042190.2630.1004173873×40023.802.03.572.151150.2430.07784564203+1芯、XLPE绝缘铝合金钢带连锁铠装PVC外护套低压铝合金电力电缆
导体
标称截面导体
直径绝缘
厚度护套
厚度电缆
近似外径电缆
近似重量绝缘电阻20℃时导体
直流电阻德昊电缆载流量在空气中直埋土壤中mm2mmmmmmmmkg/km≥MΩ/km≤Ω/kmAA3×16+1×104.800.72.024.75820.4311.9164763×25+1×166.000.92.026.86790.4441.20841013×35+1×167.000.92.029.18190.3790.8681151263×50+1×258.401.02.033.010670.3550.6411411523×70+1×3510.001.12.536.012940.3350.4431861923×95+1×5011.601.12.543.919090.2900.3202392483×120+1×7013.001.23.047.622480.2820.2532922903×150+1×7014.601.43.051.025690.2940.2063393293×185+1×9516.201.63.055.730730.3030.1643763663×240+1×12018.401.73.063.240660.2830.1254053833×300+1×15020.601.83.568.447630.2630.1004514293×400+1×18523.802.03.574.757540.2430.07784914753+2芯、XLPE绝缘铝合金钢带连锁铠装PVC外护套低压铝合金电力电缆
导体
标称截面导体
直径绝缘
厚度护套
厚度电缆
近似外径电缆
近似重量绝缘电阻20℃时导体
直流电阻德昊电缆载流量在空气中直埋土壤中mm2mmmmmmmmkg/km≥MΩ/km≤Ω/kmAA3×16+2×104.800.71.2725.716380.4311.9164773×25+2×166.000.91.2729.197470.4441.2084973×35+2×167.000.91.2731.008610.3790.8681151253×50+2×258.401.01.2734.1412940.3550.6411241293×70+2×3510.001.11.5238.6415450.3350.4431531583×95+2×5011.601.11.5243.2423330.2900.3201851883×120+2×7013.001.21.5248.0426780.2820.2532142133×150+2×7014.601.41.5252.4430160.2940.2062422373×185+2×9516.201.61.9056.4435810.3030.1642772683×240+2×12018.401.71.9063.0046690.2830.1253353183×300+2×15020.601.81.9065.6054880.2630.1004054003×400+2×18523.802.01.9080.6066460.2430.07784684664芯、XLPE绝缘铝合金钢带连锁铠装PVC外护套低压铝合金电力电缆
导体
标称截面导体
直径绝缘
厚度护套
厚度电缆
近似外径电缆
近似重量绝缘电阻20℃时导体
直流电阻德昊电缆载流量在空气中直埋土壤中mm2mmmmmmmmkg/km≥MΩ/km≤Ω/kmAA4×103.800.72.023.74930.5233.0857654×164.800.72.025.65980.4311.9164764×256.000.92.027.77310.4441.20841014×357.000.92.029.58370.3790.8681151264×508.401.02.034.711900.3550.6411411524×7010.001.12.538.014380.3350.4431861924×9511.601.12.546.221380.2900.3202392484×12013.001.23.050.124680.2820.2532922904×15014.601.43.054.229210.2940.2063393294×18516.201.63.058.433870.3030.1643763664×24018.401.73.067.045700.2830.1254053834×30020.601.83.572.753940.2630.1004514294×40023.802.03.579.665510.2430.07784914754+1芯、XLPE绝缘铝合金钢带连锁铠装PVC外护套低压铝合金电力电缆
导体
标称截面导体
直径绝缘
厚度护套
厚度电缆
近似外径电缆
近似重量20℃时导体
直流电阻德昊电缆载流量在空气中直埋土壤中mm2mmmmmmmmkg/km≤Ω/kmAA4×16+1×104.800.72.026.46671.9164774×25+1×166.000.92.028.98081.2088974×35+1×167.000.92.031.69770.8681151254×50+1×258.401.02.035.913120.6411501594×70+1×3510.001.12.541.316710.4431781834×95+1×5011.601.12.548.423740.3202282374×120+1×7013.001.23.052.227610.2532792874×150+1×7014.601.43.055.631770.2063233384×185+1×9516.201.63.061.038110.1643593644×240+1×12018.401.73.069.450500.1254154194×300+1×15020.601.83.575.359700.1004614664×400+1×18523.802.03.582.372160.0778529535