2013

一次エネルギー消費量算定プログラム(建築物用)XML フォーマット仕様書
2013.12.17

内容
基本構造 ................................................................................................................................. 4
基本的事項 .............................................................................................................................. 5
文字コード .......................................................................................................................... 5
名前空間 .............................................................................................................................. 5
基本設定 ................................................................................................................................. 6
Building 要素...................................................................................................................... 6
共通室の設定 .......................................................................................................................... 8
Rooms 要素 ......................................................................................................................... 8
Room 要素........................................................................................................................... 9
MinorRoom 要素 .............................................................................................................. 18
空調の設定 ............................................................................................................................ 19
AirConditioningSystems 要素 ......................................................................................... 19
AirConditioningZone 要素 ............................................................................................... 20
RoomRef 要素 ................................................................................................................... 21
AirHandlingUnitSetRef 要素 .......................................................................................... 22
EnvelopeSet 要素 ............................................................................................................. 23
Envelope 要素................................................................................................................... 24
WallConfigure 要素 .......................................................................................................... 26
Material 要素 ................................................................................................................... 27
WindowConfigure 要素 .................................................................................................... 31
HeatSourceSet 要素 ......................................................................................................... 40
HeatSource 要素 .............................................................................................................. 42
SecondaryPumpSet 要素 ................................................................................................. 45
SecondaryPump 要素....................................................................................................... 46
AirHandlingUnitSet 要素................................................................................................ 47
AirHandlingUnit 要素 ..................................................................................................... 48
HeatSourceSetRef 要素 ................................................................................................... 51
SecondaryPumpSetRef 要素 ........................................................................................... 52
空調以外の機械換気の設定 .................................................................................................. 53
VentilationSystems 要素 ................................................................................................. 53
VentilationRoom 要素 ...................................................................................................... 54
VentilationUnitRef 要素 .................................................................................................. 55
VentilationFanUnit 要素 ................................................................................................. 56
VentilationACUnit 要素 .................................................................................................. 57
1

照明の設定 ............................................................................................................................ 58
LightingSystems 要素 ..................................................................................................... 58
LightingRoom 要素 .......................................................................................................... 59
LightingUnit 要素 ............................................................................................................ 61
給湯の設定 ............................................................................................................................ 63
HotwaterSystems 要素 .................................................................................................... 63
HotwaterRoom 要素......................................................................................................... 64
BoilerRef 要素 .................................................................................................................. 65
Boiler 要素 ........................................................................................................................ 66
昇降機の設定 ........................................................................................................................ 68
Elevators 要素 .................................................................................................................. 68
効率化設備の設定 ................................................................................................................. 70
PhotovoltaicGenerationSystems・PhotovoltaicGeneration 要素 ................................. 70
CogenerationSystems 要素 ............................................................................................. 72
CogenerationUnit 要素 .................................................................................................... 73

2

はじめに
「一次エネルギー消費量算定プログラム(建築物用)」(http://building.app.lowenergy.jp/)に
おいて Ver1.x 以降で採用されている電子データを作成するための仕様を示します。このフォーマットは World Wide Web Consortium(W3C)による規格である XML 1.0 (JIS X
4159:2002)に準拠しています。

対象範囲
本仕様書では、電子データの作成に必要な全ての定義について扱います。ただし、電子データ作成の基盤となる XML 1.0 および計算手順に関わる内容を扱いません。

3

基本構造
XML 文書のルート要素として Building 要素を定義します。Building 要素は建築物全体を表し、1 つの XML 文書には 1 つしか存在しません。
Building 要素には、共通室を表す Rooms
要素、空調を表す AirConditioningSystems 要素、換気を表す VentilationSystems 要素、照明を表す LightingSystems 要素、給湯を表す HotwaterSystems 要素、昇降機を表す
Elevators 要素、太陽光発電システムを表す PhotovoltaicGenerationSystems 要素、コジェ
ネレーションシステムを表す CogenerationSystems 要素がそれぞれ最大 1 つずつ存在します。

4

基本的事項
文字コード
XML 文書の文字コードは UTF-8 とします。従って、XML 文書の先頭に次の XML 宣言があることを期待します。
XML 宣言<?xml version="1.0" encoding="UTF-8">

名前空間
他の XML 仕様との混合利用を想定しないため、名前空間は未定義とします。

5

基本設定
Building 要素■概要
住戸全体を表すルート要素です。8 の子要素から構成されます。
■属性
属性名

説明

UniqueId

モデルの識別子です。任意です。

FileVer

ファイル形式バージョンです。”1”を指定します。

Name

建物の名称を指定します。任意です。

Description

建物の説明を指定します。任意です。

Region

省エネルギー基準地域区分を次の中から指定します。必須です。

TotalArea

値

意味

1

1 地域

2

2 地域

3

3 地域

4

4 地域

5

5 地域

6

6 地域

7

7 地域

8

8 地域

床面積の合計[㎡]を小数(小数点以下 2 桁まで)で指定します。必須です。

PersonInCharge

入力責任者を指定します。任意です。

Address1

建物所在地のうち都道府県を指定します。任意です。

Address2

建物所在地のうち市区町村を指定します。任意です。

Address3

建物所在地のうち市区町村以降を指定します。任意です。

Structure

構造を指定します。任意です。

GroundFloor

地上階数を整数で指定します。任意です。

BasementFloor

地下階数を整数で指定します。任意です。

SiteArea

敷地面積[㎡]を小数(小数点以下 x 桁まで)で指定します。任意です。

BuildingArea

建物面積[㎡]を小数(小数点以下 x 桁まで)で指定します。任意です。

DHCReducedValue

他人から供給された熱の一次エネルギー換算値 (一次エネルギー6

= 二次エネルギー * 換算値)を指定します。単位は kJ/kJ です。任意です。
AnnualSolarLevel

年間日射地域区分を次の中から指定します。太陽光発電設備又は太陽熱利用給湯設備を採用する場合は必須です。
値

意味

A1

A1 区分(年間の日射量が特に少ない地域)

A2

A2 区分(年間の日射量が少ない地域)

A3

A3 区分(年間の日射量が中程度の地域)

A4

A4 区分(年間の日射量が多い地域)

A5

A5 区分(年間の日射量が特に多い地域)

CreateDate

作成日時です。ISO 8601 に従います。任意です。

UpdateDate

作成日時です。ISO 8601 に従います。任意です。

■子要素
要素型

説明

Rooms

共通室を定義します。1 つのみ定義できます。

AirConditioningSystems

空調を定義します。1 つのみ定義できます。

VentilationSystems

空調以外の機械換気を定義します。１つのみ定義できます。

LightingSystems

照明を定義します。１つのみ定義できます。

HotwaterSystems

給湯を定義します。１つのみ定義できます。

Elevators

昇降機を定義します。1 つのみ定義できます。

PhotovoltaicGenerationSystems

太陽光発電を定義します。１つのみ定義できます。

CogenerationSystems

コージェネレーションを定義できます。１つのみ定義できます。

7

共通室の設定
Rooms 要素■概要
Rooms 要素は共通室全体を表す要素です。個別の共通室を表す Room 要素および非主要室を表す MinorRoom 要素を子要素として持ちます。Rooms 要素が定義されると、プログラ
ムは空調室、換気室、照明室、給湯室の定義との一貫性を確認します。
■属性
なし
■子要素
要素型

説明

Room

共通室を定義します。任意の数定義できます。

MinorRoom

非主要室を定義します。任意の数定義できます。

■例
例1)

事務室と倉庫の定義<Rooms><Room Floor=”1F” Name=”1F 事 務 室 ” BuildingType=”Office” RoomType=”Office”
Area=”80” AirConditioning=”True” Ventilation=”True” Lighting=”True” Hotwater=”True” /><Room Floor=”2F” Name=”2F 事 務 室 ” BuildingType=”Office” RoomType=”Office”
Area=”70” AirConditioning=”True” Ventilation=”True” Lighting=”True” Hotwater=”True” /><MinorRoom

Floor=”1F”

Name=”1F

RoomType=”StorageRoom” Area=”10” /></Rooms>

8

倉

庫

”

BuildingType=”Office”

Room 要素■概要
Rooms 要素は共通室全体を表す要素です。個別の共通室を表す Room 要素を子要素として持ちます。Rooms 要素は次の属性を持ちます。
■属性
属性名

