For Australia and New ZealandSE5K-AUB / SE7K-AUB / SE8.25K-AUB / SE10K-AUB
12 – 25INVERTER

SolarEdge Residential
Three Phase Solar Inverter

YEAR
WARRANTY

The ideal solution for residential PV installations
Supports optional smart energy devices andexpansion of system capabilities

Excellent reliability with standard 12-year warranty(extendable to 20 or 25 years)

Ready for use with energy storage – one inverter
for both PV system and battery energy storage

Advanced safety features, including SafeDC™ andintegrated arc fault protection

Single vendor solution for seamless operation of
all system components, and one address forwarranty and service issues

Quick inverter commissioning directly from asmartphone using SolarEdge’s SetApp

Built-in module-level monitoring for greater
visibility into system performancesolaredge.com

Suitable for outdoor or indoor installations

SolarEdge Residential Three Phase Solar Inverter
For Australia and New ZealandSE5K-AUB / SE7K-AUB / SE8.25K-AUB / SE10K-AUB
SE5K-AUB
Applicable to inverters with part number

SE7K-AUB

SE8.25K-AUB

SE10K-AUBSEXXK- AUBTEBEU4OUTPUT
Rated AC Power Output

5000

7000825010,000

Maximum AC Power Output

5000

7000

8250

10,000

VA
VA

Rated Current (per phase)

8121416a.cA

AC Output Voltage – Line to Line / Line to Neutral (Nominal)

400 / 230

Vac

AC Output Voltage – Line to Neutral Range

184 – 264.7

Vac

AC Frequency

50 ± 5%

Maximum Continuous Output Current (per Phase)

8Hz

1214

Maximum Inrush Current AC (Peak / Duration)

16A

3 / 20Maximum Output Fault Current

26

Maximum Output Continuous Overcurrent Protection

851
11.5

14

Overvoltage Category (Mains)

OVC III

Overvoltage Category (PV)OVC II

Protective ClassA16A

13,500WI

Grids Supported – Three Phase

3 / N / PE (WYE with Neutral)

Power Factor Range

1 ± 0.8

Utility Monitoring, Islanding Protection,Configurable Power Factor, Country Configurable Thresholds

Yes

Active Anti-Islanding Method

Slip mode frequency shift

INPUT – DC (PV AND BATTERY)
Maximum DC Power (Module STC)

6750

9450

Transformer-less, Ungrounded
Maximum Array Input Voltage
PV Input Operating Voltage Range
Maximum Voltage to Earth (DC to GND)
Maximum Input Current

11,135
Yes450Vdc

375 – 450

d.c V450
14Maximum Inverter Backfeed Current to Array0Reverse-Polarity Protection

Yes

Ground-Fault Isolation Detection

2328

Adc

2328

d.c A

97.1

97.4

350kΩ Sensitivity

Maximum Inverter Efficiency

97.8

Isc PV (Absolute Maximum)

1420

European Weighted Efficiency

96.3

97

Nighttime Power Consumption%<4Inverter Topology
Short Circuit Current from the PV Array

Vdc

20

Non-isolated
1420

2328

BATTERY STORAGE(1)Supported Battery Types

SolarEdge Home Battery 400V, using SolarEdge Home Network only

Number of Batteries per Inverter

Single battery

Continuous Power (Charge / Discharge)

Up to 5kW

ADDITIONAL FEATURES
Supported Communication Interfaces(2)Inverter Commissioning
Smart Energy Management(5)2 x RS485, Ethernet, Wi-Fi(3), ZigBee for Smart Energy (optional)(4)With the SetApp mobile application using built-in Wi-Fi access point for local connection
Export Limitation, Home Energy Management (Device Control)

STANDARD COMPLIANCE
SafetyGrid Connection Standards
Emissions
RoHS%
W

IEC62109, AS/NZS3100
AS/NSZ 4777.2:2020, EN 50549-1
IEC61000-6-2, IEC61000-6-3, IEC61000-3-11, IEC61000-3-12
Yes(1) Requires firmware version 4.21.1xx and up, for sites with only one inverter.
(2) Specifications of optional communication options are available in the Knowledge Center.
(3) Wi-Fi connectivity requires connection of an additional Wi-Fi component, ordered separately. For details, ask your SolarEdge salesperson or check the Communication product page.
(4) For details, see the Zigbee Plugin for Inverters with SetApp Configuration datasheet.
(5) An export meter is required for export limitation and most of home energy management functions.

Adc

SolarEdge Residential Three Phase Solar Inverter
For Australia and New ZealandSE5K-AUB / SE7K-AUB / SE8.25K-AUB / SE10K-AUB
SE5K-AUB
Applicable to inverters with part number

SE7K-AUB

SE8.25K-AUB

SE10K-AUBSEXXK- AUBTEBEU4INSTALLATION SPECIFICATIONSAC Output Conduit Size / Wire Cross Section

20mm minimum / 3 – 13mm2

DC Input Conduit Size / Wire Cross Section

20mm conduit size minimum

DC Input
Dimensions with Safety Switch (H x W x D)
WeightOperating Temperature Range
Cooling
Noise
Protection Rating
Mounting
Manufacturing Countries(6) For power derating information, see the Temperature Derating technical note.

Single DC terminal block
775 x 315 x 260

mm30kg-40 to +60(6)°C

Fan (user replaceable)< 50
IP65 – outdoor and indoor
Bracket provided
China / Vietnam / HungarydBA

SolarEdge is a global leader in smart energy technology.
By leveraging world-class engineering capabilities and witha relentless focus on innovation, SolarEdge creates smart
energy solutions that power our lives and drive future
progress.
SolarEdge developed an intelligent inverter solution thatchanged the way power is harvested and managed inphotovoltaic (PV) systems. The SolarEdge DC optimized
inverter maximizes power generation while lowering thecost of energy produced by the PV system.
Continuing to advance smart energy, SolarEdge addresses
a broad range of energy market segments through its PV,storage, EV charging, UPS, and grid services solutions.

SolarEdge@SolarEdgePV@SolarEdgePV
SolarEdgePV
SolarEdgewww.solaredge.com/corporate/contact

solaredge.com© SolarEdge Technologies, Ltd. All rights reserved.
SOLAREDGE, the SolarEdge logo, OPTIMIZED BYSOLAREDGE are trademarks or registered trademarksof SolarEdge Technologies, Inc. All other trademarks
mentioned herein are trademarks of their respective
owners. Date: 22 July, 2024 DS-000109-AUS
Subject to change without notice.
Cautionary Note Regarding Market Data andIndustry Forecasts: This brochure may containmarket data and industry forecasts fromcertain third-party sources. This information
is based on industry surveys and thepreparer’s expertise in the industry andthere can be no assurance that any suchmarket data is accurate or that any suchindustry forecasts will be achieved.
Although we have not independently
verified the accuracy of such market
data and industry forecasts, webelieve that the market data isreliable and that the industry
forecasts are reasonable.

solaredge.com