HVAC 23: A teensy tiny leak... and it's finally running
Channel: Brian Greul
Date: 21/07/2022

I discovered a tiny leak in the liquid line at the air handler.  In this video I recover the refrigerant using the outdoor compressor, flow nitrogen in the line, braze the problem area, vacuum it, and re-start the unit.  I still need to build a plenum transition, but the unit is working fine and cooling with no issues.