敷設マニュアル（第２版）

著作権のお知らせ© Copyright 2006 ODVA, Inc. All rights reserved.
事前に ODVA から書面による許可を取得せずに、本書の一部を何らかの媒体で複製またはコピーしたり、他の言語に翻訳したりすることはできません。
CompoNet およびそのロゴは ODVA, Inc.の商標です。

ODVA
4220 Varsity Drive, Suite A
Ann Arbor, MI 48108-5006
USA
電話：1-734-975-8840
ファクス：1-734-922-0027
www.odva.org

2

目次

目次
はじめに

本書について ······························································ 5
本書の対象者 ········································································································ 5
本書の内容 ··········································································································· 5

第1章

ネットワーク敷設手順 ·················································· 6フローチャート ····································································································· 6

第2章

ネットワーク構成の概要 ··············································· 7
ネットワーク構成要素 ···························································································· 7セグメント ········································································································· 10接続形態 ············································································································ 11
分岐パターン ······································································································ 12
延長 ·················································································································· 14
終端抵抗 ············································································································ 14
実配線例 ············································································································ 16

第3章

ネットワーク構成の制限 ············································· 18
制限事項の概要 ··································································································· 18
伝送速度別の制限事項 ·························································································· 19

第4章

通信電源の供給方法 ··················································· 26
フラットケーブル使用時 ······················································································· 26
丸型ケーブルⅠ使用時 ·························································································· 26
許容電流制限 ······································································································ 28
電源 ·················································································································· 28

第5章

接続機器の選定 ························································· 29
通信ケーブル ······································································································ 29
コネクタ ············································································································ 31

第6章

ユニットの表示と設定 ················································ 35
表示部 ··············································································································· 35
設定部 ··············································································································· 36

第7章

取付けと配線 ···························································· 37
コネクタの圧接加工方法（フラットケーブルⅠの場合）············································· 37
コネクタの圧接加工方法（フラットケーブルⅡの場合）············································· 39
T 分岐コネクタの加工 ·························································································· 41
丸型ケーブルⅠの加工方法 ···················································································· 43
ノイズ対策上の留意事項 ······················································································· 44

3

目次

第8章

配線チェックリスト ···················································· 45
ネットワーク設計チェック ····················································································45
ユニット設定チェック ··························································································45
配線チェック·······································································································45

付録

接続関連機器一覧 ······················································· 46
マスタ・スレーブユニット ····················································································46
ケーブル・電線····································································································46
コネクタ·············································································································46
リピータ·············································································································46
終端抵抗·············································································································46
電源 ···················································································································46
工具 ···················································································································46

4本書についてはじめに本書について本書の対象者
本書は、CompoNet を使った産業用制御システムの設計、インプリメンテーション、
および保守を担当する制御系エンジニアが使用することを意図して作成されています。本書では、必要となる敷設、確認、トラブルシューティングの方法を解説します。

本書の内容
本書は、CompoNet 製品をネットワーク構築する際に、事前に検討しておくべき事柄
や、制限事項および、敷設に必要な機器の選定、施工上の留意点、手順などを示します。
本書を活用することにより、CompoNet のネットワーク構築を迅速かつスムーズに設計・施工し、立ち上げトラブルを未然に防ぐことができます。
本書に関するお問合せは、巻末に記載しております ODVA 日本支部までご連絡お願いいたします。
なお、本書は「CompoNet 仕様書」に準じていますが、一部 ODVA 日本ベンダ協議会
が独自に推奨している事項があります。それらについては、事項毎にその旨の記載をしています。

5

ネットワーク敷設手順

第1章

ネットワーク敷設手順
フローチャート
以下に CompoNet を使用した機器・設備の設計から立ち上げまでの手順をフローチャートで示しています。なお、この手順は CompoNet 仕様書に規定された内容ではありません。

ネットワーク仕様の決定
配置・通信速度・配線長・ケーブル種類

第 3 章へ

電源容量・給電方法決定第 4 章へチェックリストで確認

第 8 章へ必要機器の選定

第 5 章へ

敷設工事

第 7 章へチェックリストで確認

第 8 章へマスタユニット設定
第 6 章へスレーブユニット設定

チェックリストで確認

設定完了

6

第 8 章へネットワーク構成の概要

第2章

ネットワーク構成の概要
ネットワーク構成要素
以下に CompoNet の標準的なトポロジを示します。

7

ネットワーク構成の概要

ネットワークを構成する要素は次のとおりです。

●通信ケーブル
本ネットワークでは通信ケーブルとして、丸型ケーブルⅠ※1、丸型ケーブルⅡ※1、フラットケーブルⅠおよびフラットケーブルⅡ（シース付）を使用します。
※1）CompoNet に適合するメーカおよび型番は、ODVA HP でご確認ください。
（http://securesite.jp/ODVA/catalog/cn_catalog.html）●マスタユニット
本ネットワークを管理し、PLC と各スレーブユニットとの I/O データのやり取りをおこないます。マスタユニットはネットワーク全体で 1 台のみ接続します。また、マス
タユニットは幹線の端に接続する必要があります。

