FSA-219-225

INSTRUCTION MANUAL(DETAILED VERSION)
ANNUNCIATOR
FSA-110

FSA-219-225

Contents

Safety precautions ...............................................................

2Composition of type ..............................................................

2

1 Product outline ................................................................

3

2 Name and function of each part .................................................

3

3 Included items .................................................................

3

4 Dimension diagram ..............................................................

4

5 Installation instructions ......................................................

4

6 Connection .....................................................................

4

7 Operation ......................................................................

5

8 Monitoring mode ................................................................

6

8.1 Display (LED) ..............................................................

6

8.2 Operation ..................................................................

6

8.3 Sequence ...................................................................

7

9 Setting mode ...................................................................

8

9.1 Setting flow ...............................................................

8

9.2 Setting method .............................................................

8

9.3 Setting menu ...............................................................

9

10 Test mode ..................................................................... 1010.1 Test flow ................................................................. 1010.2 Test method ............................................................... 10
11 Specification ................................................................. 1111.1 Rating .................................................................... 1111.2 Detailed specifications ................................................... 11
12 Trouble shooting .............................................................. 131

FSA-219-225
Thank you for purchasing DAIICHI ELECTRONICS product.
Please read this instruction manual carefully before using.

Safety precautions
 Environment conditions
Please be sure to use this product in a place that meets the following conditions.
In places that do not meet this condition, it may cause malfunction or failure and product life decline.
 Within the range of ambient temperature -10 to +55 ℃, humidity 5 to 90% RH.
 Place free of dust, corrosive gas, salt and oily smoke. (Corrosive gas：SO2 / H2S, etc.)
 Location that is not affected by vibration and shock.
 Location that is not affected by external noise.
 Altitude 2000m or less.
 Outdoor use conditions
 These products are not a dustproof, waterproof, and splash proof construction. Please avoid the placewith much dust. Moreover, please install in the place not exposed to rain or water drop.
 Please do not install in the place where sunlight hits directly. Discoloration and degradation of aname plate, and deformation of the case by the surface temperature rise may occur.
 Mounting and wiring
Please refer to this instruction manual for mounting and the wiring.
 Please refer to connection diagram for the wiring.
 Please avoid hot line work.
 Please use an electrical wire size suitable with the rated current.
 Please check the tightening of the screw.
 Preparation
This product must be set before use.

Please set correctly after reading this instruction manual.

 Maintenance and inspection
 Inspection in energized state is dangerous.
 No replacement in periodic inspection.
 After wiring change and maintenance, attach the terminal cover.
 Please wipe off lightly with the dry soft cloth. Please do not use the organic solvent, chemicals, cleaners,
etc., such as alcohol, for cleaning.
 Storage
Please store in a place that meets the following conditions.
 The ambient temperature within -25 to +70 ℃ (storage temperature).
 Daily average temperature 40 ℃ or less.
 Location corresponding to the usage environment and use conditions.
 Aluminum electrolytic capacitors are used in products. Please energize the power supply within one
year after purchase.
 Countermeasures against troubles
If trouble occurs within the warranty period, DAIICHI ELECTRONICS will repair this product.
 Disposal
Please dispose this product as industrial waste (non-combustible).
Mercury parts and a nickel-cadmium battery are not used for this product.
 Product replacement cycle
The recommended replacement period for this product is 10 years.
 Warranty period
The warranty period of the product is one year after the date of delivery.

Composition of typeType

Specification code

FSA - 110 -① Auxiliary supply② Communication output

1

100/110V AC

0

None

2

100/110V DC

1

CC-Link2

FSA-219-225

1 Product outline
 Fault / operation input ×8, External operation input ×2, Alarm output ×2 (Warning, Caution) are equipped
as standard.
 The operation mode (Warning, Caution, Operation) can be selected freely for each input.
 Remote monitoring of failure information is possible by CC-Link communication (option).
 Sequence operation (alarm display, alarm output, communication data) can be checked without adding input.
 The guidance display by OLED makes setting easy.

2 Name and function of each partName label(31mm×11mm Max.)
BI1 LED

BI5 LED

BI2 LED

BI6 LED

BI3 LED

BI7 LED

BI4 LED

BI8 LEDOLED

Switch ×7

Name
BI 1 to BI8 LED

Name label
OLED
SET
MODE
－／＋
LAMP
TEST
ALARM
STOP
LAMP
RESET

Function
When fault / operation input (BI1 to BI8) is applied, it flashes or lights
in the following color.
Warning：Red, Caution：Amber, Operation：White / Green / Blue / Red(Inputs can be set individually)
Paste the name label of the fault or operation corresponding to each input.
(Name label need to be prepared by the user.)
Provides guidance on configuration and testing.
Used for transition to setting mode, test mode, and confirmation of setting(test) items and settings.
Used to shift to test mode, to return to monitoring mode, and to return tothe previous screen.
Used for setting, selecting test items / elements, and changing set values.