説明

Floor

階を指定します。必須です。

Name

室名を指定します。必須です。

BuildingType

建物用途を次の中から指定します。必須です。
値

意味

Office

事務所等

Hotel

ホテル等

Hospital

病院等

Store

物販店舗等

School学校等

Restaurant

飲食店等

MeetingPlace

集会場等

Factory

工場等

ApartmentHouse 共同住宅
RoomType

室用途を指定します。指定できる値は建物用途によって異なり、表 1
から表 9 までから選択します。必須です。

Area

室面積[㎡]を小数(小数点以下 2 桁まで)で指定します。必須です。

FloorHeight

階高[㎡]を小数(小数点以下 1 桁まで)で指定します。任意です。

RoomHeight

天井高[㎡]を小数(小数点以下 1 桁まで)で指定します。任意です。

AirConditioning

空調計算の対象であるかを次から指定します。

Ventilation

Lighting

値

意味

True

空調計算対象室である

False

空調計算対象室でない

換気計算の対象であるかを次から指定します。
値

意味

True

換気計算対象室である

False

換気計算対象室でない

照明計算の対象であるかを次から指定します。
9

Hotwater

Info

値

意味

True

照明計算対象室である

False

照明計算対象室でない

給湯計算の対象であるかを次から指定します。
値

意味

True

給湯計算対象室である

False

給湯計算対象室でない

備考を指定します。任意です。

表 1 建物用途が事務所の場合の室用途

値

意味

OfficeRoom

事務室

ComputerSpace

電算事務室

MeetingRoom

会議室

TeaRoom

喫茶室

Canteen

社員食堂

CentralMonitoringRoom

中央監視室

LockerRoom

更衣室

Corridor

廊下

Lobby

ロビー

Toilet

便所

SmokingRoom

喫煙室

Kitchen

厨房

IndoorParikng

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室

Kitchenette

湯沸室等

StorageRoom

食品庫等

CopyRoom

コピー室等

GarbageStorage

ゴミ置場等

表 2 建物用途がホテル等の場合の室用途

値意味

GuestRoom

客室

Bathroom

洗面室
10FrontDeskInAccommodation

客室部フロント

OfficeRoomInAccommodation

客室部事務室CorridorInAccommodation

客室部廊下

LobbyInAccommodation

客室部ロビー

ToiletInAccommodation

客室部便所

SmokingRoomInAccommodation

客室部喫煙室BanquetHall

宴会場

ConferenceRoom

大会議室

WeddingHall

結婚式場

Restaurant

レストラン

Lounge

ラウンジ

Bar

バー

Shop

店舗

Canteen

社員食堂

LockerRoom

更衣室

FrontDesk

フロント

OfficeRoom

事務室

Corridor

廊下

Lobby

ロビー

Toilet

便所

SmokingRoom

喫煙室

Kitchen

厨房

IndoorParikng

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室

Kitchenette

湯沸室等

StorageRoom

食品庫等

CopyRoom

コピー室等

GarbageStorage

ゴミ置場等

表 3 建物用途が病院等の場合の室用途

値

意味

Ward

病室

Bathroom

洗面室

StaffStation

スタッフステーション
11

CorridorInWard

病室部廊下

LobbyInWard

病室部ロビー

ToiletInWard

病室部便所

SmokingRoomInWard

病室部喫煙室ConsultingRoom

診察室

WaitingLounge

待合室

OperatingRoom

手術室

ExaminingRoom

検査室

IntensiveCareUnit

集中治療室

AnimalRoom

動物室

Restaurant

レストラン

OfficeRoom

事務室

LockerRoom

更衣室

Corridor

廊下

Lobby

ロビー

Toilet

便所

SmokingRoom

喫煙室

Kitchen

厨房

IndoorParikng

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室

Kitchenette

湯沸室等

StorageRoom

食品庫等

CopyRoom

コピー室等

GarbageStorage

ゴミ置場等

表 4 建物用途が物販店舗等の場合の室用途

値意味

LargeScaleRetailStore

大型店売場

SpecializedStore

専門店売場

Supermarket

スーパーマーケット売場

Backyard

バックヤードOfficeRoom

事務室

LockerRoom

更衣室

Lobby

ロビー
12

Toilet便所

SmokingRoom

喫煙室

Kitchen

厨房

IndoorParikng

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室

Kitchenette

湯沸室等

StorageRoom

食品庫等

CopyRoom

コピー室等

GarbageStorage

ゴミ置場等

表 5 建物用途が学校などの場合の室用途

値意味

ClassroomInPrimarySchool

小中学校教室ClassroomInHighSchool

高校教室

StaffRoom

職員室

SchoolCanteen

食堂

ClassroomInCollege

大学教室

CollegeCanteen

大学食堂

OfficeRoom

事務室

ResearchRoom

研究室

ComputerRoom

パソコン室

Laboratory

実験室

PracticalRoom

実習室

Hall

講堂

NightDutyRoom

宿直室

LockerRoom

更衣室

Corridor

廊下

Lobby

ロビー

Toilet

便所

SmokingRoom

喫煙室

Kitchen

厨房

IndoorParikng

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室13Kitchenette

湯沸室等

StorageRoom

食品庫等

CopyRoom

コピー室等

GarbageStorage

ゴミ置場等

表 6 建物用途が飲食店等の場合の室用途

値意味

Restaurant

レストラン客室

LightRestaurant

軽食店客室

CoffeeShop

喫茶店客室

Bar

バー

FrontDesk

フロント

OfficeRoom

事務室

LockerRoom

更衣室

Corridor

廊下

Lobby

ロビー

Toilet

便所

SmokingRoom

喫煙室

Kitchen

厨房

IndoorParikng

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室

Kitchenette

湯沸室等

StorageRoom

食品庫等

CopyRoom

コピー室等

GarbageStorage

ゴミ置場等

表 7 建物用途が集会場等の場合の室用途

値

意味

Athletic

アスレチック場

LobbyInAthletic

アスレチック場ロビー

ToiletInAthletic

アスレチック場便所

SmokingRoomInAthletic

アスレチック場喫煙室

IceHockeyRinkForOfficialCompetition

アイスホッケーフィギュア公式

ArenaForOfficialCompetition

体育館アリーナ水泳公式
14

IceHockeyRinkForGeneralGame

アイスホッケーフィギュア一般

ArenaForGeneralGame

体育館アリーナ水泳一般

IceHockeyRinkForRecreation

アイスホッケーフィギュア

ArenaForRecreation

体育館アリーナ水泳

CheeringSectionInGymnasium

体育館応援席LobbyInGymnasium

体育館ロビー

ToiletInGymnasium

体育館便所

SmokingRoomInGymnasium

体育館喫煙室BathroomInBathingFacility

浴場施設浴室LockerRoomInBathingFacility

浴場施設脱衣室RestingRoomInBathingFacility

浴場施設休憩室

LobbyInBathingFacility

浴場施設ロビー

ToiletInBathingFacility

浴場施設便所

SmokingRoomInBathingFacility

浴場施設喫煙室

AuditoriumInMovieTheater

映画館観客席LobbyInMovieTheater

映画館ロビー

ToiletInMovieTheater

映画館便所

SmokingRoomInMovieTheater

映画館喫煙室Library

図書館

LobbyInLibrary

図書館ロビー

ToiletInLibrary

図書館便所

SmokingRoomInLibrary

図書館喫煙室Museum

博物館

LobbyInMuseum

博物館ロビー

ToiletInMuseum

博物館便所

SmokingRoomInMuseum

博物館喫煙室DressingRoom

楽屋

BoardInTheater

劇場舞台

AudienceSeatInTheater

劇場観客席

LobbyInTheater

劇場ロビー

ToiletInTheater

劇場便所

SmokingRoomInTheater

劇場喫煙室

InternetCafe

インターネットカフェ

Karaoke

カラオケ

Bowlling

ボーリング
15

Pachinko

パチンコ

AuditoriumInReaceCourse

競馬競輪場観客席

TicketOfficeInReaceCourse

競馬競輪場券売場

ShopInReaceCourse

競馬競輪場売店

LobbyInReaceCourse

競馬競輪場ロビー

ToiletInReaceCourse

競馬競輪場便所

SmokingRoomInReaceCourse

競馬競輪場喫煙室

MainHallInTemple

社寺本殿

LobbyInTemple

社寺本殿ロビー

ToiletInTemple

社寺本殿便所

SmokingRoomInTemple

社寺本殿喫煙室

Kitchen

厨房

IndoorParikng

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室

Kitchenette

湯沸室等

StorageRoom

食品庫等

CopyRoom

コピー室等

GarbageStorage

ゴミ置場等

表 8 建物用途が工場等の場合の室用途

値

意味

WareHouse

倉庫

OutdoorParking

屋外駐車場又は駐輪場

表 9 建物用途が共同住宅の場合の室用途

値意味

IndoorCorridor

屋内廊下

Lobby

ロビー

ManagerRoom

管理人室

AssemblyRoom

集会室

OutdoorCorridor

屋外廊下

IndoorParking

屋内駐車場

MechanicalRoom

機械室

ElectricalRoom

電気室
16GarbageStorage

廃棄物保管場所等

■子要素
なし
■説明
AirConditioning 属 性 が True の 場 合 、 AirConditioningZone 要 素 の 子 要 素 で あ る
RoomRef 要素の Floor 属性、Name 属性、BuildingType 属性、RoomType 属性、Area 属
性、FloorHeight 属性、RoomHeight 属性の値がすべて一致する RoomRef 要素が定義されている必要があります。
Ventilation 属性が True の場合、VentilationRoom 要素の Floor 属性、Name 属性、BuildingType 属性、RoomType 属性、Area 属性の値がすべて一致する VentilationRoom
要素が定義されている必要があります。
Lighting 属性 が True の 場 合、 LightingRoom 要 素 の Floor 属 性、 Name 属 性、BuildingType 属性、RoomType 属性、Area 属性、FloorHeight 属性、RoomHeight 属性の値がすべて一致する LightingRoom 要素が定義されている必要があります。
Hotwater 属性が True の場合、HotwaterRoom 要素の Floor 属性、Name 属性、BuildingType 属性、RoomType 属性、Area 属性の値がすべて一致する HotwaterRoom 要素が定義されている必要があります。
Elevator 要素が定義される場合、RoomFloor、RoomName、BuildingType、RoomTypeの 4 属性がそれぞれ Room 要素の Floor、Name、BuildingType、RoomType に同時に一致する Room 要素が存在する必要があります。
■例
例1)

事務室

<Room Floor=”1F” Name=”1F 事務室” BuildingType=”Office” RoomType=”Office” Area=”80”
AirConditioning=”True” Ventilation=”True” Lighting=”True” Hotwater=”True” />17MinorRoom 要素■概要
非主要室を表す要素です。次に示す属性から構成されます。
■属性
属性名

説明

Floor

階を指定します。

Name

室名を指定します。

BuildingType

建物用途を指定します。指定できる値は Room 要素の BuildingType
属性と同じです。必須です。

RoomType

室用途を指定します。

Area

室面積を指定します。

■子要素
なし
■例
例1)

倉庫の定義

<MinorRoom Floor=”1F” Name=”1F 倉庫” BuildingType=”Office” RoomType=”StorageRoom”
Area=”10” />18

空調の設定AirConditioningSystems 要素■概要
空調全体を表す要素です。空調ゾーン、熱源群、二次ポンプ群、空調機群、外皮、壁構成、窓構成、非主要室から構成されます。
■属性
なし
■子要素
要素型

説明

AirConditioningZone

空調ゾーンを定義します。

HeatSourceSet

熱源群を定義します。

SecondayPumpSet

二次ポンプ群を定義します。

AirHandlingUnit

空調機を定義します。

EnvelopeSet

外皮を定義します。

WallConfigure

壁構成を定義します。

WindowConfigure

窓構成を定義します。

MinorRoom

非主要室を定義します。

19

AirConditioningZone 要素■概要
AirConditioningZone 要素は空調ゾーンを表す要素です。１つの空調ゾーンは 1 つ以上のの共通室に対応します。対応する共通室を RoomRef 要素を子要素として定義します。空調
ゾーンに接続される空調機を指定するには AirHandlingUnitSetRef 要素を子要素として定
義します。
■属性
属性名

説明

Floor

階を指定します。必須です。

Name

空調ゾーン名を指定します。必須です。

Info

備考を指定します。任意です。

■子要素
要素型

説明

RoomRef

空調ゾーンに対応する共通室の参照を定義します。

AirHandlingUnitSetRef

接続される空調機を定義します。

■例
例1)<AirConditioningZone Floor=”1F” Name=”Office1F”><RoomRef Floor=”1F” Name=”Office1F-1” BuildingType=”Office” RoomType=”Office”
Area=”150” FloorHeight=”4.0” RoomHeight=”2.5” /><RoomRef Floor=”1F” Name=”Office1F-2” BuildingType=”Office” RoomType=”Office”
Area=”150” FloorHeight=”4.0” RoomHeight=”2.5” /><AirHandlingUnitSetRef Name=”AHU1” Load=”RoomLoad” /><AirHandlingUnitSetRef Name=”AHU2” Load=”OutsideAirLoad” /></AirConditioningZone>