●スレーブユニット
本ネットワークを通じてマスタユニットから受け取った OUT データを出力します。
また、入力された IN データをネットワーク経由でマスタユニットに送ります。
スレーブには使用点数の大小により、2 種類のタイプが存在します。
・ワードスレーブ：16 点単位で割り付けられるスレーブ
・ビットスレーブ：2 点単位で割り付けられるスレーブ●リピータユニット
リピータユニットを使用することで、次のような接続性の拡張ができます。
・ケーブルの延長
・接続ノード数の増加
・幹線または副幹線からの長距離 T 分岐
・ケーブル種類の変換（丸型ケーブルⅠ、丸型ケーブルⅡ、フラットケーブルⅠ、フラットケーブルⅡ間の変換）
リピータユニットのマスタポート（副幹線）は、幹線と同じ通信仕様（距離、台数）で配線することが可能です。
マスタユニットから直列に接続して延長する場合は、2 段まで接続可能です。
マルチドロップ接続を併用することで、1 ネットワーク（1 マスタ）で最大 64 台接続可能です。なお、リピータユニットには、次の 2 つのポートが存在します。
・マスタポート
マスタポートは終端抵抗を内蔵しているポートです。マスタユニットまたは、リピー
タユニットの下流側のポートです。
・スレーブポート
スレーブポートは終端抵抗を内蔵していないポートです。スレーブユニットまたは、
リピータユニットの上流側のポートです。

8

ネットワーク構成の概要●終端抵抗本ネットワークでは幹線の端にマスタユニットを配置し、もう一方の幹線の端には終端抵抗を接続します。
また、リピータユニットをご使用になる場合は、リピータユニットマスタポート側の、最も離れた端に取り付けます。
注：終端抵抗は伝送路の品質を満足させるために必ず接続する必要があります。

●幹線・支線
本ネットワークでは幹線・支線を以下のとおり定義しています。
・幹線：マスタユニットから終端抵抗までの伝送路
・副幹線：リピータユニットから終端抵抗までの伝送路
・支線：幹線または副幹線から、T 分岐させた伝送路
・副支線：支線から、T 分岐させた伝送路（この副支線から T 分岐することは不可）
注：1 セグメント内では、同じ種類のケーブルを使用します。
（フラットケーブルⅠとⅡのように異なる種類のケーブルを混在することはできません）
異なるセグメントでは、異なる種類のケーブルを混在することが可能です。

●分岐
分岐の方法には、以下の 2 つの方法があります。
1）マルチドロップ方式
・圧接コネクタ－マルチ配線用コネクタによるマルチドロップ
・オープン型コネクタプラグによるマルチドロップ
2）T 分岐方式
・市販の中継端子台による T 分岐
・圧接コネクタによる T 分岐

●通信電源
市販の DC24V 電源を使用します。
通信電源は「幹線」「副幹線」に 1 箇所だけ接続することができます。
「幹線」へはマ
スタユニットから、「副幹線」へはリピータユニットから通信電源を供給します。
複数の「幹線」「副幹線」に対して、1 台の電源を共通の通信電源として供給することはできません。

9ネットワーク構成の概要

セグメント●セグメントの階層
CompoNet は、リピータユニットにより分けられたセグメントを構成します。各セグ
メントはネットワーク上では接続されていますが、電気的には分離されています。この分離された区間をセグメントと呼び、マスタユニットから順番に数えて、第 1 セグ
メント、第 2 セグメント、第 3 セグメントと呼び、3 階層まで形成することができます。すなわちリピータユニットは、最大 2 段まで増設することが可能です。
なお、1 ネットワーク（1 台のマスタユニット）で使用できるリピータユニットは、
マルチドロップ接続されたリピータユニットも含めると、最大 64 台となります。