Description page
6 to 9－5, 8 to 11
5, 8 to 10
5, 8 to 10
5, 8 to 10

Used to check the lighting of the LED.

6, 7

Stop the alarm state.

6, 7

Resets fault indication (LED).

6, 7

3 Included items① Instruction Manual (Installation and Operation) 8 pages (A4 size) ･････ 1 pc
② M5 flange nut (for mounting) ･･････････････････････････････････････････ 2 pcs

3

FSA-219-225

4 Dimension diagram
M4 screwM4 screwM3 screw

90±0.51±
101

Panel cut

(4.3)

2-M5 screwφ

90±0.5

103.5

φ99

16.5

110

110

2-φ7

（Front view)

5 Installation instructions(1) Unit is put in a cut hole of a panel from the front.
Its body is inserted until it exceeds retaining
stopper of the lower base.
(2) Please fix the unit in place with attached
M5 flange nut with tightening torque of
2.0 to 2.5N･m.

6 Connection
Remove the terminal cover and connect correctly according to the connection diagram.
After wiring, attach the terminal cover.
＋ －
～ ～

Input

BI1 (＋)
BI2 (＋)
BI3 (＋)
BI4 (＋)
BI5 (＋)
BI6 (＋)
BI7 (＋)
BI8 (＋)
ALARM STOP (＋)
LAMP RESET (＋)
BI COM (－)

Aux. supply
＋ －
～ ～
1
2

5
6
7

8
9
10
11
12
13
14
15

17
19
21
25
27
29

16
18
20
24
26

DA
DB
DG
Ter.( 2 )SLD
FG ( 3 )

BL
BZ

(1)
Communication output
CC-Link
Alarm output

28

Note(１) Option.
Note(２) By shorting number 17 (DB) and number 19 (Ter.), termination resistor of 110Ω is internally connected.
Please use it only for the equipment which becomes terminated in connection form.
Note(３) FG is equivalent to functional ground, so dedicated ground or common ground is recommended.
SLD and FG are connected internally.

4

FSA-219-225

7 Operation
This product can switch to each mode (monitoring mode, setting mode, test mode) by switch operation.
You can also operate while checking the OLED display.
For the operation method in each mode, please refer to section 8 to 10.
POWER ON

Monitoring mode
Setting mode

Screen OFF
Start-up

Setting item selection
SET[ OLED ]Operation
guidance

SET
Press 3 seconds

Test mode
Test element selection

SET

MODE

SET and MODE
Press 3 seconds

MODE

(４)

10 minutes without
operation

Screen OFF
SET

MODE

－

Screen OFF＋

Pressing any will display
the operation guidance.

Note(４) From any screen, press MODE for 3 seconds or more to return to monitoring mode.

5

FSA-219-225

8 Monitoring mode
8.1 Display (LED)
Displayed according to the sequence in Section 8.3.
Display

The lighting color of the LED is as follows.
Operation mode setting
CautionWarning
Red

Amber

Operation (５)
White
Green

LED lighting color
Blue
Red
Note(５) The lighting color of the LED can be set individually for each input.

8.2 Operation
Operates according to the sequence in Section 8.3.
Operation (６)
LAMP
TEST

Switch

ALARM
STOP

SwitchLAMP
RESET

SwitchExternal operation input
External operation input

The operation is as follows.
Operation mode setting

Warning
CautionOperation
The BI1 to BI8 LEDs light up when the switch is pressed, regardlessof the input status.
Stop the alarm state.
LED：Flicker stop, Alarm output：OFF

UnusedResets (turns off) the fault indication (LED)during the manual recovery sequence.

UnusedNote(６) Operation in setting mode is invalid.

6

FSA-219-225

8.3 Sequence(1) Operation Mode：Warning, Caution■ Automatic reset [A-14] (７)Fault input recovers after "ALARM STOP" operation.
The display also returns automatically.
Fault input(BI)
Fault indication(LED)

Instantaneous fault

Flashing■ Manual reset [M-14] (７)After recovery from the fault input, the display
recovers by the "LAMP RESET" operation.

