For Australia and New Zealand
SE25K / SE30K / SE33.3K
12 – 20YEARWARRANTY

INVERTERS

Three Phase Inverter

Specifically designed to work with power optimizers
Fixed voltage inverter for superior efficiency(98.3%) and longer strings
Quick and easy inverter commissioning directlyfrom a smartphone using the SolarEdge
SetAppSmall, lightest in its class, and easy to install
Optional Type 2 DC and AC surge protection,
to better withstand lightning events

solaredge.com

Built-in module-level monitoring with Ethernet
or wireless communication for full systemvisibility
IP65 outdoor and indoor installation
Smart Energy Management control
Future-ready for the SolarEdge energy storagesolution
Integrated DC Safety Unit - eliminates theneed for external DC isolators

Three Phase Inverter
For Australia and New Zealand
SE25K / SE30K / SE33.3K
Applicable to inverters with part number

SEXXK-AUX0IXXX
SE25K

SE30K

SE33.3K

UNITS

25000
25000

30000
30000
380 / 220; 400 / 230
176 - 253; 184 - 264
3W + PE, 4W + PE
WYE: TN-C, TN-S, TN-C-S, IT; Delta: IT
50 ± 5%43.5
43.5
100 / 3033300
33300W
VAVacVacOUTPUT
Rated AC Power OutputRated Maximum Apparent AC Output PowerAC Output Voltage - Line to Line / Line to Neutral (Nominal)
AC Output Voltage - Line to Neutral Range
AC Output Line Connections
Grids Supported - Three Phase
AC Frequency
Rated Continuous Output Current (per Phase)
Maximum Continuous Overcurrent Protection
Residual Current Detector / Residual Current Step Detector

3838

Inrush current AC (Peak / Duration)

48.25
48.25

3.6 / 20

Maximum Residual Current Injection
Maximum Output Fault Current
Utility Monitoring, Islanding Protection, Configurable Power Factor,
Country Configurable Thresholds
Total Harmonic Distortion
Protective Class
Overvoltage Category
Active Anti-Islanding Method
Power Factor Range(1)541006671HzAacAacmAAacrms / msmA
AacYes<3Class lIll
Slip Mode Frequency Shift+/-0.8 to 1%

INPUT
Maximum DC Power (Module STC)
Transformer-less, Ungrounded
Operating Voltage Range DC+ to DCMinimum Input Voltage DC to Gnd
Maximum Input Voltage DC to Gnd
Maximum Input Voltage DC+ to DCMaximum Operating Input Current
Short Circuit Current From The PV Array
Maximum Back-Feed Current
Overvoltage Category
Reverse-Polarity Protection
Ground-Fault Isolation Detection
Protective Class
Overvoltage Category
Maximum Inverter Efficiency
European Weighted Efficiency
Nighttime Power Consumption

43750

3752500
Yes
680 – 1000
340415
1000
43.5
48.25
0Il
Yes
167kΩ Sensitivity(2)Class lll
98.3
98<458275

48.25

W
Vdc
Vdc
Vdc
Vdc
Adc
Adc
Adc%%
W

ADDITIONAL FEATURES
Supported Communication Interfaces
Smart Energy Management
Inverter Commissioning
Arc Fault Protection
RS485 Surge Protection
DC / AC Surge Protection
Maximum Altitude
Inverter Topology

2 x RS485, Ethernet, Wi-Fi(3)Export Limitation
With the SetApp mobile application using built-in Wi-Fi access point for local connection
Integrated, User Configurable (According to UL1699B)
Supplied with the inverter
Type II, field replaceable, Optional
2000
Non-Isolated Photovoltaic Inverter

DC SAFETY UNIT
DC Disconnect

Provided

STANDARD COMPLIANCE
SafetyGrid Connection Standards(4)Emissions
RoHS

IEC62109, AS/NZS3100
AS/NZS4777:2020
IEC61000-6-2, IEC61000-6-3 Class A, IEC61000-3-11, IEC61000-3-12
Yes(1) If an external RCD is required, its trip value must be ≥ 100mA.
(2) Where permitted by local regulations.
(3) Wi-Fi connectivity requires connection of an additional Wi-Fi component, ordered separately. For more details ask your SolarEdge salesperson or refer to the Communication product page.
(4) For all standards refer to the Knowledge Center.

mThree Phase Inverter
For Australia and New Zealand
SE25K / SE30K / SE33.3K
Applicable to inverters with part number

SEXXK-AUX0IXXX
SE25K

SE30K

SE33.3K

UNITS

INSTALLATION SPECIFICATIONSAC Output Conduit Size / Wire Cross Section
DC Input Conduit Size / Wire Cross Section
Dimensions with Safety Unit (H x W x D)
Weight with Safety UnitOperating Temperature Range
Cooling
Noise
Protection Rating
Mounting

20 mm minimum / 4-16 mm2
20 mm minimum / 6-35 mm2808 x 317 x 300
35-40 to+60(5)Fan (user replaceable)< 62
IP65 - Outdoor and Indoor
Bracket Provided

ADDITIONAL INFORMATION
Manufacturing Countries(5) For power de-rating information, refer to the Temperature De-rating Technical Note.

China, Vietnam, Hungarymmkg
˚CdBA

SolarEdge is a global leader in smart energy technology.
By leveraging world-class engineering capabilities and witha relentless focus on innovation, SolarEdge creates smart
energy solutions that power our lives and drive future
progress.
SolarEdge developed an intelligent inverter solution thatchanged the way power is harvested and managed inphotovoltaic (PV) systems. The SolarEdge DC optimized
inverter maximizes power generation while lowering thecost of energy produced by the PV system.
Continuing to advance smart energy, SolarEdge addresses
a broad range of energy market segments through its PV,
storage, EV charging, UPS, and grid services solutions.

SolarEdge@SolarEdgePV@SolarEdgePV
SolarEdgePVSolarEdge
www.solaredge.com/corporate/contact

solaredge.com© SolarEdge Technologies, Ltd. All rights reserved.
SOLAREDGE, the SolarEdge logo, OPTIMIZED BYSOLAREDGE are trademarks or registered trademarksof SolarEdge Technologies, Inc. All other trademarks
mentioned herein are trademarks of their respectiveowners. Date: March 28, 2023 DS-000107-AUS-NZ
Subject to change without notice.
Cautionary Note Regarding Market Data andIndustry Forecasts: This brochure may containmarket data and industry forecasts fromcertain third-party sources. This information
is based on industry surveys and thepreparer’s expertise in the industry andthere can be no assurance that any suchmarket data is accurate or that any suchindustry forecasts will be achieved.
Although we have not independently
verified the accuracy of such market
data and industry forecasts, webelieve that the market data isreliable and that the industry
forecasts are reasonable.

solaredge.com