マスタ
第 1 セグメント

スレーブ

1 段目リピータ

1 段目リピータ
第 2 セグメント

スレーブ

2 段目リピータ

2 段目リピータ
第 3 セグメント

スレーブ

スレーブ

スレーブ

●1 セグメントあたりのユニット数
同一セグメント内でスレーブユニットとリピータユニット合せて 32 台まで接続できます。

スレーブユニットとリピータユニット合せて 32 台接続可能

10

ネットワーク構成の概要

接続形態
CompoNet の接続形態をケーブルの種類で分類すると、次のようになります。

●丸型ケーブルⅠ／Ⅱの場合の接続形態
マスタユニットの接続

スレーブ/リピータの接続

オープン型コネクタプラグ

オープン型コネクタプラグ

マスタユニット

オープン型
コネクタプラグ

支線または副支線

ケーブルの分岐T 分岐接続マルチドロップ接続

市販中継端子台

オープン型コネクタプラグ

中継端子台
または支線

幹線/副幹線

オープン型
コネクタプラグ

幹線/副幹線
または支線

オープン型
コネクタプラグ

スレーブ/リピータ

支線または副支線幹線

スレーブ/リピータ

スレーブ/リピータ●フラットケーブルの場合の接続形態
マスタユニットの接続

スレーブ/リピータの接続

フラットコネクタⅠプラグ

フラットコネクタⅠプラグ

マスタユニット

フラットコネクタⅠ
プラグ

ケーブルの分岐T 分岐接続フラットコネクタⅠソケット

マルチドロップ接続
マルチ配線用コネクタ／フラットコネクタⅠプラグ
フラットコネクタⅠ
プラグ

マルチ配線用コネクタ
幹線/副幹線

支線または副支線

または支線

フラットコネクタⅠソケット
幹線/副幹線または支線

スレーブ/リピータ

支線または副支線幹線

スレーブ/リピータ

フラットコネクタ
Ⅰプラグ

フラットコネクタⅠプラグ（またはケーブル付属）

フラットコネクタⅠ

フラットコネクタⅠ

プラグ

プラグ

注：フラットケーブルⅡはマル
スレーブ/リピータ

チ配線用コネクタを使用したマルチドロップ接続は不可。

11

ネットワーク構成の概要

分岐パターン
接続形態から、ケーブル毎の詳細な分岐パターンは次のとおりです。

●T 分岐：フラットケーブルⅠの場合
フラットコネクタⅠプラグ

フラットコネクタⅠ
ソケット

曲げ寸法は各ケーブルメーカの仕様にしたがってください。

スレーブ●T 分岐：フラットケーブルⅡ（シース付）の場合
フラットコネクタⅡプラグ

フラットコネクタⅡ
ソケット
スレーブ

曲げ寸法は各ケーブルメーカの仕様にしたがってください。

● T 分岐：丸型ケーブルⅠ／Ⅱ使用時（市販中継端子台を使用）
例：丸型ケーブルⅠの場合

中継端子台

スレーブ

12

ネットワーク構成の概要●マルチドロップ：フラットケーブルの場合（シース付含む）

フラットコネクタⅠ
プラグ

マルチ配線用コネクタ

スレーブ／
リピータユニット●マルチドロップ：丸型ケーブルⅠ／Ⅱの場合
M3 端子台オープン型コネクタ
プラグ
通信コネクタスレーブ／
リピータユニット

13

ネットワーク構成の概要

延長
幹線・副幹線・支線・副支線は、フラットコネクタⅠ（Ⅱ）ソケットおよびフラット
コネクタⅠ（Ⅱ）プラグにより、ケーブルを延長できます。
フラットコネクタⅠソケット

フラットコネクタⅠソケット
幹線／副幹線

幹線／副幹線

終端抵抗

フラットコネクタⅠ
プラグ

フラットコネクタⅠ
プラグ

終端抵抗
終端抵抗は、幹線・副幹線の片端に 1 個だけ接続します。マスタユニットには終端抵抗が内蔵されているので接続不要です。

マスタユニット

幹線の終端抵抗はマスタ
ユニットの反対側に 1 個だ
け配置してください。

マスタユニットは幹線の端に配置してください。
マスタユニット側には終端抵抗は接続しないでください。

終端抵抗

幹線
b

リピータ

a
スレーブ

副幹線
リピータ側には終端抵抗は接続しないでください。

スレーブ

ケーブル端間際の分岐箇所は、ケーブル長が a＞b となるようしてください。

支線の端には終端抵抗を配置しないようにしてください。

スレーブ

終端抵抗

14

副幹線の終端抵抗はリ
ピータの反対側に 1 個だ
け配置してください。

ネットワーク構成の概要●方法 1
幹線（または副幹線）ケーブルに、フラットコネクタⅠ（Ⅱ）ソケットを接続し、そのコネクタに終端抵抗を挿入する方法
フラットケーブルⅠの場合

フラットコネクタ フラットケーブルⅠ用コネクタ型終端抵抗器
Ⅰソケット

フラットケーブルⅡの場合

フラットコネクタⅡ
ソケット

フラットケーブルⅡ用コネクタ型終端抵抗器●方法 2
スレーブ/リピータ（スレーブポート）の通信コネクタにマルチ配線用コネクタを装着し、そのコネクタに幹線（または副幹線）ケーブルとコネクタ型終端抵抗器を挿入する方法
フラットケーブルⅠの場合
フラットケーブルⅠ用コネクタ型
終端抵抗器

フラットコネクタⅠ
プラグ

マルチ配線用コネクタ
通
信
コ
ネ
ク
タ

スレーブ／リピータ（スレーブポート）●方法 3幹線（または副幹線）ケーブルに終端抵抗付き端子台を接続する方法
丸型ケーブルⅠの場合

丸型ケーブルⅡの場合

15

ネットワーク構成の概要

実配線例●フラットケーブルⅠで T 分岐の例

16

ネットワーク構成の概要●フラットケーブルⅠでマルチドロップの例●丸型ケーブルⅠの場合

17

ネットワーク構成の制限

第3章

ネットワーク構成の制限
制限事項の概要
CompoNet は、ケーブルの種類によって、ネットワーク構成の制限があります。

●丸型ケーブルⅠの場合
伝送速度

最大

接続

最大

幹線長

スレーブ

支線長

支線総長

台数

1 支線あたりで

副支線

副支線

接続可能な

最大長

総長

スレーブユニット
最大台数

4Mbit/s
3Mbit/s
1.5Mbit/s
93.75kbit/s

30m

32

0m

0m

0

0m

0m

30m

32

0.5m

8m

1

0m

0m

100m

32

0m

0m

0

0m

0m

30m

32

2.5m

25m

3

0m

0m

500m

32

6m

120m

1

0m

0m

1 支線あたりの

副支線

副支線

スレーブユニット

最大長

総長※表中の値は全て 1 セグメントあたりの制限事項となります。

●丸型ケーブルⅡ、フラットケーブルⅠ／Ⅱの場合
伝送速度

最大

接続

最大

幹線長

スレーブ

支線長

支線総長

台数

最大台数

4Mbit/s

30m

32

0m

0m

0

0m

0m

3Mbit/s

30m

32

0.5m

8m

1

0m

0m

1.5Mbit/s

30m

32

2.5m

25m

3

0.1m

2m

93.75kbit/s

200m

32

配線長 200m 以内のフリー配線※表中の値は全て 1 セグメントあたりの制限事項となります。

18

ネットワーク構成の制限

伝送速度別の制限事項
前述のケーブル種類別の制限事項を通信速度別に図にすると、次のようになります。

●配線例（伝送速度：4Mbit/s 時）
マスタ
30m×3セグメント(リピータ2段) = 9 0 mMAX

フラットケーブルⅠ・ Ⅱ
丸型ケーブルが使用可能

3 0 m（1セグメントの最大長）

リピータ1段目

マルチドロップ接続可能

リピータ2段目

幹線･副幹線の最後は必ず終端抵抗を接続
幹線(第1セグメント)
副幹線(第2セグメント)
副幹線(第3セグメント)
副幹線(無効)支線
副支線

幹線および副幹線からのT分岐接続不可(マルチドロップ接続のみ可能)