20

RoomRef 要素■概要
RoomRef 要素は共通室への参照を定義する要素です。
■属性
属性名

説明

Floor

階を指定します。必須です。

Name

室名を指定します。必須です。

BuildingType

建物用途を指定します。指定できる値は Room 要素の BuildingType 属
性と同じです。必須です。

RoomType

室用途を指定します。指定できる値は Room 要素の RoomType 属性と同じです。必須です。

Area

室面積を小数で指定します。単位は平方メートルです。必須です。

FloorHeight

階高を小数で指定します。単位はメートルです。必須です。

RoomHeight

天井高を小数で指定します。単位はメートルです。必須です。

■例
例1)<RoomRef

Floor=”1F”

Name=”Office1F”

BuildingType=”Office”

Area=”150” FloorHeight=”4.0” RoomHeight=”2.5” />21

RoomType=”Office”

AirHandlingUnitSetRef 要素■概要
AirHandlingUnitSetRef 要素は空調機群への参照を表す要素です。親要素である空調ゾー
ンに対して接続される空調機の名称と処理する負荷を指定します。
■属性
属性名

説明

Name

空調機群名称を指定します。必須です。指定する名称は、必ず別途
AirHandlingUnitSet 要素の Name 属性で定義される名称と一致する必要があります。

Load

処理する空調負荷を次の中から指定します。必須です。
値

意味

Room

室負荷

OutsideAir

外気負荷

■子要素
なし
■例
例1)
<AirHandlingUnitSetRef Name=”AHU1” Load=”Room” />22

EnvelopeSet 要素■概要
空調ゾーンの外皮群を表す要素。各外皮を表す Envelope 要素を子要素として持ちます。
■属性
属性名

内容

ACZoneFloor

空調ゾーン階を指定します。必須です。

ACZoneName

空調ゾーン名称を指定します。必須です。

■子要素
要素型

説明

Envelope

外皮を定義します。

■例
例1)<EnvelopeSet ACZoneFloor=”1F” ACZoneName=”Office-1F” ><Envelope Direction=”N” WallName=”OW1” Area=”68”
WindowName=”WNDW1” WindowArea=”20.4” Blind=”True” /><Envelope Direction=”E” WallName=”OW1” Area=”148”
WindowName=”WNDW1” WindowArea=”44.4” Blind=”True” /><Envelope Direction=”S” WallName=”OW1” Area=”46.4”
WindowName=”WNDW1” WindowArea=”13.9” Blind=”True” /></EnvelopeSet>

23

Envelope 要素■概要
外皮を表す要素。
■属性
属性名

内容

Direction

設置場所を次から選択します。必須です。

CoolingEaves

値

意味

N

北

NE

北東

E

東

SE

南東

S

南

SW

南西

W

西

NW

北西

Horizontal

水平

Shade

日陰

Underground

地中

日除け効果係数(冷房）を小数(小数点以下 2 桁まで)で指定します。必須です。

HeatingEaves

日除け効果係数(暖房）を小数(小数点以下 2 桁まで)で指定します。必須です。

WallName

外壁構成名称を指定します。必須です。

Area

外皮面積[m2]を指定します。必須です。

WindowName

窓仕様名称を指定します。窓が存在する場合は必須です。

WindowArea

窓面積[m2]を指定します。窓が存在する場合は必須です。

Blind

設置場所を次から選択します。任意です。
値

意味

True

ブラインド有False

ブラインド無

■子要素
なし

24

■例
例1)
<Envelope Direction=”N”
WallName=”OW1” Area=”68”
WindowName=”WNDW1” WindowArea=”20.4” Blind=”True” />25WallConfigure 要素■概要
外壁構成を表す要素。
■属性
属性名

内容

Name

一意な外壁名称を指定します。必須です。

Type

壁の種類を次から選択します。必須です。

Uvalue

値

意味

Air

外壁

Ground

接地壁

Internal

内壁（選択させない）

総熱貫流率[W/m2K]

■子要素
要素型

説明

Material

建材を定義します。

■例
例1)<WallConfigure Name=”OW1” Type=”Air”><Material Layer=”1” Number=”62” Name=”せっこうボード” Thickness=”8” /><Material Layer=”1” Number=”302” Name=”非密閉空気層” /><Material Layer=”1” Number=”181” Name=”押出法ポリスチレンフォーム保温板 1 種”
Thickness=”25” /><Material Layer=”1” Number=”41” Name=”コンクリート” Thickness=”150” /><Material Layer=”1” Number=”47” Name=”セメント・モルタル” Thickness=”25” /><Material Layer=”1” Number=”67” Name=”タイル” Thickness=”10” /></WallConfigure>26

Material 要素■概要
建材を表す要素。
■属性
属性名

内容

Layer

層番号を指定します。層番号は室内側から 1,2,3 の順に指定します。

Number

建材番号を表 10 から選択します。必須です。

Name

建材名称を入力します。任意です。計算には影響しません。

Thickness

厚み[mm]を小数(小数点以下 1 桁まで)で指定します。

Info

備考を指定します。任意です。

表 10 建材一覧
建材番号

建材名称

1

鋼

2

アルミニウム3

銅

4

ステンレス鋼

21

岩石

22

土壌

41

コンクリート42

軽量コンクリート(軽量 1 種)

43

軽量コンクリート(軽量 2 種)

44

気泡コンクリート(ALC)

45

コンクリートブロック(重量)46

コンクリートブロック(軽量)47

セメント・モルタル

48

押出成型セメント板

61

せっこうプラスター

62

せっこうボード

63

硬質せっこうボード

64

しっくい

65

土壁

27

66

ガラス

67

タイル

68

れんが

69

かわら

70

ロックウール化粧吸音板

71

火山性ガラス質複合板

72

ケイ酸カルシウム板 0.8mm

73

ケイ酸カルシウム板 1.0mm

81

天然木材

82

合板

83

タタミボード84

シージングボード85

A 級インシュレーションボード

86

パーティクルボード

87

木毛セメント板

88

木片セメント板

89

ハードファイバーボード(ハードボード)

90

ミディアムデンシティファイバーボード(MDF)

101

ビニル系床材

102

FRP

103

アスファルト類

104

畳床

105

建材畳床(Ⅲ型 50mm 厚)106

建材畳床(K,N 型 50mm 厚)

107

カーペット類

121

グラスウール断熱材 10K 相当

122

グラスウール断熱材 16K 相当

123

グラスウール断熱材 20K 相当

124

グラスウール断熱材 24K 相当

125

グラスウール断熱材 32K 相当

126

高性能グラスウール断熱材

16K 相当127

高性能グラスウール断熱材

24K 相当128

高性能グラスウール断熱材

32K 相当129

高性能グラスウール断熱材

40K 相当130

高性能グラスウール断熱材

48K 相当28

131

吹込み用グラスウール 13K 相当

132

吹込み用グラスウール 18K 相当

133

吹込み用グラスウール 30K 相当

134

吹込み用グラスウール 35K 相当

141

吹付けロックウール

142

ロックウール断熱材(マット)143

ロックウール断熱材(フェルト)144

ロックウール断熱材(ボード)145

吹込み用ロックウール 25K 相当

146

吹込み用ロックウール 65K 相当

161

吹込み用セルローズファイバー 25K

162

吹込み用セルローズファイバー 45K

163

吹込み用セルローズファイバー 55K

181

押出法ポリスチレンフォーム 保温板 1 種

182

押出法ポリスチレンフォーム 保温板 2 種183

押出法ポリスチレンフォーム 保温板 3 種

184

A 種ポリエチレンフォーム

保温板 1 種 2 号

185

A 種ポリエチレンフォーム

保温板 2 種186

ビーズ法ポリスチレンフォーム 保温板 特号

187

ビーズ法ポリスチレンフォーム 保温板 1 号

188

ビーズ法ポリスチレンフォーム 保温板 2 号

189

ビーズ法ポリスチレンフォーム 保温板 3 号

190

ビーズ法ポリスチレンフォーム 保温板 4 号

202

硬質ウレタンフォーム 保温板 2 種 2 号

203

吹付け硬質ウレタンフォーム A 種１

204

吹付け硬質ウレタンフォーム A 種 3

221

フェノールフォーム 保温板 1 種 1 号

222

フェノールフォーム 保温板 1 種 2 号

301

密閉中空層

302

非密閉中空層

■子要素
なし
■例
29

例1)

厚さ 12.5mm のせっこうボード<Material Layer=”1” Number=”62” Name=”せっこうボード” Thickness=”12.5” />30

WindowConfigure 要素■概要
窓仕様を表す要素。
■属性
属性名

内容

Name

一意な窓名称を指定します。必須です。

WindowTypeNumber

ガラス番号を表 11 から選択します。任意です。

Uvalue

熱貫流率[W/m2K]を指定します。ガラス番号を指定しない場
合には必須です。ガラス番号を指定する場合は指定しないでください。

WindowTypeClass

ガラス種類を次から選択します。任意です。(計算結果に影響しません。)

Mvalue値

意味

Single

単板ガラス

Double6

複層ガラス中空層 6mm

Double12複層ガラス中空層 12mm

日射侵入率[-]を指定します。ガラス種類を指定しない場合は必須です。ガラス種類を指定する場合は指定しないでくださ
い。

Info

備考を指定します。任意です。

表 11 ガラス番号一覧
ガラス

種類

厚み
[mm]

番号
1

単層

透明

3

2

単層

透明

5

3

単層

透明

6

4

単層

透明

8

5

単層

透明

10

6

単層

透明

12

7

単層

透明

15

8

単層

透明

19

11

単層

網入り

6.8

31

12

単層

網入り

10

21

単層

高透過

3

22

単層

高透過

5

23

単層

高透過

6

24

単層

高透過

8

25

単層

高透過

10

26

単層

高透過

12

31

単層

熱吸グリーン

632

単層

熱吸グリーン833

単層

熱吸グリーン1034

単層

熱吸グリーン1241

単層

熱反シルバー

642

単層

熱反シルバー

843

単層

熱反シルバー

1044

単層

熱反シルバー

1251

単層高性能熱線反射(可視光透過率 40%)

6

52

単層

高性能熱線反射(可視光透過率 40%)

8

53

単層

高性能熱線反射(可視光透過率 40%)

10

54

単層

高性能熱線反射(可視光透過率 40%)

12

55

単層

高性能熱線反射(可視光透過率 30%)

6

56

単層

高性能熱線反射(可視光透過率 30%)

8

57

単層

高性能熱線反射(可視光透過率 30%)

