How to Fix an Air Conditoner | Honeywell Zone System
Channel: Travis Poe
Date: 14/08/2019

On this service call the customer stated that the air conditioner seemed to run continuously and never seemed to turn off and not the house to the correct temperature.

Upon diagnosing the system I found that the system had a honeywell zone system installed on the air conditioner. While checking the air conditioner I found the ac system to be working properly but the zone damper motor which feeds downstairs was stuck closed not allowing air flow downstairs. I put in an order for a replacement zone damper motor.


Contact info: travispoe1975@gmail.com