終端抵抗

リピータ3段目

リピータは2 段まで接続可能
このリピータは3段目

スレーブユニット
リピータユニット●制限事項（4Mbit/s 設定時（T 分岐接続不可））19

ネットワーク構成の制限●配線例（伝送速度：3Mbit/s 時）
フラットケーブルⅠ・ Ⅱ
丸型ケーブルが使用可能

マスタ
30m×3セグメント(リピータ2段) = 9 0 mMAX
3 0 m（1セグメントの最大長）

リピータ1段目

マルチドロップ
接続可能

1m以上

幹線･副幹線の最後には必ず終端抵抗を接続
リピータ2段目

支線あたりの接続台数は
1 台のみ
支線個所制限より、支線は
1 m以内に3 本まで
幹線(第1セグメント)
副幹線(第2セグメント)
副幹線(第3セグメント)
副幹線(無効)支線
副支線

T分岐接続可能支線からのT分岐接続不可

リピータ3段目

終端抵抗
スレーブユニット
リピータユニット
リピータは2 段まで接続可能
このリピータは3段目●制限事項（3Mbit/s 設定時）

20

ネットワーク構成の制限

21

ネットワーク構成の制限●配線例（伝送速度：1.5Mbit/s 時）
マスタ

フラットケーブルⅠ・ Ⅱ
丸型ケーブルが使用可能

30m×3セグメント(リピータ2段) = 9 0 mMAX
ただし、丸型ケーブル(支線なし時)は3 0 0 mMAX
3 0 m（1セグメントの最大長）
ただし、丸型ケーブル(支線なし時)は1 0 0 m

リピータ1段目

マルチドロップ
接続可能

1m以上

幹線･副幹線の最後には必ず終端抵抗を接続

幹線(第1セグメント)
副幹線(第2セグメント)
副幹線(第3セグメント)
副幹線(無効)支線
副支線

リピータ2段目

支線からのT分岐接続可能(フラットケーブルⅠ・Ⅱ使用時のみ)

支線個所制限より、支線は
1 m以内に3 本までT分岐接続可能(丸型ケーブル支線なし時不可)

リピータ3段目

終端抵抗
スレーブユニット
リピータユニット

リピータは2 段まで接続可能
このリピータは3段目●制限事項（1.5Mbit/s 設定時）

※1：
「支線あたり接続台数制限」は、1 支線にマルチドロップ接続または T 分岐接続（副支線）で、接続可能なスレーブまたはリピータユニットの最大台数です。
※2：リピータユニットを含めた台数です。
※3：T 分岐接続できません。
（マルチドロップ接続のみ可）22

ネットワーク構成の制限●配線例（伝送速度：93.75kbit/s 時）
丸型ケーブルⅠ使用時の制限事項
マスタ

フラットケーブルⅠ・ Ⅱ
丸型ケーブルが使用可能

丸型ケーブル使用時
500m×3セグメント(リピータ2段) = 1 5 0 0 mMAX
丸型ケーブル使用時5 0 0 m（1セグメントの最大長）

リピータ1段目

マルチドロップ
接続可能

1m以上

幹線･副幹線の最後には必ず終端抵抗を接続

支線あたりの接続台数は
1 台のみ(丸型ケーブル使用時)

支線個所制限より、支線は
1 m以内に3 本まで(丸型ケーブル使用
時のみ)

リピータ2段目

T分岐接続可能幹線(第1セグメント)
副幹線(第2セグメント)
副幹線(第3セグメント)
副幹線(無効)支線
副支線

リピータ3段目

終端抵抗
リピータは2 段まで接続可能
このリピータは3段目

スレーブユニット
リピータユニット

フラットケーブルⅠ・Ⅱ使用時は、1セグメントあたりの総配線長200m(リピータ使用時600m)フリー配線●制限事項（93.75kbit/s 設定時）

23

ネットワーク構成の制限

24

ネットワーク構成の制限●配線例（伝送速度：93.75kbit/s 時）
フラットケーブルⅠ・Ⅱ使用時の制限事項（フリー配線）
フリー配線は、幹線と支線の区別がない接続形態です。1 セグメントあたりの総配線
長 200m 以内であれば、分岐の回数に制限無く配線することが可能です。
・マスタユニットは、ネットワーク上のどこでも配置ができます。
・終端抵抗はマスタポートからセグメント上の一番遠い端に取付けます。
マスタユニット

終端抵抗
リピータユニット
スレーブ
スレーブ
終端抵抗

スレーブ
スレーブ
スレーブ

25

通信電源の供給方法

第4章

通信電源の供給方法
丸型ケーブルⅡまたはフラットケーブル使用時
マスタユニットの「通信電源供給用コネクタ」に、通信電源（BS+、BS-）を接続します。これにより、フラットケーブルから、幹線上のスレーブへ通信電源を供給します。
注 1：幹線または副幹線 1 本に対して、通信電源の供給は、1 箇所のみが可能です。
注 2：副幹線への給電は、リピータの「マスタポート通信電源供給用コネクタ」に接続します。

