CATALOGUEMAKE ENERGY USAGE SMARTER

Table Of Content
About Accuenergy. . ................................................................................................ 4
Accuenergy Meters................................................................................................ 6
Acuvim 3 - Advanced Power Quality Meter.....................................................6
Acuvim II - Advanced Multi-Function Power & Energy Meter Series.............8Acuvim II - Expansion Modules. . .................................................................. 10
Acuvim II + AXM-WEB2. . ................................................................................ 11
Acuvim L - Standard Multi-Function Power & Energy Meter Series........... 12
AcuRev 1310 - DIN-Rail Digital Panel Meter. . ............................................. 14
EV300 - Panel Meter Series . . ........................................................................ 16
AcuPanel 9100 - Pre-Wired Metering Panels. . ........................................... 18
AcuRev 2100 - Multi-Circuit Submeter with SnapOn CT Technology......... 20
AcuDC 240 - DC Energy Meter. . ................................................................... 22
Communications & Software Solutions............................................................ 24
AcuCloud - Cloud-Based Metering Platform.............................................. 24
AcuLink 810 - Data Acquisition Gateway. . .................................................. 26
AcuMesh - Wireless RS485 Metering Network.......................................... 28
Current Transformers......................................................................................... 29
AcuCT Flex - Rogowski Coils......................................................................... 29
RIK Series - Rogowski Integrator Kit . . .......................................................... 30
AcuCT R - Revenue-Grade Split-Core Current Transformer.. ................... 31
AcuCT mV - 333mV Split-Core Current Transformer................................ 31
AcuCT 5A - 5A Split-Core Current Transformer. . ....................................... 32
AcuCT Hinged - 5A Split-Core Current Transformer................................. 32
AcuCT S113 - Solid-Core Current Transformer......................................... 33
AcuCT S77 - Revenue-Grade Solid-Core Current Transformer............... 33
AcuCT S220 - Switchgear Solid-Core Current Transformer..................... 34
AcuCT S335 - Busbar Solid-Core Current Transformer. . .......................... 34
AcuCT S433 - Instrument Solid-Core Current Transformer..................... 35
AcuCT S650 - Solid-Core Current Transformer......................................... 35
HAB 16555 - DC Current Sensors............................................................... 36
HAK - Hall Effect Current Sensors............................................................... 36
HV2 - DC Voltage Sensor.............................................................................. 37
DC Shunts - Shunt Series............................................................................. 37
AcuCT C - Current Transformer Converter................................................ 38|3

We Are Accuenergy
Accuenergy Inc. specializes in power metering solutions
that lead the industry in revenue grade energy
metering, power quality analysis, ease of deployment
and advanced communication methods. Our reliable
power meters have been used globally to monitor
electrical systems in commercial and industrial facilities,
multi-tenant buildings, data centres, and cell towers formore than 20 years.
Our goal is to provide users with well-designed
products that are easy to implement without sacrificing
key functionality. Our pre-wired panel meters andwireless submeters are designed to offer the simplest
tenant billing and metering solutions on the market,
while providing ease of installation.

|5Power Meter SolutionsACUVIM 3
Advanced Power Quality Meter
The Acuvim 3 Series an advanced power quality
and revenue grade meter. IEC 61000-4-30 ClassA certified by third-party NMi for PQ.
High accuracy ANSI C12.20 Class 0.1/IEC 6155712 Class 0.1 rated. Optional 7-inch touchscreen
display unit can be install in a panel or DIN
rail mounted. Multi-protocol industrial
communication support for IEC 61850,
EtherNet/IP, Modbus, BACnet, and more.

NEW PRODUCTACCUENERGY.COM/ACUVIM-3
EN55011
IEC 61000-4-30
CertifiedC12.20 .1 CLASSKey Specifications•

IEC 61000-4-30 Class A compliant PQ analyzer••

PMU (IEEE C37.118) for fast and reliable
synchrophasor measurement

Power quality event detection on half-cycle RMS totrigger email notification, or DO/RO•

Meter sampling rate at 1024 samples/cycle•

Waveform Capture detection up to 512 samples/cycle
and stored in COMTRADE or CSV file•

Fast log report, download from webpage/SFTP, or
post via HTTP(S), FTP, SFTP•

Reporting EN50160 compliance report, IEEE 519
compliance report, ITIC (CBEMA) Curve, SEMI Curvewith AcuCloud•

Flicker & transient measurement and logging

ANSI C12.20 Class 0.1 Accuracy / IEC 62053-22 Class
0.1S active energy and IEC 62053-24 Class 0.5S
reactive energy•

TOU with 8 tariff and up to 12 billing periods•

Multiple dataloggers with user-selectable logging
interval and parameters•

32 GB onboard memory for data logging andhistorical trend analysis*

Selected models only

PRODUCT COMPATIBILITYDATA ACQUISITION SERVER

ACULINK 810

1

COMM ISSUE

NO COMMCOMM OKSTATION MODESTATUSRSSIAP MODERX

POWER ON
GND

Control Power

24Vdc

8

ASSOC

TX
DI5-COM

7

DI5

DI6

6

DI4-COM

DI6-COM

5

DI4

DI7

4

2

DI3-COM

DI7-COM

3

3

DI3

DI8

2

4

DI2-COM

DI8-COM

1

5

DI2

RS485+

8

6

DI1-COM

RS485-

7

7

DI1

Shield6

8

M E T E R I N G

5

B A S E D

4

C L O U D

RS485

3

ACUCLOUD

WIFI

2

AcuMesh1•

ACULINK 810

Waveform Capture

PMU Synchrophaser

Identify power system anomalies

Detect waveform for both voltage &High precision, real-timein critical infrastructure. Common

current power quality events up tomeasurements of voltage, current,

voltage sags & swells on half-cycle

512 samples per cycle. Capture prephase angle and frequency across

RMS, and transient overvoltage

and post-trigger events up to 360

power distribution systems.

at 32 ksps. Detect harmonic

cylces. Set up PQ trigger conditions

Detects abnormal PQ events overdistortions caused by non-linear

for email alert integration and savea wide area grid for early warning

loads, and frequency variation

as COMTRADE files for transfer toalerts.

deviations.

a remote server via HTTP/FTP for
analysis.

Datalogger Fast Log

PQ Compliant Reports

Revenue Grade

Measure and log energy, demand,

Power quality compliance reports

ANSI C12.20/IEC 62053-22 Class

RMS, power, fundamental,

based on EN50160 for standard

0.1S accuracy with four-quadrant

THD, phase angle, unbalance

PQ characteristics, and IEEE 519

active energy monitoring forparameters. Configure multiple

pass/fail report for voltage/current

critical applications that rely

data loggers with user-selectableharmonic distortion. ITIC/CBEMBA

on consistent, high-accuracy

file length, parameters, and logging

and SEMI curve analysis for for IT

readings. Voltage/current half-interval. Recording interval up to

equipment power tolerance.

cycle RMS, and frequency accuracy

200ms to 7 days depending on

at 1 mHz, 40 to 70 Hz.

parameter.

Industrial Communication Protocols
Multi-protocol support for a wide range of industry-standard protocols.
•
•
•
•
•
•
•
•

PMU (Synchrophasor )Modbus-RTU via RS485
BACnet-IP via RS485
Dual Ethernet
Wi-Fi
Modbus-TCP/IPHTTPS Webserver
HTTP/HTTPS Post

•
•
•
•
•
•
•

IEC 61850
EtherNet/IP
FTP/sFTP Post
SMTP
SNMP
SNTP
DNP3 over IP

I/O Module Options
AXM-IO1

AXM-IO2

AXM-IO3

Digital Input

6

4

4

Digital Output

-

2

-

Relay Output

2

-

2

Analog Inputs

-

-

2

Analog Outputs

-

2

-

|7

Power Meter Solutions

Power Quality Analyzer

Power Meter SolutionsACUVIM II
Advanced Multi-Function
Power & Energy Meter Series
The Acuvim II series energy submeters are thesimple, robust solution for power monitoring,
power quality analysis, kW metering, and more.
Designed for easy integration in almost any
metering application, a wide array of plug-in
expansion modules allows communication onover 15 different industry-standard protocols.