10

58

単層

高性能熱線反射(可視光透過率 30%)

12

59

単層

高性能熱線反射(可視光透過率 20%)

6

60

単層

高性能熱線反射(可視光透過率 20%)

8

61

単層

高性能熱線反射(可視光透過率 20%)

10

62

単層

高性能熱線反射(可視光透過率 20%)

12

63

単層

高性能熱線反射(可視光透過率 8%)

6

64

単層

高性能熱線反射(可視光透過率 8%)

8

65

単層

高性能熱線反射(可視光透過率 8%)

10

66

単層

高性能熱線反射(可視光透過率 8%)

12

81

単層

セラミック印刷（白面積 30%）

6

82

単層

セラミック印刷（白面積 30%）

8

83

単層

セラミック印刷（白面積 30%）

10

84

単層

セラミック印刷（白面積 30%）

12

32

85

単層

セラミック印刷（白面積 50%）

6

86

単層

セラミック印刷（白面積 50%）

8

87

単層

セラミック印刷（白面積 50%）

10

88

単層

セラミック印刷（白面積 50%）

12

89

単層

セラミック印刷（白面積 70%）

6

90

単層

セラミック印刷（白面積 70%）

8

91

単層

セラミック印刷（白面積 70%）

10

92

単層

セラミック印刷（白面積 70%）

12

93

単層

セラミック印刷（白面積 100%）

6

94

単層

セラミック印刷（白面積 100%）

8

95

単層

セラミック印刷（白面積 100%）

10

96

単層

セラミック印刷（白面積 100%）

12

103

複層（空気層 6mm）

透明+透明

6

104

複層（空気層 6mm）

透明+透明

8

105

複層（空気層 6mm）

透明+透明

10

106

複層（空気層 6mm）

透明+透明

12

123

複層（空気層 6mm）

高透過+高透過6124

複層（空気層 6mm）

高透過+高透過8125

複層（空気層 6mm）

高透過+高透過10126

複層（空気層 6mm）

高透過+高透過12131

複層（空気層 6mm）

熱吸グリーン+透明

6132

複層（空気層 6mm）

熱吸グリーン+透明

8133

複層（空気層 6mm）

熱吸グリーン+透明

10134

複層（空気層 6mm）

熱吸グリーン+透明

12141

複層（空気層 6mm）

熱反シルバー+透明6142

複層（空気層 6mm）

熱反シルバー+透明8143

複層（空気層 6mm）

熱反シルバー+透明10144

複層（空気層 6mm）

熱反シルバー+透明12151

複層（空気層 6mm）

高性能熱線反射(可視光透過率 40%+透明)

6152

複層（空気層 6mm）

高性能熱線反射(可視光透過率 40%+透明)

8153

複層（空気層 6mm）

高性能熱線反射(可視光透過率 40%+透明)

10

154

複層（空気層 6mm）

高性能熱線反射(可視光透過率 40%+透明)

12

155

複層（空気層 6mm）

高性能熱線反射(可視光透過率 30%+透明

6156

複層（空気層 6mm）

高性能熱線反射(可視光透過率 30%+透明)

8157

複層（空気層 6mm）

高性能熱線反射(可視光透過率 30%+透明)

10

33

158

複層（空気層 6mm）

高性能熱線反射(可視光透過率 30%+透明)

12

159

複層（空気層 6mm）

高性能熱線反射(可視光透過率 20%+透明)

6160

複層（空気層 6mm）

高性能熱線反射(可視光透過率 20%+透明)

8161

複層（空気層 6mm）

高性能熱線反射(可視光透過率 20%+透明)

10

162

複層（空気層 6mm）

高性能熱線反射(可視光透過率 20%+透明)

12

163

複層（空気層 6mm）

高性能熱線反射(可視光透過率 8%+透明)

6164

複層（空気層 6mm）

高性能熱線反射(可視光透過率 8%+透明)

8165

複層（空気層 6mm）

高性能熱線反射(可視光透過率 8%+透明)

10

166

複層（空気層 6mm）

高性能熱線反射(可視光透過率 8%+透明)

12

181

複層（空気層 6mm）

セラミック印刷(白面積 30%）+透明

6182

複層（空気層 6mm）

セラミック印刷(白面積 30%）+透明

8183

複層（空気層 6mm）

セラミック印刷(白面積 30%）+透明

10

184

複層（空気層 6mm）

セラミック印刷(白面積 30%）+透明

12

185

複層（空気層 6mm）

セラミック印刷(白面積 50%）+透明

6186

複層（空気層 6mm）

セラミック印刷(白面積 50%）+透明

8187

複層（空気層 6mm）

セラミック印刷(白面積 50%）+透明

10

188

複層（空気層 6mm）

セラミック印刷(白面積 50%）+透明

12

189

複層（空気層 6mm）

セラミック印刷(白面積 70%）+透明

6190

複層（空気層 6mm）

セラミック印刷(白面積 70%）+透明

8191

複層（空気層 6mm）

セラミック印刷(白面積 70%）+透明

10

192

複層（空気層 6mm）

セラミック印刷(白面積 70%）+透明

12

193

複層（空気層 6mm）

セラミック印刷(白面積 100%）+透明

6194

複層（空気層 6mm）

セラミック印刷(白面積 100%）+透明

8195

複層（空気層 6mm）

セラミック印刷(白面積 100%）+透明

10

196

複層（空気層 6mm）

セラミック印刷(白面積 100%）+透明

12

201

複層（空気層 6mm）

Low-E（高日射遮蔽型）+透明

6202

複層（空気層 6mm）

Low-E（高日射遮蔽型）+透明8203

複層（空気層 6mm）

Low-E（高日射遮蔽型）+透明

10

204

複層（空気層 6mm）

Low-E（高日射遮蔽型）+透明

12

205

複層（空気層 6mm）

Low-E（日射遮蔽型）+透明

6206

複層（空気層 6mm）

Low-E（日射遮蔽型）+透明8207

複層（空気層 6mm）

Low-E（日射遮蔽型）+透明

10

208

複層（空気層 6mm）

Low-E（日射遮蔽型）+透明

12

209

複層（空気層 6mm）

Low-E（日射取得型）+透明

6210

複層（空気層 6mm）

Low-E（日射取得型）+透明

8

34

211

複層（空気層 6mm）

Low-E（日射取得型）+透明

10

212

複層（空気層 6mm）

Low-E（日射取得型）+透明

12

213

複層（空気層 6mm）

Low-E（高日射取得型）+透明

6214

複層（空気層 6mm）

Low-E（高日射取得型）+透明

8215

複層（空気層 6mm）

Low-E（高日射取得型）+透明

10

216

複層（空気層 6mm）

Low-E（高日射取得型）+透明

12

251

複層（空気層 6mm）

透明+Low-E（日射取得型）

6252

複層（空気層 6mm）

透明+Low-E（日射取得型）

8253

複層（空気層 6mm）

透明+Low-E（日射取得型）

10

254

複層（空気層 6mm）

透明+Low-E（日射取得型）

12

255

複層（空気層 6mm）

透明+Low-E（高日射取得型）

6

256

複層（空気層 6mm）

透明+Low-E（高日射取得型）

8257

複層（空気層 6mm）

透明+Low-E（高日射取得型）

10

258

複層（空気層 6mm）

透明+Low-E（高日射取得型）

12

303

複層（空気層 12mm）

透明+透明

6

304

複層（空気層 12mm）

透明+透明

8

305

複層（空気層 12mm）

透明+透明

10

306

複層（空気層 12mm）

透明+透明

12

323

複層（空気層 12mm）

高透過+高透過6324

複層（空気層 12mm）

高透過+高透過8325

複層（空気層 12mm）

高透過+高透過10326

複層（空気層 12mm）

高透過+高透過12331

複層（空気層 12mm）

熱吸グリーン+透明

6332

複層（空気層 12mm）

熱吸グリーン+透明

8333

複層（空気層 12mm）

熱吸グリーン+透明

10334

複層（空気層 12mm）

熱吸グリーン+透明

12341

複層（空気層 12mm）

熱反シルバー+透明

6342

複層（空気層 12mm）

熱反シルバー+透明8343

複層（空気層 12mm）

熱反シルバー+透明10344

複層（空気層 12mm）

熱反シルバー+透明12351

複層（空気層 12mm）

高性能熱線反射(可視光透過率 40%+透明)

6352

複層（空気層 12mm）

高性能熱線反射(可視光透過率 40%+透明)

8353

複層（空気層 12mm）

高性能熱線反射(可視光透過率 40%+透明)

10

354

複層（空気層 12mm）

高性能熱線反射(可視光透過率 40%+透明)

12

355

複層（空気層 12mm）

高性能熱線反射(可視光透過率 30%+透明)

6

35

356

複層（空気層 12mm）

高性能熱線反射(可視光透過率 30%+透明)

8357

複層（空気層 12mm）

高性能熱線反射(可視光透過率 30%+透明)

10

358

複層（空気層 12mm）

高性能熱線反射(可視光透過率 30%+透明)

12

359

複層（空気層 12mm）

高性能熱線反射(可視光透過率 20%+透明)

6360

複層（空気層 12mm）

高性能熱線反射(可視光透過率 20%+透明)

8361

複層（空気層 12mm）

高性能熱線反射(可視光透過率 20%+透明)

10

362

複層（空気層 12mm）

高性能熱線反射(可視光透過率 20%+透明)

12

363

複層（空気層 12mm）

高性能熱線反射(可視光透過率 8%+透明)

6364

複層（空気層 12mm）

高性能熱線反射(可視光透過率 8%+透明)

8365

複層（空気層 12mm）

高性能熱線反射(可視光透過率 8%+透明)

10

366

複層（空気層 12mm）

高性能熱線反射(可視光透過率 8%+透明)

