标题：C60塑壳断路器
产品简介
性能描述N1：电流等级630A至1600A，分断能力50KA  C60 塑壳断路器[1]N2：电流等级800A至2500A，分断能力50KA 
H1：电流等级800A至6300A，分断能力65KA 
H1b：电流等级800A至4000A，分断能力85kA 
H2：电流等级800A至6300A，分断能力100KA 
H3：电流等级800A至4000A，分断能力150KA 
L1：电流等级800A至2000A，分断能力150KA 
具有抽屉式/固定式，3/4极开关
提供负荷开关、1000V、以及直流产品   
优势十四种Micrologic控制单元可以提供完备的保护，并方便用户维护与监控，多样的可选附件可以满足使用要求的变化，模块化的组件可随时在现场完成组装。 
应用范围五大市场：工业、能源及基础设施、公商建、民用住宅、数据中心 
适用于低压配电领域内的配电线路和设备的保护与控制：
> N1 - 标准型，适用于分断低等级的短路电流
> N2 - 适用于一般的短路电流
> H1 - 适用于分断工业环境的高等级短路电流
> H1b - 适用于分断能力要求高的工业场合
> H2 - 高性能型，适用于可能产生非常高的短路电流的重工业领域
> H3 - 两台变压器并联运行的电气系统中
> L1 - 具有高限流能力，用以保护馈电单元或当变压器额定功率提高时提高开关柜的性能水平
性能描述额定电流 : 1~63 A 
工作电压 : 240/415/440 V AC 
工作频率：50/60Hz 
分断能力 :根据 IEC/EN60947-2, GB14048.2，在额定电压（1P:240VAC 2/3/4P:415VAC)下
> C60N: 10 kA
> C60H: 15 kA 
脱扣特性 :C型曲线：8.2In±20% ； D型曲线：12In±20% 
机械寿命 : 20,000次 
电气寿命：10,000次 
环境
> 使用环境温度 : -30°C至 +70°C
> 存储环境温度 : -40°C至 +80°C 
接线
> 1～25A :25 mm2及以下导线
> 32～63A :35 mm2及以下导线
> 可实现上进下出或下进上出的接线方式 
标准及认证
符合IEC60947-2/GB14048.2  拥有CCC证书 
优势完善的国际船级社认证：拥有ABS,BV,DNV,GL,LRS,RINA,RMRoS,即将获得CCS KRS 
产品型号齐全，性能卓越，方便选型 
具有CCC认证，本地充足现货库存 
全球售后服务及技术支援 
应用范围广泛运用在船舶制造，海洋平台等海事行业
英文说明
Performance Description 
N1: current level of 630A to 1600A, 50KA breaking capacity 
N2: current rating 800A to 2500A, 50KA breaking capacity 
H1: current rating 800A to 6300A, 65KA breaking capacity 
H1b: current rating 800A to 4000A, breaking capacity 85kA 
H2: current rating 800A to 6300A, breaking capacity 100KA 
H3: current rating 800A to 4000A, breaking capacity 150KA 
L1: current rating 800A to 2000A, breaking capacity 150KA 
With drawer / fixed, 3 / 4 pole switch 
Provide load switch, 1000V, and DC products 
Superiority 
14 kinds of Micrologic control unit can provide complete protection, and user-friendly maintenance and monitoring, using a variety of optional accessories to meet the changing requirements of modular components that can be assembled on site at any time. 
Applications 
Five major markets: industrial, energy and infrastructure, public construction business, residential, data centers 
Applies to low voltage power distribution in the field of power distribution lines and equipment protection and control: 
> N1 - standard for low-level short-circuit breaking current 
> N2 - for general short-circuit current 
> H1 - suitable for the environment breaking industrial grade short-circuit current 
> H1b - breaking capacity requirements applicable to the industrial situation of high 
> H2 - high-performance model for the possible very high short-circuit current of heavy industry 
> H3 - two transformers in parallel operation of electrical system 
> L1 - high limiting capacity for the protection of feed unit or when the transformer rated power to improve the performance to raise the level of switchgear 
Performance Description 
Rated current: 1 ~ 63 A 
Operating voltage: 240/415/440 V AC 
Operating frequency: 50/60Hz 
Breaking capacity: According to the IEC/EN60947-2, GB14048.2, at rated voltage (1P: 240VAC 2/3/4P: 415VAC) under 
> C60N: 10 kA 
> C60H: 15 kA 
Tripping characteristics: C-type curve: 8.2In ± 20%; D curve: 12In ± 20% 
Mechanical life: 20,000 times 
Electrical Life: 10,000 times 
Environment 
> Ambient temperature: -30 ° C to +70 ° C 
> Storage temperature: -40 ° C to +80 ° C 
Wiring 
> 1 ~ 25A: 25 mm2 and below wire 
> 32 ~ 63A: 35 mm2 and below wire 
> Can achieve upward mobility into the upper or lower under the wiring out 
Standards and Certification 
Meet IEC60947-2/GB14048.2 have CCC certificate 
Superiority 
Improve the international classification society certification: have ABS, BV, DNV, GL, LRS, RINA, RMRoS, will be CCS KRS 
Product range, excellent performance, easy selection 
With CCC, the local stock in sufficient 
Global after-sales service and technical support 
Applications 
Widely used in shipbuilding, offshore platforms and other maritime industry