F• F OR

Reflecta-Cell Plus™

WAL
LSORLLS
WATHERMAL & SOUND INSULATION

FORLS

•F

OR WALLS •OR WALLS ••FINSTALLGUIDELLWAS • FORWAL

CORRECT INSTALLATION METHOD
FOR WALLMETAL AND TIMBER FRAMES – WITH BRICK OR
LIGHTWEIGHT WALL
1	Roll out the suitable Reflecta-Range™ insulation producthorizontally on the outside of studs or framing.
2	Install the product from the bottom of stud or framing.
3	Roll out the next roll of Insulation allowing 150mm overlap(residential building) or 50mm overlap (commercialbuilding).
4	Where overlap is less than 50mm or 150mm, use 72 mm
wide reinforced aluminium foil joining tape.
5	Allow a nominal air space of 25 mm either side of theInsulation to achieve required R-values. This is easily
achievable by pushing Insulation inwards between thestuds.

DOUBLE BRICK CAVITY WALL

MASONRY OR TILT PANEL WALL USINGMETAL BATTENS
1	Construct block wall or tilt panel wall and install
adjustable furring channel clips (Eg. Betafix/ BETAFIL)
2	Roll out the Reflecta-Range™ product horizontally acrossthe wall over the top of furring channel clips.
3	Slit Insulation with sharp knife so the clip can passthrough the Insulation. The slit should only be big
enough to allow the leg(s) of the clip to pass through theInsulation.
4	Push the insulation onto the clip to provide a 25mm
airgap to both the front and back of the insulation. An
insulation spacer may also be used to assist with this.
5	When installing the next run of insulation overlap by
150mm (residential building) or 50mm (commercialbuilding) and tape to suit AS4200.2.
6	Clip Furring Channels/ Battens into clips to secureinsulation. Fix linings as normal.

1	Construct internal brick wall with wire ties in place.

VAPOUR CONTROL MEMBRANE

2	Install Insulation from bottom of the wall.

If the product is installed and used as a vapour control
membrane, Class 1 or Class 2, or as an air barrier, it shall be
continuously sealed at all discontinuities, end laps, joints
and penetrations by3	Roll out the Reflecta-Range™ product horizontally acrossthe wall on top of wire ties
4	Slit Insulation with sharp knife or push wire tires throughInsulation.
5	Overlap installed Insulation by 150mm (residentialbuilding) or 50mm (commercial building).
6	Where overlap is less than 50mm or 150mm, use 72 mm
wide reinforced aluminium joining tape (available fromInsulation).
7	Allow a nominal air space of 25 mm either side of theInsulation to achieve required R-values. This is easily
achievable by pushing Insulation inwards between the
brick cavity.

•A pressure sensitive, heat and moisture resistant tape;•Adhesive of equal or greater vapour resistance thanthe vapour control membrane;•

Heat and moisture resistant adhesive tape;•Mechanical fixing with adhesive sealant; or•Adhesive bond.

Products are to be stored standing upright and on pallets not more than two high. Product warranty is voided for any productstored horizontally resulting in squeeze or crush. Returns of product displaying effects of deformation due to incorrect
storage practices will not be accepted.
The product information included in this publication is provided in good faith in order to ensure the optimum performanceof this product. However, no warranty is given or implied with respect to this information or the product itself regarding theproduct’s suitability for any particular purpose, as factors outside our knowledge and control may affect its use. The usageof this and other building membranes will affect moisture migration in the building element. The purchaser is responsible forindependently determining the sustainability of the product for the intended purpose. GI Building Services Pty Ltd reserves
the right to amend product specifications without prior notice. Information provided is considered to be true and correct atthe time of publication.

Issued July 2022gibs.com.au