ACCUENERGY.COM/ACUVIM-II

EN55011

C12.20 .1 CLASSKey Specifications•

Revenue grade ANSI C12.20 Class 0.1 & IEC 62053-22
Class 0.1s•

COMTRADE Waveform file format*•

Threshold alarms can be set to notify users ofpotential issues•

Built-in Modbus-RTU and BACnet-MS/TP via RS485 port•

Expand with dual RJ45, WiFi, Fiber optic, Profibusand more interfaces•

Time-of-Use (TOU) capability allows time-based ortier-based rate structure*•

Add up to three expansion communications & I/O modules••

MV90 compatibility

Support Modbus, BACnet, IEC 61850, EtherNet/IP, IPv6,
RSTP, SNMP, HTTPS, sFTP, MQTT & other protocols•

Datalogging with up to 1-second interval, max/min/average, and instantaneous reading*•

Cloud metering data storage & analytics*

Selected models only

PRODUCT COMPATIBILITYDATA ACQUISITION SERVER

ACULINK 810

GND

1

COMM ISSUE

NO COMMCOMM OKSTATION MODESTATUSRSSIPOWER ON
24Vdc

8

RX

AP MODE

7

ASSOC

TX
DI5-COM

DI6

6

DI5

DI6-COM

5

DI4-COM

DI7

4

DI4

DI7-COM

32

DI3-COM

DI8

2

3

DI3

DI8-COM

1

4

DI2-COM

RS485+

8

5

DI2

RS485-

7

6

DI1-COM

Shield6

7

DI1

Control Power

58

M E T E R I N G

4

B A S E D

3

C L O U D

RS485

2

ACUCLOUD

WIFI

1

AcuMeshACULINK 810

Alarms

Waveform Capture

Essential to trend analysis andQuickly set over or under limit

The Acuvim IIW can record 100

reporting, the Acuvim IIR and IIW

alarms for up to 16 indicatedgroups of voltage and current

offer a robust data logging featureparameters with a specified time

waveforms. The instrument

where most metering parametersinterval. If a parameter goes outside

supports a settable triggering

can be recorded for later review.

its setting limit, the alarm output iscondition and provides a waveform

The integrated real-time clock

triggered, and the event is recorded

record of 10 cycles before and after

ensures logged events arewith a time and date stamp for later

each triggering point. Data can be

accurately time stamped. 16MB ofanalysis. Easy to manage andstored in the COMTRADE waveform

non-volatile memory is built into thecustomize, the alarm can be configured

file format for later analysis.

meter and, by equipping the AXM-

using any of 80 available parameters.

WEB2 module, an additional 8GBof memory with up to a 1-second

Power Quality Monitoring

Time-Of-Use

Power quality monitoring ensures

Time-based tariffs can lead tosystems run at maximum efficiency.

higher power bills when energy-

The Acuvim IIW can detect energy

intensive devices are run during

Much like a utility meter, thedeviations using harmonic analysis,

peak hours. Time-of-use metering

Acuvim II can be physically sealed

event logging, and waveform

allows facility managers to reduceto protect against tampering. All

capture. Facility managers can use

energy costs where TOU rates

metrological programming andthe detailed PQ data to diagnose

have been applied. Gain valuable

user-defined parameters are

power quality issues before they

insight into a facility’s load profile

safeguarded with the physical seal.

result in system inefficiency.

with built-in peak analysis tools.

logging interval is made available.

Anti-Tampering Seal

AXM-DIN Rail Mounting Adapter

IP66/NEMA4X Adapter Protection Cover

The AXM-DIN RailDefend against dust, water, or other contaminants:

Adapter is the easy

The Protection Cover is designed for all Acuvim

solution for panel-

II panel meters. It

mount Acuvim II series

increases the IP

meters on either

environmental rating

horizontal or verticalof a meter’s display to

DIN rail.

IP66 or NEMA 4X.

Acuvim II Series Models
Acuvim IIR

Acuvim IIW

Application

Billing / Data Logging

Power Quality

Metering

400 Parameters

400 Parameters

Onboard Memory

16MB

16MB

With AXM-WEB2

8GB

8GB

Data Logging

Time-of-Use
Power Quality|9

Power Meter Solutions

Data Logging

Power Meter Solutions

EXPANSION MODULES
Snap-On Communication Modules for Acuvim II Series Meters

Acuvim II Communication Modules
The AXM modules are designed to expand thecommunication capabilities of the Acuvim II meter.
Easy to deploy, the field-expandable modules
connect directly to the meter to boost the numberof compatible communication protocols or increase
the number of I/O ports.
ACCUENERGY.COM/AXM-MODULES

I/O Module Options
AXM-IO1

AXM-IO2

AXM-IO3

Digital Input

6

4

4

Digital Output

-

2

-

Relay Output

2

-

2

Analog Inputs

-

-

2

Analog Outputs

-

2

-

Acuvim II AXM Expansion Modules
Meter Only

AXM
WEB2 FOLC

AXM
WEB2

AXM
WEB2-DAXM
WEB PUSH

16MB

8GB

8GB

8GB

4GB

1

2

2

1

Modbus-RTU
BACnet-MS/TP
DNP 3.0 Over IP
IEC 61850
Modbus-TCP/IP
HTTP/HTTPs Webserver
SMTP Email
SNMP V3
MQTT
EtherNet/IP, RSTP, IPv6
HTTP/HTTPs PushFTP PostsFTP Server
Datalogging
BACnet-IP
PROFIBUS
WiFi
RJ45 Ports
Fiber Optics LC

AXM
PROFI

AXM
RS485

WiFi + Dual Ethernet

AXM-WEB2-D

lesDual Ethernet

les

AXM-WEB2 FOLC
WiFi + Ethernet + Fiber Optics LC

ACCUENERGY.COM/AXM-WEB2
ACCUENERGY.COM/AXM-WEB2-D
ACCUENERGY.COM/AXM-WEB2-FOLC

AXM-WEB2

AXM-WEB2 FOLCKey Specifications•

Graphical display for easy analysis•

Custom Modbus register list groups key parameters•

Metered data is backed up in 8GB non-volatile memory•

Compliant with industry-standard security protocols•

RJ45 daisy chain using dual Ethernet ports•

IPV6 & IPV4 dual IP network support•

Maintain high availability with RSTP•

Over-the-air (OTA) firmware updates•

Industry-leading 40ms response rates via Modbus TCP/IP•

Easy integration with Allen Bradley & Rockwell systems

WEB2 Interface Provides Remote Access

Flexible Communication Support

Take full control of the Acuvim II power meter through

Designed to securely meet a wide range of industrial

the web browser interface. Access complete energy

communication requirements, each module is equippedfrom anywhere in the world. Manage and update meterwith both Ethernet and WiFi channels. Additionally, theconfiguration settings including 16 over/under alarm

AXM-WEB2 FOLC includes a fiber optic LC port for fast,settings. Two-tier user control settings ensure reliable

reliable signal transmission. Communication ports canaccess without compromising meter security.

be utilized simultaneously across different networks ordata acquisition systems.

IEC 61850 Certification

Data Logging & Event Storage

The Acuvim IIW power meter with AXM-WEB2 Series

The AXM-WEB2 Series module expands the meter’scommunication module has been 3rd party certified tomemory to an industry-leading 8GB with 1-second

meet stringent IEC 61850 (2nd ed.) requirements forinterval datalogging. Most metering parameters can beseamless deployment in substations and other critical facilities.

recorded for later download or analysis.

Datalogging andEvent Storage

WPA2 Enterprisesecurity protocol

Access anywhere via
SerialNumber.accuenergy.io

COMtrade Waveform
FormatDaisy-chain support
via Ethernet ports,

| 11

les

Power Meter Solutions

AXM-WEB2ACUVIM II +

Power Meter SolutionsACUVIM L
Standard Multifunction
Power & Energy Meter Series
The Acuvim L is a cost-effective power
meter that offers performance and value
for standard metering solutions. Designed
to be easily integrated in panels, as a DIN
rail transducer, or as a pre-wired panel.
Ideal for a variety of different industrial &commercial applications.

PRODUCT UPDATEACCUENERGY.COM/ACUVIM-L

EN55011
C12.20 .1 CLASSKey Specifications•

Revenue grade: ANSI C12.20 class 0.2 & IEC 62053-22
class 0.2s•

Data Logging available in 16MB onboard and 8GB with
WEB2 module•

4th CT input – measure neutral current•

Designed with industry leading cybersecurity•

Dual Ethernet ports with both RSTP bridge daisy-chainmode and separately configurable network•

Available compatibility with multiple CT output options
including 5A, RCT (Rogowski), or 333mV•

Remote channel mapping and four channel multi-circuit
metering••

Dual source meter to monitor energy usage fromseparate energy sources

Modbus-RTU & BACnet MS/ TP ready. Optional
modules add support for multiple industrial protocols &interfaces such as Modbus- TCP/IP, BACnet-IP, and WiFi*

Selected models only.

