920MHz 帯 無線信号伝送ユニット（標準 1 対 1 通信）

UMDI-41AXS・UMDO-41AXS 取扱説明書

本製品を正しくご利用いただくためにこの取扱説明書をよくお読みください。
Version 1.00

株式会社アローセブン

目次
1 はじめに ······································································································································· 1

1.1 警告表示 ··························································································································· 1
1.2 安全上のご注意とお断り ········································································································ 12 概要 ············································································································································ 3

2.1 UMDI-41AXS・UMDO-41AXS とは ·························································································· 32.2 製品一覧 ··························································································································· 32.3 特長 ································································································································· 42.3.1 共通 ····························································································································· 42.3.2 UMDI-41AXS ·················································································································· 4
2.3.3 UMDO-41AXS ················································································································ 42.4 外観図 ······························································································································ 52.4.1 UMDI-41AXS ·················································································································· 52.4.2 UMDO-41AXS ················································································································ 53 製品仕様 ······································································································································ 63.1 一般仕様 ··························································································································· 63.1.1 UMDI-41AXS ·················································································································· 63.1.2 UMDO-41AXS ················································································································ 73.2 端子台 ······························································································································ 83.2.1 適合線サイズ ·················································································································· 83.2.2 UMDI-41AXS 端子台 ········································································································ 83.2.3 UMDO-41AXS 端子台 ···································································································· 103.3 モニタ－LED 表示 ·············································································································· 123.3.1 UMDI-41AXS 通常動作 ··································································································· 123.3.2 UMDO-41AXS 通常動作 ································································································· 133.3.3 内部エラー ··················································································································· 133.4 寸法図 ···························································································································· 143.4.1 UMDI-41AXS ················································································································ 143.4.2 UMDO-41AXS ·············································································································· 154 動作設定 ···································································································································· 164.1 電源の接続 ······················································································································ 164.1.1 AC アダプタによる電源供給 ······························································································ 164.1.2 UMDI-41AXS 端子台による電源供給 ·················································································· 164.1.3 UMDO-41AXS 端子台による電源供給 ················································································ 164.2 入出力設定（ジャンパーピン） ································································································ 174.2.1 UMDI-41AXS ················································································································ 174.2.2 UMDO-41AXS ·············································································································· 17
4.3 UMS 設定ソフトによる設定 ··································································································· 184.3.1 端末情報 ····················································································································· 19
4.3.2 端末設定内容 ··············································································································· 20

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）
4.3.3 端末操作 ····················································································································· 204.4 周波数一覧 ······················································································································ 214.5 設定例 ···························································································································· 224.5.1 マスター側設定（UMDO-41AXS） ······················································································· 224.5.2 スレーブ側設定（UMDI-41AXS） ························································································ 225 動作説明 ···································································································································· 235.1 標準 1 対 1 通信 ··············································································································· 235.2 UMDI-41AXS のデジタル出力（OUT1）について········································································· 23
5.3 UMDO-41AXS のリレー出力について ····················································································· 23
6 アンテナタイプ ······························································································································ 256.1 可倒式アンテナ ················································································································· 256.2 プレート付アンテナ ············································································································· 256.3 フランジ付アンテナ ············································································································· 26
7 本製品を使用する上での注意点 ········································································································ 27
8 アフターサービス ··························································································································· 282

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

1 はじめに
1.1 警告表示
記号の意味
危険警告
注意

誤った取扱いをした場合、死亡または重傷を負う危険性があり、その切迫の度合いが高いことを示します。
誤った取扱いをした場合、死亡または重傷を負う危険性があることを示します。
誤った取扱いをした場合、傷害を負うことが想定されるか、または物的損害に関して知っておいてほしい内容を示します。

1.2 安全上のご注意とお断り

警告◼

本体内部に異物を入れないでください。また、水などの液体が入らないように注意してください。故障、感電、火災の原因になります。

◼

分解しないでください。修理技術者以外の人は、絶対に分解や、修理・改造は行わないでください。感電の危険があります。また、発火などの異常動作でケガをすることがあります。

