V ++++ The XRGI" is a combined heat and power plant (CHP) that works on the principle of cogeneration. An XRGI" system consists of three main components – the Power Unit, Q-Heat Distributor and the iQ-Control Panel. In addition, you can also extend your XRGI' system with a storage tank with a capacity of 500, 800 or 1,000 litres for optimum operation. O R D E R I N G D ATA
E r P - L A B E L D ATA²
' Return temperatures as per EN 50465 2015 7.6.1: Without condensing technology 47 °C, with condensing technology 30 °C.

² The values were rounded in accordance with the re * HCV = higher caloring value, LCV = lower caloring value O U T P U T
EFFICIENCIES & OPERATING PARAMETERS P O W E R MODULATION Continuous modulation of 4 – 6 kW in power-controlled mode XRGI° 6 LowNOx total efficiency / return temperature * Continuous modulation in power-controlled mode ¹ Return temperatures as per EN 50465 2015 7.6.1:Without condensing technology 47 °C, with condensing technology 30 °C. ² LCV = lower calcrific value 1 This values are based on independent, certified and authorised inspection bodies. Test reports are available upon request. ° Efficiency at rated heat output as per the delegated Commission Regulation (EU) No. 811/2013; 813/2013. TOTAL EFFICIENCY AT F ULL LOAD HYDRAULIC INTEGRATION More principle circuit diagrams and information can be found in the EC POWER „Hydraulic Solutions”. NOTE: lf products from other companies are used in the system in addition to EC POWER products, EC POWER assumes no liability for the accuracy of the energy efficiency class calculation for the entire system.
* Continuous modulation in power-controlled mode ' Return temperatures as per EN 50465 2015 7.6.1: Without condensing technology 47 °C, with condensing technology 30 °C. ² as per the delegated Commission Regulation (EU) No. 811/2013; 813/2013 * HCV = higher calorinc value Deviations in values depend on the ambient and operating conditions, tolerance +/+ 5 %. Subject to technical modifications, deviations from design and errors. F U L S EXHAUST GAS SOUND
SERVICE DIMENSIONS A ND WEIGHT
+++++ The Flow Master including Flow Master Control regulates the supply of heat from the XRGI* and from the storage tank to the consumer network. This technology enables a significantly higher heat output to be temporarily made available to the consumer side. This allows peaks of heat demand to be handled by the XRGI", thereby extending its service life and increasing electricity production. The 4 models can deliver a heat output of 50, 150, 250 or 350 at a ΔT of 20 K. O R D E R I N G D ATA
E r P -L A B E L D ATA²
Return temperatures as per EN 50465 2015 7.6.1: Without condensing technology 47 °C, with condensing technology 30 °C ² The values were rounded in accordance with the requisements governing product data sheets by Regulation (EU) No. 811/2013;813/2013
% ( -'l') x 'll' = Solar contribution (From fiche of solar device) Collector size Tank volume (in m²) (in m²) Collector efficiency Tank rating = 0,95, A = 0,91, B = 0,86, C = 0,83, D G = 0,81 (in %) / 100)  x 'IV' x ) x 0,7 x ( ( 'III' x Seasonal space heating energy efficiency of package Seasonal space heating energy efficiency class of package 163 % B efficiency once installed in a building, as this  officiency is nced by further factors such as heat less in the de- m and the dimensioning of the products in tribution system station to building size and character % 1 50 Subject to technical modifications, deviations from design and errors. WWW.ECPOWER.EU