PRODUCT COMPATIBILITYDATA ACQUISITION SERVER

ACULINK 810

GND

1

COMM ISSUE

NO COMMCOMM OKSTATION MODESTATUSRSSIPOWER ON
24Vdc

8

RX

AP MODE

7

ASSOC

TX
DI5-COM

DI6

6

DI5

DI6-COM

5

DI4-COM

DI7

4

DI4

DI7-COM

32

DI3-COM

DI8

2

3

DI3

DI8-COM

1

4

DI2-COM

RS485+

8

5

DI2

RS485-

7

6

DI1-COM

Shield6

7

DI1

Control Power

58

M E T E R I N G

4

B A S E D

3

C L O U D

RS485

2

ACUCLOUD

WIFI

1

AcuMeshACULINK 810

Time-of-Use (TOU)

AlarmsUsers can assign up to four tariffs

Limits can be set for up to 16

The Acuvim L meters are equipped(sharp, peak, valley, & normal) toindicated parameters with awith Modbus-RTU & BACnet-MS/TP

different time periods within a

specified time interval. Parameters

protocol, allowing for interoperability

day, as well 12 seasons, and 14

that are over or under setting

between devices that utilize serial

schedules. The Acuvim L meter will

limit and persist longer than thecommunication.

calculate and accumulate energy

specified time interval will be

Through an expansion module,

to different tariffs according to therecorded and trigger the Alarm

add optional PROFIBUS protocol

meter’s internal clock and TOU

DO. Choose from 80 available

ideal for factory automation systems.

settings.

parameters.

Data Logging
Acuvim L meters offer three,assignable historical logs and areal time clock to record meteringparameters with accurate
timestamping. Add the AXM-WEB2
module to expand the memory to
8GB with an adjustable log size.

AXM-DIN Rail
Mounting Adapter

IP66/NEMA4X Adapter
Protection Cover

The AXM-DIN Rail Adapter is the

The protection cover is designed

easy solution for panel-mountto defend against dust, water,

Acuvim L series meters onor other contaminants. It

eitherincreases the IP environmental

horizontal

rating ofor verticala meter’s

DIN rail.

display.

Communication Module Comparison
Meter
Only

AXM
WEB2 FOLC

AXM
WEB2

AXM
WEB2-D

Modbus-RTU

Acuvim L Series Models
AXM
PROFI

AXM
RS485
Metering

BACnet-MS/TP
DNP 3.0 Over IP

Energy & Demand

IEC 61850

Time-of-use

Modbus-TCP/IP

Accuracy

HTTP/HTTPs
Webserver

Power Quality
Individual
Harmonics

SMTP EmailCL

EL

Voltage (V), Current(Amp), Power (kW)

Voltage (V), Current(Amp), Power (kW)

0.5%

0.2%

2nd to 31st

2nd to 63rd

SNMP V3
EtherNet/IP
MQTT
RSTP
IPv6
HTTP/HTTPs PushFTP PostsFTP Server
Datalogging

16MB

8GB

8GB

8GB

1

2

2

BACnet-IP
PROFIBUS
WiFi
RJ45 Ports
Fiber Optics LC| 13

Power Meter Solutions

Modbus, BACnet withPROFIBUS OptionPower Meter Solutions

ACUREV 1310
DIN-Rail Digital Panel Meter
The AcuRev 1310 combines highperformance with easy integration toprovide a cost-effective power and energy
monitoring solution for three-phaseAC systems. It’s robust design features abuilt-in LCD, Modbus-RTU communications,and 4 current input channels.

ACCUENERGY.COM/ACUREV-1310

C12.20 .1 CLASSKey Specifications•

Utility revenue grade accuracy - IEC 62053-22 0.5s
Class / ANSI C12.20 0.5 Class•

10-690Vac direct voltage input; fits all voltage rating
system with one model•

Measurement Canada approved••

Compatible with a variety of CT options: 5A/1A,
333mV, Flexible Rogowski Coil, and 80/100/200mA

Integrated RS485 port with Modbus-RTU and BACnet
MS/TP for communication with most systems.

•

Standard DIN-rail mount for ease-of-installation

4 Channel current input including neutral
current measurement•

Compatible with both 50Hz and 60Hz systems•

Built-in energy pulse output and alarm output

Residual current measurement available•

Optional relay output for alarm and remote control

PRODUCT COMPATIBILITYDATA ACQUISITION SERVER

ACULINK 810

1

COMM ISSUE

NO COMMCOMM OKSTATION MODESTATUSRSSIAP MODERX

POWER ON
GND

ShieldControl Power

24Vdc

8

ASSOC

TX
DI5

DI5-COM

7

DI4-COM

DI6

6

DI4

DI6-COM

52

DI3-COM

DI7

4

3

DI3

DI7-COM

34

DI2-COM

DI8

2

5

DI2

DI8-COM

1

6

DI1-COM

RS485+

8

7

DI1

RS485-

7

8

M E T E R I N G

6B A S E D

5

C L O U D

RS485

4

ACUCLOUD

WIFI

3

AcuMesh

2

•

1

•

ACULINK 810

LINE
A

Accurately measure neutral current with 4th CT channel

B

C

N

1A FUSEto provide residual current measurement.

Auto Phase-Check
Designed to automatically check most common wiring

I11
I12
I21
I22
I31
I32
I41
I42

mistakes including CT orientation, as well as voltage andcurrent phase alignment.

Supports All Electrical Systems
Monitor a variety of electrical systems including threephase three wire (3P3W), three-phase four-wire (3P4W),
single-phase three-wire (1P3W two element), single-phase

VN V3 V2 V1AcuRev 1310

two-wire (1P2W one element), and more.

LOAD

NEMA 4X Rated Wall Mount
Enclosure For AcuRev 1310 Series
The AcuRev 1310 enclosure (AcuRev 1310-ENC) offers a mounting option
for AcuRev1310 Series energy meters that helps protect from tamperingand the elements.

AcuRev 1310 Series Models
1311

1312

1313

1314

Application

DIN-Rail mounted realtime
energy monitoring

DIN-Rail mounted realtime power and energy
monitoring

DIN-Rail mounted real-timebi-directional power andenergy monitoring

DIN-Rail mounted realtime multifunction
monitoring with neutral
current measurement andcalculated residual current

Metering

Energy, Voltage, Current,
Active Power

Energy, Time-of-Use, Power
Demand, Current Demand,
Voltage, Current, Power,
Power Factor, Frequency

Energy, Time-of-Use, Power
Demand, Current Demand,
Voltage, Current, Power,
Power Factor, Frequency

Energy, Time-of-Use, Power
Demand, Current Demand,
Voltage, Current, Power,
Power Factor, Frequency

Current Input

5A/1A: Field-Configurable 5A or 1A Current Transformer Input
333mV: 333mV Current Transformer Input
RCT: Flexible Rogowski Coil Current Transformer Input
80/100/200mA: Field Configurable 80mA, 100mA or 200mA Current Transformer Input

I/O Options

One relay output for alarm and remote control| 15Power Meter Solutions

4 Channel CT Input

Power Meter Solutions

EV300
Panel Meter Series
The EV300 energy meter is equipped withkey essential metering parameters for anaffordable, reliable solution. Combining
revenue grade accuracy and custom I/O
options, this panel-mountable meter’s
compact form-factor is ideal for a wide
range of applications.

ACCUENERGY.COM/EV300

C12.20 .1 CLASSKey Specifications•

Bi-directional energy metering•

Switch status monitoring and controlling•

Utility revenue grade accuracy•

Energy pulse output•

Field configurable 5A/1A CT input•

4-20mA analog transducer output•

Compatible with both 50Hz and 60Hz systems•

Over/Under limit alarm-triggered relay output•

RS485 port built-in with Modbus-RTU•

Lowest cost in the same class guaranteed•

Standard panel mount 96mm DIN-direct retrofit

PRODUCT COMPATIBILITYDATA ACQUISITION SERVER

ACULINK 810

GND

1

COMM ISSUE

NO COMMCOMM OKSTATION MODESTATUSRSSIPOWER ON
24Vdc

8

RX

AP MODE

7

ASSOC

TX
DI5-COM

DI6

6

DI5

DI6-COM

5

DI4-COM

DI7

4

DI4

DI7-COM

32

DI3-COM

DI8

2

3

DI3

DI8-COM

1

4

DI2-COM

RS485+

8

5

DI2

RS485-

7

6

DI1-COM

Shield6

7

DI1

Control Power

58

M E T E R I N G

4

B A S E D

3

C L O U D

RS485

2

ACUCLOUD

WIFI

1

AcuMeshACULINK 810

Voltage

Current

EV300 series meters are Modbus-

Supports any voltage system

Field-configurable 5A and 1A CT

RTU protocol ready, allowing

with a rating between 10V to

input to suit any industrial current

meter data interoperability

230V/400V. It also allows potential

transformer.

between devices that utilizes

transformer ratio configuration.

serial communication.