◼

落とさないようにしてください。
本体は安定した場所に設置してください。誤って落としたりすると、破損やケガなどの恐れがあります。

注意◼

指示された電源で使用してください。

◼

使用・保管上の注意
高温・多湿の場所、長時間直射日光の当たる場所での使用・保管は避けてください。
また、周辺の温度変化が激しいと、内部結露によって誤動作する場合があります。

◼

設置場所の注意
衝撃や振動の加わりやすい場所での使用・保管は避けてください。故障の原因になります。

1

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）－ お断り －◼

本製品を医療機器、航空機等には使用しないでください。もし、ご使用になる場合は当社までご相談ください。

◼

当社は品質の向上に努めておりますが、半導体製品は故障、誤動作する場合があります。
本製品の故障または誤動作によって結果的に、人身事故、火災事故等が発生しないよう安全設計に十分ご注意願います。

◼

この取扱説明書の記載内容は、2023 年 2 月現在のものです。
記載内容を予告なく変更あるいは製造中止することがありますのでご了承ください。

◼

無線通信は外来のノイズ、障害物等により一時的に通信できなくなることがあります。このような時でも安全に稼動するようにシステム設計してください。
また、その場合データの収集ができない場合があります。

◼

本製品は日本国内専用です。

2

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

2 概要
2.1 UMDI-41AXS・UMDO-41AXS とはＩ／Ｏ信号を無線伝送する装置です。
UMDI-41AXS に入力したデジタル信号を無線転送し、UMDO-41AXS でデジタル出力します。
マスター設定機器とスレーブ設定機器を１セットで使用します。
各動作設定は、USB ポートを使用し、UMS 設定ソフトにより行います。

スレーブ設定マスター設定2.2 製品一覧
製品名

特長

UMDI-41AXS

デジタル入力 4 点 920MHz 帯無線モデム内蔵 外部アンテナ接続

UMDO-41AXS

デジタル出力 4 点 920MHz 帯無線モデム内蔵 外部アンテナ接続

アンテナ
UAS-AM01

920MHz 帯 可倒式アンテナ（屋内用） アンテナ長さ：全長 約 108mm

UAS-AK01

920MHz 帯 可倒式アンテナ（屋内・屋外用） アンテナ長さ：全長 約 204mm

UAS-PM01

920MHz 帯 プレート付可倒式アンテナ（屋内用） ケーブル 1ｍ

UAS-PM02

920MHz 帯 プレート付可倒式アンテナ（屋内用） ケーブル 2ｍ

UAS-PK01

920MHz 帯 プレート付可倒式アンテナ（屋内・屋外用） ケーブル 1ｍ

UAS-PK02

920MHz 帯 プレート付可倒式アンテナ（屋内・屋外用） ケーブル 2ｍ

UAS-FK01

920MHz 帯 フランジ付可倒式アンテナ ケーブル 1m

UAS-FK02920MHz 帯 フランジ付可倒式アンテナ ケーブル 2m

電源用供給用 AC アダプタ（各機種共通）
UMD-ACA12AC アダプタ 12V
3

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

2.3 特長2.3.1 共通◼

920MHz 帯無線データ伝送です。

◼

免許の申請、資格が不要です。

◼

アンテナは用途に応じて、選択可能です。

◼

信号線の接続はスクリューレスのプッシュタイプで配線が容易です。

◼

電源は DC9-28V または AC アダプタ（DC12V）が使用できます。

◼

LED モニターにて動作状態が確認できます。

2.3.2 UMDI-41AXS◼

デジタル入力信号点数 4 点（フォトカプラ入力）です。

◼

デジタル出力信号点数 1 点（オープンコレクタ出力）です。

2.3.3 UMDO-41AXS◼

デジタル出力信号点数 4 点（オープンコレクタ出力）です。

◼

リレー出力信号点数 1 点（A 接点タイプ）です。

4

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

2.4 外観図
2.4.1 UMDI-41AXS

モニターLEDUSB 接続コネクタ
アンテナ

AC アダプタ用コネクタ

信号接続端子台2.4.2 UMDO-41AXS

モニターLEDUSB 接続コネクタ
アンテナ

信号接続端子台AC アダプタ用コネクタ

5UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3 製品仕様3.1 一般仕様
3.1.1 UMDI-41AXS
項目