12

381

複層（空気層 12mm）

セラミック印刷(白面積 30%）+透明

6382

複層（空気層 12mm）

セラミック印刷(白面積 30%）+透明

8383

複層（空気層 12mm）

セラミック印刷(白面積 30%）+透明

10

384

複層（空気層 12mm）

セラミック印刷(白面積 30%）+透明

12

385

複層（空気層 12mm）

セラミック印刷(白面積 50%）+透明

6386

複層（空気層 12mm）

セラミック印刷(白面積 50%）+透明

8387

複層（空気層 12mm）

セラミック印刷(白面積 50%）+透明

10

388

複層（空気層 12mm）

セラミック印刷(白面積 50%）+透明

12

389

複層（空気層 12mm）

セラミック印刷(白面積 70%）+透明

6390

複層（空気層 12mm）

セラミック印刷(白面積 70%）+透明

8391

複層（空気層 12mm）

セラミック印刷(白面積 70%）+透明

10

392

複層（空気層 12mm）

セラミック印刷(白面積 70%）+透明

12

393

複層（空気層 12mm）

セラミック印刷(白面積 100%）+透明

6394

複層（空気層 12mm）

セラミック印刷(白面積 100%）+透明

8395

複層（空気層 12mm）

セラミック印刷(白面積 100%）+透明

10

396

複層（空気層 12mm）

セラミック印刷(白面積 100%）+透明

12

401

複層（空気層 12mm）

Low-E（高日射遮蔽型）+透明

6402

複層（空気層 12mm）

Low-E（高日射遮蔽型）+透明

8403

複層（空気層 12mm）

Low-E（高日射遮蔽型）+透明

10

404

複層（空気層 12mm）

Low-E（高日射遮蔽型）+透明

12

405

複層（空気層 12mm）

Low-E（日射遮蔽型）+透明

6406

複層（空気層 12mm）

Low-E（日射遮蔽型）+透明

8407

複層（空気層 12mm）

Low-E（日射遮蔽型）+透明

10

408

複層（空気層 12mm）

Low-E（日射遮蔽型）+透明

12

36

409

複層（空気層 12mm）

Low-E（日射取得型）+透明

6410

複層（空気層 12mm）

Low-E（日射取得型）+透明

8411

複層（空気層 12mm）

Low-E（日射取得型）+透明

10

412

複層（空気層 12mm）

Low-E（日射取得型）+透明

12

413

複層（空気層 12mm）

Low-E（高日射取得型）+透明

6414

複層（空気層 12mm）

Low-E（高日射取得型）+透明

8415

複層（空気層 12mm）

Low-E（高日射取得型）+透明

10

416

複層（空気層 12mm）

Low-E（高日射取得型）+透明

12

451

複層（空気層 12mm）

透明+Low-E（日射取得型）

6452

複層（空気層 12mm）

透明+Low-E（日射取得型）

8453

複層（空気層 12mm）

透明+Low-E（日射取得型）

10

454

複層（空気層 12mm）

透明+Low-E（日射取得型）

12

455

複層（空気層 12mm）

透明+Low-E（高日射取得型）

6456

複層（空気層 12mm）

透明+Low-E（高日射取得型）

8457

複層（空気層 12mm）

透明+Low-E（高日射取得型）

10

458

複層（空気層 12mm）

透明+Low-E（高日射取得型）

12

601

複層（アルゴン層 6mm）

Low-E（高日射遮蔽型）+透明

6602

複層（アルゴン層 6mm）

Low-E（高日射遮蔽型）+透明

8603

複層（アルゴン層 6mm）

Low-E（高日射遮蔽型）+透明

10

604

複層（アルゴン層 6mm）

Low-E（高日射遮蔽型）+透明

12

605

複層（アルゴン層 6mm）

Low-E（日射遮蔽型）+透明

6606

複層（アルゴン層 6mm）

Low-E（日射遮蔽型）+透明

8607

複層（アルゴン層 6mm）

Low-E（日射遮蔽型）+透明

10

608

複層（アルゴン層 6mm）

Low-E（日射遮蔽型）+透明

12

609

複層（アルゴン層 6mm）

Low-E（日射取得型）+透明6610

複層（アルゴン層 6mm）

Low-E（日射取得型）+透明

8611

複層（アルゴン層 6mm）

Low-E（日射取得型）+透明

10

612

複層（アルゴン層 6mm）

Low-E（日射取得型）+透明

12

613

複層（アルゴン層 6mm）

Low-E（高日射取得型）+透明

6614

複層（アルゴン層 6mm）

Low-E（高日射取得型）+透明

8615

複層（アルゴン層 6mm）

Low-E（高日射取得型）+透明

10

616

複層（アルゴン層 6mm）

Low-E（高日射取得型）+透明

12

651

複層（アルゴン層 6mm）

透明+Low-E（日射取得型）

6652

複層（アルゴン層 6mm）

透明+Low-E（日射取得型）

8653

複層（アルゴン層 6mm）

透明+Low-E（日射取得型）

10

37

654

複層（アルゴン層 6mm）

透明+Low-E（日射取得型）

12

655

複層（アルゴン層 6mm）

透明+Low-E（高日射取得型）

6656

複層（アルゴン層 6mm）

透明+Low-E（高日射取得型）

8657

複層（アルゴン層 6mm）

透明+Low-E（高日射取得型）

10

658

複層（アルゴン層 6mm）

透明+Low-E（高日射取得型）

12

801

複層（アルゴン層 12mm）

Low-E（高日射遮蔽型）+透明

6802

複層（アルゴン層 12mm）

Low-E（高日射遮蔽型）+透明

8803

複層（アルゴン層 12mm）

Low-E（高日射遮蔽型）+透明

10

804

複層（アルゴン層 12mm）

Low-E（高日射遮蔽型）+透明

12

805

複層（アルゴン層 12mm）

Low-E（日射遮蔽型）+透明

6806

複層（アルゴン層 12mm）

Low-E（日射遮蔽型）+透明

8807

複層（アルゴン層 12mm）

Low-E（日射遮蔽型）+透明

10

808

複層（アルゴン層 12mm）

Low-E（日射遮蔽型）+透明

12

809

複層（アルゴン層 12mm）

Low-E（日射取得型）+透明

6810

複層（アルゴン層 12mm）

Low-E（日射取得型）+透明

8811

複層（アルゴン層 12mm）

Low-E（日射取得型）+透明

10

812

複層（アルゴン層 12mm）

Low-E（日射取得型）+透明

12

813

複層（アルゴン層 12mm）

Low-E（高日射取得型）+透明

6814

複層（アルゴン層 12mm）

Low-E（高日射取得型）+透明

8815

複層（アルゴン層 12mm）

Low-E（高日射取得型）+透明

10

816

複層（アルゴン層 12mm）

Low-E（高日射取得型）+透明

12

851

複層（アルゴン層 12mm）

透明+Low-E（日射取得型）

6852

複層（アルゴン層 12mm）

透明+Low-E（日射取得型）

8853

複層（アルゴン層 12mm）

透明+Low-E（日射取得型）

10

854

複層（アルゴン層 12mm）

透明+Low-E（日射取得型）

12

855

複層（アルゴン層 12mm）

透明+Low-E（高日射取得型）

6856

複層（アルゴン層 12mm）

透明+Low-E（高日射取得型）

8857

複層（アルゴン層 12mm）

透明+Low-E（高日射取得型）

10

858

複層（アルゴン層 12mm）

透明+Low-E（高日射取得型）

12

■子要素
なし
■例

38

例1)

ガラス番号、ガラス種類による指定<WindowConfigure Name=”WND1” WindowTypeNumber=”1” WindowTypeClass=”Single”/>

例2)

U 値、M 値の直接指定<WindowConfigure Name=”WND1” Uvalue=”0.055” WindowTypeClass=”Single” />39

HeatSourceSet 要素■概要
熱源群を表す要素。
■属性
属性名

内容

Name

熱源群名称を指定します。必須です。

Simultaneous

冷暖同時供給有無を次から選択します。必須です。

QuantityControl

StorageMode

StorageSize

値

意味

True

冷暖同時供給有り

False

冷暖同時供給無し

台数制御を次から選択します。必須です。
値

意味

True

台数制御有りFalse

台数制御無し蓄熱時運転モードを次から選択します。必須です。
値

意味

None

無

Charge蓄熱

CompressorAided

追掛

蓄熱容量

■子要素
なし
■例
例1)

2 台の熱源を台数制御する熱源群<HeatSourceSet Name=”AHP”
Simutlaneous=”False” QuantityControl=”True” StorageMode=”None”><HeatSource Type=”AirSourceHeatPump”
CoolingSupplyWaterTemp=”7” CoolingOrder=”1” CoolingCount=”1”
CoolingCapacity=”510” CoolingMainPower=”157.4” CoolingSubPower=”0”
CoolingPrimaryPumpPower=”11”40

HeaingSupplyWaterTemp=”45” HeatingOrder=”1” HeatingCount=”1”
HeatingCapacity=”540” HeatingMainPower=”166.7” HeatingSubPower=”0”
HeatingPrimaryPumpPower=”15” /><HeatSource Type=”AirSourceHeatPump”
CoolingSupplyWaterTemp=”7” CoolingOrder=”2” CoolingCount=”1”
CoolingCapacity=”510” CoolingMainPower=”157.4” CoolingSubPower=”0”
CoolingPrimaryPumpPower=”11”
HeaingSupplyWaterTemp=”45” HeatingOrder=”2” HeatingCount=”1”
HeatingCapacity=”540” HeatingMainPower=”166.7” HeatingSubPower=”0”
HeatingPrimaryPumpPower=”15” /></HeatSourceSet>

41

HeatSource 要素■概要
熱源を表す要素。
■属性
属性値

説明

Type

温水暖房用熱源機の種類を表 12 から選択します。必須です。

CoolingSupplyWaterTemp

送水温度（冷房）[°]を小数(小数点以下 1 桁まで)で指定します。

CoolingOrder

運転順位（冷房）を整数で指定ます。

CoolingCount

台数（冷房）[台]を整数で指定します。

CoolingCapacity

定格冷却能力（冷房）[kW/台] を小数(小数点以下 2 桁まで)で指定します。

CoolingMainPower

主機定格消費エネルギー（冷房）を小数(小数点以下 2 桁まで)で指定します。
。単位は、電気式なら[kW/台]、ガス式なら[m3/h 台]、油式なら[L/h 台]です。

CoolingSubPower

補機 定格消費電力（冷房）[kW/台] を小数(小数点以下2 桁まで)で指定します。

CoolingPrimaryPumpPower

一次ポンプ 定格消費電力（冷房）[kW/台] を小数(小数点以下 2 桁まで)で指定します。

CoolingCTCapacity

冷却塔 定格冷却能力（冷房）[kW/台] を小数(小数点以下 2 桁まで)で指定します。

CoolingCTFanPower

冷却塔

冷却塔ファン消費電力（冷房）[kW/台] を小数(小数点以下 2 桁まで)で指定します。
CoolingCTPumpPower

冷却塔

冷却水ポンプ消費電力（冷房）[kW/台] を小数(小数点以下 2 桁まで)で指定します。
HeatingSupplyWaterTemp

送水温度（暖房）[°] を小数(小数点以下 1 桁まで)で指定します。

HeatingOrder

運転順位（暖房）を整数で指定します。

HeatingCount

台数（暖房）[台]を整数で指定します。

HeatingCapacity

定格暖房能力（暖房）[kW/台] を小数(小数点以下 2 桁まで)で指定します。

HeatingMainPower

主機 定格消費エネルギー（暖房）を小数(小数点以下 2桁まで)で指定します。。単位は、電気式なら[kW/台]、ガ42

ス式なら[m3/h 台]、油式なら[L/h 台]です。
HeatingSubPower

補機 定格消費電力（暖房）[kW/台] を小数(小数点以下2 桁まで)で指定します。

HeatingPrimaryPumpPower

一次ポンプ 定格消費電力（暖房）[kW/台] を小数(小数点以下 2 桁まで)で指定します。

表 12 熱源種類一覧
値

意味

AirSourceHeatPump

空冷ヒートポンプ

AirSourceHeatPumpMultiCompressor

空冷ヒートポンプ(圧縮機台数制御)