Frequency

Digital Output

Analog Output

Automatic frequency detection

Pulse output monitors all utilities

Industry standard signal 4-20mA

adapts to 50Hz or 60Hz systems

including water, gas, & electricity

analog output is used forwithout compromising accuracy,

provides energy data to any

automation and process control

simplifying the design anddata acquisition server without

and can be directly used witheliminating international OEM

communication.

any programmable logic
controller (PLC).

frequency issues.

EV300 Series Models
EV387

EV390

Voltage (V)Current (Amp)
Power (kW)
Reactive Power (kVar)
Apparent Power (kVA)Power Factor (PF)Frequency (Hz)Energy(Import/Export/Total/Net)

Reactive Energy(Import/Export/Total/Net)

Modbus-RTU via RS485
LCD Display

EV300 Series Input/Output Selection Table
E0

E1

E2

E3

E4

Digital Input

2

6

6

6

6

Digital Output (Pulse)

-

-

2

2

-

Analog Output (4-20mA)

-

-

-

2

2

Relay Output

-

2

-

-

2

Auxiliary Power 24Vdc

-

1

1

-

-

| 17

Power Meter Solutions

Modbus-RTU via RS485

Power Meter Solutions

AcuPanel 9100
Pre-Wired Metering Panels
Cut down on costly installation & avoid
wiring error with these pre-configured
and pre-installed panel metering systems.
The AcuPanel series also feature someof Accuenergy’s most powerful meters
including the Acuvim II, Acuvim L, and
AcuRev 2100 series, secured in a either a
NEMA 4 or NEMA 4X enclosure for versatile
installation options.

ACCUENERGY.COM/ACUPANELKey Specifications•

Factory pre-wired for fast, reliable installation•

Factory pre-configuration eliminates meter
programming on-site•

Required accessory components are all pre-installed•

Self-powered panel does not require separate
power supply•

Durable enclosures provide high tolerance for external
force with well protection•

Housed in either a NEMA 4 rated industrial steel
enclosure, or NEMA 4X rated polycarbonate enclosurefor either indoor or outdoor implementation•

Available metering options include the Acuvim II Series,
Acuvim L Series, AcuDC 240, and AcuRev 2100.

PRODUCT COMPATIBILITYNO COMMCOMM OKCOMM ISSUE

AP MODESTATUS

GND

1

RSSI

RX

POWER ON
Control Power

24Vdc

8

ASSOC

STATION MODE

Shield

DI6-COM

DI5

DI5-COM

7

DI4-COM

DI6

6

DI4

TX

5

2

DI3-COM

DI7

4

3

DI3

DI8

3

4

DI2-COM

DI7-COM

25

DI2

DI8-COM

1

6

DI1-COM

RS485+

8

7

DI1

RS485-

7

8

ACUVIM-L

RS485

6

ACUVIM II

WIFI

5AcuMesh

ACUDC240

DATA ACQUISITION SERVER

ACULINK 810

Hz

4

kVA

Hz

3

kvar

kVA

2

kW

kvar

1

kW

ACULINK 810

ACUREV 2100

Power Meter Solutions

Clean Factory Wiring

Components Included

Pre-Cut Enclosure

Factory installed connections

Pre-assembled shorting blocks

Two pluggable, pre-cut holes allow

and components have been

for current transformers andwires to be securely fed throughdiligently tested to be reliable

fused terminal blocks for voltage

the enclosure without any addedand dependable for an error-freeconnections are colour coded andmodifications to the enclosure.

integration into your system.

clearly labeled to allow for time-saving

Simple grounding wire are firmly

maintenance and identification.

installed inside.

NEMA 4 EnclosureStandard pre-wired enclosure includes:

Made from durable steel, this indoor rated enclosure
provides a degree of protection against dirt, dust, and•Terminal blocks for current
transformer input•

Shorting block forcurrent transformer•

Terminals blocks forvoltage input•

3 Industrial-grade fuses

other solid objects.

NEMA 4X Enclosure
Rated for indoor and outdoor use, this NEMA 4X enclosure
provides the ultimate shield against hostile environmental
hazards including adverse weather & corrosion.

AcuPanel Series Models
Compatible Meters

AcuPanel 9104

AcuPanel 9104X

AcuPanel 9104X-DC

AcuPanel 9106X

Acuvim II, Acuvim L

Acuvim II, Acuvim L

AcuDC 240

AcuRev 2100

Application

Indoor installations that require rugged protection, but
not weather resistance

NEMA Rating

NEMA 4

NEMA 4X

NEMA 4X

NEMA 4X

Steel

Polycarbonate

Polycarbonate

Polycarbonate

Material

Indoor or outdoor installations that require exceptional environmental protection andweather resistanceAnti-Corosive
Dust-Proof
Suitable for
Indoor Use
Suitable for
Outdoor Use
Pre-Wired
Pre-Configured| 19

Power Meter Solutions

AcuRev 2100
Multi-Circuit Submeter with
SnapOn CT Technology
Monitor Multiple Circuits with SnapOn CT
Technology. The AcuRev 2100 is the nextgeneration multi-circuit power and energy meter
designed to measure 18 single-phase circuits
using SnapOn CT technology for quick andeasy installations in high-density, multi-point
applications. Reliably monitor real-time energy
consumption and power quality in commercial,residential, and industrial multi-tenant energy
ACCUENERGY.COM/ACUREV-2100

management systems.

C12.20.1 CLASS
C12.20.1 CLASS

Key Specifications•

18 single-phase or 6 (or 9) polyphase circuits••

Measurement Canada approved revenue-grade(ANSI C12.2 Class 0.5 & IEC 62053-22 Class 0.5s)

Dual Ethernet ports for unparalleled communicationand daisy-chain connection•

Secure and encrypted HTTPS web server for meterreading and configuration•

Advanced power quality analysis•

Built-in WEB2 module meets all communication
protocol needs•

8GB onboard memory for data logging and historical
trend analysis•

Modbus, BACnet, SMTP, HTTP/HTTPS Post, FTP & NTP,
SFTP, SNMPv3, and RSTP•

Programming and terminal tamper-proof seal•

18 Digital Inputs for water and gas metering•

WiFi communication channel, with IPv6•

6 Digital Outputs, 2 Relay Outputs•

Remote meter access via SerialNumber.accuenergy.io•

Optional cloud-based data storage with AcuCloud

PRODUCT COMPATIBILITYDATA ACQUISITION SERVER

ACULINK 810

GND

1

COMM ISSUE

NO COMMCOMM OKSTATION MODESTATUSRSSIPOWER ON
24Vdc

8

RX

AP MODE

7

ASSOC

TX
DI5-COM

DI6

6

DI5

DI6-COM

5

DI4-COM

DI7

4

DI4

DI7-COM

32

DI3-COM

DI8

2

3

DI3

DI8-COM

1

4

DI2-COM

RS485+

8

5

DI2

RS485-

7

6

DI1-COM

Shield6

7

DI1

Control Power

58

M E T E R I N G

4

B A S E D

3

C L O U D

RS485

2

ACUCLOUD

WIFI

1

AcuMeshACULINK 810

Over/Under Limit Alarms

Power Quality Analysis

Accuenergy has designed an

Ten limit alarms can be assigned

Power quality analysis is essential ininnovative CT technology thatto various conditions. The alarm

industrial & commercial applications

allows any 80mA, 100mA, or

function effectively alerts andwhere protecting sensitive electronic

333mV current transformer to plug

protects systems by sending out

equipment is critical. AcuRev 2100

into the AcuRev 2100 submeter

notifications and automaticallyseries meters provide power

without the use of traditional

shutting down equipment. Alarms

quality parameters such as voltage

terminal blocks or error prone

can be configured for peakand current THD, individual voltage

wiring configuration. Simply attachdemand, current, or power quality

and current harmonics up to thethe SnapOn connector to a CT

thresholds. Use the web interface

31st order, voltage crest factor,

and plug into the meter for a fast,

to view active and historicalcurrent K factor, and voltage

convenient installation experience.

alarms, as well as configure

and current unbalance. These

20 SnapOn CT connectors are

new alarms.

parameters are monitored inincluded with the meter.

real-time and logged in memory.