内容

電源電圧

DC9V～28V または、専用 AC アダプタ

消費電流 (DC12V 時)

50mA 以下＜入出力仕様＞
デジタル入力デジタル出力点数

4（IN1～IN4）

入力形式

フォトカプラ 無電圧接点

点数

1（OUT1）

出力形式

オープンコレクタ シンク型

電流容量200mA／点

耐電圧

30V

＜通信ポート＞
USB ポート

Micro USB Type-B PC 設定用＜無線部仕様＞
技術基準

ARIB STD-T108 適合証明取得済み

空中線電力20mW

電波形式

F1D

無線周波数帯920.6MHz～928.0MHz

データ変調速度50kBps

通信距離 （ 環境による ）屋外見通し環境 1200m（アンテナ UAS-AK01［地上高 2m］使用時）

＜その他＞
重量

約 130g

外形サイズ

寸法図参照

動作温度

－10℃ ～＋50℃

6UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3.1.2 UMDO-41AXS
項目内容

電源電圧

DC9V～28V または、専用 AC アダプタ

消費電流 (DC12V 時)

50mA 以下＜入出力仕様＞
デジタル出力

リレー出力点数4（OUT1～OUT4）

出力形式

オープンコレクタ シンク型

電流容量200mA／点耐電圧

30V

点数1（RELAY）

接点容量

DC30V 2A 以下＜通信ポート＞
USB ポート

USB Type-C PC 設定用＜無線部仕様＞
技術基準

ARIB STD-T108 適合証明取得済み

空中線電力20mW

電波形式

F1D

無線周波数帯920.6MHz～928.0MHz

データ変調速度50kBps

通信距離 （ 環境による ）屋外見通し環境 1200m（アンテナ UAS-AK01［地上高 2m］使用時）

＜その他＞
重量

約 130g

外形サイズ

寸法図参照

動作温度

－10℃ ～＋50℃

7UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3.2 端子台3.2.1 適合線サイズ
単線(㎟)

より線(㎟)AWG

推奨むき線長さ(㎜)0.2-1.5

0.2-1.5

16-2483.2.2 UMDI-41AXS 端子台

電源・信号入出力用端子

電源・信号入出力用端子

内容IN 1

デジタル入力 1IN 2

デジタル入力 2IN 3

デジタル入力 3IN 4

デジタル入力 4

OUT1

デジタル出力

GND

デジタル入出力用 GND

DC9～28V

外部電源入力／出力兼用

GND

外部電源 GND

8

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）
デジタル入力信号
入力状態

電気的状態

OFF

デジタル入力 n – GND 間がオープン

ON

デジタル入力 n – GND 間がショート

デジタル出力信号

9UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3.2.3 UMDO-41AXS 端子台

電源・信号出力端子
リレー出力端子電源・信号出力端子

内容OUT(+)

外部電源出力OUT(G)

外部電源 GND

IN(+)

外部電源入力

IN(G)外部電源 GND

OUT 1

デジタル出力 1

OUT 2デジタル出力 2OUT 3

デジタル出力 3OUT 4

デジタル出力 4COM

出力 GND

リレー出力端子

内容N.O－COM

10

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）
デジタル出力信号

リレー出力信号11

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3.3 モニタ－LED 表示
3.3.1 UMDI-41AXS 通常動作

LED

色機能

内容POWER

赤電源モニター

電源 ON 時点灯

MON1

赤状態モニター

通常消灯

MON2

緑無線通信モニター

送信時 20ms 点灯

MON3

緑

無線通信モニター

受信時 20ms 点灯

STATUS

緑無線通信モニター

正常時消灯、通信エラー発生時 点滅(0.5s)