WaterSourceScrewChiller

水冷式スクリューチラー

WaterSourceScrollChiller

水冷式スクロールチラー

TurboRefrigerator

ターボ冷凍機InvertorTurboRefrigerator

インバータターボ冷凍機

BrineTurboRefrigeratorForStorage

ブラインターボ冷凍機(蓄熱時)

BrineTurboRefrigeratorForCompressorAided

ブラインターボ冷凍機(追掛時)

AirSourceHeatPumpForIceStorage

氷蓄熱用空冷式ヒートポンプ

AirSourceHeatPumpMultiCompressorForIceStora

氷蓄熱用空冷式ヒートポンプ(圧縮ge

機台数制御)

WaterSourceScrewChillerForIceStorage

氷蓄熱用水冷式スクリューチラー

WaterSourceScrollChillerForIceStorage

氷蓄熱用水冷式スクロールチラー

AbsorptionChillerHeaterWithCityGas

直焚吸収冷温水機(都市ガス)

AbsorptionChillerHeaterWithLPG

直焚吸収冷温水機(LPG)

AbsorptionChillerHeaterWithOil

直焚吸収冷温水機(重油)AbsorptionChillerHeaterWithKerosene

直焚吸収冷温水機(灯油)SteamAbsorptionChiller

蒸気吸収冷凍機

HotWaterAbsorptionChiller

温水焚吸収冷凍機

OnePassBoilerWithCityGas

小型貫流ボイラ(都市ガス)

OnePassBoilerWithLPG

小型貫流ボイラ(LPG)

OnePassBoilerWithOil

小型貫流ボイラ(重油)

OnePassBoilerWithKerosene

小型貫流ボイラ(灯油)

VacuumBoilerWithCityGas

真空温水ヒータ(都市ガス)

VacuumBoilerWithLPG

真空温水ヒータ(LPG)

VacuumBoilerWithOil

真空温水ヒータ(重油)

VacuumBoilerWithKerosene

真空温水ヒータ(灯油)43VariableRefrigerantFlowSystemWithElectricity

ビル用マルチエアコン(電気式)

VariableRefrigerantFlowSystemWithCityGas

ビル用マルチエアコン(都市ガス式)

VariableRefrigerantFlowSystemWithLPG

ビル用マルチエアコン(LPG)

RoomAirConditioner

ルームエアコン

FFtypeHeaterWithCityGas

FF 式暖房機(都市ガス)

FFtypeHeaterWithLPG

FF 式暖房機(LPG)

FFtypeHeaterWithKerosene

FF 式暖房機(灯油)

CoolingWaterByDistrictHeatingAndCooling

地域熱供給(冷水)HeatingWaterByDistrictHeatingAndCooling

地域熱供給(温水)SteamByDistrictHeatingAndCooling

地域熱供給(蒸気)HeatExchanger

熱交換器

■子要素
なし
■例
例1)
<HeatSource Type=”AirSourceHeatPump”
CoolingSupplyWaterTemp=”7” CoolingOrder=”1” CoolingCount=”1”
CoolingCapacity=”510” CoolingMainPower=”157.4” CoolingSubPower=”0”
CoolingPrimaryPumpPower=”11”
HeaingSupplyWaterTemp=”45” HeatingOrder=”1” HeatingCount=”1”
HeatingCapacity=”540” HeatingMainPower=”166.7” HeatingSubPower=”0”
HeatingPrimaryPumpPower=”15” />44SecondaryPumpSet 要素■概要
二次ポンプ群を表す要素。
■属性
属性名

内容

Name

二次ポンプ群名称を指定します。必須です。

QuantityControl

台数制御を次から選択します。必須です。
値

意味

True

台数制御有りFalse

台数制御無しCoolingTempDiff

冷房時温度差を指定します。単位は℃です。必須です。

HeatingTempDiff

暖房時温度差を指定します。単位は℃です。必須です。

■子要素
要素型

説明

SecondaryPump

二次ポンプ群に属する二次ポンプを定義します。

■例
例1)<SecondaryPumpSet Name=”PC1” QuantityControl=”True”
CoolingTempDiff=”7” HeatingTempDiff=”7”><SecondaryPump Order=”1” Count=”1”
RatedFlow=”62.5” RatedPower=”26” FlowControl=”CWV”/><SecondaryPump Order=”2” Count=”1”
RatedFlow=”62.5” RatedPower=”26” FlowControl=”CWV”/></SecondaryPumpSet/>

45

SecondaryPump 要素■概要
二次ポンプを表す要素。
■属性
属性名

内容

Order

運転順位を指定します。優先度の高い方から順に 1,2,3 と指定します。必須です。

Count

台数を指定します。

RatedFlow

定格流量[m3/h 台] を小数(小数点以下 2 桁まで)で指定します。必須です。
定格消費電力[kW/台] を小数(小数点以下 2 桁まで)で指定します。

RatedPower

必須です。
FlowControl

流量制御方式を次の表から選択します。

MinValveOpening

値

意味

CWV

定風量制御

VWVInverter

回転数制御

変流量時最小流量比を小数(小数点以下 2 桁まで)で指定します。必須です。流量制御方式が回転数制御の場合には必須です。

Info

備考を指定します。任意です。

■子要素
なし
■例
例1)
<SecondaryPump Order=”1” Count=”1”
RatedFlow=”62.5” RatedPower=”26” FlowControl=”CWV” />46

AirHandlingUnitSet 要素■概要
空調機群を表す要素。
■属性
属性名

内容

Name

空調機群名称を指定します。必須です。

■子要素
要素型

説明

AirHandlingUnit

空調機を定義します。

HeatSourceSetRef

熱源群参照を定義します。

SecondaryPumpSetRef

二次ポンプ群参照を定義します。

■例
例1)<AirHandlingUnitSet Name=”AC1F”><AirHandlingUnit Count=”1” Type=”AirHandlingUnit”
CoolingCapacity=”72.6” HeatingCapacity=”72.6”
SupplyAirVolume=”13100” SupplyFanPower=”11” ExhaustFanPower=”1.1”
FlowControl=”CAV”
OutsideAirCutControl=”True” FreeCoolingControl=”False”
HeatExchanger=”True” HeatExchangerVolume=”3050”
HeatExchangerEfficiency=”60” HeatExchangerBypass=”False”
HeatExchangerPower=”0.06” /><HeatSourceSetRef CoolingName=”AHP” HeatingName=”AHP”/><SecondaryPumpSetRef CoolingName=”PC1” HeatingName=”PH2”/></AirHandlingUnitSet/>

47

AirHandlingUnit 要素■概要
空調機を表す要素。
■属性
属性名

内容

Count

台数を整数で指定します。必須です。

Type

空調機の種類を次から選択します。必須です。

CoolingCapacity

値

意味

AirHandlingUnit

空調機

FanCoilUnit

FCU

IndoorUnit

室内機

AirHeatExchanger

全熱交ユニット

Fan

送風機

Radiator

放熱器

定格冷却(冷房)能力[kW/台]を小数(小数点以下 2 桁まで)で指定します。必須です。

HeatingCapacit

定格加熱(暖房)能力[kW/台]を小数(小数点以下 2 桁まで)で指定しまyす。必須です。

SupplyAirVolum

給気送風機定格風量[m3/h]を小数(小数点以下 2 桁まで)で指定しまeす。必須です。

SupplyFanPowe

送風機定格消費電力(給気)[kW/台]を小数(小数点以下 2 桁まで)で指定rします。必須です。

ReturnFanPowe

送風機定格消費電力(還気) [kW/台]を小数(小数点以下 2 桁まで)で指r

定します。必須です。

OutsideAirFanP

送風機定格消費電力(外気) [kW/台]を小数(小数点以下 2 桁まで)で指ower

定します。必須です。

ExhaustFanPow

送風機定格消費電力(排気) [kW/台]を小数(小数点以下 2 桁まで)で指er

定します。必須です。

FlowControl

風量制御方式を次から指定します。

MinDamperOpe

値

意味

CAV

定風量制御

VAVInverter

回転数制御

変風量時最小風量比[-]を指定します。風量制御方式が回転数制御の場

48

ning

合には必須です。

OutsideAirCutC

外気カット制御の有無を次の表から指定します。任意です。

ontrol

値

意味

True

外気カット制御あり

False

外気カット制御なし

FreeCoolingCon

外気冷房制御の有無を次の表から指定します。任意です。

trol

値

意味

True

外気冷房制御あり

False

外気冷房制御なし

HeatExchanger

全熱交換器の有無を次の表から指定します。任意です。
値

意味

True

全熱交換器ありFalse

全熱交換器なし

HeatExchanger

全熱交換器定格風量[m3/h 台]を小数(小数点以下 2 桁まで)で指定しま

Volumeす。全熱交換器がある場合は必須です。

HeatExchanger

定格全熱交換効率[-]を小数(小数点以下 2 桁まで)で指定します。全熱Effciency

交換器がある場合は必須です。

HeatExchanger

全熱交換器がある場合は全熱交換器バイパス制御の有無を次の表か

Bypassら指定します。
値

意味

True

全熱交換器 バイパス制御あり

False

全熱交換器 バイパス制御なし

HeatExchanger

全熱交換器ロータ消費電力[kW/台] を小数(小数点以下 1 桁まで)で指Power定します。全熱交換器がある場合は必須です。

Info

備考を指定します。任意です。

■子要素
なし
■例
例1)
<AirHandlingUnit Count=”1” Type=”AirHandlingUnit”
CoolingCapacity=”72.6” HeatingCapacity=”72.6”
SupplyAirVolume=”13100” SupplyFanPower=”11” ExitFanPower=”1.1”

49

FlowControl=”CAV”
OutsideAirCutControl=”True” FreeCoolingControl=”False”
HeatExchanger=”True” HeatExchangerVolume=”3050”
HeatExchangerEfficiency=”60” HeatExchangerBypass=”False”
HeatExchangerPower=”0.06” />50