Measurement Canada
Approved

WEB2

Data Logging

The built-in WEB2 module provides

Real-time energy metering, power

The AcuRev 2100 is approved

remote access to real-time energy

quality analysis, and I/O data

to meet stringent Measurement

data monitoring. View details on

can be stored in the onboard,

Canada specifications andpower & energy, power quality,

non-volatile memory. Logged

ANSI C12.20 Class 0.5 and IEC

and other critical measurements.

information can be retrieved via

62053-22 Class 0.5s accuracy

A wide range of communication

serial connection or remotely byrequirements. Terminal sealing

methods are supported including

Ethernet in Excel, CSV, or text

provides added security, prevents

dual Ethernet & WiFi. Additionally, it

format for historical trending

tampering with metering settings,

provides compatibility with an arrayand system analysis. The ample

and safeguards data integrity.

of industrial protocols includinginternal memory provides class-

Modbus TCP/IP, BACnet IP, MQTT,

leading storage capacity suitable

SMTP, HTTP/ HTTPs Post, and more.

for any advanced application. For
instance, it will take over 100 years
to fill the memory if the meter is

IP66/67 Rated
Wall Mount Enclosure

configured to monitor 100 energy
parameters at 5-minute intervals.

The AcuRev 2100 enclosure (ENC-12127PIP67)
offers a mounting option for AcuRev 2100
Series energy meters that helps protect fromtampering and the elements.

AcuRev 2100 Series Models
AcuRev 2110
Application

Multi-Tenant & High-Density Submetering

Number of Single Phase Circuits Monitored

18

Number of Three Phase Circuits Monitored

6

CT Input
Communication

80mA, 100mA, 333mV, Rogowski Coil
RS485, Dual RJ45, WiFi

| 21

Power Meter Solutions

SnapOn CT Technology

Power Meter Solutions

AcuDC 240
DC Energy Meter
The AcuDC 240 series of DC powerand energy meters are designed
for monitoring DC consumption
and generation in applications likerenewable energy. The AcuDC 240
is a effective metering device able toread voltage, current, power, energy
and ampere-hour.

ACCUENERGY.COM/ACUDC-240

Key Specifications
NEW•

DC shunts with 0.1% accuracy, ranging from 50A to
2000A input•

Built-in three-line LCD•

Modbus-RTU communications.

•Monitor and control power switches•

Standard 72x72mm size allows for drawer-type
panel installation•

0.2% accuracy on voltage and current; 0.5% on
power and energy parameters.

•

Accessible with SCADA, PLC systems•

Onboard datalogging provides historical logging
of all DC metering parameters for analysis•

Built-in Hall effect sensor power supply (+/-15Vdc)
for ease-of-measuring•

Optional digital input and output, analog andrelay output I/O expansions

PRODUCT COMPATIBILITYDATA ACQUISITION SERVER

ACULINK 810

GND

1

COMM ISSUE

NO COMMCOMM OKSTATION MODESTATUSRSSIPOWER ON
24Vdc

8

RX

AP MODE

7

ASSOC

TX
DI5-COM

DI6

6

DI5

DI6-COM

5

DI4-COM

DI7

4

DI4

DI7-COM

32

DI3-COM

DI8

2

3

DI3

DI8-COM

1

4

DI2-COM

RS485+

8

5

DI2

RS485-

7

6

DI1-COM

Shield6

7

DI1

Control Power

58

M E T E R I N G

4

B A S E D

3

C L O U D

RS485

2

ACUCLOUD

WIFI

1

AcuMeshACULINK 810

Wind Turbines

Directly monitor the power andMeter the production andenergy produced from the solar

effectiveness of wind generated

array, before the inverter, for theenergy before its sent into themost accurate analysis of solar

grid and integrate with existingproduction.

systems through Modbus-RTU.

Communications
Modules
These plug-in expansion
modules are available for the
AcuDC line of DC power andenergy meters.

Electric Vehicle Charging Stations
Audit and observe the electrical consumption of charging stations or
individual EV motors from a charge station in real time, as an accumulated
total, and with historical data logging. Compatible with brand new highprecision DC shunts, offering various input options from 50A to 2000A.

AcuDC 240 Series
Din Rail Mounting Adapter
AcuDC 240 Series DIN Rail adapter(DC-DIN) provides an easy installation
for all panel-mounted AcuDC 240
meter models and I/O options that
require a DIN rail solution.

AcuDC 240 Series Models
Function

AcuDC 243

Application

All DC Monitoring & Metering Applications

Metering Parameters

Voltage, Current, Power, Energy, Ampere-Hour

I/O Modules Available
Data Logging

Optional

Communication Protocol

Modbus-RTU

AcuDC 240X Expansion Modules
DigitalInput (DI)

AnalogOutput (AO)

X1

2

2

X2

2 (4-20mA / 0-20mA)

2 (0~5V / 1~5V)

X3

2

X4

2

X5

2

AnalogInput (AI)

Relay
Output (RO)DigitalOutput (DO)Hall Effect Sensor
Power Supply

2
2+/-15Vdc

X6

2 (4-20mA / 0-20mA)+/-15Vdc

X7

2 (0-5V / 1-5V)+/-15Vdc| 23

Power Meter Solutions

Solar Arrays

Communications & Software Solutions

AcuCloud
Energy Management Software
AcuCloud Software is a cloud-based energy
data management platform that provides
facilities professionals access to real-time

ACUCLOUDC L O U D

B A S E D

and historical data from power and energy

M E T E R I N G

meters. Users can view, download, and shareenergy data as well as perform sophisticatedanalysis and report creation.

ACCUENERGY.COM/ACUCLOUDKey Features•

Feature-rich set of tools for monitoring real timeenergy, performing M&V, interpreting energy trends,
and analysing a complete energy portfolio.

•

Efficient delivery of complex data in an intuitive,user-friendly format.

•

Seamless integration with Accuenergy web-enabled
devices or via AcuLink 810 as a gateway for serial
and third party devices.

PRODUCT COMPATIBILITY
ALL
METERSFlexible Reporting

Convenient Alerts

Energy managers have access to

Collaborate with colleagues

When energy usage reaches

energy data in unparalleled detail.

on critical facility decisions:a threshold or if a meter goes

AcuCloud stores the history for

AcuCloud features a powerfuloffline, a timely alert can beimportant energy parameters

sharing tool which allows data

critical to ongoing facility

including per phase and system

to be downloaded & emailed for

operations. AcuCloud offers

voltage, current, power, energy,

insightful project coordination.

configurable email alerts thatpower factor, demand, and pulse

Easily send all reports or choose

are automatically triggered.

data in 5-minute intervals.

from a range of valuable,

Data Sharing + Integration
Successful energy management

pre-configured dashboards
that highlight key energy

Powerful Data Analysis

management metrics.

Metered data has no value

depends on the stable integration

without additional analysisof energy data across platforms.

from sophisticated software.

AcuCloud makes it easy to forward

Simple, yet powerful data

all metered data to a 3rd party

analytics tools provide

software system for analysis,

actionable insight. Monitor

reporting, billing, efficiency

trends, perform analysis,

studies, or measurement &manage energy projects,

verification projects. Multiple

and more.

data formats are supported.

APPLICATIONS:
Tenant Kilowatt-Hour Profiles

Tenant Billing Management•

Provide each tenant with account access to view
real-time energy & consumption trends•

Manage tenant bills individually•

Adapt to various billing structures•

Tenant profiles raise awareness of energy usage andcan be compared against building averages•

Generate bills from multiple submeters forinternal rebilling or cost allocation•

Analyze the energy usage for multiple tenant groups•

Use custom rate structures and formulas tocreate bills that fit any circumstance

ACUCLOUD INTEGRATION EXTENSIONS:
Tariff Analytics

Measurement and Verification

Quickly assess the anticipated savings whennegotiating new energy contracts with utilities. Entera proposed rate and the tariff analysis tool calculates
payments based on the past energy consumption.

An advanced alternative to tedious spreadsheets:track energy conservation, calculate average
consumption, and verify outcomes after upgrades.

Trending Analytics

Dashboard

Energy profiles make it easy to analyze usage patterns
and identify irregularities.

Use configurable widgets to monitor measurements,
metrics, and savings.

| 25

Communications & Software Solutions

Data Storage + History

Communications & Software Solutions

AcuLink 810
Data Acquisition Server &Gateway
Accuenergy’s AcuLink 810 is a comprehensive
DAQ BACnet gateway and server. Devices
and metering data can be managed andaccessed through a central hub before
distributed to an energy management
system. Energy data is available to be
stored locally or transferred via an IP-based
network to a remote server or controller.