IN 1- IN 4

赤デジタル入力 1-4 モニター

入力 ON 時点灯／OFF 時消灯

OUT 1

緑

デジタル出力 1 モニター

出力 ON 時点灯／OFF 時消灯12

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3.3.2 UMDO-41AXS 通常動作

LED

色

機能

内容

POWER

赤電源モニター

電源 ON 時点灯

MON1

赤状態モニター

通常消灯

MON2

緑無線通信モニター

送信時 20ms 点灯

MON3

緑無線通信モニター

受信時 20ms 点灯

OUT 1～OUT 4

赤デジタル出力モニター

出力 ON 時点灯／OFF 時消灯

RELAY

赤リレー出力モニター

Close 時点灯／Open 時消灯

緑無線通信モニター

正常時消灯

STATUS

通信エラー発生時 点滅(0.5s)

3.3.3 内部エラー
内部エラー発生時は、異常検出後以下のモニター表示をして動作停止します。
異常内容LED

色機能

動作設定異常MON1

赤点滅(0.1s)

内部不揮発性メモリ異常

STATUS

緑点滅(0.1s)

内部エラーが発生した場合は、弊社までお問合せ下さい。

13

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3.4 寸法図3.4.1 UMDI-41AXS

14

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

3.4.2 UMDO-41AXS

15

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

4 動作設定4.1 電源の接続
4.1.1 AC アダプタによる電源供給専用の AC アダプタをご使用ください。やむを得ずその他のＡＣアダプタを使用する場合には下記のものをお使いください。
DC13.5V 2A EIAJ TYPE4

4.1.2 UMDI-41AXS 端子台による電源供給
端子台の GND 端子、DC9-28V 端子に入力してください。

4.1.3 UMDO-41AXS 端子台による電源供給
端子台の IN（G）端子、IN(+)端子に入力してください。

電源入力は AC アダプタの入力端子と接続されています。
AC アダプタとの同時入力はしないでください。

USB ケーブル接続しても電源は供給されません。AC アダプタまたは、端子台より電源供給をお願いします。

16

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

4.2 入出力設定（ジャンパーピン）
4.2.1 UMDI-41AXS
UMDI-41AXS ではジャンパーピンの設定はありません。

4.2.2 UMDO-41AXS

JP1【ジャンパー設定】
名称

内容

JP1

接続機器 GND との接続選択

短絡箇所

機能

有

GND 共通無GND 分離

出荷時設定

ジャンパーピンは機器の電源が OFF の状態で変更してください。

17

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

4.3 UMS 設定ソフトによる設定
以下の設定は UMS 設定ソフトで機器毎に個別設定する必要があります。
Windows PC に“UMS 設定ソフト”をインストールします。UMDI-41AXS／UMDO-41AXS に電源を供給し、PC とUSB ケーブルで接続します。ご使用の PC にシリアル USB ドライバがインストール済みだと、シリアルポートが追加されます。
UMS 設定ソフトを起動します。
（ご使用の PC にシリアル USB ドライバが必要です。）

USB ケーブル MicroB
UMDI-41AXS
Windows PC

電源入力

UMS 設定ソフト

AC アダプタ又は DC 入力

USB ケーブル Type-C
UMDO-41AXS
Windows PC

電源入力

UMS 設定ソフト

AC アダプタ又は DC 入力

UMS 設定ソフトを起動すると以下の画面が表示されます。

18

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）
機器と接続した「COM ポート」をリストから選択し、「端末接続」ボタンをクリックします。
正常に接続すると以下の詳細設定画面が表示されます。
接続が失敗した場合は、機器の接続構成、電源状態を再確認後、「端末スキャン」ボタンをクリックして、接続の確認を行ってください。

4.3.1 端末情報機器の機種情報やソフトウェアバージョンなどが表示されます。

19

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

4.3.2 端末設定内容
内容
動作PAN ID周波数
ポーリング間隔

説明

設定範囲

機器の動作設定を行います。使用する組み合わせでマスターとスレーブが１対マスター／スレーブ／リピータとなるようにして下さい。
無線グループの設定行います。使用する組み合わせで同一の PANID を設定00h～FFhする必要があります。
無線の周波数の設定を行います。使用する組み合わせで同一の周波数を設0～37定する必要があります。(周波数一覧参照)
マスター機がポーリングを送信するタイミングを設定します。