HeatSourceSetRef 要素■概要
熱源群参照を表す要素。
■属性
属性名

内容

CooolingName

熱源群 名称（冷房） を指定し ます。任意です。 指定 する値は 、HeatSourceSet 要素の Name 属性の値と一致する必要があります。

HeatingName

熱源群 名称（暖房） を指定し ます。任意です。 指定 する値は 、HeatSourceSet 要素の Name 属性の値と一致する必要があります。

■子要素
なし
■例
例1)
<HeatSourceSetRef CoolingName=”AHP” HeatingName=”AHP”/>

51

SecondaryPumpSetRef 要素■概要
二次ポンプ群参照を表す要素。
■属性
属性名

内容

CooolingName

二次ポンプ群名称(冷房)を指定します。任意です。指定する値は、SecondaryPumpSet 要素の Name 属性の値と一致する必要があります。

HeatingName

二次ポンプ群名称(暖房) を指定します。任意です。指定する値は、SecondaryPumpSet 要素の Name 属性の値と一致する必要がありま
す。

■子要素
なし
■例
例1)
<SecondaryPumpSetRef CoolingName=”PC1” HeatingName=”PH2”/>52

空調以外の機械換気の設定
VentilationSystems 要素■概要
換気設備全体を表す要素です。
■属性
なし
■子要素
要素型

説明

VentilationRoom

換気室を定義します。

VentilationFanUnit

換気設備（送風機）を定義します。

VentilationACUnit

換気設備（冷房）を定義します。

MinorRoom

非主要室を定義します。

■例
例1)<VentilationSystem><VentilationRoom Floor=”1F” Name=”1F 湯沸コーナー”
BuildingType=”Office” RoomType=”Kitchenette” Area=”7.7”><VentilationUnitRef UnitType=”ExhaustFan” Name=”FE-16” /></VentilationRoom><VentilationFanUnit Name=”FE-16” FanVolume=”100” FanPower=”0.03”
Motor=”Standard” Inverter=”False” VolumeControl=”None” /></VentilationSystem>

53

VentilationRoom 要素■概要
換気室を表す要素です。次に示す属性から構成されます。
■属性
属性名

説明

Floor

換気室の階を指定します。

Name

換気室の室名を指定します。

BuildingType

建物用途を次の中から指定します。指定できる値は Room 要素のBuildingType 属性と同じです。必須です。

RoomType

室用途を次の中から指定します。指定できる値は Room 要素のRoomType 属性と同じです。必須です。
室面積[㎡]を小数(小数点以下 2 桁まで)で指定します。必須です。

Area
■子要素
要素型

説明

VentilationUnitRef

換気室に接続される換気設備の参照を定義します。

■例
例2)<VentilationRoom Floor=”1F” Name=”1F 湯沸コーナー”
BuildingType=”Office” RoomType=”Kitchenette” Area=”7.7”><VentilationUnitRef UnitType=”ExhaustFan” Name=”FE-16” /></VentilationRoom>

54

VentilationUnitRef 要素■概要
換気設備の参照を表す要素です。次に示す属性から構成されます。
■属性
属性名

説明

UnitType

換気種類を次の中から指定します。必須です。

Name

値

意味

SupplyFan

給気

ExhaustFan

排気CirculationFan

循環

AC

空調

換気機器名称を指定します。必須です。指定する値は、換気種類が空調でない場合は VentilationFanUnit 要素の Name 属性に指定されている値と一致する必要があります。換気種類が空調の場合は、VentilationACUnit 要素の Name 属性に指定されている値と一致する必要があります。

■子要素
なし
■例
例1)
<VentilationUnitRef UnitType=”ExhaustFan” Name=”FE-1” />55VentilationFanUnit 要素■概要
機械換気設備（送風機）を表す要素です。
■属性
属性値

説明

Name

一意の換気機器名称を指定します。

FanVolume

定格風量[m3/m] を小数(小数点以下 2 桁まで)で指定します。
必須です。

FanPower

電動機消費電力[kW] を小数(小数点以下 3 桁まで)で指定します。必須
です。

Motor

電動機の種類を次の表から指定します。
値

意味

HighEfficiency 高効率電動機を採用する
Standard
InverterVolumeControl

高効率電動機を採用しない

インバータの有無を次の表から指定します。
値

意味

True

インバータあり

False

インバータなし

送風量制御の次の表から指定します。
値

意味

COconcentration CO・CO2 濃度制御
Temperature

温度制御

None

無

■子要素
なし
■例
例1)
<VentilationFanUnit Name=”FE1” FanVolume=”300” FanPower=”0.07”
Motor=”Standard” Inverter=”False” VolumeControl=”None” />56VentilationACUnit 要素■概要
機械換気設備（冷房）を表す要素です。
■属性
属性値

説明

Name

一意の換気機器名称を指定します。必須です。

CoolingCapacity

必要冷却能力[kW] を小数(小数点以下 2 桁まで)で指定します。必須
です。

COP

熱源効率[-]を小数(小数点以下 2 桁まで)で指定します。必須です。

FanPower

送風機消費電力[kW] を小数(小数点以下 3 桁まで)で指定します。必須です。

PumpPower

ポンプ消費電力[kW] を小数(小数点以下 3 桁まで)で指定します。必
須です。

■子要素
なし
■例
例1)
<VentilationACUnit Name=”VAC1” CoolingCapacity=”5.00”
COP=”4.51” FanPower=”1.21” PumpPower=”0.567” />57

照明の設定LightingSystems 要素■概要
照明全体を表す要素です。
■属性
なし
■子要素
要素型

説明

LightingRoom

照明室を定義します。

MinorRoom

非主要室を定義します。

■例
例1)<LightingSystem><LightingRoom Floor=”1F” Name=”事務室” BuildingType=”Office” RoomType=”Office”
Area=”605.2” FloorHeight=”4.0” RoomHeight=”2.6” RoomIndex=”5.32”><LightingUnit UnitType=”埋込下面ルーバ” Power=”95” Count=”104”
OccupantSensing=”None” TimeSchedule=”None”
InitialIlluminationCorrection=”False” DaylightSensing=”None”/></LightingRoom></LightingSystem>

58

LightingRoom 要素■概要
照明室を表す要素です。次に示す属性から構成されます。
■属性
属性名

説明

Floor

照明室の階を指定します。

Name

照明室の室名を指定します。

BuildingType

建物用途を次の中から指定します。指定できる値は Room 要素のBuildingType 属性と同じです。必須です。

RoomType

室用途を次の中から指定します。指定できる値は Room 要素のRoomType 属性と同じです。必須です。

Area

室面積[㎡]を小数(小数点以下 2 桁まで)で指定します。必須です。

FloorHeight

階高[㎡]を小数(小数点以下 1 桁まで)で指定します。任意です。

RoomHeight

天井高[㎡]を小数(小数点以下 1 桁まで)で指定します。任意です。

Depth

室の間口[m]を小数(小数点以下 1 桁まで)で指定します。任意です。

Width

室の奥行[m]を小数(小数点以下 1 桁まで)で指定します。任意です。

RoomIndex

室指数[-]を小数(小数点以下 3 桁まで)で指定します。任意です。ただし、Depth 属性または Width 属性を指定しない場合には入力が必要です。また、Depth 属性または Width 属性を指定する場合には
RoomIndex 属性の指定を行いません。

■子要素
要素型

説明

LightingUnit

照明器具を定義します。

■例
例2)<LightingRoom Floor=”1F” Name=”事務室” BuildingType=”Office” RoomType=”Office”
Area=”605.2” FloorHeight=”4.0” RoomHeight=”2.6” RoomIndex=”5.32”><LightingUnit UnitType=”埋込下面ルーバ” Power=”95” Count=”104”
OccupantSensing=”None” TimeSchedule=”None”
InitialIlluminationCorrection=”False” DaylightSensing=”None”

59IlluminanceSensing=”False” DimmingControl=”False” /></LightingRoom>60

LightingUnit 要素■概要
LightingUnit 要素は照明器具を表します。
■属性
属性値

説明

UnitType

照明器具形式を指定します。任意です。

UnitName

機器名称を指定します。任意です。

Power

定格消費電力[W/台]を小数(小数点以下 2 桁まで)で指定します。必
須です。

Count

台数[台]を小数(小数点以下 2 桁まで)で指定します。必須です。

OccupantSensing

在室検知制御を次から選択します。必須です。

TimeSchedule

値

意味

None

無

Dimmer

減光

OnOff

一括点滅

Sensing64

6.4m 角点滅

Sensing32

3.2m 角点滅

EachUnit

器具毎点滅

タイムスケジュール制御を次から選択します。必須です。
値

意味

None

無

Dimmer

減光

OnOff

消灯

InitialIlluminatio

初期照度補正を次から選択します。必須です。

nCorrection

値

意味

True

有り

False

無

DaylightSensing

在室検知制御を次から選択します。必須です。
値

意味

None

無

EachSideWithBlind

片側採光かつブラインド自動制御なしEachSideWithoutBli

片側採光かつブラインド自動制御あ
61

nd

り

BothSidesWithBlind

両側採光かつブラインド自動制御なしBothSidesWithoutBli

両側採光かつブラインド自動制御あnd

りIlluminanceSensi

初期照度補正を次から選択します。必須です。

ng

値

意味

True

有り

False

無

DimmingControl

初期照度補正を次から選択します。必須です。
値

意味

True

有り

False

無

■例
例1)
<LightingUnit UnitType=”埋込下面ルーバ” Power=”95” Count=”104”
OccupantSensing=”None” TimeSchedule=”None”
InitialIlluminationCorrection=”False” DaylightSensing=”None”
IlluminanceSensing=”False” DimmingControl=”False” />62

給湯の設定HotwaterSystems 要素■概要
給湯設備全体を表す要素です。
■属性
なし
■子要素
要素型

説明

HotwaterRoom

給湯室を定義します。

Boiler

給湯器を定義します。

MinorRoom

非主要室を定義します。

■例
例1)<HotwaterSystems><HotwaterRoom Floor=”1F” Name=”1F 事務室”
BuildingType=”Office” RoomType=”Office” Area=”605.2”><BoilerRef Location=”1F 女子便所” WaterSaving=”None” Name=”EH1-1F”/><BoilerRef Location=”1F 男子便所” WaterSaving=”None” Name=”EH2-1F”/><BoilerRef Location=”1F 湯沸コーナー” WaterSaving=”None” Name=”EH3-1F”/></HotwaterRoom><Boiler Name=”EH1-1F” FuelType=“Electricity” Capacity=“1.50” Efficiency=“0.37”
Insulation = “Level1” PipeSize = “15” SolarSystem = “False” /><Boiler Name=”EH1-2F” FuelType=“Electricity” Capacity=“1.10” Efficiency=“0.37”
Insulation = “Level1” PipeSize = “15” SolarSystem = “False” /><Boiler Name=”EH1-3F” FuelType=“Electricity” Capacity=“3.00” Efficiency=“0.37”
Insulation = “Level1” PipeSize = “15” SolarSystem = “False” /></HotwaterSystems>