ACCUENERGY.COM/ACULINK-810

Key Specifications•

Track energy usage, peak demand and otherenergy parameters•

BACnet-MS/TP data acquisition and logging with
8GB on-board memory•

BACnet gateway (Converts Modbus-RTU and
BACnet-MS/TP to BACnet IP)•

Remote access to monitor and configure devices•

RSTP high availability to reduce network downtime•

Poll data from all RTU devices via Modbus-TCP/IP•

Ethernet Gateway for Modbus RS485 and Digital
Output Devices•

Remote web-server access for real-time data and easy
configurations•

Dual Ethernet RJ45 port and WiFi communication channels•

SSL and TLS1.2 compliant enhanced cybersecurity protection•

Over/Under alarm monitoring for connected devices

PRODUCT COMPATIBILITYALL
ACUCLOUDC L O U D

B A S E D

M E T E R I N GMETERSData Logging

Embedded Web Server

AcuLink 810 can read Modbus,

Critical data, such as energy andAccess and monitor all connected

BACnet, and MBus devices

power quality measurements, isdevices anytime, anywhere using aoffering integrators the option

stored in 8GB non-volatile memory

web browser. A friendly UI allows

to retrofit existing systems

with a capacity for over threeusers to easily view of all collectedsaving time and costs. Support

years of energy data collected

devices with detailed real-time

for multiple protocols facilitatesat 15-minute intervals. Logged

metering summary, setup, alarms,

the intercommunication of

information is easily retrieved

and configurable upload channels.

devices by allowing such devices

from a web browser or posted to

to interoperate on a BACnet IP

a remote sever via HTTP/HTTPs,

network.

FTP in CSV or JSON format.

Water & Gas Meters

Cloud Network

EMS Software

Aculink 810

DATA ACQUISITION SERVER

ACULINK 810

81

POWER ON

NO COMMCOMM ISSUE

COMM OKSTATUSRSSISTATION MODE

GND

7

RX

AP MODE
DI6-COM

DI6

6

ASSOC

TX

5

DI5-COM

DI7

4

DI5

DI8

3

DI4-COM

DI7-COM

2

DI4

DI8-COM

1

2

DI3-COM

RS485+

8

3

DI3

RS485-

7

4

DI2-COM

24Vdc

6

5

DI2

Control Power

5

6

DI1-COM

Shield4

7

DI1

AcuCloud

Local Access

RS485

3

WIFI

2

AcuMesh1

Power/ Energy Meters
8

AcuBilling

Other Software/
Remote Servers

IoT Connectivity

Poll Downstream Data

Daisy Chain 32 Devices

Support for MQTT protocol allows

Allow a Modbus master on aUsers can daisy-chain multiple

subscribers to instantly receive

remote network to poll downstream

devices using the RSTP protocol.

up-to-date device data to theirmetering data directly from all

This can cut down the amountmobile phone or other Internet of

RTU devices that are connectedof network switches required inThings devices. Messages can beto the DAQ BACnet gateway. The

different applications and allows

configured to send at intervals for

AcuLink 810 supports Modbus

the use of 1 network switch/ routerspecific connected devices.

polling for eight pulse counters

to be used with multiple devices.

used for water, heat, gas andMultiple Modbus- RTU devices canelectricity metering.

be connected via USB port.

AcuLink 810 Gateway Conversion
AcuLink 810-X
Gateway

Digital Input

AcuLink 810-900

AcuLink 810-868

Incoming Protocols

Modbus-RTU, Modbus-TCP/IP, BACnet-MS/TP, BACnet-IP, SunSpec, Mbus, Pulse Counter, Virtual Meter

Outgoing Protocols

Modbus-TCP/IP, BACnet-IP, SNMP, HTTP, HTTPs, FTP, sFTP, MQTT
8 Pulse Counters

Onboard Memory

8GBInterval Logging

1 to 1,440 Minutes

AcuMesh 900Mz
AcuMesh 868Mz| 27

Communications & Software Solutions

BACnet Gateway

Communications & Software Solutions

AcuMeshWireless RS485 Transceiver
The AcuMesh network solution is designed
to connect RS485-enabled devices including
meters, sensors, gateways, PLCs, and more
into a seamless wireless network. It offers
a cost-effective, non-intrusive installationthat eliminates the need for additional
communications wiring.

ACCUENERGY.COM/ACUMESH

Key Specifications•

Devices are connected automatically on power up
without configuration or software•

Compatible with Modbus-RTU protocol•

Utilizes either the 900MHz or 868MHz frequency
band available in most countries.

•

Highly secure communication with 128-bit
Advanced Encryption Standard (AES)•

Field-upgradable firmware•

Complex networks are easily configured using
free software•

Communicate wirelessly between meters and other
RS485 devices running any protocol within a building
or campus•

Long-range communication: 1000 ft (305m) indoor /4 Miles (6.5km) outdoor in a single hop

AcuMesh Wireless RS485 Network
The AcuMesh wireless RS485 network solution eliminates the need for physical RS485 communication wiring.
Devices directly connect to an AcuMesh transceiver and the job is done. The AcuMesh transceiver transmits data andcommands wirelessly within the network.

Current Transformers

AcuCT Flex
Rogowski Coils
Designed for unmatched ease-of-installation,
this specialized line of flexible AC current
transformers is ideal for deployment in power
metering, power quality, and general use
applications where space is limited.

ACCUENERGY.COM/ACUCT-FLEX

Key Specifications• High accuracy for demanding applications• Wide current input range 5A - 50,000A AC• Four coil lengths available: 16”, 24”, 36”, or 47”• A broad frequency range makes it an excellent choice
for monitoring harmonics and power quality• Directly compatible with Accuenergy RCT input devices no external power supply or integrator needed

4 Standard Lengths

Wide Current Sensing

High Accuracy & Linearity

We offer four coil lengths: 16”,

Measure current from 5A to

Accuracy is 0.5% across the entire24”, 36”, and 47”. Custom lengths

50,000A on a standard coil.

range of measurement.

available upon request.

Higher current range available upon request.

Flexible Style CT

Standard & Custom Output

Rope-like coil allows it to fit into

Wide Frequency
Response Range

limited spaces where regular,Standard frequency response

available, including: 100mV/1000A,

ridged CTs cannot be used.

range 10 Hz - 20kHz.

40mV/1000A, 25mV/1000A,

Higher frequency range available upon request.

10mV/1000A.

Multiple output ratio options

AcuCT Flex Series Options
Input Range

RCT16

RCT24

RCT36

RCT47

5A - 50000A

5A - 50000A

5A - 50000A

5A - 50000A

Output Option

Output to Specified RCT input

Window Size

4.17” (106mm)

7.01” (178mm)

10.67” (271mm)

14.53” (369mm)

Length

15.75” (400mm)

23.62” (600mm)

35.43” (900mm)

47.24” (1200mm)

Accuracy

0.5% Combined with Acuvim II Series at Any Point| 29

Current Transformers

RIK Series
Rogowski Integrator
The integrators are a versatile, plug-and-playsolution that allows Rogowski coils to be
field-configurable for multiple CT input ratios.
Single-phase and three-phase options areavailable.

ACCUENERGY.COM/ACUCT-RIK

Key Specifications• CT ratios are field-configurable for on-site flexibility.

• Individual CT ratios can be configured for each channel.

• Output types include 0-5A, 0-1A, 0-333mV, 4-20mA,
0-20mA, 0-5V, 0-10V• Works in any single-phase or three-phase applications.

• RIK 1AR: 0-A Output Relay Class (5P20).

• Four coil lengths available (sold separately).

• Works in both 50Hz and 60Hz systems.

RIK Series Options
RIK 1AR*
Current Measurement Range
Sensing Range
Output Rated Options
Accuracy

RIK mV*RIK mA*RIK V*

0.25A - 100kA

2.5A - 60,000A

50A, 200A, 500A,
2000A and 5000A(User Selectable)

500A, 1000A, 2500A, 5000A, 10000A, 25000A and 50000A (Field Configurable)

0-1A

0 – 6A RMS(0 – 5A RMS Nominal)

0-333mVac

4-20mAdc, 0-20mAdc

0-5Vdc, 0-10Vdc% at 1A, 5% at 20A

1.0%

1.0%

1.0%

1.0%

Rogowski Coil Sizes
Frequency

RIK 5A16”, 24”, 36”, 47”
50Hz and 60Hz

Single-Phase
Three-Phase*Rogowski coil and power supply sold separately.