丸型ケーブルⅠ使用時
スレーブ、リピータユニット※1 に通信電源（BS+、BS-）を個別に供給します。
マスタユニットの通信電源供給コネクタには給電しません。
※1）リピータユニット自体の通信電源の配線は、スレーブポートの BS＋、BS-に供給することが必要です。

26

通信電源の供給方法

電源は個別に給電しても構いません。
CompoNet マスタユニット

スレーブへは通信用信号線
を並列接続（パラ取り）します。＊

BDH
BDL

専用終端抵抗（121Ω）

通信用信号線×2 本

×

×
×

×
通信

通信

通信

スレーブ

BS-

× ×

BS+

× ×

BDL BDH

BS-

× ×

BS+

× ×

BDL BDH

通信電源 DC24V

スレーブ

スレーブ

BS-

× ×

BS+

× ×

BDL BDH

通信電源 DC24V

通信電源 DC24V＊ ：信号線の並列接続の方法は、市販の中継端子台、マルチドロップ（スレーブでの直接渡り配線）のいずれでもかまいません。

マスタユニットの幹線またはリピータユニットのマスタ側の幹線と、スレーブ側の副幹線の電源は、必ず別電源とすることが必要です。

27

通信電源の供給方法

許容電流制限各スレーブの消費電流合計が、通信ケーブルや通信用コネクタの許容電流を超えないよう注意してください。
フラットコネクタⅠプラグ(5A 以下)フラットコネクタ
Ⅰプラグ(5A 以下)

ケーブル
マスタ

終端抵抗

(a)

電源
(DC24V)

スレーブ
消費電流 I1

スレーブ
消費電流 I2

スレーブ
消費電流 I3

スレーブ
消費電流 In※電圧降下による各ユニットの電源電圧は、14V 以上としてください。

電源
電源の仕様は、下表を満足するものを選択してください。

28

仕様

パラメータ

出力電圧

24V±10％

出力リップル

600mV p-p（最大）

温度範囲

ベンダ指定

過電圧保護

あり

過電流保護

あり

電源投入時オーバーシュート

最大 5％

出力電流

最大 5A

絶縁

AC2.3kV（IEC61131 準拠）

接続機器の選定

第5章

接続機器の選定
通信ケーブルCompoNet で使用可能な通信ケーブルの仕様を示しています。
市販の汎用ケーブルを使用する場合は、この仕様を満足するものを選択するようにしてください。
種類
丸型ケーブルⅠ、Ⅱ仕様
公称断面積：（導体径）0.75mm2
仕上がり径：φ2.3mm
CompoNet 適合品をメーカに確認してご使用ください。

フラット

標準

ケーブルⅠ

4 芯フラットケーブル
導体径：0.75mm2×2 本、0.5mm2×2 本。
CompoNet 仕様に準拠したケーブルをご使用ください。

フラット

シース付き

ケーブルⅡ

シース付き 4 芯フラットケーブル
導体径：0.75mm2×2 本、0.5mm2×2 本。
CompoNet 仕様に準拠したケーブルをご使用ください。

●丸型ケーブルⅠ外観●丸型ケーブルⅡ外観

29接続機器の選定

赤：BS+

白：BDH 青：BDL

Φ2.54±0 . 0 6●フラットケーブルⅠ外観

黒：BS-

2.54±0.06

10.16 －00 . 0 0●フラットケーブルⅡ外観
2.20±0.52.54±0.1

2-R1

赤：BS+ 白：BDH 青：BDL 黒：BS-30

Φ2.54±0.06

4.56±0.2

2-R2.1

12.15±0.3接続機器の選定

コネクタ
CompoNet は、通信ケーブルに以下のコネクタを接続することにより、ケーブルの延長、分岐、スレーブとの配線などが可能となります。

●フラットコネクタⅠソケット（フラットケーブルⅠ用）
通信ケーブル
名称

外観

用途

フラット

以下の用途で、フラットコネクタⅠプラグとセットで使コネクタⅠソケ用します。

ット

・幹線または副幹線を延長するとき・幹線または副幹線を、支線に T 分岐するとき（○：使用可能、×使用不可）
丸型ケー 丸 型 ケ ー フラット フラット
ブルⅠ
ブルⅡ
ケーブル ケーブル
Ⅰ
Ⅱ

×

○
（注）

○

×

・支線を副支線に T 分岐するとき（注）丸型ケーブルⅡの場合、終端抵抗を接続する場合のみ使用します。

● フラットコネクタⅡソケット（フラットケーブルⅡ用）
通信ケーブル
名称

外観

用途

フラット

以下の用途で、フラットコネクタⅡプラグとセットで使

コネクタⅡ

用します。

ソケット

・幹線または副幹線を延長するとき（○：使用可能、×使用不可）
丸型ケー 丸 型 ケ ー フラット フラット
ブルⅠ
ブルⅡ
ケーブル ケーブルⅠ
Ⅱ

×・幹線または副幹線を、支線に T 分岐するとき・支線を副支線に T 分岐するとき

×

○

×

注：ビットスレーブ（IP54 タイプ）接続時に使用します。

31

接続機器の選定● フラットコネクタⅠプラグ（フラットケーブルⅠ用）
通信ケーブル
名称

外観

フラット

用途

（○：使用可能、×使用不可）
丸型ケー 丸 型 ケ ー フラット フラット
ブルⅠ
ブルⅡ
ケーブル ケーブルⅠⅡa）以下の用途で、フラットコネクタⅠソケットとセット