63HotwaterRoom 要素■概要
給湯室を表す要素です。次に示す属性から構成されます。

■属性
属性名

説明

Floor

給湯室の階を指定します。

Name

給湯室の室名を指定します。

BuildingType

建物用途を次の中から指定します。指定できる値は Room 要素のBuildingType 属性と同じです。必須です。

RoomType

室用途を次の中から指定します。指定できる値は Room 要素のRoomType 属性と同じです。必須です。
室面積[㎡]を小数(小数点以下 2 桁まで)で指定します。必須です。

Area
■子要素
要素型

説明

BoilerRef

給湯箇所と給湯器の参照を定義します。

■例
例2)<HotwaterRoom Floor=”1F” Name=”1F 事務室” BuildingType=”Office” RoomType=”Office”
Area=”605.2”><BoilerRef Location=”1F 女子便所” WaterSaving=”None” Name=”EH1-1F”/><BoilerRef Location=”1F 男子便所” WaterSaving=”None” Name=”EH2-1F”/><BoilerRef Location=”1F 湯沸コーナー” WaterSaving=”None” Name=”EH3-1F”/></HotwaterRoom>64

BoilerRef 要素■概要
給湯箇所および給湯器の参照を表す要素です。次に示す属性から構成されます。
■属性
属性名

説明

Location

給湯箇所を指定します。任意です。

WaterSaving

節湯器具の種類を次の中から指定します。必須です。

Name

値

意味

None

無し

MixingTap

自動給湯栓

WaterSavingShowerHead

節水型シャワー

給湯機器名称を指定します。必須です。Boiler 要素の Name 属性として定義されるいずれかの値と一致する必要があります。

■子要素
なし
■例
例1)
<BoilerRef Location=”B1F 湯沸コーナー WaterSaving=”None” Name=”EH3-B1F”/>

65Boiler 要素■概要
給湯器を表します。
■属性
属性名

説明

Name

一意な給湯器名称を指定します。必須です。

FuelType

燃料種類を次の中から指定します。必須です。

Capacity

値

意味Electricity

電力

CityGas

都市ガス

LPG

液化石油ガス

Oil

重油

Kerosene

灯油

HotWater

他人から供給された熱(温水)Steam

他人から供給された熱(蒸気)

定格加熱能力[kW]を小数(小数点以下 2 桁まで)で指定します。
必須です。

Efficiency

定格熱源効率[-]を小数(小数点以下 2 桁まで)で指定します。必須です。

Insulation

PipeSize

建物用途を次の中から指定します。必須です。
値

意味

None

裸管

Level1保温仕様 1

Level2保温仕様 2

Level3保温仕様 3接続口径[mm] を小数(小数点以下 3 桁まで)で指定します。必須です。

SolarSystem

SolarSystemArea

太陽熱利用の有無
値

意味

True

太陽熱利用ありFalse

太陽熱利用なし

太陽熱利用時の集熱パネルの有効集熱面積[㎡] を小数(小数点以下 2 桁まで)で指定します。太陽熱を利用する場合は必須です。

66

SolarSystemDirection

太陽熱利用の集熱面の方位角[°] を小数(-360 から 360 の範囲の小数点以下 2 桁まで)で指定します。太陽熱を利用する場合は必須です。

SolarSystemAngle

太陽熱利用の集熱面の傾斜角[°] を小数(-360 から 360 の範囲の小数点以下 2 桁まで)で指定します。太陽熱を利用する場合は
必須です。

Info

備考を指定します。任意です。

■子要素
なし
■例
例1)
<Boiler Name=”EH1-1F”
FuelType = “Electricity”
Capacity = “2.00”
Efficiency = “0.35”
Insulation = “Level3”
PipeSize = “20”SolarSystem = “False”/>

67

昇降機の設定
Elevators 要素■概要
Elevators 要素は昇降機の集合を表します。子要素には Elevator 要素を複数持ちます。
Elevator 要素は次の属性で構成されます。
■属性
属性名

説明

Name

昇降機の機器名称（機器表の記号等）を指定します。任意です。

RoomFloor

主要な対象室の階を指定します。必須です。

RoomName

主要な対象室の室名を指定します。必須です。

BuildingType

主要な対象室の建物用途を指定します。指定できる値は Room 要素のBuildingType 属性と同じです。必須です。

RoomType

主要な対象室の室用途を指定します。指定できる値は Room 要素のRoomType 属性と同じです。必須です。

Count

台数[台]を小数(小数点以下 2 桁まで)で指定します。必須です。

LoadLimit

積載量[kg]を小数(小数点以下 2 桁まで)で指定します。必須です。

Velocity

速度[m/min]を小数(小数点以下 2 桁まで)で指定します。必須です。

TransportCapa

輸送能力係数[-]を小数(小数点以下 2 桁まで)で指定します。必須です。

cityFactor
ControlType

Regeneration

速度制御方式を次の表から指定します。
値

意味

VVVF

可変電圧可変周波数制御

ACFeedBack

交流帰還制御速度制御方式が VVVF の場合に、電力回生の有無を次の表から指定します。速度制御方式が VVVF の場合には必須です。

GearLess

値

意味

True

電力回生ありFalse

電力回生なし速度制御方式が VVVF の場合に、ギアレスかどうかを次の表から指定します。速度制御方式が VVVF の場合には必須です。
値

意味

True

ギアレス

68

False

ギアレスではない

■子要素
なし
■例
例1)

OfficeA が主要な対象室の VVVF の EV1 および OfficeB が主要な対象室の交流帰還制御式の EV2<Building><Rooms><Room Floor=”1F” Name=”OfficeA” BuilingType=”Office” RoomType=”Office” /><Room Floor=”1F” Name=”OfficeB” BuilingType=”Office” RoomType=”Office” /></Room>< Elevators >< Elevator Name=”EV1” RoomFloor=”1F”
RoomName=”OfficeA” BuildingType=”Office” RoomType=”Office”
Count=”2” LoadLimit=”400” Velocity=”2.5” TransportCapacityFactor=”0.2”
ControlType=”VVVF” Regeneration=”True” GearLess=”False” />< Elevator Name=”EV2” RoomFloor=”1F”
RoomName=”OfficeB” BuildingType=”Office” RoomType=”Office”
Count=”2” LoadLimit=”400” Velocity=”2.5” TransportCapacityFactor=”0.2”
ControlType=”ACFeedBack” /></ Elevators ></Building>69効率化設備の設定
PhotovoltaicGenerationSystems・PhotovoltaicGeneration 要素■概要
PhotovoltaicGenerationSystems 要素は太陽光発電設備の集合を表します。子要素にはPhotovoltaicGeneration 要素を複数持ちます。PhotovoltaicGeneration 要素は次の属性で構成されます。
■属性
属性値

説明

Name

太陽光発電システム名称を指定します。任意です。

Capacity

太陽電池アレイのシステム容量を小数で指定します。小数点以下は 2桁までとします。単位はキロワットです。必須です。

Cell

太陽電池アレイの種類を次から選択します。必須です。

Setup

値

意味

Crystal

結晶系

Other

結晶系以外

太陽電池アレイ設置方式を次から選択します。必須です。

Direction

値

意味

Frame

架台設置形

RoofMount

屋根置き形

Other

その他

パネル設置方位角[°] を小数(-360 から 360 の範囲の小数点以下 2 桁まで)で指定します。必須です。

Angle

パネル設置傾斜角方位角[°] を小数(-360 から 360 の範囲の小数点以下 2 桁まで)で指定します。必須です。

Info

備考を指定します。任意です。

■例
例1)< PhotovoltaicGenerationSystems ><PhotovoltaicGenerationCapacity=”1” Cell=”Crystal”
Setup=”Frame” Direction=”45” Angle=”30” />70

<PhotovoltaicGenerationCapacity=”2” Cell=” Crystal”
Setup=”Frame” Direction=”135” Angle=”30” /></ PhotovoltaicGenerationSystems >71

CogenerationSystems 要素■概要
CogenerationSystems 要素はコージェネレーションシステムの集合を表します。子要素には CogenerationUnitSet 要素を複数持ちます。CogenerationUnitSet 要素は次の属性と要素から構成されます。
■属性
属性名

説明

Name

コジェネレーションシステム名称

ACElectricDemand

空調年間電力需要[MWh] を小数(小数点以下 2 桁まで)で指定します。必須です。

VentilationElectricDemand

換気年間電力需要[MWh] を小数(小数点以下 2 桁まで)で指定します。必須です。

LightingElectricDemand

照明年間電力需要[MWh] を小数(小数点以下 2 桁まで)で指定します。必須です。

HotwaterElectricDemand

給湯年間電力需要[MWh] を小数(小数点以下 2 桁まで)で指定します。必須です。

ElevatorElectricDemand

昇降機年間電力需要[MWh] を小数(小数点以下 2 桁まで)で指定します。必須です。

OtherElectricDemand

その他の年間電力需要 [MWh] を小数(小数点以下 2 桁まで)で指定します。必須です。

■子要素
要素型

説明

CogenerationUnit

コージェネレーション設備を定義します。

72

CogenerationUnit 要素■概要
コージェネレーション設備を表します。
■属性
属性値

説明

Name

機器名称を指定します。必須です。

GeneratingEfficiency

発電効率[-]を小数(小数点以下 3 桁まで)で指定します。必須です。

ExhaustHeatRecoveryRatio

排熱回収率[-]を小数(小数点以下 3 桁まで)で指定します。
必須です。

ElectricalDependencyRatio

発電依存率[-]を小数(小数点以下 3 桁まで)で指定します。
必須です。

HeatUtilizationRatio

有効熱利用率[-]を小数(小数点以下 3 桁まで)で指定します。必須です。

CoolingRatio

有効排熱量の冷熱利用比[-]を小数(小数点以下 3 桁まで)で指定します。必須です。

RefrigeratorCOP

温水吸収冷凍機または排熱投入型冷温水機の成績係数[-]を小数(小数点以下 2 桁まで)で指定します。必須です。

Info

備考を指定します。任意です。

■例
例1)<CogenerationUnit
Name=”COG1”
GenerationgEfficiency=”0.852”
ExhaustHeatRecoveryRatio=”0.921”
ElectricalDependencyRatio=”0.212”
HeatUtilizationRatio=”0.952”
CoolingRatio=”0.712”
RefrigeratorCOP=”4.52” />73