45Hz to 65Hz

AcuCT R

High-accuracy split core current transformers witha unique press-to-open hinged design and current
input range from 5A to 5000A AC. AcuCT R also offers
revenue grade accuracy for billing applications.
ACCUENERGY.COM/ACUCT-R

AcuCT R Series Options
AcuCT-075R

AcuCT-100R

AcuCT-125R

AcuCT-200R

AcuCT-3135R

AcuCT-4161R

AcuCT-5170R

Input Range

1A - 150A

5A - 250A

5A - 400A

5A - 1000A

5A - 1000A

5A - 5000A

5A - 5000A

Typical Input

50A, 100A,
150A

100A, 200A,
250A

100A, 200A,
300A, 400A

400A, 600A,
800A, 1000A

600A, 800A,
1000A, 1200A,
1500A

1200A, 1600A,
2000A, 2500A,
3000A, 4000A,
5000A

2000A, 3000A,
4000A, 5000A

OutputOption333mV, 80mA,
100mA, 200mA

1A, 333mV,
80mA, 100mA,
200mA

1A, 333mV,
80mA, 100mA,
200mA

1A, 333mV,
80mA, 100mA,
200mA

5A, 1A, 333mV,
80mA, 100mA,
200mA

5A, 1A, 333mV,
80mA, 100mA,
200mA

5A, 1A, 333mV,
80mA, 100mA,
200mA

WindowSize

0.75" x 0.75"

1" x 1"

1.25" x 1.25"

2" x 2"

3.1" x 3.5"

4.1" x 6.1"

(19.5 x 19.5 mm)(25 x 25 mm)(32 x 32 mm)(51 x 51 mm)(80 x 90 mm)(105 x 155 mm)

5.1" x 7"(130 x 180 mm)

2.3” x 2.3” x 0.9”

2.6” x 2.6” x 0.9”

3.2” x 3.2” x 0.9”

4.4” x 4.4” x 1.25”

5.7” x 6.1” x 1.25”

7.3” x 9.3” x 1.8”

8.3” x 10.2” x 1.8”

(58 x 58 x 22 mm)(65 x 65 x 22 mm)(82 x 82 x 22 mm)(111 x 111 x 32 mm)(144 x 154 x 32 mm)(185 x 235 x 45 mm)(210 x 260 x 45 mm)Exterior
Dimensions
Accuracy

IEC 60044-1 0.5s class

AcuCT mV

333mV Split-Core CT
Split-core CT with 333mV output is designed for
retrofit projects used in general panel metering
applications. It can be pulled apart and securely
pushed back together to allow installation without
disrupting the existing system.
ACCUENERGY.COM/ACUCT-MV

AcuCT mV Series Options
AcuCT-075

AcuCT-125

AcuCT-200

AcuCT-3050

Input Range

10A - 200A

30A - 600A

60A - 1500A

40A - 5000A

Typical Input

100A, 200A

300A, 400A, 600A

600A, 800A, 1000A, 1200A,
1500A

400A, 600A, 1000A, 1500A,
2000A, 3000A, 5000A

Rated Option

333mV0.75” x 0.75”

1.25” x 1.25”

2” x 2”3” x 5”(19.1 x 19.1 mm)(31.8 x 31.8 mm)(50.8 x 50.8 mm)(76.2 x 127 mm)

Exterior
Dimensions

2” x 2.098” x 0.669”

3.248” x 3.35” x 1.025”

4.764” x 5” x 1.81”

5.748” x 7.5” x 1.402”(50.8 x 53.3 x 17 mm)(82.5 x 85.1 x 26 mm)(121 x 127 x 30 mm)(146 x 190.5 x 35.6 mm)

Accuracy

0.5%

0.5%

0.5%

0.5%

Window Size

| 31

Current Transformers

Revenue-Grade Split-Core CT

AcuCT 5A

5A Split-Core CT

Current Transformers

range of industrial metering solutions whereaccuracy is critical. Designed with specialized
mounting clips and tension screws for optimal
installation.
ACCUENERGY.COM/ACUCT-5A

AcuCT 5A Series Options
AcuCT-0812

AcuCT-2031

AcuCT-3147

AcuCT-3163

Input Range

5A - 400A

5A - 1000A

5A - 1600A

5A - 5000A

Typical Input

100A, 150A, 200A, 250A,
300A, 400A

400A, 600A, 800A, 1000A

1000A, 1200A, 1600A

2000A, 2500A, 3000A,
4000A, 5000A

Output Option

5A, 1A

5A, 1A

5A, 1A

5A, 1A0.83” x 1.22”

1.97” x 3.15”

3.15” x 4.72”

3.15” x 6.3”

(21 x 31 mm)(50 x 80 mm)(80 x 120 mm)(80 x 160 mm)

Exterior
Dimensions

3.5” x 4.13” x 1.57”

3.5” x 4.13” x 1.57”

5.67” x 7.28” x 1.97”

6.93” x 9.72” x 2.76”(89 x 105 x 40 mm)(89 x 105 x 40 mm)(144 x 185 x 50 mm)(176 x 247 x 70 mm)

Accuracy

0.5%

0.5%

0.5%

0.5%

Window Size

AcuCT Hinged

Compact Split-Core CT
Ultra small hinged split-core CT can be used onbranch circuits within an electrical panel with spatial
contraints. Simple to install and quick to deploy inretrofit applications with a 333mV rated output.
ACCUENERGY.COM/ACUCT-HINGED

AcuCT mV Series Options
AcuCT-H040

AcuCT-H063

AcuCT-H100

AcuCT-H138

Input Range

5A - 75A

5A - 150A

5A - 250A

10A - 630A

Typical Input

20A, 30A, 40A, 50A, 60A

50A, 100A, 150A

100A, 120A, 200A, 250A

200A, 400A, 600A

Rated Option
Window Size
Exterior
Dimensions
Accuracy

333mV
0.4”

0.63”

1”

1.38”

(10.2 mm)

(16 mm)(25.4 mm)

(35 mm)1.16” x 1.64” x 1.04”

1.42” x 2.09” x 1.2”

2” x 2.76” x 1.52”

2.56” x 3.27” x 1.57”(29.4 x 41.7 x 26.4 mm)(36 x 53 x 30.5 mm)(50.8 x 70.1 x 38.6 mm)(65 x 83 x 40 mm)

0.5%

Current Transformers

Split-core CT with 5A output is ideal for a wideSolid-Core Current Transformer
Accuenergy solid core CTs are compact, cost-efficient,and provide high accuracy measurements in a rugged
form factor. Designed specifically for integration into
products that require accurate 1% signaltransformation, the solid core design makes themespecially resilient in harsh, industrial environments.
ACCUENERGY.COM/ACUCT-S113

AcuCT S113 Solid-Core Series Options
AcuCT S113-200

AcuCT S113-300

AcuCT S113-400

Primary Input

200A

300A

400A

Rated Output

1A, 5A, 333mV

1A, 5A, 333mV

1A, 5A, 333mV

Rated Voltage<1,000V<1,000V<1,000V

Burden≤3.75VA≤3.75VA≤3.75VA

Rated Frequency
Exterior
Dimension

50Hz - 60Hz

50Hz - 60Hz

50Hz - 60Hz

2.38” x 2.68” x 0.96”

2.38” x 2.68” x 0.96”

2.38” x 2.68” x 0.96”(60.5 x 68.0 x 24.5 mm)(60.5 x 68.0 x 24.5 mm)(60.5 x 68.0 x 24.5 mm)

AcuCT S77

Revenue-Grade Solid-Core CT
Solid-core CT feature a class-leading 0.15%
accuracy while exceeding Measurement Canadarequirements for use in metering installations. Its
compact size can be used for applications that
requires high precision signal transformation.

ACCUENERGY.COM/ACUCT-S77

AcuCT S77 Series Options
AcuCT S77-100

AcuCT S77-200

Primary Input

100A

200A

Rated Output

80mA, 100mA

80mA, 100mA

Resistance

50 MΩ

50 MΩ

Burden

0.005

0.005

Window Radius
Exterior Radius (in)

0.78”

0.78”

(19.7 mm)

(19.7 mm)

2.01

2.01

| 33

Current Transformers

AcuCT S113

AcuCT S335

NEW PRODUCTNEW PRODUCTSwitchgear Solid-Core Current
Transformer

Busbar Solid-Core Current
Transformer

High precision solid-core current transformer

Ideal for mounting to a busbar or a cable, thefor permanent installations. The AcuCT S220

AcuCT S335 is a solid-core current transformer

features multiple input and output options

for permanent installations. Features multiple

in a small compact form factor. It provides

input and output options in a compact

consistent, reliable measurements acrossform factor. It provides consistent, reliableindustrial and commercial for general metering

measurements across industrial and commercial

or switchgear applications.

for general metering applications.