コネクタⅠ

で使用します。

プラグ

・幹線または副幹線を延長するとき・幹線または副幹線を、支線に T 分岐するとき・支線を副支線に T 分岐するときb）以下の用途で、単独で使用します。

×

×

○

×

・通信ケーブルをユニット（マスタ/ワードスレーブ/リピ
ータユニット）に接続するとき・通信ケーブルをマルチ配線用コネクタに接続するとき● フラットコネクタⅡプラグ（フラットケーブルⅡ用）
通信ケーブル
名称

フラット
コネクタⅡ
プラグ

外観

用途

（○：使用可能、×使用不可）
丸型ケー 丸 型 ケ ー フラット フラット
ブルⅠ
ブルⅡ
ケーブル ケーブルⅠⅡa）以下の用途で、フラットコネクタⅡソケットとセットで使用します。
・幹線または副幹線を延長するとき・幹線または副幹線を、支線に T 分岐するとき・支線を副支線に T 分岐するときb）以下の用途で、単独で使用します。
・通信ケーブルをユニット（マスタ/ワードスレーブ/リピ
ータユニット）に接続するとき・通信ケーブルをマルチ配線用コネクタに接続するとき
注：ビットスレーブ（IP54 タイプ）接続時に使用します。

32

×
×

×

○

接続機器の選定● マルチ配線用コネクタ
通信ケーブル
名称

外観

用途

マルチ配線用コネク

2 つのフラットコネクタⅠ（Ⅱ）プラグを、2 つのポート

タに接続します。

（○：使用可能、×使用不可）
丸型ケー 丸 型 ケ ー フラット フラット
ブルⅠ
ブルⅡ
ケーブル ケーブルⅠ
Ⅱ

ユニット（マスタ/スレーブ/リピータユニット）を、幹線、
副幹線、または支線に、マルチドロップ配線する際に使

×

用します。

×

○

×

注：通信速度が 4M ビット/s の場合、
（おもに専用ケーブ
ル使用時）本コネクタを使用して、ワードスレーブのみを接続してください。

● オープン型コネクタプラグ（端子台タイプ）
通信ケーブル
名称

外観

用途

オープン型

丸型ケーブルⅠ／Ⅱをスレーブ／リピータユニットに接コネクタ

続する場合、ユニットの通信用コネクタをねじ式端子台

プラグに変換します。端子台サイズは M3 です。

（○：使用可能、×使用不可）
丸型ケー 丸 型 ケ ー フラット フラット
ブルⅠ
ブルⅡ
ケーブル ケーブル
Ⅰ
Ⅱ

×

×

○

×

33

接続機器の選定● 終端抵抗通信ケーブル
名称

外観（○：使用可能、×使用不可）
丸型ケー 丸 型 ケ ー フラット フラット
ブルⅠ
ブルⅡ
ケーブル ケーブル
Ⅰ
Ⅱ

用途

フラットケーブ

コネクタ型の終端抵抗器です。

ルⅠ用コネクタ幹線（副幹線）ケーブルにフラットコネクタⅠ（Ⅱ）ソ型終端抵抗器

ケットを接続し、コネクタ部にこのコネクタ型終端抵抗

×

○

○

×

×

×

○

×

×

×

器を挿入します。
フラットケーブ

コネクタ型の終端抵抗器です。

ルⅡ用コネクタ幹線（副幹線）ケーブルにフラットコネクタⅠ（Ⅱ）ソ型終端抵抗器

ケットを接続し、このコネクタ型終端抵抗器を挿入しま×

す。
注：IP54 タイプのビットスレーブ接続時に使用します。
終端抵抗付端子終端抵抗付きの端子台です。

台○

終端抵抗に市販の抵抗を使用される場合は、下表の仕様としてください。
項目

特性

定格出力

1/4（W）

抵抗

121（Ω）

精度

1％以下
金属皮膜

34

ユニットの表示と設定

第6章

ユニットの表示と設定
設定方法の詳細は、各メーカの取扱説明書を確認してください。
ここでは、オープン仕様で規定されている表示と設定について記載しています。

表示部●通信用 LED（マスタユニットの場合）
通信用 LED として以下の LED を実装しています。設定時およびトラブルシューティ
ング時の参考にしてください。
・MS(Module Status)：ノード自身の状態を示します（緑／赤の 2 色表示）
・NS(Network Status)：通信の状態を示します（緑／赤の 2 色表示）
・SD(Send Data)：マスタの送信状態を示します（黄の 1 色表示）
・RD(Receive Data)：マスタの受信状態を示します（黄の 1 色表示）
LED 名称LED 状態

MS

状態定義

意味

緑点灯

正常状態

ユニット正常動作中。

赤点灯

致命的な異常ユニットハード異常（ウォッチドッグタイマ（WDT）
異常を含む）

NS

赤点滅

軽微な異常

モード No.、または号機 No.の設定異常

消灯

電源 OFF／準備中

電源 OFF／リセット中／初期処理中

緑点灯

オンライン／リモート I/O

電源が供給され、リモート I/O 通信が起動していて、通信動作中

かつ 1 つのスレーブまたはリピータも通信異常が発生していない、登録テーブル異常が発生していない、
1 つのスレーブまたはリピータもノードアドレス二重異常が発生していない。