0~255[ ×0.1 秒 ]中継機器を使用する場合に設定します。

-リピータの機器 ID を設定します。同一環境では重複しないように設定して下さ

33～48（マスター設定時のみ）
中継ルート設定（マスター設定時のみ）
リピータ ID(リピータ時）い。
無線通信ができなくなり通信エラー処理を開始するまでの時間を設定します。

通信エラー判定時間

1～60[秒]

本設定時間無線通信が行われない状態が継続すると通信エラー処理を行います。

ポート出力論理
通信エラー時出力

ステータス出力

デジタル出力ポートの出力論理を選択します。

正論理／負論理

無線通信エラー処理において、デジタル出力ポートの状態を選択します。出力OFF／保持ポートの状態を保持したい場合は保持を選択します。
UMDI-41AXS、UMDO-41AXS では、ステータス出力端子がない為、無効-です。

4.3.3 端末操作
各パラメータを変更後、書き込みボタンで書き込みを実行します。書き込み実行後、再起動ボタンで端末を再起動するか、電源 OFF→ON により再起動してください。
内容

説明

読出し

端末の設定内容を参照し、PC 画面に表示します。

書込み

PC 画面の設定を端末に送信し、端末は設定保存します。

無線通信テスト

無線通信テスト用の画面を開きます。

再起動

端末の再起動をします。

20

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

4.4 周波数一覧
周波数番号

使用周波数［MHz］

周波数番号

使用周波数［MHz］

0920.6

19924.4

1920.820924.6

2921.021924.8

3921.222925.04921.423925.2

5921.624925.4

6921.825925.6

7922.026925.8

8922.227926.09922.428926.2

10922.629926.4

11922.830926.6

12923.031926.813923.2

32927.014923.4

33927.2

15923.6

34927.4

16923.835927.6

17924.036927.8

18924.2

37928.021

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

4.5 設定例
マスターを UMDO-41AXS、スレーブを UMDI-41AXS とした場合

4.5.1 マスター側設定（UMDO-41AXS）

4.5.2 スレーブ側設定（UMDI-41AXS）

22

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

5 動作説明5.1 標準 1 対 1 通信
マスター側機器からスレーブ側機器に無線ポーリングを行います。
スレーブはマスターからの無線ポーリングを受信すると応答送信を行います。
無線通信データに入出力信号を付加することで、マスター、スレーブ間の信号伝送を行います。

マスター

無線通信

スレーブ

Tpoll
Tpoll

×Ttouｔ

・・・

内容

設定値

説明

マスター側ポーリング間隔

0.1[秒]UMS 設定ソフト：ポーリング間隔 0~255[ ×0.1 秒 ]設定により変更可

Tpoll
マスター側応答タイムアウト
Ttout

能です。0 の場合は、50ms となります。
0.1[秒]

マスター側ポーリング送信後、スレーブからの応答を監視する時間です。
この時間スレーブからの応答を受信できない場合に、タイムアウト後、マスターは次のポーリングタイミングで送信処理を行います。リピータ（中継器）を使用する場合は、リピータ台数*0.1 秒となります。

5.2 UMDI-41AXS のデジタル出力（OUT1）について
UMDI-41AXS のデジタル出力（OUT1）は、UMDO-41AXS との組み合わせで使用時は未使用です。

5.3 UMDO-41AXS のリレー出力について
UMDO-41AXS のリレー出力は、OUT1～OUT4 のいずれかが ON の場合に Close します。

23

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

OUT1

OUT2

OUT3

OUT4リレー出力（N.O）

OFF

OFF

OFF

OFF

Open

ON

OFF

OFF

OFF

Close

OFF

ON

OFF

OFF

Close

OFF

OFF

ON

OFF

Close

OFF

OFF

OFF

ON

Close

全て OFF 以外

Close

無線通信するマスター機器とスレーブ機器では周波数、PANID が同じ設定である必要があります。周波数の変更が必要な場合はそれぞれの機器に対し、UMS 設定ソフトを使用し、設定を行ってください。
無線送信開始前にキャリアセンスを行いますので、同一周波数が使用中の場合は無線送信できない場合があります。

