From: david.roensch@enron.com
To: rich.jolly@enron.com
Cc: rick.cates@enron.com, jeffery.fawcett@enron.com, dan.pribble@enron.com, larry.campbell@enron.com, earl.chanley@enron.com, arnie.bailey@enron.com, roger.osborn@enron.com, rick.smith@enron.com, louis.soldano@enron.com
Date: 1999-04-09 18:29:00+00:00
Subject: PG&E UPDATE

Mike   
We completed the decontamination on both of the filter separators on the 
discharge of the Solexol Plant.  There was a thin film of an oily substance 
(presumably Solexol) on the interior wall of the filter separators.  However, 
both sets of filters were very clean.  No moisture was present on the filters 
and there was not any sludge or build up on any of the filters.  The filters 
that were removed had the same appearance of a brand new filter.  As a matter 
or fact, when you laid a new filter beside a used filter you could not tell a 
difference.  The filters being used are a Sock type filter and when you ran 
your hand across the filters you could not detect the presence of any 
moisture at all.

So, it's presumed that the system has been completely absent of any liquid.  
The small amounts of liquid being collected from week to week for sampling 
must have been accumulated from the run down or film, pre-existing on the 
interior of the filter separator housing.  A decontamination and triple rinse 
of each filter separator should result in a total absence of any liquid for 
future samples, other than the remaining soap and water used for the final 
rinse that could not be drained from the vessels.

Rich and I visited the Topock compressor station this morning and reviewed 
the sampling point on PG&E's inlet scrubber.  Rich made the recommendation to 
Randy Williams and Rick Bezanson (PG&E) that future samples be taken straight 
off the bottom of the scrubber rather than from PG&E's 1000 gallon blow down 
tank.  The purpose of this was to reduce the exposure to contaminating future 
samples with pre-existing PCB's that may have collected in the 1000 gallon 
blow down tank over a period of time.  PG&E agreed to sample from this point 
on future collections.

Both of the discharge lines on each filter separator at the Solexol plant 
have been hot tapped in preparation of Solexol injection.  Piping has been 
installed and pumps are in place to accommodate the Solexol injection as 
well.  However, NO injection of Solexol will take place until after our 
meeting next Tuesday with PG&E.

Transwestern has agreed with PG&E today to postpone our planned 
decontamination of the filter separator at Transwesterns PG&E meter station 
until April 28th, at which time Transwestern and PG&E will perform a 
decontamination of both TW's and PG&E's filter separators simultaneously.   

                                                                              
               Thanks, Tiny

---------------------- Forwarded by David Roensch/ET&S/Enron on 04/09/99 
05:51 PM ---------------------------

Rich Jolly
04/08/99 11:46 PM


To: Michel E Nelson@Enron
cc: Rick Cates/ET&S/Enron@Enron, Jeffery Fawcett/ET&S/Enron@Enron, Dan 
Pribble/ET&S/Enron@Enron, Larry Campbell/ET&S/Enron@Enron, Earl 
Chanley/ET&S/Enron@Enron, Arnie Bailey/ET&S/Enron@Enron, Bob Bandel@Enron, 
Roger Osborn/ET&S/Enron@Enron, David Roensch@ENRON, Rick 
Smith/ET&S/Enron@Enron, Louis Soldano/ET&S/Enron@Enron 

Subject: PG&E UPDATE

Mike
We completed decontamination of the inlet filter at the selexol plant today. 
It was dirty but 
no liquid. There was some dried sludge in the bottom of the vessel and the 
filters were 
extremely dirty. We plan to do both of the filters on the discharge side 
tomorrow.I got a phone 
messsage from Jeff and he hasn't heard anything from PGE since the letter was 
sent . We will 
plan to bypass and clean the filter on the west side of the river, last one 
on our system Saturday
unless we hear something different tomorrow. We will notify the PGE operators 
of their plant 
tomorrow of our plans.If anyone needs to contact me my pager number is 
1-800-921-9564 and office
phone number is 505-260-4003. Leave a message on the office phone and it will 
automatically
page me. I'll give everyone an update late tomorrow. We should have the hot 
tap valves on location 
tomorrow for the selexol injection. We plan to install the valves as soon as 
they arrive.

Thanks RJ

By the way Bisti came on line today and they plan to run it tonight and be 
back on location to 
check on the unit tomorrow.