緑点滅

オンライン／リモート I/O

リモート I/O 通信開始前、通信準備中

またはリモート I/O 通信停止中（通信異常により通信停止以外）

赤点灯

致命的な通信関連の異常

通信回路に異常が発生している。

赤点滅

軽微な通信関連の異常

1 つ以上のスレーブまたはリピータが通信異常となっている。
または 1 つ以上のスレーブで照合異常（スレーブ不在）/照合異常（未登録スレーブ）が発生している。
または通信異常により通信停止
または不正構成異常（リピータ段数異常）
または 1 つ以上のスレーブまたはリピータがアドレ
ス二重異常となっている。

SD
RD

消灯

電源 OFF／準備中

電源 OFF／リセット中／初期処理中

黄点灯

正常送信中

マスタから正常フレーム送信中

消灯

非送信

マスタ非送信状態

黄点灯

正常受信中

スレーブから正常フレーム受信中

消灯

非受信

マスタ非受信状態

スレーブユニットには MS と NS のみの表示となります。

35

ユニットの表示と設定

設定部
●スイッチ
マスタユニット
マスタユニットには、伝送速度設定スイッチが実装されています。
使用する伝送速度に合せた設定を、各メーカの説明書を見て実施してください。
伝送速度

スイッチ設定4Mbit/s
3Mbit/s
1.5Mbit/s
93.75kbit/s

0
1
2
3

スレーブユニット
スレーブユニットには、ノードアドレスを設定するためのスイッチが実装されています。通信設定に関するスイッチ設定は、このノードアドレスのみです。
伝送速度はマスタユニットの設定に自動追従します。よって設定スイッチはありません。

①ワードスレーブユニットの場合
4 5
2
1

0

4 5

6

3

7

3

8

2

9

設定範囲： 0～63

6
7

64 以上のアドレスは通信に参加できません

8
1

×10

0

9

×1

②ビットスレーブユニットの場合
4 5

4 5

6
7

3
2

8
1

0

9

7
9

0

7
8
1

×10
4 5

ON

×100

4 5

6
7

3

2

8

2

128 以上のアドレスは通信に参加できません

9

×10

6
7
8

1

9

0

0

×1

3
1

OFF

設定範囲: 0 ～ 127

6

3
2

8
1

×100

4 5

6

3
2

0

9

×1

③リピータユニットの場合
4 5
2
1

0

×10

36

4 5

6

3
9

7

3

8

2

設定範囲： 0～63

6
7
8

1

0

×1

9

64 以上のアドレスは通信に参加できません

取付けと配線

第7章

取付けと配線
ケーブル毎の配線方法を次に示します。

コネクタの圧接加工方法（フラットケーブルⅠの場合）●専用工具
専用工具以外での圧接加工は、接続不良・コネクタ破損の原因になることがあります。
必ず専用工具で作業してください。

●ケーブルの末端部の加工
ケーブルを長手方向に垂直に切断します。

末端は短絡を防止するため、芯線の露出が無いようにしてください。

●フラットコネクタⅠプラグの加工方法
ケーブル識別シールとケーブルの色を合せ、ケーブルを挿入します。カバーは半透明になっているので、ケーブルが奥まで入っていることを確認します。
専用工具を用いて圧接結線します。
専用工具
この位置までケーブルが挿入されていることを確認してください。

37

取付けと配線●フラットコネクタⅠソケットの加工方法
延長用または終端用の場合、ケーブルはそのコネクタまでの配線となるため、事前にケーブルストッパを作ります。
（この作業は、延長用または終端用の場合のみ）
ケーブルストッパ

音がして、戻らなくなるまで押さえる

ケーブル識別シールとケーブルの色を合せ、ケーブルを乗せます。
カバーではさみ込み、フックをかけて固定します。

延長用/終端用：ケーブルを、ストッパ作成済みのカバーの奥まで挿入します。

ストッパの位置

ケーブル識別シールとケーブルの色が合っていることを再度確認し、カバーにハウジ
ングを仮固定します。
専用工具を用いて圧接結線します。
専用工具

38

取付けと配線

コネクタの圧接加工方法（フラットケーブルⅡの場合）●専用工具
専用工具以外での圧接加工は、接続不良・コネクタ破損の原因になることがあります。
必ず専用工具で作業してください。

●ケーブルの末端部の加工延長用または終端用に使用するケーブルを長手方向に垂直に切断します。

短絡防止のため、切断は鋭利な刃物で行い、芯線のひげなどが無いように確認してください。

●フラットコネクタⅡプラグの加工方法
ケーブルの白線が図の方向になるようにケーブルを挿入します。ケーブルが奥まで入っていることを確認します。
図のように、ケーブルの端面を合わせながらセットします。
この際、ケーブル端面の赤い線がカバーの反対方向にくるように、ケーブルをセットしてください。
白線

ケーブルの端面の線色が左から、赤、白、青、黒になっていることを確認してください。

39

取付けと配線

ケーブルが抜けないようにカバーを閉じます。

40

取付けと配線専用工具を用いて圧接結線します。
下図のとおり、各コネクタを専用圧接工具の圧接ブロックにセットして、矢印の方向に圧接します。
フラットコネクタⅡプラグ

専用工具

圧接後、ケーブルが正しく圧接されたことを確認します。
フラットコネクタⅡプラグ

ロックがされていること

この面に隙間がないこと

T 分岐コネクタの加工
ストッパのセット（延長用または終端用の場合のみ）
延長用または終端用の場合、ケーブルはそのコネクタまでの配線となるため、事前にケーブルストッパをセットします。
カバーにケーブルを通し、端末をケーブルストッパに当てて、位置決めしてください。

