8 Channel Combine Fault / Operation
Annunciator with CC-Link.

ANNUNCIATOR

110mm Annunciator to contribute to saving space &wiring of MV/LV switchboard.

FSA-110FEATURES■ STANDARD SPECIFICATION- 8 Fault / Operation inputs- 2 External operation inputs- 2 Alarm outputs■ FREE SETTING FOR OPERATION MODE

- Fault Alarm: Red color- Warning: Amber color- Operation Indication: White, Green, Blue, Red (selectable)■ COMMUNICATION OUTPUT (OPTION)- Remote monitoring of fault or operation informaiton by CC-Link communication.

■ TEST FUNCTION- Fault, Operation, Alarm output, Communication output Sequence can be checked
without adding input.

■ SETTING FUNCTION- Easy setting with Organic EL Display (OLED).

SPECIFICATIONSName sticker on image are for example only.

Items
Input
Input Range and Input Current *1
Auxiliary Supply

Range and Consumption VA
Inrush Current (Time Constant)

Display

Alarm Output

Communication output(Option)

LED
OLED
Contact Configuration
Contact Capacity
Response Time
ProtocolTransmission Method
Synchronization Method
Communication Speed
Encoding Method
Transmission Path Format
Transmission Format
Error Control Method
Number of Occupied StationsNumber of Connected Units
Station Number Setting
Connection Cable
Terminating ResistanceSpeciﬁcations
Fault or operation input (BI): 8 inputs, ALARM STOP: 1 input, LAMP RESET: 1 input
Input pulse width 50ms or more, Minus Common(1) AC85...127V Approx. 5mA (AC110V) (rated voltage AC100/110V)(2) DC80...143V Approx. 5mA (DC110V) (rated voltage DC100/110V)(1) AC85...127V 4.5VA (rated voltage AC100/110V)(2) DC80...143V 3W (rated voltage DC100/110V)
Rated Voltage AC110V 1.1A or less (approx. 14ms), Rated Voltage DC110V 0.8A or less (approx 14ms)
Fault Alarm: Red, Warning: Amber, Operation: White/Green/Blue/Red (Total: 8 inputs, Selectable)
The function name of each LED can be labeled by attaching a name sticker *2 to the right space (31mm x 11mm).
Setting & test guidance display
BL: Fault Alarm, BZ: Warning, 2 output: N.O.
AC125V 8A, DC125V 0.3A (resistance load), AC125V 5A, DC125V 0.1A (inductive load)
100ms or less
CC-Link Ver.1.10
Broadcast Polling Method
Frame Synchronization Method
156kbps/625kbps/2.5Mbps/5Mbps/10Mbps
NRZI
Bus format (TIA-485-A compliant)
HDLC compliant
CRC (x16+x12+x5+1)
Remote device station occupies 1 station
42 (remote device station)
1...64CC-Link Ver.1.10 dedicated cable
An internal termination resistor is connected with a 110Ω terminal short circuit.

*1: Input is the same as the auxiliary supply. *2: The name sticker is not included with the product. Please prepare your own.

SEQUENCES
ModeRestoration

Fault Alarm / Warning
Manual Reset (M-14)*3
Automatic Reset (A-14)*3

Fault Input (BI) and Fault Display (LED) will be
automatic reset after ALARM STOP (switch/BI).

Operation-Fault Display (LED) must be reset by LAMP RESET(Switch/BI) after Fault Input (BI) return.
*3: By ISA standard ANSI/ISA-S18.1-1979.

ORDERING INFORMATIONType

Please specify product type, specification code, number of units.

Specification CodeFSA-110 -1

Auxiliary Supply
AC100/110V 2 DC100/110V

0Communication output
none
1CC-Link

DIMENSIONS Weight：500g

Unit：mmFRONTRIGHT SIDECONNECTION DIAGRAM* Communication output is optional.

①BACK

②

LEFT SIDE③PANEL CUT(FRONT VIEW)②①

SYSTEM CONFIGURATION
EXAMPLE③*SAFETY PRECAUTIONSHEAD OFFICE

For ensure safety, Technical knowledge is necessary when using this product. Please refer to manual instruction
for correct operation. Please check connection diagram carefully before performing connections. Please DO NOT
work with live wires. There is a risk of electric shock, device malfunction or fire.

11-13, Hitotsuya 1-chome,
Adachi-ku, Tokyo 121-8639 Japan
TEL: +81-3-3885-2411
FAX: +81-3-3858-3966

http://www.daiichi-ele.co.jp/

NOTE: Reserves the right to update the specification without notification.
befd8dd98-146e