ACCUENERGY.COM/ACUCT-S220

ACCUENERGY.COM/ACUCT-S335

AcuCT S220 Series Options

AcuCT S335 Series Options

Current Transformers

AcuCT S220

AcuCT S220

AcuCT S335

Primary Input

300A, 500A, 600A, 800A, 1000A, 1200A,
1500A

Primary Input

500A, 600A, 800A, 1000A, 1200A, 1500A,
2000A, 2500A, 3000A

Rated Output

5A, 1A, 333mV

Rated Output

5A, 1A, 333mV

Insulation Resistance
Burden500V/100MΩ min
2.5-5VA
4.53” x 4.92” x 1.26”

Insulation Resistance
Burden500V/100MΩ min
2.5-5VA

Exterior
Dimension(115.0 x 125.0 x 32.0mm)

Exterior
Dimension(146.0 x 156.0 x 32.0mm)

Window Size

Ø 57.0mm (2.24”)

Window Size

Ø 72.0mm (2.83”)

5.75” x 6.14” x 1.26”

AcuCT S650

NEW PRODUCTNEW PRODUCTInstrument Solid-Core Current
Transformer

Solid-Core Current Transformer

The AcuCT 433 is used in permanent metering
installations with rated outputs for 5A, 1A, or
333mV. Accuracy rating at 0.5%, it provides
consistent, reliable measurements acrossindustrial and commercial for general metering

Current Transformers

AcuCT S433

High accuracy solid-core current transformer
for permanent installations. The AcuCT
S650 features multiple input and output
options in a small compact form factor. It
provides consistent, reliable measurements
across industrial and commercial for generalapplications.

metering applications.

ACCUENERGY.COM/ACUCT-S433

ACCUENERGY.COM/ACUCT-S650

AcuCT S433 Series Options

AcuCT S650 Series Options

AcuCT S433

AcuCT S650

Primary Input

800A, 1000A, 1500, 2000A, 2500A, 3000A,
3500A, 4000A

Primary Input

800A, 1000A, 1500A, 2000A, 2500A,
3000A, 3500A, 4000A

Rated Output

5A, 1A, 333mV

Rated Output

5A, 1A, 333mV

Insulation Resistance
Burden500V/100MΩ min
2.5-5VA
4.53” x 4.92” x 1.26”

Insulation Resistance
BurdenExterior
Dimension(115.0 x 125.0 x 32.0mm)

Exterior
Dimension

Window Size

Ø 3.66” (93.0mm)

Window Size

500V/100MΩ min
2.5-5VA
8.66” x 9.06” x 1.38”(220.0 x 230.0 x 35.0mm)

6.30” x 6.30”(160.0 x 160.0mm)

| 35

HAK

Current Transformers

HAB 16555

DC Current Sensors

Hall Effect Current Sensors

Ideal for retrofit installation, the split-core,

The HAK Hall Effect current sensor measures

nonintrusive design offers seamless integration

DC current up to 1000A with a rated output

into any existing DC electrical system using a bus

signal at either 4-20mA or 0-5V. Ideal forbar or other large conductor. Available in bothsensitive environments, the Hall Effect provides

unidirectional and bidirectional options, measurea natural, protective field that isolates theup to 5000A with a rated output signal of either

sensor from high electrical fluctuation from the

4-20mA or 0-5V.

conductor.

ACCUENERGY.COM/HAB

DC Current Sensor Series Options

ACCUENERGY.COM/HAKHall Effect Current Series Options
HAK21

HAK40

Primary Input

50A, 100A, 200A

400A, 600A, 1000A

Rated Output

4-20mA, 0-5V

4-20mA, 0-5V

0.83

1.58

HAB-16555
Primary Input

1000A, 2000A, 3000A, 4000A, 5000A

Rated Output

4-20mA, 0-5V

Window Diameter Size (in)6.50 x 2.17

Window Size (mm)165 x 55

Exterior
Dimension

3.80” x 9.25” x 1.93”

Accuracy

0.5%

Bidirectional(96 x 235 x 49 mm)

Optional

Window Diameter Size (in)Window Size (mm)Exterior
Dimension
Accuracy
Bidirectional

21

40

2.36” x 2.40” x 0.63”

3.94” x 3.94” x 0.94”(60 x 61 x 16 mm)(100 x 100 x 24 mm)

0.5%
Optional

HV2
The HV2 Hall effect DC voltage sensor series is designed toprovide reliable, accurate voltage measurements in DC
applications up to 1500V. Ideal for railway, DC coupledenergy storage, solar systems, or other high voltage DC
installations.
ACCUENERGY.COM/HV2

HV2 Series Options
HV2-1000

HV2-1200

HV2-1500

Primary Input

1000V

1200V

1500V

Rated Output

0-5Vdc0-5Vdc0-5VdcExterior Dimension

6.57” x 2.44” x 3.58” (167.0 x 62.0 x 91.0mm)

Accuracy

0.50%

0.50%

0.50%

Polarity

Terminal Connection

Terminal Connection

Terminal Connection

DC Shunts

Shunt Series
DC current shunts are engineered for precision
measurement in DC current systems. Pair with a
DC power meter in renewable energy, mass transit,
battery charging, heavy industrial environments, andother DC current applications.
ACCUENERGY.COM/DC-SHUNTS

DC Current Shunt Series Options
Shunt

50A

100A

200A

300A

400A

500A

600A

1000A

2000A

Voltage Drop

75mV

75mV

75mV

75mV

75mV

75mV

75mV

75mV

75mV

Primary Input

50A

100A

200A

300A

400A

500A

600A

1000A

2000A

Operation
Temperature-40°C to80°C / -40°F
to 176°F-40°C to80°C / -40°F
to 176°F-40°C to80°C / -40°F
to 176°F-40°C to80°C / -40°F
to 176°F-40°C to80°C / -40°F
to 176°F-40°C to80°C /-40°F to176°F

-40°C to80°C /-40°F to176°F

-40°C to80°C / -40°F
to 176°F-40°C to 80°C
/ -40°F to
176°F

4.09” x 0.85”
x 0.08”4.09” x 0.85”
x 0.08”4.09” x 0.87”
x 0.12”4.72” x 1.77”
x 0.16”

4.72” x 1.77”
x 0.16”

4.72” x 1.77”
x 0.16”

4.72” x 2.44”
x 0.16”

4.92” x 2.76”
x 0.83”

7.87” x 3.31”
x 3.82”

0.1%

0.1%

0.1%

0.1%

0.1%

0.1%

0.1%

0.2%

0.5%

Exterior
Dimension
Accuracy(104.0 x 21.5
x 2.0 mm)(104.0 x 21.5
x 2.0 mm)(104.0 x 22.0
x 3.0 mm)(120.0 x 45.0
x 4.0 mm)(120.0 x 45.0
x 4.0 mm)(120.0 x 45.0
x 4.0 mm)(120.0 x 62.0
x 4.0 mm)

(125.0 x 70.0
x 21.0 mm)(200.0 x 84.0
x 97.0 mm)| 37

Current Transformers

HV2 SeriesCurrent Transformers

AcuCT C
Current Transformer Converter
AcuCT-C Series access-type precision 5A current
transformer is approved by Measurement Canada for
rated systems higher than 400A and 800A. Designedwith a closed magnetic core, the CT’s main benefit
is derived from its ultra-micro crystal magnetic core
and an advanced secondary winding process toprovide stable performance and high accuracy 0.15
measurement.

NEW PRODUCTACCUENERGY.COM/ACUCT-C

Key Specifications• Measurement Canada Approved• Phase error < 8′

• IEEE Std C57.13-2016 0.15 class accuracy• Ratio error < 0.5%

• 500V/100MΩ min insulation resistance• Frequency: 50-60Hz• 3,000Vac withstand voltage

AcuCT C Series Options
AcuCT C
Input Rating

5A

Rated Output

80mA, 100mA

Phase Error< 8’

Accuracy

0.15

Exterior Dimension

2.11” x 3.10” x 1.20”(53.5mm x 78.5mm x 30.5mm)

ACCUENERGY (CANADA) INC.
440 Comstock Road,
Toronto, ON M1L 2H6, Canada
TF:

1-877-721-8908

INT:+1-416-497-4100

FAX:+1-416-497-4130

E:marketing@accuenergy.com

ACCUENERGY PACIFIC AUTOMATIONACCUENERGY SOUTH AFRICA (PTY) LTD.

COMPANY LTD.

Castle Walk Corporate Park, Block B, Cnr.

400 Continental Blvd., Suite 600
LOS ANGELES

ISO 9001, 14001& 45001 Certified

El Segundo, CA 90245, USA
TF:

1-877-721-8908

PRETORIA

Nossob & Swakop Street, Erasmuskloof,
Pretoria, 0181, South Africa
TF:+27 (0) 87 802 6136

All specifications are subject to change without notice.
| 39

www.accuenergy.com

September, 2024 Version: 1.6.8