ストッパ

・T 分岐用

・延長用/終端用
白線

41

取付けと配線

カバーを閉じます。

専用工具を用いて圧接結線します。
下図のとおり、コネクタを専用工具の圧接ブロックにセットして圧接します。
フラットコネクタⅡソケット

圧接が確実にできたか、確認してください。

42

専用工具

取付けと配線

丸型ケーブルⅠ／Ⅱの加工方法
ここでは、丸型ケーブルⅠの場合を例に加工方法について説明します。
（丸型ケーブルⅡの場合は、信号線が４線になるだけで加工方法は同様です。
）
シース剥き長、信号線被覆剥き長や信号線端末処理は参考値です。お使いになるコネ
クタの作業基準書の指示に従ってください。

①外被除去
内部信号線の被覆を傷つけないように注意しながら、外被をむいてください。

30～80mm②信号線の被覆除去
信号線の被覆を使用する圧着端子の圧着部の長さに合わせてむきます。

③圧着端子取付け
配線には圧着端子を使用してください。撚り合わせただけの電線を、端子台に直接接続しないでください。

④コネクタへ取付け
市販の端子台への接続は、端子台メーカの指示にしたがってください。
オープン型コネクタプラグは、マスタユニットの通信用コネクタを、端子台に変換することができます。使用できる圧着端子は M3 用圧着端子です。
端子ネジの締め付けトルクはメーカの指定にしたがってください。

43

取付けと配線

ノイズ対策上の留意事項
以下は ODVA 日本ベンダ協議会が推奨するものです。
・誘導ノイズを防止するために、通信線、電源線、動力線はそれぞれ極力離して配線してください。

・高圧機器が設置されている盤内への取り付けは避けてください。
・ノイズを発生しやすい機器（特に、モータ、トランス、ソレノイド、マグネットコ
イルなどのインダクタ成分を持つもの）にはサージキラーを取り付けてください。

・金属物（筐体など）にはノイズ電流が流れることがありますので、通信線は金属物（筐体など）からできるだけ離してください。
・通信電源の一次側にはラインフィルタを挿入してください。
・フラットケーブルはケーブル同士を重ねたり束ねたりしないようにしてください。

44

配線チェックリスト

第8章

配線チェックリスト
設計時・設定時・配線時の各段階において、次のチェックを実施してください。

ネットワーク設計チェック
対象

ポイント

内容

仕様

伝送速度

システムの応答性を満足しますか？

ネットワーク最大長

ネットワークの最大長は、伝送速度に応じて規定範囲になチェックっていますか？
支線長

支線長は伝送速度に応じて規定範囲になっていますか？

総支線長

総支線長は伝送速度に応じて規定範囲になっています
か？

通信電源

ケーブル許容電流

ケーブルの許容電流（5A）以内ですか？

接続位置

接続位置は正しいですか？

電源容量

電源容量は、総消費電流に対して余裕がありますか？（起動電流が考慮されていますか）

ユニット設定チェック
対象

ポイント

内容

マスタユニッ

設定 SW

伝送速度の設定は正しいですか？

ト
スレーブユニチェック

ノードアドレスは正しいですか？
設定 SW

ノードアドレスが他のユニットと重複していませんか？

ット

配線チェック
対象

ポイント

内容

通信線

コネクタ

コネクタの接続不良はありませんか？

終端抵抗

終端抵抗は正しく取付けていますか？

ケーブル

動力線などのノイズ源と分離していますか？

チェック

１セグメント内に異なる種類のケーブルは混在していませんか？
フラットケーブルを重ねたり束ねたりしていませんか？
電源線

丸 型 ケ ーブル Ⅰの場

各ユニットに電源は正しく接続されていますか？

合絶縁

AC 入力と DC 入力が絶縁された電源ですか？

45

接続関連機器一覧

付録

接続関連機器一覧
マスタ・スレーブユニット
取り扱い会社

品名

形式／仕様

問い合わせ先
最新は ODVA の HP をご確認ください（http://securesite.jp/ODVA/catalog/cn_catalog.html）

ケーブル・電線取り扱い会社

品名

形式／仕様

問い合わせ先
最新は ODVA の HP をご確認ください（http://securesite.jp/ODVA/catalog/cn_catalog.html）

コネクタ
取り扱い会社

品名

形式／仕様

問い合わせ先
最新は ODVA の HP をご確認ください（http://securesite.jp/ODVA/catalog/cn_catalog.html）

リピータ
取り扱い会社

品名

形式／仕様

問い合わせ先
最新は ODVA の HP をご確認ください（http://securesite.jp/ODVA/catalog/cn_catalog.html）

終端抵抗
取り扱い会社

品名

形式／仕様

問い合わせ先
最新は ODVA の HP をご確認ください（http://securesite.jp/ODVA/catalog/cn_catalog.html）

電源取り扱い会社

品名

形式／仕様

問い合わせ先
最新は ODVA の HP をご確認ください（http://securesite.jp/ODVA/catalog/cn_catalog.html）

工具取り扱い会社

品名

形式／仕様

問い合わせ先
最新は ODVA の HP をご確認ください（http://securesite.jp/ODVA/catalog/cn_catalog.html）

46

ODVA TAG Japan 事務局
e-mail：ODVA-TAG.Japan@odva.org
ODVA Headquarters
4220 Varsity Drive, Suite A, Ann Arbor, MI 48108-5006 USA

Phone: 1-734-975-8840
Fax: 1-734-922-0027

E-mail: odva@odva.org
http://www.odva.org/