Continued fault

Fault input(BI)
Fault indication(LED)

Flashing

ALARM STOP
(Switch, BI)

ALARM STOP
(Switch, BI)

LAMP RESET(Switch, BI)

LAMP RESET(Switch, BI)

LAMP TESTLAMP TEST

Alarm output(BL/BZ) (８)Alarm output(BL/BZ) (８)Communication
output (BI)Communication
output (BI)Communication
output (LED)Communication
output (LED)

Note(７) Expression by the ISA standard ANSI / ISA-S18.1-1979
Note(８) BL：Warning, BZ：Caution(2) Operation mode：Operation
Operation input(BI)
Operation
indication (LED)
ALARM STOP
(Switch, BI)
LAMP RESET(Switch, BI)
LAMP TEST
Alarm output(BL/BZ)
Communication
output (BI)Communication
output (LED)7Instantaneous fault

Flashing

Continued fault

Flashing

FSA-219-225

9 Setting mode
9.1 Setting flow
Monitoring mode

MODE

SET

3 seconds

BI operation
mode setting

MODE

－

Sequence setting

SET

＋

＋

＋

－

－

－

MODE

SET

MODE

SET

－

＋

BI1
operation mode

Communication
output setting

Configuration

Sequence

BI2
operation mode

MODE

＋

SET

－

＋

LED
brightness

Address

Setting
initialization

Transmission
rate

SoftwareversionCPU reset

BI8
operation mode

With option only

<Note>
When in setting mode, the fault / operation input becomes invalid and all sequence operations are cleared.

9.2 Setting method(1) Display
Example：BI element selection■ Setting item
■ Setting element
Select with ＋,－.

(2) Operation

Example：BI1 operation mode setting■ Switch icon
Expresses that it
operates by ＋，－.
■ Current setting (ﾚ)■ Setting value
Select with ＋,－.

● Setting item / element selection display① Select the setting item / element with ＋ －. Confirm with SET .
② When confirmed, it will shift to the setting display of the selected item / element.
● Setting screen① Select the setting value with ＋ －. Confirm with SET .
② Once confirmed, the “mark (レ)” indicating the current set value will be displayed to the left ofthe changed set value.
③ When there are many setting values (address of communication output), press ＋ － for a longer time tochange at high speed.

8

FSA-219-225

9.3 Setting menu
(1) BI operation mode setting BI
Thick frame：Initial setting value

Item

Setting description
Set the operation modeof fault / operation
input (BI1 to BI8).

BI operationmode

Set the lighting color
for the operation〔BI1 to BI8〕 indication.
Lighting color for
warning and caution
cannot be set.

Setting content【Operation mode】【Element】
SETMODE

The corresponding LED lights up during
setting.
<Note> "Operation" (Lighting color：Red)
has the same lighting color as"Warning". Please check theapplication before setting.

Setting range (10)WARNING (９)Red
CAUTION (９)Amber
OPERATION (WHITE) WhiteOPERATION (GREEN) GreenOPERATION (BLUE)Blue
OPERATION (RED)Red

Note(９) Initial setting value. BI1 to BI4：WARNING, BI5 to BI8：CAUTION
Note(10) Unit display is indicated as below.
WARNING ：MAJOR FAILURE
CAUTION ：MINOR FAILURE
Operation：STATUS(2) Sequence setting SEQ
Thick frame：Initial setting value

Item

Setting description

Setting content【Sequence】

Sequence〔 SEQUENCE 〕

Set the sequence
operation of theannunciator.

Setting range
Automatic reset AUTO
Manual reset
MANUAL

This applies to inputs whose operation
mode is set to warning or caution.
Also, it does not affect the operation
indication.

(3) Configuration setting CFG
Thick frame：Initial setting value

Item

Setting description

Setting content【Element】【Item】

LED
brightness

Set the brightness of
the LED.

〔 LUMINANCE 〕

SET

SET

MODE

MODE

Brightness can be set for each lighting color.
Setting range
Setting element
5
Bright
RED
4
↑
AMBER
WHITE
3
GREEN
2
↓
BLUE
1
Dark
【Item】

Set value
initialization

Softwareversion【Initialization】
SET

All set values can beinitialized.

〔 DEFAULT 〕【Brightness】

MODE【After initialization】
SET

3 seconds

Press SET for 3 seconds to initialize all settings.
When initialization is complete, the "レ" mark appears on the left.
【Item】【Version】
Display the software
version.

SET
MODE〔 SOFTWARE 〕

9Version：4-digit alphanumericFSA-219-225(4) Communication output setting COM (Communication output option only)
Thick frame：Initial setting value

Item

Setting description

Setting content【Address】【Item】
Address〔 ADDRESS 〕

SET

Set the communication
address.