24

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

6 アンテナタイプ
本製品は、以降のアンテナを使用可能（別売）です。

アンテナタイプ掲載のアンテナ以外は電波法違反となりますので、ご使用しないで下さい。

6.1 可倒式アンテナ
本体に可倒式アンテナを接続します。防滴・防塵が必要な場所でご使用の際は、樹脂ケースに入れてご使用ください。
写真は、UAS-AM01 を接続したものです。
UAS-AK01

UAS-AM01

1/4λモノポールアンテナ
全長 10.8cm

1/2λダイポールアンテナ
全長 20.4cm

6.2 プレート付アンテナ
本体にプレート付アンテナを接続します。本体を盤ケース内、アンテナを外部に取り付ける場合などにこのタイプを使用します。写真は、プレート付アンテナ UAS-PK01 と、設置金具 UAB-U01 を接続したものです。
UAS-PK01

設置金具

UAS-PM01

UAB-L01

設置金具
UAB-U01

1/4λモノポールアンテナ
ケーブル長 1ｍ [UAS-PM01]
ケーブル長 2ｍ [UAS-PM02]

1/2λダイポールアンテナ
ケーブル長 1ｍ [UAS-PK01]
ケーブル長 2ｍ [UAS-PK02]25

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

6.3 フランジ付アンテナ
本体にフランジ付アンテナを接続します。本体を盤ケース内、アンテナを外部に取り付ける場合などにこのタイプを使用します。写真は、フランジ付アンテナ UAS-FK01 を接続したものです。
UAS-FK01

設置金具
AMB-01

1/2λダイポールアンテナ
ケーブル長 1ｍ [UAS-FK01]
ケーブル長 2ｍ [UAS-FK02]

26

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）

7 本製品を使用する上での注意点◼ 金属製の物体の近くにアンテナを設置すると、通信距離が短くなることがありますので、なるべく離して設置してください。
◼ 本製品を屋外で使用する場合には防水ケースに入れるなどの対策が必要です。屋内であっても、湿気の多い場所、オイルミストや塵の多いところでは、防水ケースなどに入れて保護してください。
◼ 無線通信状態が良好な場所に本製品を固定してください。（設置する前に通信状態を確認してください。）◼ 本製品に強い力が加わると、破損する恐れがあります。
◼ 異なるユニットのアンテナ間は、できるだけ離してください。アンテナが近いと相互に影響し合うため、それぞれの無線通信に影響を与え、無線区間の再送が増加し通信可能距離が低下します。アンテナ間は 2m 以上離して設置してください。
◼ 同一エリアで本製品を 2 セット以上動作させる場合は、無線周波数を変えて使用して下さい。電波干渉の原因となります。

27

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）8 アフターサービス◼ 保証期間中の場合、保守規定ならびに保証書の記載内容に基づいて修理いたします。
◼ 保証期間経過後の場合、修理によって機能が維持できる場合はご要望により有料修理いたします。
◼ 備品の供給年限について本製品の補修用部品の供給及び保守対応の期限は、製造打ち切り後 5 年です。
ただし、供給年限内であっても、部品メーカーの生産及び市場供給が途絶えた場合などについては対応できない場合があります。
補修用部品の供給及び保守対応は、原則的に上記期限で終了いたしますが、供給期限経過後であっても必要部品の入手等が可能な場合には、納期および価格についてご相談させていただきます。

修理・点検・アフターサービスについては購入先または弊社までお問い合わせください。

28

UMDI-41AXS・UMDO-41AXS 取扱説明書（920MHz 帯 標準 1 対 1 通信）
2023 年 2 月 15 日

Version 1.00

株式会社 アローセブン〒 433－8122 静岡県浜松市中区上島 3 丁目 27 番 7 号
Tel : 053（469）0031
Fax : 053（469）0037
Web サイト : http://www.arrow7.co.jp/