For Australia and New Zealand
SE50K / SE66.6K / SE82.8K / SE100K
12-20
YEAR
WARRANTY

INVERTERS

Three Phase Inverterwith Synergy Technology

Powered by unique pre-commissioning process for rapid system installation
Pre-commissioning feature for automatedvalidation of system components and wiring
during the site installation process and prior
to grid connection

Built-in arc fault protection
Built-in PID mitigation for maximised system
performance

Easy 2-person installation with lightweight,
modular design (each inverter consists of 2 or
3 Synergy Units and one Synergy Manager)

Monitored* and field-replaceable surge protection
devices, to better withstand surges caused bylightning or other events: integrated RS485 andoptional Type 2 DC and AC SPDs

Independent operation of each inverter unit
enables higher uptime and easy serviceability

Built-in DC safety switch eliminates the need forexternal DC isolators

Built-in thermal sensors detect faulty wiring
ensuring enhanced protection and safety

Built-in module-level monitoring with Ethernet or
cellular communication for full system visibility* Applicable only for DC and AC SPDs

solaredge.com

Three Phase Inverter with Synergy Technology
For Australia and New Zealand
SE50K / SE66.6K / SE82.8K / SE100K
Applicable to Inverter with Part Number

SExxK-AUxxIxxxx
SE50K

SE66.6K

SE82.8K

SE100K

Rated AC Active Output Power

50000

66600

82800

100000W

Maximum AC Apparent Output Power

50000

66600

82800

100000VA

OUTPUT

AC Output Voltage — Line to Line / Line to Neutral (Nominal)

380 / 220 ; 400 / 230

Vac

AC Output Voltage - Line to Neutral Range

176 - 253 ; 184 - 264

Vac

AC Output Line Connections

3W + PE, 4W + PE

Supported Grids

WYE: TN-C, TN-S, TN-C-S, TT, IT; Delta: IT

AC Frequency

50 ± 5%

Maximum Continuous Output Current (per Phase)

72.5

96.5

Maximum Continuous Overcurrent Protection

72.5

96.5

Hz
120

145

Aac

120

145

Aac

100 / 30

Residual Current Detector / Residual Current Step DetectormA

7.2 / 20

Inrush current AC (Peak / Duration)
Maximum Residual Current Injection
Maximum Output Fault Current

10.8 / 20

200

(1)

109

Aac
rms / ms
mA

300
142

176

Utility Monitoring, Islanding Protection, Configurable Power Factor,
Country Configurable Thresholds

213

Aac

Yes

Total Harmonic Distortion≤3

Protective ClassClass lOvervoltage Category%

Ill

Active Anti-Islanding Method

Slip Mode Frequency Shift

Power Factor Range+/-0.8 to 1

INPUT
Maximum DC Power (Module STC) Inverter / Synergy Unit

87500 / 43750

116550 / 58275

Transformer-less, Ungrounded

144900 / 48300

175000 / 58300

W

Yes

Operating Voltage Range DC+ to DC-

680 - 830

Vdc

Minimum Input Voltage DC to Gnd

340

Vdc

Maximum Input Voltage DC to Gnd

415

Vdc

Maximum Input Voltage DC+ to DC-

830

Maximum Input Current

2 x 36.25

2 x 48.25

Short Circuit Current From The PV Array per Synergy Unit

3 x 48.25

Adc

48.25

Maximum Back-Feed Current0

Overvoltage Category

Il

Reverse-Polarity Protection

Adc

Yes

Ground-Fault Isolation Detection

167kΩ sensitivity per Synergy Unit(2)Protective ClassClass lOvervoltage CategoryllMaximum Inverter Efficiency

98.3

European Weighted Efficiency

98

Nighttime Power Consumption

Vdc
3 x 40

<8

%
%
< 12

W

ADDITIONAL FEATURES
Supported Communication Interfaces(3)Smart Energy Management
Inverter Commissioning
Arc Fault Protection
PID Rectifier
RS485 Surge Protection (ports 1 + 2)

2x RS485, Ethernet, Wi-Fi (optional), Cellular (optional)
Export Limitation
With the SetApp mobile application using built-in Wi-Fi access point for local connection
Built-in, user configurable (according to UL1699B)
Nighttime, built-in
Type II, field replaceable, integrated

DC Surge Protection

Type II, field replaceable, optional

AC Surge Protection

Type II, field replaceable, optional

DC Disconnect Switch

ProvidedMaximum Altitude

2000

Inverter Topology

Non-Isolated Photovoltaic Inverter

Pre-Commissioning(4)Built-in

STANDARD COMPLIANCE
SafetyGrid Connection Standards(5)Emissions
RoHS

IEC-62109-1, IEC-62109-2, AS3100
AS/NZS4777:2020
IEC61000-6-2, IEC61000-6-3 Class A, IEC61000-3-11, IEC61000-3-12
Yes(1) If an external RCD is required, its trip value must be ≥ 200mA for SE50K/SE66.6K; ≥ 300mA for SE82.8K/SE100K(2) Where permitted by local regulations(3) For specifications of the optional communication options, visit https://www.solaredge.com/products/communication or the
Resource Library webpage: https://www.solaredge.com/resource-library, to download the relevant product datasheet(4) Not available for P/Ns SExxK-xxxxxBPxx(5) For all standards and certificates download, refer to the Certifications category on the Resource library webpage: https://www.solaredge.com/resource-librarymThree Phase Inverter with Synergy Technology
For Australia and New Zealand
SE50K / SE66.6K / SE82.8K / SE100K
Applicable to Inverter with Part Number

SExxK-AUxxIxxxx
SE50K

SE66.6K

SE82.8K

SE100K

INSTALLATION SPECIFICATIONS
Number of Synergy Units per Inverter
AC Max Conduit Size
AC Wire Cross Section Line/PE (Aluminum or Copper)
DC Max Conduit Size
DC Max Wire Cross Section (Copper) / Number of PV Arrays

2

3
63

95 / 50

120 / 70

2 x 40 mm

3 x 40 mm

50 mm / 2 x PV arrays

50 mm2 / 3 x PV arrays2

Dimensions (H x W x D)
WeightOperating Temperature Range
Cooling
Noise
Protection Rating
Mounting

Synergy Unit: 558 x 328 x 273
Synergy Manager: 360 x 560 x 295
Synergy Unit: 32
Synergy Manager: 18-40 to +60(6)

mm2
mm
kg
˚C

Fan (user replaceable)< 67
IP65 — outdoor and indoor
Brackets provided

ADDITIONAL INFORMATION
Manufacturing Countries

mmmm2

China, Vietnam, Hungary(6) For power de-rating information refer to: https://www.solaredge.com/sites/default/files/se-temperature-derating-note.pdf© SolarEdge Technologies, Ltd. All rights reserved. SOLAREDGE, the SolarEdge logo, OPTIMIZED BY SOLAREDGE are trademarks or registered trademarks of SolarEdge Technologies, Inc.
All other trademarks mentioned herein are trademarks of their respective owners. Date: 09/2022 DS-000039-1.2-AUS-NZ. Subject to change without notice.

dBA