MODE【Item】
Transmission
rate〔 BIT RATE 〕【Transmission rate】
SET

Set the transmission
speed ofcommunication.

The equipment can bereset while auxiliary
CPU reset
power is applied, suchas during recovery from〔 CPU RESET 〕
the communication stop
state.

MODE【Item】

Setting range
1･･･
64
Setting range
156kbps
625kbps
2.5Mbps
5Mbps
10Mbps【Reset】
SET
MODE

Press SET for 5 seconds
to reset the device.
(It will be in monitoringmode after reset)

10 Test mode
10.1 Test flow
SET

Monitoring mode

MODE

Test mode

Press 3 seconds
MODE<Note> When in test mode, the fault / operation input becomes invalid and all sequence operations are cleared.

10.2 Test method
The sequence operation can be checked without applying input to the fault / operation input (BI1 to BI8).
Test item
Test content
・Select the fault / operation input (BI1 to BI8) to be tested with ＋ or － .
・Press SET to ON the selected BI, and press SET again to OFF the BI.
Sequence test

SET・After ON / OFF of operation, it operates according to the sequence set for each input (referto section 8.3). LED, switch, external operation input, alarm output, communication output
can be checked.

10

FSA-219-225

11 Specification
11.1 Rating
Item
Input
Input range and input current
Power supply range
and consumption VA
Inrush current(Time constant)

Auxiliary
supplySpecification
Fault / operation input (BI)：8 points, ALARM STOP：1 point, LAMP RESET：1 point
Input pulse width：More than 50ms. Negative common
The input rating is the same as the auxiliary power supply.
(1) 85 to 127V AC
Approx. 5mA (110V AC) (Rated voltage 100/110V AC)(2) 80 to 143V DC
Approx. 5mA (110V DC) (Rated voltage 100/110V DC)(1) 85 to 127V AC
4.5VA (Rated voltage 100/110V AC)(2) 80 to 143V DC
3W(Rated voltage 100/110V DC)
Rated voltage 110V AC Less than 1.1A (Approx. 14ms)
Rated voltage 110V DC Less than 0.8A (Approx. 14ms)

11.2 Detailed specifications
Item
Display

LED
OLED
Contact configuration

Alarm output

Communication
output(Option)Contact capacity
Response time
ProtocolTransmission method
Synchronous method
Transmission rate
Encoding method
Transmission path format
Transmission format
Error control method
Number of occupied stations
Remote input / output
Remote register
Maximum transmission
distance

Number of connections

Address setting
Connection cable
Terminating resistor

Specification
Warning：Red, Caution：Amber, Operation：White, Green, Blue, Red
Total 8 points, Can be set for each input.
Display guidance on settings and tests.
BL：Warning BZ：Caution Normally-open contact (a contact) 2 points
125V AC 8A, 125V DC 0.3A (Resistance load)
125V AC 5A, 125V DC 0.1A (Inductive load)Less than 100ms
CC-Link Ver.1.10
Broadcast polling method
Frame synchronization method
156kbps / 625kbps / 2.5Mbps / 5Mbps / 10Mbps
NRZI
Bus format (compliance standards, TIA-485-A)
HDLC compliant
CRC (X16 ＋ X12 ＋ X5 ＋1)
Remote device station. 1 station is occupied.
RX：32 points RY：32 points
RWr：4 points RWw：4 points
1200m (156kbps) / 900m (625kbps) / 400m (2.5Mbps) / 160m (5Mbps)/ 100m (10Mbps)① { (1×a) ＋ (2×b) ＋ (3×c) ＋ (4×d) } ≦ 64 stations
a：Number of units occupied by 1 stationb：Number of units occupied by 2 stations
b：Number of units occupied by 3 stations
d：Number of units occupied by 4 stations② { (16×A) ＋ (54×B) ＋ (88×C) } ≦ 2304
A：Number of connected of remote I/O stations ･･･ MAX. 64 units
B：Remote device station ･･･････････････････････ Max. 42 units
C：Number of connected of local stations and intelligent device
stations ･･････ MAX.26 units
1 to 64
Ver.1.10 compatible CC-Link dedicated cable110Ω Internal termination resistor is connected when the terminal
is short-circuited

11

FSA-219-225

Item
Insulation resistance

Voltage test
(Power frequency
withstand voltage)

Impulse voltage test
(Impulse withstandvoltage)Damped oscillatory wave
immunity test
IEC 61000-4-12
Square impulse immunity
test
B-402 Standards

