INSTRUCTION MANUALPNP TRANSISTOR OUTPUT EXTENSION MODULE, 8 points(LONWORKS)

BEFORE USE ....
Thank you for choosing us. Before use, please check contents of the package you received as outlined below.
If you have any problems or questions with the product,
please contact our sales office or representatives.

R7L-EC8B

MODEL

COMPONENT IDENTIFICATION
Discrete Output Status Indicator LED■ PACKAGE INCLUDES:
Transistor output extension module...................................(1)0 1 2 3 4 5 6 7■ MODEL NO.
Confirm Model No. marking on the product to be exactlywhat you ordered.

61728394■ INSTRUCTION MANUALThis manual describes necessary points of caution whenyou use this product, including installation, connection andbasic maintenance procedures.

POINTS OF CAUTION■ POWER INPUT RATING & OPERATIONAL RANGE• Locate the power input rating marked on the product andconfirm its operational range as indicated below:		 24V AC rating: 24V ±10%, 50/60 Hz, approx. 15mA		 24V DC rating: 24V ±10%, approx. 10mA
■ GENERAL PRECAUTIONS• Before you remove the unit or mount it, turn off the powersupply and output signal for safety.
■ ENVIRONMENT• Indoor use.
• When heavy dust or metal particles are present in theair, install the unit inside proper housing with sufficientventilation.
• Do not install the unit where it is subjected to continuous
vibration. Do not subject the unit to physical impact.
• Environmental temperature must be within -10 to +55°C(14 to 131°F) with relative humidity within 30 to 90% RH
in order to ensure adequate life span and operation.

105Output Terminals■ DISCRETE OUTPUT STATUS INDICATOR LED
Used to show discrete output signal status.			 ON		 : LED ON			 OFF : LED OFF■ OUTPUT TERMINAL ASSIGNMENT678910+24V Y1Y3Y5Y7123450V
Y0Y2Y4Y6NO.
12345ID0VY0
Y2Y4Y6FUNCTION0V
Output 0
Output 2
Output 4
Output 6NO.
ID
6 +24V
7Y1
8Y39Y510Y7FUNCTION
24V DC (common)
Output 1
Output 3
Output 5
Output 7CONNECTING THE EXTENSION MODULE
1) Remove the extension connector cover located at the sideof the basic module.
2) Connect the extension module.

■ WIRING• Do not install cables close to noise sources (relay drivecable, high frequency line, etc.).
• Do not bind these cables together with those in which
noises are present. Do not install them in the same duct.
■ FUNCTIONAL BLOCK SETTING• Functional blocks regarding the extension module are set
by the basic module. Refer to the instruction manual forthe basic module for detailed information.
■ AND ....
• The unit is designed to function as soon as power is supplied, however, a warm up for 10 minutes is required forsatisfying complete performance described in the datasheet.

3) Mount the combined module on a DIN rail.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-7804-P Rev.2

P. 1 / 2

R7L-EC8BTERMINAL CONNECTIONSConnect the unit as in the diagram below.
■ EXTERNAL DIMENSIONS unit: mm (inch)
17 (.66)

65 (2.56)

54 (2.13)

18.5 (.73)

11.5(.45)

50 (1.97)

DIN RAIL
35mm wide

67283941053 (.12)

15.5 (.22)

30 (1.18)[5 (.20)]

6 (.24)
10–M3 SCREWTERMINALS
for OUTPUT■ CONNECTION DIAGRAMWIRING INSTRUCTIONSEXTENSION CONNECTOR

6 +24V
2 Y03 Y24 Y45 Y67 Y1■ SCREW TERMINALTorque: 0.5 N·m■ SOLDERLESS TERMINAL
Refer to the drawing below for recommended ring tongue
terminal size. Spade tongue type is also applicable.
Applicable wire size: 0.25 to 1.65 mm2 (AWG 22 to 16)
Recommended manufacturer: Japan Solderless Terminal
MFG. Co., Ltd, Nichifu Co., Ltd

8 Y3

10 Y71 0V

6 (.24) max

9 Y53.3 (.13) maxmm (inch)■ Output Connection Example+24V 6+ –0V 1
Y0 2

Y7 10

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-7804-P Rev.2

P. 2 / 2