Radio wave immunity test

Electrostatic discharge
immunity test
IEC 61000-4-2
Vibration
ShockPower outage guarantee
Overload capacity

Specification・Performance
Between auxiliary supply, input, alarm output andground (communication output is grounded).
Above 50MΩ at DC500V.
Between auxiliary supply and input and alarm output.
Between alarm outputs.
Between auxiliary supply, input, alarm output andground (communication output is grounded).
2210V AC (50/60Hz) 5 seconds
Between auxiliary supply and input and alarm output.
Between alarm outputs
1390V AC (50/60Hz) 5 seconds
Between auxiliary supply, input, alarm output andground (communication output is grounded).
Between auxiliary supply and input, alarm output,
communication output.
5kV 1.2/50μs
Between input and auxiliary supply, alarm output,
communication output.
Between alarm output and auxiliary supply, input,
communication output
Peak voltage：2.5kV, frequency：1MHz ±10%, Add 3 times for 30 seconds.
Malfunction and communication stop must not occur.
・Auxiliary supply (Normal / Common)
Add noise (1μs, 100 ns width) repeatedly for 5 minutes.
Malfunction and communication stop must not occur.
・Auxiliary supply (Normal / Common)
2.0kV or more・Input (BI) (Common)
1.5kV or more・Alarm output (Common)
1.5kV or more・Communication output (Induction)
1.0kV or more
・There should be no malfunction or communication stop when the radio waves of
the rated output 5W transceiver (150MHz band, 400MHz band) are contacted andintermittently irradiated.
・There should be no malfunction or communication stop when the radio waves of themobile phone or wireless LAN (2.4GHz, 5GHz) are contacted and intermittently
irradiated.
Conducted under normal usage conditions.
No malfunction or communication stop at air discharge 15kV, contact discharge 8kV.
Capacitor charge method.
IEC 60068-2-6：2007
Frequency range：10 to 55 Hz, Single amplitude：0.15 mm, Sweep cycle：10 times
IEC 60068-2-27：2008
Peak acceleration：500 m/s2
Each set value is data-saved by non-volatilized memory.
1.5 times 10 seconds, 1.2 times continuation (AC power supply), 1.3 times continuation(DC power supply) of rated voltage.

Construction
Material
color
Protection rating

110×110×103.5mm [W×H×D] , Body diameter：99mmφ , With terminal coverCase：ABS (V-0) , Terminal block：PBT , Terminal cover: Polycarbonate
Black（Munsell N1.5）
IP40

Terminal screw
Mass
Operating temperatureand humidity limits
Storage temperature
limits

M4×15 ，M3×14
Approx. 500g
-10 to 55℃ , 5 to 95％ RH（Non condensing）-25 to 70℃

12

FSA-219-225

12 Trouble shooting
TroubleLED does not light.

Even if the LAMP RESET switch
is pressed (external
operation input is applied),the LED does not turn off.
OLED display does not light.

Probable cause
No auxiliary power is applied to terminal
1-2.
Fault / operation input is not applied.

Fault / operation input is applied.

Auto display off function (Display off
without operation for 10 minutes)

Alarm output (BL) does not
output.

The BI operation mode is

Alarm output (BZ) does not
output.

The BI operation mode isData link error.
Communication error.

OPERATION

Treatment method
Please apply auxiliary power supply.
If no fault / operation input isapplied, the LED will not light.
By pressing the LAMP TEST switch,lighting can be confirmed.
The LED cannot be turned off when afault / operation input is applied.

CAUTIONor

Press any switch ( SET MODE ＋ －) todisplay the operation guidance on the
OLED display.。
Check the setting.

WARNINGor

Check the setting.

.

OPERATION .
Communication settings (Address, Bitrate) are not correct.
Communication cable is disconnected or
not connected correctly (polarity, etc.)
Ver.1.10 compatible communication cable
is not used
Incorrect communication procedure.
Communication is stopped.
Termination resistor is not connected.

Check the setting.
Check the communication cable.

Check the communication specification.
Please perform the CPU reset.
Make sure that a terminating resistor
is connected to the terminating device.

Tokyo Office : 11-13, Hitotsuya 1-chome, Adachi-ku, Tokyo, 121-8639, JAPAN.
TEL：+81-3-3885-2411 , Fax：+81-3-3858-3966
Kyoto Office : 1-19, Ichinobe-Nishikawahara, Jyoyou-shi, Kyoto, 610-0114, JAPAN.
TEL：+81-774-55-1391 , Fax：+81-774-54-1353
DATE：December 25, 201913